Explosion Proof Type Emergency High Frequency Fluorescent Lighting Fittings (with internal battery unit)
Products conforming to the international standard (IEC Standard 60079)◦Type of protection : Exde II CT5X
The BZAC lighting fittings are qualified for use inhazardous areas of Zone. 1 and 2 by the TIIS. They
are composed of a flameproof lamp holder unit, anincreased safety body and an Explosion Proof ballast.
They are designed and constructed thoroughly withcarefully selected materials to provide high reliabilityin protection against explosion.
◦Degree of protection : IP65
They have a dust- and jet-proof structure which meetsthe requirements of the IEC standards, IP65, ensuring
operation in outdoor use.
◦The body and socket are made of corrosion-proof
aluminium alloy and the bolts are made of stainlesssteel, so that the products are highly corrosion- andweather-proof.
◦The lamp can be easily replaced by inclining the lamp
holder unit.
◦Installation is easy since the lamp is suspended by acoupling at the terminal box side and a hook at thenon-electric side suspension pipe.
◦Guard and stainless steel reflector can be optionallysupplied.
◦Our products, which combine high-frequency fluorescentlamps with electronic ballasts, achieve high-efficiency
power usage with a high level of luminous intensity.

Zone. 1 and 2 Areas

45W×1 (direct)

BZAC45111

45W×1 (ceiling)

BZAC45141

45W×1 (pipe pendant)

BZAC45142

45W×1 (bracket)

BZAC45146

Mass : 14.5kgNB) to be cabled

Mass : 17.0kg■ SPECIFICATIONS◦Rated voltage : 100V, 200V
(Other voltages can be supplied uponrequest.)◦Lamp : FHF32EX (45W)◦Start : normal : high frequency startemergency : high frequency start◦Materials of main components
Body : corrosion-proof aluminium alloy
Socket box : corrosion-proof aluminium alloy
Reflector : sheet steel
Lamp protector : hard glass
Terminal box : aluminium die casting
Suspension pipe : stainless steel◦Colour : body : Mild grey (Munsell 10YR7/1)
reflector & socket box : white◦Finish : melamine resin coating◦Entries : four ways (G1/2 or 3/4 thread) with threeblind plugs

Mass : 17.5kg＊BZAC45111 and 45211 use power cables. Explosion Proof cableglands (ZCGS) must be used for cabling.

Mass : 17.0kg※Also available in a wall-mounted type.

9

Explosion Proof Type Emergency High Frequency Fluorescent Lighting Fittings (with internal battery unit)
Products conforming to the international standard (IEC Standard 60079)
Zone. 1 and 2 Areas●Installation drawings

45W×2 (direct)

BZAC45111, 45211

BZAC45211

Mass : 17.5kgNB) to be cabled

500
150

4-9×12holes

176

176

188

188

696

170

170

40

77

1398

Lamp replacement(inclination is possible)

45W×2 (ceiling)

Mass : 19.5kg

BZAC45141, 45241

BZAC45241

5002-8×12holes

1398

696

345

345

3585

□85

4-φ8holes

188

188

Lamp replacement(inclination is possible)

45W×2 (pipe pendant)

BZAC45142, 45242

BZAC45242

Mass : 20.0kg

500

2-8×12holes

1398

696

540

540

35

85

□85

4-φ8holes

188

188
Lamp replacement(inclination is possible)

696

188370

60゜

1398

3518
Lamp replacement8(inclination is possible)

1035

250

2-8×12holes

゜
60

4-φ8holes □120

230

370

500

85
105

Mass : 19.5kg

BZAC45146, 45246

BZAC45246□85

45W×2 (bracket)