B-2345(0)FT2JInstruction ManualSAFETY PRECAUTIONSSAFETY PRECAUTIONS• Be certain to read this document carefully before performing installation, wiring, or maintenance and inspection
works, or operating the SmartAXIS FT2J (Hereinafter referred to as "SmartAXIS"). If the SmartAXIS is used in amanner not specified by the manufacturer, the protection provided by the equipment may be impaired.
• The SmartAXIS has been manufactured with careful regard to quality. However, if you intend to use this product inapplications where failure of this equipment may result in damage to property or injury, ensure that it used inconjunction with appropriate fail-safe backup equipment.
• Precautionary measure should be taken to avoid unauthorized access from the outside network to the SmartAXIS.
Please note that the Company shall not be liable for any loss, damage or other expenses incurred directly or
indirectly by unauthorized access, etc.
• In this document, safety precautions are categorized depending on the severity as Warning or Caution:
Warning notices are used to emphasize that improper operation may cause severe
personal injury or death.
Caution notices are used where inattention might cause personal injury or damage toequipment.

• This product is not designed for use in applications requiring a high degree of reliability and safety, such as
applications for medical devices, nuclear power, railroads, aerospace, and automotive devices. This productshould not be used for such applications.
• Turn off the power of this product before installation, removal, wiring, maintenance, and inspection of thisproduct. Failure to turn power off may cause electrical shock or fire hazard.
• Special expertise is required to install, wire, configure, and operate this product. Person without such expertisemust not use this product.
• This product uses an LCD (liquid crystal display) as a display device. The liquid inside the LCD is harmful to theskin. If the LCD is broken and the liquid attaches to your skin or clothing, wash the liquid off using soap, andconsult a doctor immediately.
• An emergency circuit that uses emergency stop switch or an interlocking circuit must be configured outside ofthis product.
• Do not use touch switches for an emergency circuit or an interlocking circuit. If this product fails, serious injury
to operators and equipment damage may be caused.
• If relays or transistors in this product output circuits should fail, outputs may remain at on or off state. For
output signals which may cause serious accidents, configure monitor circuits outside this product.
• This product self-diagnostic function may detect internal circuit or program errors, stop programs, and turnoutputs off. Configure circuits so that the system containing this product is not jeopardized when outputs turnoff.
• In case this product is accidentally dropped or exposed to significant shock, stop using this product, check thisproduct for damage, and confirm that its various functions work safely and correctly.
• Connect SmartAXIS's FG wire to grounding resistance of 100 Ω or less. Otherwise, there is a risk of electric
shock or malfunction.
• The screen will not be visible if the backlight of this product burns out. However, the touch panel will remainfunctional. Thus, erroneous touch panel operation may occur while controlling the touch panel. Because such
erroneous operations could result in damage, the touch panel should not be used once the backlight is burnedout.

Preface-1

SmartAXIS FT2J Instruction ManualSAFETY PRECAUTIONS• Prevent this product from falling while moving or transporting, otherwise it may cause damage or malfunction tothis product as a result.
• Use the product within the environmental limits given in the catalog and this document. Use of the product inhightemperature or high-humidity environments, or in locations where it is exposed to condensation, corrosive
gas, or large shock loads can create the risk of electrocution and fire.
• This product is designed for use in pollution degree 2. Use this product in environments of pollution degree 2.
(based on the IEC 60664-1 rating)• Install this product according to the this document. Improper installation will result in falling, failure, electricalshock, fire hazard, or malfunction of this product.
• Prevent metal fragments or wire chips from dropping inside this product housing. Ingress of such fragments andchips may cause fire hazard, damage, and malfunction.
• Use a power supply of the rated value. Using a wrong power supply may cause fire hazard.
• The main unit uses “PS2” as DC power supply. (based on the IEC/EN 61131 rating)• Use wire of a proper size to meet the voltage and current requirements.
• When exporting this product to Europe, use an EN 60127 (IEC 60127) approved fuse on the power line outside
this product.
• When exporting this product to Europe, use an EU-approved circuit protector.
• Make sure of safety before starting and stopping this product. Incorrect operation of this product may cause
mechanical damage or accidents.
• This product cannot be directly connected to the communication lines (including public wireless LAN) of
telecommunication carriers (mobile communication companies, fixed-line communication companies, Internet
providers, etc.). When connecting this product to the Internet, be sure to connect via a device, such as a router.
• The touch panel of this product is made of glass, and will break if exposed to excessive shock. Take due carewhen handling it.
• When operating the touch panel in an environment where the ambient operating temperature exceeds 50°C,
there is a risk of getting burn injury. So please use heat-resistant gloves, touch pen, and such to prevent burninjury.
• The protective film attached to the display of this product is to protect the product from scratches duringtransportation. Please remove the protective film before use. If the display is used with protective film, the film
may become cloudy and stick to the display depending on the usage environment and may become
unremovable.
• Do not push hard or scratch the touch panel and protection sheet with a hard object like hand tool. Touch panel
and protection sheet can be easily damaged.
• Do not install this product in areas subjected to strong ultraviolet rays.
• Do not attempt to disassemble, repair or modify this product. This can create the risk of fire or electrocution.
• When disposing of this product, do so as an industrial waste.
• When using this product in a system that requires clock accuracy, set the time regularly.
• Do not switch off the power or pull out the USB flash drive while it is being accessed, as this may result in
destruction of the stored data. If the data on the USB flash drive is corrupted, format the USB flash drive.
• Turn off the power supply of this product before connecting or disconnecting USB devices other than USB
memory.

SmartAXIS FT2J Instruction Manual

Preface-2

Revision history

Revision history
September 2023:

First Edition

Caution• All rights in this document belong to IDEC Corporation. It may not be reproduced, reprinted, sold, transferred orrented without our permission.
• The contents of this document are subject to change without notice.
• Please contact your vendor or IDEC Corporation with any problems regarding the operation of this product.

Trademarks

WindO/I and SmartAXIS are registered trademarks of IDEC CORPORATION in JAPAN.
All other company names and product names used in this document are trademarks of their respective owners.

UL 121201 / CSA C22.2 No.213 (Under application)• This product is for indoor use only.
• Open type or panel mounted when installed in a Listed Type 4X "Indoor Use Only",Type 13 enclosure.
• The use of an SELV source.
• When wiring this product at the field, use copper conductors only.
Test item particulars
Type of item

Open Type/enclosed type when panel mounted in appropriate end enclosure

Description of equipment function

Control

Connection to mains supply

N/A connected to SELV source

Overvoltage Category

None

Pollution Degree

2

Environmental Conditions

Extended:

Temperature:-20 to +55ºC, see RATINGS section for detail.

