ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 1 of 42

製 品 仕 様 書
品名 ： ハイブリッドパワーコンディショナ
型式 ： NXB-MHP40330

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 2 of 42

目次
１．適用 ··························································································································································································3
１．１ 適用範囲 ·····································································································································································3
１．２ 準拠規格 ·····································································································································································3
２．概要 ··························································································································································································4
２．１ 製品構成 ·····································································································································································4
２．２ システム概要·····························································································································································5
２．３ システムブロック図 ·················································································································································6３．仕様 ··························································································································································································7
３．１ 定格仕様 ·····································································································································································7
３．２ ECHONET Lite······················································································································································· 10
３．３ 動作モード ······························································································································································· 10４．系統連系保護 ···································································································································································· 11
５．蓄電システムアダプタ仕様··········································································································································· 13
５．１ 概要············································································································································································ 13
５．２ 仕様············································································································································································ 13
５．３ 外観及び各部名称 ·············································································································································· 14
５．４ 表示・設定 ······························································································································································· 15
６．エラー・ワーニングコード一覧 ····································································································································· 17
７．一般事項·············································································································································································· 22
７．１ 周囲条件 ·································································································································································· 22
７．２ 外観仕様 ·································································································································································· 23
７．２．１ 外形寸法 ······················································································································································ 23
７．２．２ 外部 I/F ························································································································································ 25
７．２．３ 表面仕様 ······················································································································································ 29
７．２．４ 銘板・ラベル ················································································································································ 30
７．３ 梱包仕様 ·································································································································································· 34
８．据付工事に関する注意事項 ······································································································································· 37
８．１ 設置条件 ·································································································································································· 38
８．２ 設置スペース ························································································································································· 39
８．３ 固定ピッチ ······························································································································································· 40
９．本製品ご使用に関してのご承諾事項 ······················································································································ 40

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 3 of 42

１． 適用
１．１ 適用範囲
この仕様書は、ハイブリッドパワーコンディショナ NXB-MHP40330(以下 PCS) に適用する。 尚、本モデ
ルは蓄電池ユニット NXA-LU30100、NE コネクト NEDL-103FS、表示モニターNEMT-101S とセットで使用するものとする。
１．２ 準拠規格１）日本産業規格（JIS）
・JIS C 4412-1：低圧蓄電システムの安全要求事項
・JIS C 8961：太陽光発電用パワーコンディショナの効率測定方法
・JIS C 8980：小出力太陽光発電用パワーコンディショナ
２）「蓄電池システムの一般及び安全要求事項（１）」 １０
３）ECHONET Lite AIF 認証
４）日本電機工業会規格（JEM）
５）系統連系規定
・JEAC9701-2017

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 4 of 42

２．概要
２．１ 製品構成
本システムの構成を以下に示す。
表２－１ 製品構成
No.
1

項目

数量

PCS

NXB-MHP40330

1

2

通信ケーブル(6m)

-

1

3

主幹 CT

CTF-16-S

2

4

主幹用 CT ケーブル(20m)CT-M2015

蓄電システムアダプタユニット

NXB-RCR01-NF

1

6

蓄電システムアダプタユニット用タッピングネジ

M4×10

2

ケーブルグランド

RMW16S-8S

1

取扱説明書

-

1

9

製品保証書

-

1

10

施工説明書

-

1

11

個別試験成績書

-1

出荷品リスト-1

主幹 CT 用延長ケーブル(20m)

CT-M-EXT201

外部計測用 CT キット

CT-P201

外部計測 CT 用延長ケーブル(20m)

CT-P-EXT20

1

7
8

本体

型式

付属品

（系統連系申請用）
12
13
14
15

別売り
オプション

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 5 of 42

２．２ システム概要
本システムは、太陽電池モジュール及び蓄電池ユニットを直流電源とし、系統（商用電源）に接続して動作する住宅用ハイブリッド蓄電システムである。さらに、自立運転機能を有し、住宅内負荷に交流電源を供給する。蓄電池ユニットは NXA-LU30100 を使用し、ハイブリッドパワーコンディショナと蓄電池ユニットの別体型の構成となる。

図２－１ システム概要

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

２．３ システムブロック図
本システムのブロック図を以下に示す。

図２－２ ブロック図

Ver1.00

Page 6 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 7 of 42

３．仕様
３．１ 定格仕様
ハイブリッドパワーコンディショナの定格仕様を以下に示す。
表３－１ 定格仕様
項目

仕様

定格電圧

AC101V/202V

電圧変動範囲AC202V(±10%)

定格周波数50/60Hz(±2%)
システム

15kVA

単相 3 線(3W+PE)

PCS：4kVA+系統：11kVA

定格出力
電力

備考

PCS

4kW（力率 1.0 時）
4kW（力率 0.95 時）

定格電流

75A
PV 入力～AC

系統連系
入出力

変換効率

（AC）

PCS：20A+系統：55A

92.5%

出力間
蓄電池入力～

放電：89%

AC 出力間

充電：89%

定格時

力率一定制御（指定力率）

指定力率

：0.95

高調波電流歪率

総合 5%以下（各次 3%以下）
系統連系規定（JEAC9701-2017）準拠
系 統 過 電 圧 (OVR) 、 系 統 不 足 電 圧

詳細は「４．系統連系保護」を参照のこと(UVR)、系統過周波数(OFR)、系統不保護機能

足周波数(UFR)
単独運転検出（受動、能動）FRT 機能他装置内部保護

自立
出力
（AC）

定格電圧

AC101V/202V

電圧変動範囲AC202V(±12V)

定格周波数50/60Hz(±2%)

自動設定

3kVA

負荷の力率は 0.8 以上

定格出力電力

変換効率

蓄電池入力～
AC 出力間単相 3 線(3W+PE)

