Automation solutions
Visualization solutions, modular and compact control systems, remote I/O systems andsoftware: Eaton offer a wide spectrum of automation solutions.
XV - visualisation solutions
Simple operation relieves operators of machinery, installations or in individual applications+++ Simultaneous high performance PLC +++ Resistive touch displays or robust infrared touch
displays from 3.5 – 15 inches
XC - modular PLCs
Construction scalable within wide limits +++ Different PLC performance classes, multiple
expansion modules +++ Integration into communication concept +++ Data exchange through
Ethernet and integrated Web server facilitate innovative solutions
EC4P – Compact control system
Many functions in one device +++ Automation of smaller applications +++ Ethernet variants
allow remote programming +++ Numerous local expansion modules, eayNet extensions,
CANopen extensions and network modules
XI/ON – Remote I/O system
Control movements, measure temperature or speed, record currents and voltages +++Ideal for solutions focused on remote signal processing +++ Modular concept and simple
handling

SoftwareAll controls programmed with CoDeSys in compliance with IEC 61131-3 +++ Easy andefficient generation of operator guidance with interactive visualization software Galileo +++Mask generation for HMI-PLC devices (XV100, XV400); also with integrated CoDeSys
visualization +++ Convenient, uncomplicated planning and realization of XI/ON stations withthe cost-free I/O Assistant +++ Generate SmartWire-DT configurations with cost-free
SWD-Assist
2010 CA08103002Z-EN   www.eaton.com

Automation products

System overview
Touch Panel XVSystem overview
14/2

14/4

Ordering
Touch Panel XVHMI(-PLC) XV100

14/5

HMI-PLC XV200

14/6

HMI-PLC MFD4, HMI XVH300

14/7

HMI-PLC XVS400

14/8

HMI Mobile Panel XVM400

14/9

HMI-PLC XV400

14/10

XV accessories

14/12

Engineering
Communication protocols, licensing

14/14

Technical data
Touch Panel XVHMI(-PLC) XV100

14/18

HMI-PLC XV200

14/20

HMI-PLC MFD4

14/22

HMI Mobile Panel

14/23

HMI XVH300

14/24

HMI-PLC XV400

14/28

HMI-PLC XVS400

14/32

Dimensions
Touch Panel XV

14/34

System overview
XC100, XC121, XC200 modular PLCs

14/62

Ordering

Description
Touch Panel XV

EC4P compact PLCs

14/36

Ordering
XC100, XC121, XC200 modular PLCs

14/38

XI/OC input/output expansion

14/39

Accessories

14/40

Technical data

EC4P compact PLCs

14/64

Expansion devices

14/65

Accessories

14/66

Technical data
EC4P compact PLCs

14/70

I/O expansions EC4E

14/75

MFD-CP4-CO communication modules

14/79

Dimensions
Compact PLCs, I/O expansions, communication modules

14/80

System overview
Remote I/O XI/ON

14/82

Description
Remote I/O XI/ON

14/84

Selection chart

14/85

Maximum system configuration

14/86

Ordering
Gateways

14/88Power supply modules

14/90

I/O modules

14/91

Technology modules

14/93

Basic modules

14/94

I/O expansions, SWD, accessories

14/97

Engineering
Gateways, supply modules

14/99

I/O modules

14/100Technology modules

14/110Technical data
General information, terminals

14/111

Gateways

14/112

Supply modules

14/113

I/O modules

14/114

Technology Modules

14/122

XC100 modular PLCs

14/42

Text display for XC100 modular PLC14/44

XC121 modular PLCs

14/45

Gateways, XNE electronics modules

14/124

Input/output expansion for XC121

14/47

XN Electronics modules

14/125

XC200 modular PLCs

14/49

Base modules

14/126I/O expansions XI/OC

14/51

Dimensions
XC100, XC200 Modular PLCs

14/59

XI/OC input/output expansion

14/59

Text display for XC100 modular PLC14/60

XC121 modular PLCs, XIO-EXT expansion

14/60

Dimensions

Software

14/128

Power supplies

14/131

14/2

Automation products

Visualization

System overview
Visualization

1
1

3

2

180

4
4

11

5

180

10
5
8

6

7

6

9

2010 CA08103002Z-EN

www.eaton.com

Visualization
XV100 HMI/PLC withtouch display

Automation products
1

Compact operator
panels with wide rangeof functions.
Fully-graphical 3.5”, 5.7”
or 7” wide-screen
devices.
TFT display, color ormonochrome
Resistive touch
Ethernet interface on
board.
In addition CAN,PROFIBUS, RS232 or
RS485 possible.
￫ Page 14/5

SD memory card

Expansion of device
functionality throughassignment of license
points.
Licensing is through theInternet.
￫ Page 14/12

4

Fully graphic 5.7” devices
with monochrome or color
display (STN).
Resistive touch
Ethernet interface on
board.
In addition CAN,PROFIBUS, or RS232
possible.
￫ Page 14/6

Compact-Flash memorycard

2

Optional memory for
project, recipe data, etc.
￫ Page 14/12

XV license productcertificate

XV200 HMI/PLC withtouch display

3

Memory for project,
recipe data, etc.
With or without preinstalled Win CE operating
system.
￫ Page 14/12

5

XV400 HMI/PLC withtouch display

65.7”, 8.4”, 10.4”, 12.1”,
15” devices
TFT color display
Infra-red or Resistivetouch.
Numerous communication
possibilities throughpluggable communication
cards.
Also available in stainlesssteel design.
￫ Page 14/10

XV license productcertificate

Communication card for
XV400

9

Depending on device
size 1 or 2 cards can beplugged in.
￫ Page 14/13

Mounting kit

7

Expansion of device
functionality throughassignment of license
points.
Licensing is through theInternet.
￫ Page 14/12

Windows CE licence

14/3

10

Additional fixing kits for all
XV devices.
Fixing kit are generally
included as standard.
The illustration shows an
XV-100 fixing kit.
￫ Page 14/12

Software11

Visualization software
Galileo
Programming softwareXSOFT-CODESYS, EPAM
￫ Page 14/130
8Win CE license withlicense label.
￫ Page 14/12

2010 CA08103002Z-EN

www.eaton.com

14/4

Automation products

Visualization

Description
Visualization

HMI with integratable
PLC
The modern touch displays XV can
optionally be used as fully-featured
PLCs. This cost-saving, leading-edge
concept offers the perfect solution forevery application, whether in the
low-cost segment or in the demanding
high-end segment, where performance is key. The devices areavailable in display sizes from 3.5” to
15” and, depending on model withresistive or infrared touch. Alternatively, the panels can also be
mounted edgewise.

XV100: Designed for the low-cost
segment, these devices excel witha compact design, light-weightplastic housing and a wide rangeof onboard interfaces. Despite its
small size, the XV100 with 3.5” touch
display has an exceptional range ofperformance features, including PLC
function.

XVS400 and XV400: These multipurpose devices with their rugged metal
housing are exceptionally flexible andprovide comprehensive communication possibilities. The XVS400 featuresa PROFIBUS-DP master/MPI interface
as standard as well as Ethernet, RS232
and onboard USB host. With optional
communication modules the XV400
can be easily and quickly expanded
and adapted.
The XV400 with stainless steel frontis also ideally equipped for special
applications:• IP69K: cleaning using high-pressure
and steam jets (5.7“)• Ex zone 1: For use in potentiallyexplosive atmospheres (10.4” and12.1”)The touch panels with 5.7”
and 7” display feature an
additional USB host and an RS232
interface.

XVM400: The mobile version with its
round, ergonomic design is easy tooperate with just one hand.

Licencing procedure
To make sure that you pay for only
those functions that you actually need,the devices work with a license point
system. Use the points to activate
specific functions, such as:• Runtime for the visualization(GALILEO or EPAM)• Communication (e.g. Ethernet,
CANopen, Siemens MPI)
• Tools (e.g. CE Telediag,
S7 PG Router)• XSOFT-CODESYS-2 runtime for
the PLC function
With license product certificates you
can buy additional license points. Thishas the following benefits for you:• Cost optimization• Low warehousing costs• Flexible handling￫ For detailed information about this
topic see chapter Licensing

2010 CA08103002Z-EN

www.eaton.com

Visualization

Automation products

14/5

HMI(-PLC) XV100
HPL14005EN

Ordering
VisualizationHMI(-PLC) XV100

Display

Front design

Screendiagonal
InchesResolution

CommunicationinterfacePart No.
Article No.

–

XV-102-A0-35MQR-10
141759
XV-102-A2-35MQR-10
141820
XV-102-A3-35MQR-10
141821
XV-102-A4-35MQR-10
141822
XV-102-A5-35MQR-10
141823

1 off

XV-102-B0-35TQR-10
140007
XV-102-B2-35TQR-10
140008
XV-102-B3-35TQR-10
140009
XV-102-B4-35TQR-10
140010
XV-102-B5-35TQR-10
140011

1 off

XV-102-B0-35MQR-10-PLC
140012
XV-102-B3-35MQR-10-PLC
140013
XV-102-B4-35MQR-10-PLC
140014
XV-102-B5-35MQR-10-PLC
140015
XV-102-B6-35MQR-10-PLC
140016
XV-102-B8-35MQR-10-PLC
140017
XV-102-B0-35TQR-10-PLC
140018
XV-102-B3-35TQR-10-PLC
140019
XV-102-B4-35TQR-10-PLC
140020
XV-102-B5-35TQR-10-PLC
140021
XV-102-B6-35TQR-10-PLC
140022
XV-102-B8-35TQR-10-PLC
140023

1 off

PixelsPrice
Seeprice list

Std. pack

XV100• HMI or HMI PLC with communication through on-board interface.
• Communication scope extendable through licensing, ￫ Page 14/12.
• Standard front, special front please inquire• Insulating enclosure and front plate• Processor: RISC central processing unit, 32-bit, 400 MHz• OS, program and data memory: 64 MB• 1 slot for 1 SD card
• Software (engineering): Visualization = GALILEO or EPAM, PLC = XSOFT-CODESYS-2(depending on version)• Windows CE Core 5.0 license (incl.)– Built-in interfaces: 1 × Ethernet 100/10, 1 × USB device, communications interface– No PLC function possible
Resistive touch
Standard
3.5
320 x 240
3.5'' TFT LCD
membrane
32 grey levels(fully3.5
320 x 240
enclosed)
3.5

320 x 240

RS232

3.5

320 x 240

RS485

3.5

320 x 240

CAN
RS232

320 x 240–

320 x 240

PROFIBUS

3.5

320 x 240

RS232

3.5

320 x 240

RS485

3.5

320 x 240

CAN
RS232

320 x 240–

320 x 240

RS232

3.5

320 x 240

RS485

3.5

320 x 240

3.5

320 x 240

3.5

320 x 240

3.5

320 x 240

CAN
RS232
CAN
RS485
PROFIBUS
RS485
–

3.5

320 x 240

RS232

3.5

320 x 240

RS485

3.5

320 x 240

3.5

320 x 240

3.5

320 x 240

CAN
RS232
CAN
RS485
PROFIBUS
RS485– Built-in interfaces: 1 × Ethernet 100/10, 1 × USB device, communications interface– Can be expanded with PLC function, ￫ Page 14/14
Resistive touch
Standard
3.5
3.5'' TFT LCD
membrane
64 k Colors(fully3.5
enclosed)– Including PLC function– Built-in interfaces: 1 × Ethernet 100/10, 1 × USB device, communications interface
Resistive touch
Standard
3.5
3.5'' TFT LCD
membrane
32 grey levels(fully3.5
enclosed)

Resistive touch
3.5'' TFT LCD
64 k Colors

Information relevant
for export toNorth America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

PROFIBUSUL 60950-01; cUL;
IEC/EN 61131-2; CE marking
E208621NWGQ2, NWGQ8UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada

Conditions of Acceptability
The investigated Pollution Degree is: 2
The following end-product enclosures are required:Fire. The unit must be supplied via a SELV source. The
provided Ethernet Connection is only allowed toconnect to inhouse networks
Degree of Protection
IEC: IP65, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/6

Automation products

Visualization

HMI(-PLC) XV100, HMI-PLC XV200
HPL14006EN
VisualizationHMI(-PLC) XV100, HMI-PLC XV200

Display

Front design

Screendiagonal
InchesResolution

CommunicationinterfacePart No.
Article No.

RS232

XV-102-D0-57TVR-10
142530
XV-102-D6-57TVR-10
142531Price
Seeprice list

PixelsStd. pack

XV100– Built-in interfaces: 1 × Ethernet 100/10, 1 × USB device, 1 × USB host, communications interface– Can be expanded with PLC function, ￫ Page 14/14
Resistive touch
Standard membrane
5.7
640 x 4805.7" TFT LCD(fully enclosed)
64 k Colors
5.7
640 x 480

Resistive touch
7" TFT LCD
64 k Colors

5.7

640 x 4807

800 x 4807

800 x 4807

800 x 480

CAN
RS232
RS485
PROFIBUS
RS232
RS485

– Including PLC function– Built-in interfaces: 1 × Ethernet 100/10, 1 × USB device, 1 × USB host, communications interface
Resistive touch
Standard membrane
5.7
640 x 4805.7" TFT LCD(fully enclosed)
64 k Colors
5.7
640 x 480

Resistive touch
7" TFT LCD
64 k Colors

Display

Front design

7

800 x 4807

800 x 480

Screendiagonal
InchesResolution

CAN
RS232
RS485
PROFIBUS
RS232
RS485
RS232

CAN
RS232
RS485
PROFIBUS
RS232
RS485
CAN
RS232
RS485
PROFIBUS
RS232
RS485

1 off

XV-102-D8-57TVR-10
142532
XV-102-D0-70TWR-10
142535
XV-102-D6-70TWR-10
142536
XV-102-D8-70TWR-10
142537

XV-102-D6-57TVR-10-PLC
142533

1 off

XV-102-D8-57TVR-10-PLC
142534
XV-102-D6-70TWR-10-PLC
142538
XV-102-D8-70TWR-10-PLC
142539CommunicationinterfacePart No.
Article No.

XV-230-57CNN-1-10
139951
XV-230-57MPN-1-10
139952
XV-232-57BAS-1-10
139950
XV-252-57CNN-1-10
139956
XV-252-57MPN-1-10
139957

PixelsPrice
See price
list

Std. pack

XV200• HMI or HMI PLC with communication through on-board interface.
• PLC function and communications scope can be upgraded with licenses, ￫ Page 14/12.
• Standard front, special front please inquire• Insulating enclosure and front plate• Processor: RISC central processing unit, 32-bit, 200 MHz• OS, program and data memory: 32 MB.
• Built-in interfaces: 1 × Ethernet, 1 × USB device, communications interface• 1 slot for 1 Compact Flash™ card.
• Software (engineering): visualization = GALILEO or EPAM, PLC = XSOFT-CODESYS-2• Windows CE license required• Compact Flash™ required ￫ XV accessories• Flush mounting compatible with 5.7” XV-400 devices and older predecessors
Resistive touch
5.7" FSTN LCD(monochrome display)
256 grey levels

Information
relevant for export
to North America

2010 CA08103002Z-EN

5.7

320 x 240

CAN

5.7

320 x 240

PROFIBUS

5.7

320 x 240

RS232

Resistive touch
5.7" CSTN LCD(Color display)

5.7

320 x 240

5.7

320 x 240

CAN
RS232
PROFIBUS
RS232

Product Standards

UL 60950-01; cUL;
IEC/EN 61131-2; CE marking
E208621NWGQ2, NWGQ8UL report applies to both US and Canada–
UL Recognized, certified by UL for use in
CanadaUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certificationwww.eaton.com

Standard
membrane

1 offConditions of Acceptability The investigated Pollution Degree is: 2
The following end-product enclosures are
required: Fire, Electrical
The unit must be supplied via a SELV source.
The provided Ethernet Connection is only
allowed to connect to inhouse networks.
Degree of Protection
IEC: IP65, UL/CSA Type: -Visualization

Automation products

14/7

HMI-PLC MFD4, HMI XVH300
HPL14007EN
VisualizationHMI-PLC MFD4, HMI XVH300Visualization

Display

CommunicationinterfacePart No.
Article No.

320 x 240

Ethernet
CANopen/easyNet
RS232

MFD4-5-XRC-30
1094281 off

5.7

320 x 240

–

1 off

5.7

320 x 240

CAN

5.7

320 x 240

PROFIBUS

5.7

320 x 240

5.7

320 x 240

RS485 (Suconet K)
RS232 (Sucom A)
CAN

XVH-340-57BAS-1-10
139869
XVH-340-57CAN-1-10
139870
XVH-340-57MPI-1-10
139871
XVH-342-57SKS-1-10
139873
XVH-340-57CAN-1-501)
1398725.7

320 x 240–

5.7

320 x 240

CAN

5.7

320 x 240

PROFIBUS

Screendiagonal
InchesResolution

5.7

PixelsPrice
See price
list

Std. pack

MFD4• Memory card pluggable (optional) ￫ Page 14/41• Real-time clock• Operating system: Windows CE
Resistive touch
5.7" TFT LCD
32 k Colors

Visualization

XVH300• HMI (No PLC function possible) with communication through on-board interface.
• Communication scope extendable through licensing, ￫ Page 14/12.
• Standard front, special front please inquire• Metal enclosure and front plate• Processor: RISC central processing unit, 32-bit, 200 MHz• OS, program and data memory: 64 MB• Display: 5.7" CSTN LCD (Color display), 256 colors• Built-in interfaces: 1 × Ethernet, 1 × USB device, communications interface• 1 slot for 1 Compact Flash™ card
• Software (engineering): visualization = GALILEO or EPAM
• WinCE license required ￫ XV accessories• Compact Flash™ required ￫ XV accessories
Infra-red touch
5.7" CSTN LCD(Color display)

Resistive touch
5.7" CSTN LCD(Color display)Standard front withstandard membrane
Laminated safety glass,non-reflective

Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective
Standard front withstandard membrane (fullylaminated)

Notes
Information relevant for export to North America

XVH-330-57BAS-1-10
139866
XVH-330-57CAN-1-10
139867
XVH-330-57MPI-1-10
1398681) Approved for IP69K.
Observe installation instructions to IP69K.
Product Standards
UL 60950-01; cUL; IEC/EN 61131-2;
CE marking
UL File No.
E208621
UL CCNNWGQ2, NWGQ8CSA File No.
UL report applies to both US and Canada
CSA Class No.
–
NA Certification
UL Recognized, certified by UL for use in Canada
Conditions of Acceptability
The investigated Pollution Degree is: 2
Proper bonding to the end-product main protective earthingtermination is: Required
The following end-product enclosures are required: Fire,Electrical
The unit must be supplied via a SELV source.
The provided Ethernet Connection is only allowed to connect
to inhouse networks.
Degree of Protection
IEC: IP65, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/8

Automation products

Visualization

HMI-PLC XVS400
HPL14008EN
Visualization
VisualizationHMI-PLC XVS400

Display

Front design

Screendiagonal
InchesResolution

Part No.
Article No.

PixelsPrice
See price
list

Std. pack

XVS400• HMI or HMI PLC with communication through on-board interface.
• PLC function and communications scope can be upgraded with licenses, ￫ Page 14/12.
• Standard front, special front please inquire• Metal enclosure and front plate• Processor: RISC central processing unit, 32-bit, 400 MHz• OS, program and data memory: 64 MB• Software (engineering): visualization = GALILEO or EPAM, PLC = XSOFT-CODESYS-2• WinCE license required ￫ XV accessories• Compact Flash™ required ￫ XV accessories– Display: 5.7" CSTN LCD (color display), 256 colors– 1 slot for Compact Flash™ cards– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × PROFIBUS, 1 × USB host, 1 × USB device
Resistive touch
5.7" CSTN LCD(Color display)Standard membrane(fully laminated)

5.7

320 x 240

XVS-430-57MPI-1-10
139967

Infra-red touch
5.7" TFT LCD

Standard membrane
Laminated safety glass,non-reflective

5.7

320 x 240

XVS-460-57MPI-1-10
1399705.7

320 x 240

XVS-440-57MPI-1-10
1399685.7

320 x 2408.4

640 x 480

XVS-450-57MPI-1-10
139969
XVS-460-84MPI-1-10
139971

1 off– Display: 5.7" or 8.4" TFT LCD (Color display), adjustable: 65536 or 256 colors– 1 slot for Compact Flash™ card
– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × PROFIBUS, 1 × USB host, 1 × USB device
Infra-red touch
5.7" CSTN LCD (Color
display)
Resistive touch
5.7" TFT LCD
Infra-red touch
8.4" TFT LCD

Standard membrane
Laminated safety glass,non-reflective
Standard membrane(fully laminated)Standard membrane
Laminated safety glass,non-reflective

1 off– Display: 10.4", 12.1" or 15" TFT LCD (Color display), adjustable: 65536 or 256 colors– 2 slots for Compact Flash™ cards– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × PROFIBUS, 2 × USB host, 1 × USB device
Infra-red touch
10.4" TFT LCD
Resistive touch
10.4" TFT LCD
Infra-red touch
12.1" TFT LCD
Resistive touch
12.1" TFT LCD
Infra-red touch
15" TFT LCD

Information relevant for export to North America

Standard membrane
Laminated safety glass,non-reflective
Standard membrane(fully laminated)Standard membrane
Laminated safety glass,non-reflective
Standard membrane(fully laminated)Standard membrane
Laminated safety glass,non-reflective

www.eaton.com

640 x 480

XVS-440-10MPI-1-10
13997310.4

640 x 480

12.1

800 x 600

XVS-430-10MPI-1-10
139972
XVS-440-12MPI-1-10
13997512.1

800 x 600

151024 x 768

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Conditions of Acceptability

Degree of Protection2010 CA08103002Z-EN

10.4

1 off

XVS-430-12MPI-1-10
139974
XVS-460-15MPI-1-10
139976

UL 60950-01; cUL; IEC/EN 61131-2; CE marking
E208621NWGQ2, NWGQ8UL report applies to both US and Canada–
UL Recognized, certified by UL for use in Canada
The investigated Pollution Degree is: 2
Proper bonding to the end-product main protective earthing termination is:
Required
The following end-product enclosures are required: Fire, Electrical
The unit must be supplied via a SELV source.
The provided Ethernet Connection is only allowed to connect to inhouse networks.
IEC: IP65, UL/CSA Type: -Visualization

Automation products

14/9

HMI Mobile Panel
HPL14009EN
VisualizationHMI Mobile Panel

Display

Operating elements

Part No.
Article No.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

XVM400• Mobile HMI (No PLC function possible) with communication
through on-board interface.
• Communication scope extendable through licensing,￫ Page 14/12.
• Standard front, 31 membrane keys, 4 status LEDs
• Insulating enclosure and front plate• Processor: RISC central processing unit, 32-bit, 400 MHz• OS, program and data memory : min 64 MB• Built-in interfaces: 1 × Ethernet, 1 × RS232-C, 1 × USB host
• Software (engineering): Visualization = GALILEO(runtime already installed)• Windows CE 5.0 license (incl.)
Resistive touch
6.5" TFT LCD
64 k Colors

Resistive touch
6.5" TFT LCD
64 k Colors

Resistive touch
6.5" TFT LCD
64 k Colors

2 acknowledgement keys
(3-stage, 2-circuit)externally wired
Emergency switching off
button (2-circuit),
externally wired
2 acknowledgement keys
(3-stage, 2-circuit)externally wired
Emergency switching off
button (2-circuit),
externally wired
Key switch (3-position),internally wired
Electronic hand wheel,internally wired
2 acknowledgement keys
(3-stage, 2-circuit)externally wired
Key switch (3-position),internally wired
Electronic hand wheel,internally wired

XVM-430-65TVB-1-11
139996

UL File No.
UL CCNCSA File No.
XVM-450-65TVB-1-11
139998CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL; IEC/EN
6113-2; CE marking
E176666
NRAQ, NRAQ7
UL report applies to both
US and Canada
UL Recognized, certified
by UL for use in Canada
IEC: IP65, UL/CSA Type: -XVM-410-65TVB-1-11
1399972010 CA08103002Z-EN

www.eaton.com

14/10Automation products

Visualization

HMI-PLC XV400
HPL14010EN
VisualizationHMI-PLC XV400

Display

Front design

Screendiagonal
InchesResolution

Part No.
Article No.

PixelsPrice
See price
list

Std. pack

Notes

1 off

–

XV400
• HMI or HMI PLC with communication through on-board interface.
• PLC function and communications scope can be upgraded with licenses, ￫ Page 14/12.
• Standard front, stainless steel front, special fronts please inquire• Metal enclosure and front plate• Processor: RISC central processing unit, 32-bit, 400 MHz• OS, program and data memory: 64 MB• Software (engineering): visualization = GALILEO or EPAM, PLC = XSOFT-CODESYS-2• WinCE license required ￫ XV accessories• Compact Flash™ required ￫S XV accessories– Display: 5.7" CSTN LCD (color display), 256 colors– 1 slot for Compact Flash™ cards– 1 slot for communication cards– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × CAN, 1 × USB host, 1 × USB device
Infra-red touch
5.7" CSTN LCD(Color display)
Infra-red touch
5.7" CSTN LCD(Color display)
Infra-red touch
5.7" CSTN LCD(Color display)
Resistive touch
5.7" CSTN LCD(Color display)Standard front withstandard membrane
Laminated safety glass,non-reflective
Four-hole front withstandard membrane
Laminated safety glass,non-reflective
Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective
Standard front withstandard membrane (fullylaminated)

5.7

320 x 240

XV-442-57CQB-1-10
1398925.7

320 x 240

XV-442-57CQB-1-20
1398941)

5.7

320 x 240

XV-442-57CQB-1-50
1398961) 2)

5.7

320 x 240

XV-432-57CQB-1-10
139890–– Display: 5.7" or 8.4" TFT LCD (Color display), adjustable: 65536 or 256 colors– 1 slot for Compact Flash™ card
– 1 slot for communication cards– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × CAN, 1 × USB host, 1 × USB device
Infra-red touch
5.7" TFT LCD

Infra-red touch
5.7" TFT LCD

Resistive touch
5.7" TFT LCD
Infra-red touch
8.4" TFT LCD

Standard front withstandard membrane
Laminated safety glass,non-reflective
Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective
Standard front withstandard membrane (fullylaminated)Standard front withstandard membrane
Laminated safety glass,non-reflective

5.7

320 x 240

XV-460-57TQB-1-10
139897

5.7

320 x 240

XV-460-57TQB-1-50
1398982)

5.7

320 x 240

XV-450-57TQB-1-10
139899–8.4

640 x 480

XV-460-84TVB-1-10
139900

–

1 off

–

1) Not for new applications.
2) Approved for II 2G Ex px II IP5x (ATEX 94/9/EC):

Instructions

Observe installation instructions to IP69K.
Information relevant for export to North America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Conditions of Acceptability

Degree of Protection2010 CA08103002Z-EN

www.eaton.com

UL 60950-01; cUL; IEC/EN 61131-2; CE marking
E208621NWGQ2, NWGQ8UL report applies to both US and Canada–
UL Recognized, certified by UL for use in Canada
The investigated Pollution Degree is: 2
Proper bonding to the end-product main protective earthingtermination is: Required
The following end-product enclosures are required: Fire, Electrical
The unit must be supplied via a SELV source.
The provided Ethernet Connection is only allowed to connect toinhouse networks.
IEC: IP65, UL/CSA Type: -Visualization

Automation products

14/11

HMI-PLC XV400
HPL14011EN
Display

Front design

Screendiagonal
InchesResolution

Part No.
Article No.

PixelsPrice
See price
list

Std. pack

Notes

XV400

– Display: 10.4", 12.1" or 15" TFT LCD (Color display), adjustable: 65536 or 256 colors– 2 slots for Compact Flash™ cards– 2 slots for communication cards– Built-in interfaces: 1 × Ethernet 100/10, 1 × RS232, 1 × CAN, 2 × USB host, 1 × USB device
Infra-red touch
10.4" TFT LCD

Infra-red touch
10.4" TFT LCD

Infra-red touch
10.4" TFT LCD

Resistive touch
10.4" TFT LCD
Infra-red touch
12.1" TFT LCD

Infra-red touch
12.1" TFT LCD

Infra-red touch
12.1" TFT LCD

Resistive touch
12.1" TFT LCD
Infra-red touch
15" TFT LCD

Infra-red touch
15" TFT LCD

Infra-red touch
15" TFT LCD

Standard front withstandard membrane
Laminated safety glass,non-reflective
Four-hole front withstandard membrane
Laminated safety glass,non-reflective
Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective
Standard front withstandard membrane (fullylaminated)Standard front withstandard membrane
Laminated safety glass,non-reflective
Four-hole front withstandard membrane
Laminated safety glass,non-reflective
Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective
Standard front withstandard membrane (fullylaminated)Standard front withstandard membrane
Laminated safety glass,non-reflective
Four-hole front withstandard membrane
Laminated safety glass,non-reflective
Satin-finish brushed
stainless steel
Laminated safety glass,non-reflective

Instructions

10.4

640 x 480

XV-440-10TVB-1-10
139904

1 off

–

10.4

640 x 480

XV-440-10TVB-1-20
139906

1 off

1)

10.4

640 x 480

XV-440-10TVB-1-50
139908

1 off

2)

10.4

640 x 480

XV-430-10TVB-1-10
139902

1 off

–

12.1

800 x 600

XV-440-12TSB-1-10
139911

1 off

–

12.1

800 x 600

XV-440-12TSB-1-20
139913

1 off

1)

12.1

800 x 600

XV-440-12TSB-1-50
139915

1 off

2)

12.1

800 x 600

XV-430-12TSB-1-10
139909

1 off

–

15

1024 x 768

XV-460-15TXB-1-10
139916

1 off

–

15

1024 x 768

XV-460-15TXB-1-20
139917

1 off

1)

15

1024 x 768

XV-460-15TXB-1-50
1399181 off–

1) Not for new applications.
2) Approved for II 2G Ex px II IP5x (ATEX 94/9/EC):

Zone 1, Category 2G (Only for flush-mounting in a pressurized enclosure!
Max. permissible excess pressure: 10 mbar continuous.)
Zone 2, Category 3G (Only for flush-mounting in a pressurized enclosure!
Max. permissible excess pressure: 10 mbar continuous.)
Information relevant for export to North America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Conditions of Acceptability

Degree of Protection

UL 60950-01; cUL; IEC/EN 61131-2; CE marking
E208621NWGQ2, NWGQ8UL report applies to both US and Canada–
UL Recognized, certified by UL for use in Canada
The investigated Pollution Degree is: 2
Proper bonding to the end-product main protective earthingtermination is: Required
The following end-product enclosures are required: Fire, Electrical
The unit must be supplied via a SELV source.
The provided Ethernet Connection is only allowed to connect toinhouse networks.
IEC: IP65, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/12

Automation products

Visualization

XV accessories
HPL14012EN
VisualizationXV accessories

Description

For use withPart No.
Article No.

XV-2…
XVH-3…
XV-4…
XVS-4…

XV-1…

Price
See price
list

Std. pack

Information relevant for export toNorth America

LIC-OS-CE30
140405
LIC-OS-CE50-C
140406
LIC-OS-CE50-PP
140408

1 off

UL/CSA certification not required

MEMORY-SD-A1-S
139807MEMORY-CF-A1-S
139528

1 off

UL/CSA certification not required

1 off

UL/CSA certification not required

1 off

UL/CSA certification not required

Windows CE licenses
License for Windows CE 3.0 incl. license label
License for Windows CE 5.0 Core incl. license label
License for Windows CE 5.0 Professional Plus
incl. license label

Memory cards
SD memory card with min. 128 MByte
Without operating system
Compact flash with min. 128 MByte
Without operating system

Compact flash with min. 128 MByte
Windows CE 3.0 preinstalled
Without Windows license (license required(LIC-OS-CE30))
Compact flash with min. 128 MByte
Windows CE 5.0 Core preinstalled
Without Windows license (license required(LIC-OS-CE 50-C))

XV-2…
XVH-3…
XV-4…
XVS-4…
XV-2…
XVH-3…
XV-4…
XVS-4…

OS-FLASH-A1-S
140366OS-FLASH-A1-C
140368

XV license product certificates
License product certificate PLC with license label
COMPACT
License product certificate PLC with license label
LIGHT

License product certificate PLC with license label
SMALL

License product certificate PLC with license label
MEDIUM

License product certificate 40 POINTS
License product certificate 80 POINTS
License product certificate 160 POINTS

XV-1…-B…
XV-1…-D…
XV-2…57BAS…
XV-2…57CNN…
XV-2…57MPN…
XV-4…-57…
XV-4…-84…
XVS-4…-57…
XVS-4…-84…
XV-4…-10…
XV-4…-12…
XV-4…-15…
XVS-4…-10…
XVS-4…-12…
XVS-4…-15…
XV-1…
XV-2…
XVH-3…
XV-4…
XVS-4…
XVM-4...

LIC-PLC-MXP-COMPACT
142581
LIC-PLC-MXP-LIGHT
140388

XVH-3…
XV-4…
XVS-4…

ACCESSORIES-HKS-IP65
139809ACCESSORIES-HKS-IP65-100
139810LIC-PLC-MXP-SMALL
140389LIC-PLC-MXP-MEDIUM
140390LIC-OPT-1ST-LEVEL
140391
LIC-OPT-2ND-LEVEL
140392
LIC-OPT-3RD-LEVEL
140393

Additional fixing brackets
4 mounting brackets with grub screw
100 mounting brackets with grub screw

2010 CA08103002Z-EN

www.eaton.com

Visualization

Automation products

14/13

XV accessories
HPL14013EN
For use withPart No.
Article No.

Device accessories as replacement for insulated
devices:
8 mounting brackets with grub screw for flush
mounting
1 sealing profile for flush mounting device
1 power supply plug
1 touch pen
Device accessories as replacement for5.7” devices with resistive touch and metal front:
4 mounting brackets with grub screw for flush mounting
1 sealing profile for flush mounting device
1 power supply plug
1 touch pen
Device accessories as replacement for5.7” devices with infrared touch and standard front:
4 mounting brackets with grub screw for flush
mounting
1 sealing profile for flush mounting device
1 power supply plug

XV-1…
XV-2…

ACCESSORIES-TP-57-KG-1
139837

XVH-330…
XV-432-57…
XV-450-57…
XVS-430-57…
XVS-450-57…

ACCESSORIES-TP-57-RES-1
139827

XVH-34…
XV-442-57…
XV-460-57…
XVS-440-57…
XVS-460-57…

ACCESSORIES-TP-57-IR-11)
139828Device accessories as replacement for 5.7” devices
with infrared touch and stainless steel front:
8 mounting brackets with grub screw for flush
mounting
1 seal for flush mounting device
1 power supply plug
Device accessories as replacement for 10.4” and12.1” devices with resistive touch:
6 mounting brackets with grub screw for flush
mounting
1 sealing profile for flush mounting device
1 power supply plug
1 touch pen
Device accessories as replacement for 10.4”, 12.1”
and 15” devices with infrared touch:
8 mounting brackets with grub screw for flush
mounting
1 sealing profile for flush mounting device
1 power supply plug

XVH-340-57…-50
XV-442-57…-50
XV-460-57…-50

ACCESSORIES-TP-57-EST-1
139830

XV-430-10…
XV-430-12…
XVS-430-10…
XVS-430-12…

ACCESSORIES-TP-10/12RES-1
139831

XV-440-10…
XV-440-12…
XV-440-15…
XVS-440-10…
XVS-440-12…
XVS-460-15…
XP-7…-10…
XP-7…-12…
XP-7…-15…

ACCESSORIES-TP-15-IR-1
139843

XV-4…

COM-MPB1-TP
139850COM-MPB2-TP
139847
COM-DPM-MC2
139853
COM-PDP-TP
139849
COM-EIB2-TP
139852

1 off

UL/CSA certification refer to main
component information

XVM-4…

KETOP-WB095
139999KETOP-CB211
140002JB001/ASET
140003
KETOP-TT050-MV1
140000KETOP-TT100-MV1
140001KETOP-TT150-MV1
140005KETOP-BC001
140004

1 off

UL/CSA certification not required

1 off

–

1 off

–

1 off

UL/CSA certification not required

Description

Price
See price
list

Std. pack

Information relevant for export toNorth America

1 off

UL/CSA certification not requiredStandard accessories
Supplied as standard with devices

Communication cards
Protocols for communication cards￫ Page 14/14
Multiple protocol card
Multiple protocol card MPIPROFIBUS-DP master (12 MBaud)PROFIBUS-DP slave (12 MBaud)EIB (3rd release)

UL/CSA certification not required

Accessories for Mobile Panel
Wall mount with cable holder
Switch box outside control panel IP65
Switch box for installation inside control panel
Connection cable, 5 m
Connection cable, 10 m
Connection cable, 15 m
Jumper plug for emergency switching off
Spare keys, 2 off
Notes

XVM-410…
XVM-450…

KETOP-EKY001
140006

1) XVH-340-57CAN-1-50, XV-442-57CQB-1-50 and XV-460-57TQB-1-50 have a special seal.

2010 CA08103002Z-EN

www.eaton.com

14/14

Automation products

Visualization

HMI, HMI-PLC

Engineering
VisualizationHMI, HMI-PLC

Protocols for communication cards for panel XV400
For panels XV400, communications protocols are available through optional plug-in communication cards (No license products required):
Excerpt From the most common protocols, which are available for XV400 devices through optional plug-in communication cards:
ProtocolEIB (3rd release)
Matsushita FP series
Mitsubishi A series/F series
Moeller Suconet K
Omron C, H, or K series
PROFIBUS-DP master (12 Mbaud)
PROFIBUS-DP slave (12 Mbaud)
Siemens MPI
Telemecanique Unitelway new

Required communication cards for XV400
COM-EIB2-TP
COM-MPB1-TP / COM-MPB2-TP
COM-MPB1-TP / COM-MPB2-TP
COM-MPB1-TP / COM-MPB2-TP
COM-MPB1-TP / COM-MPB2-TP
COM-DPM-MC2
COM-PDP-TP
COM-MPB2-TP
COM-MPB1-TP / COM-MPB2-TP

To inquire about further protocols, contact your vendor.