Humidity:

10 to 90%RH (no condensation)

For use in wet locations

NO

Equipment mobility

Panel mounted

Operating Conditions

Continuous• This product is suitable for use in Class I, Division 2, Groups A, B, C, D or Non-Hazardous locations only.
• RATINGS:
Input: 24 Vde, 17W, SELV, LIM
Maximum Surrounding Air: -20 to +55ºC
Enclosure Type 4X Indoor Use only, Type 13• Temperature Code: T4A• Equipment to be installed in an environmentally suitable enclosure that requires the use of a tool to access.
• L'appareil FT2J est convu pour etre utilise uniquement dans des emplacements de classe I, division 2, groupes A, B,
C, Dou non dangereux.
• Caracteristiques:Entree: 24 Vde, 17W, Tres basse tension de securite (SELV), LIMITES Air ambiant maximal: -20 a+55ºC
Boitiers de type 4X pour une utilisation interieure, de type 13.
• Code de temperature: T4A• L'appareil FT2J doit etre installe dans un boitier adapte a l'environnement et uniquementaccessible a l'aide d'outils.

Preface-3

SmartAXIS FT2J Instruction ManualPreface

PrefaceThank you for purchasing the SmartAXIS manufactured by IDEC Corporation.
this document describes the specifications of the SmartAXIS FT2J, how to install it, and various functions.
Read this document to ensure the correct understanding of the entire functions of this product.
IDEC Corporation makes the latest product manual PDFs available on our website at no additional cost. Please
download the latest product manual PDFs from our website.
Read the following materials as necessary for your particular application.
References

Content

SmartAXIS FT2J Instruction Manual(This document)

Describes the product specifications, installation and wiring, or
maintenance and inspection works for the FT2J.

WindO/I-NV4 User's Manual (PDF)

Describes the basic operations of the FT2J, how to create the project
necessary for operation, and the various drawings and parts that make up
the project.

Ladder Programming Manual (PDF)

Describes basic operations for programming with ladders, monitoring
methods on the WindLDR, instruction lists, and details of each instruction.

SmartAXIS Hardware Manual (PDF)

Describes the product specifications, installation and wiring instructions of
the FT2J, optional items, and I/O cartridges.

WindO/I-NV4 External Device Setup Manual(PDF)

Describes the connection procedures and available device addresses forvarious communication including the Device Link Communication, O/I Link
communication, and DM Link communication.

SmartAXIS FT2J Instruction Manual

Preface-4

Symbols Used in this document

Symbols Used in this document
This document uses the following symbols to facilitate explanation.

Symbols……

Information that requires special attention. Failure to operate the product in accordancewith the information provided can lead to serious injury or damage.

……

Information relating to requests or material to reference in the use of a function……

Useful information relating to a function

OK……

Screen buttons are indicated by bold text or by using the actual graphic icon.

****

……

Controls are indicated by bold text.

Preface-5

SmartAXIS FT2J Instruction ManualAbbreviations, Generic Terms, and Terminology Used in this document

Abbreviations, Generic Terms, and Terminology Used in this document
Item

Description

FT2J

The name is short for SmartAXIS FT2J-7U22*AF-* .

SmartAXIS

Generic term for integrated display controller FT2J.

External Device

Generic term used to refer to a PLC or micro computer that is connected to andcommunicates with the main unit.

Device Address

Memory that is capable of storing values in unit of bits or words loaded on the main unit
and external device.

WindO/I-NV4

Integrated configuration software application for creating projects of the main unit.

Operating System

Software used to manage and control system software.

System Software

Software that performs basic control and management of the main unit.

Project

Data including image data required for operating the main unit, which is created with
WindO/I-NV4.

Internal Device

The generic term for internal device addressing on the main unit such as internal relays,
registers, etc.

SmartAXIS FT2J Instruction Manual

Preface-6

Contents

Contents
SAFETY PRECAUTIONS ................................................................................ Preface-1
Revision history ........................................................................................... Preface-3
Caution ....................................................................................................... Preface-3
Trademarks ................................................................................................. Preface-3
UL 121201 / CSA C22.2 No.213 (Under application) ....................................... Preface-3
Preface ....................................................................................................... Preface-4
Symbols Used in this document .................................................................... Preface-5
Abbreviations, Generic Terms, and Terminology Used in this document ........... Preface-6

Chapter 1
1

Preface-7

Main Unit Specifications
FT2J .................................................................................................................... 1-1
1.1

Packing Content..............................................................................................1-1

1.2

Type Number..................................................................................................1-1

1.3

Part Names.....................................................................................................1-2

1.4

External Interfaces..........................................................................................1-3

1.5

Specifications................................................................................................ 1-11

1.6

Dimensions................................................................................................... 1-14

1.7

Installation ................................................................................................... 1-15

1.8

Wiring .......................................................................................................... 1-20

1.9

Maintenance and Inspection .......................................................................... 1-24

1.10

Software License Information......................................................................... 1-25

SmartAXIS FT2J Instruction Manual

Main Unit Specifications

Chapter 1

1.1

FT2J
Packing Content
Before installing the main unit, make sure that the model you have received is what you actually ordered, and noparts are damaged to accidents during shipping.
Product Name & Dimensions

Quantity

Description

1

Main unit

4-1

Removable terminal block 9-pin

1Removable terminal block 16-pin

1Removable terminal block 11-pin

2Attached to the main unit

FT2J

Mounting clips

Serial interface connector

Input terminal connector

Output terminal connector

Dummy cartridge

1.2

Type Number
LCD

7.0 inch wide
TFT Color

Bezel
Color

Black

Output Terminal
Specification

Input Terminal Specification

Digital input (shared sink/source): 10
Analog input (shared digital sink input): 4

Type Number

Relay output: 8

FT2J-7U22RAF-B

Transistor sink output: 6
Analog output: 2

FT2J-7U22KAF-B

Transistor source output: 6
Analog output: 2

FT2J-7U22SAF-B

SmartAXIS FT2J Instruction Manual

1-1

Main Unit Specifications

11

1 FT2J

1.3

Part Names
(2)

(3)

(13) (11) (14)
TOP

(5)

USB1

(6)

USB2

(7)

LAN

IN

RESET

Slot1

COM

(1)

No.

(1)

1-2

(8)

Name

POWER LED

(9)

(10)

(4)

Green (lit):

Normal Operation

Green (flash):Operating system is booting. (Normal Operation)

Orange (lit):

Operating system is booting. (Boot mode)

Orange (flash):Preparing to boot the operating system, running in boot mode.