とする
88.8%

定格時

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

定格電圧

DC102.4V

動作電圧範囲DC97.6～112V

放電時
蓄電池
入出力
（DC）

Ver1.00

2kW/蓄電池変換効率

（連系時）
定格入力

充電時

電力

（連系時）
充電時

Page 8 of 42

蓄電池入力～
AC 出力間の効率

2kW：CCCV（CC:20A、CV:108.5V）

3kW

（自立時）
最大入力電流

42A

入力回路数

1

定格電圧

DC330V

入力電圧範囲DC0～450V

動作電圧範囲

DC70～435V

MPPT 電圧範囲

DC75～435V

過積載時の動作点方
向は低電流、高電圧側

PV 入力

最大許容入力電圧

（DC）

1 回路

DC450V
2kW/PV 入力変換効率

効率

定格入力
電力

PV 入力～AC 出力間の3 回路合計4kW/PV 入力変換効率

PV 入力～AC 出力間の
効率

主回路
方式

その他

最大入力電流

11A

入力回路数

3

変換方式

連系時

電圧型電流制御方式

自立時

電圧型電圧制御方式

スイッチング方式

正弦波 PWM 方式

絶縁方式

トランスレス方式

制御電源系統及び内部バスより給電

絶縁耐圧

AC1500V、1 分間

冷却方式

自然空冷

保護等級

IP55 相当

騒音レベル

瞬時：60dB 以下、連続：40dB 以下

A 特性

輸送振動試験＋跳ね上がり振動試

JIS Z 0200：2013

験（ランダム振動試験：振動数 3.0～

レベル 2200Hz、上下方向に 90+20 分間加

PCS は梱包状態耐振動振）を行い、性能に異常無きこと

系統側優先

内部循環ファン付きハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 9 of 42

定格銘板、型式銘板、注意銘板、警本体表示

告銘板、ブランドロゴ

梱包表示

製造番号銘板、輸送時ケアラベル、
ブランドロゴ

その他
外形寸法

質量

PCS

W694mm×D310mm×H1150mm

梱包状態

W750mm×D330mm×H1195mm

PCS

約 98kg

梱包状態

約 105kg

突起部除く

付属品含む

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 10 of 42

３．２ ECHONET Lite
本システムは蓄電システムアダプタを介し ECHONET Lite ネットワークに接続され、蓄電システムの動作状況取得や制御が可能となる。本システムは ECHONET Lite の蓄電池クラス及び住宅用太陽光発電ク
ラス規定に則しております。（Release K 対応（2019 年 11 月 29 日現在））
３．３ 動作モード
本システムの動作モードを以下に示す。
表３－４ 動作モード
No.

項目

1

モード
経済モード

内容
昼間、太陽光発電の余剰電力は売電する。
夜間、系統の電力でバッテリを充電する。ダブル発電とならないように動作する。ただし、本システム外の発電機と併用する場合はダブル発電となる。

23

自家消費モード系
統
連系
時

昼間、太陽光の余剰電力でバッテリを充電する。
バッテリが満充電時には売電する。
夜間、系統の電力でバッテリを充電する。

バックアップモード

バッテリをほぼ満充電状態にし、停電時に備える。
昼間、太陽光発電の電力でバッテリを充電する。
バッテリが満充電時には売電する。
夜間、系統の電力でバッテリを充電する。
停電時に備えるため、バッテリからの放電はしない。

4
5

HEMS モード
自立時

発電状態によらず、上位側の指令により動作する。
系統が停電した場合、自動的に家庭内負荷（U,O,W）に単相

自立モード

3 線（200V/100V）を出力する。
また、復電した場合、自動的に連系運転に復帰する。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 11 of 42

４．系統連系保護系統連系運転に対する保護として有する機能を以下に示す。
表４－１ 系統連系保護整定値一覧
継電器名

設置
相数

系統過電圧(OVR)

2

系統不足電圧(UVR)

2

整定値（初期値）

整定範囲

検出レベル

115V

105～125V（5V ｽﾃｯﾌﾟ）

検出時限

1.0s

0.5～2s（0.5s ｽﾃｯﾌﾟ）

検出レベル

80V

80～100V（5V ｽﾃｯﾌﾟ）

検出時限

1.0s

0.5～2s（0.5s ｽﾃｯﾌﾟ）

51Hz

系統過周波数(OFR)

1

検出レベル

（50Hz 時）61.2Hz（60Hz 時）

検出時限

1.0s
47.5Hz系統不足周波数(UFR)

1

検出レベル

（50Hz 時）57.0Hz（60Hz 時）逆電力(RPR)
受動的方式
単独運転

電圧位相跳躍

2

－

能動的方式

検出機能
ｽﾃｯﾌﾟ注入付周波数

50.5～52.0Hz（0.5Hz ｽﾃｯﾌﾟ）

60.6～62.4Hz（0.6Hz ｽﾃｯﾌﾟ）
0.5s～2s（0.5s ｽﾃｯﾌﾟ）
47.5～49.5Hz（0.5Hz ｽﾃｯﾌﾟ）

57.0～59.4Hz（0.6Hz ｽﾃｯﾌﾟ）

検出時限

2.0s

0.5～2s

検出レベル

100W

固定

検出時限

0.5s 以内

固定

検出レベル±7.2 度

固定

検出時限

0.5s

固定

検出レベル

-

-

検出時限

0.2s

固定

検出時限

150s

5s～300s（5s ｽﾃｯﾌﾟ）

検出レベル28Arms

固定

検出時限

0.5s 以内

固定

検出レベル

125V

固定

検出時限

1s 以内

固定

検出レベル

109V

－

ﾌｨｰﾄﾞﾊﾞｯｸ方式

復電後再投入阻止機能－

過電流(OCR－H)

1

瞬時系統過電圧2

電圧上昇抑制機能2

抑制方式：出力制御（有効電力制御）
出力抑制値：0%ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 12 of 42

制定範囲：107～113V(0.5V ｽﾃｯﾌﾟ)
直流分検出

-

直流過電圧（PV）-

直流不足電圧（PV）-

直流過電圧（蓄電池）-

直流不足電圧（蓄電池）

-

検出レベル

200mA

固定

検出時限

0.5s

固定

検出レベル

450V

固定

検出時限

0.5s

固定

検出レベル

50V

固定

検出時限

0.5s

固定

検出レベル

110V

固定

検出時限

0.5s

固定

検出レベル

86V

固定

検出時限

0.5s

固定

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 13 of 42

５．蓄電システムアダプタ仕様
５．１ 概要本蓄電システムアダプタは、NE コネクトとハイブリッドパワーコンディショナ間で、ECHONET Lite（以下 EL）変換アダプタとして機能し、ハイブリッドパワーコンディショナを EL ネットワークへ接続可能とする。
EL ノードとして、蓄電池クラスと住宅用太陽光発電クラスを搭載する。

図５－１ 蓄電システムアダプタ概要
５．２ 仕様
蓄電システムアダプタの仕様を以下に示す。
表５－１ 蓄電システムアダプタ仕様
項目
電源
通信
表示

スイッチ
一般仕様

仕様

入力電圧

DC24V

消費電力

4W 以下

RS-4852 線式 1 系統

Ethernet

10BASE-T/100BASE-TX

LCD Display

16 文字×2 行、バックライト付き

LED

6 種類

リセットスイッチ

1個

操作スイッチ6個

サイズ

180×100×39.1mm

質量

約 250g

ケース材質

UL94-V0

動作温度範囲0～40℃

備考
DC10～25V
非絶縁
パラレル I/F

突起部除く

難燃性 ABSハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

５．３ 外観及び各部名称
外観及び各部の名称とはたらきを以下に示す。
詳細寸法及び外部 I/F については「７．２ 外観仕様」を参照。

図５－３ 蓄電システムアダプタ外観図

図５－４ 各部の名称とはたらき

Page 14 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 15 of 42

５．４ 表示・設定
蓄電システムアダプタの表示及び設定項目を以下に示す。
表５－２ スイッチ仕様
No.