Licensing for Panel XV…
The panels XV100, XV200, XVH300, XV400, XVS400 and XVM400 are supplied with license points saved to the device. License points are required to be able toperform certain functions with the device:• XSOFT-CODESYS-2 runtime for the PLC function (not possible with XV-102-A…,XVH300 and XVM400)• Runtime for the visualization (GALILEO or EPAM)• Tools (e. g. CE Telediag, S7 PG Router)• Communication (e.g. Ethernet, CANopen, Siemens MPI)
Number of license points supplied with standard devices:• 140 license points: XV100 (without PLC function), XV200, XVH300, XV400, XVS400• 240 license points: XV100 with PLC function• 260 licence points: XVM400
If the device does not contain enough license points for the required functions or to add the PLC function to the HMI, you must purchase additional license points.
To do this you need one or more license product certificates. The following are available:• License product certificates for the PLC function: To enable the PLC function (XSOFT-CODESYS-2) special license product certificates are required. These
contain a license label for the device type, which must be applied to the device fir legal reasons.
• License product certificates for visualization, communication and tools

Determining required license points
For the visualization and tools and communication features used, add the license points required for each function. Communication connections to several
devices with the same protocol must be counted only once. From this total, subtract the points already contained on the devices (e.g. 140 points).
The difference is the number of license points that you must install for communication protocols and tools through license product certificates.
Table: Required license points for runtime and tools
Visualization/Tools

Required on-board interface

Licence points

GALILEO-Runtime
EPAM runtime
XSOFT-CODESYS-2 runtime(PLC function)
XSOFT-CODESYS-2 runtime (PLC
function and TargetVisu function)
CE Telediag
S7 PG Router
CAN Monitor
Domain Server

None
None
None

100
100
100

None

200

RS232
Ethernet and PROFIBUS
CAN
Ethernet

40
80
0
80

2010 CA08103002Z-EN

www.eaton.com

Visualization

Automation products

14/15

Visualization

Table: Required license points for communication through on-board interface
Manufacturer

PLC

ProtocolEaton

XV with PLC function
XV with PLC function
CANopen, master
CANopen, PDO
CANopen, SDO
XV200 DP master(1.5 MBaud)
XV100/XVS400 DP master(1.5 Mbaud)
Modbus RTU
Modbus TCP

Required
on-board
interface

Licence points
XSOFT-CODESYS-2

Licence points
GALILEO

Licence points EPAM

Local
Ethernet

0

0
40

0
0

CAN
CAN
CAN
PROFIBUS

0
0
0
40

40
40
-

-

PROFIBUS

0

-

-

0
0
0
-

40
80
40
120
120
40

0
-

CoDeSys
Logix
Logix
MicroLogix

DF1
Ethernet/IP
SLC5/03 MicroLogix DF1

RS232
Ethernet
Ethernet
RS232
Ethernet
RS232

Beckhoff

TwinCAT
BC9000ADS
ADS

Ethernet
Ethernet

-

80
80

-

HIMA
Mitsubishi

HIMatrix
PG-AX/PG-FX

Modbus TCP

Ethernet
RS232

-

80
40

-

Eaton

easy500/easy700
easy800/MFD-Titan
PS4
XC100, XC200
XC100, XC200
PS4

RS232
RS232
RS232
CAN
Ethernet
Suconet K

-

40
40
40
40
40
0

-

EthernetPROFIBUS
PROFIBUS

-

80
40
40

-

S7-200Industrial Ethernet
MPI
PROFIBUS-DP (1.5 Mbaud)
S7 default profile
PPI

PROFIBUS

-

40

-

-

XVM400 keypad

Local

-

40

-

A. Bradley

Siemens

-

S7
S7
S7

Suconet K(to XVH342-57SKS)- Communication currently not available
To inquire about further protocols, contact your vendor.

Communication cards for MICRO PANEL XV400
For panels XV400 further communications protocols are available through optional plug-in communication cards (No license products required).
Depending on the required functionality the following license product certificates are available (￫ XV accessories):

Licensing examples

PointsPointsPointsPointsPointsPointsNo

HMI

Ethernet
CoDeSys

100
40
40
180
-140
40

MPI

HMI application: XV100, XV200, XVS400
Visualization, communication
Visualization (GALILEO)
Communication MPICommunication CoDeSys external
Total
Contained in device on delivery
Additionally required points forcommunication
PLC
PLC application
Required license product certificates:
1 x LIC-OPT-1ST-LEVEL (40 points)

2010 CA08103002Z-EN

www.eaton.com

Automation products

HMI+
S7 PG Router

Ethernet

HMI application: XV100, XV200, XVS400, with additional software S7 PG Router
Visualization, communication
Visualization (GALILEO)
100
PointsCommunication MPI
40
PointsS7 PG Router
80
Points
Total
220
PointsContained in device on delivery-140
PointsAdditionally required points for
80
Pointscommunication
PLC
PLC application
No

Visualization

MPI

14/16

Required license product certificates:
1 x LIC-OPT-2ND-LEVEL (80 points)

100
0
0

PointsPointsPoints

HMI-PLC100-140
0

PointsPointsPoints100

PointsRequired license product certificates:
1 x LIC-PLC-MXP-COMPACT (100 points)

For device versions XV-102-…-PLC license LIC-PLC-MXP-COMPACT is
included with the device as standard (the device therefore has 240 license
points).

2010 CA08103002Z-EN

www.eaton.com

Profibus DP

HMI-PLC Application: XV100
Visualization, communication
Visualization (GALILEO)
Communication HMI-PLC local
Communication CANopen or
PROFIBUS-DP master(XSOFT-CODESYS-2)
Total
Contained in device on delivery
Additionally required points forcommunication
PLC
PLC application

Visualization

PointsPoints80

Points0

Points180-140

PointsPoints40

Points100

Points

14/17

HMI-PLC

Ethernet
Modbus TCP

100
0

CAN

HMI-PLC Application: XV400 10.4“Visualization, communication
Visualization (GALILEO)
Communication HMI-PLC
local
Communication Modbus TCP client(GALILEO)
Communication CANopen(XSOFT-CODESYS-2)
Total
Contained in device ondelivery
Additionally required points forcommunication
PLC
PLC application

Automation products

Required license product certificates:
1 x LIC-OPT-1ST-LEVEL (40 points)
1 x LIC-PLC-MXP-MEDIUM (100 points)

For device versions XV-102-…-PLC license LIC-PLC-MXP-COMPACT is
included with the device as standard (the device therefore has 240 license
points).

Redeeming a license product certificate (XV100, XV200, XV400, XVS400, XVH300)
12

Order the required license product certificate.
Keep the following information available:– Certificate number of license product certificate– The serial number of your device– Your e-mail address
3 On the Micro Innovation website (www.microinnovation.com/license), select menu item “Validate License” and click [Start Licensing].
4 In the new window that opens, enter your certificate number. The license product certificate is associated with a specific device through its serial number.
The website generates a license code, which is immediately shown on the web page.
5 Enter the license code in your device:– On the device, select [Start] > [Programs] > [Control Panel].
– Double-click the Licence icon.
– Enter the license code with the License Administrator tool (Change Licence).
6 Restart the device.
After the device has been restarted the new license points are available.

Redeeming a license product certificate for XVM400 devices
Follow the procedure described in document M002379(Mobile PANEL XVM400), which you can find on the Micro Innovation website under“Downloads”.

2010 CA08103002Z-EN

www.eaton.com

14/18Automation products

Visualization

Visualization

Automation products

HMI(-PLC)

14/19

HMI(-PLC)

VisualizationHMI(-PLC)

Technical data
Display
Screen diagonal/type
Resolution
Visible screen area
Color resolution (grayscale or color)
Contrast ratio
Brightness
Backlight
Lifespan of backlight
Resistive touch protective screen
Operation
Technology
SystemProcessor
Internal memory
DRAM (OS, program and data memory)
NAND FLASH (can be used for data backup)
NVRAM (Retain data)
External memory
SD Memory Card Slot
Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system
Engineering
Visualization software
PLC programming software
Interfaces, communication
Ethernet
USB Host
USB device
Part No.

XV-102-B...-35MQR-10-PLC

XV-102B...-35TQR-10

XV-102-B...-35TQR-10-PLC

XV-102-D...-57TVR-10

XV-102-D...70TWR-10...

3.5" TFT LCD (monochrome)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait
format)
70 mm x 53 mm
32 grey levels
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

3.5" TFT LCD (monochrome)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait
format)
70 mm x 53 mm
32 grey levels
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

3.5" TFT LCD (color)
QVGA (320 × 240 pixels or 240 × 320
pixels in portrait format)
70 mm x 53 mm
64 k Colors
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

3.5" TFT LCD (color)
QVGA (320 × 240 pixels or 240 × 320
pixels in portrait format)
70 mm x 53 mm
64 k Colors
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

5.7" TFT LCD (color)
VGA (640 × 480 pixels or 480 × 640 pixels in
portrait format)
115 mm x 86 mm
64 k Colors
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

7" TFT LCD (color)
WVGA (800 × 480 pixels or 480 × 800
pixels in portrait format)
152 mm x 91 mm
64 k Colors
Normally 300:1
Normally 250 cd/m²
LED, dimmable via software
Normally 40000 h
Touch sensor (glass with membrane)

Resistive touch, 4-conductor

Resistive touch, 4-conductor

Resistive touch, 4-conductor

Resistive touch, 4-conductor

Resistive touch, 4-conductor

Resistive touch, 4-conductor

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

64 MByte
Approx. 128 Byte available–

64 MByte
Approx. 128 Byte available
Approx. 32 kByte available

64 MByte
Approx. 128 Byte available
Approx. 32 kByte available

64 MByte
Approx. 128 Byte available
Approx. 32 kByte available

64 MByte
Approx. 128 Byte available
Approx. 32 kByte available

64 MByte
Approx. 128 Byte available
Approx. 32 kByte available

SDA Specification 1.00

SDA Specification 1.00

SDA Specification 1.00

SDA Specification 1.00

SDA Specification 1.00

SDA Specification 1.00

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

GALILEO/EPAM–GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

100Base-TX/10Base-T–
USB 2.0, not isolated...A0…
...A2…
...A3…

100Base-TX/10Base-T–
USB 2.0, not isolated...B0… ...B2… ...B3… ...B4… ...B5…

100Base-TX/10Base-T–
USB 2.0, not isolated...B0 ...B3 ...B4 ...B5
…
…
…
…
–
●1) –
●1)
–
–
–
●2)
–
–
–
–
–
–
●4) –

100Base-TX/10Base-T
USB 2.0 (1.5 - 12 Mbit/s), not isolated
USB 2.0, not isolated...D0… ...D6… ...D8… ...D6... ...D8...
PLC
PLC
●1)
●1)
●1)
●1)
●1)
–
●2)
–
●2)
–
–
–
●3)
–
●3)
–
●4)
●4)
●4)
●4)

100Base-TX/10Base-T

–
–
–
–

System Port (RS232)CAN
PROFIBUS
RS485
Power supply
Nominal voltage
Permissible voltage

Voltage dips
Input powerProtection against polarity reversal
Fuse
Potential isolation
GeneralFront design
Degree of protection
Front
Rear
Approvals
Approvals
Explosion protection (According to ATEX 94/9/EC)
Applied standards and directives
EMC (relevant for CE)
Explosion protection (relevant for CE)
SafetyProduct standards
WeightEnvironmental Conditions
Temperature
Operation
Storage/transport
Relative humidity
Impact resistanceVibration
Notes

2010 CA08103002Z-EN

XV-102-A...-35MQR-10

www.eaton.com

–
–
●3)
–

●1)
–
–
–

...A4…

...A5…

100Base-TX/10Base-T–
USB 2.0, not isolated...B0… ...B3… ...B4… ...B5… ...B6… ...B8…

–
–
–
●4)

●1)
●2)
–
–

–
–
–
–

●1)
–
–
–

–
–
–
●4)

●1)
●2)
–
–

–
●2)
–
●4)

–
–
●3)
●4)

–
–
–
–

–
–
●3)
–

●1)
–
–
–

–
–
–
●4)

●1)
●2)
–
–

...B6
…
–
●2)
–
●4)

...B8
…
–
–
●3)
●4)

USB 2.0, not isolated...D0… ...D6… ...D8… ...D6...
PLC
●1)
●1)
●1)
●1)
–
●2)
–
●2)
–
–
●3)
–
–
●4)
●4)
●4)

...D8...
PLC
●1)
–
●3)
●4)

24 V DC SELV (safety extra low voltage)
24 V DC SELV (safety extra low voltage)
R.m.s.: 19.2 – 30.0 V DC (rated operating voltage -20 %/+25 %)Absolute with ripple: 18.0 – 31.2 V DC
Battery operation: 18.0 – 31.2 V DC (rated operating voltage -25 %/+30 %)35 V DC for a duration of < 100 ms
10 ms from nominal voltage (24 V DC), 5 ms from undervoltage (20.4 V DC)
Max. 5 W
Max. 5 W
Yes
Yes
Yes (fuse not accessible)
Yes (fuse not accessible)
No
No

24 V DC SELV (safety extra low voltage) 24 V DC SELV (safety extra low voltage)
R.m.s.: 19.2 – 30.0 V DC (rated operating voltage -20 %/+25 %)Absolute with ripple: 18.0 – 31.2 V DC
Battery operation: 18.0 – 31.2 V DC (rated operating voltage -25 %/+30 %)35 V DC for a duration of < 100 ms
10 ms from nominal voltage (24 V DC), 5 ms from undervoltage (20.4 V DC)
Max. 5 W
Max. 5 W
Yes
Yes
Yes (fuse not accessible)
No
No

24 V DC SELV (safety extra low voltage)

24 V DC SELV (safety extra low voltage)

Max. 10 W
Yes

Max. 10 W
Yes

No

No

Standard membrane (fully enclosed)Standard membrane (fully enclosed)Standard membrane (fully enclosed)Standard membrane (fully enclosed)Standard membrane (fully enclosed)Standard membrane (fully enclosed)

IP65
IP20

IP65
IP20

IP65
IP20

IP65
IP20

IP65
IP20

IP65
IP20

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.3 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.3 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.3 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.3 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.6 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.6 kg

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-61) RS232, not isolated (D-sub 9-pin, UNC)

3) PROFIBUS, not isolated, max. 1.5 MBit/s (D-sub 9-pin socket, UNC)

2) CAN, not isolated (D-sub 9-pin, UNC)

4) RS485, not isolated (D-sub 9-pin, UNC)

2010 CA08103002Z-EN

www.eaton.com

14/20Automation products

Visualization

HMI-PLC XV200
VisualizationHMI-PLC XV200

XV-230-57CNN-1-10
Display
Screen diagonal/type
Resolution
Visible screen area
Color resolution (grayscale or color)
Contrast ratio
Brightness
Backlight
Lifespan of backlight
Resistive touch protective screen

XV-230-57MPN-1-10

XV-232-57BAS-1-10

5.7" FSTN LCD (monochrome display)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait format)
115 mm x 86 mm
256 grey levels
256 grey levels
256 grey levels
Normally 10:1
Normally 10:1
Normally 10:1
Normally 150 cd/m²
1 x CCFL, dimmable via software
Normally 50000 h
Touch sensor (glass with membrane)

XV-252-57CNN-1-10

XV-252-57MPN-1-10

5.7" CSTN LCD (Color display)

256 colors
Normally 35:1

256 colors
Normally 35:1

32 MByte

32 MByte

Operation

Technology
SystemProcessor
Internal memory
DRAM (OS, program and data
memory)FLASH (can be used for data
backup)
NVRAM (Retain data)
External memory
CF slot
Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system
Engineering
Visualization software
PLC programming software
Interfaces, communication
Ethernet
System port
CAN
PROFIBUS

USB device
Power supply
Nominal voltage
Permissible voltage

Voltage dips
Input powerProtection against polarity reversal
Fuse
Potential isolation2010 CA08103002Z-EN

www.eaton.com

Resistive touch, 4-conductor
RISC, 32-bit, 200 MHz
32 MByte

32 MByte

32 MByte

Approx. 1.5 MByte available
Approx. 100 Byte available
1 x CompactFlash card type I for operating system, programs and data
Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

100Base-TX/10Base-T––
CAN, not isolated–(D-sub 9-pin, UNC)–PROFIBUS,
not isolated,max. 1.5 MBit/s(D-sub 9-pin socket,
UNC)
USB 1.1, not isolated

RS232, not isolated (D-sub 9-pin, UNC)–
CAN, not isolated(D-sub 9-pin, UNC)––

24 V DC SELV (safety extra low voltage)
R.m.s.: 19.2 – 30.0 V DC (rated operating voltage -20 %/+25 %)Absolute with ripple: 18.0 – 31.2 V DC
Battery operation: 18.0 – 31.2 V DC (rated operating voltage -25 %/+30 %)35 V DC for a duration of < 100 ms
20 ms from nominal voltage (24 V DC), 10 ms from undervoltage (20.4 V DC)
Max. 8 W
Max. 8 W
Max. 8 W
Max. 8 W
Yes
Yes
Yes
Yes
Yes (zero
Yes (zero
Yes (zero
Yes (zero
maintenance)
maintenance)
maintenance)
maintenance)
No
No
No
No

–
PROFIBUS,
not isolated,max. 1.5 MBit/s(D-sub 9-pin, UNC)

Max. 8 W
Yes
Yes (zero
maintenance)NoVisualization

Automation products

14/21

HMI-PLC XV200

GeneralFront design
Degree of protection
Front
Rear
Approvals
Approvals
Explosion protection(According to ATEX 94/9/EC)
Applied standards and directives
EMC (relevant for CE)
Explosion protection(relevant for CE)
SafetyProduct standards
WeightEnvironmental Conditions
Temperature
Operation
Storage/transport
Relative humidity
Impact resistanceVibration

XV-230-57CNN-1-10

XV-230-57MPN-1-10

XV-232-57BAS-1-10

XV-252-57CNN-1-10

XV-252-57MPN-1-10

Standard
membraneStandard
membraneStandard
membraneStandard
membraneStandard
membrane

IP65
IP20

IP65
IP20

IP65
IP20

IP65
IP20

IP65
IP20

cUL
cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL

cUL

cUL

EN 61000-6-2, EN 61000-6-3, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 0.7 kg
Approx. 0.7 kg

EN 60950/UL 60950

EN 60950/UL 60950

EN 60950/UL 60950

Approx. 0.7 kg

Approx. 0.7 kg

Approx. 0.7 kg

0 – 50°C
0 – 50°C-20 – 60°C
-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-27
To IEC 68-2-6
To IEC 68-2-6

0 – 50°C-20 – 60°C

0 – 50°C-20 – 60°C

0 – 50°C-20 – 60°C

To IEC 68-2-27
To IEC 68-2-6

To IEC 68-2-27
To IEC 68-2-6

To IEC 68-2-27
To IEC 68-2-6

2010 CA08103002Z-EN

www.eaton.com

14/22

Automation products

Visualization

HMI-PLC MFD4VisualizationHMI-PLC MFD4

MFD4-5-XRC-30
Display
Screen diagonal/type
Resolution
Visible screen area
Color resolution (grayscale or color)
Contrast ratio
Brightness
Backlight
Lifespan of backlight
Resistive touch protective screen
Operation
Technology
SystemProcessor
Internal memory
DRAM (OS, program and data memory)
FLASH (can be used for data backup)
NVRAM (Retain data)
External memory
Slot
Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system
Engineering
Visualization software
PLC programming software
Interfaces, communication
Ethernet
System port
CAN
PROFIBUS
USB device
Power supply
Nominal voltage
Permissible voltage
Voltage dips
Input powerProtection against polarity reversal
Fuse
Potential isolation
GeneralEnclosure
Front design
Degree of protection
Front
Rear
Approvals
Approvals
Explosion protection (According to ATEX 94/9/EC)
Applied standards and directives
EMC (relevant for CE)
Explosion protection (relevant for CE)
SafetyProduct standards
WeightEnvironmental Conditions
Temperature
Operation
Storage/transport
Relative humidity
Impact resistanceVibration2010 CA08103002Z-EN

www.eaton.com

5.7" TFT Color display
QVGA (320 x 240 pixels)
118 mm x 89 mm
32 K
Normally 350:1
Normally 500 cd/m²
1 x CCFL, dimmable via software
Normally 50000 h
Touch sensor (glass with membrane)
Resistive touch, 4-conductor
Risc, 32-bit 130 MHz
4 MByte
512 kByte
32 kByte
1 x MMC for operating system, programs and data
Lithium, 1/2AA(3.6V)
Normally 5 years
Windows CE
XSOFT-CODESYS-2
XSOFT-CODESYS-2
100Base-TX/10Base-T
RS232, not isolated (D-sub 9-pin, UNC)
CAN, galvanically isolated (D-sub 9-pin, UNC)––
24 V DC SELV (safety extra low voltage)
20.4 to 28.8 V DC, residual ripple ≤ 5 %Duration of dip to IEC/EN 61131-2: 10 ms
Max. 10 W
Yes
No
No
Metal
Seamless membrane
IP65
IP20
LR, GL, DNV,BV, ABS
II 3D Ex II T85°C IP5x:
Zone 22, Category 3D
EN 61000-6-2, EN 61000-6-3, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950
EN 50178, EN 61131-2
Approx. 1.3 kg

0 – 50°C- 20 to 70 °C
10 – 95 %, non-condensing
15 g/11 ms
10 to 57 Hz ± 0.075 mm; 57 to 150 Hz ± 1.0 g

Visualization

Automation products

14/23

HMI Mobile Panel
VisualizationHMI Mobile Panel

XVM-430-65TVB-1-11

XVM-450-65TVB-1-11

XVM-410-65TVB-1-11

Screen diagonal/type6.5" TFT LCD

6.5" TFT LCD

6.5" TFT LCD

Resolution

VGA (640 x 480 pixel)

VGA (640 x 480 pixel)

VGA (640 x 480 pixel)

Visible screen area

132 mm x 99 mm

132 mm x 99 mm

132 mm x 99 mm

Color resolution (grayscale or color)

64k Colors

64k Colors

64k Colors

Backlight

2 CCFT cold cathode tubes

2 CCFT cold cathode tubes

2 CCFT cold cathode tubes

Lifespan of backlight

Normally 50000 h

Normally 50000 h

Normally 50000 h

Resistive touch protective screen

Touch sensor(glass with membrane)

Touch sensor(glass with membrane)

Touch sensor(glass with membrane)

Technology

Resistive touch

Resistive touch

Resistive touch

Keypad31 membrane keys with tactile
feedback, 4 status LEDs
2 acknowledgement keys (3-stage,
2-circuit), externally wired
Emergency switching off button(2-circuit), externally wired

31 membrane keys with tactile
feedback, 4 status LEDs
2 acknowledgement keys (3-stage,
2-circuit), externally wired
Emergency switching off button(2-circuit), externally wired
Keyswitch (3-position),internally wired
Electronic hand wheel, internallywired

31 membrane keys with tactile
feedback, 4 status LEDs
2 acknowledgement keys (3-stage,
2-circuit), externally wired
Keyswitch (3-position),internally wired
Electronic hand wheel,internally wired

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

DRAM (OS, program and data memory)

Min. 64 MByte

Min. 64 MByte

Min. 64 MByte

FLASH

Min. 64 MByte

Min. 64 MByte

Min. 64 MByte

NVRAM (Retain data)

–

–

–

Operating system

Windows CE

Windows CE

Windows CE

GALILEOGALILEOGALILEO

Ethernet

100Base-TX/10Base-T

100Base-TX/10Base-T

100Base-TX/10Base-T

RS232

RS232-C

RS232-C

RS232-C

USB Host

USB 1.1 (12 Mbit/s)

USB 1.1 (12 Mbit/s)

USB 1.1 (12 Mbit/s)

Nominal voltage

24 V DC

24 V DC

24 V DC

Permissible voltage

R.m.s.: 19.2 – 30.0 V DC

R.m.s.: 19.2 – 30.0 V DC

R.m.s.: 19.2 – 30.0 V DC

Voltage dips

≦ 10 ms≦ 10 ms≦ 10 ms

Input power

9.6 W

9.6 W

9.6 W

Standard membrane
Membrane keypad with tactile
feedback

Standard membrane
Membrane keypad with tactile
feedback

Standard membrane
Membrane keypad with tactile
feedback

Front

IP65

IP65

IP65

Rear

IP65

IP65

IP65

cUL (UL508)

cUL (UL508)

cUL (UL508)

Product standards

EN 50178, EN 61131-2

EN 50178, EN 61131-2

EN 50178, EN 61131-2

WeightApprox. 1.3 kg

Approx. 1.3 kg

Approx. 1.3 kg

Display

Operation

Operating elements

SystemProcessor
Internal memory

Engineering
Visualization software
Interfaces, communication

Power supply

GeneralFront design
Degree of protection

Approvals
Approvals
Applied standards and directives

Environmental Conditions
Temperature
Operation

0 – 50°C

0 – 50°C

0 – 50°C

Storage/transport-20 – 70°C

-20 – 70°C

-20 – 70°C

Relative humidity

5 - 95%, non-condensing

5 - 95%, non-condensing

5 - 95%, non-condensing

Shock (IEC 60068-2-27)

25 g/11ms

25 g/11ms

25 g/11ms

Vibration (IEC 60068-2-6)

10 Hz ≧ f > 57 Hz with 0.15 mm
9 Hz ≧ f > 150 Hz with 2 g

10 Hz ≧ f > 57 Hz with 0.15 mm
9 Hz ≧ f > 150 Hz with 2 g

10 Hz ≧ f > 57 Hz with 0.15 mm
9 Hz ≧ f > 150 Hz with 2 g

2010 CA08103002Z-EN

www.eaton.com

14/24

Automation products

Visualization

Visualization

Automation products

HMI XVH300

14/25

HMI XVH300

VisualizationHMI XVH300

XVH-340-57BAS-1-10
Display
Screen diagonal/type
Resolution
Visible screen area
Color resolution (grayscale or color)
Contrast ratio
Brightness
Backlight
Lifespan of backlight
Resistive touch protective screen

XVH-340-57CAN-1-10

5.7" CSTN LCD (color)5.7" CSTN LCD (color)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait format)
115 mm x 86 mm
115 mm x 86 mm
256 colors
256 colors
Normally 35:1
Normally 35:1
Normally 150 cd/m²
Normally 150 cd/m²
1 x CCFL, dimmable via software
Normally 50000 h
Normally 50000 h––

XVH-340-57MPI-1-10

XVH-342-57SKS-1-10

5.7" CSTN LCD (color)5.7" CSTN LCD (color)5.7" CSTN LCD (color)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait format)
115 mm x 86 mm
115 mm x 86 mm
256 colors
256 colors
Normally 35:1
Normally 35:1
Normally 150 cd/m²
Normally 150 cd/m²
1 x CCFL, dimmable via software
Normally 50000 h
Normally 50000 h––

115 mm x 86 mm
256 colors
Normally 35:1
Normally 150 cd/m²
Normally 50000 h–

XVH-340-57CAN-1-50

XVH-330-57BAS-1-10

XVH-330-57CAN-1-10

XVH-330-57MPI-1-10

5.7" CSTN LCD (color)5.7" CSTN LCD (color)5.7" CSTN LCD (color)

115 mm x 86 mm
256 colors
Normally 35:1
Normally 150 cd/m²

115 mm x 86 mm
256 colors
Normally 35:1
Normally 150 cd/m²

115 mm x 86 mm
256 colors
Normally 35:1
Normally 150 cd/m²

Normally 50000 h
Touch sensor(glass with membrane)–

Normally 50000 h
Touch sensor(glass with membrane)–

Infra-red touch protective screen
Operation
Technology
SystemProcessor
Internal memory
DRAM (OS, program and data memory)
FLASH (can be used for data backup)
NVRAM (Retain data)
External memory
CF slot
Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system
Engineering
Visualization software
PLC programming software
Interfaces, communication
Ethernet
System port

Laminated safety glass, non-reflective

Laminated safety glass, non-reflective

Normally 50000 h
Touch sensor(glass with membrane)–

Infra-red touch, 47 × 31 logic channels

Infra-red touch, 47 × 31 logic channels

Resistive touch, 4-conductor

Resistive touch, 4-conductor

Resistive touch, 4-conductor

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

RISC, 32-bit, 200 MHz

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

64 MByte
Approx. 1.5 MByte available–

1 x CompactFlash card type I/II for operating system, programs and data

1 x CompactFlash card type I/II for operating system, programs and data

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–GALILEO/EPAM–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

100Base-TX/10Base-T–

Com Port

–

–

–

–

–

–

–

CAN

–

–

CAN, galvanically isolated(D-sub 9-pin, UNC)–––

CAN, galvanically isolated(D-sub 9-pin, UNC)––PROFIBUS

CAN, isolated(Sub-D 9-pin plug)–

100Base-TX/10Base-T
RS232 (Sucom A), not isolated(Sub-D 9.pin plug, UNC)
RS485 (Suconet K), isolated(Sub-D 9-pin socket, UNC)–

USB device
Power supply
Nominal voltage
Permissible voltage

USB 1.1, not isolated

USB 1.1, not isolated

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (rated operating voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from nominal voltage (24 V DC), 2 ms from undervoltage (20.4 V DC)
Max. 16 W (normally 12 W)
Max. 16 W (normally 12 W)
Max. 16 W (normally 12 W)
Yes
Yes
Yes
Yes (fuse not accessible)
No (0V connection to housing potential)

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (rated operating voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from nominal voltage (24 V DC), 2 ms from undervoltage (20.4 V DC)
Max. 21 W (normally 17 W)
Max. 16 W (normally 12 W)
Max. 16 W (normally 12 W)
Yes
Yes
Yes
Yes (fuse not accessible)
No (0V connection to housing potential)

Max. 16 W (normally 12 W)
YesMax. 16 W (normally 12 W)
Yes

Voltage dips
Input powerProtection against polarity reversal
Fuse
Potential isolation2010 CA08103002Z-EN

www.eaton.com

PROFIBUS galvanically isolated,max. 1.5 MBit/s (D-sub 9-pin
socket, UNC)––PROFIBUS galvanicallyisolated, max. 1.5 MBit/s(D-sub 9-pin socket, UNC)

2010 CA08103002Z-EN

www.eaton.com

14/26

Automation products

Visualization

Visualization

Automation products

HMI XVH300

GeneralFront design
Degree of protection
Front

Rear
Approvals
Approvals
Explosion protection(According to ATEX 94/9/EC)

Applied standards and directives
EMC (relevant for CE)
Explosion protection (relevant for CE)
SafetyProduct standards
WeightEnvironmental Conditions
Temperature
Operation
Storage/transport
Relative humidity
Impact resistanceVibration2010 CA08103002Z-EN

www.eaton.com

14/27

HMI XVH300

XVH-340-57BAS-1-10

XVH-340-57CAN-1-10

XVH-340-57MPI-1-10

XVH-342-57SKS-1-10

XVH-340-57CAN-1-50

XVH-330-57BAS-1-10

XVH-330-57CAN-1-10

XVH-330-57MPI-1-10

Standard front with standard
membraneStandard front with standard
membraneStandard front with standard
membraneStandard front with standard
membraneSatin-finish brushed stainlesssteelStandard front with standard
membrane (fully laminated)Standard front with standard
membrane (fully laminated)Standard front with standard
membrane (fully laminated)

IP65
Additional mounting bracket set
required for flush mounting(￫ Accessories)
IP20

IP65
Additional mounting bracket set
required for flush mounting(￫ Accessories)
IP20

IP65
Additional mounting bracket set
required for flush mounting(￫ Accessories)
IP20

IP65
Additional mounting
bracket set required for flush
mounting (￫ Accessories)
IP20

IP65, IP69K
Observe installation
instructions to IP69K

IP65
Additional mounting
bracket set required for flush
mounting (￫ Accessories)
IP20

IP65
Additional mounting
bracket set required for flush
mounting (￫ Accessories)
IP20

IP65
Additional mounting
bracket set required for flush
mounting (￫ Accessories)
IP20

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket set
required for flush mounting(￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket set
required for flush mounting(￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket set
required for flush mounting(￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket
set required for flush
mounting (￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D

cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket
set required for flush
mounting (￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket
set required for flush
mounting (￫ Accessories)cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket
set required for flush
mounting (￫ Accessories)

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.9 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 2.1 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

EN 61000-6-2, EN 61000-6-3,
EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1,
EN 13463
EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 1.7 kg

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 - 95%, non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C

0 – 50°C-20 – 60°C

0 – 50°C-20 – 60°C

0 – 50°C-20 – 60°C

To IEC 68-2-27
To IEC 68-2-6

To IEC 68-2-27
To IEC 68-2-6

To IEC 68-2-27
To IEC 68-2-6

To IEC 68-2-27
To IEC 68-2-6

IP20

2010 CA08103002Z-EN

www.eaton.com

14/28Automation products

Visualization

Visualization

Automation products

HMI-PLC XV400

14/29

HMI-PLC XV400

VisualizationHMI-PLC XV400

XV-44257CQB-1-10
XV-44257CQB-1-20

XV-44257CQB-1-50

XV-43257CQB-1-10

XV-460-57TQB1-10

XV-460-57TQB1-50

XV-450-57TQB1-10

XV-460-84TVB1-10

XV-440-10TVB1-10
XV-440-10TVB1-20

XV-440-10TVB1-50

XV-430-10TVB1-10

XV-440-12TSB1-10
XV-440-12TSB1-20

XV-440-12TSB1-50

XV-430-12TSB1-10

XV-460-15TXB1-10

XV-460-15TXB1-50

5.7" CSTN LCD 5.7" CSTN LCD 5.7" CSTN LCD 5.7" TFT LCD(color)(color)(color)(color)QVGA (320 × 240 pixels or 240 × 320 pixels in portrait format)

5.7" TFT LCD(color)5.7" TFT LCD(color)8.4" TFT LCD
10.4" TFT LCD
10.4" TFT LCD
10.4" TFT LCD(color)(color)(color)(color)VGA (640 × 480 pixels or 480 × 640 pixels in portrait format)

12.1" TFT LCD(color)SVGA (800 ×
600 pixels or
600 × 800 pixels
in portrait
format)
246 mm x
185 mmAdjustable:
65536 or256 colors
Normally 350:1

12.1" TFT LCD(color)SVGA (800 ×
600 pixels or
600 × 800 pixels
in portrait
format)
246 mm x
185 mmAdjustable:
65536 or256 colors
Normally 350:1

12.1" TFT LCD(color)SVGA (800 ×
600 pixels or
600 × 800 pixels
in portrait
format)
246 mm x
185 mmAdjustable:
65536 or256 colors
Normally 350:1

15" TFT LCD(color)XGA (1024 x
768 pixel)

15" TFT LCD(color)XGA (1024 x 768
pixel)

Color resolution (grayscale or color)

115 mm x
86 mm
256 colors

115 mm x
86 mm
256 colors

115 mm x
86 mm
256 colors

Contrast ratio

Normally 35:1

Normally 35:1

Normally 35:1

115 mm x
86 mm
Adjustable:
65536 or256 colors
Normally 400:1

115 mm x
86 mm
Adjustable:
65536 or256 colors
Normally 400:1

115 mm x
86 mm
Adjustable:
65536 or256 colors
Normally 400:1

170 mm x
128 mmAdjustable:
65536 or256 colors
Normally 400:1

211 mm x
158 mmAdjustable:
65536 or256 colors
Normally 350:1

211 mm x
158 mmAdjustable:
65536 or256 colors
Normally 350:1

211 mm x
158 mmAdjustable:
65536 or256 colors
Normally 350:1

304 mm x
228 mmAdjustable:
65536 or256 colors
Normally 350:1

304 mm x
228 mmAdjustable:
65536 or256 colors
Normally 350:1

Brightness

Normally
150 cd/m²
1 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
150 cd/m²
1 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
350 cd/m²
LED, dimmable
via software

Normally
350 cd/m²
LED, dimmable
via software

Normally
350 cd/m²
LED, dimmable
via software

Normally
40000 h–Normally
40000 h–Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 h–Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Normally
40000 hTouch sensor(glass withmembrane)–

Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 h–Laminatedsafety glass,non-reflecting

Normally
150 cd/m²
1 x CCFL,
dimmable via
softwareNormally
50000 hTouch sensor(glass withmembrane)–

Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 hTouch sensor(glass withmembrane)–

Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
400 cd/m²
4 x CCFL,
dimmable via
softwareNormally
50000 h–Normally
400 cd/m²
4 x CCFL,
dimmable via
softwareNormally
50000 h–Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Normally
350 cd/m²
2 x CCFL,
dimmable via
softwareNormally
50000 hTouch sensor(glass withmembrane)–Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Laminatedsafety glass,non-reflecting

Infra-redtouch,
47 x 31 logic
channels

Infra-redtouch,
47 x 31 logic
channels

Resistive
touch,
4-conductor

Infra-redtouch,
47 x 31 logic
channels

Infra-redtouch,
47 x 31 logic
channels

Infra-redtouch,
63 x 47 logic
channelInfra-redtouch,
79 x 59 logic
channels

Infra-redtouch,
79 x 59 logic
channels

Resistive
touch,
4-conductor

Infra-redtouch,
95 x 71 logic
channels

Infra-redtouch,
95 x 71 logic
channels

Resistive
touch,
4-conductor

Infra-redtouch,
107 x 83 logic
channels

Infra-red touch,
107 x 83 logic
channels

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs anddata

Display
Screen diagonal/type
Resolution

Visible screen area

Backlight
Lifespan of backlight
Resistive touch protective screen
Infra-red touch protective screen
Operation
Technology

Resistive
touch,
4-conductor

SystemProcessor

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

DRAM(OS, program and data memory)
FLASH (can be used for data backup)

64 MByte

64 MByte

Approx. 1.5 MByte available

Approx. 1.5 MByte available

NVRAM (Retain data)

Approx. 32 kByte available

Approx. 32 kByte available

Internal memory

External memory
CF slot

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

1 × Compact
Flash card, type
I/II for operating
system,programs anddata

2 × Compact
Flash card, type
I/II for operating
system,programs and
data

Zero
Zero
maintenancemaintenance
Normally 10 years

ZeromaintenanceZeromaintenanceZeromaintenanceZeromaintenance

Zero
Zero
maintenancemaintenance
Normally 10 years

ZeromaintenanceZeromaintenanceZeromaintenanceZeromaintenanceZeromaintenanceZeromaintenanceZeromaintenanceWindows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Windows CE

Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system

Windows CE

Windows CE

Engineering
Visualization software

GALILEO/EPAMGALILEO/EPAM

PLC programming softwareXSOFT-CODESYS-2

XSOFT-CODESYS-2

Ethernet

100Base-TX/10Base-T

100Base-TX/10Base-T

System port
CAN
PROFIBUS

RS232, not isolated (D-sub 9-pin, UNC)
CAN, galvanically isolated (D-sub 9-pin, UNC)
–
–
–

–

RS232, not isolated (D-sub 9-pin, UNC)
CAN, galvanically isolated (D-sub 9-pin, UNC)
–
–
–

–

–

–

–

–

–

USB Host
USB device
Slots for communication cards

USB 2.0 (1.5/12 MBit/s), not isolated
USB 1.1, not isolated
1
1
1

1

USB 2.0 (1.5/12 MBit/s), not isolated
USB 1.1, not isolated
1
2
2

2

2

2

2

2

2

Interfaces, communication2010 CA08103002Z-EN

www.eaton.com

–

1

–

1

2010 CA08103002Z-EN

www.eaton.com

14/30Automation products

Visualization

Visualization

Automation products

HMI-PLC XV400

14/31

HMI-PLC XV400

XV-44257CQB-1-10
XV-44257CQB-1-20

XV-44257CQB-1-50

XV-43257CQB-1-10

XV-460-57TQB1-10

XV-460-57TQB1-50

XV-450-57TQB1-10

XV-460-84TVB1-10

XV-440-10TVB1-10
XV-440-10TVB1-20

XV-440-10TVB1-50

XV-430-10TVB1-10

XV-440-12TSB1-10
XV-440-12TSB1-20

XV-440-12TSB1-50

XV-430-12TSB1-10

XV-460-15TXB1-10

XV-460-15TXB1-50

Max. 24 W(Normally 13 W)
Yes

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (rated operating voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from
10 ms from nominal voltage (24 V DC), 5 ms from undervoltage (20.4 V DC)
rated operating
voltage(24 V DC),
2 ms fromundervoltage(20.4 V DC)
Max. 26 W
Max. 32 W
Max. 32 W
Max. 32 W
Max. 32 W
Max. 32 W(Normally 15 W) (Normally 14 W) (Normally 14 W) (Normally 14 W) (Normally 14 W) (Normally 14 W)
Yes
Yes
Yes
Yes
Yes
Yes

Max. 32 W(Normally 14 W)
YesMax. 44 W(Normally 28 W)
YesMax. 44 W(Normally 28 W)
YesPower supply
Nominal voltage
Permissible voltage

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (rated operating voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from nominal voltage (24 V DC), 2 ms from undervoltage (20.4 V DC)

Voltage dips

Input powerProtection against polarity reversal

Max. 24 W(Normally 13 W)
Yes

Max. 24 W(Normally 13 W)
Yes

Max. 24 W(Normally 13 W)
Yes

Max. 24 W(Normally 13 W)
Yes

Max. 24 W(Normally 13 W)
Yes

Fuse
Potential isolation
GeneralYes (fuse not accessible)
No (0V connection to housing potential)

Front designStandard front
with standard
membraneSatin-finish
brushed stainless steelStandard front
with standard
membrane (fullylaminated)Standard front
with standard
membraneSatin-finish
brushed stainless steelStandard front
with standard
membrane (fullylaminated)Standard front
with standard
membraneStandard front
with standard
membraneSatin-finish
brushedstainless steelStandard front
with standard
membrane (fullylaminated)Standard front
with standard
membraneSatin-finish
brushedstainless steelStandard front
with standard
membrane (fullylaminated)Standard front
with standard
membraneSatin-finish
brushedstainless steel

Front

IP65

IP65, IP69K

IP65

IP65

IP65, IP69K

IP65

IP65

IP65

IP65

IP65

IP65

IP65

IP65

IP65

IP65

Observeinstallation
instructions to
IP69K
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Observeinstallation
instructions to
IP69K

Rear

Additional
mounting
bracket set
required forflush mounting
IP20

IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Additional
mounting
bracket set
required forflush mounting
IP20

Approvals

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

cUL

Explosion protection(According to ATEX 94/9/EC)

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

II 3D Ex II T70°C
IP5x:Zone 22,
category 3D

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

II 2G Ex px II
IP5x:Zone 1,category 2G
Zone 2,
category 3G
Zone 22,
category 3D
Zone 1, Category 2G andZone 2, Category 3G: Only
when flushmounted in apressurized
enclosure!
Max. permissible excesspressure:
10 mbar continuous

II 3D Ex II
T70°C IP5x:
Zone 22,
category 3D

Additional
mounting
bracket set
required forflush mounting

II 2G Ex px II
IP5x:Zone 1,category 2G
Zone 2,
category 3G
Zone 22,
category 3D
Zone 1, Category 2G andZone 2, Category 3G: Only
when flushmounted in apressurized
enclosure!
Max. permissible excesspressure:
10 mbar continuous

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

Additional
mounting
bracket set
required forflush mounting

EN 60079-0,
EN 61241-1,
EN 13463

EN 60079-0,
EN 61241-1,
EN 13463

EN 60079-0,
EN 61241-1,
EN 13463,
EN 1127-1,
EN 60079-2

EN 60079-0,
EN 61241-1,
EN 13463

EN 60079-0,
EN 61241-1,
EN 13463

EN 60079-0,
EN 61241-1,
EN 13463

Yes (fuse not accessible)
No (0V connection to housing potential)

Degree of protection

Approvals

Additional
mounting
bracket set
required forflush mounting

Applied standards and directives
EMC (relevant for CE)
Explosion protection (relevant for CE)

EN 61000-6-2, EN 61000-6-3, EN 61000-6-4, EN 61131-2
EN 60079-0,
EN 60079-0,
EN 60079-0,
EN 60079-0,
EN 61241-1,
EN 61241-1,
EN 61241-1,
EN 61241-1,
EN 13463
EN 13463
EN 13463
EN 13463

SafetyEN 60950/UL 60950

Product standards

EN 50178, EN 61131-2

Weight

EN 60079-0,
EN 61241-1,
EN 13463

EN 60079-0,
EN 61241-1,
EN 13463

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0,
EN 60079-0,
EN 60079-0,
EN 61241-1,
EN 61241-1,
EN 61241-1,
EN 13463
EN 13463
EN 13463,
EN 1127-1,
EN 60079-2
EN 60950/UL 60950
EN 50178, EN 61131-2

Approx. 1.9 kg

Approx. 2.3 kg

Approx. 1.9 kg

Approx. 1.9 kg

Approx. 2.3 kg

Approx. 1.9 kg

Approx. 3.0 kg

Approx. 4.1 kg

Approx. 5.3 kg

Approx. 4.1 kg

Approx. 4.5 kg

Approx. 5.7 kg

Approx. 4.5 kg

Approx. 6.2 kg

Approx. 7.5 kg

Operation

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

0 – 50°C

Storage/transport-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

-20 – 60°C

Environmental Conditions
Temperature

Relative humidity
Impact resistance

10 - 95%, non-condensing
To IEC 68-2-27

10 - 95%, non-condensing
To IEC 68-2-27

Vibration

To IEC 68-2-6

To IEC 68-2-6

2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

14/32

Automation products

Visualization

Visualization

Automation products

HMI-PLC XVS400

14/33

HMI-PLC XVS400

VisualizationHMI-PLC XVS400

XVS-440-57MPI-1-10

XVS-430-57MPI-1-10

XVS-460-57MPI-1-10

Display
Screen diagonal/type
Resolution

5.7" CSTN LCD (color)5.7" TFT LCD (color)
QVGA (320 × 240 pixels or 240 × 320 pixels in portrait format)

Visible screen area
Color resolution (grayscale or color)

115 mm x 86 mm
256 colors

115 mm x 86 mm
256 colors

Contrast ratio
Brightness
Backlight

Normally 35:1
Normally 150 cd/m²
1 x CCFL, dimmable via
softwareNormally 50000 h–

Normally 35:1
Normally 150 cd/m²
1 x CCFL, dimmable via
softwareNormally 50000 h
Touch sensor(glass with membrane)–

Lifespan of backlight
Resistive touch protective screen
Infra-red touch protective screen
Operation
Technology
SystemProcessor
Internal memory
DRAM (OS, program and data memory)
FLASH (can be used for data backup)
NVRAM (Retain data)
External memory
CF slot

Real-time clock (battery backup)
Battery
Backup time at zero voltage
Operating system
Engineering
Visualization software
PLC programming software
Interfaces, communication
Ethernet
System port
CAN
PROFIBUS
USB Host
USB device
Power supply
Nominal voltage
Permissible voltage
Voltage dips

Input powerProtection against polarity reversal
Fuse
Potential isolation2010 CA08103002Z-EN

www.eaton.com

Laminated safety glass,non-reflective

115 mm x 86 mm
Adjustable: 65536 or
256 colors
Normally 400:1
Normally 350 cd/m²
LED, dimmable via
softwareNormally 40000 h–
Laminated safety glass,non-reflective

XVS-450-57MPI-1-10

115 mm x 86 mm
Adjustable: 65536 or
256 colors
Normally 400:1
Normally 350 cd/m²
LED, dimmable via
softwareNormally 40000 h
Touch sensor(glass with membrane)–

XVS-460-84MPI-1-10

XVS-440-10MPI-1-10

8.4" TFT LCD (color)10.4" TFT LCD (color)
VGA (640 × 480 pixels or 480 × 640 pixels in
portrait format)
170 mm x 128 mm
211 mm x 158 mm
Adjustable: 65536 or
Adjustable: 65536 or
256 colors
256 colors
Normally 400:1
Normally 350:1
Normally 350 cd/m²
Normally 350 cd/m²
2 x CCFL, dimmable via
2 x CCFL, dimmable via
softwaresoftwareNormally 50000 h
Normally 50000 h––
Laminated safety glass,non-reflective

Laminated safety glass,non-reflective

XVS-430-10MPI-1-10

XVS-440-12MPI-1-10

10.4" TFT LCD (color)12.1" TFT LCD (color)12.1" TFT LCD (color)
SVGA (800 × 600 pixels or 600 × 800 pixels in
portrait format)
246 mm x 185 mm
246 mm x 185 mm
Adjustable: 65536 or
Adjustable: 65536 or
256 colors
256 colors
Normally 350:1
Normally 350:1
Normally 350 cd/m²
Normally 350 cd/m²
2 x CCFL, dimmable via
2 x CCFL, dimmable via
softwaresoftwareNormally 50000 h
Normally 50000 h–
Touch sensor(glass with membrane)
Laminated safety glass, –non-reflective

15" TFT LCD (color)
XGA (1024 x 768 pixel)

211 mm x 158 mm
Adjustable: 65536 or
256 colors
Normally 350:1
Normally 350 cd/m²
2 x CCFL, dimmable via
softwareNormally 50000 h
Touch sensor(glass with membrane)–

XVS-430-12MPI-1-10

XVS-460-15MPI-1-10

304 mm x 228 mm
Adjustable: 65536 or
256 colors
Normally 350:1
Normally 400 cd/m²
4 x CCFL, dimmable via
softwareNormally 50000 h–
Laminated safety glass,non-reflective

Infra-red touch,
47 x 31 logic channels

Resistive touch,
4-conductor

Infra-red touch,
47 × 31 logic channels

Resistive touch,
4-conductor

Infra-red touch,
63 x 47 logic channels

Infra-red touch,
79 x 59 logic channels

Resistive touch, 4-conductor

Infra-red touch,
95 x 71 logic channels

Resistive touch, 4-conductor

Infra-red touch,
107 x 83 logic channels

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

RISC, 32 bit, 400 MHz

64 MByte

64 MByte

64 MByte
64 MByte
Approx. 1.5 MByte available
Approx. 32 kByte available

64 MByte

64 MByte

64 MByte

64 MByte

64 MByte
64 MByte
Approx. 1.5 MByte available
Approx. 32 kByte available

1 x CompactFlash card type I/II for operating system, programs and data

1 x CompactFlash card
type I/II for operating
System, programs anddata

2 x CompactFlash card type I/II for operating system, programs and data

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

Zero maintenance
Normally 10 years
Windows CE

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

GALILEO/EPAM
XSOFT-CODESYS-2

100Base-TX/10Base-T

100Base-TX/10Base-T

100Base-TX/10Base-T

100Base-TX/10Base-T

–

–

–

USB 1.1, not isolated

100Base-TX/10Base-T
100Base-TX/10Base-T
100Base-TX/10Base-T
RS232, not isolated (D-sub 9-pin, UNC)–––PROFIBUS galvanically isolated, max. 1.5 MBit/s (D-sub 9-pin socket, UNC)
USB 2.0 (1.5/12 MBit/s), 2 x USB 2.0 (1.5/12 MBit/s), not isolated
not isolated
USB 1.1, not isolated

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (nominal voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from nominal
20 ms from nominal
20 ms from nominal
voltage (24 V DC),
voltage (24 V DC),
voltage (24 V DC),
2 ms from undervoltage
2 ms from undervoltage
2 ms from undervoltage(20.4 V DC)(20.4 V DC)(20.4 V DC)
Max. 19 W
Max. 19 W
Max. 19 W(Normally 12 W)(Normally 12 W)(normally 12 W)
Yes
Yes
Yes
Yes (fuse not accessible)
No (0V connection to housing potential)

24 V DC SELV (safety extra low voltage)
R.m.s.: 20.4 – 28.8 V DC (nominal voltage -15 %/+20 %)Absolute with ripple: 19.2 – 30.0 V DC
35 V DC for a duration < 100 ms
20 ms from nominal
10 ms from rated
10 ms from rated
voltage (24 V DC),
operating voltage
operating voltage
2 ms from undervoltage (24 V DC), 5 ms from(24 V DC), 5 ms from(20.4 V DC)
undervoltage (20.4 V DC) undervoltage (20.4 V DC)
Max. 22 W
Max. 24 W
Max. 24 W(normally 15 W)(normally 14 W)(normally 14 W)
Yes
Yes
Yes
Yes (fuse not accessible)
No (0 V connection to housing potential)

10 ms from rated
operating voltage(24 V DC), 5 ms fromundervoltage (20.4 V DC)
Max. 24 W(normally 14 W)
Yes

10 ms from rated
operating voltage(24 V DC), 5 ms fromundervoltage (20.4 V DC)
Max. 24 W(normally 14 W)
Yes

10 ms from rated
operating voltage(24 V DC), 5 ms fromundervoltage (20.4 V DC)
Max. 36 W(normally 28 W)
Yes

100Base-TX/10Base-T
100Base-TX/10Base-T
100Base-TX/10Base-T
RS232, not isolated (D-sub 9-pin, UNC)–––PROFIBUS galvanically isolated, max. 1.5 MBit/s (D-sub 9-pin socket, UNC)
USB 2.0 (1.5/12 MBit/s), not isolated–

20 ms from nominal
voltage (24 V DC),
2 ms from undervoltage(20.4 V DC)
Max. 19 W(normally 12 W)
Yes

2010 CA08103002Z-EN

www.eaton.com

14/34Visualization, XV-Dimensions

Visualization, XV-Dimensions

HMI-PLC XVS400

14/35

HMI-PLC XVS400

GeneralFront design
Degree of protection
Front
Rear
Approvals
Approvals
Explosion protection(According to ATEX 94/9/EC)
Applied standards and directives
EMC (relevant for CE)
Explosion protection (relevant for CE)
SafetyProduct standards
WeightEnvironmental Conditions
Temperature
Operation
Storage/transport
Relative humidity
Impact resistanceVibration

XVS-440-57MPI-1-10

XVS-430-57MPI-1-10

XVS-460-57MPI-1-10

XVS-450-57MPI-1-10

XVS-460-84MPI-1-10

XVS-440-10MPI-1-10

XVS-430-10MPI-1-10

XVS-440-12MPI-1-10

XVS-430-12MPI-1-10

XVS-460-15MPI-1-10

Standard membraneStandard membrane(fully laminated)Standard membraneStandard membrane(fully laminated)Standard membraneStandard membraneStandard membrane(fully laminated)Standard membraneStandard membrane(fully laminated)Standard membrane

IP65
IP65
IP65
Additional mounting bracket set required for flush mounting (￫ Page 14/12)
IP20
IP20
IP20

IP65

IP65
IP65
IP65
Additional mounting bracket set required for flush mounting (￫ Page 14/12)
IP20
IP20
IP20

IP65

IP65

IP65

IP20

IP20

IP20

cUL
cUL
cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket set required for flush mounting (￫ Page 14/12)

cUL

cUL
cUL
cUL
II 3D Ex II T70°C IP5x:
Zone 22, Category 3D
Additional mounting bracket set required for flush mounting (￫ Page 14/12)

cUL

cUL

cUL

EN 61000-6-2, EN 61000-6-3, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60950
EN 60950/UL 60950
EN 60950/UL 60950
EN 50178, EN 61131-2
EN 50178, EN 61131-2
EN 50178, EN 61131-2
Approx. 1.8 kg
Approx. 1.8 kg
Approx. 1.8 kg

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

IP20

EN 60950/UL 60951
EN 50178, EN 61131-2
Approx. 1.8 kg

EN 61000-6-2, EN 61000-6-4, EN 61131-2
EN 60079-0, EN 61241-1, EN 13463
EN 60950/UL 60952
EN 60950/UL 60950
EN 50178, EN 61131-2
EN 50178, EN 61131-2
Approx. 2.6 kg
Approx. 3.7 kg

EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 3.7 kg

EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 4.1 kg

EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 4.1 kg

EN 60950/UL 60950
EN 50178, EN 61131-2
Approx. 5.8 kg

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

0 – 50°C-20 – 60°C
10 – 95%,
non-condensing
To IEC 68-2-27
To IEC 68-2-6

Dimensions
XV-..., XVH-3..., XVS-4..., MFD4...

XVM-4...
XV-102-…-35...
XV-102-…-57...
XV-102-…-70...

a
136
170
210

b
100
130
135

c
25
34
33

d
5
5
5

e
123
157
197

f
87
117
122

XV-2…-57...

212

156

50

5

198

142

MFD4...

212

156

54

5

198

142

XVH-3…-57BAS...

212

55
55
55
76

5
5
5
5

198
198
198
198

142
142
142
142

21.5

55.3

37.2

o 252

a

c

d

XVH-3…-57SKS...

212

156
156
156
156

XVS-4…-57...

212
275
345
361
427

156
208
260
279
332

55
70
62
62
68

5
5
5
5
5

198
261
329
344
410

142
194
238
262
315

212
275
345
361
427

156
208
260
279
332

76
90
88
88
94

5
5
5
5
5

198
261
329
344
410

142
194
238
262
315

XVH-3…-57CAN... 212
XVH-3…-57MPI... 212

o 240

b

Part No.

Mounting dimensions
XVS-4…-84...

XVS-4…-10...
XVS-4…-12...
f

XVS-4…-15...
XV-4…-57...
XV-4…-84...

XV-4…-10...
XV-4…-12...
XV-4…-15...
e2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

14/36

Automation products

Modular PLC

System overview
Modular PLC

1
1

F1

F2

F3

F10

F11

+/-

F12

F13

,

F14

F15

0

F4

F5

F6

7

8

9

4

5

6

1

2

3

F7

180
F8

F9

SHIFT

ESC

CLEAR

ENTER

2

6

0 1 2
3
4 5 6
0 1 2 73
4 5 14
15

0 1 2
3
4 5 6
8 9 10 7
11
12 13 1415

XC-CPU101

7

DC INPU
T

3

0 1 2
3
4 5 6
8 9 10 7
11
12 13 14
15

EH-XD16

DC INPU
T

0 1 2
3
4 5 6
8 9 10 7
11
12 13 14
15

EH-XD16

DC INPUT

EH-XD16

4
4
4

5

6

3

0 1 2
3
4 5 6
0 1 2 73
4 5 14
15

0 1 2
3
4 5 6
8 9 10 7
11
12 13 1415

XC-CPU201

7

DC INPUT

EH-XD16

0 1 2
3
4 5 6
8 9 10 7
11
12 13 14
15

DC INPUT

EH-XD16

9
10

7

8

8
8

2010 CA08103002Z-EN

www.eaton.com

8Modular PLC
XV101 text display

Automation products
1

Always in conjunction
with XC100-XV and XI/OC(MMI-PLC)
Displays: 4 lines ×
20 characters (or 8 × 40)
LCD display with STN
technology
9 (or 15) function keys withinsert strips
Numerical key block andarrow keys
Controller status LED￫ Page 14/38

XC100
Modular PLC
8 digital inputs
6 digital outputs
4 interrupt inputs
CANopen fieldbus interface
RS232 interface
Locally expandable
with XI/OC
Can be combinedwith XV text displays￫ Page 14/38

XI/OC I/O modules

3

Space-optimized input/
output modules
Local extension on
XC100/200
Digital, analog, technology,
counter and communication cards
XI/OC modules can beexchanged without theneed to undo wiring￫ Page 14/39

Module backplane
2

XI/OC backplane
For connecting the
XC100/200 controller and
the XI/OC modules with the
top-hat rail
￫ Page 14/40

4

XC200

5

Modular PLC with Ethernet
interface
8 digital inputs
6 digital outputs
2 counters
2 interrupt inputs
1 incremental input
CANopen fieldbus interface
Web server
RS232 interface
Locally expandable with
XI/OC￫ Page 14/38

Battery

14/37

XI/OC terminal block8

Connection options throughspring-loaded or screw
terminals
Exchange/remove without
disconnecting wiring￫ Page 14/40

XC121

6

9

Compact PLC
2 CANopen interfaces
RS232 interface
RS232/RS485 interface
MMC Memory card
OPC server￫ Page 14/38￫ Page 14/41

EXT121-1
Memory card
(multi-media card)
Memory for program,
operating system, recipes,
and visualization texts￫ Page 14/41

7

10

Expansion for compact PLC
10 digital inputs, of which,
6 interrupt inputs
8 digital outputs
6 analog inputs:
2 Pt100 RTD,
2 x 0-10 V, 2 x 0-20 mA
2 analog outputs 0 - 10 V
￫ Page 14/38

2010 CA08103002Z-EN

www.eaton.com

14/38Automation products

Modular PLCs

PLCs
HPL14038EN

PLCs

Modular PLCs

Ordering

Description

Part No.
Article No.

Price
See price
list

Std. pack

XC100• 24 V supply • Can be locally expanded with 15 XI/OC is remotely expandable• The following accessories are required: terminals, backplane, battery• Controller with 8 digital inputs (4 interrupt inputs) • 6 digital outputs; RS232 interface for programming andcommunication • CANopen interface • slot for MMC memory card • optional expansion with text display •RUN/STOP switch and LED indicators.
64 kByte user memory
128 kByte user memory
256 kByte user memory
Optical CAN interface:
128 kByte user memory
Operation with display XV-101-…
64 kByte user memory
Operation with display XV-101-…
128 kByte user memory
Operation with display XV-101-…
256 kByte user memory

XC-CPU101-C64K-8DI-6DO
262152
XC-CPU101-C128K-8DI-6DO
262146
XC-CPU101-C256K-8DI-6DO
274399XC-CPU101-FC128K-8DI-6DO
289169XC-CPU101-C64K-8DI-6DO-XV
262247
XC-CPU101-C128K-8DI-6DO-XV
262150XC-CPU101-C256K-8DI-6DO-XV
279280

1 off

XV-101-K42
262403
XV-101-K84
262404

1 off

XC-CPU121-2C256K
290446

1 off

XIO-EXT121-1
290450

1 off

XC-CPU201-EC256K-8DI-6DO
262155
XC-CPU201-EC512K-8DI-6DO
262157
XC-CPU201-EC256K-8DI-6DO-XV
262156
XC-CPU201-EC512K-8DI-6DO-XV
262158
XC-CPU202-EC4M-8DI-6DO-XV
134238

1 off

Text display for XC100• Backlit LCD • membrane keypad • 1 slot for XC100 • 3 spare slots for XI/OC modules • numerical keypad •arrow keys • contrast setting adjustable via software
Operation with XC-CPU101-…-XV
4 lines x 20 characters, resolution 122 x 32 pixels, 9 function keys
Operation with XC-CPU101-…-XV
8 lines x 40 characters, resolution 240 x 64 pixels, 15 function keys

1 off

XC121
• Compact PLC • 24 V supply • 2 CANopen interfaces • RS232 interface for programming and communication• second RS232/RS485 interface • Slot for MMC memory card • Connection through spring-cage terminal
blocks • OPC server
Can be locally expanded with I/O module XIO-EXT-121-1
256 kByte program memory, 244 kByte data memory

I/O expansion for XC121• Expansion unit with digital and analog inputs/outputs • expandable with XI/OC signal modules(except XIOC-NET-DP-M) • pluggable spring-cage terminals
Local I/O expansions for PLC XC121
10 digital inputs 24 V DC, of which 6 interrupt
8 digital inputs/outputs 24 V DC, 0.5 A
2 analog inputs 0 - 10 V
2 analog inputs 0 - 20 mA
2 analog inputs Pt100 RTD
2 analog outputs 0 - 10 V

XC200
• 24 V supply • Can be locally expanded with 15 XI/OC is remotely expandable• The following accessories are required: terminals, backplane, battery• Controller with 8 digital inputs (2 counter, 2 interrupt inputs, 1 incremental input) • 6 digital outputs; Ethernet
and RS232 interface for programming and communication • CANopen interface • slot for memory card
(MMC) XC-CPU202 (MMC and SD) • USB interface • RUN/STOP switch and LED indicators
256 kByte user memory
2 MByte user memory
256 kByte user memory
Integrated web server
2 MByte user memory,
Integrated web server
4 Mbyte user memory, integrated Web server
Information relevant for export to North America
Product Standards
UL File No.
UL CCN2010 CA08103002Z-EN

IEC: see Technical Data; UL508; CSA-C22.2 No. 0-M; CSA-C22.2 No. 142-M; CE marking
E135462
NRAQ

www.eaton.com

CSA File No.
CSA Class No.
NA Certification
Degree of Protection

0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Modular PLCs

Automation products

14/39

I/O expansions XI/OC
HPL14039EN
Modular PLCsI/O expansions XI/OC

Description

Part No.
Article No.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

XI/OC• Compact I/O system for connection to XC100/200
Modular PLCs
• XC100/200 expandable with up to 15 XI/OC modules• Optionally, screw terminals or spring-loaded terminals
for digital/analog modules
Digital modules
8 inputs, 24 V DC
16 inputs, 24 V DC
32 inputs, 24 V DC
8 outputs, 24 V DC, 0.3 A
12 relay outputs
16 outputs, 24 V DC, 0.3 A
16 outputs, 24 V DC, 0.8 A,
short-circuit proof
16 terminals, 4 inputs, 12 freely
parameterizable as inputs/outputs, 24 V DC
Outputs 0.5 A
32 outputs, 24 V DC, 0.2 A

XIOC-8DI
257891
XIOC-16DI
257892
XIOC-32DI
267411
XIOC-8DO
257894
XIOC-12DO-R
257897
XIOC-16DO
257896
XIOC-16DO-S257895
XIOC-16DX
262322UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2
No. 142-M; CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -XIOC-32DO
267413

Analog modules
Inputs
8 inputs 4 - 20 mA
Inputs8 voltage inputs 0 - 10 V
Inputs8 voltage inputs, ±10 V
Inputs4 inputs for temperature monitoring,Pt100/1000
Inputs4 inputs for thermocouples
Type K, J, L, B, N, E, R, S, T
Outputs
2 outputs, ±10 V
Outputs
2 outputs 0 - 10 V, 2 outputs 4 - 20 mA
Outputs
4 outputs 0 - 10 V
Combination modules
2 inputs and 1 output 0 - 10 V
1 ms conversion time
Combination modules
2 inputs and 1 output 0 - 10 V, 0 - 20 mA
1 ms conversion time, individualchangeover
Combination modules
4 inputs und 2 outputs 0 - 10 V
1 ms conversion time
Combination modules
4 inputs and 2 outputs 0 - 10 V, 0 - 20 mA
1 ms conversion time, individualchangeover

XIOC-8AI-I2
262549XIOC-8AI-U1
257899XIOC-8AI-U2
257900XIOC-4T-Pt
257901

1 off

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2
No. 142-M; CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -XIOC-4AI-T
289933
XIOC-2AO-U2
257904
XIOC-2AO-U1-2AO-I2
257902
XIOC-4AO-U1
257903
XIOC-2AI-1AO-U1
262409XIOC-2AI-1AO-U1-I1
281545

XIOC-4AI-2AO-U1
262405
XIOC-4AI-2AO-U1-I1
281544

Counter modules
1 input up to 100 kHz, 24 V DC, 5 V DC,
2 digital transistor outputs, opto-isolated,
24 V DC30 pin connector required for counter module
2 inputs up to 100 kHz, (24 V DC or 5 V diff),
4 digital transistor outputs,
opto-isolated, 24 V DC
30 pin connector required for counter module
2 incremental encoders up to 400 kHz,
5 V DC, 2 analog outputs ±10 V

XIOC-1CNT-100KHZ
257906

XIOC-2CNT-100KHZ
257907

XIOC-2CNT-2AO-INC
262417

1 off

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2
No. 142-M; CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/40Automation products

Modular PLCs

Communication modules XI/OC, accessories
HPL14040EN
Modular PLCsCommunication modules XI/OC, accessories

Description

Part No.
Article No.

Price
See price
list

Std. pack

Information relevant for export to North America

XIOC-NET-DP-M
257908XIOC-NET-DP-S
286419XIOC-NET-SK-M
289982
XIOC-SER
267191

1 off

Product Standards

XIOC-TC1
135265

Communication cards
PROFIBUS-DP master module

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2
No. 142-M; CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -1 off

NA Certification

Request filed for UL and CSA

XIOC-TERM-18T
258104
XIOC-TERM-18S
25810210 off

NA Certification

Request filed for UL and CSA

30 pin connector for counter module,with 4 m cable
XIOC-1CNT-100KHZ
XIOC-2CNT-100KHZ
40 pin connector for digital module,with 4 m cable
XIOC-32DI
XIOC-32DO

XIOC-TERM30-CNT4
262248

1 off

Basic backplane for mounting
XC100/200 on top-hat rail, can be
expanded
Width: 2 slots for controller

XIOC-BP-XC
260792

Product Standards

Expansion backplane for mounting
XI/OC modules on top-hat rail,
can be expanded
Width: 2 slots for XI/OC modules

XIOC-BP-2
260794

1 off

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2
No. 142-M; CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Basic backplane for mounting
XC100/200 on top-hat rail, can be
expanded
Width: 3 slots for controller and one
XI/OC module

XIOC-BP-XC1
260793

1 off

Expansion backplane for mounting
XI/OC modules on top-hat rail,
can be expanded
Width: 3 slots for XI/OC modules
Expansion backplane for mounting
XI/OC modules on top-hat rail,
can be expanded
Width: 3 slots for XI/OC modules
Note: Module Backplane for expansion
with up to 15 modules, must be plugged
into the 6th slot

XIOC-BP-3
260795

1 off

XIOC-BP-EXT
274291

1 off

PROFIBUS-DP slave module
Suconet K master module
Serial interfaces
RS232C, RS485, RS422
Modes of operation:
Transparent mode
Modbus master/slave
SUCOM-A
Suconet-K slave
Serial interfaces
RS232C, RS485, RS422
Modes of operation:
Transparent mode
Modbus master/slave
SUCOM-ADNP protocol

Accessories
Terminals
One 18 pole terminal plug is required for each digital andanalog module.
–
18-pin connector with spring-cageterminal for digital or analog I/O.
–
18-pin connector with screw terminals
for digital or analog I/O.
––

XIOC-TERM32
267414Module backplane2010 CA08103002Z-EN

www.eaton.com

1 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Modular PLCs

Automation products

14/41

Accessories
HPL14041EN
Modular PLCsAccessories

Std. pack

Information relevant for export to North America

XT-MEM-MM512M
138257
XT-MEM-MM32M
262731

1 off

NA Certification

1 off

Product Standards

For backup of real-time clock andretentive data of the MFD4

XT-CPU-BAT1
2562091 off

2m
D-sub 9-pin, serial

XT-SUB-D/RJ45
262186

1 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

2m
Ethernet cross
5m
Ethernet cross

XT-CAT5-X-2
256487
XT-CAT5-X-5
2564881 off

Programming cable for XC, EC4P,
EU5C through USB interface

EU4A-RJ45-USB-CAB1
1157350.3 m
Connection cable for XC200 tointerface switch
0.8 m
Connection cable for XC200 tointerface switch
1.5 m
Connection cable for XC200 tointerface switch

EASY-NT-30
256283

Description

Part No.
Article No.

Price
See price list

Accessories
Memory card
For storage of programs, data, recipes
for XC100, XC121, XC200, MFD4–512 MByte–

32 MByte

Battery

Programming cables

Request filed for UL and
CSA
IEC: see Technical Data;
UL508; CSA-C22.2 No. 0-M;
CSA-C22.2 No. 142-M; CE
marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Connection cables
1 off

EASY-NT-80
256284

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

EASY-NT-150
256285

IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987; CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -CAN cable to ISO 11898
Recommendation:
UNITRONIC bus LD, from LAPPKABEL
2 x 2 x 0.22 mm²
Characteristic impedance: 100 - 120 Ω
Effective capacitance: 800 Hz, max. 60 nF/km
Empty module
Empty module to cover free XI/OC
slots

XIOC-NOP
288894

1 off

Product Standards

Interface adapter to split the
combined RS232/Ethernet interface of
the XC200 into RJ45 sockets
Connection cable EASY-NT-30/80/150
usable for connection to XC200.

XT-RJ45-ETH-RS232
289170

1 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection–

Interference suppression of theexternal 24 V DC supply of the
XC100/200
Max. current consumption: 2.2 A

XT-FIL-1
285316

1 off–

Power supply interference
suppression of I/O modules of
XC100/200. Max. current
consumption: 12 A

XT-FIL-2
118980

1 off

Insert labels for user inscription
For 3 devices: XV-101-K42
For 3 devices: XV-101-K84

XT-BS1265365

1 off–
Interface switch–

Filter

IEC: see Technical Data;
UL508; CSA-C22.2 No. 0-M;
CSA-C22.2 No. 142-M; CE
marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Insert labels–

UL/CSA certification not required

Programming software ￫ Page 14/130

2010 CA08103002Z-EN

www.eaton.com

14/42

Automation products

Modular PLCs

PLCs

Technical data
Modular PLCsPLCs

XC-CPU101- C64K-8DI6DO(-XV)

XC-CPU101- C128K-8DI6DO(-XV)

XC-CPU101-FC128K-8DI6DO(-XV)

XC-CPU101- C256K-8DI6DO(-XV)

IEC/EN 61131-2
EN 50178
0 - +55

IEC/EN 61131-2
EN 50178
0 - +55

IEC/EN 61131-2
EN 50178
0 - +55

GeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 to +70-25 to +70-25 to +70-25 to +70

Horizontal

Horizontal

Horizontal

Horizontal%

10 - 95

10 - 95

10 - 95

10 - 95hPa

795 - 1080

795 - 1080

795 - 1080

795 - 1080

Mechanical shock resistance

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

Overvoltage category

II

II

II

II

Pollution degree

2

2

2

2

Degree of Protection

IP20

IP20

IP20

IP20

500

500

500

500

Emitted interference

EN 61000-6-4, Class A

EN 61000-6-4, Class A

EN 61000-6-4, Class A

EN 61000-6-4, Class A

Interference immunity

EN 61000-6-2

EN 61000-6-2

EN 61000-6-2

EN 61000-6-2

Battery (lifespan)

Normally 5 years

Normally 5 years

Normally 5 years

Normally 5 years

0.23

0.23

0.23

0.23

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Mounting position
Relative humidity, non-condensing(IEC/EN 60068-2-30)
Air pressure (in operation)
Vibration resistance

Rated insulation voltage

Ui

WeightV

kg

Terminals
Terminal capacity
Screw terminals
Flexible with ferrule

mm2

0.5 - 1.5

0.5 - 1.5

0.5 - 1.5

0.5 - 1.5

Solid

mm2

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

Flexible

mm20.34 - 1.0

0.34 - 1.0

0.34 - 1.0

0.34 - 1.0

Solid

mm2

0.14 - 1.0

0.14 - 1.0

0.14 - 1.0

0.14 - 1.0

Spring-cage terminal￫ Page 14/58

Electromagnetic compatibility (EMC)
Power supply
Mains failure duration

ms

10

10

10

10

Repetition rate

s

1

1

1

1

Input voltage

V DC

24

24

24

24

Permissible range

V DC

20.4…28.8

20.4…28.8

20.4…28.8

20.4…28.8

Input power

W

Max. 26

Max. 26

Max. 26

Max. 26

Ripple

%

≦5

≦5

≦5

≦5

W

6

6

6

6

Maximum heat dissipation(without local I/O)
Overvoltage protection

Pv

Yes

Yes

Yes

Yes

Protection against polarity reversal

Yes

Yes

Yes

Yes

Mains filter (external)

Yes

Yes

Yes

Yes

Inrush current

x In

Not limited, (limiting only by a supply-side 24 V DC PSU)

Rated value

V DC

5

5

5

5

Output current

A

3.2

3.2

3.2

3.2

Short-circuit rating

Yes

Yes

Yes

Yes

Isolated from supply voltage

No

No

No

No

Infineon C164

Infineon C164

Infineon C164

Infineon C164

Output voltage for signal modules

CPU
Microprocessor
MemoryProgram code/program data

kByte

64/64

128/128

128/128

256/256

Marker/retain data

kByte

4/4

8/8

8/8

8/8

Cycle time for 1 k of instructions(bits, bytes)

ms

< 0.5

< 0.5

< 0.5

< 0.5

2010 CA08103002Z-EN

www.eaton.com

Modular PLCs

Automation products

14/43

PLCs

XC-CPU101- C64K-8DI6DO(-XV)

XC-CPU101- C128K-8DI6DO(-XV)

XC-CPU101-FC128K-8DI6DO(-XV)

XC-CPU101- C256K-8DI6DO(-XV)

Interfaces
Serial interface (RS232)
without handshake lines
Baud rate

Max. 57.6

Max. 57.6

Max. 57.6

Max. 57.6

Connections

kbit/s

RJ45

RJ45

RJ45

RJ45

Potential isolation

No

No

No

No

CANopen
500000500000500000500000Potential isolation

Maximum data transfer rate

bit/s

Yes

Yes

Yes

Yes

Device profile

To DS 301 V4

To DS 301 V4

To DS 301 V4

To DS 301 V4

PDO type

Asyn., cyc., acyc.