Red (lit):

Main unit is damaged.

Not lit :Power is off.

Display

TFT color LCD(3)Touch Panel

PCAP touchscreen (Projected capacitive)(4)

Serial Interface (COM)

RS232C, RS422/485 Connector: Terminal Block 9-pin (Push-in type)
Maximum cable length: 15m (RS232C), 1200m (RS422/485)(5)

USB Interface (USB1)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(6)

USB Interface (USB2)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(7)

Ethernet Interface (LAN)IEEE802.3u 10BASE-T/100BASE-TX Connector: RJ-45(With Auto MDI/MDI-X function)
Maximum cable length: 100m

(8)Power Supply Terminal

Connector: Terminal Block 3-pin (Push-in type)4 places(9)

Mounting Clip Position
RESET Switch(11)

Input terminal (IN)(12)

Description

(2)

(10)

Slot2

OUT

Connector:

Removable terminal block 16-pin (Push-in type)
Digital input (shared sink/source) (I0 to I7, I10, I11)
Analog input (shared digital sink input) (I12 to I15)

Connector:

Removable terminal block 11-pin (Push-in type)
Relay Output (Q0 to Q7)
Transistor sink output (Q0 to Q5), Analog output (AQ0, AQ1)
Transistor source output (Q0 to Q5), Analog output (AQ0, AQ1)

(11)

Output terminal (OUT)(13)

Cartridge Slot (Slot1)

Slots for connecting the following I/O cartridges. For details about the cartridges,
refer to Chapter 2 “I/O Cartridge” in the Smart AXIS Hardware Manual.

(14)

Cartridge Slot (Slot2)

Digital I/O cartridge:
Analog I/O cartridge:

FC6A-PN4, FC6A-PTK4, FC6A-PTS4
FC6A-PJ2A, FC6A-PJ2CP, FC6A-PK2AV, FC6A-PK2AW

SmartAXIS FT2J Instruction Manual

1 FT2J

1.4

1External Interfaces• Make sure to turn off the power to the FT2J before wiring each interface.
• The serial interface (COM) can be used as the RS232C and RS422/485 interfaces at same time.
• Use the SELV (Safety Extra-Low Voltage) circuit to connect the Serial, USB and Ethernet interfaces.
• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) when connecting a DC power

supply to the Input and Output terminals.
• When using the relay output load that exceeds AC200V, please connect COM2 and COM3 to the same voltage
circuit.
● Serial Interface (COM)Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Interface Specification

RS232C, RS422/485

Connector

Removable terminal block 9-pin

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

ST3L-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

No.1

No.

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

No.9

Name

I/O

Function

1

SD

OUT

Send Data

2

RD

IN

Receive Data

3

RS

OUT

Request to Send

4

CS

IN

Clear to Send

5

SG

―

Signal Ground

6

SDA

OUT

Send Data (+)

7

SDB

OUT

Send Data (-)

8

RDA

IN

Receive Data (+)

9

RDB

IN

Receive Data (-)

Communication type

RS232C

RS422/485*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

SmartAXIS FT2J Instruction Manual

1-3

Main Unit Specifications

CAUTION

1 FT2J
Using RS422/485 interface
FT2J is not equipped with terminating resistor. Insert a terminating resistor of an appropriate value (about 100 to 120
Ohm, 1/2 W minimum) between terminal number 8 (RDA) and terminal number 9 (RDB), if necessary.
TOP
USB1

IN

USB2
LAN

RESET

Slot1

COM

Terminal Number 8 (RDA)

Slot2

OUT

Terminal Number 9 (RDB)

For inserting and removing wires, refer to “1.8 Wiring” on page 1-20
● Input Terminal (IN)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Connector

Removable terminal block 16-pin (Push-in type)

Applicable cable

AWG 16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

ST3L-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

Input Points

14

Rated Input Voltage

24V DC

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

Input Voltage Range

0 to 28.8V DC

Effect of Improper
Input Connection

No damage
However, if high voltage is applied that exceeds the operating input voltage range, there isa risk of permanent damage.

*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

1-4

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

SmartAXIS FT2J Instruction Manual

1 FT2J

1

Digital Input
Shared sink/source

Input Points(Terminal Number/Common Line Name)

10 points in 1 common line
(I0 to I7, I10, I11 / COM0 terminal)

Rated Input Current
Input Impedance
Turn ON Time
Input Delay Time
Turn OFF Time

I0 to I5

4 mA/point (at 24V DC)

I6, I7, I10, I11

5 mA/point (at 24V DC)

I0 to I5

6.3 kΩ

I6, I7, I10, I11

4.5 kΩ

I0 to I5

25 μs maximum + software filter setting

I6, I7, I10, I11

100 μs maximum + software filter setting

I0 to I5

25 μs maximum + software filter setting

I6, I7, I10, I11

100 μs maximum + software filter setting

Main Unit Specifications

Input Type

Between Input Terminal and Internal
Photocoupler isolated
Circuit

Isolation

Between Input Terminals

Not isolated

Input TypeType1 (IEC 61131-2)

External Load for I/O Interconnection

Not isolated

Signal Determination Method

StaticEffect of Improper Input Connection

Even if wiring for sink or source connection is incorrect, nodamages are caused.
However, if high voltage is applied that exceeds the operating
input voltage range, there is a risk of permanent damage.

Cable Length in compliance with electromagnetic immunity 3 m■ Operating Ranges
I0 to I5

I6, I7, I10, I11

Voltage

Voltage28.8 V28.8 VON Area

ON Area

24 V

24 V

15 V

15 V

Transition
Area

Transition
Area
5V

5V

OFF Area

OFF AreaCurrent

0.5 mA

2.2 mA

3.8 mA

Current

4.7 mA

0.9 mA

3.2 mA

5.3 mA

6.4 mA■ Input Equivalent Circuit
I0 to I5

I6, I7, I10, I11
5.6 kΩ

Input

COM0

SmartAXIS FT2J Instruction Manual

Internal Circuit

COM0Internal Circuit

4.3 KΩ
Input

1-5

1 FT2J
Analog Input (shared digital sink input)
Input Type*1

Voltage

Input Points(Terminal Number/Common Line Name)

4 points in 1 common line
(I12 to I15/ COM1(-) terminal)

Input Range

0 to 10V DC

4 to 20 mA

Input Impedance

78kΩ

250kΩ

Digital Resolution

4096 (12 bit)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

Current

Optional range*2: -32768 to 32767

AD Conversion

Input Error

Sampling time

5 msec max.