領域

モード

1
ユーザ操作

時間

用途

[運転/停止]3秒

運転⇔停止切替

5秒

異常リセット

3秒

ユーザ操作移行

状態表示[ﾓｰﾄﾞ]＋[ｾｯﾄ]

2

3

SW 操作

＋[▼]

メンテナンス

設定中

操作

でない

［ｾｯﾄ］

表５－３ LED 仕様
No.

最終表示

内容

条件

備考

運転状態が
1

STATUS

運転状態を表示・連系運転中：点灯

2 秒周期：

・自立運転中：点滅(2 秒周期)

1 秒点灯、1 秒消灯

・停止：消灯・異常状態が有：点灯
2

ERROR

異常状態を表示・警報状態が有：点滅 (2 秒周期)
・両方無：消灯

異常/警報両方有りの場合は点灯とする

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 16 of 42

表５－４ 蓄電システムアダプタ設定項目（ユーザ）
No.

領域

項目

1

運転モード

2

放電残量

内容（選択肢）

経済モード/自家消費モード/
バックアップモード/HEMＳモード

0～100%
充電開始時間 1:0～23 時、0～59 分
充電終了時間 1:0～23 時、0～59 分

3

ユーザ

充放電時刻

放電開始時間 1:0～23 時、0～59 分
放電終了時間 1:0～23 時、0～59 分
放電開始時間 2:0～23 時、0～59 分
放電終了時間 2:0～23 時、0～59 分
YYYY/MM/DD

4

日付

YYYY:0x07E3～0x0801(2019～2049)
MM :0x01～0x0C(1～12)
DD :0x01～0x1F(1～31)
hh:mm

5

時刻

hh:0x00～0x17(0～23)
mm:0x00～0x3B(0～59)

6

自動復帰機能無効/有効ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 17 of 42

６．エラー・ワーニングコード一覧
エラー及びワーニングコードを以下に示す。
表６－１ エラーコード一覧
ｴﾗｰｺｰﾄﾞ

内容

E01

IPM 異常(インバータ)

E02

インバータ過負荷原因

対処方法
蓄電システムアダプタにてエラーリセット後、再度、運転を開始する。エラー表示が消えない場合は、お買い上げの販売店へ製品型

PCS が異常な状態を検E03

式・エラーコードをご連絡下さい。

インバータ過電流
知E04

インバータ瞬時出力過電流 1E05インバータ瞬時出力過電流 2インバータ出力電流直流分検

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して出下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

E07
E08

製品型式・エラーコードをご連絡下さい。

中間過電圧
PCS が異常な状態を検E09

中間瞬時過電圧知
蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E0A

交流漏電検出下さい。エラー表示が消えない場合は、以下の絶縁抵抗を測定し
て下さい。

E0F

不平衡過電圧(自立)1

蓄電システムアダプタにてエラーリセット後、再度、運転を開始してPCS が異常な状態を検E10

不平衡過電圧(自立)2E11出力電流制御知下さ い。エラー表示が消えない場合は、お買い上げの販売店へ
製品型式・エラーコードをご連絡下さい。
蓄電システムアダプタにてエラーリセット後、再度、運転を開始してPCS が異常な状態を検E12下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

中間電圧制御知E13

製品型式・エラーコードをご連絡下さい。

出力電圧制御パワーコンディショナと商用電圧が正しく配線されているか確認し
E1C

商用電圧センサて下さい。配線に問題が無い場合は、お買い上げの販売店へ製品型式・エラーコードをご連絡下さい。

E1D

出力電流センサ

E1E

中間電圧センサ

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して下さ い。エラー表示が消えない場合は、お買い上げの販売店へ
PCS が異常な状態を検E1F

連系起動異常知E20

自立起動異常E21

リレー異常（MC1）E22リレー異常（MC2）E23リレー異常（MC6）E24リレー異常（MC9）

製品型式・エラーコードをご連絡下さい。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

PCS と蓄電システムア
蓄電システムアダプタ通信異E2B

ダプタ間の通信異常を常検出。

Ver1.00

Page 18 of 42

PCS と蓄電システムアダプタの通信ケーブルおよび配線接続が正しく配線されているか確認して下さい。配線に問題が無い場合は、お買い上げの販売店へ製品型式・エラーコードをご連絡下さい。

蓄電システムアダプタにてエラーリセット後、再度、運転を開始してPCS が異常な状態を検E31インバータ制御基板異常下さい。エラー表示が消えない場合は、お買い上げの販売店へ製知
品型式・エラーコードをご連絡下さい。

E39

IPM 異常(蓄電池)

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E3A

IPM 異常(PV)下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

E3B

中間過電圧 2

製品型式・エラーコードをご連絡下さい。

E3C

中間瞬時過電圧 2E3D

中間過電圧 3

E3E

中間瞬時過電圧 3E3F

蓄電池過電圧E40

蓄電池瞬時過電圧
PCS と蓄電池が正しく配線されているか確認し、蓄電池入出力端子の電圧を測定して下さい。

E41

蓄電池低電圧PCS が異常な状態を検蓄電システムアダプタにてエラーリセット後、再度、運転を開始して知下さ い。エラー表示が消えない場合は、お買い上げの販売店へ
製品型式・エラーコードをご連絡下さい。

E42

蓄電池瞬時過電圧

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E43

蓄電池過電流下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

E44

蓄電池瞬時過電流

製品型式・エラーコードをご連絡下さい。

E45

蓄電池過負荷蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E46

蓄電池漏洩電流下さ い。エラー表示が消えない場合は、お買い上げの販売店へ
製品型式・エラーコードをご連絡下さい。

E47

・太陽電池の絶縁抵抗

PV 漏洩電流・蓄電池の絶縁抵抗
E49

蓄電池電流制御

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E4A

蓄電池電圧制御下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

E4B

中間電圧制御PCS が異常な状態を検E4C

PV1 電圧制御出E4D

PV2 電圧制御E4E

PV3 電圧制御製品型式・エラーコードをご連絡下さい。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 19 of 42