Asyn., cyc., acyc.

Asyn., cyc., acyc.

Asyn., cyc., acyc.

Connection

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

External

External

Optical fiber interface,wavelength 660 mm,
plug e.g. HFBR-4516
Agilent Technologies
ExternalMax. 126

Max. 126

Max. 126

Max. 126

Watchdog

Yes

Yes

Yes

Yes

RTC (real-time clock)

Yes

Yes

Yes

Yes

Bus terminating resistors
Stations

NumberExternal

Power supply of local inputs/outputs(24 VQ/0 VQ)
Input voltage

V DC

24

24

24

24

Voltage range

V DC

19.2 - 30, observe polarity

19.2 - 30, observe polarity

19.2 - 30, observe polarity

19.2 - 30, observe polarity

Between power supply andCPU voltage
Overvoltage protection

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Protection against polarity reversal

Yes

Yes

Yes

Yes

Normally 3.5

Normally 3.5

Normally 3.5

Normally 3.5

Normally 85 m W

Normally 85 m W

Normally 85 m W

Normally 85 m W

Low < 5 V DC,
High > 15 V DC

Low < 5 V DC,
High > 15 V DC

Low < 5 V DC,
High > 15 V DC

Low < 5 V DC,
High > 15 V DC

Potential isolation

Digital inputs
Input current for channel at rated voltage

mA

Heat dissipation for channel
Voltage level to IEC/EN 61131-2
Limit value type 1
Input delay
OFF → ONms

Normally 0.1

Normally 0.1

Normally 0.1

Normally 0.1

ON → OFFms

Normally 0.1

Normally 0.1

Normally 0.1

Normally 0.1

InputsNumberChannels with the same reference
potential
Status indication

Number8 (of which 4 interrupt
inputs)88 (of which 4 interrupt
inputs)88 (of which 4 interrupt
inputs)88 (of which 4 interrupt
inputs)
8

LED

LED

LED

LED

Digital outputs
Channels

Number6

6

6

6

Heat dissipation for channel

W

0.08

0.08

0.08

0.08

Load circuits

A

0.5

0.5

0.5

0.5

OFF → ON

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

ON → OFF

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

6

6

6

6

LED

LED

LED

LED

IEC/EN 60947-5-1,
utilization category
DC-13
100

IEC/EN 60947-5-1,
utilization category
DC-13
100

IEC/EN 60947-5-1,
utilization category
DC-13
100

1

1

1

Output delay

Channels with the same reference
potential
Status indication

NumberDuty factor% DF

IEC/EN 60947-5-1,
utilization category
DC-13
100

Utilization factorg1

Switching capacity

2010 CA08103002Z-EN

www.eaton.com

14/44

Automation products

Modular PLCs

PLCs
Modular PLCsPLCs

XV-101-K42

XV-101-K84

IEC/EN 60131-2
EN 50178

IEC/EN 60131-2
EN 50178

°C

0…50

0…50

°C

-20 - 70

-20 - 70%

10 - 95

10 - 95

Front

IP65

IP65

Enclosure

IP20

IP20

10 - 57 Hz ± 0.075 mm
57 - 150 Hz ±1 g
15 g/11 ms

10 - 57 Hz ± 0.075 mm
57 - 150 Hz ±1 g
15 g/11 ms

GeneralStandards
Ambient temperature
Operation
When mounted vertically, up to 45° fitting angle
Storage
Relative humidity, non-condensing (IEC/EN 60068-2-30)
Protection typeVibration resistanceMechanical shock resistance

850

850

Overvoltage category

II

II

Pollution degree22Interference immunity

EN 61000-6-2

EN 61000-6-2

Emitted interference

EN 50081-2, Class A

EN 50081-2, Class A

kg

Approx. 0.9

Approx. 0.9

V DC

24

24

V DC

18…30

18…30

LED

LED

100000100000Character height

5 mm/10 mm

5 mm/10 mm

User-definable characters

256

256

29

35

> 3000000> 3000000

Memory type

SRAM, 32 KB

SRAM, 32 KB

Status indication

LED (RUN, STOP, SF)

LED (RUN, STOP, SF)

Expansions

3 XI/OC signal modules

3 XI/OC signal modules

Real-time clock

Yes

Yes

Rated impulse withstand voltage

Uimp

WeightV

Power supply
Rated voltage

Ue

Permissible range
Display
Backlight
Lifespan of backlight

Operating hours

Pushbuttons
Total number of pushbuttons
Keypad service life

Operations

Features2010 CA08103002Z-EN

www.eaton.com

Modular PLCs

Automation products

14/45

PLCs
Modular PLCsPLCs

XC-CPU121-2C256K
GeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 to +70

Mounting position

Horizontal

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

10 - 95

Air pressure (in operation)hPa

795 - 1080

Vibration resistanceMechanical shock resistanceFrequency 5 - 9 Hz; 3.5 mm amplitude
9 - 150 Hz; 1.0 g constant acceleration
15 g/11 ms

Overvoltage category

II

Pollution degree

2

Degree of protection
Rated insulation voltage

IP20
Ui

V

500

Emitted interference

EN 61000-6-4

Interference immunity

EN 61000-6-2
At least 72 hours

Backup time
Weightkg

Electromagnetic compatibility (EMC)

0.15￫ Page 14/58

Connections
Supply voltage
Connection type

mm2

Terminal capacity

0.14 - 1 (AWG28-18)

COM1 interface
Connection type

RJ45

COM2, CAN1, CAN2 interfaces
Connection type

Spring-loaded terminal block, 6pole

Terminal capacity

mm²

0.14 - 0.5 (AWG28-20)

Input voltage

V DC

24

Permissible range

V DC

20.4…28.8

Input power

W

Max. 1.44

Input current

mA

60

Ripple

%

≦5

W

6

Power supply

Maximum heat dissipation (without local I/O)

Pv

Yes

Overvoltage protection
Protection against polarity reversal
Inrush current

Yes
x In

No limitation (limited only by upstream 24 V DC power supply unit)

Duration of power failurems

10

Repetition rates

1

Supply failure bridging

Part No.: XT-FIL-1, ￫ Page 14/41

External supply filter
MemoryProgram code/program data

kByte

256/244

Marker/input/output/retain datakByte

16/4/4/8

Cycle time for 1 k of instructions (bits, bytes)

ms

< 0.3

Baud ratekbit/s–Baud ratekbit/sConnector type

Programming(character format: 8 data bits, No parity, 1 stop bit)
19.2, 38.4 (default), 57.6
RJ45

Potential isolation

No

Interfaces
Serial interface (RS232) without handshake lines

In transparent mode
Baud ratekbit/s0.3, 0.6, 1.2, 2.4, 4.8, 9.6, 19.2, 38.4, 57.6, 115.2

Character formats

8E1, 8O1, 8N1, 8N2, 7E2, 7O2, 7N2, 7E1

Number of Send bytes for block190

Number of Receive bytes for block190

2010 CA08103002Z-EN

www.eaton.com

14/46

Automation products

Modular PLCs

PLCs

XC-CPU121-2C256K
COM2 (RS232/RS485) without handshake lines
Baud ratekbit/sPotential isolation

Transparent mode(setting through function blocks)
0.3, 0.6, 1.2, 2.4, 4.8, 9.6, 19.2, 38.4, 57.6
8E1, 8O1, 8N1, 8N2, 7E2, 7O2, 7N2, 7E1(setting through function blocks)
No

Bus termination

External, for RS485

Character formats

CAN1/CAN2 interface
Baud ratekbit/s

10 … 500

Potential isolation

No

Stations

126

Bus termination

Adjustable for each interface (CAN1/CAN2)

PDO type

Asyn., cyc., acyc.

Power supply of local inputs/outputs (24 VQ/0 VQ)
Input voltage

V DC

24

Voltage range

V DC

19.2 - 30, observe polarity

Potential isolation
Between power supply and CPU voltage
Overvoltage protection2010 CA08103002Z-EN

Yes
Yes

www.eaton.com

Modular PLCs

Automation products

14/47

I/O expansions for XC121
Modular PLCsI/O expansions for XC121

XIO-EXT121-1
GeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 to +70

Mounting position

Horizontal

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

10 - 95

Air pressure (in operation)hPa

795 - 1080

Vibration resistanceMechanical shock resistanceFrequency 5 - 9 Hz; 3.5 mm amplitude
9 - 150 Hz; 1.0 g constant acceleration
15 g/11 ms

Overvoltage category

II

Pollution degree

2

Degree of protection
Rated insulation voltage

IP20
Ui

V

500

Emitted interference

EN 61000-6-4

Interference immunity

EN 61000-6-2
At least 72 hours

Backup time
Weightkg

Electromagnetic compatibility (EMC)

0.15￫ Page 14/58

Connections
X1 connector
Connector type

Spring-loaded terminal block, 20 pole, B2L 3.5 (Weidmüller)
mm2

0.5 - 1

mm²

Spring-loaded terminal block, 10 pole, BLZF 3.5/180 or BLI/O 3.5/10F
with LEDs (Weidmüller)
0.5 - 1

Duration of power failurems

10

Repetition rates

1

Input voltage

V DC

24

Permissible range

V DC

20.4…28.8

Input power

W

Max. 1.68

Input current

mA

70

Ripple%≦5Terminal capacity (solid)
X2/X3 connector
Connector type
Terminal capacity (solid)
Power supply
Supply failure bridging

Overvoltage protection

Yes
Yes

Protection against polarity reversal
Inrush current

x In

Max. 1 A

A

2

Output voltage for signal modules
Max. field current IL
Digital inputs
Number

X2: 9 with plug BLI/O 3.5/10F or 10 with plug BLZF 3.5/180
X3: 8 (can also be used as outputs)

Rated voltage
Rated voltage

Ue

V DC

24

At state ”0”

Ue

V DC

<5

At state ”1”

Ue

V DC

> 15

Ie

mA

3.3

Rated operational current
At state ”1”
Delay time
X2: DI0…DI3μs

20

X2: DI4…DI9

μs

250

X2: DX0…DX7ms

20

Potential isolationNo2010 CA08103002Z-EN

www.eaton.com

14/48Automation products

Modular PLCs

I/O expansions for XC121

XIO-EXT121-1
Digital outputs
NumberAt X3: 8 (can also be used as inputs)

Rated voltage
Rated voltage

Ue

V DC

24
20.4 … 28.8 V DC

Permissible range
Ripple

%

≦5

Ie

A

0.5 at 24 V AC

%

g

1

Maximum duty factor

ms

100 %

Lamp load without Rv

W

5

Rated operational current
At state “1”Utilization factor

Potential isolation

No

Residual current at state “0” per channel

mA

< 0.1

At state “0” with external load < 10 MΩ

V

2.5

At state “1” at Ie = 0.5 A

V

U = Ue - 1 V

Short-circuit tripping current for Ra ≦ 10 mΩ

A

0.7 ≦ Ie ≦ 2 for output

Total short-circuit current

A

16

Peak short-circuit current

A

32

Ops/h

40000

Max. output voltage

Short-circuit tripping current

Max. operating frequency
Parallel connection capability

Yes

Analog inputs 0…10 V
Number of channels

2

Primary voltage range

V

0…10

Resolution

bit

10

Conversion timems≦5Overall accuracy≦ ± 1 % (of full-scale value)

Input resistance

kΩ

200

Analog inputs 0…20 mA
Number of channels

2

Primary voltage range

mA

0…20

Resolution

bit

10

Conversion timems≦5Overall accuracy≦ ± 1 % (of full-scale value)

Input resistanceΩ50

Pt100 RTD
Number of channels

2

Temperature range°C-200…+200

Resistance rangeΩ

18.5…175.8

Resolution

bit

10
≦ ±2%

Overall accuracy
Analog outputs
Number of channels

2Secondary voltage range

V

0…10

Resolution

bit

12

Conversion timems≦5Overall accuracy≦ ± 1 % (of full-scale value)

External load resistance2010 CA08103002Z-EN

R

www.eaton.comkΩ

10Modular PLCs

Automation products

14/49

PLCs
Modular PLCsPLCs

XC-CPU201-EC256K-8DI6DO(-XV)

XC-CPU201-EC512K-8DI6DO(-XV)

XC-CPU202-EC4M-8DI6DO-XV

IEC/EN 61131-2
EN 50178
0 - +55

IEC/EN 61131-2
EN 50178
0 - +55

GeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 to +70-25 to +70-25 to +70

Horizontal

Horizontal

Horizontal

Mounting position
Relative humidity, non-condensing (IEC/EN 60068-2-30)%

10 - 95

10 - 95

10 - 95

Air pressure (in operation)hPa

795 - 1080

795 - 1080

795 - 1080

Mechanical shock resistance

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

10 - 57 Hz ±0.075 mm
57 - 150 Hz ±1.0 g
15 g/11 ms

Overvoltage category

II

II

II

Pollution degree

2

2

2

Degree of protection

IP20

IP20

IP20

850

850

850

Emitted interference

EN 61000-6-4, Class A

EN 61000-6-4, Class A

EN 61000-6-4, Class A

Interference immunity

EN 61000-6-2

EN 61000-6-2

EN 61000-6-2

Battery (lifespan)

Normally 5 years

Normally 5 years

Normally 5 years

0.23

0.23

0.23

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Vibration resistance

Rated impulse withstand voltage

Uimp

WeightV

kg

Terminals
Terminal capacity
Screw terminals
Flexible with ferrule

mm2

0.5 - 1.5

0.5 - 1.5

0.5 - 1.5

Solid

mm2

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

Flexible

mm20.34 - 1.0

0.34 - 1.0

0.34 - 1.0

Solid

mm2

0.14 - 1.0

0.14 - 1.0

0.14 - 1.0

Spring-cage terminal

Electromagnetic compatibility (EMC)￫ Page 14/58

Power supply
Duration of mains failure

ms

10

10

10

Repetition rate

s

1

1

1

Input voltage

V DC

24

24

24

Permissible range

V DC

20.4…28.8

20.4…28.8

20.4…28.8

Input power

W

Max. 33

Max. 33

Max. 33

Ripple

%

≦5

≦5

≦5

W

6

6

6

Overvoltage protection

Yes

Yes

Yes

Protection against polarity reversal

Yes

Yes

Yes

Line filter

Yes

Yes

Yes

Maximum heat dissipation

Inrush current

Pv

x In

Not limited, (limiting only by a supply-side 24 V DC PSU)

Rated value

V DC

5

5

5

Output current

A

3.2

3.2

3.2

Short-circuit rating

Yes

Yes

Yes

Isolated from supply voltage

No

No

No

NEC VR4181 A MIPSNEC VR4181 A MIPS

ARM 532 MHz

Output voltage for signal modules

CPU
Microprocessor
MemoryProgram code/program data

256 kByte/256 kByte

2 MB/512 kByte

4 MB/512 kByte

Marker/retain data

kByte

16/32

16/32

16/64

Cycle time for 1 k of instructions (bits, bytes)

ms< 0.15< 0.15< 0.025

2010 CA08103002Z-EN

www.eaton.com

14/50Automation products

Modular PLCs

PLCs

XC-CPU201-EC256K-8DI6DO(-XV)

XC-CPU201-EC512K-8DI6DO(-XV)

XC-CPU202-EC4M-8DI6DO-XVInterfaces
Ethernet
Baud rate

10/100 - Autodetect

10/100 - Autodetect

10/100 - Autodetect

Connector type

MBit/s

RJ45

RJ45

RJ45

Potential isolation

No

No

No

Serial interface (RS232) without handshake lines
Baud rate

Max. 115.2

Max. 115.2

Max. 115.2

Connector typekbit/s

RJ45

RJ45

RJ45

Potential isolation

No

No

No

1.0

1.0

2.0

USB interface
CANopenMaximum data transfer rate

1

1

1

Potential isolation

Yes

Yes

Yes

Device profile

To DS 301 V4

To DS 301 V4

To DS 301 V4

PDO type

Asyn., cyc., acyc.

Asyn., cyc., acyc.

Asyn., cyc., acyc.

Connection

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Bus terminating resistors

External

External

internalMax. 126

Max. 126

Max. 126

Watchdog

Yes

Yes

Yes

RTC (real-time clock)

Yes

Yes

Yes

Stations

MBit/sNumberPower supply of local inputs/outputs (24 VQ/0 VQ)
Input voltage

V DC

24

24

24

Voltage range

V DC

19.2 - 30, observe polarity

19.2 - 30, observe polarity

19.2 - 30, observe polarity

Between power supply and CPU voltage

Yes

Yes

Yes

Between power supply and inputs/outputs

No

No

No

Status indication

LED

LED

LED

Terminals

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Overvoltage protection

Yes

Yes

Yes

Protection against polarity reversal

Yes

Yes

Yes

Normally 3.5

Normally 3.5

Normally 3.5

Normally 85 m W

Normally 85 m W

Normally 85 m W

Low < 5 V DC,
High > 15 V DC

Low < 5 V DC,
High > 15 V DC

Low < 5 V DC,
High > 15 V DC

Potential isolation

Digital inputs
Input current per channel at rated voltage

mA

Heat dissipation per channel
Voltage level to IEC/EN 61131-2
Limit value type 1
Input delay
OFF → ON

ms

Type 0.1

Type 0.1

Type 0.1

ON → OFFms

Type 0.1

Type 0.1

Type 0.1

InputsNumber8, of which parameterizable: 2 counters, 50 kHz, 2 interrupt inputs, 1 incremental input

Channels with the same reference potential

Number

8

8

8

LED

LED

LED

Status indication
Digital outputs
Channels

Number6

6

6

Heat dissipation per channel

W

0.08

0.08

0.08

Load circuits

A

0.5

0.5

0.5

OFF → ON

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

ON → OFF

Normally 0.1 ms

Normally 0.1 ms

Normally 0.1 ms

6

6

6

Status indication

LED

LED

LED

Switching capacity

IEC/EN 60947-5-1, utilization category DC-13

Output delay

Channels with the same reference potential

NumberDuty factor

% DF

100

100

100

Utilization factor

g

1

1

1

2010 CA08103002Z-EN

www.eaton.com

Modular PLCs

Automation products

14/51

I/O expansions XI/OC
Modular PLCsI/O expansions XI/OCGeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 to +70

Vibration resistanceMechanical shock resistance

10 - 57 Hz ± 0.075 mm
57 - 150 Hz ± 1.0 g
15 g/11 ms

Impact strength

500 g/50 mm ±25 g

Overvoltage category

II

Pollution degree

2Protection class1

Protection type

IP20

Emitted interference

DIN/EN 55011/22, Class A

Electromagnetic compatibility (EMC)￫ Page 14/58

Power supply
Rated voltage

Ue

V DC

Permissible range

24 (12)20.4 – 28.8 (11.8 – 14.4)%≦5

Duration of power failurems

10

Repetition rates

1

RippleSupply failure bridging

Technical dataXI/OC Digital Input Modules

XIOC-8DI

XIOC-16DI

XIOC-32DI

Modules
Input type

DC input

DC input

DC input

Input voltage

V DC

24

24

24

Permissible range

V DC

20.4…28.8

20.4…28.8

20.4…28.8

Input voltage

V AC

–

–

–

Permissible range

V AC

Input resistance

Normally 3.5 kΩ

Normally 5.9 kΩ

Normally 5.6 kΩ

mA

Normally 6.9

Normally 4.0

Normally 4.3

ONV≧ 15 DC≧ 15 DC≧ 15 DCOFFV≦ 5 DC≦ 5 DC≦ 5 DC

OFF → ONms

5 (normally 4)

5 (normally 4)

5 (normally 4)

OFF → ONms

5 (normally 4)

5 (normally 4)

5 (normally 4)

Input channels

Number8

16

32

Channels with the same reference potential

Number8

16

32

Potential isolation

With optocouplers

With optocouplers

With optocouplers

Indication

LED (green)

LED (green)

Terminals

Plug-in terminal block

Plug-in terminal block

Input current
Voltage level to IEC 61131-2, limit value type 1

Input delay

Internal current consumption (5 V DC)

mA

Normally 26

Normally 51

16 LEDs (green), switchable:
0 – 15, 16 – 31
XIOC-TERM32 (connector
and cable)
Normally 100

Weight

kg

0.16

0.16

0.16

2010 CA08103002Z-EN

www.eaton.com

14/52

Automation products

Modular PLCs

I/O expansions XI/OC
Modular PLCsI/O expansions XI/OC

XIOC-8DO

XIOC-16DO

XIOC-16DO-S

XIOC-32DO

Modules
Output typeTransistor (source type)Output voltage

V DC

24 (-15…+20 %)24 (-15…+20 %)24 (-15…+20 %)24 (-15…20 %)Switching current, minimum

mA

1

1

1

1

Leakage current

mA

0.1

0.1

0.1

0.1

Per circuit

A

0.3

0.3

0.8

0.2

Per common potential terminal

A

2.4

4

5

3.2

OFF → ON

ms

≦ 0.3

≦ 0.3

≦ 0.3

≦ 0.3

OFF → ON

ms

≦1

≦1

≦1

≦1

Output channels

Number

8

16

16

32

Channels with the same reference
potential
Overvoltage protection

Number

8

16

16

32

Diode

Diode

Integrated

Diode

Fuse rating

A

4

8

None

8

LED (green)

LED (green)

Maximum load current

Output delay

Potential isolation

With optocouplers

Indication

LED (green)

Terminals

Plug-in terminal block

Internal current consumption (5 V DC)
External voltage for outputs/module(30 mA for module supply)
Short-circuit protection

Us

WeightmA

Normally 30

Normally 50

Normally 50

16 LEDs (green),
switchable: 0 – 15, 16 – 31
XIOC-TERM32(connector and cable)
Normally 250

V

24 DC (-15/+20%)

24 DC (-15/+20%)

24 DC (-15/+20%)

24 DC (-15/+20%)

–

–

Yes

–

0.16

0.16

0.16

0.16

kg

XIOC-12DO-R

Modules
Output type

Relays

Output voltage

V DC

24

Output voltage

V AC

100/240

Switching current, minimummA

1

Per circuit

A

2

Per common potential terminalA

5

OFF → ONms

≦ 10

OFF → ONms

≦ 10

Output channels

Number12

Channels with the same reference potential

Number12

Maximum load current

Output delay

Overvoltage protection

External

Fuse ratingA

External

Potential isolation

With optocouplers

Indication

LED (green)

Terminals

Plug-in terminal block

Internal current consumption (5 V DC)

mA

External voltage for operating the relay
Weight2010 CA08103002Z-EN

24 V DC (-15 - +20%, max. 70 mA)kg

www.eaton.com

Normally 40
0.2Modular PLCs

Automation products

14/53

I/O expansions XI/OC
Modular PLCsI/O expansions XI/OC

XIOC-16DX

Power supply
Supply voltage
Ripple24 V DC (-15/+20%)%≦5

Overvoltage protection

Yes

Protection against polarity reversal

Yes

Potential isolation
Between power supply and I/O bus

Yes

Between power supply and I/O

NoInternal current consumption (5 V DC)

mA

Normally 80

Channels

Number16

Terminals

Plug-in terminal block

Status indication

LED

Inputs
Input type

DC input

Input voltage

V DC

24 V DC

InputsNumber4, 12, configurable

Input current

mA

Normally 4

ONV≧ 15 DCOFFV≦ 5 DC

OFF → ONms

Normally 0.1

OFF → ONms

Normally 0.1

Voltage level to IEC 61131-2, limit value type 1

Input delay

Outputs
Output typeTransistor (source type)Output voltage

V DC

12/24 (-15…+20 %)Output current

A

Normally 0.5

Outputs

NumberMax. 12, configurable

Short-circuit tripping current

A

Max. 1.2 over 3 ms for output

Lamp load

W

Max. 3Drop-out delay (High → Low)

μs

Normally 100

Switching capacity

IEC/EN 60947-5-1, utilization category DC-13

Short-circuit rating

Yes

Parallel connection of outputs

In groups 0 – 3, 4 – 7, 8 – 11;
Actuation of the outputs within a group only in the same program cycle
Max. 3

Number of outputs that can be switched in parallel
Total maximum currentA

2 for group

Weightkg

0.16

2010 CA08103002Z-EN

www.eaton.com

14/54

Automation products

Modular PLCs

I/O expansions XI/OC
Modular PLCsI/O expansions XI/OC

XIOC-8AI-I2

XIOC-8AI-U1

XIOC-8AI-U2

XIOC-4T-Pt

Modules
Input voltage

V DC

–

0 to 10-10 to +10–

Input currentmA

4 - 20–––Resolution, digital

bit

12

12

12

15 bit with sign

≦ 5 ms≦ 5 ms≦ 5 msConversion time
Total errors%≦ ± 1 (of full-scale value)

Input resistance

kΩ

–

–

100

100

–

No

No

No

no

8

8

8

4

Potential isolation
Circuit within each channel

With optocouplers

Between the input channels
Input channels

NumberTerminals

Plug-in terminal block

External power supply

24 V DC (-15/+20 %), approx. 150 mA

External resistance

R

kΩ

–

–

24 V DC (-15/+20 %), 100 mA–

max 0.4, 4 channels

Connection type2-core shielded cable (≦20 m)

Platinum RTD

–

–

–

Pt100 (IEC 751), Pt1000

Shielded cable

Accuracy-20 to 40 °C (Pt100)

°C

–

–

–

±0.5

-50 to 400 °C (Pt100)

°C

–

–

–

±3

-50 to 400 °C (Pt1000)

°C

–

–

–

±6

–

–

–

Normally 100

Normally 100

Normally 100-20 to +40 °C/-50 to +400 °C(uninterrupted current: 2 mA)
Max. 200–––

Linearisation-20 to 40 °C

–

–

–

-50 to 400 °C

–

–

–

–

–

–

0.18

0.18

0.18

≦ -25 °C or ≧ +45 °C = resistance value
7FFFFhex≦ -60 °C or ≧ +410 °C = resistance value
7FFFFhex
In these cases, the resistance value
is 7FFFhex
0.18

Temperature measuring range
Internal current consumption(5 V DC)
Additional function

mA

Fault detection

Response to cable break or unused
inputs
Weightkg

XIOC-4AI-T

Channels
Number4

Temperature measuring range

cold-junction compensation

Type K: -270…1370
Type J: -210…1200
Type B: 100…1800
Type N: -270…1300
Type E: -270…1000
Type R: -50…1760
Type T: -200…400- 50 mV…50 mV-100 mV…100 mV-500 mV…500 mV-1000 mV…1000 mV
Yes, built-in

Interference suppression

50 Hz, 60 Hz

Voltage measurement

Unit

0.1 °C, 0.1 F

Resolution

bit

16

Total errors%±0.5 of measurement range

Conversion time

<1s

Temperature coefficient< 200 ppm/°C of measurement range

2010 CA08103002Z-EN

www.eaton.com

Modular PLCs

Automation products

14/55

I/O expansions XI/OCI/O expansions XI/OC

Modular PLCs

XIOC-2AO-U1-2AO-I2

XIOC-4AO-U1

XIOC-2AO-U2

Modules
Output voltage

V DC

0 - 100 - 10-10 - 10Output currentmA

4 - 20––Resolution

bit

12

12

12

≦ 5 ms≦ 5 ms≦ 5 ms≧ 10 kΩ≧ 10 kΩ≧ 10 kΩ0 to 500 Ω––Conversion time
Total errors≦ ± 1 (of full-scale value)%

External load resistance
Voltage output
Current outputΩ

Potential isolation
Circuit within each channel

With optocouplers

Between channels

No

No

No

Output voltage

2 (channels 0 and 1)

4

2

Output current

2 (channels 2 and 3)––

Normally 100

Normally 100

Number of outputs

Terminals
Internal current consumption(5 V DC)
External power supply

Plug-in terminal block
Normally 100

mA

24 V DC (-15/+20 %), approx. 150 mA

Connection type2-core shielded cable (≦ 20 m)

XIOC-2AI-1AO-U1

XIOC-2AI-1AO-U1-I1

XIOC-4AI-2AO-U1

XIOC-4AI-2AO-U1-I1

Inputs
Input voltage

V DC

0 - 100 - 100 - 100 - 10

Input currentmA–

0 - 20–0 - 20Resolution

bit

14

14

14

14

< 1 ms< 1 ms< 1 ms< 1 msNormally 0.4

Normally 0.4

Normally 0.4

Normally 0.4

Conversion time
Total errors%

Potential isolation
Circuit within each channel

No

No

No

No

Between the input channels

No

No

No

No

Between input/output channels

No

No

No

No

Channels

Number2

2

4

4

Input resistance

kΩ

40

40

40

40

Outputs
Output voltage

V DC

0 - 100 - 100 - 100 - 10

Output currentmA–

0 - 20–0 - 20Resolution

bit

12

12

12

12

Normally 0.4 %Normally 0.4 %Normally 0.4 %Normally 0.4 %Circuit within each channel

No

No

No

No

Between the output channels

No

No

No

No

Number of channels

1

1

2

2

External load resistance≧ 2 kΩ≧ 2 kΩ≧ 2 kΩ≧ 2 kΩ

Short-circuit rating

Yes

Yes

Yes

Yes

ErrorsPotential isolation

Terminal connection
Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Plug-in terminal block

Internal current consumption (5 V DC)

Terminals
mA

Normally 200

Normally 200

Normally 200

Normally 200

Weight

kg

0.16

0.16

0.16

0.16

2010 CA08103002Z-EN

www.eaton.com

14/56

Automation products

Modular PLCs

I/O expansions IX/OC
Modular PLCsI/O expansions IX/OC

XIOC-NET-DP-M

XIOC-NET-DP-S

XIOC-NET-SK-M

XIOC-SERXIOC-TC1

PROFIBUS-DP, RS485,
EN 50170
PROFIBUS-DP master(class 1)

PROFIBUS-DP, RS485,
EN 50170
PROFIBUS-DP slave

RS485

RS232(C), RS422, RS485

RS232(C), RS422, RS485

Suconet K, K1

Character formats

–

–

–

Control and signal cables

–

–

–

9.6 to 12000

9.6 to 12000

187.5, 375

Tranparent mode,
Modbus Master/Slave,
SUCOM-A, DNP3
protocol8E1, 8O1, 8N1, 8N2, 7E2,
7O2, 7N2, 7E1
RTS, CTS, DTR, DSR,
DCD
0.3 …57.6

Potential isolation

Yes

Yes

Yes

Transparent mode,
Modbus master/slave,
SUCOM-A, Suconet-K
slave
8E1, 8O1, 8N1, 8N2, 7E2,
7O2, 7N2, 7E1
RTS, CTS, DTR, DSR,
DCD
0.3 …57.6
187.5, 375 (Suconet)Yes (RS485, RS422)

Number of slaves

124

–

16

–

–

Send/receive data

3500 Byte eachMax. 244 Byte

250 Byte each

250/500

Bus terminating resistors

Switchable

Switchable

Switchable

Connector typeD-sub 9-pin socket

D-sub 9-pin socket

Plug-in terminal block

Interfaces
Interfaces
ProtocolTransfer ratekbit/sYes (RS485, RS422)

Current consumption

mA

< 300

< 300

< 275

250 Byte per slave
120 Byte per slave(Suconet-K slave)
Switchable for RS485,
RS422
RS232: D-sub 9-pin
RS485, 422: plug-in
terminal block< 275

Weightkg

Approx. 0.2

Approx. 0.2

Approx. 0.2

Approx. 0.2

Approx. 0.2

XC100: 1
XC200: 3
1, 2, 3

XC100: 1
XC200: 3
1, 2, 3

XC100: 2
XC200: 4
Any

XC100: 2
XC200: 4
Any

XC200: 4

Number of modules
Slots

2010 CA08103002Z-EN

www.eaton.com

Switchable for RS485,
RS422
RS232: D-sub 9-pin
RS485, 422: plug-in
terminal block
< 275

Any

Modular PLCs

Automation products

14/57

I/O expansions IX/OC
Modular PLCsI/O expansions IX/OC

XIOC-1CNT-100KHZ

XIOC-2CNT-100KHZ

XIOC-2CNT-2AO-INC

InputsCounter limits

0 - 4294967295 (32 bit)

0 - 4294967295 (32 bit)

0 - 4294967295 (32 bit)Internal current consumption

mA

200

200

450

FrequencykHz

100 (25 with four times
resolution)
1

100 (25 with four times
resolution)
2

400 (100 with four times
resolution)
2

Input voltage

V DC

12 - 24

12 - 24–

Voltage for ON

V DC

> 10

> 10

–

Voltage for OFF

VA/W

<4

<4

–

Input current

mA

≧4

≧4

–

Differential input voltage

V DC

±5

±5

±5

Voltage for ON

V DC

2-5

2-5

0.2 - 5

Voltage for OFF

V DC-5 - 8-5 - 8-5 - -0.2

Differential input current

mA

35

35

5

Minimum pulse widthμs

ON ≧ 4OFF ≧ 4
With optocouplers

ON ≧ 4OFF ≧ 4
With optocouplers–

30-pin plug:
XIOC-TERM30-CNT4
Shielded, twisted pair cable

30-pin plug:
XIOC-TERM30-CNT4
Shielded, twisted pair cable

Plug-in terminal block

Output typeTransistor (open collector)

Transistor (open collector)

AnalogExternal power supply

12/24 V DC (30 max.)

12/24 V DC (30 max.)

–

mA

1

1

–

mA

20

20

–

Max. leakage current

mA

0.5

0.5

–

Max. voltage drop at ON

V

1.5

1.5

–

OFF → ON

ms

≦1

≦1

–

OFF → ON

ms

≦1

≦1

–

Number2

4

2

With optocouplers

With optocouplers–

Number of channels

Potential isolation
Connection for external cabling
External cabling–

Shielded, twisted pair cable

Outputs

Minimum load current
Maximum load current

Ie

Debounce OFF

Output channels
Potential isolation
Output voltage

V DC

–

–

-10 - 10

Resolution

bit

–

–

12

–

–

≦ 1 ms––Normally 0.4

Load resistance––≧ 1 kΩ

Connection for external cabling

30-pin plug:
XIOC-TERM30-CNT4
Shielded, twisted pair cable

30-pin plug:
XIOC-TERM30-CNT4
Shielded, twisted pair cable

Plug-in terminal block

–

–

≦ 300

–

–

5 V DC

Conversion time
Total errors%

External cabling
Current per channel

mA

Power supply of encoders

Shielded 2-core cable

Current consumption

mA

200

200

Max. 450

Weight

kg

0.16

0.16

0.18

2010 CA08103002Z-EN

www.eaton.com

14/58Automation products

Modular PLCs

I/O expansions XI/OC, EMC
Modular PLCsI/O expansions XI/OC, EMC

XT-FIL-1

XT-FIL-2

IEC/EN 61131-2
EN 50178
0 - +55

GeneralStandards
Ambient temperature°C

IEC/EN 61131-2
EN 50178
0 - +55

Storage°C-25 - +70

-25 - +70

Mounting position

Vertical or horizontal

Vertical or horizontal

Vibration resistanceMechanical shock resistance

10 - 57 Hz ± 0.075 mm
57 - 150 Hz ± 1.0 g
15 g/11 ms

10 - 57 Hz ± 0.075 mm
57 - 150 Hz ± 1.0 g
15 g/11 ms

Impact strength

500 g /50 mm ±25 g

500 g/50 mm ±25 g

Overvoltage category

II

II

Pollution degree22Protection type

IP20

IP20

850

850

EN 61000-6-2

EN 61000-6-2

Rated impulse withstand voltage

Uimp

V

Interference immunity
Weight

kg

0.1

0.1

Dimensions (W x H x D)mm

35 x 90 x 30

35 x 90 x 57

Screw terminals

Screw terminals

Terminals
Terminal capacity
Screw terminals
Flexible with ferrulemm2

0.2 - 2.5 (AWG22 - 12)

0.2 - 2.5 (AWG22 - 12)

Solid

mm2

0.2 - 2.5 (AWG22 - 12)

0.2 - 2.5 (AWG22 - 12)

Power supply
Input voltage

V DC

24

24

Permissible range

V DC

20.4…28.8

20.4…28.8

Ripple

%

≦5

≦5

Yes

Yes

Mains overvoltage protection
Potential isolation
Between input voltage and PE

Yes

Yes

Between input voltage and output voltage

No

No

Between output voltage and PE

Yes

Yes

Rated value

V DC

24

24

Output current

A

2.2

12

General information on electromagnetic compatibility (EMC) of automation systems
Emitted interference
Interference immunity
ESD

EN 55011/22 Class A (VDE 0875, Part 11)
IEC/EN 61000-4-2

RFI
Mobile phones/cellphones
Burst

IEC/EN 61000-4-3
IEC/EN 61000-4-3
IEC/EN 61000-4-4

Surge

IEC/EN 61000-4-5

Conducted interference,induced by high-frequency fields

IEC/EN 61000-4-6;
2003

2010 CA08103002Z-EN

www.eaton.com

Contact discharge
Air discharge
AM (80 %)80 - 1000 MHz
PM
800 - 960 MHz
Mains/digital I/O (direct)
Analog I/O, fieldbus (capacitive coupling)
Digital I/O, asymmetric, analog I/O, asymmetric, connection to shielding
Mains DC, asymmetric
Mains DC, symmetric
Mains AC, asymmetric
Mains AC, symmetricAM (80 %)150 kHz - 80 MHz

4 kV
8 kV
10 V/m
10 V/m
2 kV
1 kV
0.5 kV
1 kV
1 kV
0.5 kV
2 kV
1 kV
3V

Modular PLCs

Automation products

14/59

Dimensions
Modular PLCs

100

XC-CPU101
XC-CPU201
XC-CPU202

60

100

73

100

XIOC…

50

95

21

95

5

30

Backplanes
XIOC-BP-2
XIOC-BP-XC

XIOC-BP-3
XIOC-BP-EXT
XIOC-BP-XC1
39

53.5

90

3

50

53.5

50
1

1

50

53.5

50

53.5

8.5

88

3.5

3

35.5
4.5

M4

39
60

3.5

14
21

16

16

60

2010 CA08103002Z-EN

www.eaton.com

14/60Automation products

Modular PLCs

156

XV-101…

134

212

6

142

Mounting dimensions

198

XT-RJ45-ETH-RS232

50

35

100

90 mm (3.54”)

50

XC-CPU-121...
XIO-EXT121-1

35 mm(1.38”)

47

90

22.75

37.25

8.5

6.8

88

6

16

4.5

2010 CA08103002Z-EN

www.eaton.com

30 mm(1.18”)

Modular PLCs

Automation products

14/61

2010 CA08103002Z-EN

www.eaton.com

90

XT-FIL-1

35

30

XT-FIL-2

110

102

90

45

7.5

4.5
47.5
56.5
M4
7.5
35.5

14/62

Automation productsCompact PLCs

System overview
Compact PLCs

3
4
2
2

2
2

1

1

5

6

7

8

C

ES
POW

T
AL

L

DE

BUS

POWER
COM-ERR

ERR

C

ES

MS

OK

ADR

NS

14

11
12

10, 13

9

14

11

13

2010 CA08103002Z-EN

www.eaton.com

Compact PLCs

Automation products

Basic device
EC4P

I/O expansion modules
1

Expandable: Digital and analog inputs/
outputs and bus systems AS-Interface,
CANopen, PROFIBUS-DP, DeviceNet;
Ethernet optional
Bus system easyNet on board
24 V DC
12 digital inputs
4 of which usable as analog inputs
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
1 analog output optional
Display and keypad optional
Screw and top-hat rail fixing
Screw terminals￫ Page 14/64

Remote text display
Consists of:• Text display MFD-80..(-B)• CANopen interface module
MFD-CP4-CO (order connection cable
EU4A-RJ45-CAB2 separately)• Power supply unit/communication
card, including connection cable(5 m, can be cut to desired length)
for EC4P
24 V DC = MFD-CP4-800
100 - 240 V AC = MFD-AC-CP4-800
Spring-cage terminals￫ Page 14/66

EASY411-DC-ME

2, 3, 42
3
4

EASY200-EASY

12

For remote connection of a digital I/O
expansion module through two-poleconnection cable (max. 30 m);e.g. NYM 3 × 1.5 mm2￫ Page 14/65

CANopen expansion modules
EC4E-221…

10

14

24 V DC
6 digital inputs
4 relay outputs or
4 transistor outputs￫ Page 14/65

11

24 V DC
12 digital inputs
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
Screw and top-hat rail fixing
Screw terminals￫ Page 14/65
5

6

AS-Interface connection as slave,
24 V DC￫ Page 14/66

EASY221-CO

10

24 V DC
1 digital input
6 analog inputs (2 × 0-10 V and2 × 0-20 mA and 2 × Pt100 RTD;
voltage inputs 0-10 V can optionallybe used as digital inputs)
2 analog outputs (0 - 10 V)
2 transistor outputs
Screw and top-hat rail fixing
Screw terminals￫ Page 14/65

EASY6...