Sample Repetition Time

5 msec max.

Total Input Delay Time

6 msec + 1 scan time

Type of Input

Single-ended

Operation Mode

Self-scan

Conversion Method

SAR

Maximum Error at 25°C

±3.0% of full scale

Temperature Coefficient±0.04% of full scale/°C

Maximum Error±5.0% of full scale

Status Display

Noise Resistance

Device Monitor screen (LCD display)
Maximum Temporary Deviation during
Electrical Noise Tests±5.0% of full scale

Input Filter

Yes

Recommended Cable for Noise
Immunity

Shielded cable

Calibration to Maintain Rated Accuracy

Not possible

Maximum Permanent Allowed Overload (No Damage)

28.8V DC

Overload Status (Outside Input Range) Detection

Detectable

Isolation

Used as Digital Input

Between Input Terminal and Internal
Circuit

Not isolated

Between Input Terminals

Not isolated

Digital Input Type— (IEC 61131-2 digital input type is not supported)

Input Threshold

ON voltage: 15V min.

ON current: 0.20 mA min.

OFF voltage: 5V max.

OFF current: 0.06 mA max.

Pulse Intput
The maximum input frequency varies based on the input terminal and function.
Input Terminal

I0

I1

I2

I3

I4

I5

Adding counter

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzUp/down selection reversible
counter

20 kHz

-

-

-

-

-

Dual-pulse reversible counter

20 kHz

20 kHz----2-edge count

10 kHz

10 kHz----4-edge count

5 kHz

5 kHz

-

-

-

-

Catch input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzInterrupt input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHz--

20 kHz

20 kHz

20 kHz-High-speed counter
Function

Frequency measurement*1 Can be set by application software.
*2 This function is used the analog value converting it to the specified range.

1-6

SmartAXIS FT2J Instruction Manual

1 FT2J

1■ Operating Ranges

Main Unit Specifications

I12 to I15
Voltage28.8 VON Area
24 V

15 V

Transition
Area
5V

OFF AreaCurrent
0.06mA

0.2mA

0.3mA

0.37mA■ Input Equivalent Circuit
I12 to I15

56kΩ
Input circuit
120kΩ
22kΩ

130kΩ

0V

Internal Circuit

24V DC

0V

SmartAXIS FT2J Instruction Manual

1-7

1 FT2J● Output Terminal (OUT)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Connector

Removable terminal block 11-pin (Push-in type)

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

ST3L-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

Relay Output
Type Number

FT2J-7U22RAF-B

Output Points (Terminal Number)

8 (Q0 to Q7)

Output Type1a contact

Maximum Load Current

1

2 A max.

1 common line

7 A max.

Minimum Switching Load

1 mA, 5V DC (reference value)

Initial Contact Resistance

30 mΩ max.

Electrical Life

100,000 operations min.
(rated resistive load 1,800 operations/hour)

Mechanical Life

20,000,000 operations min. (no load 18,000 operations/hour)

Rated Load

240V AC 2 A, 30V DC 2 A
Between Output Terminal andInternal Circuit

Withstand Voltage

Between Output Terminals(COM2 and COM3)

Status Display

2,300V AC 5 mA, 1 minuteDevice Monitor screen (LCD display)

Output Delay
ON

Input to Relay
OFF
ON

Output Relay StatusOFF

OFF Bounce: 6 ms maximum
OFF Delay: 10 ms maximum
ON Bounce: 6 ms maximum
ON Delay:
6 ms maximum*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

1-8

SmartAXIS FT2J Instruction Manual

1 FT2J

1

Transistor Output
FT2J-7U22KAF-B

Output Points

6 (Q0 to Q5)

Output TypeSink output

Rated Load Voltage

24V DCOperating Input Voltage Range

20.4 to 28.8 DC

Maximum Load Current

1

0.5 A

1 common line

3A

Main Unit Specifications

Type Number

FT2J-7U22SAF-B
Source output

Voltage Drop (ON Voltage)

1V max. (Voltage between COM and output terminal when ON)

Maximum Inrush Current

1 A max.

Leakage Current

0.1 mA max.
L/R=10 ms (28.8V DC, 1 Hz)

Inductive Load

100 mA max., 24V DC

External Current Draw

V(+) terminal supply power

Isolation

Photocoupler isolated

Status Display

Device Monitor screen (LCD display)COM2(+) terminal supply power■ Output Equivalent Circuit
FT2J-7U22KAF-B

FT2J-7U22SAF-B

OutputT2
T1

COM2(+)
Internal Circuit

Internal Circuit

V(+)

COM2(-)

SmartAXIS FT2J Instruction Manual

OutputV(-)

1-9

1 FT2J
Analog Output
Type Number

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Output Type*1

Voltage

Output Points (Terminal Number/Common Line Name)

2 / 1 common line (AQ0, AQ1 / COM3(-) terminal)

Output Range
Output LoadDA Conversion

Output Error

Data

Noise Resistance

Current

0 to 10V DC

4 to 20 mA DC

Impedance

2 kΩ or higher

500 Ω or lower

Load Type

Resistive load

Scan Time

1 scanSettling time

1 ms or lower

Total Output System Transfer Time

1 ms + 1 scan time

Maximum Error at 25°C

±0.3% of full scale

Temperature Coefficient±0.02% of full scale

Reproducibility after Stabilization Time

±0.4% of full scale

Non-linearity±0.01% of full scale

Output Ripple

30 mV maximum

Overshoot0%*2

Maximum Error±1.0% of full scale

Digital Resolution

4,096 (12 bits)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

Monotonicity

Yes

Current Loop OpenNot detectable

Maximum Temporary Deviation during
Electrical Noise Tests±5.0% or less of full scale

Optional range*3: -32768 to 32767

Recommended Cable for Noise Immunity

Shielded cable

Effect of Improper Output Connection

No damageCalibration to Maintain Rated Accuracy

Not possible■ Output Equivalent Circuit+

Analog Signal
Analog Output
Element–

Switching Signal

Pulse Output
Type Number

FT2J-7U22KAF-B

FT2J-7U22SAF-B

Output Points

4 (Q0 to Q3)

Maximum output pulse frequency

20kHz

PWM output

Duty cycle: 0.1 to 100.0 (increments of 0.1%)
Output pulse frequency: 30 to 1000 (increments of 1Hz)
When the pulse OFF time is shorter than 25μs, the pulse ON ratio is adjusted so that
the OFF time is 25us and output the signal.
When the pulse ON time is shorter than 25μs, the pulse OFF ratio is adjusted so that
the ON time is 25us and output the signal.