E50

中間電圧 2 センサ

運転を停止したあと、再度、運転を開始してください。エラーが解消

E51

中間電圧 3 センサ

されれば運転を再開します。エラーが解消されない場合は、システ

E52

蓄電池 DC/DC 起動異常

ムを完全停止させてお買い上げの販売店 へ連絡してください。

E53

PV1 DC/DC 起動異常

E54

PV2 DC/DC 起動異常

E55

PV3 DC/DC 起動異常

E56

PV 接続シーケンス異常

PCS が異常な状態を検知PCS と蓄電池の通信ケーブルおよび配線接続が正しく配線されているか確認して下さい。配線に問題が無い場合は、お買い上げのE57

蓄電池起動異常販売店へ製品型式・エラーコードをご連絡下さい。

お買い上げの販売店へ製品型式・エラーコードをご連絡下さい。
蓄電池が内部の異常を
E58

BMS 異常検知E59

リレー異常（MC3）

蓄電システムアダプタにてエラーリセット後、再度、運転を開始して

E5A

リレー異常（MC5）下さ い。エラー表示が消えない場合は、お買い上げの販売店へ

E5B

リレー異常（MC10）PCS が異常な状態を検E5C

リレー異常（MC11）

知E5D

リレー異常（MC12）E5E

リレー異常（MC13）

製品型式・エラーコードをご連絡下さい。

PCS と蓄電システムアダプタの通信ケーブルおよび配線接続が正PCS と蓄電システムア
しく配線されているか確認して下さい。配線に問題が無い場合は、蓄電システムアダプタ通信異E63

ダプタ間の通信異常をお買い上げの販売店へ製品型式・エラーコードをご連絡下さい。

常検知

蓄電システムアダプタにてエラーリセット後、再度、運転を開始してPCS が異常な状態を検E69

コンバータ制御基板異常下さ い。エラー表示が消えない場合は、お買い上げの販売店へ
知
製品型式・エラーコードをご連絡下さい。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 20 of 42

表６－２ ワーニングコード一覧
ﾜｰﾆｸﾞｺｰﾄﾞ

内容

原因

対処方法
商用電圧が正常復帰すると、自動的に運転を再開します。

商用電圧で瞬間的に過W02

出力電圧瞬時過電圧

エラー表示が消えない場合は、お買い上げの販売店へ製品型式・
電圧を検知
エラーコードをご連絡下さい。
正常復帰すると、自動的に運転を再開します。
PCS が異常な状態を検W04

中間電圧瞬時不足電圧

エラー表示が消えない場合は、お買い上げの販売店へ製品型式・
知
エラーコードをご連絡下さい。

W0D
W0E

ファン 1
ファン 2

PCS が異常な状態を検知

エラー表示が消えない場合は、お買い上げの販売店へ製品型式・
エラーコードをご連絡下さい。

温度が正常に復帰すると、自動的に運転を再開します。
W0F

温度上昇

PCS 内部が高温を検知

PCS の設置環境（直射日光があたっていないか等）を確認して下さい。
エラー表示が消えない場合は、お買い上げの販売店へ製品型式・

W10

温度低下

PCS 内部が低温を検知
エラーコードをご連絡下さい。

W11

W12

商用電圧の周波数が上

商用電圧の周波数が正常に復帰すると、自動的に運転を再開しま

昇を検知

す。表示が継続するときは、お買い上げの販売店へ製品型式・エ

商用電圧の周波数が低ラーコードをご連絡下さい。

商用過周波数商用不足周波数
下を検知
表示が継続するときは、お買い上げの販売店へ製品型式・エラー
負荷急変による逆電力

W13

コードをご連絡下さい。

逆潮流
を検知

W14

W15

単独運転検出(受動)

商用過電圧

商用電圧の周波数に異商用の周波数が正常に復帰すると、自動的に運転を再開

常が発生し、単独運転します。 継続的に発生する場合は、お買い上げの販売店へ製品を検知

型式・エラーコードをご連絡下さい。

商用電圧が上昇を検知

商用電圧が正常に復帰すると、自動的に運転を再開します。表示が継続的する場合は、お買い上げの販売店へ製品型式・エラーコ

W16

W17

商用不足電圧単独運転検出(能動)商用電圧が低下を検知

ードをご連絡下さい。

商用電圧の周波数に異商用電圧の周波数が正常に復帰すると、自動的に運転を再開しま常が発生し、単独運転

す。継続的に発生する場合は、お買い上げの販売店へ製品型式・を検知

エラーコードをご連絡下さい。

W18

商用（R 相)過電圧

商用電圧が上昇を検知

W19

商用（R 相)不足電圧

商用電圧が低下を検知

W1A

商用（S 相)過電圧

商用電圧が上昇しました。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

W1B

商用（S 相)不足電圧

W1C

商用（R 相)不平衡過電圧

W1E

商用電圧が正常に復帰すると、自動的に運転を再開します。継続

W1F

商用（S 相)不平衡過電圧

単独運転検出(受動)的に発生する場合は、お買い上げの販売店へ製品型式・エラーコ
ードをご連絡下さい。

商用電圧の周波数に異商用電圧の周波数が正常に復帰すると、自動的に運転を常が発生し、単独運転再開します。継続的に発生する場合は、お買い上げの販売店へ製を検知

品型式・エラーコードをご連絡下さい。
商用電圧が正常に復帰すると、自動的に運転を再開します。継続

商用（R 相)不平衡過電圧
商用電圧の異常を検知

W20

Page 21 of 42

商用電圧が低下を検知

商用電圧の異常を検知
W1D

Ver1.00

商用（S 相)不平衡過電圧

的に発生する場合は、お買い上げの販売店へ製品型式・エラーコ
ードをご連絡下さい。
正常に復帰すると、自動的に運転を再開します。

PCS が異常な状態を検W21

中間 2 不足電圧(瞬時)エラー表示が消えない場合は、お買い上げの販売店へ製品型式・
知
エラーコードをご連絡下さい。
正常に復帰すると、自動的に運転を再開します。
PCS が異常な状態を検W23

中間 3 不足電圧(瞬時)エラー表示が消えない場合は、お買い上げの販売店へ製品型式・
知
エラーコードをご連絡下さい。
太陽電池の電圧（直流）を測定して下さい。PCS の入力電圧範囲

W27PV1 過電圧(瞬時)W28

PV2 過電圧(瞬時)W29

PV3 過電圧(瞬時)W2B

PV1 過電流(瞬時)W2C

PV2 過電流(瞬時)W2D

PV3 過電流(瞬時)

太陽電池入力電圧が入を超えている場合は、以下の原因が考えられます。

力電圧上限を検知

・太陽電池の異常発生。
・太陽電池の誤接続。
正常に復帰すると、自動的に運転を再開します。

PCS が異常な状態を検

エラー表示が消えない場合は、お買い上げの販売店へ製品型式・

知

エラーコードをご連絡下さい。

温度が正常に復帰すると、自動的に運転を再開します。
W2F

温度上昇

PCS 内部が高温を検知

PCS の設置環境（直射日光があたっていないか等）を確認して下さい。
エラー表示が消えない場合は、お買い上げの販売店へ製

W30

温度低下

PCS 内部が低温を検知

品型式・エラーコードをご連絡下さい。
太陽電池と PCS の接続を確認してください。

W32

PV1 誤接続
太陽電池入力電流が異W33

PV2 誤接続W34

PV3 誤接続W35

PV1 過電圧(過積載)常な状態を検出

太陽電池入力電圧が入配線に問題がない場合は、太陽光発電用ブレーカを「オフ」にして、お買い上げの販売店へ連絡してください。

太陽電池の電圧（直流）を測定して下さい。PCS の入力電圧範囲

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

W36

PV2 過電圧(過積載)W37

PV3 過電圧(過積載)