PROFIBUS-DP interface,connection as slave
24 V DC￫ Page 14/66

EASY205-ASI

Coupling module

24 V DC
1 digital input
2 analog inputs (2 × 0-10 V or
2 × 0-20 mA or 2 × Pt100 RTD;
voltage inputs 0-10 V can optionallybe used as digital inputs)
1 analog output (0 - 10 V)
2 transistor outputs
Screw and top-hat rail fixing
Screw terminals￫ Page 14/65

Bus modules
EASY204-DP

EASY406-DC-ME

14/63

EASY410...

13

24 V DC
6 digital inputs
4 relay outputs (max. 10 A, UL) or
4 transistor outputs
Screw and top-hat rail fixing
Screw terminals￫ Page 14/65

7

CANopen interface, 24 V DC
￫ Page 14/66

EASY222-DN

8DeviceNet interface, 24 V DC
￫ Page 14/66

Output expansion
EASY202-RE

9

2 relay outputs (max. 10 A, UL)
Screw and top-hat rail fixing
Screw terminals￫ Page 14/65

2010 CA08103002Z-EN

www.eaton.com

14/64

Automation productsCompact PLCs

PLCs
HPL14064EN
Compact PLCsPLCs

Inputs

Outputs

DigitalOf which can beused as analog

Relay 10 A
(UL)Transistor

AnalogOtherfeatures
Display +keypadSupply voltage
connection

Part no.
Article no.

Price
See price list

24 V DC

EC4P-221-MTXD1
106391
EC4P-221-MTXX1
106392
EC4P-221-MRXD1106393
EC4P-221-MRXX1
106394EC4P-221-MTAD1
106395
EC4P-221-MTAX1
106396
EC4P-221-MRAD1
106397
EC4P-221-MRAX1
1063981 off

24 V DC

EC4P-222-MTXD1
106399EC4P-222-MTXX1106400EC4P-222-MRXD1
106401
EC4P-222-MRXX1
106402
EC4P-222-MTAD1
106403
EC4P-222-MTAX1
106404EC4P-222-MRAD1
106405
EC4P-222-MRAX1
106406

1 off

Std. packeasyControl
Expandable: Inputs/outputs and bus systems
Individual laser inscription possible with EC4-COMBINATION-* ￫ Page 14/69

easy NET/CANopen on board
12

4

–

8

–

✓

12

4

–

8

–

–

12

4

6

–

–

✓

12

4

6

–

–

–

12

4

–

8

1

✓

12

4

–

8

1

–

12

4

6

–

1

✓

12

4

6

–

1

–

easyNet/CANopen and Ethernet on board
12

4

–

8

–

✓

12

4

–

8

–

–

12

4

6

–

–

✓

12

4

6

–

–

–

12

4

–

8

1

✓

12

4

–

8

1

–

12

4

6

–

1

✓

12

4

6

–

1

–

Notes
1
2
3

1
4
CANopen/easyNet

Accessories
1 Power supply unit/communication card
2 Display/keypad
3 Programming software
4 PC programming cable
5 Switched-mode power supply unit
6 Memory card
7 Input/output expansion module
8 Output expansion, bus module, coupling module

Ethernet

Power

Information relevant for export to North America
EC4P

5

EC4P

6

4

Product Standards

7
1

7

Power

8

2010 CA08103002Z-EN

www.eaton.com

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC: see Technical Data; UL508;
CSA-C22.2 No. 0-M; CSA-C22.2 No. 142-M;
CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Pagea 14/66
a 14/66
a 14/130a 14/67
a 14/131
a 14/67
a 14/65
a 14/65

Compact PLCs

Automation products

14/65

Expansion Devices
HPL14065EN
Compact PLCsExpansion Devices

Inputs

Outputs

DigitalRelay
10 A (UL)

Transistor

6

–

–

8

SupplyvoltagePart no.
Article no.

Price
See pricelist

100 - 240 V
AC
24 V DCEASY618-AC-RE
212314
EASY620-DC-TE
212313

Std. pack

Information relevant for export toNorth America

1 off

Product Standards

I/O expansion modules
Can be used through easyLink
12
12
Power

12

6

–

24 V DC–2–

24 V DC

6

4–

24 V DC

6–

4

24 V DCUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

EASY618-DC-RE
232112
EASY202-RE1)
232186

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

EASY410-DC-RE
114293
EASY410-DC-TE
114294NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508; CE marking
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical
Data; UL 508; CE marking
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
E135462
NRAQ, NRAQ70125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: Request filed for UL and
CSA
IEC: IP20, UL/CSA Type: -Can be used through CANopen for: XC100/200, EC4P, MFD4, XV
6

4–24 V DC

6–

4

24 V DC

EC4E-221-6D4R1
114296
EC4E-221-6D4T1
114297

1 off

NA Certification

1 off

Degree of Protection

EASY200-EASY
212315

1 off

Product Standards

Request filed for UL and
CSA
IEC: IP20, UL/CSA Type: -Coupling modules
Can be used through easyLink
For remote connection of a digital I/O
expansion up to 30 m.

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

InputsDigital / Analog

Supply voltage

Part no.
Article no.

1

24 V DC2

24 V DCEASY406-DC-ME
114295
EASY411-DC-ME116567

Outputs
Of whichusable as
digitalRelay
10 A (UL)

Transistor

Analog

1 / 2 2)2–

2

1 / 6 3)

2–

2

IEC/EN see Technical
Data; UL 508; CE marking;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -

Price
See
price list

Std. pack

I/O expansion modules
Can be used through easyLink

Notes1) Not for use in combination with basic device EASY719-DA-…

Cannot be used on coupling module EASY200‐EASY coupling
module2) 2 × 0 - 10 V, 2 × 0 - 20 mA, 2 × Pt100 RTD (2/3-conductor
connection); any combination
Voltage inputs (0 -10 V) can optionally be used as digital inputs
3) 2 x 0 - 10 V, 2 x 0 - 20 mA, 2 x Pt100 RTD(2/3 conductor
connection);
Voltage inputs (0 -10 V) can optionally be used as digital inputs

1 off
1 off

Information relevant for export to North America
NA Certification
Degree of Protection

Request filed for UL and CSA
IEC: IP20,
UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/66

Automation productsCompact PLCs

Accessories
HPL14066EN
Compact PLCsAccessories

Supplyvoltageconnection

Part no.
Article no.

Slave
4 inputs,
4 outputs,
4 parameter
bits
Assignable
addresses
0 to 31
Slave
Assignable
addresses
1 to 126

24 V DCEASY205-ASI
22159824 V DCEASY204-DP
212316

CANopen

Assignable
addresses
1 to 127

24 V DCEASY221-CO
233539DeviceNet

Assignable
addresses
0 to 63

24 V DCEASY222-DN
233540Description

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Bus modules
ASInterface

PROFIBUS-DPUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see TechnicalData;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Remote text display
Display/keypad
Monochrome display, 132 × 64 pixels with switchable backlight
IP65, removable titanium front frameWith keypad and Moeller logotype
NEMA 4x in combination with protective
membrane MFD-XM-80 ￫ 14/69
With keypad, without Moeller logotype
NEMA 4x in combination with protective
membrane MFD-XM-80 ￫ 14/69

Power supply unit/communication cards
IP20, can be combined with display/operating unit MFD-80...
as remote text display for easyRelay
Without connection cable
24 V DC
Without connection cable

100 - 240 V AC

MFD-80-B
265251

1 off

MFD-80-B-X
284905

1 off

MFD-CP4
280888MFD-AC-CP4
286822

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, in combination
with MFD-XM-80: UL/CSA
Type: 4X

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Compact PLCs

Automation products

14/67

Accessories
HPL14067EN
Supplyvoltageconnection

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export toNorth America

MFD-CP4-CO
115736

1 off

NA Certification

Request filed for UL and CSA

NA Certification

Request filed for UL and CSA

CANopen communication card
Communication card with CANopen interface
For use with display/operating unit MFD-80-B(-X) and connection
cable EU4A-RJ45-CAB2 (￫ Page 14/67)
Automatic baud rate setting up to 1 MBaud;Up to 64 display pages can be saved.
24 V DC–

Programming cable–USB, 2 m

EASY800-USB-CAB
106408

1 off–

D-sub 9-pin, serial, 2 m

EU4A-RJ45-CAB1
106726

1 off

For EU5C, XC and EC4P via
USB interface

EU4A-RJ45-USBCAB1
1157351 off

2m
Ethernet cross
5m
Ethernet cross

XT-CAT5-X-2
256487
XT-CAT5-X-5
256488

1 off

Configurable modem, printer andprogramming cable, possible transfer
rate 56 kBaud,D-sub 9-pin(plug + socket for assembly by user)

EASY800-MO-CAB
2860791 off–

For connecting EC4P (RJ45)
to MFD-CP4-CO or EC4E
(terminal block)

EU4A-RJ45-CAB2
115387

1 off

NA Certification

Request filed for UL and CSA–

Adapter with at least
64 MByte memory card

EU4A-MEM-CARD11064091 off

NA Certification

Request filed for UL and CSAWith plug-in power
supply unit
100 - 240 V AC/
24 V DCEASY800-DC-SIM
256278––1 off

Modem cable

Connecting cables

Memory cards

Input/output simulator
24 V DC2010 CA08103002Z-EN

www.eaton.com

14/68Automation productsCompact PLCs

Accessories
HPL14068EN
For use withPart no.
Article no.

Std. pack

Information relevant for export to North America

Length: 0.3 m

easyNet

EASY-NT-30
256283
EASY-NT-80
256284EASY-NT-150
256285

1 off

Product Standards

Length: 0.8 m

easyNetLength: 1.5 m

easyNet8-pin, RJ45, 124 ΩConnection to PIN 1
and PIN 2

easyNet

EASY-NT-R
256281

2 off

4 x 0.14 mm², twisted
pair, AWG 26
Length: 100 m

easyNet

EASY-NT-CAB
2562868-pin, RJ45

easyNet

EASY-NT-RJ45
256280Description

Price
See pricelist

Network connection cables

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -1 off

UL File No.
UL CCN
NA Certification
Degree of Protection

E135462
NRAQ
UL Listed
IEC: IP 20, UL/CSA Type: -10 offProduct Standards

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Bus termination resistor

Data cableBus connector plug

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Crimping tool–

EASY-RJ45-TOOL
256282

1 off

ZB4-900-KB1
206983100 m

9-pin male
Cable entry, angled 90°

ZB4-209-DS2
206982

1 off

Metalized insulated housing
Maximum transfer rate 12 MBit/s
Integrated switch (accessible From
the outside) for the bus terminating
resistors
Terminal block for two cable entries,
with straight or 90° angled cable entry,
as required

ZB4-209-DS3
217820

1 off

Bus connector plug between base unit
and expansion unit/bus module

EASY-LINK-DS
221607

1 off

UL/CSA certification not required

ZB4-101-GF1
061360

9 off

UL/CSA certification not required

For RJ45 plug

EASY-NTCABEASY-NTRJ45

PROFIBUS-DP data cable
Twisted pair, without plug, 2-core,2 x 0.64 mm²(only suitable for fixed wiring)
100 m

PROFIBUS-DP bus connector plug

Connection plug

Fixing bracket
For screw fixing to mounting plate
3 fixing brackets
for easy400, 500, 600, 700, 800, EC4P,
ES4P
2 fixing brackets for easy200
3 fixing brackets for MFD-CP8…,
MFD-AC-CP8…

2010 CA08103002Z-EN

www.eaton.com

Compact PLCs

Automation products

14/69

Accessories
HPL14069EN
Description

For use withPart no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Telescopic clip
For use with 35 mm top-hat rail to IEC/EN
60715 for mounting depth compensation
when rear mounting in enclosures CI-K... andpanels.
Stepless adjustment via scale from75 – 115 mm.
Screw and snap mounting

M22-TA
226161UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN 60947-5; UL 508;
CSA-C22.2 No. 14-05; CSAC22.2 No. 94-91; CE marking
E29184NKCR
0125283211-03
UL Listed, CSA certified

Top-hat rail adapter for hinged inspection window
SKF-HA
233782

1 off

UL/CSA certification not required

94 mm x 77 mm x 25 mm (4 space units)
For use with easy500
130 mm x 77 mm x 25 mm (6 space units)
For use with EASY700, EASY800, EC4P, ES4P

SKF-FF4
233780SKF-FF6
233781

1 off

UL/CSA certification not required

Transparent
Protection against
accidental actuation
SealableUse without front frame

MFD-80…

MFD-XS-80
2652591 off

Product Standards

Transparent type for harshenvironmental conditions
and application in the foodindustry
For increasing the degree ofprotection to NEMA 4X for
MFD-80-B

MFD-80…

12 mm x 66 mm x 82 mm
Installation on hinged inspection window, forfront fitting of devices.
Complete set, consisting of 2 brackets and4 screws

Hinged inspection window

Protective cover

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN see Technical Data;
UL 508; CSA C22.2
No. 142-M1987; CSA C22.2
No. 213-M1987; CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified

Protective diaphragm
MFD-XM-80
265258

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508; CSA C22.2
No. 142-M1987; CSA C22.2
No. 213-M1987; CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, UL/CSA Type:°4X

Supply voltage
connection

Description

For use withPart no.
Article no.

Price
See price
list

Std. pack

Information relevant for export toNorth America

MFD-COMBINATION-*
265260

1 off

UL/CSA certification not required

EC4-COMBINATION-*1)
107600

1 off

Custom labeling, user program• Custom labeling of multi-function display with labeling MFD-80-X
software Labeleditor or
MFD-80-B-X• Supply of multi-function display programmed with user
program• Custom labeling of easy Control with labeling software EC4P
Labeleditor or supply of easyControls programmedwith user program
Notes

Example for using the Labeleditor la beling software
Individually label your device in 4 stages:– Download the labeling software: www.moeller.net/support, keyword: "Labeleditor"– Create a label template (menu-guided in the software)– Mail the label template to the factory. The program automatically selects the correct e-mail address for the selected product and assigns a file
name, such as “EASY_12345.zip”. This file name is part of the article to be ordered (see Ordering examples).
– Send your order to your Eaton sales office or your electrical wholesaler.
Ordering example: MFD-Titan
MFD-80-B multi-function display with “company name”:
1 x MFD-COMBINATION-*
1 x MFD-80-B
1 x the file name “MFD_xxxxx.zip” issued by the Labeleditor

Ordering example: EC4P
EC4P-221-MTXD1 with “company name”:
1 x EC4-COMBINATION-*
1 x EC4P-221-MTXD1
1 x the file name “EC4P_xxxxx.zip” issued by the Labeleditor

2010 CA08103002Z-EN

www.eaton.com

14/70Automation productsCompact PLCs

PLCs

Technical data
Compact PLCsPLCs

EC4P…
GeneralStandards

EN 55011, EN 55022, IEC/EN 61000-4, IEC 60068-2-6, IEC 60068-2-27

Dimensions (W x H x D)mm

107.5 x 90 x 72 without/79 with adapter for memory card

Weightkg

0.3

Mounting

Top-hat rail IEC/EN 60715, 35 mm or screw fixing with 3 fixing brackets
ZB4-101-GF1 (accessories)

Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

Max. tightening torque

Nm

0.6

°C

-25…55, low temperatures to IEC 60068-2-1, high temperatures to IEC 60068-2-2

Ambient climatic conditions
Operating ambient temperature
Condensation

Prevent condensation by means of suitable measures

LCD display (clearly legible)°C

0 - 55Storage°C-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 95Air pressure (in operation)hPa

795 - 1080

Ambient mechanical conditions
Pollution degree

2

Degree of protection (IEC/EN 60529, EN50178, VBG 4)

IP20

Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

Constant acceleration, 2 g

Hz57 - 150

Shocks

18

mm

50

m

1

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to (IEC/EN 60068-2-31)
Free fall, packaged (IEC/EN 60068-2-32)

DropheightMounting position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Electrostatic discharge (IEC/EN 61000-4-2, Level 3, ESD)
Air dischargekV

8Contact discharge

kV

6

V/m

10

Electromagnetic fields (RFI), to IEC EN 61000-4-2
Radio interference suppression

EN 55011 Class B, EN 55022 Class B

Burst pulses (IEC/EN 61000-4-4, Level 3)
Supply cableskV

2

Signal cableskV

2

Surge pulses (IEC/EN 61000-4-5, Level 2)kV

0.5 (supply cables, symmetrical, EASY…DC)

Line-conducted interference (IEC/EN 61000-4-6)

V

10

Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

Real-time clock accuracy/backup time
Back-up timeaAccuracy of the real-time clock

s/day

200
180
160
140
120
100
80
60
40
20
0

25°C
55°C

0

1

2 3

4

5

6

7

8

9

① Backup time (hours)② Service life (years)
Normally ± 5 (± 0.5 h ⁄ year)

Retentive memory
Write cycles of the retentive memory (minimum)2010 CA08103002Z-EN

www.eaton.com

10 11 12 13 14 15 16 17 18 19 20b

10000000 (10¹0) (read ⁄ write cycles)Compact PLCs

Automation products

14/71

PLCs
Compact PLCsPLCs

EC4P-221...

EC4P-222...

Power supply
Rated operational voltage

V

24 DC (-15/+20%)

24 DC (-15/+20%)

Permissible range

Ue

V DC

20.4 - 28.8

20.4 - 28.8

Ripple%≦5≦5At rated voltage

mA

Normally 140

Normally 140

At rated operating voltage with load

A

–

–

Voltage dips (IEC/EN 61131-2)

ms

10

10

Heat dissipation

W

Normally 3.4

Normally 3.4

Infineon XC161

Infineon XC161

Input current

CPU
Microprocessor
MemoryProgram code/data

kByte

256/14 segments of 16 KB each

256/14 segments of 16 KB eachMarker/input/output/retain datakByte

16/4/4/8

16/4/4/8

Cycle time for 1 k of instructions (bits, bytes)

ms

< 0.3

< 0.3

kBit/s4.8, 9.6, 19.2, 38.4, 57.6, 115.2 (character format: 8 data bits, no parity, 1 stop bit)Interfaces
COM1 (RS232) without control cables
Data transfer rate for programming
Connections

RJ45 bus

RJ45 bus

Potential isolation

None

None

In the transparent mode
0.3, 0.6, 1.2, 2.4, 4.8, 9.6, 19.2, 38.4, 57.6

0.3, 0.6, 1.2, 2.4, 4.8, 9.6, 19.2, 38.4, 57.6

Character formats

Baud rate

kBit/s

8E1, 8O1, 8N1, 8N2, 7E2, 7O2, 7N2, 7E1

8E1, 8O1, 8N1, 8N2, 7E2, 7O2, 7N2, 7E1

Number of transmission bytes in a block

190 Byte

190 Byte

Number of received bytes in a block

190 Byte

190 Byte

Ethernet (for programming)–

10 MBit/s, 100 m

Connection type

Data transfer rate/distance

MBit/s–

RJ45

Potential isolation–

No

500 kBit/s, 25 m
250 kBit/s, 60m
125 kBit/s, 125 m
50 kBit/s, 300 m
20 kBit/s, 700 m
10 kBit/s, 1000 m

500 kBit/s, 25 m
250 kBit/s, 60m
125 kBit/s, 125 m
50 kBit/s, 300 m
20 kBit/s, 700 m
10 kBit/s, 1000 m

CANopen/easyNet
Data transfer rate/distance

Potential isolation
From power supply

Yes

Yes

From the inputs

Yes

Yes

From the outputs

Yes

Yes

Bus termination (first and last station)

EASY-NT-R plug (incl. bus terminating resistor 120 Ω)Connections

2 x RJ45, 8-pin

2 x RJ45, 8-pin

88Max. 126

Max. 126

Control operating mode easyNet
Number of users
CANopen operating mode
Stations

Number

PDO type

Asynchronous, cyclic, acyclic

Device profile

To DS 301 V4

To DS 301 V4––

Analog outputs
NumberPotential isolation
From power supply

No

No

From the digital inputs

No

No

From the digital outputs––

To network easyNet, easyLink

–

–

–

–

Output type
Signal range

V DC

0 - 100 - 10Conversion time, analog/digital

ms

bit

bit

2010 CA08103002Z-EN

www.eaton.com

14/72

Automation productsCompact PLCs

PLCs
Compact PLCsPLCs

EC4P…
Digital inputs 24 V DC
Number12

Inputs can be used as analog inputs

4 (I7, I8, I11, I12)

Status indication

LCD display (if fitted)

Potential isolation
From power supplyNo

Between digital inputs

No

From the outputs

Yes

From network easyNet, easyLink

Yes

Rated operating voltage

Ue

V DC

24

At state ”0”

Ue

V DC

< 5 (I1 - I6, I9, I10) < 8 (I7, I8, I11, I12)

At state ”1”

Ue

V DC

> 15.0 (I1 - I6, I9, I10), > 8.0 (I7, I8, I11, I12)

Input current at state “1”I1 to I6mA

3.3 (at 24 V DC)

I7, I8mA

2.2 (at 24 V DC)

I9, I10mA

3.3 (at 24 V DC)

I11, I12mA

2.2 (at 24 V DC)

Delay time from 0 to 1

msNormally 0.02 (I1 - I4), Normally 0.25 (I5 - I12)

Delay time from 1 to 0msNormally 0.02 (I1 - I4), Normally 0.25 (I5 - I12)

Cable length (unshielded)m100

Incremental encoder
Number1 (I1, I2, I3, I4)

Value range

32 bitCounter frequency

kHz

≦ 40

Pulse shape

SquareCounter inputs

I1, I2

Reference input

I3

Input for reference switch

I4

Signal offset

90°

Rapid counter inputs
Number2 (I1, I2) at 16 bit or 1 (I1) at 32-bit

Value range

16/32-bit

Cable length, shielded

m

< 20

Counter frequency

kHz

< 50

Pulse shape

SquareAnalog inputs
Number4 (I7, I8, I11, I12)

Potential isolation
From power supply

No

From the digital inputs

No

From the outputs

Yes

From network easyNet, easyLink

Yes
DC voltage

Input type
Signal range

V DC

0 - 10Resolution, analog

V

0.01

Resolution, digital

V

0.01

Resolution, digitalbit

10 (value 0 - 1023)

Input impedance

kΩ

11.2

Two devices%±3

Within a single device%± 2, (I7, I8, I11, I12) ± 0.12 V

Conversion time, analog/digitalmseach CPU cycle

Input current

mA<1

Cable length shielded

m

< 30

Accuracy of actual value

2010 CA08103002Z-EN

www.eaton.com

Compact PLCs

Automation products

14/73

PLCs
Compact PLCs

EC4P-…-MT…
Transistor outputs
Number8

Rated operating voltage

Ue

V DC

24

Permissible range

Ue

V DC

20.4 - 28.8

%

≦5

mA

18/32

mA

24/44

RippleSupply current
At state ”0”

Normally.⁄max.
Normally.⁄max.

At state ”1”
Protection against polarity reversal

Yes (Caution: A short circuit will result if 0 V or GND
is applied to the outputs if the supply voltage isconnected to the wrong poles.)Potential isolation
From power supply

Yes

To PC interface, memory card, network NET, easyLink

Yes

From the inputs

Yes

Rated operational current at state “1” DC

Ie

AMax. 0.5

Lamp load without Rv

W

5

Residual current at state “0” for channel

mA

< 0.1

At state “0” with external load < 10 MΩ

V

2.5

At state “1” at Ie = 0.5 A

V

U = Ue -1 V

Short-circuit tripping current for Ra ≦ 10 mΩ

A

Yes, electronic (Q1 – Q4), thermal (Q5 – Q8),
(analysis via diagnostics input I16, I15)
0.7 ≦ Ie ≦ 2 for output

Total short-circuit current

A

16

Peak short-circuit current

A

32

Max. output voltage

Short-circuit protection

Thermal cutout

Yes

Max. operating frequency at constant resistive load RL < 100 kΩ(dependent on program and load)
Parallel connection of outputs
With resistive load, inductive load with external suppressor circuit,
combination within a group
Number of outputs
Max. total current

Ops/h

40000

Group 1: Q1 to Q4
Group 2: Q5 to Q8
4

max.
A

2 (Caution! Outputs must be actuated simultaneously
and for the same duration.)
LCD display (if fitted)

Utilization factor

g

0.25

Duty factor

% DF

100

Max. operating frequency f = 0.5 Hz(max. DF = 50 %)Operations

1500

Utilization factor

g

0.25

Duty factor

% DF

100

Max. operating frequency f = 0.5 Hz(max. DF = 50 %)Operations

1500

Utilization factor

g

0.25

Duty factor

% DF

100

Max. operating frequency f = 0.5 Hz(max. DF = 50 %)Operations

1500

Output status indication
Inductive load to EN 60947-5-1
Without outer suppressor circuit
T0.95 = 1 ms, R = 48 Ω, L = 16 mH

DC-13, T0.95 = 72 ms, R = 48 Ω, L = 1.15 H

T0.95 = 15 ms, R = 48 Ω, L = 0.24 H

With outer suppressor circuit
Utilization factorg1

Duty factor

% DF

100

Max. operating frequency, max. duty factor

Operations

Depending on the suppressor circuit

2010 CA08103002Z-EN

www.eaton.com

14/74

Automation productsCompact PLCs

PLCs

EC4P-...-MR...
Relay outputs
Number6

Outputs in groups of1

Parallel switching of outputs to increase performance

Not permissible

Protection of an output relay

Miniature circuit-breaker B16 or fuse 8 A (slow)

Potential isolation
From power supply

Yes

From the inputs

Yes

From PC interface, memory card, network NET, easyLink

Yes

Safe isolation

V AC

300

Basic insulation

V AC

600

x 106

10

Lifespan, mechanical

Operations

Contacts
Conventional thermal current (10 A UL)A

8Recommended for 12 V AC/DC load

mA

> 500

Short-circuit proof p.f. = 1, characteristic B16 at 600 A

A

16

Short-circuit proof p.f. = 0.5 - 0.7; characteristic B16 at 900 A

A

16

Rated impulse withstand voltage Uimp contact coil

kV

6

Ue

V AC

250

Ui

V AC

250

Safe isolation to EN 50178 between coil and contact

V AC

300

Safe isolation to EN 50178 between two contacts

V AC

300

Rated operating voltage
Rated insulation voltage

Making capacity
AC-15, 230 V AC, 3 A

Operations

300000DC-13, 24 V DC, 0.1 Hz

Operations

200000AC-15, 250 V AC, 3 A (600 ops./h)Operations

300000DC-13, L/R ≦ 150 ms, 24 V DC, 1 A (500 ops./h)Operations

2000001000 W at 230/240 V AC

Operations

25000

500 W at 115/120 V AC

Operations

25000

With series-connected electrical device

Operations

25000

UncompensatedOperations

25000

Operations

25000

Breaking capacity

Filament bulb loadFluorescent lamp loadFluorescent lamp load 10 x 58 W at 230/240 V AC

Fluorescent lamp load 1 x 58 W at 230/240 V AC, conventionally compensatedSwitching frequency
Mechanical operations

x 106

10

Switching frequency

Hz

10

Resistive load/lamp load

Hz

2

Inductive load

Hz

0.5

Continuous current at 240 V AC

A

10Continuous current at 24 V DC

A

8

UL/CSAAC
Control circuit rating codes (utilization category)

B 300 Light Pilot Duty

Max. rated operational voltage

V AC

300

Max. thermal continuous current p.f. = 1 at B 300

A

5Max. make/break capacity p.f. ≠ 1 at B 300

VA

3600/360

DC
Control circuit rating codes (utilization category)

R 300 Light Pilot Duty

Max. rated operational voltage

V DC

300

Max. thermal continuous current p.f. at R 300

A

1

Max. make/break capacity at R 300

VA

28/28

2010 CA08103002Z-EN

www.eaton.com

Compact PLCs

Automation products

14/75

I/O expansions
I/O expansions

EC4E-221-…
GeneralStandards

EN 55011, EN 55022, IEC/EN 61000-4, IEC 60068-2-6, IEC 60068-2-27

Dimensions (W x H x D)mm

71.5 x 90 x 58 (4 space units)

Weightkg

0.2

Mounting

Top-hat rail IEC/EN 60715, 35 mm or screw fixing using fixing brackets
ZB4-101-GF1 (accessories).

Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

Max. tightening torque

Nm

0.6

°C

-25…55, low temperatures to IEC 60068-2-1, high temperatures to
IEC 60068-2-2
Prevent condensation by means of suitable measures

Storage°C-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 95Air pressure (in operation)hPa

795 - 1080

Ambient climatic conditions
Operating ambient temperature
Condensation

Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)

IP20

Vibrations (IEC/EN 60068-2-6)
Constant amplitude 3.5 mm

Hz

10 - 57

Constant acceleration, 1 g

Hz57 - 150

Shocks

18

mm

50

m

1

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Free fall, packaged (IEC/EN 60068-2-32)

DropheightMounted position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree

II/2

Electrostatic discharge (IEC/EN 61000-4-2, Level 3, ESD)
Air dischargekV

8Contact discharge

kV

6

V/m

10

Electromagnetic fields (RFI), to IEC EN 61000-4-2
Radio interference suppression

EN 55011 Class B, EN 55022 Class B

Burst pulses (IEC/EN 61000-4-4, Level 3)
Supply cableskV

2

Signal cableskV

2

Surge pulses (IEC/EN 61000-4-5, Level 2)kV

0.5 (supply cables, symmetrical, EASY…DC)

Line-conducted interference (IEC/EN 61000-4-6)

V

10

Insulation resistance
Clearance in air and creepage distances
Insulation resistance
Notes

EN 50178, UL 508, CSA C22.2, No. 142
EN 50178
Technical data for the expansion units EASY... ￫ Chapter 122010 CA08103002Z-EN

www.eaton.com

14/76

Automation productsCompact PLCs

I/O expansions

EC4E-221-…
Power supply
Rated operational voltage

UeV

24 DC (-15/+20%)

Permissible range min.

V DC

20.4

Permissible range max.

V DC

28.8

%

≦5

At rated operating voltage without loadmA

Normally 150

At rated operating voltage with loadA–

Voltage dips (IEC/EN 61131-2)

ms

10

Heat dissipation

W

Normally 3.5

Permissible range

RippleInput current

Interfaces
CANopen
Data transfer rate/distance

Potential isolation

500 kBit/s, 25 m
250 kBit/s, 40 m
125 kBit/s, 125 m
50 kBit/s, 300 m
20 kBit/s, 700 m
10 kBit/s, 1000 m
No

Bus termination (first and last station)

Through integrated Dip switch

Connections

2 x terminals (see terminal capacity)

CANopen operating mode
Stations

NumberMax. 62

PDO type

Asynchronous, cyclic, acyclic

Device profile

To DS 301 V4

Digital inputs 24 V DC
Number6

Potential isolation
From power supplyNo

Between digital inputs

No

From the outputs

Yes

Rated operating voltage

Ue

V DC

24

At state ”0”

Ue

V DC

< 5 (R1 - R6)

At state ”1”

Ue

V DC

> 15 (R1 - R6)

Input current at state “1”R1 - R6 (R12)mA

3.3 (at 24 V DC)

R1

mA

–

R2, R3mA–

Debounce ON

ms

20

Debounce OFF

ms

Normally 0.25 (R1 - R12)

Delay time from 1 to 0

ms

20

Cable length (unshielded)m100

Delay time from 0 to 1

Notes

2010 CA08103002Z-EN

Technical data for the expansion units EASY... ￫ Chapter 12

www.eaton.com

Compact PLCs

Automation products

14/77

I/O expansions

EC4E-221-6D4R1
Relay outputs
Number4

Outputs in groups of1

Parallel switching of outputs to increase performance

Not permissible

Protection of an output relay

Miniature circuit-breakers B16 orfuse 8 A (T)Potential isolation
From power supply

Yes

From the inputs

Yes

From PC interface, memory card, network NET, easyLink

Yes

Safe isolation According to EN 50178

V AC

300

Basic insulation

V AC

600

x 106

10

Conventional thermal current (10 A UL)A

8Recommended for 12 V AC/DC load

mA

> 500

Short-circuit proof p.f. = 1, characteristic B16 at 600 A

A

16

Short-circuit proof p.f. = 0.5 - 0.7; characteristic B16 at 900 A

A

16

Rated impulse withstand voltage Uimp contact coil

kV

6

Ue

V AC

250

Ui

V AC

250

Safe isolation to EN 50178 between coil and contact

V AC

300

Safe isolation to EN 50178 between two contacts

V AC

300

Lifespan, mechanical

Operations

Contacts

Rated operating voltage
Rated insulation voltage

Making capacity
AC-15, 230 V AC, 3 A

Operations

300000DC-13, 24 V DC, 0.1 Hz

Operations

200000AC-15, 250 V AC, 3 A (600 ops./h)Operations

300000DC-13, L/R ≦ 150 ms, 24 V DC, 1 A (500 ops./h)Operations

2000001000 W at 230/240 V AC

Operations

25000

500 W at 115/120 V AC

Operations

25000

With series-connected electrical device

Operations

25000

UncompensatedOperations

25000

Operations

25000

Breaking capacity

Filament bulb loadFluorescent lamp loadFluorescent lamp load 10 x 58 W at 230/240 V AC

Fluorescent lamp load 1 x 58 W at 230/240 V AC, conventionally compensatedSwitching frequency
Mechanical operations

x 106

10

Switching frequency

Hz

10

Resistive load/lamp load

Hz

2

Inductive load

Hz

0.5

Continuous current at 240 V AC

A

10Continuous current at 24 V DC

A

8

UL/CSAAC
Control circuit rating codes (utilization category)

B 300 Light Pilot Duty

Max. rated operational voltage

V AC

300

Max. thermal continuous current p.f. = 1 at B 300

A

5Max. make/break capacity p.f. ≠ 1 at B 300

VA

3600/360

DC
Control circuit rating codes (utilization category)

R 300 Light Pilot Duty

Max. rated operational voltage

V DC

300

Max. thermal continuous current p.f. at R 300

A

1

Max. make/break capacity at R 300

VA

28/28

2010 CA08103002Z-EN

www.eaton.com

14/78Automation productsCompact PLCs

I/O expansions

EC4E-221-6D4T1
Transistor outputs
Number4

Rated operating voltage

Ue

V DC

24

Permissible range

Ue

V DC

20.4 - 28.8

%

≦5

mA

9/16

mA

12/22

RippleSupply current
At state ”0”

Normally.⁄max.
Normally.⁄max.

At state ”1”
Protection against polarity reversal

Yes (Caution: A short circuit will result if 0 V or GND is applied tothe outputs if that the supply voltage is connected to the wrong
poles.)

Potential isolation
From power supply

Yes

From PC interface, memory card, network NET, easyLink
Rated operational current at state “1” DC for channel

Yes
Ie

A

Max. 0.5

Lamp load without Rv for channel

W

5

Residual current at state “0” for channel

mA

< 0.1

At state “0” with external load < 10 MΩ

V

2.5

At state “1” at Ie = 0.5 A

V

U = Ue -1 V

Max. output voltage

Short-circuit protection

Yes, thermal (analysis via diagnostics input R16)

Short-circuit tripping current for Ra ≦ 10 mΩ

A

0.7 ≦ Ie ≦ 2 for output

Total short-circuit current

A

8

Peak short-circuit current

A

16

Thermal cutout

Yes

Max. operating frequency at constant resistive load RL < 100 kΩ(dependent on program and load)
Parallel connection of outputs
With resistive load, inductive load with external suppressor
circuit, combination within a group
Number of outputs
Max. total current

2010 CA08103002Z-EN

www.eaton.com

Ops/h

40000

Group 1: Q1 to Q4
Max.

