Increased Safety Fluorescent Lighting Fitting (Recessed)
Type of protection:ed3aG4 (23W), ed3aG3 (45W)◦High reliability in protection against explosion
SEIWA AGAC lighting fittings are designed andconstructed thoroughly with carefully selectedmaterials to provide high reliability in protection
against explosion.
Their quality is certified by the TIIS.
◦Made of stainless steel-high corrosion resistanceThe body, reflector, suspension pipe and bolts are
made of stainless steel.
◦Weatherproof-for outdoor use
The body, socket and ballast are weatherproof so thatthey can be used outdoors.
◦Easy cleaning of the lamp protector
The guard can be easily opened, which allows easycleaning of the lamp protector.
◦Easy installation, wiring and maintenanceInstallation is easy since the lamp is suspended by acoupling at the terminal box side and a hook at the
non-electric side suspension pipe.
◦Lamp inclination for replacement
The lamp can be inclined to facilitate replacement in aconfined space.
◦Our products, which combine high-frequency fluorescentlamps with electronic ballasts, achieve high-efficiency
power usage with a high level of luminous intensity.

AGAC23142

23W×1 (bracket)

AGAC23146

Mass : 9.0kg

55 2-8×12holes

3585
108

□85

23W×1 (pipe pendant)

Mass : 9.5kg■ Mounting dimension□120

AGAC23141

Mass : 9.0kg■ SPECIFICATIONS◦Rated voltage : 100V～242V◦Lamp : FHF32EX (45W)
FHF16EX (23W)◦Start : high frequency start◦Materials of main components
Body, reflector : stainless sheet steel
Socket : synthetic resin
Guard : nylon-coated steel bars
Lamp protector : hard glass
Terminal box : aluminium die casting
Suspension pipe: stainless steel pipe◦Colour : body : Mild grey (Munsell 10YR7/1)
reflector : white◦Finish : melamine resin coating◦Entries : four ways (G1/2 or 3/4 thread) with threeblind plugs◦Photometric data : see p.31

4-φ8holes

23W×1 (ceiling)500

6Increased Safety Fluorescent Lighting Fittings (stainless steel)
45W×1 (ceiling)

AGAC45141

45W×1 (pipe pendant)

AGAC45142

45W×1 (bracket)

AGAC45146

45W×1 (direct)

AGAC45112

Mass : 11.5kg

Mass : 12.0kg

Mass : 11.5kg

Mass : 11.0kg

45W×2 (ceiling)

AGAC45241

45W×2 (pipe pendant)

AGAC45242

45W×2 (bracket)

AGAC45246

45W×2 (direct)

AGAC45212

Mass : 13.5kg

Mass : 14.0kg

Mass : 13.5kg

Mass : 13.0kg

7Increased Safety Fluorescent Lighting Fittings (stainless steel)◦Installation drawings Type of protection : ed3aG4 (23W), ed3aG3 (45W)

AGAC45241 (45W×2)
AGAC45141 (45W×1)

335

1350 (45W)
732 (23W)

AGAC45242 (45W×2)
AGAC45142 (45W×1)

335500

AGAC23141 (23W×1)

181

181

500

1350 (45W)
732 (23W)

530

530AGAC23142 (23W×1)

181

181

AGAC45246 (45W×2)
AGAC45146 (45W×1)
500250

゜
60

゜60

18181

11350 (45W)
732 (23W)

4-8×12holes
150

1350

181

8

160

500
160

AGAC45212 (45W×2)
AGAC45112 (45W×1)

370

370

250

AGAC23146 (23W×1)

181

Increased Safety Fluorescent Lighting Fittings (stainless steel)◦Installation drawings Type of protection : ed3aG4 (23W), ed3aG3 (45W)