力電圧上限を検知

Ver1.00

Page 22 of 42を超えている場合は、以下の原因が考えられます。
・太陽電池の異常発生。
・太陽電池の誤接続。

７．一般事項７．１ 周囲条件
PCS の周囲条件を以下に示す。
表７－１ 周囲条件
項目
設置場所

仕様

ハイブリッドパワーコンディショナ

屋外設置（自立据置型）

蓄電システムアダプタ

屋内設置

設置標高

1000ｍ以下

使用温度－10℃～40℃

保存温度

0℃～35℃

備考

動作周囲湿度

90%以下

結露なきこと

保存湿度

90%以下

結露なきことハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 23 of 42

７．２ 外観仕様
７．２．１ 外形寸法
PCS 及び蓄電システムアダプタの外形寸法を以下に示す。（以下単位は mm とする）
１）PCS

図７－１ PCS 外形寸法

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 24 of 42２）蓄電システムアダプタ

図７－２ 蓄電システムアダプタ外形寸法※蓄電システムアダプタは、蓄電システムアダプタユニットとして以下の形態で納入される。

図７－３ 蓄電アダプタユニット外形寸法図

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 25 of 42

７．２．２ 外部 I/F
PCS 及び蓄電システムアダプタの外部 I/F を以下に示す。
１）PCS

図７－４ 主回路端子台
表７－２ 主回路端子台詳細
No.

端子名称

用途

備考

1

R

交流入力 R 相

M6-8P ネジアップ端子台

2N

交流入力 N 相

締付トルク：3.5～4.0N・m

3

S

交流入力 S 相

4U

交流出力 U 相

5O

交流出力 O 相

6W

交流出力 W 相

7

N (-)

バッテリ-

8

P (+)

バッテリ+

9

E

バッテリ 接地

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 26 of 42

図７－５ アース端子台
表７－３ アース端子台詳細
No.
1

端子名称
PE

用途
アース接続

備考
M8-1P セルフアップ端子台
締付トルク：5.5～6.0N・m

図７－６ PV 入力ブレーカ
表７－４ PV 入力ブレーカ詳細
No.

端子名称

用途

備考

1

N1

PV1-

板端子接続

2

P1

PV1+

締付トルク：1.3～2.0N・m

3

N2

PV2-

推奨端子：5.5-AF4A-S(JST)

4

P2

PV2+

5

N3

PV3-

6

P3

PV3+

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 27 of 42

図７－７ 蓄電システムアダプタ端子台（PCS 側）
表７－５ 蓄電システムアダプタ端子台詳細
No.

端子名称

用途

備考

1

P24

入力電源+

M4-4P ネジアップ端子台

2

N24

入力電源-

締付トルク：1.0～1.3N・m

3

A(+)

通信信号+

シールド付きツイストペアケー

4

B(-)

通信信号-

ブル 2P×2※シールド線の編組銅線を付属の固定具によりクランプし、シールドする。

図７－８ CT 接続コネクタ(PB1100C)
表７－６ CT 接続コネクタ詳細
No.

端子名称

用途

備考

1

BMU

バッテリとの通信

付属の通信ケーブルと接続

2主幹

主幹電流計測付属の主幹用 CT ケーブルと接
続

3

分岐

外部 PV 電流計測

付属の外部計測用 CT キットと接続

※ケーブルのシールド線を付属の M3 ねじで接続し、シールドする。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 28 of 42２）蓄電システムアダプタ

図７－９ 蓄電システムアダプタ端子台
表７－７ 蓄電システムアダプタ端子台詳細【RS485】
No.

端子名称

用途

備考

1

P24

入力電源+

棒端子接続

2

N24

入力電源-

推奨端子：FE-0.5-8N(WAGO)

3

SG

シグナルグランド

未接続

4

A(+)

通信信号+

RS-485（2 線式）

5

B(-)

通信信号-

6

N.C

不使用

未接続

7

N.C

不使用

未接続

表７－８ 蓄電システムアダプタ端子台詳細【RJ-45】
No.

用途

1

Ethernet 通信

備考
10BASE-T/100BASE-TX
表７－９ LED 表示

No.

名称

色

用途

1

POWER

緑

電源状態

2

ETHER

黄

Ethernet 通信状態

3

TXD

黄

RS-485 送信状態

4

RXD

黄

RS-485 受信状態

5

STATUS黄系統連系状態

6

ERROR

赤

異常/警報状態

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 29 of 42

表７－１０ スイッチ操作
No.

名称

用途

1

運転/停止

PCS の運転/停止

2

モード

メンテナンス操作の項目を移動し選択

3

クリア

変更なし

4

セット

確定

5

▲

前の「項目」や「数値」に移動

6▼

次の「項目」や「数値」に移動

７．２．３ 表面仕様
PCS 及び蓄電システムアダプタの表面仕様を以下に示す。
表７－１１ 表面仕様
部品
PCS（表面）
蓄電システム
アダプタ

材質
電気亜鉛メッキ鋼板
ABS色
5Y9/0.5
白

備考
レザートーン調
難燃性 UL94-V0

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

７．２．４ 銘板・ラベル
PCS 及び蓄電システムアダプタのラベル位置図及びラベル図を以下に示す。
１）PCSPage 30 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

図７－１０ PCS ラベル位置

Ver1.00

Page 31 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

図７－１１ PCS ラベル図

Ver1.00

Page 32 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00２）蓄電システムアダプタ

図７－１２ 蓄電システムアダプタラベル位置

図７－１３ 蓄電システムアダプタラベル図Page 33 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

７．３ 梱包仕様
PCS 及び付属品の梱包仕様を以下に示す。

図７－１４ 梱包仕様

Ver1.00

Page 34 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

また、PCS は 4 台を 1 個口とし、以下のようにパレットに搭載後、輸送する。

図７－１５ 荷姿図

Page 35 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 36 of 42

梱包材に表示されるケアラベル及び梱包銘板を以下に示す。また、ラベル位置を以下に示す。

図７－１６ 輸送時ケアラベル図

図７－１７ 梱包銘板

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

８．据付工事に関する注意事項（１） 施工組立手順書に沿って設置すること。
（２） 施工 ID 取得者にて設置を行うこと。
（３） 装置重量に耐えうる基礎を準備すること。
（４） 水平に設置すること。
（５） 雨天時の施工は極力実施しないこと。
実施する場合は、雨滴が装置に触れないように養生を実施すること。