4
A

2 (Caution! Outputs must be activated simultaneously and forthe same duration)

Compact PLCs

Automation products

14/79

Communication card
Compact PLCsCommunication card

MFD-CP4-CO
GeneralStandards

EN 61000-6-1/-2/-3/-4, IEC 60068-2-6, IEC 60068-2-27

Dimensions (W x H x D)mm

75 x 58 x 36.2

Weightkg

0.16

Mounting

Plug-fitted to the display fixing shaft

Terminal capacity
Power supply
Solid

mm2

0.5 - 2.5 (AWG 20 - 14)

Flexible with ferrule

mm2

0.5 - 1.5 (AWG 20 - 16)

Flat-blade screwdrivermm

3.5 x 0.6

Solid

mm2

0.2 - 0.5 (AWG 24 - 20)°C-25 - 55, low temperatures to IEC 60068-2-1,
high temperatures to IEC 60068-2-2
Prevent condensation by means of suitable measures

Storage°C-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 95Air pressure (in operation)hPa

795 - 1080

Data cable
Ambient climatic conditions
Operating ambient temperature
Condensation

Ambient mechanical conditions
Pollution degree

2Protection type (IEC/EN 60529, EN50178, VBG 4)

IP20

Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

Constant acceleration, 2 g

Hz57 - 150

Shocks

18

mm

50

m

1

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Mounted position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree–

Electrostatic discharge (IEC/EN 61000-4-2, Level 3, ESD)
Air dischargekV

8Contact discharge

kV

6

V/m

10

Electromagnetic fields (RFI), to IEC EN 61000-4-2
Radio interference suppression

EN 55011 Class B, EN 55022 Class B

Burst pulses (IEC/EN 61000-4-4, Level 3)
Supply cableskV

2

Signal cableskV

2

Surge pulses (IEC/EN 61000-4-5, Level 2)

kV

0.5

Line-conducted interference (IEC/EN 61000-4-6)

V

10

Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

Power supplyV

24 DC (-15⁄+20 %)Permissible range

Rated operational voltage

Ue

V DC

20.4 - 28.8

Ripple%≦5Input current
At 24 V DC

mA

Normally 185

Voltage dips (IEC/EN 61131-2)

ms

10

Heat dissipation at 24 V DC

W

1.5

Interfaces
CANopenDevice profile

To DS301V4

PDO type

Asynchronous (event controlled)

Addresses
Baud rate/length

1 to 63 can be set through display
kBd

10 kByte up to 1 MByte, Automatic detection
Manual setting via display possible.
6 pole spring-cage terminalΩExternal 120

Connections
Terminal resistor

2010 CA08103002Z-EN

www.eaton.com

14/80Automation productsCompact PLCs

Communication card
Compact PLCs

Dimensions
EC4P…
16.25

75

16.25

45

110

90

102

M4

4.5
16

21

48.5

107.5

70.5
72
79

58

86.5

MFD-CP4-CO

29.3

75

36.2
65.5

86.5

EC4E…
10.75

110

90

102

45

50

4.5
47.5
56.5
58

M4
35.75
71.5

Notes

2010 CA08103002Z-EN

Further dimensions for EASY... and MFD... devices ￫ Chapter 12

www.eaton.com

Compact PLCs

Automation products

14/81

Notes
Notes

2010 CA08103002Z-EN

www.eaton.com

14/82

Automation products

Remote I/O XI/ON

System overview
Remote I/O XI/ON

5

3

1

2

4
4
7

8

8

XI/ON

6

13

14

2010 CA08103002Z-EN

www.eaton.com

12

11

10

9

5

Remote I/O XI/ON
Gateways

1

Gateways XNE:
XNE-GWBR-PBDP
XNE-GWBR-CANOPEN
XNE-GWBR-2ETH-IP
XN gateways:
XN-GWBR-PBDP
XN-GWBR-CANOPEN
XN-GWBR-DNET
XN-GWBR-MODBUS-TCP
XN-PLC-CANOPEN
XN-GW-PBDP-1.5MB
XN-GW-PBDP-12MB
XN-GW-CANOPEN
XN-GW-DNET￫ Page 14/88

Digital input modules
XNE electronics modules:
XNE-8DI-24VDC-P
XNE-16DI-24VDC-P
XN electronics modules:
XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-16DI-24VDC-P
XN-32DI-24VDC-P￫ Page 14/90

Automation products
Relay modules

3

XN electronics modules:
XN-2DO-R-CO
XN-2DO-R-NC
XN-2DO-R-NO￫ Page 14/91

Basic modules

5

3 connection levels
4 connection levels
6 connection levels￫ Page 14/91

Supply modules

2

Analog input modules

11

Analog output modules

10

XNE electronics modules:
XNE-4AO-U/I
XN electronics modules:
XN-1AO-I(0/4...20MA)
XN-2AO-I(0/4...20MA)
XN-2AO-U(-10/0...+10VDC)￫ Page 14/92

Technology modules

13

XNE electronics modules:
XNE-2CNT-2PWM
XNE-1SWIRE
XN electronics modules:
XN-1CNT-24VDC
XN-1RS232
XN-1RS485/422
XN-1SSI￫ Page 14/93

Accessories

9

XN electronics modules:
XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D￫ Page 14/90

XNE electronics modules:
XNE-8AI-U/I-4Pt/Ni
XN electronics modules:
XN-1AI-I(0/4...20MA)
XN-2AI-I(0/4...20MA)
XN-1AI-U(-10/0...+10VDC)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-2AI-THERMO-PI
XN-4AI-U/I￫ Page 14/92

Digital output modules
XNE electronics modules:
XNE-8DO-24VDC-0.5A-P
XNE-16DO-24VDC-0.5A-P
XN electronics modules:
XN-2DO-24VDC-0.5A-P
XN-2DO-24VDC-0.5A-N
XN-2DO-24VDC-2A-P
XN-2DO-120/230VAC-0.5A
XN-4DO-24VDC-0.5A-P
XN-16DO-24VDC-0.5A-P
XN-32DO-24VDC-0.5A-P￫ Page 14/91

14/83

12

End coverEnd bracket
Relay jumpers
Marker
Coding element
Screw terminals￫ Page 14/97

2010 CA08103002Z-EN

7
8
6
14
4
–

www.eaton.com

14/84
Remote I/O XI/ON

Automation products

Remote I/O XI/ON

Description

Ethernet

As much as necessary, as little
as possible - is the design principleof the modular I/O system XI/ON,
which provides a comprehensive
range of digital and analog I/Os
and technology modules. The
gateway products are available
for fieldbus systems CANopen,
PROFIBUS-DP, DeviceNet andEthernet.

XI/ON standard gateways andmodulesIn the standard version, the pluggable
I/O modules are wired to basemodules.
• Bus-independent modules• Hot-swapping of modules• Screw or spring-cage terminals• Mechanical coding of modules
prevents incorrect connection• Serial interface modules
allow connection of various
peripherals, such as printers,
scanners and bar code
readers• Programmable CANopen
gateway for decentralizing
automation tasks or reducing
the burden on higher-level
PLCs.

XI/ON ECO gateways andmodules
XI/ON ECO adds cost- andspace-optimized I/O modules
and gateways to the XI/ON I/O
system.
• High channel density:
up to 16 DI/DO over 12.5 mm• No base modules required• Cost saving throughelectronics with built-in
connection level• Connection through “push-in”
spring-cage terminal saves
mounting time
• Can be combined with XI/ON
standard• Multi-function modules reduce thenumber of required slices• ECO gateways with built-in bus
termination resistors/auto-baudfunction.

SWD I/O modules

The EC4E modules can be connected
to all control systems with CANopen
master. The modules can be expandedwith a digital or analog easy expansion
module.

SmartWire-Darwin station for theconnecting digital I/O.

SWD gateways
Gateways for connecting to field
busses PROFIBUS-DP and
CANopen and for power supply of
the SmartWire-Darwin nodes andswitchgear.

12.5 mm

16 I/O

Configuration tool
I/OassistantWith the free software I/Oassistant
XI/ON stations can be planned simply
and conveniently.
• I/Oassistant automaticallygenerates a complete parts list
for your order. With the “Checksurface mounting” function, you
can easily check the configured
station design.
• Commissioning the I/O level without
connected controller possible;
Servicing interface• EPLAN support• I/Oassistant can be integrated withXSOFT-CODESYS-2.

2010 CA08103002Z-EN

CANopen expansion modules

www.eaton.com

Configuration tool
SWD-Assistant
The software SWD-Assist helps you
easily and quickly plan SmartWireDarwin lines.
Free download at
http://downloadcenter.moeller.net

Remote I/O XI/ON

Automation products

14/85

Selection chart

XN-P4...-SBBC

●3)

●2)
●
●

XN-P4...-SBBC-B

XN-P3...-SBB-B

XN-P3...-SBB

XN-B6...-SBCSBCXN-B6...-SBBSBB

XN-B4...-SBBC

XN-B3...-SBC

XN-B3...-SBB

XN-S6...-SBCSBCXN-S6...-SBBSBBXN-S4...-SBBS-CJ

XN-S4...-SBCS

XN-S4...-SBBS

XN-S4...-SBBC

XN-S3...-SBC

XN-S3...-SBB

Basic modules

Remote I/O XI/ONSelection chart

Electronics modules
Digital input modules
XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-16DI-24VDC-P
XN-32DI-24VDC-P
XNE-8DI-24VDC-P1)
XNE-16DI-24VDC-P1)

●
●
●

●
●
●
●
●

●
●
●

●

Digital output modules
XN-2DO-24VDC-0.5A-P
XN-2DO-24VDC-0.5A-N
XN-2DO-24VDC-2A-P
XN-2DO-120/230VAC-0.5A
XN-4DO-24VDC-0.5A-P
XN-16DO-24VDC-0.5A-P
XN-32DO-24VDC-0.5A-P
XNE-8DO-24VDC-0.5A-P1)
XNE-16DO-24VDC-0.5A-P1)

●
●
●
●

●
●
●
●
●

●
●
●

Relay modules
XN-2DO-R-NC
XN-2DO-R-NO
XN-2DO-R-CO●●●

Analog input modules
XN-1AI-I(0/4...20MA)
XN-2AI-I(0/4...20MA)
XN-1AI-U(-10/0...+10VDC)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-2AI-THERMO-PI
XN-4AI-U/I
XNE-8AI-U/I-4Pt/Ni1)

●
●
●
●
●

●
●

●
●
●
●
●
●
●

Analog output modules
XN-1AO-I(0/4...20MA)
XN-2AO-I(0/4...20MA)
XN-2AO-U(-10/0...+10VDC)
XNE-4AO-U/I1)●●●

Technology modules
XN-1CNT-24VDC
XN-1RS232
XN-1RS485/422
XN-1SSI
XNE-1SWIRE1)
XNE-2CNT-2PWM1)

●
●
●
●

Supply modules
XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D
Notes

●

●2)
●
●
1)
2)
3)

●3)

No base modules required
Base module for gateway supply
Base module for bus refreshing within the station2010 CA08103002Z-EN

www.eaton.com

14/86

Automation products

Remote I/O XI/ON

Remote I/O XI/ON

Automation products

Maximum system configuration

14/87

Maximum system configuration

Remote I/O XI/ONMaximum system configuration

Max. 74 XI/ON modules in slice design
Plan your XI/ON station with the software ""I/Oassistant""(free download at www.microinnovation.com).
Advantage 1:
Automatically generates a full parts list for your order.
Advantage 2:
Generates an error message as soon as the system limits are exceeded.
Notes:
When extending your system, make sure that you have a sufficient number of bus
refresh or power feed modules.

Max.
number/stationModules
XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-16DI-24VDC-P
XN-32DI-24VDC-P
XNE-8DI-24VDC-P
XNE-16DI-24VDC-P
XN-4DO-24VDC-0.5A-P
XN-16DO-24VDC-0.5A-P
XN-32DO-24VDC-0.5A-P
XNE-8DO-24VDC-0.5A-P
XNE-16DO-24VDC-0.5A-P
XN-2DO-R-…
XN-2AI-I(0/4…20MA)
XN-2AI-U(-10/0…+10VDC)
XN-2AI-Pt/Ni-2/3
XN-2AI-THERMO-PI
XN-4AI-U/I
XNE-8AI-U/I-4Pt/Ni
XN-2AO-I(0/4…20MA)
XN-2AO-U(-10/0…+10VDC)
XNE-4AO-U/I
XN-1CNT-24VDC
XN-1RS232
XN-1RS485/422
XN-1SSI
Notes

2010 CA08103002Z-EN

Part no.
140045
XNE-GWBR-PBDP

Part no.
140044
XNE-GWBR-CANOPENPart no.
140047
XNE-GWBR-2ETH-IP

Part no.
140154XN-GWBR-PBDP

Part no.
140055XN-GWBR-CANOPENPart no.
140156
XN-GWBR-DNET

Part no.
140162XN-GWBR-MODBUS-TCP

Part no.
140049XN-GW-PBDP-1.5MB

Part no.
140048XN-GW-PBDP-12MB

Part no.
140050XN-GW-CANOPENPart no.
140051XN-GW-DNET

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

Channels

Modules

136
136
128
256
384
768
132
128
256
384
640
70
56
56
44
44
64 (132)
72 (120)50
46
64 (76)
13
7
16
20

34
34
8
8
48
48
33
8
8
48
40
35
28
28
22
22
16 (33)9 (15)
25
23
16 (19)
13
7
16
20

244
244
128
256
512
512
244
128
256
488
512
122
100
100
98
98
108
144
70
70
108
27
27
27
27

61
61
8
8
64
32
61
8
8
61
32
61
50
50
49
49
27
18
35
35
27
27
27
27
27

288
288
128
256
512
512
288
128
256
512
512
144
126
126
126
126
124
128
126
126
64
31
31
31
31

72
72
8
8
64
32
72
8
8
64
32
72
63
63
63
63
31
16
63
63
16
31
31
31
31

288
288
128
256
592
1184
288
128
256
592
1168
144
78
78
46
58 (76)
112
88
38
38
36
7
22
22
22

72
72
8
8
74
74
72
8
8
74
73
72
39
39
23
29 (38)
28
11
19
19
9
7
22
22
22

288
288
128
256
512
512
288
128
256
512
512
144
144
144
144
144
144
144
144
144
144
72
68
72
72

72
72
8
8
64
32
72
8
8
64
32
72
72
72
72
72
36
18
72
72
36
72
68
72
72

288
288
128
256
576
1152
128
128
256
256
512
64
32
32
32
32
64
128
32
32
64
16
8
8
8

72
72
8
8
72
72
32
8
8
32
32
32
16
16
16
16
16
16
16
16
16
16
8
8
8

288
288
128
256
512
512
288
128
256
512
512
144
144
144
144
144
144
144
144
144
124
72
68
72
72

72
72
8
8
64
32
72
8
8
64
32
72
72
72
72
72
36
18
72
72
31
72
68
72
72

288
288
128
256

72
72
8
8

288
288
128
256

72
72
8
8

288
288
128
256

72
72
8
8

288
288
128
256

72
72
8
8

288
128
256

72
8
8

288
128
256

72
8
8

288
128
256

72
8
8

288
128
256

72
8
8

144
78
78
46
58 (76)
112

72
39
39
23
29 (38)
28

144
78
78
46
58 (76)
112

72
39
39
23
29 (38)
28

144
144
144
142
142
144

72
72
72
71
71
36

144
126
126
126
126
124

72
63
63
63
63
31

38
38

19
19

38
38

19
19

142
142

71
71

126
126

63
63

7
22
22
22

7
22
22
22

7
22
22
22

7
22
22
22

71
67
70
71

71
67
70
71

31
31
31
31

31
31
31
31

Numeric values in brackets: max. number when diagnostic alarm disabled.
The supply module XN-BR-24VDC-D must be mounted immediately next to the gateway XN-GW-... to provide power
for the gateways.

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

14/88Automation products

Remote I/O XI/ON

Gateways
HPL14088EN

Ordering
Remote I/O XI/ONGateways

Fieldbus
connection

Terminal capacity(field bus/supply voltage)

Servicinginterface

Transfer rate

Part no.
Article no.

Price
See
price list

PS/2 socket

9.6 kbit/s to
12 Mbit/s

XNE-GWBR-PBDP 1)2)
140045

1 off

PS/2 socket

1000 kbit/s
800 kbit/s
500 kbit/s
250 kbit/s
125 kbit/s
50 kbit/s
20 kbit/s

XNE-GWBR-CANOPEN 1)2)
140044

1 off

XNE-GWBR-2ETH-IP 1)3)
1400471 off

9.6 kbit/s to
12 Mbit/s

XN-GWBR-PBDP 1)4)
140154

1 off

1000 kbit/s
800 kbit/s
500 kbit/s
250 kbit/s
125 kbit/s
50 kbit/s
20 kbit/s
10 kbit/s

XN-GWBR-CANOPEN 1)4)
140155

1 off

500 kbit/s
250 kbit/s
125 kbit/s

XN-GWBR-DNET 1)4)
140156

1 off

Std. packGateway XNE with integrated supply• Supports up to 48 slice-type modules (XN, XNE)
• Address setting through DIP switch• Address range: 1 – 125 (dec.)
PROFIBUS-DP
Push-in spring-cage terminals(DPV0/DPV1
protocol)• Supports up to 62 disc type modules (XN, XNE)
• Address set with DIP switch• Address range: 1 – 63 (dec.)
CANopenPush-in spring-cage terminals• Supports up to 74 disc type modules (XN, XNE)
• 2 x RJ45 socket• Address set with decimal rotary coding switches, BootP, DHCP or I/Oassistant• Address range: 1 – 254 (dec.)
Ethernet
Push-in spring-cage terminals
Mini USB
10/100 MBit/s(Ethernet-IP
protocol)XN-Gateway with integrated supply• Supports up to 74 disc type modules (XN, XNE)
• 1 x D-sub 9-pin socket• Address set with two decimal rotary coding switches• Address range: 1 – 99 (dec.)
PROFIBUS-DP
Screw terminals
PS/2 socket(DPV0 protocol)• Supports up to 74 disc type modules (XN, XNE)
• 1 x open-style connector• Address set with two decimal rotary coding switches• Address range: 1 – 99 (dec.)
CANopenScrew terminals
PS/2 socket• Supports up to 74 disc type modules (XN, XNE)
• 1 x open-style connector• Address set with two decimal rotary coding switches• Address range: 0 – 63 (dec.)
DeviceNet
Screw terminals
PS/2 socket

Notes1) Bus refreshing modules is already integrated.

The following are included as standard with all
gateways:
2 x end bracket XN-WEW-32/2-SW,
1 x end plate XN-ABPL

Information relevant for export to North America
2) Product Standards

NA Certification
Degree of Protection
3) Product Standards

NA Certification
Degree of Protection
4) Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

IEC/EN 6113-2; CE marking
Request filed for UL and CSA
IEC: IP20, UL/CSA Type: IEC/EN 6113-2; CE marking
Planned for UL and CSA
IEC: IP20, UL/CSA Type: UL 508; cUL
IEC/EN 6113-2; CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -Remote I/O XI/ON

Automation products

14/89

Gateways
HPL14089EN
Fieldbus
connection

Terminal capacity(field bus/supply voltage)

Servicinginterface

Transfer rate

Part no.
Article no.

Price
See
price list

Std. pack• Supports up to 74 disc type modules (XN, XNE)
• 1 x RJ45 socket• Address set with decimal rotary coding switches, BootP, DHCP or I/Oassistant• Address range: 1…254 (dec.)
Ethernet(Modbus-TCP
protocol)Screw terminals

PS/2 socket

10/100 MBit/s

XN-GWBR-MODBUS-TCP1) 3)
140162

1 off

XN-PLC-CANOPEN1) 4)
140157

1 off

XN-Gateway with integrated supply, programmable• Supports up to 74 disc type modules (XN, XNE to limited extent)• 1 x open-style connector• Operating mode and address setting with two hexadecimal rotary coding switches• Address range: 1 – 99 (dec.)
CANopenScrew terminals
PS/2 socket
Adjustable up to
1 Mbit/s

XN gateway without integrated supply• Supports up to 74 disc type modules (XN)
• 2 x D-sub 9-pin sockets• Address setting with two hexadecimal rotary coding switches• Address range: 1– 125 (dec.)
PROFIBUS-DP
2 × spring-cage terminal strips for PS/2 socket(DPV0 protocol) direct wiring

9.6 Kbits/s to
1.5 MBit/s

XN-GW-PBDP-1.5MB 2) 4)
1400491 off• Supports up to 74 disc type modules (XN)
• 1 x D-sub 9-pin socket• Address setting with two hexadecimal rotary coding switches• Address range: 1– 125 (dec.)
PROFIBUS-DP–
PS/2 socket(DPV0 protocol)

9.6 kbit/s to
12 Mbit/s

XN-GW-PBDP-12MB 2) 4)
1400481 off

1000 kbit/s
800 kbit/s
500 kbit/s
250 kbit/s
125 kbit/s
50 kbit/s
20 kbit/s
10 kbit/s

XN-GW-CANOPEN 2) 4)
140050

1 off

500 kbit/s
250 kbit/s
125 kbit/s

XN-GW-DNET 2) 4)
140051

1 off• Supports up to 74 disc type modules (XN)
• 1 x 9 pole SUB-D socket, 1 × D-sub 9-pin• Address setting with two hexadecimal rotary coding switches• Address range: 1– 127 (dec.)
CANopen2 × spring-cage terminals for
PS/2 socket
direct wiring• Supports up to 64 disc type modules (XN)
• 1 x open-style connector• Address set with two decimal rotary coding switches• Address range: 0…63 (dec)
DeviceNet–
PS/2 socket

Notes1) Bus refreshing modules is already integrated.

Information relevant for export to North America

2) The supply module XN-BR-24VDC-D must be

mounted immediately next to the gateway toprovide the supply for the gateways.
The following are included as standard with all
gateways:
2 x end bracket XN-WEW-32/2-SW,
1 x end plate XN-ABPL

3) Product Standards

Degree of Protection
4) Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN 6113-2; CE marking
IEC: IP20, UL/CSA Type: UL 508; cUL; IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/90Automation products

Remote I/O XI/ON

Power supply modules, I/O modules
HPL14090EN
Remote I/O XI/ONPower supply modules, I/O modules

For use withPart no.
Article no.

XN-P3T-SBB
XN-P3S-SBB
XN-P4T-SBBC
XN-P4S-SBBC
XN-P3T-SBB-B
XN-P3S-SBB-B
XN-P4T-SBBC-B
XN-P4S-SBBC-B

XN-BR-24VDC-D
140071

1 off

Field power supply at a rated voltage of 24 V DC

XN-P3T-SBB
XN-P3S-SBB
XN-P4T-SBBC
XN-P4S-SBBC

XN-PF-24VDC-D
140070

1 off

Field power supply at a rated voltage of 120/230 V AC
nominal voltage

XN-P3T-SBB
XN-P3S-SBB
XN-P4T-SBBC
XN-P4S-SBBC

XN-PF-120/230VAC-D
140072

2 digital inputs, 24 V DC
Positive switching
2 digital inputs, 24 V DC
Negative switching
2 digital inputs,
120/230 V AC
4 digital inputs, 24 V DC
Positive switching
4 digital inputs, 24 V DC
Negative switching
16 digital inputs,
24 V DC
Positive switching

XN-S3T-SBB
XN-S3S-SBB
XN-S4T-SBBC
XN-S4S-SBBC

XN-2DI-24VDC-P
140056
XN-2DI-24VDC-N
140057
XN-2DI-120/230VAC
140058XN-4DI-24VDC-P
140052
XN-4DI-24VDC-N
140059
XN-16DI-24VDC-P
140142

Description

Price
See
price list

Std. packBus refreshing modules
Slice modules XN

Provides system and field power
System power supply 24 V DC for generation of power
for module bus and gateway(XN-GW-... )Field power supply at a rated voltage of 24 V DC

Power feeding modules
Slice modules XN

Digital input modules
Slice modules XN

Block modules XN

32 digital inputs,
24 V DC
Positive switching
Slice modules XNE

8 digital inputs, 24 V DC
Positive switching
16 digital inputs,
24 V DC
Positive switching

Information relevant for export to North America
Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection2010 CA08103002Z-EN

UL 508; cUL; IEC/EN 6113-2; CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -www.eaton.com

XN-S4T-SBBS
XN-S4S-SBBS
XN-S6T-SBBSBB
XN-S6S-SBBSBB
XN-B3T-SBB
XN-B3S-SBB
XN-B4T-SBBC
XN-B4S-SBBC
XN-B6T-SBBSBB
XN-B6S-SBBSBB––

XN-32DI-24VDC-P
140147
XNE-8DI-24VDC-P
140035
XNE-16DI-24VDC-P
140040

1 offRemote I/O XI/ON

Automation products

14/91

I/O modules
HPL14091EN
Remote I/O XI/ONI/O modules

Description

For use withPart no.
Article no.

XN-S3T-SBC
XN-S3S-SBC
XN-S4T-SBCS
XN-S4S-SBCS

XN-2DO-24VDC-0.5A-P
140053Price
Seeprice list

Std. pack

Digital output modules
Slice modules XN

Block modules XN

Slice modules XNE

2 digital outputs,
24 V DC/0.5 A
Positive switching
2 digital outputs,
24 V DC/0.5 A
Negative switching
2 digital outputs,
24 V DC/2 A
Positive switching
2 digital outputs,
120/230 V AC/0.5 A
4 digital outputs,
24 V DC/0.5 A
Positive switching
16 digital outputs,
24 V DC/0.5 A
Positive switching
32 digital outputs,
24 V DC/0.5 A
Positive switching
8 digital outputs,
24 V DC/0.5 A
Positive switching
16 digital outputs,
24 V DC/0.5 A
Positive switching

1 off

XN-2DO-24VDC-0.5A-N
140060XN-2DO-24VDC-2A-P
140055

XN-S4T-SBCS
XN-S4S-SBCS
XN-S6T-SBCSBCXN-S6S-SBCSBC

XN-2DO-120/230VAC-0.5A
140150XN-4DO-24VDC-0.5A-P
140148

XN-B3T-SBC
XN-B3S-SBC

XN-16DO-24VDC-0.5A-P
140141

XN-B6T-SBCSBCXN-B6S-SBCSBC

XN-32DO-24VDC-0.5A-P
140161–

XNE-8DO-24VDC-0.5A-P
140036–

XNE-16DO-24VDC-0.5A-P
140039

XN-S4T-SBBS
XN-S4S-SBBS
XN-S4T-SBBS
XN-S4S-SBBS
XN-S4T-SBCS
XN-S4S-SBCS

XN-2DO-R-CO
140054XN-2DO-R-NC
140061XN-2DO-R-NO
140062

Relay modules
Slice modules XN

2 changeover contacts, isolated
230 V AC / 30 V DC
2 NC
230 V AC / 30 V DC
2 N/O
230 V AC / 30 V DC

1 offInformation relevant for export to North America
Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL; IEC/EN 6113-2; CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

14/92

Automation products

Remote I/O XI/ON

I/O modules
HPL14092EN
Remote I/O XI/ONI/O modules

Description

For use withPart no.
Article no.

1 analog input
0/4 to 20 mA
2 analog inputs
0/4 to 20 mA
1 analog input-10/0 to +10 V DC
2 analog inputs-10/0 to +10 V DC
2 analog inputs
Reading of standardized signals for temperature
measurement
Connection of RTDs Pt100, Pt200, Pt500, Pt1000, Ni100,
Ni1000, and Ni1000TK5000 in 2- or 3-wire circuit

XN-S3T-SBB
XN-S3S-SBB
XN-S4T-SBBS
XN-S4S-SBBS

XN-1AI-I(0/4...20MA)1)
140063
XN-2AI-I(0/4...20MA)1)
140144
XN-1AI-U(-10/0...+10VDC)1)
140064
XN-2AI-U(-10/0...+10VDC)1)
140145
XN-2AI-Pt/Ni-2/31)
140067

2 analog inputs
Acquisition of normalized signals for measuring temperatures or voltages up to ± 1 V
Connection of thermocouples of types B, E,
J, K, N, R, S, T
4 analog inputs-10/0 to +10 V DC,
0/4 to 20 mA
Selectable for channel

XN-S4T-SBBS-CJ
XN-S4S-SBBS-CJ

XN-2AI-THERMO-PI1)
140068

XN-S6T-SBCSBCXN-S6S-SBCSBC

XN-4AI-U/I1)
140158

8 analog inputs U/I or 4 analog inputs Pt/Ni-10/0 to +10 V DC, 0/4 to 20 mA
Reading of standardized signals for temperature
measurement
Connection of RTDs Pt100, Pt200, Pt500, Pt1000, Ni100,
Ni1000, and Ni1000TK5000, Ni1000TK5000 in 2- or
3-wire circuit
Selectable for channel–

XNE-8AI-U/I-4Pt/Ni 2)
140037Price
Seeprice list

Std. packAnalog input modules
Slice modules XN

Slice modules XNE

1 off

Analog output modules
Slice modules XN

1 analog output
0/4 to 20 mA
2 analog outputs
0/4 to 20 mA
2 analog outputs-10/0 to +10 V DC

XN-S3T-SBB
XN-S3S-SBB

XN-1AO-I(0/4...20MA)3)
140065
XN-2AO-I(0/4...20MA)3)
140146
XN-2AO-U(-10/0...+10VDC)3)
140066

Slice modules XNE

4 analog outputs-10/0 to +10 V DC, 0/4 to 20 mA
Selectable for channel–

XNE-4AO-U/I 4)140034

Information relevant for export to North America
1)

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL; IEC/EN 6113-2; CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -2)

Product Standards
NA Certification
Degree of Protection

IEC/EN 6113-2; CE marking
Request filed for UL and CSA
IEC: IP20, UL/CSA Type: -3)

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL; IEC/EN 6113-2; CE marking
E205091
NRAQ, NRAQ7
UL report applies to both US and Canada
UL Recognized, certified by UL for use in Canada
IEC: IP20, UL/CSA Type: -4)

Product Standards
NA Certification
Degree of Protection2010 CA08103002Z-EN

IEC/EN 6113-2; CE marking
Request filed for UL and CSA
IEC: IP20, UL/CSA Type: -www.eaton.com

1 offRemote I/O XI/ON

Automation products

14/93

Technology modules
HPL14093EN
Remote I/O XI/ONTechnology modules

Description

For use withPart no.
Article no.

1 digital input/24 V DC
1 digital output/24 V DCCounting modes: infinite,
once only or periodic countFrequency, rotational speed
or period duration countReading signals from rotary
encoders (track A/B)

XN-S4T-SBBS
XN-S4S-SBBS

XN-1CNT-24VDC
140069Price
Seeprice list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards

Counter modules
Slice modules XN

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508;cUL; IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized, certified by UL for use in
Canada
IEC: IP20, UL/CSA
Type: -

Serial interfaces
Slice modules XN

Data transfer rate adjustable
up to 115200 bit/s
Data transfer rate adjustable
up to 115200 bit/s
Connection of SSI encoders
up to 32-bit.
Data transfer rate adjustable
up to 1 bit/s

XN-S4T-SBBS
XN-S4S-SBBS

XN-1RS232
140151XN-1RS485/422
140152
XN-1SSI
140153

1 off

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508;cUL; IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized, certified by UL for use in
Canada
IEC: IP20, UL/CSA
Type: -

SmartWire-Darwin Interface
Slice modules XNE

Connection of up to
16 motor starters (Eaton)
Up to 3 XNE-1SWIRE for XI/ON
node–

XNE-1SWIRE
140043

1 off

Product Standards
NA Certification
Degree of Protection

IEC/EN 6113-2;
CE marking
Request filed for UL
and CSA
IEC: IP20, UL/CSA
Type: -Counter/PWM modules
Slice modules XNE

2 counter channels and2 PWM channels
Counting modes: infinite,
once only or periodic countFrequency, rotational speed
or period duration countReading signals from rotary
encoders (track A/B)
Output of a defined digital
signalOutput of a defined number ofpulses–XNE-2CNT-2PWM
140038

1 off

Product Standards
NA Certification
Degree of Protection2010 CA08103002Z-EN

IEC/EN 6113-2;
CE marking
Planned for UL and
CSA
IEC: IP20, UL/CSA
Type: -

www.eaton.com

14/94

Automation products

Remote I/O XI/ON

Basic modules
HPL14094EN
Remote I/O XI/ONBasic modules

Description

For use withPart no.
Article no.

Base module for fieldpower supply
Base module for the
gateway supply (with
XN-BR-24VDC-D)
Base module for bus
refresh within thestation–

XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D

XN-P3T-SBB
140074

Price
See
price
list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards

Basic modules
Spring-cage terminals• 3 connection levels
Slice modules

Block modules

Connection to
C rail–XN-BR-24VDC-D

XN-P3T-SBB-B
140073

XN-2DI-...
XN-1AI-...
XN-2AI-I(0/4...20MA)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-1AO-I(0/4...20MA)
XN-2AO-...
XN-2DO-24VDC-...
XN-2DO-120/230VAC-0.5A
XN-16DI-24VDC-P

XN-S3T-SBB
140077

Connection to
C rail

XN-16DO-24VDC-0.5-P

Base module for fieldpower supply
Base module for the
gateway supply (with
XN-BR-24VDC-D)
Connection to
C railBase module for bus
refresh within thestationConnection to
C railConnection to
C railXN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL;
IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized,
certified by UL for use
in Canada
IEC: IP20, UL/CSA
Type: -

XN-S3T-SBC
140079XN-B3T-SBB
140133
XN-B3T-SBC
140134• 4 connection levels
Slice modules

Connection to
C rail–Base module withtemperature sensors
for cold-junction
compensation2010 CA08103002Z-EN

www.eaton.com

XN-P4T-SBBC
140076

1 off

Product Standards
UL File No.
UL CCNCSA File No.

XN-BR-24VDC-D

XN-P4T-SBBC-B
140075

CSA Class No.
NA Certification
Degree of Protection

XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-2DO-24VDC-...
XN-2DO-120/230VAC-0.5A
XN-4DO-24VDC-0.5A-P
XN-2DO-R-NO
XN-2DO-R-NC
XN-4DI-...
XN-2DO-R-...
XN-1AI-...
XN-2AI-I(0/4...20MA)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-1CNT-24VDC
XN-1RS...

XN-S4T-SBBC
140078

XN-2AI-THERMO-PI

XN-S4T-SBBS-CJ
140084

XN-S4T-SBCS
140080XN-S4T-SBBS
140081

UL 508; cUL;
IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized,
certified by UL for use
in Canada
IEC: IP20, UL/CSA
Type: -

Remote I/O XI/ON

Automation products

14/95

Basic modules
HPL14095EN
Description

For use withPart no.
Article no.

Connection to
C rail

XN-16DI-24VDC-P

XN-B4T-SBBC
140135

Price
See
price
list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards• 4 connection levels
Block modules

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection• 6 connection levels
Slice modules

Block modules

Screw terminals• 3 connection levels
Slice modules

Connection to
C rail

XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-4DO-24VDC-0.5A-P
XN-4AI-U/I

XN-S6T-SBBSBB
140082
XN-S6T-SBCSBC
140083–

XN-32DI-24VDC-P

Connection to
C rail

XN-32DO-24VDC-0.5A-P

XN-B6T-SBBSBB
140136
XN-B6T-SBCSBC
140159Base module for fieldpower supply
Base module for the
gateway supply (with
XN-BR-24VDC-D)–

XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D––

XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-1AI-...
XN-2AI-I(0/4...20MA)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-1AO-I(0/4...20MA)
XN-2AO-...
XN-2DO-24VDC-...
XN-2DO-120/230VAC-0.5A
XN-16DI-24VDC-P

Connection to C rail

XN-16DO-24VDC-0.5A-P

Base module for fieldpower supply
Base module for the
gateway supply (with
XN-BR-24VDC-D)
Connection to
C railXN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D

Connection to C rail
Block modules

XN-P3S-SBB
140085

1 off

1 off

Product Standards
UL File No.
UL CCNCSA File No.

XN-S3S-SBB
140088CSA Class No.
NA Certification
Degree of Protection

UL 508; cUL;
IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized,
certified by UL for use
in Canada
IEC: IP20, UL/CSA
Type: -UL 508; cUL;
IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized,
certified by UL for use
in Canada
IEC: IP20, UL/CSA
Type: -

XN-S3S-SBC
140090
XN-B3S-SBB
140137
XN-B3S-SBC
140138• 4 connection levels
Slice modules

XN-P4S-SBBC
1400871 off2010 CA08103002Z-EN

www.eaton.com

14/96

Automation products

Remote I/O XI/ON

Basic modules
HPL14096EN

Screw terminals• 4 connection levels
Slice modules

Description

For use withPart no.
Article no.

Base module for bus
refresh within thestationConnection to
C railConnection to
C railXN-BR-24VDC-D

XN-P4S-SBBC-B
140086

XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-2DO-24VDC-...
XN-2DO-120/230VAC-0.5A
XN-4DO-24VDC-0.5A-P
XN-2DO-R-NO
XN-2DO-R-NC
XN-4DI-...
XN-2DO-R-...
XN-1AI-...
XN-2AI-I(0/4...20MA)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-1CNT-24VDC
XN-1RS...
XN-1SSI
XN-2AI-THERMO-PI

XN-S4S-SBBC
140089

XN-16DI-24VDC-P

XN-B4S-SBBC
140139XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-4DO-24VDC-0.5A-P
XN-4AI-U/I

XN-S6S-SBBSBB
140093
XN-S6S-SBCSBC
140094–

XN-32DI-24VDC-P

XN-B6S-SBBSBB
140140Connection to
C rail

XN-32DO-24VDC-0.5A-P

XN-B6S-SBCSBC
140160Connection to
C rail–Block modules

Base module withtemperature sensors
for cold-junction
compensation
Connection to
C rail

Price
See
price
list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

XN-S4S-SBCS
140091Degree of Protection
XN-S4S-SBBS
140092

XN-S4S-SBBS-CJ
140095• 6 connection levels
Slice modules–
Connection to C rail

Block modules

2010 CA08103002Z-EN

www.eaton.com

1 off

UL 508;cUL; IEC/EN 6113-2;
CE marking
E205091
NRAQ, NRAQ7
UL report applies toboth US and Canada
UL Recognized,
certified by UL for use
in Canada
IEC: IP20, UL/CSA
Type: -

Remote I/O EC4E, SWD

Automation products

14/97

Expansion modules, accessories
HPL14097EN
Remote I/O EC4E, SWDExpansion modules, accessories

InputsDigitalOutputs

AnalogOf which Relay
usable as 10 A
digital(UL)

Transistor

Supplyvoltageconnection

Part no.
Article no.

