Explosion-Proof Type Incandescent Lamp Lighting Fittings (battery-powered, emergency lighting only)
Products conforming to the international standard (IEC Standard 60079)
Zone. 1 and 2 Areas◦Type of protection : ExdⅡBT4X
The KZAB lighting fittings are qualified for use inhazardous areas of Divs. 1 and 2 by the TISS'. They
are designed and constructed thoroughly with carefully
selected materials to provide high reliability inprotection against explosion.
◦A very light and compact body is realized thanks tothe small but efficient halogen lamp. KZAB fittings aremost suitable as emergency lights for passages, stairsand pits.
◦Degree of protection : IP65
They have a dust-and jet-proof structure which meetsthe requirements of the IEC standards, IP65, ensuring
operation in outdoor use.
◦The body is made of corrosion-proof aluminium alloy
and the bolts are made of stainless steel, so that theproducts are highly corrosion- and weatherproof.
◦Installation is easy since the lamp is suspended by aunion coupling at the terminal box and a suspension
pipe. Also the box has power cable entries and aremovable cover to permit wiring after installation of
the lamp fitment, eliminating the need for supporting it
during wiring.

■ SPECIFICATIONS◦Rated voltage : 100V, 200V
(Other voltages can be supplied uponrequest.)◦Lighting : normal : off (battery charge only)(charge indicator green LED on)
emergency : on (DC)(charge indicator green LED off)
◦Lamp : halogen lamp for emergency (12V, 23W)
◦Materials of main components
corrosion-proof aluminium alloy casting
Body :
Front glass :tempered glass
Terminal box :aluminium die casting
Suspension pipe : carbon steel◦Colour : Mild grey (Munsell 10YR7/1)◦Finish : melamine resin coating◦Entries : four ways (G1/2 or 3/4 thread) with threeblind plugs
4-φ8hole

85

120

85

25120385

25

23W (ceilling)
WattageCat.No.

Mass (kg)23W

KZAB02341

7.5

WattageCat.No.

Mass (kg)23W

KZAB02342

8.0

WattageCat.No.

Mass (kg)23W

KZAB02346

8.0

φ122
207

530

2523W (pipe pendant)

φ12220723W (bracket)
360

31525゜60
207φ1226

Emergency Incandescent Lamp Lighting Fittings
Explosion-proof Typewith external power source

Type of protection : ExdeIIB+H2T3X

Zone. 1 and 2 Areas

Colour : Mild grey (Munsell 10YR7/1)

40W-200W (ceillng)

40W-200W (pipe pendant)

40W-200W (bracket)

60
゜380

470

0476

626

0
φ2φ200

Wattage
40W
60W
100W
150W
200W

φ200

Cat.No.
BZAB04041
BZAB06041
BZAB10041
BZAB15041
BZAB20041

Wattage
40W
60W
100W
150W
200W

Cat.No.
BZAB04042
BZAB06042
BZAB10042
BZAB15042
BZAB20042

Wattage
40W
60W
100W
150W
200W

Cat.No.
BZAB04046
BZAB06046
BZAB10046
BZAB15046
BZAB20046■ Mounting dimensions□13025□854-φ9Incresed safety typewith external source

Type of protection : eG1Zone. 2 Areas

Colour : Mild grey (Munsell 10YR7/1)

40W-200W (ceillng)

40W-200W (pipe pendant)

40W-200W (bracket)

60
゜325

365

6405

590

9φ1

φ196

Cat.No.
BGLB04042
BGLB06042
BGLB10042
BGLB15042
BGLB20042

Wattage
40W
60W
100W
150W
200W

Cat.No.
BGLB04046
BGLB06046
BGLB10046
BGLB15046
BGLB20046■ Mounting dimensions
85120

74-φ8hole120

Wattage
40W
60W
100W
150W
200W85Cat.No.
BGLB04041
BGLB06041
BGLB10041
BGLB15041
BGLB20041

25Wattage
40W
60W
100W
150W
200W

φ196

Emergency Incandescent Lamp Lighting Fittings
Vapour-tight typewith external power source

Colour : Mild grey (Munsell 10YR7/1)

40W-200W (ceillng)

40W-200W (pipe pendant)

40W-200W (bracket)

60
゜305

355

6580

395

φ196

Cat.No.
BCLB04042
BCLB06042
BCLB10042
BCLB15042
BCLB20042

Wattage
40W
60W
100W
150W
200W

Cat.No.
BCLB04046
BCLB06046
BCLB10046
BCLB15046
BCLB20046■ Mounting dimensions85120

84-φ8hole120

Wattage
40W
60W
100W
150W
200W

85

Cat.No.
BCLB04041
BCLB06041
BCLB10041
BCLB15041
BCLB20041

φ196

25

Wattage
40W
60W
100W
150W
200W

9φ1