*1 Can be set by application software.
*2 Overshoot may occur at light loads. The occurrence of overshoot can be controlled by inserting damping resistance into
the circuit. A general guide for the damping resistance value is about 150 Ω including the input line impedance for thedestination.
*3 This function is used the analog value converting it to the specified range.

1-10

SmartAXIS FT2J Instruction Manual

1 FT2J

1.5

1Specifications

Safety Standards

UL61010-1, UL61010-2-201, CSA C22.2 No.61010-2-201 (c-UL), UL121201,
CSA C22.2 No.61010-1-12 (c-UL), CSA C22.2 No.213 (c-UL)

EMC Standards

IEC/EN 61131-2■ Environmental Specifications
Ambient Operating Temperature-20 to +55°C*1 (no freezing)Ambient Operating Humidity

10 to 95% RH (no condensation)

Ambient Storage Temperature-20 to +70°C (no freezing)Ambient Storage Humidity

10 to 95% RH (no condensation)

Altitude

Up to 2000m

Pollution Degree2

Corrosion Immunity

Free from corrosive gases■ Electrical Specifications
Rated Voltage

24V DCPower Consumption

17W maximum

Not using the USB1 and USB2
interfaces, the IN and OUT terminals,
and the Slot1 and Slot2 slots.
When Backlight OFF

5W maximum
3W maximum

Power Voltage Range

20.4 to 28.8V DC

Allowable Momentary Power Interruption

10 ms maximum (Power supply voltage: 24.0V DC to 28.8V DC)
5 ms maximum (Power supply voltage: 20.4V DC to 24.0V DC)

Inrush Current

40 A maximum

Dielectric Withstand Voltage

500V AC, 5 mA, 1 minute (between power and earth terminals)
500 V AC, 5 mA, 1 minute (between input and earth terminals)
2300 V AC, 5 mA, 1 minute (between relay output and earth terminals)
500 V AC, 5 mA, 1 minute (between transistor output and earth terminals)
500 V AC, 5 mA, 1 minute (between power and input terminals)
500 V AC, 5 mA, 1 minute (between power and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between power and relay output terminals)
500 V AC, 5 mA, 1 minute (between input and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between input and relay output terminals)■ Construction Specifications
Type Number

FT2J-7U22RAF-B

FT2J-7U22KAF-B, FT2J-7U22SAF-B

5 to 8.4Hz amplitude 3.5mm,
Vibration Resistance

Shock Resistance

8.4 to 150Hz acceleration 9.8m/s2
10 times on each of three mutually perpendicular axes
(IEC 61131-2)
98m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)

147m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)*1 For details about the restrictions due to the ambient operating temperature, refer to “Restrictions due to mounting
orientation” on page 1-17.

SmartAXIS FT2J Instruction Manual

1-11

Main Unit Specifications■ Applicable Standards

1 FT2J■ Function Specifications

Display

Touch PanelLCD Type*2

TFT color LCD

Display Colors

65,536 Colors

Effective Display Area

154.08 (W) × 85.92 (H) mm

Display Resolution

800 (W) × 480 (H) dots

Dot pitch

0.1926 (W) x 0.179 (H) mm

View angle

Left/Right/Top: 80°, Bottom: 60°

Brightness of LCD only

500 cd/m2

Brightness Adjustment

48 levels

Backlight

LED (white)

Backlight Life*3

Approx. 50,000 hours (The time until brightness becomes 50% of the initial value)

Switch Type

Projected Capacitive

Multiple Operations

Possible (2-point touch)User Memory

Approx. 24 MB

Backup time of the real-time clock(Ambient Operating Temperature at
25°C)

Min. 20 days*5

Backup Data

Keep by a largecapacity capacitor

Clock Data

Save to non-volatilememoryLog data, HMI Keep Relays, HMI Keep Registers, Internal Relays, Shift Registers,
Counters, Data Registers

Buzzer output

Single tone (tone length is adjustable)

Degree of Protection

Panel thickness is 1mm or more and less than 1.6mm: IP65F (IEC 60529)
Panel thickness is 1.6mm or more and 5mm or less: IP66F, IP67F (IEC 60529),
TYPE 4X (indoor use only),
TYPE 13Weight (approx.)

600g

*4

*2 Please be aware that small black and bright dots might show up on LCD Screen: it is not a failure or malfunction.
*3 The life of the LCD itself at an ambient operating temperature of 25°C. This is not a guaranteed value. The actual life
depends on the environment and conditions of use.
*4 It is a protection structure for the operating surface of HMI, which is attached to a panel. Although protection structure
suffices every test conditions, it does not guarantee to operate under all of the environmental condition.
As for IP65F/IP66F/IP67F oilproof structure, it suffices oilproof test conditions. Conditions are listed in the document thatcomes with Japanese Industrial Standard JIS C 0920.
Protection structure do not gurantee usage under long exposure to oil or usage of oil that is not prescribed in the
document. Please test/check beforehand to avoid trouble.
IP ratings are not applicable to UL certification.
*5 If the power interruption period exceeds the Backup time of the real-time clock, the error message "Initialize clock data"
will be displayed when the power is turned on, and the clock data will be initialized to 00:00:00 on January 1, 2000.

1-12

SmartAXIS FT2J Instruction Manual

1 FT2J

1■ EMC Specifications

Electrostatic Discharge

Contact: ±6kV
Air: ±8kVElectromagnetic Field

10V/m (80M to 1000MHz)
3V/m (1.4G to 2.0GHz)
3V/m (2.0G to 2.7GHz)
3V/m (2.7G to 6.0GHz)
80% AM (1kHz)

Fast Transient Burst

Power: ±2kV
Communication cable: ±1kV

Surge Immunity±500V (between +24V and 0V)±500V (between +24V and FE, 0 and FE)

Conducted Radio
Frequency Immunity

10V (Power, Communication cable) (150k to 80MHz)
80% AM (1kHz)

SmartAXIS FT2J Instruction Manual

Main Unit Specifications

Radiated Emission

Class A: 10m
40dBµV/m quasi-peak (30M to 230MHz)
47dBµV/m quasi-peak (230M to 1GHz)Class A: 3m
76dBµV/m (Peak), 56dBµV/m (AVG) (1G to 3GHz)
80dBµV/m (Peak), 60dBµV/m (AVG) (3G to 6GHz)

1-13

1 FT2J

1.6

Dimensions
Unit: mm
35.7

186.0

35.3

6.0

128.0

118.2

32.9

176.2

<Cable Attached Dimensions>
56

176.2

TOP
USB1

IN

118.2

USB2
LAN

RESET

Slot1

COM

Depending on the type of connection cable used the dimensions shown above will change.
The dimensions given here are representative values and are intended for reference only.