Price
See
price list

Std. pack

Information relevant for export toNorth America

EC4E-221-6D4R1
114296
EC4E-221-6D4T1
114297

1 off

NA Certification

EU5C-SWD-DP
116308

1 off

NA Certification

Request filed
for UL and
CSA

EU5E-SWD-8DX
116381
EU5E-SWD4D4D
116382
EU5E-SWD4D2R
116383

1 off

NA Certification

Request filed
for UL and
CSA

XN-KO/2
140114
XN-KO/5
140117
XN-KO/6
140118XN-KO/8
140119XN-KO/9
140120XN-KO/10
140121XN-KO/11
140122
XN-KO/12
140123

1 off

UL/CSA certification not required

AnalogI/O expansion modules
Can be used through CANopen for: XC100/200, EC4P, MFD4

Notes

6

–

–

4

–

–

24 V DC

6

–

–

–

4

–

24 V DC

1 off

Degree of Protection

Request filed
for UL and
CSA
IEC: IP20, UL/
CSA Type: -Technical data for the EASY...expansion units ￫ Chapter 12

SWD gateways
Gateway for connecting to the fieldbus and for supplying the SmartWire-Darwin (SWD)slaves and switchgear.
Connection to PROFIBUS-DP as slave.
Automatic baud rate detection from 9.6 kbit/s to 12 Mbit/s.
Address range 1 - 126.
D-sub 9-pin socket.
Connection of up to 58 SWD slaves.
Connection to CANopen as slave.
Automatic baud rate detection from 10 kbit/s to 1 Mbit/s.
Address range 1 - 32.
D-sub 9-pin plug.
Connection of up to 99 SWD slaves.

EU5C-SWD-CAN
116307SWD I/O modules
SmartWire-Darwin slaves for the connecting digital I/O.
Digital module with 8 digital inputs 24 V DC
Digital module with 4 digital inputs 24 V DC and 4 transistor outputs
24 V DC/0.5 A
Digital module with 4 digital inputs 24 V DC and 2 relay outputs
250 V AC

Coding elements
Included as standard with every
electronics module.
Prevents incorrect connection of theelectronics modules.

For use with
XN-...DI-24VDC…
XN-2DI-120/230VAC
XN-xDO-24VDC…
XN-2DO-R-NO
XN-2DO-R-NC
XN-2DO-R-CO
XN-1AI-I(0/4…20MA)
XN-2AI-I(0/4…20MA)
XN-1AI-U(-10/0...+10VDC)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-2AI-THERMO-PI
XN-4AI-U/I
XN-1AO-I(0/4...20MA)
XN-2AO-I(0/4...20MA)
XN-2AO-U(-10/0...+10VDC)
XN-1CNT-24VDC
XN-1RS232
XN-1RS485/422
XN-1SSI
XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D

XN-KO/13
140124
XN-KO/14
140125
XN-KO/15
140126

XN-KO/16
140127
XN-KO/17
1401282010 CA08103002Z-EN

www.eaton.com

14/98Automation products

Remote I/O XI/ON

Accessories
HPL14098EN
Remote I/O XI/ONAccessories

Description

For use withPart no.
Article no.

1-grid–2-grid–3-grid–4-grid–5-grid–6-grid–7-grid–8-grid–For fixing the XI/ON station on the top-hat rail.
2 end brackets are supplied as standard with thegateways.

For covering an XI/ON station.
An end cover is supplied with the gateway as
standard

Price
Seeprice list

Std. pack

Information relevant for export toNorth America

XN-QV/1
140097XN-QV/2
140098XN-QV/3
140099XN-QV/4
140100XN-QV/5
140101XN-QV/6
140102XN-QV/7
140103
XN-QV/8
140104

1 off

UL/CSA certification not required–

XN-WEW-35/2SW
140130

1 off

UL/CSA certification not required–

XN-ABPL
140129

1 off

UL/CSA certification not required

Blue

–

1 off

UL/CSA certification not required

Red

–

Green

–

Black

–

Brown

–

Red/blue–

Yellow/green

–

White

–

XN-ANBZ-BL
140105XN-ANBZ-RT
140106
XN-ANBZ-GN
140107
XN-ANBZ-SW
140108XN-ANBZ-BR
140109XN-ANBZ-RT/
BL-BED
140110XN-ANBZ-GN/
GE-BED
140111XN-ANBZ-WS
140112–

SCH-1WINBLOC
140236

1 off

UL/CSA certification not required

Establishes the connection between I/O assistantand the service interface at the gateway.

–

XN-PS2-CABLE
140096

1 off

UL/CSA certification not required–

A5 sheet, perforated, 1 x 57 labels

–

1 off

UL/CSA certification not required–

A5 sheet, perforated, 1 x 6 labels–

XN-LABEL/SCHEIBE
140131XN-LABEL/
BLOCK
140132

Relay jumpers

End bracket

End coverConnection level labels

Shield connection for gateway–

Shield connection for direct bus connection.
Can be used only for XI/ON gateways
XN-GW-PBDP-1.5MB and XN-GW-CANOPEN.

Servicing cable–Labels2010 CA08103002Z-EN

www.eaton.com

Remote I/O XI/ON

Automation products

14/99

Gateways, supply modules

Engineering
Remote I/O XI/ONGateways, supply modules

Gateway XN...GWBR...

GNDL

+ = -

UL

GNDSysUSys

24 V supply from gateway (UL) and system bus (Usys)+ = -24 V HBus refreshing modules
XN-P3x-SBB with gateway power supply
XN-P3…-SBB-B without gateway power supply

XN-P4…-SBBC with gateway power supply
XN-P4…-SBBC-B without gateway power supply

24 V H
Module bus supply+–

24 V H
Module bus supply+––

24 V H
Fieldbus
supply

11

21

12

22

+

13

23

–

24 V H
Fieldbus
supply

11

21

12

22

13

23

14

24

+

PE

Power feeding modules
XN-P3…-SBB for XN-PF-24VDC-D

XN-P4…-SBBC for XN-PF-24VDC-D

11

21

11

21

12

22

12

22

13

23

13

23

14

24

24 V H

24 V HPE

XN-P3...-SBB for XN-PF-120/230VAC-D

11

21

12

22

13

23

XN-P4...-SBB for XN-PF-120/230VAC-D

N

L

11

21

12

22

13

23

14

24

N

L

PE

2010 CA08103002Z-EN

www.eaton.com

14/100 Automation products

Remote I/O XI/ON

Digital input modules
Remote I/O XI/ONDigital input modules

Digital input modules
XN-S3…-SBB for XN-2DI-24VDC-P

SS

XN-S4…-SBBC for XN-2DI-24VDC-P

S

11

21

22

12

22

23

13

23

14

24

11

21

12

13

PE

XN-S3…-SBB for XN-2DI-24VDC-N

S

11

21

12

13

S

S

21

22

12

22

23

13

23

14

24

PE

S

N
L

11

21

12

22

13

23

S

S

L

L

11

21

12

22

13

23

14

24

N

N

www.eaton.com

SPE

XN-S4…-SBBC for XN-2DI-120/230VAC

PE

2010 CA08103002Z-EN

PE

XN-S4…-SBBC for XN-2DI-24VDC-N

11

XN-S3…-SBB for XN-2DI-120/230VAC

S

S

N
L

PE

Remote I/O XI/ON

Automation products 14/101
Digital input modules

Digital input modules
XN-S4…-SBBS for XN-4DI-24VDC-P

SS

XN-S6…-SBBSBB for XN-4DI-24VDC-P

S
11

21

12

S

11

21

22

12

22

13

23

13

23

14

24

14

24

15

25

16

26

S

S

S

XN-S4…-SBBS for XN-4DI-24VDC-N

XN-S6…-SBBSBB for XN-4DI-24VDC-N

S

S

S

S
11

21

12

S

11

21

22

12

22

13

23

13

23

14

24

14

24

S

S

S

XN-B3…-SBB for XN-16DI-24VDC-P

S

S
15

25

16

26

XN-B4…-SBBC for XN-16DI-24VDC-P

S

S

11

21

151 161

152 1621222

152 162

153 16313

23

153 16311

21

151 161

12

22

13

23

PE

S

PE
14

24

154 164

2010 CA08103002Z-EN

www.eaton.com

14/102 Automation products

Remote I/O XI/ON

Digital input modules
Digital input modules
XN-B6…-SBBSBB for XN-32DI-24VDC-P

XNE-8DI-24VDC-P

S

1

S

11

21

S

S

151 161

2

12

22

4

23

S

6

S

153 163

8
9

14

24

154 16415

25

155 1651626

156 166

10SS

24 V H

XNE-16DI-24VDC-P

S

1

S

2

S

3

S

4

S

5

S

6

S

7

S

8

S

9

S

10

S

11

S

12

S

13

S

14

S

15
16

24 V H2010 CA08103002Z-EN

www.eaton.com

S5

152 162

7

13

S

3

S

S

S

Remote I/O XI/ON

Automation products 14/103
Digital output modules

Remote I/O XI/ONDigital output modules

Digital output modules
XN-S4…-SBCS for
XN-2DO-24VDC-0.5A-P
XN-2DO-24VDC-2A-P

XN-S3…-SBC for
XN-2DO-24VDC-0.5A-P
XN-2DO-24VDC-2A-P

S

S

PE

S

11

21

11

21

12

22

12

22

13

23

13

23

14

24

PE

PE

XN-S3…-SBC for XN-2DO-24VDC-0.5A-N

S
11

S
11

12

22

13

23

PE

XN-S3…-SBC for XN-2DO-120/230VAC-0.5A

S
11

+

PE

13

23

S

S

13

23

14

24

N

N

PE

XN-S4…-SBCS for XN-4DO-24VDC-0.5A-P

PE

S
21
N

PE
L

S

22

11

N
22

12

XN-S4…-SBCS for XN-2DO-120/230VAC-0.5A

21

12

21

+

+

PE

S

21

+

PE

XN-S4…-SBCS for XN-2DO-24VDC-0.5A-N

S

PE

S

12

22

13

23

14

24

PE
L

XN-B3…-SBC for XN-16DO-24VDC-0.5A-P

S

11

21

12

22

S

11

21

151 1611222

152 16213

23

153 163

PE

13

23

14

24

S

S

PE

S

2010 CA08103002Z-EN

www.eaton.com

14/104 Automation products

Remote I/O XI/ON

Digital output modules
Digital output modules
XN-S6…-SBCSBC for XN-4DO-24VDC-0.5A-P

XNE-8DO-24VDC-0.5A-P

S

S

S
11

1

S

2

21

S

3

S

4

12

S

5

S

22

6

PE

13

PE

23

S

8
9

S
14

24

15

25

S

7

S

10

GND
24 V H

PE

16

PE

26

XN-B6…-SBCSBC for XN-32DO-24VDC-0.5A-P

S

S

1

S
11

XNE-16DO-24VDC-0.5A-P

S

2

S

3

21

S

4

S

5

12

22

S

6

S

7

PE

13

PE

23

S

8

S

9

S

S
14

S

10

24

PE

15

25

16

26

S

11

S

12

S

13

S
PE

14

S

S 15
16

GND

2010 CA08103002Z-EN

www.eaton.com

Remote I/O XI/ON

Automation products 14/105
Analog input modules

Remote I/O XI/ONAnalog input modules

Analog input modules
XN-S3…-SBB for XN-1AI-I(0/4...20MA)
XN-S3…-SBB for XN-1AI-U(-10/0...+10VDC)
Analog sensor/transmitter, without transmitter supply

XN-S4…-SBBS for XN-1AI-I(0/4...20MA)
XN-S4…-SBBS for XN-1AI-U(-10/0...+10VDC)
Analog transmitter with non-isolated transmitter supply

Uh

Sh

11

21

12

22

Uh+

21

12

22

13

23

14

24

Sh

13

23

XN-S3…-SBB for XN-2AI-I(0/4...20MA), XN-2AI-U(-10/0...+10VDC)
Analog sensor/transmitter, without transmitter supply

Sh

11

11

21

12

22

13

XN-S4…-SBBS for XN-2AI-I(0/4...20MA), XN-2AI-U(-10/0...+10VDC),
Analog transmitter with non-isolated transmitter supply

Uh+

Sh

23

Sh

11

21

12

22

13

23

14

24

Uh+

Sh

XN-S4...-SBBS for XN-2AI-I(0/4...20MA)
Two-conductor connection without external transmitter supply

11

21

12

22

13

23

14

24

2010 CA08103002Z-EN

www.eaton.com

14/106 Automation products

Remote I/O XI/ON

Analog input modules
Analog input modules
XN-S6…-SBCSBC for XN-4AI-U/I
Analog sensor/transmitter, without transmitter supply

Ch1+

Ch2+

11

21

Ch1-

Ch2-

12

22

Sh

24 V H

13

23

14

24

15

25

16

26

21

11

21

12

22

12

22

13

23

13

23

14

24

U/I
2-conductor

+
1

PT100
2

22

14
+

24

23

a
3

PT100
4

i

5

6

7

① Cold-junction compensation in base module2010 CA08103002Z-EN

www.eaton.com

S+

XNE-8AI-U/I-4Pt/Ni

i

23

13

XN-S4…-SBBS for XN-2AI-Pt/Ni-2/3
3-conductor connection

11

XN-S4…-SBBS-CJ for XN-2AI-THERMO-PI

13

22

Sh

S+

12

12

Ch4-

XN-S3…-SBB for XN-2AI-Pt/Ni-2/3
2-conductor connection

21

21

Ch4+

Ch3-

11

11

Sh

Ch3+

Sh

XN-S3...-SSB for XN-AI-U/I
2-conductor connection without external transmitter supply

8

PT/NI
2-conductor 3-conductor
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16

Remote I/O XI/ON

Automation products 14/107
Analog output modules

Remote I/O XI/ONAnalog output modules

Analog output modules
XN-S3...-SSB for XN-1AO-I(0/4...20MA)

11

21

12

22

13

23

XN-S3...-SBB for XN-2AO-I(0/4...20MA)

Channel 1

XN-S3...-SBB for XN-2AO-U(-10/0...+10VDC)

Sh

11

21

12

22

13

23

Sh

Channel 2

XNE-4AO-U/I

U

I
1

11

21

12

22

13

23

1

2
3

Channel 1

Sh

Sh

Channel 2

Sh

Sh

4
5

2

6
7
Sh

Sh

8
9

3

10
11
Sh

Sh

12
13

4

14
15
Sh

Sh

16

2010 CA08103002Z-EN

www.eaton.com

14/108 Automation products

Remote I/O XI/ON

Relay modules
Remote I/O XI/ONRelay modules

Relay modules
XN-S4x...-SBBS with externally applied supply and common potential link for
XN-2DO-R-NC

R1

11

R2

21

12

22
a

13

23

14

24

Module circuit XN-S4x...SBBS for XN-2DO-R-NC

R2

R1

23

13

11

21

c

a
22

12

14

24

b

b
① Linked in the electronics② Cross-link via QVR in the base module③ Electronics module
XN-S4x...-SBCS supply via C-rail and common potential link for XN-2DO-R-NC

Power Relais 1
Feeding

Module circuit XN-S4x...-SBCS for XN-2DO-R-NC

Relais n

11

21 11

21

12

22 12

22

13

23 13

23

14

24 14

24

R1

a

11

21

12

22

13

23

14

24

R2

R2

11

R1

21

c
14
23

24

13

b
a
24 V Hb

24 V H① Supply via C-rail② Max. 8 relay modules① Linked in the electronics② Cross-link via QVR in the base module③ Electronics module

XN-S4x...-SBBS with externally applied supply and common potential link for
XN-2DO-R-NO

Module circuit XN-S4x...-SBBS for XN-2DO-R-NO

R1

11

21

12

22
a

13

23

14

24

R2

R2

R1

23

13

21

c

a
22

12

14

24

b

b
① Linked in the electronics② Cross-link via QVR in the base module③ Electronics module2010 CA08103002Z-EN

11

www.eaton.com

Remote I/O XI/ON

Automation products 14/109
Relay modules

Relay modules
XN-S4x...-SBCS supply via C-rail and common potential link for
XN-2DO-R-NO
Power Relais 1
Feeding

11

21 11

21

12

22 12

22

13

23 13

23

24 14

24

Module circuit XN-S4x...SBCS for XN-2DO-R-NO

Relais n

R1

a

11

21

12

22

13

23

R2

R2

11

R1

21

c
14
23

24

13

b
a

14

14

24

24 V Hb

24 V H① Supply via C-rail② Max. 8 relay modules① Top-hat rail
② Cross-link via QVR in the base module③ Electronics module

XN-S4x...-SBBS for XN-2DO-R-CO

Module circuit XN-S4x...-SBBS for XN-2DO-R-CO

R11

R21
11

21

12

22

R11

R21

R12

R22

R12
12

11

21

23

R22
13

23

14

24

a
14

24

① Electronics module
Definition
At 1000 operations, no arc with a duration > 10 ms must occur.
Load limit curve

U 103
[V]

102

101
0.1

1

10
I [A]

2010 CA08103002Z-EN

www.eaton.com

14/110 Automation products

Remote I/O XI/ON

Technology modules
Remote I/O XI/ONTechnology modules

Serial interfaces
XN-S4x...-SBBS for XN-1RS232 and D-Sub plug

XN-S4x...SBBS for XN-1RS485/422 in RS422 mode

TxD+

RxD
11

21

12

TxD

22

13

23

14

24

6
7

11

1
2

GND

21

GND

3
8
9

TxD-

12

22

13

23

14

24

SHLD

4
5

SHLD

RxD+

CTS

Data in

GND

Data out

RxD-

RTS
SHLD

SHLD

XN-S4x...-SBBS for XN-1SSI on an SSI rotary encoder
SSI device

21

12

22

GND

UL
13

23

14

24

D+

Clock

GND

GND

UL

UL

D-

TxD+/RxD+/P

TxD-/RxD-/N
11

21

GND
Opto array

11

Analog array

CL-

Parallel-serial-converter

CL+

XN-S4...-SBBS for XN-1RS485/422 in RS485 mode

Data in

GND
12

22

SHLD

TxEnable
SHLD

13

23

14

24

Data out

Data out
SHLD

Technology modules / counter
XN-S4...-SBBS for XN-1CNT-24VDC

XNE-1SWIRE
1Counter input Aorpulse input

S+

Counter input Bordirection input
21

12

22

13

23

14

24

2
3
4
5
6

SWIRE

11

24 V H =−UAUXS

XNE-2CNT-2PWM
Counter input A, Pulse input

Counter 2

1

Counter input B, Directional input

2

Synchronization Z

3

Supply 24 V DC
Supply GND

4Counter input A, Pulse input
Counter input B, Directional input

5

Synchronization Z

7

Supply 24 V DC
Supply GND

8Drive 2

M

6

9
10

Output PWM

11Output direction

12

GND

Output PWM

13Output direction

14

GND

15
16

2010 CA08103002Z-EN

www.eaton.com

Counter 1

Drive 1M

Remote I/O XI/ON

Automation products 14/111
Generl information, terminals

Technical data
Remote I/O XI/ONGenerl information, terminals

GeneralStandards
Supported fieldbus systems
Potential isolation
Ambient temperature
Ambient temperature, storage
Relative humidity
Harmful gases
SO2
H2S
Vibration resistance, operating conditions
Mechanical shock resistance
Repetitive shock resistance
Drop and free fallProtection type
Electromagnetic compatibility (EMC)
ESD
Electromagnetic fields
Burst
Surge
HF, asymmetric
Radiated interference (RFI)
Voltage fluctuations
Type test
Approvals

°C
°C
%
ppm
ppm

10 (rel. humidity < 75%, non-condensing)
1.0 (rel. humidity < 75%, non-condensing)According to IEC 60068-2-6
According to IEC 60068-2-27
According to IEC 60068-2-29
According to IEC 60068-2-31, free fall to IEC 60068-2-32
IP20
EN 61000-4-2
EN 61000-4-3
EN 61000-4-4
EN 61000-4-5
EN 61000-4-6
EN 55016-2-3
EN 61131-2
To EN 61131-2
CE, cUL (may be in preparation)

Gateways XN, basic modules

Gateways XNE, electronics modules XNEmmmm2

To VDE 0611 Part 1/8.92 /IEC/EN 60947-7-1
Spring-loaded/screw terminals
8
0.5 - 2.5

To VDE 0611 Part 1/8.92 /IEC/EN 60947-7-1
Push-in spring-cage terminals
80.14 - 1.5

mm2
mm2
mm2

0.5 - 2.5
0.5 - 1.5
0.5 - 1.5

0.25 - 1.5
0.25 - 1.5
0.25 - 1.5

mm2

0.5 - 1.5

0.25 - 0.75

A1

A1

Terminals
Dimensional data
Connection from above
Cable stripped lengthMax. terminal capacity
Connectable conductors“e” solid H07V-U“f” flexible H 07V-K“f” with ferrule without plastic collar to
DIN 46228-1 (ferrules gas-tight)“f” with ferrule with plastic collar to
DIN 46228-1 (ferrules gas-tight)
Gage pin IEC/EN 60947-1

EN 61000-6-2, EN 61000-6-4, EN 61131-2
PROFIBUS-DP, CANopen, DeviceNet, Ethernet (depending on gateway)
Yes, through optocoupler
0 - 55-25 - +85
5 – 95 (indoor), Level RH-2, non-condensing (for storage at 45°C)

2010 CA08103002Z-EN

www.eaton.com

14/112 Automation products

Remote I/O XI/ON

Gateways

Gateways XNE
Fieldbus
ProtocolMaximum number of stations
System supply
Permissible range, 5 V DC
Permissible range, 24 V DC
Field voltage
Permissible range
RippleServicing interface
Fieldbus terminals
Transfer rate
Data transfer
rate setting
Address assignment

USYS
USYS
USYS
UL
UL

V DC
V DC
V DC
V DC
V DC
%

kBit/sFieldbus termination
Number of parameter bytes
Number of diagnosis bytes
Address range

XNE-GWBR-PBDP

XNE-GWBR-CANOPEN

XNE-GWBR-2ETH-IP

PROFIBUS-DPPROFIBUS-DPV0 and PROFIBUS-DPV1
48 modules (XN, XNE) of slice design
or max. length of station: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30< 5 (to EN 61131-2)
PS/2 socket
Push-in spring-cage terminals
9.6 - 12000
Automatic

Ethernet
EtherNet-IP
74 modules (XN, XNE) of slice design
or max. length of station: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30< 5 (to EN 61131-2)
Mini USB
2x RJ45 socket
10000, 100000
Automatic

Through DIP switch

CANopenCANopen
62 modules (XN, XNE) of slice design
or max. length of station: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30< 5 (to EN 61131-2)
PS/2 socket
Push-in spring-cage terminals
20, 50, 125, 250, 500, 800, 1000
Through DIP switch
or automaticallyThrough DIP switch

Through DIP switch22
1 - 125 decimalThrough DIP switch
1 - 63 decimalThrough DIP switch,
BootP, DHCP or PGM
1 - 254 decimal

Remote I/O XI/ONGateways

Gateways XN with built-in supply module
Fieldbus
ProtocolMaximum number of stations

System supply
Permissible range, 5 V DC
Permissible range, 24 V DC
Field voltage
Permissible range
RippleServicing interface
Fieldbus terminals

USYS
USYS
USYS
UL
UL

Transfer rate

V DC
V DC
V DC
V DC
%

kBit/sData transfer
rate setting
Address assignment

Fieldbus termination
Number of parameter bytes
Number of diagnosis bytes
Address range
Program data
Program code
Cycle time for 1 k of
instructions (bits, bytes)
Real-time clock2010 CA08103002Z-EN

kByte
kByte
ms

www.eaton.com

XN-GWBR-PBDP

XN-GWBRCANOPEN

XN-GWBR-DNET

XN-GWBRMODBUS-TCP

XN-PLCCANOPENPROFIBUS-DPPROFIBUS-DPV0
74 modules(XN, XNE) of
slice design ormax. length ofstation: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30< 5 (to EN 61131-2)
PS/2 socket
1x D-sub 9-pin
socket9.6 - 12000

CANopenCANopen
74 modules(XN, XNE) of
slice design ormax. length ofstation: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30

DeviceNet
DeviceNet
74 modules(XN) ofslice design ormax. length ofstation: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30

Ethernet
Modbus-TCP
74 modules(XN, XNE) of
slice design ormax. length ofstation: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30

CANopenCANopen
74 modules(XN, XNE with limitations) of slice design
or max. length ofstation: 1 m
24 V DC/5 V DC
4.7 - 5.3
18 - 30
24
18 - 30

PS/2 socket
Open styleconnector
10, 20, 50, 125, 250,
500, 800, 1000
Through DIP switch

PS/2 socket
Open styleconnector
125, 250, 500

PS/2 socket
RJ45 bus

Through DIP switch

Automatic

PS/2 socket
Open styleconnector
10, 20, 50, 125, 250,
500, 800, 1000
Software2 decimal
rotary coding
switches

2 decimal
rotary coding
switches

2 decimal
rotary coding
switches

Decimal rotarycoding switch,
BootP, DHCP or
I/OassistantExternal
53
1 - 99 decimal-External

External

1 - 99 decimal-

1 - 63 decimal-

1 - 254 decimal-

1 - 127 decimal
128
128
0.5

-

-

-

-

Yes

10000, 100000

SoftwareExternalRemote I/O XI/ON

Automation products 14/113
Gateways, supply modules

Remote I/O XI/ONGateways, supply modules

XN gateways without built-in supply module
Fieldbus
ProtocolMaximum number of stations

Operating voltage

V DC

Permissible range
RippleRated current drawn from modulebusServicing interface
Fieldbus terminals

V DC
%
mA

IMB

Transfer rate

kBit/sData transfer rate setting
Address assignment
Fieldbus termination
Number of parameter bytes
Number of diagnosis bytes
Address range

Supply modules
Operating voltage
System supply
Permissible range, 24 V DC
Permissible range, 5 V DC

Field voltage
Permissible range
Rated current drawn from modulebus
Insulation test
RippleMaximum operating current
Maximum system supply current
Number of diagnostic bits
Base module without gateway
power supply
Without C connection

XN-GW-PBDP-12MB

XN-GW-CANOPEN

XN-GW-DNET

PROFIBUS-DPPROFIBUS-DPV0
74 modules (XN) of
slice design ormax. length of station: 1 m
5 (from bus refreshing
module)4.7 - 5.3
< 5 (to EN 61131-2)≦ 430

PROFIBUS-DPPROFIBUS-DPV0
74 modules (XN) of
slice design ormax. length of station: 1 m
5 (from bus refreshing
module)4.7 - 5.3
< 5 (to EN 61131-2)≦ 430

CANopenCANopen
74 modules (XN) of
slice design ormax. length of station: 1 m
5 (from bus refreshing
module)4.7 - 5.3
< 5 (to EN 61131-2)≦ 350

DeviceNet
DeviceNet
74 modules (XN) of
slice design ormax. length of station: 1 m
5 (from bus refreshing
module)4.7 - 5.3
< 5 (to EN 61131-2)≦ 250

PS/2 socket
2 x D-sub 9-pin sockets;
2 x spring-loaded terminal
strips for direct wiring

PS/2 socket
1x D-sub 9-pin socket

PS/2 socket
Open style connector

9.6 - 1500

9.6 - 12000

Through two hex rotarycoding switches
Through D-sub plug
53
1 - 125 decimalThrough two hex rotarycoding switches
Through D-sub plug
53
1 - 125 decimal

PS/2 socket
1 x D-sub 9-pin socket;
1 x D-sub 9-pin plug;2 x spring-loaded terminal
strips for direct wiring,
5 -pin10, 20, 50, 125, 250, 500,
800, 1000
Through DIP switch
Through two hex rotarycoding switches
Through D-sub plug
1 - 127 decimal

125, 250, 500
Through DIP switch
Through two decimalrotary coding switches
Through DIP switch
0 - 63 decimal

XN-BR-24VDC-D

XN-PF-24VDC-D

XN-PF-120/230VAC-D

24 V DC
24
18 - 301)
4.7 - 5.3

24 V DC-120⁄230 V AC-

24 V DC
18 - 30 V DC

24 V DC
18 - 30 V DC2)

USYS
USYS
UMB
(built into
system)
UL
UL

V DC
V DC
V DC

IMB

mA

-

≦ 28

120/230 V AC
102 - 132 V AC (120 V AC)
195.5 - 253 V AC (230 V AC) 3)
≦ 25

Ui

V AC
%
A
A

500
< 5 (to EN 61131-2)
10
1.5
4

500
< 5 (to EN 61131-2)
10
4

1500
< 5 (to EN 61131-2)
10
4

XN-P3...-SBB
XN-P3...-SBB-B
XN-P4...-SBBC
XN-P4...-SBBC-B

XN-P3...-SBB

XN-P3...-SBB

XN-P4...-SBBC

XN-P4...-SBBC

IL
IMB

With C connection
Notes

XN-GW-PBDP-1.5MB

1)

2)
3)

Permissible range for system supply:for USYS = 24 V DC: 18 to 30 V DC (to EN 61131-2)
Permissible range for field voltage UL: to EN 61131-2 (18 to 30 V DC)
Permissible range for rated voltage and field voltage UL: to EN 61131-2

2010 CA08103002Z-EN

www.eaton.com

14/114 Automation products

Remote I/O XI/ON

Remote I/O XI/ON

Automation products

Digital input modules

14/115

Digital input modules

Remote I/O XI/ONDigital input modules

Digital input modules
Channels
Rated voltage at supply terminal
Rated current drawn from supply terminal1), 2)
Rated current drawn from module bus2)
Insulation test
Heat dissipation
Input voltage
Input voltage, rated value
Low level
High level
Frequency range
Input current
Low level⁄active level
High level⁄active level
Input delay
trising edge
tfalling edge
Basic modules
Without C connection

XN-2DI-24VDC-P

XN-2DI-24VDC-N

XN-2DI-120/230VAC

XN-4DI-24VDC-P

XN-4DI-24VDC-N

XN-16DI-24VDC-P

XN-32DI-24VDC-P

XNE-8DI-24VDC-P

XNE-16DI-24VDC-P

mA
mA
V AC
W

2
24 V DC
≦ 20
≦ 28
500
0.7

2
24 V DC
≦ 20
≦ 28
500
0.7

2
120/230 V AC
≦ 20
≦ 28
1500
1

4
24 V DC
≦ 40
≦ 29
500
1

4
24 V DC
≦ 40
≦ 28
500
1

16
24 V DC
≦ 40
≦ 45
500
2.5

32
24 V DC
≦ 30
≦ 30
500
4.2

8
24 V DC
≦ 1.5
≦ 15
500
< 1.5

16
24 V DC
≦3
≦ 15
500
< 2.5

24 V DC
30 V - (UL - 11 V)
0-5V-

120/230 V AC
0 - 20 V AC
79 V AC - 265 V AC3)
48 - 63

24 V DC-30 V - +5 V
15 V - 30 V

24 V DC
30 V - (UL - 11 V)
0-5V

24 V DC-30 V - +5 V
15 V - 30 V

24 V DC-30 V - +5 V
15 V - 30 V

24 V DC-UL - +5 V
11 V - UL

24 V DC-UL - +5 V
11 V -ULHz

24 V DC-30 V - +5 V
11 - 30 V
0 mA - 1.5 mA
2 mA - 10 mA

0 mA - 1.7 mA
1.8 mA - 10 mA

0 mA - 1 mA
3 mA - 10 mA

0 mA - 1.5 mA
2 mA - 10 mA

0 mA - 1.2 mA
1.3 mA - 6 mA

0 mA - 1.5 mA
2 mA - 10 mA

0 mA - 1.5 mA
2 mA - 10 mA-1 mA - 1.5 mA
2 mA - 5 mA

-1 mA - 1.5 mA
2 mA - 5 mA

< 200
< 200

< 200
< 200

< 20000< 20000

< 200
< 200

< 200
< 200

< 200
< 200

< 200
< 200

< 100
< 200

< 150
< 300

XN-S3...-SBB
2-conductor proximity
switches (Bero®) can
be connected, with apermissible quiescentcurrent of up 1.5 mA.
XN-S4...-SBBC

XN-S3...-SBB
2-conductor proximity
switches (Bero®) can
be connected, with apermissible quiescentcurrent of up 1.5 mA.
XN-S4...-SBBC

XN-S3...-SBB

XN-S4...-SBBS
XN-S6...-SBBSBBXN-S4...-SBBS
XN-S6...-SBBSBB

XN-B3...-SBB

XN-B6...-SBBSBB

Already built in

Already built in

Number
UL
IL
IMB
Ui

μs
μs

With C connection
1)

Notes

2)

3)

2010 CA08103002Z-EN

www.eaton.com

XN-S4...-SBBC

XN-B4...-SBBC

The supply terminal (UL) provides power for the module electronics and for thesensors at the inputs. The total current required for each module consists of thesum of all partial currents.
Part of the XI/ON module’s electronics is supplied with module bus voltage (5 V DC),the other part through the supply terminal (UL).
Max. permissible capacity: 141 nF at 79 V AC/50 Hz; 23 nF at 265 V AC/50 Hz

2010 CA08103002Z-EN

www.eaton.com

14/116 Automation products

Remote I/O XI/ON

Remote I/O XI/ON

Automation products 14/117

Digital output modules

Digital output modules

Remote I/O XI/ONDigital output modules

Digital output modules
Channels
Rated voltage at supply terminal
Rated current drawn from supply terminal(for 0 mA load current)1)
Rated current drawn from module bus 2)
Insulation test
Heat dissipation
Output voltage
High level
Output current
High level (rated)
High level (permissible range)
Low level
Back-up fuse
Surge current
Number of parallel-switchable outputs
Total module current
Delay for signal changeover, resistive load
From Low to High level
From High to Low level
Load resistance range

Utilization factor
The following can be connected:

XN-2DO-24VDC-0.5A-P

XN-2DO-24VDC-0.5A-N

XN-2DO-120/230VAC-0.5A

XN-2DO-24VDC-2A-P

XN-4DO-24VDC-0.5A-P

XN-16DO-24VDC-0.5A-P

XN-32DO-24VDC-0.5A-P

XNE-8DO-24VDC-0.5A-P

XNE-16DO-24VDC-0.5A-P

2
24 V DC≦ 20

2
120/230 V AC (45 - 65 Hz)

mA

2
24 V DC≦ 20

2
24 V DC≦ 50

424 V DC≦ 25

16
24 V DC≦ 30

32
24 V DC≦ 50

824 V DC≦ 3 mA (all outputs OFF)16
24 V DC≦ 3 mA (all outputs OFF)

mA
V AC
W

≦ 32
500
Normally 1

≦ 32
500
Normally 1

≦ 35
1500
Normally 1

≦ 33
500
Normally 1

≦ 30
500
Normally 1

≦ 120
500
Normally 4

≦ 30
500
Normally 5≦ 15 mA
500
Normally 1.5≦ 25 mA
500
Normally 2.5> UL - 1 V DC

< GNDL + 1 V DC

> UL - 2 V AC, (zero-pointswitching triac)> UL - 1 V DC

> UL - 1 V DC

> UL - 1 V DC

> UL - 1 V DC

> UL - 1 V DC

> UL - 1 V DC

0.5
< 0.6

0.5
< 0.6

0.53)
0.02 - 0.5< 1.5
500 mA FF
8 (1 period at 60 Hz)

2
< 2.4

0.5
< 0.6

0.5
< 0.6

0.5
< 1.0

0.53)
< 1.0

0.53)
< 1.0

A

1

1

1

4

4
2

8

2
10

μs
μs

< 100
< 100
> 48 Ω

< 100
< 100

< 100
< 100
< 12 Ω< 250< 250> 48 Ω< 100< 100> 48 Ω< 300< 300> 48 Ω

< 300
< 300

< 300
< 300

g

Ω
H

100
Resistive loads
Inductive loads
Lamp loads
> 48
< 1.2

100
Resistive loads
Inductive loads
Lamp loads
> 48
< 1.2

< T/2 + 1 ms
< T/2 + 1 ms
At 120 V AC:
240 Ω - 6 kΩ
At 230 V AC:
460 Ω - 11.5 kΩ
100 (observe derating)Resistive loads
Inductive loads
Lamp loads

100
Resistive loads
Inductive loads
Lamp loads
> 12
< 1.2

100
Resistive loads
Inductive loads
Lamp loads
> 48
< 1.2

100
Resistive loads
Inductive loads
Lamp loads
> 48
< 1.2

See total module current
Resistive loads
Inductive loads
Lamp loads
> 48
< 1.2

RLL

W

<3

< 12

<6

<6

<3

<6

100
Resistive loads
Inductive loads
Lamp loads> 48
As for DC13 toIEC 60947-5-1<650%, max. 4 A
Resistive loads
Inductive loads
Lamp loads> 48
As for DC13 toIEC 60947-5-1
<6

f

Hz
Hz

< 5000 (RLO < 1 kΩ)<2< 100 (RLO < 1 kΩ)<2< 5000 (RLO < 1 kΩ)<2< 1000 (RLO < 1 kΩ)<2< 100 (RLO < 1 kΩ)< 100(RLO < 1 kΩ)

Hz

< 10
2
Yes
Protected
Self-acting

< 10
2
Yes
Protected
Self-acting

< 10
1
Yes
Short-circuit proof
Self-acting< 100
As for DC13 toIEC 60947-5-1
< 10

No

< 10
2
Yes
Protected
Self-acting< 100
As for DC13 toIEC 60947-5-1
< 10

4
Yes
Short-circuit proof
Self-acting

8
Yes
Short-circuit proof
Self-acting

Short-circuit proof
Self-acting
Already built in

Short-circuit proof
Self-acting
Already built in

XN-S3...-SBC
XN-S4...-SBCS

XN-S3...-SBC
XN-S4...-SBCS

XN-S3...-SBC
XN-S4...-SBCS

XN-S3...-SBC
XN-S4...-SBCS

XN-S4...-SBCS
XN-S4...-SBCSBC

XN-B3...-SBC

XN-B6...-SBCSBC

Number
UL
IL
IMB
Ui

A
A
A
mA
IS
max.