Page 37 of 42

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 38 of 42

８．１ 設置条件
PCS の設置条件を以下に示す。
表８－１ 設置条件
項目

説明

日射

直射日光が当たらない場所へ設置すること。北側に面した場所への設置を推奨する。

換気

換気設備のない空気が滞留するような密閉された場所へは設置しないこと。

固定方法
温度

重量物のため、装置をアンカーボルトで固定できる基礎に設置すること。
本製品は寒冷地区仕様ではないため、外気温が-10℃以下になると装置は停止する。
本蓄電システムの設置は重塩害地域（外海の海岸から約 500m 以内、沖縄や離島の場合は海岸から約 1km 以内）は設置しないこと。また塩害地域（内海の海岸から約 500m 以内、外海の海岸から約 500m～1km 以内、沖縄や離島の場合は海岸から約 1km 以内を除く地域）に設置する場合
は、潮風が直接当たらず、かつ外装に付着した塩分等が、雨水により自然に洗い流される様な場所に設置すること。さびや腐食等により故障や寿命が短くなる可能性がある。
なお、塩害による故障や損傷は，保証期間であっても有償での修理または交換となる。

塩害（塩害・重塩害地区の区分）

海

500m

内海（瀬戸内）に面する地域

塩害地域

外洋に面する地域

重塩害地域

沖縄・離島

積雪

0m

1km

2km

塩害地域

重塩害地域

塩害地域

積雪により装置が塞がれないよう、積雪の恐れがある地域へ設置する場合には基礎の高さを高く
すること。

ガス

砂塵、腐食性ガスや液体、油煙、可燃性ガスがある場所には設置しないこと。

可燃物

本装置の近くには、プラスチック・紙などの燃え易いものを置かないこと。

熱源

熱源機器（エネファーム・エコウィル・空調室外機など）は本装置から極力離して設置すること。

ノイズ

接地

スペース

医療機器の近傍や、TV 及びアマチュア無線のアンテナが近くにある場所には設置しないこと。
また、電界の影響がある場所には設置しないこと。
アース処理を確実に行うこと。ガス管・水道管・避雷針・電話などのアース線などに接続しないこと。不完全なアースは感電の原因となる。
本装置の周辺には、点検・修理の妨げになるものは置かないようにすること。
移設困難な、樹木・植栽なども考慮すること。

浸水

浸水の恐れのある場所には設置しないこと。

振動・衝撃

振勣・衝撃が加わる場所には設置しないこと。

火気

火花が発生する機器の近傍には設置しないこと。

騒音

寝室や隣家に近い場所には設置しないこと。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 39 of 42

８．２ 設置スペース
PCS の設置には、以下に示すスペースを確保すること。

500mm※2)100mm※1)200mm※1)200mm※3)600mm（※１）ドライバの入るスペースが必要。（上記寸法は目安）（※２）背面のスペースは装置より発生した熱を逃がすのに必要なため、必ず確保すること。（外壁基準：100 ㎜以上）（※３）前カバーの取り外しスペースが必要。

図８－１ 設置スペース

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 40 of 42

８．３ 固定ピッチ
PCS は以下寸法にてアンカーボルトで固定し、設置すること。

図８－２ 据え付けピッチ
９．本製品ご使用に関してのご承諾事項（１）保証内容①保証期間
PCS 本体は設置完了後 10 年保証とする。
蓄電システムアダプタユニットは設置完了後 1 年保証とする。
②保証範囲
上記保証期間中に当社側の責により本製品のマニュアルにしたがって実質的に動作しない故障が生じた場合は、代替品の提供または故障品の修理対応を、製品の購入場所において無償で実施する。ただし、故障の原因が次に該当する場合は、この保証の対象範囲から除外する。
a）カタログまたは取扱説明書、マニュアル（以下カタログ等と記載）などに記載されている以外の条件・環境・取り扱いならびにご使用による場合
b）本製品以外の原因の場合
c）当社以外による改造または修理による場合
d）本製品本来の使い方以外の使用による場合
e）当社出荷当時の科学・技術の水準では予見できなかった場合f）その他、天災、災害など当社側の責ではない原因による場合
なお、ここでの保証は、本製品単体の保証を意味するもので、本製品の故障により誘発される損害は保証の対象から除くものとする。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
文書番号

MDPD201911002

Ver1.00

Page 41 of 42（２）責任の制限①本製品に起因して生じた特別損害、間接損害、または消極損害に関しては、当社はいかなる場合も責任を負わないものとする。
②プログラミング可能な本製品については当社以外の者が行ったプログラム、またはそれにより生じた結果について当社は責任を負わないものとする。
（３）適合用途の条件①本製品を他の商品と組み合わせて使用される場合、お客様が適合すべき規格・法規または規制をご確認いただく。または、お客様が使用されるシステム、機械、装置への本製品の適合性は、お客様自身でご確認いただくとともに、当社営業担当者へ確認いただく。
これらを実施されない場合は、当社は本製品の適合性について責任を負わないものとする。
②カタログ等に記載されているアプリケーション事例は参考用のため、ご採用に際しては機器・装置 の機能や安全性をご確認のうえ、ご使用いただく。
③本製品が正しく使用されずお客様または第三者に不測の損害が生じることがないよう使用上の禁止事項および注意事項をすべてご理解のうえ遵守いただく。
（４）参考仕様書の扱い
本仕様書が参考用仕様書として発行された場合は、ご採用に際し当社営業担当者までご相談のう
え本製品の最新の仕様をご確認ください。
（５）サービスの範囲
当社商品の価格には、技術者派遣などのサービス費用は含まれていません。お客様のご要望があれば、当社窓口までご相談ください。
（６）適用範囲
以上の内容は、日本国内での取引および使用を前提としている。
日本国外での取引および使用に関しては、弊社窓口までご相談ください。
（７）省令改正による出力制御
本製品は省令改正による出力制御に対応しています。
※ただし、各電力会社に対して申請が必要となりますので、出力制御対象時は別途お問い合わせください。また、出力制御の詳細については、経済産業省ホームページ等をご確認ください。

ハイブリッドパワーコンディショナ製品仕様書(NXB-MHP40330)
MDPD201911002

文書番号

Ver1.00

Page 42 of 42

改訂履歴
No.