1-14

SmartAXIS FT2J Instruction Manual

Slot2

OUT

1 FT2JMark A<QR code>
See instr.
Manual.

1.7

Installation● Operating Environment
For designed performance and safety of the FT2J, do not install the FT2J in the following environments:• Where dust, briny air, or iron powder exist.
• Where oil or chemical splashes for a long time.
• Where space is filled with oil mist.
• Where direct sunlight falls on the FT2J.
• Where strong ultraviolet rays fall on the FT2J.
• Where corrosive or combustible gasses exist.
• Where shocks or vibrations are transmitted.
• Where condensation occurs due to rapid temperature change.
• Where high-voltage or arc-generating equipment (electromagnetic contactors or circuit protectors) exists in close
proximity.
● Ambient Temperature• Allow sufficient space for ventilation, and install the equipment away from heat sources.
• Allow at least 100mm between the FT2J and walls or other equipment.
• Do not install the FT2J where the ambient temperature exceeds the rated ambient operating temperature range.
When mounting the FT2J in such locations, provide a forced air-cooling fan or air-conditioner to keep the ambient
temperature within the rated temperature range.
• The FT2J is designed to install on a vertical plane so that natural air-cooling is provided. If you install it using anyother orientation, use forced-air cooling, or lower the ambient operating temperature.
● About Derating
FT2J suppresses the temperature rise inside the product by reducing the backlight brightness when the ambient
operating temperature becomes high.
Relationship between the ambient operating temperature and brightness is as follows.
Brightness

USB1, USB2: Not in use
IN, OUT, Slot1, Slot2: In Use

100%

USB1, USB2: Not in use
IN, OUT: In Use
Slot1, Slot2: Not in use

10%
0%
-20℃

Ambient Operating Temperature
45℃

50℃

55℃

Brightness reduction occurs depending on the usage of the USB interface, IN, OUT, and cartridge slots.
Depending on each product the values shown above will change. The values given here are representative values areintended for reference only.

SmartAXIS FT2J Instruction Manual

1-15

1Main Unit Specifications● About the printed contents of the main unit
"Mark A" indicates that you can refer to the instruction sheet by using the QR code. For details about Conductormaterial and wire size, refer to “1.4 External Interfaces” on page 1-3 and “1.8 Wiring” on page 1-20.

1 FT2J● Installation• Make a panel cut-out on the panel with the dimensions shown below.
Unit: mm

B

A
A

118.6

B
+1.0
0

176.6

Panel Thickness+1.00

1.0 to 5.0• Use the attached mounting clips to tighten the screws evenly to mount panel: screws must be applied on total offour places with the specified torque 0.5 to 0.6N∙m.
Panel
Mounting Clip

Mounting Clip

CAUTION• Mount the FT2J on a rigid panel.
• Do not tighten with excessive force, otherwise the FT2J may warp the display, or impair the waterproof
characteristics.
• If the mounting clips are tightened obliquely to the panel, the FT2J may fall off the panel.
• When installing the FT2J into a panel cut-out, make sure that the gasket is not twisted. Especially when reinstalling, take special care because any twists in the gasket will impair the waterproof characteristics. Also, if
the gasket comes off the main unit, align the convex part of the gasket with the concave part of the front case,and then insert the gasket fully into the gasket mounting groove without twisting it.
Concave part (Front case)Gasket mounting groove

Convex part (Gasket)

1-16

SmartAXIS FT2J Instruction Manual

1 FT2J

Ambient Operating Temperature: Output current limitation of
USB interface

Orientation-20 to +45℃: 1000 mA+45 to +50℃: 500 mA+50 to +55℃: 150 mA

Landscape-20 to +40℃: 1000 mA+40 to +55℃: 150 mA
VerticalPortrait (Clockwise)-20 to +40℃: 1000 mA+40 to +55℃: 150 mA
Portrait (Counter Clockwise)-20 to +50℃: 500 mA+50 to +55℃: 150 mA
Landscape (Rotate 180°)

Horizontal-20 to +50℃: 500 mA+50 to +55℃: 150 mA• When installing the FT2J in a diagonal, the limitations are same as a horizontal.
• Confirm the visibility of the display in a final installation.
• When mounting in Landscape (Rotate 180 degrees) or Horizontal orientation, it is not possible to use theUSB interface with an output current that exceeds 500mA.
• Cartridge slots (Slot1, Slot2) cannot be used in the following cases.
- Orientation is in Vertical - Portrait (Clockwise) or - Portrait (Counter Clockwise) and the ambient
operating temperature is +50 to +55℃.
- Orientation is in Horizontal and the ambient operating temperature is +45 to +55℃.
• FC6A-PK2AW cannot be used when the orientation is in Horizontal and the ambient operating
temperature is +40 to +45°C.
For details about how to install the cartridge, refer to Chapter 2 “1.6 Install and remove” or Chapter 2 “2.6 Install andremove” in the Smart AXIS Hardware Manual.

SmartAXIS FT2J Instruction Manual

1-17

1Main Unit Specifications● Restrictions due to mounting orientation
The FT2J is designed to install on a vertical landscape. The ambient operating temperature and the output current of
the USB interface (total of USB1 and USB2) are limited as shown in the table below.

1 FT2J
By reducing the input voltage and input utilization (simultaneous ON ratio: a%) of I0 to I7, I10 and I11, use within
the ambient operating temperature range appropriate for the mounting orientation.
Type No.

