ML100.200
24V 4.2A, TWO-PHASE INPUT

MiniLine

POWER SUPPLY■■■■■■■■

2AC 380-480V
2 Phase Input
No Neutral Wire Required
Input Fuse Included
Efficiency up to 90.0%
Full Output Power Between -10°C and +60°C
Quick-connect Spring-clamp Terminals
3 Year Warranty

PRODUCT DESCRIPTIONSHORT-FORM DATAThe ML100.200 is a simple and cost effective approach toconvert the AC voltage of a typical three phase system into aregulated DC voltage. It only requires two phases andthereby saves terminal space, terminal cost, wires, fuses andinstallation time.

Output voltage
Adjustment range
Output current
Output power
Output ripple

DC 24V
24-28V
4.2-3.6A
100W< 50mVpp

Input voltage
Mains frequency
AC Input current
Power factor
AC Inrush current
Hold-up time
Efficiency
LossesTemperature range

2AC 380-480V
50-60Hztyp. 0.46 / 0.4A
typ. 0.6 / 0.55
typ. 26 / 33Apeak
typ. 48 / 85ms
89.5 / 89.0%
11.7 / 12.3W-10°C to +70°C-40°C to +85°C
2.5 W/°C< 95% r.H.

The ML100.200 is very compact, high efficient and easy touse. The input is internally protected, which makes externalfuses unnecessary in many cases.
Weighing only 360g, it is a lightweight compared to the50/60Hz control transformers, which are commonly used for
low-power control voltages where a neutral wire is notavailable.
High immunity to transients and power surges as well as low
electromagnetic emission makes usage in nearly every
environment possible.

L12428V

L2
L3- -+ +DC
okML100.200

PEL2L1Derating
Humidity

Power SupplyAccessory

ML100.200
MLY02.100

20Hz to 20MHz±15%±6%at 400 / 480Vac
at 400 / 480Vac
at 400 / 480Vac, 40°C
at 400 / 480Vac
at 400 / 480Vac
at 400 / 480Vac
operationalstorage, transport+60 to +70°C
IEC 60068-2-30

Do not energize while condensation is presentVibration
ShockDimensions

ORDER NUMBERS

guaranteed
Below +60°C ambient

2g (2 hours/axis)
30g 6ms,
20g 11ms
72.5x75x103mm

IEC 60068-2-6
IEC 60068-2-27
WxHxD

MAIN APPROVALS
24-28V Power Supply
Decoupling Module
UL 508

UL 60950-1

MarineFeb. 2024 / Rev 1.1 DS-ML100.200-EN / All parameters are specified at 24V, 4.2A, 400Vac and 40°C ambient unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0 Germany

1/2ML100.200
24V 4.2A, TWO-PHASE INPUT

MiniLine

TERMINALS AND WIRINGOUTPUT
Output voltage
Adjustment range
Factory set
Output current
Line regulation
Load regulation
Serial use
Parallel use
Return voltage
OVP

nom
min
typ
nom
max
maxmaxtypmaxDC 24V
24V-28V
24.5V
4.2A at 24V, 3.6A at 28V
20mV
323…552Vac
240mV
static regulation
allowedallowed
35V
34V
39V

Adjustment
Range

28V
2416

EMC Immunity
EMC Emission

EN 61000-6-1, EN 61000-6-2
EN61000-6-3, EN 61000-6-4
EN 55011, EN 55032, FCC-15
EN61000-3-2 (PFC)
EN61000-3-3

UL 508
Listed: E198865
UL 60950-1
Information Technology Equipment
IEC 61010-2-201 Manufacturer´s Declaration
IEC 60950-1
CB Scheme
Marine DNVTAA00001STEU Declaration of 2014/35/EU (LVD), 2014/30/
Conformity
EU (EMC), 2011/65/EU (RoHS)
WEEE Regulation (2012/19/EU), WEEE-Reg.-Nr. DE 55837529

128
Output Current

012345678A

Output current vs. ambient temperature
Allowable Output
Current at 24V5AFULFILLED STANDARDS

43EN/IEC 60204-1
UL/IEC 60950-1
EN/IEC 61131-2
EN 50178

21EMC

APPROVALS

2040Solid wire
Stranded wire
AWG
Stripping lengthFerrules

Bi-stable, quick-connect spring clamp
terminals. Shipped in open position.
0.3-2.5mm20.3-2.5mm2
AWG 26-126mm
allowed, but not required

Harmonic input current
Flicker

Output voltage vs. output current, typ.
Output Voltage

TypeAmbient Temperature

0-10 020
4060 70°C
Ambient temp. is defined 2cm below the unit

Safety of Electrical Equip. of Machines
Information Technology Equipment
Programmable Controllers
Electronic Equip. Power Installations

DIMENSIONS AND WEIGHTSAFETY AND PROTECTION
Input / output insulation

Degree of pollution
Degree of protection
Class of protection
Over-voltage category
Internal input fuse
Temperature protection

SELV
PELV
3000Vac
2
IP20I
III
T3A15

IEC/UL 60950-1
EN 60204-1
2s type test
EN 50178
EN/IEC 60529
PE required
EN 50178
in L1,
not accessible
not included

Use 35mm DIN rails according to EN 60715 or EN 50022 with a height of
7.5 or 15mm. The DIN rail depth must be added to the depth (103mm) tocalculate the total required installation depth.

Weightmax

360g

The power supply shall only be installed and put into operation by qualified personnel. This power supply is designed for installation in an enclosure and is intended for thegeneral use, such as in industrial control, office, communication, and instrumentation equipment. Do not use this device in aircraft, trains and nuclear equipment, wheremalfunctioning of the power supply may cause severe personal injury or threaten human life. The information presented in this document is believed to be accurate andreliable and may change without notice.

Feb. 2024 / Rev 1.1 DS-ML100.200-EN / All parameters are specified at 24V, 4.2A, 400Vac and 40°C ambient unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0 Germany

2/2