§ PLUG-IN TRANSDUCER § 1 OUTPUT TYPE

SIGNAL TRANSDUCER

ISOLATOR
TP2 -■ Use
Amplifies various kinds of DC signals and converts them into a unifiedintersystem signal. With input and output insulated, the product offers
full advantages in transmitting insulated signals between measuringsystems, cutoff of noise, protecting a control circuit from a sneak
current, and transmitting an output directly to a distant place.

■ Features
1. Constant voltage/current output
2. Withstand voltage between input, output, auxiliary supply and outercase (earth) is AC2, 000V (50/60Hz), complete insulation for 1 minute.
3. Impulse withstands voltage 5kV, 1.2/50µs (between electric circuit andouter case), and positive/negative polarity 3 times each is guaranteed.
4. With output line surge protection. (2, 000A, ±8/20µs)

TP2-C7F5(80×50×121mm/300g)■ Specification
Output (load resistance)

Auxiliary supply

Common specification

A1 : DC0-10mV (approx.1MΩ)

Input (input resistance or voltage drop)
C1 : DC0-10μA (100mV) *1

1 : DC0-100mV (≧200Ω)

1 : AC100V±10%,

Tolerance: ±0.25% *2

A2 : DC0-50mV (approx.1MΩ)

C2 : DC0-100μA (100mV)

2 : DC0-1V (≧200Ω)

50/60HzA3 : DC0-60mV (approx.1MΩ)

C3 : DC0-1mA (approx.100Ω)

3 : DC0-5V (≧1kΩ)

2 : AC110V±10%,

A4 : DC0-100mV (approx.1MΩ)

C4 : DC0-5mA (approx.100Ω)

4 : DC 0-10V (≧2kΩ)50/60HzA5 : DC0-1V (approx.1MΩ)

C5 : DC0-10mA (approx.100Ω)

5 : DC1-5V (≧1kΩ)

3 : AC200V±10%,

AC power source:3VA

A6 : DC0-5V (approx.1MΩ)

C6 : DC0-16mA (approx.100Ω)

6 : DC±5V (≧1kΩ)50/60HzDC power source:4WA7 : DC0-10V (approx.1MΩ)

C7 : DC4-20mA (approx.100Ω)

7 : DC±10V (≧2kΩ)

4 : AC220V±10%,

A8 : DC1-5V (approx.1MΩ)

D1 : DC±10μA (±100mV)*1

A : DC0-1mA (≦10kΩ)

50/60HzAC power source:700g

B1 : DC±10mV (approx.1MΩ)D2 : DC±100μA (±100mV)

B : DC0-5mA (≦2kΩ)

5 : DC24V±10%

DC power source:300g

B2 : DC±50mV (approx.1MΩ)

D3 : DC±500μA (±100mV)C : DC0-10mA (≦1kΩ)

6 : DC48V±10%

B3 : DC±60mV (approx.1MΩ)

D4 : DC±1mA (approx.100Ω)

D : DC0-16mA (≦600Ω)

7 : DC100V/110V

B4 : DC±100mV (approx.1MΩ)

D5 : DC±5mA (approx.100Ω)

E : DC1-5mA (≦3kΩ)(88-143V)

B5 : DC±1V (approx.1MΩ)

D6 : DC±10mA (approx.100Ω)

F : DC4-20mA (≦750Ω)

0 : other thanB6 : DC±5V (approx.1MΩ)

00 : other than those above

0 : other than those above

Response time:≦0.5sec./99%
Consumption VA:Weight:

those above

B7 : DC±10V (approx.1MΩ)*1. Circuit voltage ≦15V for an input of 10μA.
*2. Tolerance becomes ±0.5% when input voltage is less than 50mV, input current is less than 100µA.
● Open of current output: even if the current output terminal is used in a state of regular open, there is no problem. Also, a voltage of approx. 25Voccurs on the output terminal.

● Option: surge absorber (5kV, 1.2/50µs positive/negative polarity)
When an inductive lightning surge occurs from input or output side, this device absorbs the surge and protects
connected equipments.
However, the device is not necessary if the connected equipment is protected by an arrester or suchlike.
● Built-in ripple filter
Even if a ripple of single-phase AC full rectification wave (50/60Hz) degree is included in input wave, it still
converts the wave into a smoothed DC signal. Please consult with us for special wave patterns such as an inverter.
● UR-1 precise resistance unit (selling separately)
Please use a UR-1 combined with an isolator of voltage input. When changing the isolator in a hot line state at thetime of current input, if measures against open are necessary, connect UR-1 to socket and convert it into a voltage
signal before using it. (UR-1, the resistance specified)

Products List1

§ PLUG-IN TRANSDUCER § 1 OUTPUT TYPE

SIGNAL TRANSDUCER■ Connection diagram

Indicated in ( ) are the polarities in the case of DC auxiliary supply.

■ Block diagram①Low-drift amplifying circuit②Pulse width modulation circuit③Pulse width demodulation circuit④Output circuit⑤Output line surge protection circuit⑥Insulated power source circuit■ Purchase specifications
TypeTP2-C 7
Input

F5

OutputAuxiliary

SSurge absorber (option)

supplyProducts List2