FT2J-7U22RAF-B
Input Voltage
28.8V

Landscape

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
45℃
Ambient
OperatingTemperature
40℃

24.0V

0V
0%

60%

Ambient Operating
Input Voltage Temperature
55℃
28.8V

Input Voltage

0V

Ambient Operating
Temperature
55℃

28.8V

Portrait(Clockwise)

Ambient
OperatingTemperature
35℃

24.0V

Input utilization
80% 100% (a%)

0%

40%

60%

Input utilization
80% 100% (a%)

Ambient Operating
Temperature
50℃
Ambient Operating
Temperature
40℃

24.0V

0V
0%

20%

Input Voltage

40%

60%

Input utilization
100% (a%)

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
50℃

28.8V

Portrait(Counter
Clockwise)

Ambient Operating
Temperature
35℃
24.0V

0V
0%

20%

40%

28.8V

Landscape(Rotate 180°)

60%

Ambient Operating
Temperature
40℃
24.0V

0V
0%

60%

Input Voltage

Ambient Operating
Temperature
55℃

28.8V

Horizontal

Input utilization
100% (a%)
Ambient Operating
Temperature
45℃
Ambient Operating
Temperature
35℃

24.0V

0V
0%

1-18

Input utilization
100% (a%)

Ambient
Operating Temperature
55℃

Input Voltage

20%

40%

Ambient Operating
Temperature
50℃
Ambient
OperatingTemperature
45℃

60%

SmartAXIS FT2J Instruction Manual

Input utilization
100% (a%)

1 FT2J
If in compliance with UL standards, please follow the diagram below to reduce the input voltage and input usage rate
(ON state ratio: a%) accordingly.
FT2J-7U22RAF-B
Input Voltage
28.8V

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
45℃

Input Voltage
28.8V

Ambient
OperatingTemperature
40℃

Landscape

0V
0%

60%

Ambient
OperatingTemperature
35℃

Input utilization
80% 100% (a%)

Input Voltage
28.8V

Ambient Operating Ambient Operating
Temperature
Temperature
50℃
Ambient
55℃
OperatingTemperature
45℃

0V
0%

40%

60%

Input utilization
80% 100% (a%)

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
50℃
Ambient Operating
Temperature
40℃

Portrait(Clockwise)

0V
0%

20%

Input Voltage

60%

Ambient Operating
Temperature
55℃

28.8V

Input utilization
100% (a%)
Ambient Operating
Temperature
50℃
Ambient Operating
Temperature
35℃

Portrait(Counter
Clockwise)

Input utilization
100% (a%)

0V
0%

20%

40%

Ambient Operating
Temperature
55℃

Input Voltage
28.8V

Ambient Operating
Temperature
40℃

Landscape(Rotate 180°)

0%

60%

Input utilization
100% (a%)

Input Voltage

Ambient Operating
Temperature
55℃

Ambient Operating
Temperature
45℃

0V

28.8V
Ambient Operating
Temperature
35℃

Horizontal

0V
0%

20%

40%

SmartAXIS FT2J Instruction Manual

Input utilization
100% (a%)

1-19Main Unit Specifications

Type No.

1

1 FT2J

1.8

WiringCAUTION• Turn off the power supply before wiring.
• Make the wiring as short as possible and run all wires as far away as possible from high-voltage and largecurrent cables. Follow all the procedures and precautions when wiring the FT2J.
• Separate the FT2J power supply wiring from the power lines of I/O devices and motor equipment.
• Ground the functional earth terminal to make sure of correct operation.
• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) circuit for power supply.
• Use Copper Conductors Only.
● Terminal Arrangement and Wiring Examples
FT2J-7U22RAF-B
Sink Input Wiring Example*1

Sink Input Wiring Example
External
power supply
24V DCͪ
2-wireSensor
ͬ

I0

I1

I2

I3

I4

I5

I6

I7

I10

External
power supply
24V DCͪͪͬͬ

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output deviceͪͬExternal
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/ͬcurrent output deviceͬ
2-wireͪͬSensor
ͪ
ͪ

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital / Analog IN

Digital IN

Ry. OUTPower supply terminal
ͪ

ͬ

COM
SD

SG

RDB

COM2 Q0

Q1

Q2

Q3

NC COM3 Q4

Q5

Q6

Q7

L

L

L

L

L

L

L

L

ͬ
ͪ

: Fuse*1 I12 to I15 cannot be used as source inputs.

1-20

SmartAXIS FT2J Instruction Manual

L : Load1 FT2J

1

FT2J-7U22KAF-B
Sink Input Wiring Example

External
power supply
24V DC
＋
2-wireSensor
−

I0

I1

I2

I3

I4

I5

I6

I7

I10

Main Unit Specifications

Sink Input Wiring Example*1

External
power supply
24V DC＋＋−−

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output device＋−
External
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/−current output device−
2-wire＋−Sensor
＋
＋

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital IN

Digital / Analog IN

Analog OUT

Tr. Sink OUTPower supply terminal
＋

−

COM
SD

SG

RDB

−

Q0

Q1

Q2

Q3

Q4

Q5

COM2 ＶCOM3
AQ0 AQ1(-) (+)
(-)

L

L

L

L

L

L

−
＋

＋

＋

−

Analog voltage/current input device
Analog Output Wiring Example: FuseL : Load*1 I12 to I15 cannot be used as source inputs.

SmartAXIS FT2J Instruction Manual

1-21

1 FT2JFT2J-7U22SAF-B
Sink Input Wiring Example *1

Sink Input Wiring Example
External
power supply
24V DC
＋
2-wireSensor
−

I0

I1

I2

I3

I4

I5

I6

I7

I10

External
power supply
24V DC＋＋−−

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output device＋−
External
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/−current output device
2-wire −＋−Sensor
＋
＋

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital IN

Digital / Analog IN

Tr. Source OUTPower supply terminal＋−

Analog OUT

COM
SD

SG

RDB

−

Q0

Q1

Q2

Q3

Q4

Q5

L

L

L

L

L

L

COM2 ＶCOM3
AQ0 AQ1(-)(+) (-)

＋
−

＋

−
＋
Analog voltage/current input device
Analog Output Wiring Example: Fuse*1 I12 to I15 cannot be used as source inputs.

1-22

SmartAXIS FT2J Instruction Manual

L : Load1 FT2J

1+Power supply (24V DC)-

Power supply (0V)
Functional Earth (FE)• Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Applicable cable

AWG14 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

7 to 9 mm

Recommended ferrule

ST3L-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)● Caution when inserting and removing wires• When connecting a wire that has not been treated with a tip, such as a stranded wire, you can connect it byinserting the wire all the way in while pressing the pusher, and then releasing the pusher.
• When connecting wires with ferrules, connect the ferrules to the terminal block so that the long side is horizontal.
(See the figure below.)COM, IN, OUT
PusherPower Supply Terminal(Push button for removal)

OK

NG

OK

NG

• Do not pull out the wire without pressing the pusher. When pulling out the wire, use a flat blade screwdriver, etc.,
and pull the wire straight out while pressing the pusher with about 20 N of force.
• Be careful not to damage the push-in terminals. When pressing the pusher, do not apply more than 40N of force.