変更日

変更内容

該当ペー
ジ

1

2019 年 11 月 25 日

初版

蓄電池ユニット製品仕様書(NXA-LU30100)
MDPD201910001

文書番号

製

品

仕

Ver1.00

様書

品名：蓄電池ユニット
型式：NXA-LU30100

Page 1 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 2 of 17

目 次
1 適応範囲 .............................................................................. 3
2 仕様 .................................................................................... 3
2.1 概略仕様 ......................................................................... 3
2.2 基本仕様 .......................................................................... 43 機能 .................................................................................... 5
4 エラー ................................................................................... 65 外観仕様 .............................................................................. 7
5.1 外形寸法 ........................................................................ 7
5.2 印刷表示位置................................................................... 8
5.3 印刷表示 ........................................................................ 8
5.4 梱包仕様・外形寸法 ......................................................... 10
5.5 梱包印刷表示................................................................. 11
6 その他 ................................................................................ 12
6.1 本仕様書の取り扱い .......................................................... 126.2 設置場所の制限 .............................................................. 13
6.3 使用上の注意事項 ........................................................... 14
6.4 問題発生時の処置 ........................................................... 14
7 本製品ご使用に際してのご承諾事項 .............................................. 14
8 保証内容 ............................................................................ 15
8.1 保証期間 ...................................................................... 15
8.2 保証範囲 ...................................................................... 15
8.3 責任の制限 .................................................................... 15
8.4 適合用途の条件 .............................................................. 16
8.5 参考用仕様書の扱い ......................................................... 16
8.6 サービスの範囲 ................................................................. 16
8.7 適用範囲 ...................................................................... 16

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 3 of 17

1 適用範囲この仕様書は、蓄電池ユニット NXA-LU30100 に適用する。 尚、本モデルはハイブリッドパワーコンディ
ショナ NXB-MHP40330、NE コネクト NEDL-103FS、表示モニターNEMT-101S とセットで使用するも
のとする。

2

仕様
2.1 概略仕様
本仕様書に定める蓄電池ユニットは、連系時/自立運転時ともに最大 3kVA 出力可能な定格容量
9.216kWh のリチウムイオン(LFP)型の蓄電池である。
保護機能として、電流や電圧、セル温度に対して監視機能を搭載することで高い安全性を具備している。
ハイブリッド蓄電システム(NXS-MHESS001)の構成機器の一つであるため、本蓄電池ユニット単体の使用はできません。

蓄電池ユニット製品仕様書(NXA-LU30100)
MDPD201910001

文書番号

Ver1.00

Page 4 of 17

2.2 基本仕様
以下に蓄電池ユニットの基本仕様を示す。
表 1-1 基本仕様一覧
項目

仕様
最大入力（充電）電流
最大出力（放電）電

電気的仕様

流
公称電圧

る。)
30A (電池温度により、最大放電電流は変化する。)
DC102.4V

電池電圧範囲

DC86～109.44V

内蔵蓄電池

リチウムイオン蓄電池（LFP タイプ）

蓄電池搭載容量

10.24kWh

定格容量9.216kWh電池仕様

充電回復時間
冷却方式
本体寸法
梱包寸法

形状および寸法

製品への印刷表示

環境条件

30A (電池温度により、最大充電電流は変化す

約 4 時間 （SOC 0%から 100%まで、環境温度
25℃、充電電圧 109.44V、充電電流 30A）
自然空冷
L:870 × W:350 × H:870 mm（据置き脚・突起含む）
L:1000 × W:550 × H:1072 mm

重量

約 148 kg

梱包重量

約 155 kg

本体表示

定格・PL ラベル，LED ラベル，モデルラベル

梱包表示

梱包ラベル，ケア表示ラベル，モデルラベル

設置場所

屋外／屋内 兼用設置標高1000m 以下

使用可能温度-10 ～ ＋40℃

充電可能温度

0 ～ ＋40℃

放電可能温度-10 ～ ＋40℃

動作湿度範囲90%ＲＨ以下(但し結露なきこと)

防塵・防水等級
準拠規格
認証済み試験

IP65 相当
IEC61000-6-1
IEC61000-6-3
JIS8715-2
UN38.3

蓄電池ユニット製品仕様書(NXA-LU30100)
MDPD201910001

文書番号

3

Ver1.00

Page 5 of 17

機能以下に蓄電池ユニットの機能を示す。

表 3-1 機能一覧
内容

項目
電圧保護
保護機能

電流保護
温度保護

セル電圧監視セル間電位差監視
センサ監視
ハード保護
セルの監視
LED A : 緑 動作中/ リセット中/ 待機中
黄 保護

表示機能

赤 異常停止黒 シャットダウン
LED B : 緑 CAN 通信 OK
黒 CAN 通信 NG

通信機能

CAN 500Kbit/s

蓄電池ユニット製品仕様書(NXA-LU30100)
MDPD201910001

文書番号

4

Ver1.00

Page 6 of 17

エラー

以下に蓄電システムアダプタに表示される、蓄電池ユニットのワーニングコード及びエラーコードを示す。
表 4-1 蓄電池ユニット ワーニングコード ・ エラーコード一覧（コードは蓄電システムアダプタに表示）
コード

原因

対処方法

W38

蓄電池内バッテリセルの使用温度範囲外です。

W39

蓄電池内バッテリセルが異常電圧になっています。

W3A

蓄電池内バッテリセルに異常電流が流れています。

蓄電システムアダプタにてエラーリセッ

W3B

蓄電池内バッテリセルの使用温度範囲外です。

ト後、再度、運転を開始して下さい。エ

W3C

蓄電池内バッテリセルに異常電流が流れています。

げの販売店、または当社インフォメーシ

W3D

蓄電池内バッテリセルが異常電圧になっています。

ョンセンターへ製品型式・エラーコード

W3E

蓄電池とパワコンの通信に問題が起こっています

W3F

蓄電池出力が短絡している可能性があります

W40

蓄電池内リレーの使用温度範囲外です

E6A

蓄電池内リレーの故障が考えられます

E6B

蓄電池内電気回路の故障が考えられます

E6C

蓄電池内バッテリセルの故障が考えられます

E6D

蓄電池内温度センサーの故障が考えられます

ラー表示が消えない場合は、お買い上をご連絡ください

E6E

指定温度以外での使用のため蓄電池内バッテリセル
がダメージを受けています。

E6F

蓄電池内バッテリセルの故障が考えられます

E70

蓄電池内配線が断裂している可能性があります。

お買い上げの販売店、または当社インフォメーションセンターへ製品型式・エ
ラーコードをご連絡ください

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

5

MDPD201910001

外観仕様
5.1 外形寸法
以下に蓄電池ユニットの外形寸法を示す。

Ver1.00

Page 7 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

5.2 印刷表示位置
以下に本体への印刷表示の位置を示す。

5.3 印刷表示
以下に本体への印刷表示を示す。
①

定格・PL ラベル

⓶

バーコード

Ver1.00

Page 8 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号②

LED ラベル③ モデルラベルMDPD201910001

Ver1.00

Page 9 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

5.4 梱包仕様・外形寸法
以下に梱包仕様及び、外形寸法を示す。

Ver1.00

Page 10 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

5.5 梱包印刷表示
以下に梱包印刷表示を示す。
① 梱包ラベル③

ケア表示ラベル

MDPD201910001

Ver1.00

Page 11 of 17

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 12 of 17③ モデルラベル

6その他
6.1 本仕様書の取り扱い
本仕様書の所有者は、ネクストエナジー・アンド・リソース株式会社の承認なしに本仕様書に関する内容
及び情報を第三者に開示しないこと。
＊但し、電力会社・公的機関への申請を目的とする開示はこれに該当しないものとする。