AGAC45151 (45W×1)
TYPE-1
AGAC45251 (45W×2)
1650
23075
゜
1350

2500

φ48.6

1022（1500）

φ48.6G3/4
Detail of A

A

AGAC45152 (45W×1) TYPE-2

AGAC45252 (45W×2) TYPE-2630630

18123075
゜

23075
゜

181

2500

φ48.6

2500

φ48.6

1022（1500）

φ48.61022（1500）

φ48.6

G3/4

G3/4

Detail of A

Detail of AAA(Finish)Stand pole : rust-proof

9

PHOTOMETRIC DATAAGAC451

AGAC231
Coeﬃcient of utilization
70%
50%30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%
tance
10%Floor
0.60 .280 .219 .176 .262 .208 .169 .197 .162
0.80 .345 .281 .234 .322 .266 .224 .252 .214
1.00 .402 .339 .291 .377 .322 .279 .305 .267
1.25 .451 .389 .340 .422 .369 .326 .349 .311
1.50 .488 .429 .381 .457 .406 .364 .384 .347
Room 2.00.540 .485 .439 .505 .459 .419 .434 .400
index
2.50 .576 .526 .483 .540 .498 .461 .470 .439
3.00 .602 .556 .515 .564 .525 .490 .496 .467
4.00 .637 .597 .561 .599 .565 .534 .533 .508
5.00 .658 .622 .589 .618 .588 .560 .555 .532
10.00 .716 .693 .672 .675 .656 .638 .621 .605
Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

cd/1000lm
0%0%.139.186.236
.277
.310
.359
.395
.421
.460.483.553

Coeﬃcient of utilization
70%50%30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%
tance
10%
Floor
0.60 .281 .219 .176 .263 .208 .169 .197 .161
0.80 .346 .281 .234 .324 .266 .224 .252 .214
1.00 .404 .340 .291 .378 .322 .279 .305 .267
1.25 .453 .391 .341 .424 .370 .326 .350 .312
1.50 .491 .431 .382 .459 .407 .465 .385 .348
Room 2.00.543 .488 .441 .508 .461 .421 .435 .401
index
2.50 .580 .529 .486 .543 .500 .463 .472 .440
3.00 .606 .559 .518 .568 .528 .493 .498 .468
4.00 .642 .602 .565 .603 .568 .537 .537 .510
5.00 .663 .627 .593 .623 .592 .563 .559 .535
10.00 .722 .699 .677 .681 .661 .643 .625 .610

180゜
150゜

150゜
120゜

120゜

90゜

90゜
50100

60゜

60゜

150
30゜

AGAC231
FHF16EX
2100m77.3%

20030゜Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

250
0゜

AGAC452
Coeﬃcient of utilization
70%50%30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%
tance
10%
Floor
0.60 .271 .214 .175 .255 .204 .168 .195 .162
0.80 .334 .275 .232 .314 .262 .223 .250 .215
1.00 .390 .333 .289 .367 .317 .278 .302 .267
1.25 .437 .381 .337 .411 .363 .324 .345 .311
1.50 .473 .420 .377 .445 .399 .362 .380 .347
Room 2.00.522 .474 .433 .492 .450 .415 .428 .398
index
2.50 .557 .513 .475 .524 .487 .455 .462 .435
3.00 .580 .540 .505 .547 .513 .483 .487 .461
4.00 .613 .579 .548 .579 .550 .524 .522 .500
5.00 .632 .602 .574 .597 .571 .547 .542 .522
10.00 .683 .664 .647 .647 .631 .616 .599 .587
Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

AGAC452
FHF32×24950m×273%

cd/1000lm
0%0%.141.189
.239
.280
.314
.361
.396
.421
.457.478.540

180゜
150゜

150゜120゜120゜90゜90゜5010060゜60゜15030゜

20030゜250
0゜

32

AGAC451
FHF32×14950m78%

cd/1000lm
0%
0%

.138
.186.235
.277
.310
.359
.396
.423
.462
.485.557

180゜150゜

150゜120゜120゜90゜90゜50
100

60゜60゜15030゜200250
0゜30゜