● Cautions for using the FT2J connected to a personal computer
When connecting the FT2J to a personal computer via the USB Interfaces, the FT2J or the personal computer may
break down depending on the conditions of the personal computer. Make sure of the following cautions, in order toprevent an accident.
• If the personal computer has a 3-pin power plug or power plug with a ground lead type, make sure to use a plug
socket including a ground input electrode or ground the earth lead, respectively.
• If the personal computer has a 2-pin power plug without ground lead, follow the procedure below when connect
the FT2J to the personal computer.
(1) Pull out the power plug of the personal computer from the AC outlet.
(2) Connect the FT2J to the personal computer.
(3) Insert the power plug of the personal computer into the AC outlet.

*1 Strip the sheath of the wire 7 to 9 mm from the end.
7 to 9 mm

SmartAXIS FT2J Instruction Manual

1-23

Main Unit Specifications● Power Supply Terminal• Pin assignment is shown in the following table.

1 FT2J● Recommended Tools
Tool Name
Normal type
Flat blade screwdriverWith insulated coverModel Number (Order Number)

Manufacturer

SDS 0.4×2.5×75 (9009030000)

Weidmüller

S3TL-D04-25-75

IDEC

SDIS 0.4×2.5×75 (9008370000)

Weidmüller

S3TL-CR06D

IDEC

PZ6/5 (90011460000)

Weidmüller

S3TL-ST06IDEC

STRIPAX(9005000000)

Weidmüller

Crimping tool
Stripping tool

1.9

Maintenance and Inspection
Maintain and inspect the FT2J periodically to ensure the best performance. Do not disassemble, repair, or modify the
FT2J during inspection.
Maintenance andInspection Parts

Description

Display

Wipe any stain of the display using a soft cloth slightly dampened with neutral detergent or
alcoholic solvent. Do not use solvents such as thinner, ammonia, strong acid, and strong alkaline.

Terminals, Connectors

Check the terminals and connectors to make sure of no loose screws, incomplete insertion, ordisconnected lines.

Mounting Clips

Make sure that all mounting clips and screws are tightened sufficiently. If the mounting clips areloose, tighten the screw to the specified torque.

Backlight

The FT2J’s backlight cannot be replaced by the customer. When the backlight needs to be
replaced. Contact your vendor or IDEC Corporation.

● Maintenance Screen
Turn on the power to the FT2J, then press and hold the touch panel on the upper-left corner of the screen for threeseconds or longer. The Maintenance Screen appears on the screen.
Maintenance
System Mode
Device Monitor
Adjust Brightness

Maintenance Screen• Permission to show the Maintenance Screen can be set using the WindO/I-NV4. For details, refer to Chapter 4 "3.1
System Tab" in the WindO/I-NV4 User's Manual.
• The Maintenance Screen is not displayed in the System Mode.
● System Mode
Press the [System Mode] at the top of the Maintenance Screen. The Top Page Screen appears.

SYSTEM MODE TOP PAGE

Run

OfflineMain Menu

MAC Address Invalid.
MAC Address 98:84:E3:8E:52:4B
IP Address 192.168.2.42(DHCP)
2021/JUN/29/TUE 08:57:36
SNTP

<<

EtherIP

BRIGHTNESS 31

ENG/JPN>>

Initial Setting, Self Diagnosis and Initialization of the data, etc can be executed in the System Mode.

1-24

SmartAXIS FT2J Instruction Manual

1 FT2J

1

1 Press the [Adjust Brightness] at the bottom of the Maintenance Screen. The Adjust Brightness Screen appears.
Maintenance
System Mode
Device Monitor
Adjust Brightness

2 Press the [<<] and [>>] at the bottom the Adjust Brightness Screen to adjust the contrast to the optimal setting.
Maintenance

Adjust Brightness

3 Press the [X] to close the Adjust Brightness Screen.
To adjust the brightness in the System Mode, use the [<<] and [>>] buttons located at the bottom of the
Top Page.

SYSTEM MODE TOP PAGE

Run

OfflineMain Menu

MAC Address Invalid.
MAC Address 98:84:E3:8E:52:4B
IP Address 192.168.2.42(DHCP)
2021/JUN/29/TUE 08:57:36
SNTP

<<

EtherIP

BRIGHTNESS 31

ENG/JPN>>

1.10 Software License Information
This product contains various open source software in addition to the software owned by IDEC Corporation.
Information about open source software can be obtained from the QR code printed on the back of the FT2J.

SmartAXIS FT2J Instruction Manual

1-25

Main Unit Specifications● Adjusting the Brightness
The brightness of the FT2J display can be adjusted on the Adjust Brightness Screen.

About the Warranty of the products
1

Warranty Period
The warranty period for IDEC products shall be three (3) year after purchase or delivery to the specified location.
However, this shall not apply in cases where there is a different specification in the Catalogs or there is anotheragreement in place between you and IDEC.

2

Warranty scope
Should a failure occur in an IDEC product during the above warranty period for reasons attributable to IDEC, then
IDEC shall replace or repair that product, free of charge, at the purchase location/delivery location of the product, or
an IDEC service base. However, failures caused by the following reasons shall be deemed outside the scope of thiswarranty.
i.

The product was handled or used deviating from the conditions/environment listed in the Catalogsii.

The failure was caused by reasons other than an IDEC productiii.

Modification or repair was performed by a party other than IDECiv.

The failure was caused by a software program of a party other than IDECv.

The product was used outside of its original purposevi.

Replacement of maintenance parts, installation of accessories, or the like was not performed properly inaccordance with the user's manual and Catalogsvii. The failure could not have been predicted with the scientific and technical standards at the time when the
product was shipped from IDEC
viii. The failure was due to other causes not attributable to IDEC (including cases of force majeure such as natural
disasters and other disasters)*

Customers assume their own risk in programming products, Company will not be held liable for damages as aresult of improper programming.

Furthermore, the warranty described here refers to a warranty on the IDEC product as a unit, and damages inducedby the failure of an IDEC product are excluded from this warranty.

3Service scope
The prices of IDEC products do not include the cost of services, such as dispatching technicians. Therefore, separate
fees are required in the following cases.
(1) Instructions for installation/adjustment and accompaniment at test operation (including creating application
software and testing operation, etc.)(2) Maintenance inspections, adjustments, and repairs(3) Technical instructions and technical training(4) Product tests or inspections specified by you

EU Authorized Representative: APEM SAS
55, Avenue Edouard Herriot BP1, 82303 Caussade Cedex, France
Specifications and other descriptions in this document are subject to change without notice.
Information in this document is current as of September, 2023.
2023 IDEC Corporation, All Rights Reserved.
B-2345(0)UK Authorized Representative: APEM COMPONENTS LIMITED
Drakes Drive, Long Crendon, Buckinghamshire, HP18 9BA, UK