蓄電池ユニット製品仕様書(NXA-LU30100)
MDPD201910001

文書番号

Ver1.00

Page 13 of 17

6.2 設置場所の制限
本製品については以下の場所には設置しないこと。
① 重塩害地域（外海の海岸から約 500m 以内、沖縄や離島の場合は海岸から約 1km 以内、又は潮風が直接当たる場所）※各距離は目安です。距離によらず、塩害に起因する故障と判定された場合、保証対象外となります。
② 周囲温度が-10℃~+40℃の範囲外の場所（ただし、電池温度が 0℃を下回ると充電動作を停止する。）③ 直接日光が当たる場所④ 浸水、冠雪の恐れがある場所⑤ 砂塵、腐食性ガスや液体、油煙、可燃性ガスがある場所⑥ 冷気が直接あたる場所⑦ 湿気が多く、風通しが悪い場所⑧ 天地逆方向の設置や横方向あるいは水平方向に設置しなければならない場所⑨ ストーブなどの熱源から熱を直接受ける場所⑩ 振勣・衝撃が加わる場所⑪ 火花が発生する機器の近傍⑫ ＴＶ及びアマチュア無線のアンテナが近くにある場所⑬ 医療用機器の近傍⑭ 寝室や隣家に近い場所⑮ 図 1 の離隔を確保できない場所

図 1 離隔（ハイブリッドパワーコンディショナと併置した場合）

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 14 of 17

6.3 使用上の注意事項① 本製品は住宅用ハイブリッド蓄電システム用の蓄電池ユニットとなっており、本用途以外の使用はしないこと。
② 本製品は住宅用ハイブリッド蓄電システム用である。他社蓄電システムには使用しないこと。
また、それ以外の用途（例：風力発電システム、燃料電池発電システムなど）には使用しないこと。
③ 分解・改造・穴加工などお客様ご自身での修理はしないこと。安全が保証出来なくなり危険な為。また、蓄電池の保守・点検などの取り扱いは、蓄電池およびその取扱注意事項について当社の定める
トレーニングを受けた人がおこなう。
④ 蓄電池に物を入れないこと。故障の原因となる為。
⑤ 本製品の転倒等によるけがなどの危険性がある為、本製品の上に乗ったり、物を置いたりしないこと。
⑥ 火災、感電の危険性がある為、本製品本体のパネルを開けないこと。
⑦ 感電や故障の危険性がある為、本製品の接続端子台に触れたり、端子間を短絡したりしないこと。
⑧ 感電の危険性がある為、雷が鳴り出したら本製品本体や配線に触れないこと。
⑨ 水没、埋雪した後は使用しないこと。
⑩ 本製品を廃棄の際は必ず販売窓口又は修理ご相談窓口に連絡すること。

6.4 問題発生時の処置
本仕様書及び適用文書に定め無き事項および定めある事項で疑義が生じた場合、双方誠意を持って協議し解決に努めるものとする。

7

本製品ご使用に際してのご承諾事項
当社の定めた使用、保管、廃棄等に関する諸条件（本製品の取扱説明書、カタログ、仕様書等に記載された注意書き、警告を含む）を遵守してください。

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 15 of 17

保証内容
8.1 保証期間
別途取り決めによります。

8.2 保証範囲
上記保証期間中に当社側の責により本製品のマニュアルにしたがって実質的に動作しない故障を生じた
場合は、代替品の提供または故障品の修理対応を、製品の購入場所において無償で実施いたします。ただし、故障の原因が次に該当する場合は、この保証の対象範囲から除外いたします。
a) カタログまたは取扱説明書、マニュアル(以下カタログ等と記載)などに記載されている以外の条件・環境・取り扱いならびにご使用による場合
b) 本製品以外の原因の場合
c) 当社、もしくは当社指定の業者以外による改造または修理による場合
d) 本製品本来の使い方以外の使用による場合
e) 当社出荷当時の科学・技術の水準では予見できなかった場合
f) その他、天災、災害など当社側の責ではない原因による場合
なお、ここでの保証は、本製品単体の保証を意味するもので、本製品の故障により誘発される損害は保証の対象から除かれるものとします。

8.3 責任の制限① 本製品に起因して生じた特別損害、間接損害、または消極損害に関しては、当社はいかなる場合も責任を負いません。
② プログラミング可能な本製品については当社以外の者が行ったプログラム、またはそれにより生じた結果について当社は責任を負いません。

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

Ver1.00

Page 16 of 17

8.4 適合用途の条件① 本製品を他の商品と組み合わせて使用される場合、お客様が適合すべき規格・法規または規制をご確認ください。または、お客様が使用されるシステム、機械、装置への本製品の適合性は、お客様自身でご確認ください。
これらを実施されない場合は、当社は本製品の適合性について責任を負いません。
② 下記用途には使用できません。
a) 潜在的な科学的汚染あるいは電気的妨害を被る用途またはカタログ等に記載のない条件や環境での使用
b) 原子力制御設備、焼却設備、鉄道・航空・車両設備、医用機械、娯楽機械、安全装置、および行政機関や個別業界の規制に従う設備
c) 人命や財産に危険が及びうるシステム・機械・装置d) ガス、水道、電気の供給システムや 24 時間連続運転システムなど高い信頼性が必要な設備その他、
上記 a)～d)に準ずる、高度な安全性が必要とされる用途③ お客様が本製品を人命や財産に重大な危険を及ぼすような用途に使用される場合には、システム全体として危険を知らせたり、冗長設計により必要な安全性を確保できるよう設計されていること、および本製品が全体の中で意図した用途に対して適切に配電・設置されていることを必ず事前に確認してください。
④ カタログ等に記載されているアプリケーション事例は参考用ですので、ご採用に際しては機器・装置の機能や安全性をご確認のうえ、ご使用ください。
⑤ 本製品が正しく使用されずお客様または第三者に不測の損害が生じることがないよう使用上の禁止事項および注意事項をすべてご理解のうえ守ってください。

8.5 参考用仕様書の扱い
本仕様書が参考用仕様書として発行された場合は、ご採用に際し当社営業担当者までご相談のうえ本
製品の最新の仕様をご確認ください。

8.6 サービスの範囲
当社商品の価格には、技術者派遣などのサービス費用は含まれておりません。お客様のご要望がございま
したら、お買い求めの販売店様、もしくは当社営業担当者までご相談ください。

8.7 適用範囲
以上の内容は、日本国内での取引および使用を前提としております。日本国外での取引および使用に関しては、お買い求めの販売店様、もしくは当社営業担当者までご相談ください。

蓄電池ユニット製品仕様書(NXA-LU30100)
文書番号

MDPD201910001

改定履歴
Version

日時

修正概要

Rev 1.00

2019/11/25

初版

Ver1.00

Page 17 of 17