Increased Safety Emergency Fluorescent Lighting Fittings (With internal battery unit, stainless steel)Type of protection : ed2G3◦High reliability in protection against explosion
SEIWA BGAC lighting fittings are designed andconstructed thoroughly with carefully selectedmaterials to provide high reliability in protection
against explosion.
Their quality is certified by the TIIS.
◦Corrosion-proof
The body, reflector and suspension pipe are made ofstainless steel, assuring high corrosion resistance.
◦Weatherproof-for outdoor use
The body, socket and ballast have a weatherproof
structure so that the products can be used outdoors.
◦Lamp inclination for replacement
The lamp can be inclined to facilitate replacement in aconfined space.
◦Easy installation and wiring work
Installation is easy since the body is suspended by acoupling at the terminal box side and a hook at theopposite side suspension pipe.
◦Easy cleaning of the lamp protector
The guard can be easily opened, which allows easycleaning of the lamp protector.
◦Built-in ballast with protector
The ballast uses a capacitor with protector to ensure
safety.
◦O u r p r o d u c t s , w h i c h c o m b i n e h i g h - f r e q u e n c yfluorescent lamps with electronic ballasts, achieve highefficiency power usage with a high level of luminous
intensity.
■SPECIFICATIONS◦Rated voltage : 100V, 200V
(Other voltages can be supplied uponrequest.)◦Lamp : FHF32EX◦Start : normal : high frequency start
emergency : high frequency start◦Lighting duration in emergency : 30 min. and over
◦Luminous flux ratio in emergency : 50% and over◦Materials of main components
Body & reflector : stainless steel
Socket : synthetic resin
Guard : nylon-coated steel bars
Lamp protector : hard glass
Terminal box : aluminium die casting
Suspension pipe : stainless steel◦Colour : body : Mild grey (Munsell 10YR7/1)
reflector : white◦Finish : melamine resin coating◦Entries : four ways (G1/2 or 3/4 thread) with threeblind plugs(three ways with two blind plugs for the direct
mounting models)■Mounting dimension□120

BGAC45141

45W×1 (pipe pendant)

BGAC45142

45W×1 (bracket)

BGAC4514645W×1 (direct)

BGAC45110

Mass : 16.5kg

Mass : 17.0kg

Mass : 16.5kg

Mass : 17.5kg

55 2-8×12holes

3585108□85

4-φ8holes

45W×1 (ceiling)

500

25

※Also available in a wall-mounted type.

Increased Safety Emergency Fluorescent Lighting Fittings (With internal battery unit, stainless steel)
Mass : 18.5kg

BGAC45241

BGAC45141 (45W×1)
BGAC45241 (45W×2)
4-φ8holes □120

85108

□85

55 2-8×12holes
335

45W×2 (ceiling)

500335181

1350
Lamp replacement(inclination is possible)

Mass : 19.0kg

BGAC45142 (45W×1)
BGAC45242 (45W×2)

BGAC45242

4-φ8holes □12085108□8555 2-8×12holes
530

45W×2 (pipe pendant)

181

500

530

181

1350
Lamp replacement(inclination is possible)

Mass : 18.5kg

BGAC45246

BGAC45146 (45W×1)
BGAC45246 (45W×2)
4-φ8holes □120370

゜
60

85108

□85

55 2-8×12holes

250

45W×2 (bracket)

181

181500゜
601350Lamp replacement(inclination is possible)

181

BGAC45110 (45W×1)
BGAC45210 (45W×2)
500

4-φ8holes
160

4-8×12holes

□85

181
40160

Mass : 19.5kg

BGAC45210

150

45W×2 (direct)

250

370

1350

181
Lamp replacement(inclination is possible)

26