Installation Guide Lighting Fixture

FOUNDATION | 連結用

MGP-F12F/FLE/DL/3［ｍｍ］

Weight1.48kg

Lamp
Input voltage
Input current

COB47.6V
0.7A Max

DriverSold separately
Please use constant current driver.

Installation Guide

Lighting Fixture

MGP-F12F/FLE/DL/3
To install the ﬁxture safely《 Read carefully and follow all the instructions in the guide 》

1212

Warning : Failure to install the ﬁxture properly could result in persona l injury.

: Prohibited

Caution : Failure to install the ﬁxture properly could result in property damage.

: Strict observanceBeforeinstallation

Warning

The ﬁxture is for indoor use only in general conditions.This ﬁxture can only be installed on a horizontal ceiling.
Can not be used following conditions (Causes of falling, electrocution and ﬁre)●On the wall

●Plases aﬀected by wind or air-conditioner mashine●On the ﬂoor

●Inclined, uneven surface●Outside●Ambient temperature under 0℃ and over 35℃●Near ﬁre●Ceiling which canʼt hold the ﬁxture weight●High humidity●Dusty areas, corrosive gas outbreaks areas●Areas get direct sunlight●Vibrated or shocked areas●Insulated inside of ceiling․•⁕ ⊡‣•⁕ ⊡※⁠⁥⁧⁞⁓⁦⁡⁤‣•⁕ ⊡※⁠⁥⁧⁞⁓⁦⁡⁤※⁠⁥⁧⁞⁓⁦⁡⁤

Please contact if you are not able to judge whether installation
environment is suitable to the places or not.
CautionEven when using it indoors, do not use it in a place where there is a sulfur component around the equipment.
(Sulfur components may also be contained in some foods, chemicals, papers, rubber products,
and car exhaust gas.)
Please follow the ﬁxturesʼ indication or speciﬁcation for the distance of irradiated area.
(Causes of change in shape, change in color of irradiated objects)
Carefully check the size of the lighting ﬁxtures and secure suﬃcient space in the ceiling.

For electricwiring

Warning

Only qualiﬁed person may work on electric wiring and equipment.(Cause of accidents)
Please use a compatible power supply and compatible driver. (Cause of non-lighting / ﬁre)Be sure power supply voltage is within ±6% mentioned in rating plate or the guide.
(Causes of short life of lamps・electriﬁcation・ﬁre)Be sure all the wires and codes are not damaged. (Causes of falling・damage)
Do not perform live-line construction. There is a risk of electric shock or product failure.
Do not install other electronic devices (devices that use a motor such as a ventilation fan)in the same circuit as it may lead to equipment failure.

At lighting
ﬁxtureinstallation

Warning

Please follow the ﬁxturesʼ instruction or this guide to installthe ﬁxture and lamp.
(Causes of falling・electriﬁcation・ﬁre)Models equipped with a safety wire (fall prevention wire) as standard equipment to prevent falling
due to an earthquake, etc. Be sure to install it securely according to this manual.
Be sure to turn oﬀ the power when installing the ﬁxture or lamp. (Cause of electric shock)
Do not touch the ﬁxture when switch is on or just turn oﬀ the switch because of high temperature.
Do not put or cover the ﬁxture by any cloths, papers, or insulators.(Causes of not lighting・ﬁre)Do not put metal or burning objects in the gaps of the equipment.
(Causes of electric shock, ﬁre, and equipment failure)
Make sure that the outer shell of the main body other than the equipment mounting partdoes not come into contact with equipment such as construction materials and ducts insideand outside the ceiling. (Causes of falling, electric shock, and ﬁre)Do not dismount or remodel ﬁxtures. (Cause of electriﬁcation・ﬁre・falling・broken ﬁxtures)
Do not operate with wet hands.
Do not grab and lift wires or cables that are not the product itself. It may be damaged.
If you smell smoke, see smoke, or ﬁnd anything unusual, please turn the switch oﬀ and ask construction
companies to repair. (Cause of electriﬁcation・ﬁre)CautionUse protective equipment such as clean gloves when installing and removing equipment. (Cause of injury)
Install so that the heat of the equipment does not aﬀect the ﬁre protection equipment
such as sprinklers. (Cause of malfunction)
Please note that noise may enter the device if it is lit near a communication device such as a radio.

Installation Guide Lighting Fixture

To install ModuleX safety

FOUNDATION | 連結用

MGP-F12F/FLE/DL/3
Installation Details

Wiring connection
Please connect according to
the description of a power supply.

When connecting the driver,careful attention should bepaid to connecting ＋ and −.
Metal part in a cable point,
please don't touch with barehand directly.

Installation Diagram

Caution

Wiring diagram
PEN

DC700mA MAX
47.6V +RED-BLACKL

NPE+

safety-wire

2
1

3

2

a

Install the V-spring to the
Metal ﬁtting hole forbody attachment(ﬁg. h)CautionaHook
1
V-spring

Install the body to the mounting

3-

Driver

Installation to ceiling

Install the V-spring to the
Metal ﬁtting hole forbody attachment

2

LED

Installation Diagram

Install the safety wire to the
Hook attaching hole

1

L

Installation Details

1Hook attaching hole

Hook

CAUTION！

Do not reverse polarity！

＋ RED− BLACK

Make sure to install the safety wire
to the hook attaching hole securely. 2

Metal ﬁtting hole forbody attachment①

Make sure the ﬁxture will not touch
any objects in ceiling.

②V-spring
Do not touch inner side of the bodywith bare hands. Use clean soft
cloth to clean up and maintaininner side of the body.
Make sure to install the safety wire
to the mounting frame securely.

3

mounting

Make sure the ﬁxture will not touch
any objects in ceiling.
body61-;1#21 AraiBldg, 1-20-6 Ebisu-MinamiShibuya-ku, Tokyo, 150-0022, Japan
Tel +81-3-5768-3681

15#-#

3-3-9 Kyutaromachi Chuo-ku Osaka-shi, Osaka
541-0056, Japan
Tel +81-3-6261-7888(7-71-#

1-8-30-1 Daimyo, Chuo-ku, Fukuoka
810-0041, Japan
Tel +81-92-732-4211