%

Resistive load
Inductive load
Lamp load
Switching frequency
For resistive load
For inductive load
For lamps
Number of diagnostic bits
Diagnostics
Outputs to EN 61131-1
Retriggering after elimination of short circuit
Basic modules
With C connection

A

Ii

1)

Notes

2)

3)

2010 CA08103002Z-EN

www.eaton.com

The supply terminal (UL) provides power for the module electronics and for the
consumers at the outputs. The total current required for each module consists ofthe sum of all partial currents.
Part of the XI/ON module’s electronics is supplied with module bus voltage (5 V DC),the other part through the supply terminal (UL).
To increase the maximum output current to up to 1 A, two outputs can be connectedin parallel.

2010 CA08103002Z-EN

www.eaton.com

14/118 Automation products

Remote I/O XI/ON

Remote I/O XI/ON

Automation products 14/119

Analog input modules

Analog input modules

Remote I/O XI/ONAnalog input modules

XN-1AI-I(0/4...20MA)

XN-2AI-I(0/4...20MA)

XN-1AI-U(-10/0...+10VDC)

XN-2AI-U(-10/0...+10VDC)

XN-4AI-U/I

XN-2AI-THERMO-PI

XN-2AI-Pt/Ni-2/3

XNE-8AI-U/I-4Pt/Ni

Current

Current

Voltage

Voltage

Voltage, current

1
24 V DC
≦ 50
≦ 41
<1
Bridged with UL and GNDL ofincoming unit; not protected2
24 V DC
≦ 12
≦ 35
<1
≦ 250 mA; bridged with UL and GNDL
of incoming unit; not protected1
24 V DC
≦ 50
≦ 41
<1
Bridged with UL and GNDL ofincoming unit; not protected2
24 V DC
≦ 12
≦ 35
<1
≦ 250 mA; bridged with UL and GNDL
of incoming unit; not protected

4
24 V DC
≦ 20
≦ 50
<1
-

Temperature (thermocouples)2
24 V DC
≦ 30
≦ 45
<1
-

Temperature Pt, Ni
resistance R
2
24 V DC
≦ 30
≦ 45
<1
-

Voltage, current, temperature Pt,
Ni resistance R
8 (U/I)/4 (Pt/Ni/R)
24 V DC
Normally 35
≦ 30
< 1.5
-

Voltage measurement
Measurement ranges---10 - 10 V DC/0 - 10 V DC

-10 - 10 V DC/0 - 10 V DC

-10 - 10 V DC/0 - 10 V DC-

-10 - 10 VDC/0 - 10 V DC

Value representation--

Standard, 16 bit/12 bit
left-aligned

Standard, 16 bit/12 bit
left-aligned

Standard, 16 bit/12 bit
left-aligned-50 - 50 mV, -100 - 100 mV-500 - 500 mV, -1000 - 1000 mVStandard, 16 bit/12 bit
left-aligned

-

-

-

2-/3-/4-conductor + shield35≧ 98.5 kΩ
200< 0.2≦ 300 ppm/°C of full-scalevalue

2-/3-conductor + shield35≧ 98.5 kΩ
50< 0.2≦ 150 ppm/°C of full-scale value

2-conductor + shield30≧ 98.5 kΩ
20< 0.3≦ 300 ppm/°C of full-scalevalue

2-conductor10< 0.2 (normally)≦ 300 ppm/°C of full-scale
value

-

Standard, 16-bit/12-bit (left-aligned)
Extended range, 16-bit/12-bit (left-aligned)
PA (NE43), 16-bit/12-bit (left-aligned)
2-conductor±20≧ 200 kΩ1.5
< 0.2
≦ 200 ppm/°C of full-scale value

0 - 20 mA/4 - 20 mA
Standard, 16 bit/12 bit
left-aligned

0 - 20 mA/4 - 20 mA
Standard, 16 bit/12 bit
left-aligned--

0 - 20 mA/4 - 20 mA
Standard, 16 bit/
12 bit left-aligned--

2-/3-/4-conductor + shield
2-/3-conductor + shield
50
50< 125 Ω
< 125 Ω
200
50
< 0.2
< 0.2
≦ 300 ppm/°C of full-scale value--

2-conductor + shield50< 62 Ω
20< 0.3≦ 300 ppm/°C of full-scale value

-

-

-

-

-

-

-

Measurement ranges

-

-

-

-

-

Value representation
The following can be connected:

-

-

-

-

-

-

-

-

-

-

-

-

-

-

-

Thermocouple type B, E, J, K, Pt100 RTD, Pt200, Pt500,
N, R, S, T to IEC 584,
Pt100 RTD0 (EN 60751)
Class 1, 2, 3
Ni100, Ni1000 (DIN 43760)
Type B: 100 - 1820 °C
Platinum RTDs:
Type E: -270 - 1000 °C-200 – 850 °C/-200 – 150 °C
Type J: -210 - 1200 °C
Nickel RTDs:
Type K: -270 - 1370 °C-60 – 250 °C/-60 – 150 °C
Type N: -270 - 1300 °C
Type R: -50 - 1760 °C
Type S: -50 - 1540 °C
Type T: -270 - 400 °C
Standard, 16 bit/12 bit left-aligned
2-conductor (cold-junction
2-conductor/3-conductor
compensation in base module)< 1 mA> 30< 0.2 (type T, -200 - 0 °C:
< 0.2
0.6%)
≦ 300 ppm/°C of full-scale value ≦ 300 ppm/°C of full-scale value

-

-

-

-

-

-

-

-

-

-

-

-

XN-S3...-SBB
XN-S4...-SBBS

XN-S3...-SBB
XN-S4...-SBBS

XN-S3...-SBB
XN-S4...-SBBS

XN-S3...-SBB
XN-S4...-SBBS

XN-S6...-SBCSBC-With integrated cold-junction
compensation XN-S4...-SBBS-CJ

Analog input modules
Measured variables
NumberChannels
Rated voltage at supply terminal
Rated current drawn from supply terminal1), 2)
Rated current drawn from module bus 2)
Heat dissipation
Sensor/transmitter supply

UL
IL
IMB

The following can be connected:
Maximum input voltage
Input resistance
Limiting frequency
Basic error limit at 23 °C
Temperature coefficient

Umax.
RL
fG

Current measurement
Measurement ranges
Value representation

mA
mA
W

V DC
kΩ
Hz
%

mA

The following can be connected:
Maximum input current
Input resistance
Limiting frequency
Basic error limit at 23 °C
Temperature coefficient
Temperature measurement
Connectable sensors

Imax.
RL
fG

Measuring current
Destruction limit
Basic error limit at 23 °C

Imess
Umax.

mA
Ω
Hz
%

V DC
%

Temperature coefficient
R (resistance measurement)
Measurement ranges
Value representation
The following can be connected:
Destruction limit
Limiting frequency
Basic error limit at 23 °C
Temperature coefficient

Umax.
fG

Basic modules
Without C connection
Without C connection,
for sensor supply
1)

Notes

2)

2010 CA08103002Z-EN

www.eaton.com

V DC
Hz
%

0 - 20 mA/4 - 20 mA
Standard, 16-bit/12-bit (left-aligned)
Extended range, 16-bit/12-bit (left-aligned)
PA (NE43), 16-bit/12-bit (left-aligned)
2-conductor
40 (Max. input voltage: < 17 V)< 52 Ω
1.5< 0.2≦ 200 ppm/°C of full-scale value
Pt100 RTD, Pt200, Pt500, Pt100 RTD0
(all: EN 60751)
Ni100, Ni1000 (DIN 43760), Ni1000TK5000
Platinum RTDs:-200 – 850 °C/-200 – 150 °C
Nickel RTDs:-60 – 250 °C/-60 – 150 °C

2-conductor/3-conductor< 0.5 mA
> 30
Pt100 RTD, Ni100: 0.35%, Pt200, Pt500, Pt100
RTD0, Ni1000, Ni1000TK5000: 0.2%
≦ 200 ppm/°C of full-scale value

0 - 100 Ω, 0 - 200 Ω, 0 - 400 Ω, 0 - 250 Ω, 0 - 400 Ω, 0 - 800 Ω, 0 - 2000 Ω,
0 - 1000 Ω
0 - 4000 ΩStandard, 16 bit/12 bit left-aligned
2-conductor/3-conductor
2-conductor/3-conductor
> 30
> 30
1.5
< 0.2
< 0.2
≦ 300 ppm/°C of full-scale≦ 200 ppm/°C of full-scale value
value
XN-S3...-SBB
XN-S4...-SBBS

Already built in-

The supply terminal (UL) provides power for the module electronics and for the analog transmitters at the inputs. The total
current required for each module consists of the sum of all partial currents.
Part of the XI/ON module’s electronics is supplied with module bus voltage (5 V DC), the other part through the supply
terminal (UL).

2010 CA08103002Z-EN

www.eaton.com

14/120 Automation products

Remote I/O XI/ON

Analog output modules
Remote I/O XI/ONAnalog output modules

Analog output modules
Measured variables
Channels
Rated voltage at supply terminal
Rated current drawn from supply
terminal1)
Rated current drawn from module bus 1)
Heat dissipation

XN-1AO-I(0/4...20MA)

XN-2AO-I(0/4...20MA)

XN-2AO-U(-10/0...+10VDC)

XNE-4AO-U/I

mA

Current
1
24 V DC≦ 50

Current
2
24 V DC≦ 50

Voltage2
24 V DC≦ 50

Voltage, current
4
24 V DC
≦ 150

mA
W

≦ 39
Normally 1≦ 40
Normally 1≦ 43
Normally 1

≦ 40
<3

V DC

-

-

-10 - 10 V DC/ 0 - 10 V DC
Standard, 16 bit/12 bit
left-aligned--

2-conductor + shield-10 - 10 V DC/ 0 - 10 V DC
Standard, 16-bit/12-bit(left-aligned)
Extended range, 16-bit/
12-bit (left-aligned)
PA (NE43), 16-bit/12-bit(left-aligned)
2-conductor> 1000<1< 100> 1000
<1
< 20

< 0.1
< 0.5
< 0.5
≦ 40
< 0.2
≦ 300 ppm/°C of full-scale
value

<1
<2
<2
≦ 40
< 0.2
≦ 200 ppm/°C of fullscale value

0 - 20 mA/4 - 20 mA
Standard, 16 bit/12 bit
left-aligned

0 - 20 mA/4 - 20 mA
Standard, 16 bit/12 bit
left-aligned-

2-conductor + shield

2-conductor + shield-

0 - 20 mA/4 - 20 mA
Standard, 16-bit/12-bit(left-aligned)
Extended range, 16-bit/
12-bit (left-aligned)
PA (NE43), 16-bit/12-bit(left-aligned)
2-conductor

Ω
μH
Hz

< 550
<1
< 200

< 450
<1
< 200

-

< 450
<1
< 20

ms
ms
ms
mA
%

< 0.1
< 0.5
< 0.5

<2
<2
-

-

< 0.2
≦ 300 ppm/°C offull-scale value< 0.2≦ 300 ppm/°C offull-scale value

-

<1
<2
<2
≦ 40
< 0.2
≦ 200 ppm/°C offull-scale value

XN-S3...-SBB

XN-S3...-SBB

XN-S3...-SBB

NumberUL
IL
IMB

Output value, Voltage
Output voltage
Value representation

The following can be connected:
Load resistor
Resistive load
Capacitive load
Transfer frequency
Recovery time
Resistive load
Inductive load
Capacitive load
Short-circuit current
Basic error limit at 23 °C
Temperature coefficient
Output value, current
Output current
Value representation

Ω
μF
Hz
ms
ms
ms
mA
%

mA

The following can be connected:
Load resistor
Resistive load
Inductive load
Transfer frequency
Recovery time
Resistive load
Inductive load
Capacitive load
Short-circuit current
Basic error limit at 23 °C
Temperature coefficient
Basic modules
Without C connection

1)2010 CA08103002Z-EN

www.eaton.com

Already built inPart of the XI/ON module’s electronics is supplied with module bus voltage (5 V DC), the other part throughthe supply terminal (UL).

Remote I/O XI/ON

Automation products 14/121
Relay modules

Remote I/O XI/ONRelay modules

Relay modules
Contact type
Rated voltage at supply terminal
Rated current drawn from supply
terminal
Rated current drawn from module bus
Insulation test
Heat dissipation
The following can be connected:

Nominal load voltage
Output current for channel / 230 V AC
Maximum continuous current
Maximum continuous
current, resistive load
Minimum load current
Output current for DC voltage(resistive)
Utilization factor
Lifespan at 230 V AC
At 5 AAt 0.5 A
Basic modules
Without C connection
With C connection

XN-2DO-R-NC

XN-2DO-R-NO

XN-2DO-R-CO

2 NC
24 V DC≦ 20

2 N/O
24 V DC≦ 20

2 change-over contacts
24 V DC
≦ 20

mA
V AC
W

≦ 28
1500, 500
Normally 1
Resistive loads
Inductive loads
Lamp loads
230 V AC, 30 V DC

≦ 28
1500, 500
Normally 1
Resistive loads
Inductive loads
Lamp loads
230 V AC, 30 V DC

≦ 28
1500, 500
Normally 1
Resistive loads
Inductive loads
Lamp loads
230 V AC, 30 V DC

A

2
5 A, load-dependent2
5 A, load-dependent2
5 A, load-dependentmA

100 mA at 12 V DC
Load limit curve ￫ Page 14/109

100 mA at 12 V DC
Load limit curve ￫ Page 14/109

100 mA at 12 V DC
Load limit curve ￫ Page 14/109

g

%

100

100

100

Operations
Operations

x 106

> 0.1

> 0.1

> 0.1

x 106

>1

>1

>1

XN-S4...-SBBS
XN-S4...-SBCS

XN-S4...-SBBS
XN-S4...-SBCS

XN-S4...-SBBS

UL
IL
IMB
Ui

mA

2010 CA08103002Z-EN

www.eaton.com

14/122 Automation products

Remote I/O XI/ON

Technology modules
Remote I/O XI/ONTechnology modules

Rated voltage at supply terminal
Rated current drawn from supply terminal
Rated current drawn from module bus
Heat dissipation
Power supply of encoders

UL
IL
IMB

Digital inputs
Input voltage
Input voltage, rated value
Low level
High level
Input current
Low level
High level
Minimum pulse width
Counter modules
Channels
Resolution

XN-1CNT-24VDC

XNE-2CNT-2PWM

24 V DC≦ 501)≦ 40< 1.3
Output voltage UL (-0.8 V)
Output current ≦ 0.5 A, short-circuit proof

24 V DC
≦ 20
≦ 50
<3
Output voltage UL, GNDL
Output current 0.5 A, not protectedt

V DC

24
-30 V DC - 5 V DC
11 V DC - 30 V DC

24
-30 V DC - 5 V DC
11 V DC - 30 V DC

mA
mA
μs

-8 mA - 1.5 mA
2 mA - 10 mA
Filter on: > 25 μs (20 kHz)
Filter off: < 2.5 μs (200 kHz)

-1 mA - 1.5 mA
2 mA - 10 mA
Filter on: > 25 μs (20 kHz)
Filter off: < 2.5 μs (200 kHz)

Number
bit

1
32

2
32

0.1 Hz - 200 kHz
1 rpm- 25000 rpm
5 ms - 120 s

0.01 Hz – 200 kHz (scaleable)
Scaleable
5 ms – 120 s (scaleable)

Pulse and direction, rotary encoder:single/double/quadruple
Endless count, count once,
count periodically
8 bit
8 bit / max. 0.51 s
Once/periodic
Upper count limit: 0 - 7FFF FFFF
Lower count limit: 8000 0000 - FFFF FFFF

Pulse and direction, rotary encoder:single/double/quadruple
Endless count, count once,
count periodically
32 bit32 bit / max. 120 s
Once/periodic
Upper count limit: 0 - 7FFF FFFF
Lower count limit: 8000 0000 - FFFF FFFF

Pulse and direction, single rotary encoder

Pulse and direction, single rotary encoder

24≦ 3 V DC≧ UL (-1 V)

24≦ 3 V DC≧ UL (-1 V)

5 mA - 2 A≦ 0.5 A (55° C)

5 mA - 0.6 A
0.5 A (55° C)

100
2
≦ 10
≦ 10
100 μs (resistive load)
Yes

20000 / 100-

20.01Hz - 20 kHz
32-bit at 41.6 ns/bit
32-bit at 41.6 ns/bit
32-bit at 41.6 ns/bit
32-bit Counter
Once, endless

1 bit
15 bit4 Byte16 ByteXN-S4...-SBBS

Already built in

mA
mA
W

Measurement ranges
Frequency
Rotational speed
Period duration
Counter modes
Signal evaluation A, B
Operating Mode
Hysteresis
Pulse duration
Synchronization
Counter limits
Measurement modes
Signal evaluation A, B
Digital outputs
Output voltage
Output voltage, nominal value
Low level
High level
Output current
High level (permissible range)
High level (nominal)
Switching frequency
For resistive load
For inductive load
For lamps
Lamp load
Output delay
Short-circuit rating
PWM module
Channels
PWM
Period duration/duty cycle
Pulse duration
Pause time
Output, number of pulses
Pulse output modes

V DC

RLL

Hz
Hz
Hz
W

Number

General data
Diagnostics
Parameters
Basic modules
No C-connection for sensor/transmitter supply

1) The figures for rated operational current from the supply terminal apply for

Notes

load current = 0 mA.

2010 CA08103002Z-EN

25 μs (resistive load)Yeswww.eaton.com

Remote I/O XI/ON

Automation products 14/123
Technology modules

Remote I/O XI/ONTechnology modules

Interfaces
Type
Rated voltage at supply terminal
Rated current drawn from supply terminal
Rated current drawn from module bus
Heat dissipation
Transfer channels
Data buffer
Receive
Send
Connection type
RS 232RS 485
RS422

UL
IL
IMB

mA
mA
W

Byte
Byte

XN-1RS485/422

XN-1SSI

RS232
24 V DC0≦ 140
Normally 1
RxD, TxD, RTS, CTS

RS485⁄RS422
24 V DC≦ 25≦ 60
Normally 1
RxD, TxD

SSI
24 V DC≦ 251)≦ 50
Normally 1
CL, D

128
64

128
64

-

Full-duplex-

2-wire, half-duplex
2-conductor, half-duplex or
4-conductor, full-duplex
Max. 115200 bits⁄s (parameterizable),Standard: 9600 bits⁄s, 7 data bits,
odd parity and 2 stop bits

4-conductor, full-duplex(clock output/signal input)
Max. 1 MHz(parameterizable), default
settings: 500 kBit/s

Veff

500

500

500

Veff
V DC
Ω
Ω
m

500
-7 - 12Max. 15
1
4

500

500

120
120 (external)
Max. 301
4120internalMax. 30
1
4

XN-S4...-SBBS

XN-S4...-SBBS

XN-S4...-SBBS

Bit transfer rate

Insulation test
Between interface and module bus⁄system
voltage
Between interface and field voltage
Common-mode range
Cable impedance
Bus termination
Cable length
Number of diagnosis bytes
Number of parameter bytes
Basic modules
No C-connection for sensor/transmitter supply

XN-1RS232

Ui

1)

Notes

The figures for rated operational current From the supply terminal apply when there is nosensor/transmitter current.

XNE-1SWIRE
SupplyRated voltage at supply terminal
Rated current drawn from supply terminal
Rated current drawn from module bus
Supply voltage connection SWIRE
Supply current SWIRE (LIN line at full load)
Contactor supply
Contactor supply current

UL
IL
IMB
USW

mA
UAUX
A

SWIRE connection
SWIRE lines
XNE-1SWIRE modules for XI/ON station
SWIRE nodes for line
Diagnostic bits
Data for SWIRE node
Supply of SWIRE nodes (short-circuit proof)
Supply current for all LIN nodes (short-circuit proof)
Insulation
Potential isolation (module bus ↔ USW/ UAUX ↔ UL)
Potential isolation (USW ↔ UAUX)
Climatic requirements
Ambient temperature
Storage temperature
Humidity (non-condensing)Protection type

mA
mA

NumberNumberNumberNumber

mA
Vrms
Vrms

24 V DC
060
24 V DC≦ 600
24 V DC
3
1
≦3
≦ 16
4
max. 4I / 4Q
17 V DC
≦ 500
500
None

°C
°C
%

0 - 55-25 - 85
5 - 95
IP20

2010 CA08103002Z-EN

www.eaton.com

14/124 Automation products

Remote I/O XI/ON

Gateways, electronics modules, accessories

Dimensions
Remote I/O XI/ONGateways, electronics modules, accessories

Gateways
Gateways XN

Gateways XNE

XN-GWBR-PBDP
XN-GWBR-CANOPEN
XN-GWBR-DNET
XN-GWBR-MODBUS-TCP

XN-GW-PDBP-1.5MB
XN-GW-PDBP-12MB
XN-GW-CANOPEN
XN-GW-DNET

XN-PLC-CANOPEN

74.4

113.2585114.7575

50.6

XNE-GWBR-PBDP
XNE-GWBR-CANOPEN
XNE-GWBR-2ETH-IP

90

33.5

129

Note:
The plugs/connectors used depend on the version.

Electronics modules XNE
XNE-16DI-24VDC-P
XNE-16DO-24VDC-0.5A-P
XNE-8AI-U/I/4Pt/Ni
XNE-4AO-U/I
XNE-2CNT-2PWM

74.5

74.5

XNE-8DO-24VDC-0.5A-P
XNE-8DI-24VDC-P
XNE-1SWIRE

13

90

90
161.5

129.5

End coverEnd bracket

XN-ABPLXN-WEW-35/2-SW
48.4

47

8

4.5

114.4

56

41.3

9.2

2010 CA08103002Z-EN

www.eaton.com

13Remote I/O XI/ON

Automation products 14/125
Electronics modules

Remote I/O XI/ONElectronics modules

Electronics modules XN in slice design
XN-2DI-24VDC-P
XN-2DI-24VDC-N
XN-2DI-120/230VAC
XN-4DI-24VDC-P
XN-4DI-24VDC-N
XN-2DO-24VDC-2A-P
XN-2DO-24VDC-0.5A-P
XN-2DO-24VDC-0.5A-N
XN-2DO-120/230VAC-0.5A
XN-4DO-24VDC-0.5A-P
XN-2DO-R-CO
XN-2DO-R-NC
XN-2DO-R-NO

XN-BR-24VDC-D
XN-PF-24VDC-D
XN-PF-120/230VAC-D

XN-1AI-I(0/4...20MA)
XN-2AI-I(0/4...20MA)
XN-1AI-U(-10/0...+10VDC)
XN-2AI-U(-10/0...+10VDC)
XN-2AI-Pt/Ni-2/3
XN-2AI-THERMO-PI
XN-4AI-U/I
XN-1AO-I(0/4...20MA)
XN-2AO-I(0/4...20MA)
XN-2AO-U(-10/0...+10VDC)

XN-1CNT-24VDC
XN-1RS232
XN-1RS485/422
XN-1SSI

55.4

72.1

74.1

72.1

74.1

46.1

12.6

47.3

Electronics modules XN in block design
XN-16DI-24VDC-P
XN-32DI-24VDC-P
XN-16DO-24VDC-0.5A-P
XN-32DO-24VDC-0.5A-P
55.4

72.1

74.1

72.1

74.1

46.1

100.8

47.3

Electronics modules XN completed with base module

90

74.5

67.8

2010 CA08103002Z-EN

www.eaton.com

14/126 Automation products

Remote I/O XI/ON

Basic modules
Remote I/O XI/ONBasic modules

Basic modules in slice design
Spring-cage terminals

17.6

3 connection levels
XN-S3T-SBB
XN-S3T-SBC
XN-P3T-SBB
XN-P3T-SBB-B

4 connection levels
XN-S4T-SBBC
XN-S4T-SBBS
XN-S4T-SBBS-CJ
XN-S4T-SBCS
XN-P4T-SBBC
XN-P4T-SBBC-B

49.9

6 connection levels
XN-S6T-SBBSBB
XN-S6T-SBCSBC

49.9

24.1

24.1

154.5

128.9

117.6

90

90

90

24.1

49.9

41.6
41.6

41.6

12.6
23.5

3 connection levels
XN-S3S-SBB
XN-S3S-SBC
XN-P3S-SBB
XN-P3S-SBB-B

Screw terminals

4 connection levels
XN-S4S-SBBC
XN-S4S-SBBS
XN-S4S-SBBS-CJ
XN-S4S-SBCS
XN-P4S-SBBC
XN-P4S-SBBC-B

49.9

17.6

6 connection levels
XN-S6S-SBBSBB
XN-S6S-SBCSBC

49.9

24.1

24.1

154.5

128.9

117.6

90

90

90

24.1

49.9

48.3
48.3

48.3

12.6
23.5

2010 CA08103002Z-EN

www.eaton.com

Remote I/O XI/ON

Automation products 14/127
Basic modules

Basic modules in block design
3 connection levels
XN-B3T-SBB
XN-B3T-SBC

Spring-cage terminals

4 connection levels
XN-B4T-SBBC

6 connection levels
XN-B6T-SBBSBB
XN-B6T-SBCSBC

100.8
17.6

49.9

49.9

24.1

24.1

154.5

128.9

117.6

90

90

90

24.1

49.9

41.6
41.6

41.6

23.5

3 connection levels
XN-B3S-SBB
XN-B3S-SBC

Screw terminals

4 connection levels
XN-B4S-SBBC

6 connection levels
XN-B6S-SBBSBB
XN-B6S-SBCSBC

100.8
17.6

49.9

49.9

24.1

24.1

154.5

128.9

117.6

90

90

90

24.1

49.9

48.3
48.3

48.3

23.5

2010 CA08103002Z-EN

www.eaton.com

14/128 Automation products

SoftwareDescription

Visualization software Galileo

Useful add-on tools

The powerful, comprehensive engineering platform Galileo is ideal for use in allmachine- and process-related applications in plant and machine construction.

S7 PG router: Programming S7 PLCs connected to the panel through the Ethernet
interface.
CE Telediag: Convenient remote maintenance through a modem connection withdial assistant and device call-back.
CAN monitor: Observing and tracing CAN messages with relative time stamp for
COB-ID and data directly on the panel.

• Fast engineering with project simulation on development PC.
• Easy-to-learn, intuitive graphical user interface with project overview window.
• Range of interface styles.
• Object placement with drag & drop WYSIWYG (what you see is what you get).
• Easy object parameterization.
• Object properties table, simple and quick attribute assignment with copy & paste.
• Pointer object.
• Extended password handling with complex password and ageing.
• Comprehensive recipe handling.
• Alarm handling with time stamp, history and diagnostics support with image
display.
• Convenient batch definition of texts and graphics for variables.
• Many graphical objects, such as bar graph, scroll bar, graph plotter, line graph,and camera.
• Object parameter list, any number of data objects for template.
• Dynamic measurement unit selection (e.g. °C <-> °F, inches <-> mm).
• Many specific objects and functions.
• Direct printing at panel (reports, forms).
• Brilliant image reproduction with up to 65536 colors.
• Import of 15 different graphic formats.
• Easy import of PLC variables.
• Online language selection.
• Unicode support (including Asian character sets).
• Text import/export in XML format, e.g. Excel.
• Full functionality always available; no performance grading.
• Dynamic objects.

2010 CA08103002Z-EN

www.eaton.com

EPAM: visualization tool for Microsoft Office
Designed as an open visualization tool for OEM machine vendors, EPAM can be
expanded with custom funtions programmed in Visual Basic at any time.
• The visualization is configured in Microsoft Excel.
• Every visualization created with EPAM is web-capable, allowing remote plant
operation from any standard PC without having to install additional Software.

Software

Automation products 14/129

PLC programming with XSOFT-CODESYS-2

I/O configuration tool I/Oassistant for XI/ON

The CoDeSys-based software XSOFT-CODESYS-2 offers matured technicalfeatures and easy operation. CoDeSys is one of the most powerful IEC 61131-3 PLC
programming tools. All five programming languages of the standard are supported.

The free software I/Oassistant is a universal tool that provides interactive support
in planning and implementing your XI/ON system. Just select the gateways,
electronics, base modules and accessories, and the program configures yourstations either online or offline. Once designed, the system can go into operation.
Integrated in XSOFT-CODESYS-2, the I/Oassistant engineering tool for XI/ON is
also available within the PLC programming software. Without having to quitXSOFT-CODESYS-2, you have access to the full functionality of I/Oassistant tointeractively plan and implement your remote XI/ON station.

• SMS/e-mail library for alarm message notifications.
• UDP/TCP library for powerful Ethernet communication with PC-based
applications.
• FTP server/client.
Web visualization (XV100, XVS400 and XV400 only):
Optionally XSOFT-CODESYS-2 can generate an XML description from thevisualization information, which is saved to the PLC together with a Java applet
and can be displayed in a web browser through TCP/IP to make the visualization
data available online on a wide range of platforms.
Target visualization (XV100, XVS400 and XV400 only):
The programming system can convert visualization information into IEC 61131-3
code and translate it for the respective target system with the code generator.

• I/Oassistant automatically generates a full parts list for your order.
• With the [Check station design] function, you can easily check the configured
station design.
• Commissioning the I/O level without connected controller possible; servicing
interface• EPLAN support.

Planning and ordering help (SWD?Assist)

Closed-loop control toolbox:
The closed-loop control toolbox contains about 120 function blocks. The standard
function blocks provide leverage of the implemented closed-loop control knowhow. Being combinable and cascadable, the function blocks allow the creation of
special application solutions.

Planning a SmartWire-Darwin line is quick and easy with the SWD-Assist software.
Generate applications easily and quickly with the system SmartWire-Darwin.

Motion control toolbox:
The motion control toolbox contains about 40 function blocks that can be
individually incorporated and optimally adapted to the automation task.

Free download fromhttp://downloadcenter.moeller.net• Built-in function for generating ordering lists.
• Built-in validity check.

2010 CA08103002Z-EN

www.eaton.com

14/130 Automation products

Software
HPL14130EN

Ordering
SoftwareDescription

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export toNorth America

1 off

UL/CSA certification not required

SW-XSOFT-CODESYS-2-S1)
142582
SW-XSOFT-CODESYS-2-M2)
142583

1 off

UL/CSA certification not required

SW-S7-PG-ROUTER
140381

1 off

Visualization software
GALILEOGALILEO OPEN

EPAM

Microsoft Windows™-based, intelligent andinteractive visualization tool.
For creating projects to operate and visualize
machines, plants and buildings.
Comprehensive help and documentation.
For continuous, unrestricted operation of the
GALILEO runtime systems on a standard PC.
The runtime system software is part of thedevelopment software GALILEO.
Open visualization system Easy Page Machine(EPAM)
An add-in for Microsoft Excel.

SW-GALILEO
140379LIC-GALILEO-OPEN-PC
140385

SW-EPAM
140380

PLC programming software
Programming to IEC 61131-1 with IL, ST, LAD, FBD, AS, CFC
Supports XV, XC, XN, EC4P
Bus configuration CAN, PROFIBUS-DP, XI/ON.
Menu selection in 5 languages
Operating systems: Win NT 4.0 SP6, Win 2000 SP3, Win XP SP2,
Windows Vista
OPC configurator
Comprehensive help and documentation.
XSOFT-CODESYS-2 Single-user license
XSOFT-CODESYS-2

Multi-user license

1 off

Add-on software
S7-PG router

CE Telediag

CAN monitor

Domain server

Notes

For programming S7 PLCs through the panel’s
Ethernet interface.
Suitable for XV100, XV200, and XVS400 devices with
on-board PROFIBUS and Ethernet Interface.
80 license points required on the device￫ Page 14/14.
Including software with documentation andlicense product certificate with 80 points forlicensing one device.
For remote maintenance through a modem
connection with dial assistant and device call-back.
Suitable for XV100, XV200, XVS400, XV400 and
XVH300 devices on-board RS232 interface
40 license points required on the device￫ Page 14/14.
Including software with documentation andlicense product certificate with 40 points forlicensing one device.
For observing and tracing CAN messages withrelative time stamp, COB-ID and data. Error frames
are not detected.
Suitable for XV100, XV200, XV400 and
XVH300 devices with on-board CAN interface.
No licence points required.
Includes software with documentation.
Connection of a Micro Panel with GALILEO project tothe central user management of a Windows 2003
Server domain.
1) Replaces ECP-Soft
2) Replaces MXPRO2010 CA08103002Z-EN

www.eaton.com

SW-CE-TELEDIAG
140383

SW-CAN-MONITOR
140382

SW-DOMAIN-SERVER
140384

UL/CSA certification not required

Mains power supply units

Automation products 14/131

HPL14131EN

Ordering
Mains power supply units

Rated input voltage 50/60 Hz

Rated output voltage(residual ripple)
V DC

Input voltage
range
V

A

Unregulated, smoothed
Single-phase230

24 (± 5 %)

–

3

230

24 (± 5 %)

–

5

230

24 (± 5 %)

–

8

230

24 (± 5 %)–

10400 (± 5 %)24 (± 3 %)–5400 (± 5 %)24 (± 3 %)–10400 (± 5 %)24 (± 3 %)–15400 (± 5 %)24 (± 3 %)–20

400 (± 5 %)24 (± 3 %)

–

30

5

V AC

Rated output current

Part no.
Article no.

Price
See
price list

Std. pack

Power supply units GW4, GD4Three-phase

GW4-030-BA3
200016
GW4-050-BA3
200017
GW4-080-BA3
200018GW4-100-BA3
200019
GD4-050-BD3
200007
GD4-100-BD3
200009
GD4-150-BD3
200011
GD4-200-BD3
200012
GD4-300-BD3
2000141 off

SN3-050-BU8100640SN3-100-BV8
100641

1 off

Switched-mode power supply units SN3
Primary switched-mode power supply unit, power reserve of up to 50 %,Up to 5 devices can be connected in parallel increase power and for redundancy
110 - 240 AC
24 V DC (fixed)(20 MHz normally < 50 mVss)
110 - 120 AC
24 V DC (fixed)(20 MHz normally < 50 mVss)
220 - 240 AC
110 - 120 AC
220 - 240 AC

24 V DC (fixed)(20 MHz normally < 50 mVss)

110 - 240 AC/DC

22 - 28 V DC (adjustable)(20 MHz normally < 50 mVss)
22 - 28 V DC (adjustable)(20 MHz normally < 50 mVss)
22 - 28 V DC (adjustable)(20 MHz normally < 50 mVss)

85 - 264 AC
100 - 350 DC1)
85 - 132 AC
184 - 264 AC
220 - 350 DC1)
85 - 132 AC
184 - 264 AC
220 - 350 DC1)
85 - 264 AC
100 - 350 DC1)
85 - 264 AC
100 - 350 DC1)
85 - 264 AC
100 - 350 DC1)

24/12

–

0.35
0.02

EASY200-POW
229424100 - 240

24 (± 3%)–

1.25

EASY400-POW
212319100 - 240

24 (± 3%)–

1.25

100 - 240

24 (± 3%)–

2.5

EASY430-POW
110940EASY500-POW
110941100 - 240

24 (± 3%)–

4.2

110 - 240 AC/DC
110 - 240 AC/DC

10

20

SN3-200-BV8
1006425

SN3-050-EU8
100643SN3-100-EU8
100644SN3-200-EU8
10064510
20

Switched-mode power supply units easyPOW
Primary-switched mode, regulated
100 - 240

1 off

Power

Power

EASY600-POW
262399Power

Signal module for power supply units SN3-...-EU8
LED display: Input OK
LED display: Output OK
LED display: Remote off
Relay output 1 changeover: Input OK
Relay output 1 changeover: Output OK
Remote On/Off function for external switchingNotes

For use with
SN3-50-EU8
SN3-100-EU8
SN3-200-EU8

SN3-000-MMEU8100646

1 off

1) At U ≧ 264 V DC, use suitable external fuse in addition
2) For UL/CSA information, technical data and dimensions see Chapter 12.

2010 CA08103002Z-EN

www.eaton.com

14/132 Switched-mode power supply units, power supply units

Switched-mode power supply units, power supply units 14/133

Power supply units GD4
GD4-050-BD3

GD4-100-BD3

Power supply units GW4
GD4-150-BD3

GD4-200-BD3

GD4-300-BD3

GW4-030-BA3

GW4-050-BA3

Notes
GW4-080-BA3

GW4-100-BA3

GeneralCurrent-voltage characteristic

Protection class1

1

Potential isolation

Yes, VDE 0551, IEC/EN 60742, SELV

Yes, VDE 0551, IEC/EN 60742, SELV
50/60

At 230 V or 3 x 400 V AC (primary side) and a load current of I = 0 A up
to the rated operational current 1x Iq
GD4... with transformer

Mains frequency
Rated value

Hz

50/60

Range

Hz

50…60

Electromagnetic compatibility (EMC)
Class B (EN 55011, 22)Class B (EN 55011, 22)

6 kV contact (Level 3), 8 kV air (Level 3), IEC/EN 61000-4-2

6 kV contact (Level 3), 8 kV air (Level 3), IEC/EN 61000-4-2

RFI

10 V/m, modulated, IEC/EN 61000 4-2

Burst

10 V/m, modulated,
IEC/EN 61000 4-2
2 kV (Level 3) IEC/EN 61000-4-4

Surge

2 kV (Inst. Class 3), IEC/EN 61000-4-5

2 kV (Inst. Class 3), IEC/EN 61000-4-5

Impulse voltage

4.9 kV, IEC EN 60947

4.9 kV, IEC EN 60947

e

Emitted interference
ESD

2 kV (Level 3) IEC/EN 61000-4-4

29
28
27
26
25
24
23
22
21
20
0

1

Environmental data
Ambient temperature°C-25 - 55

-25 - 55

Ambient temperature, storage°C-25 - 85

-25 - 85

2, EN 50178

2, EN 50178

Pollution degree

0.075 mm (10 - 57 Hz), 10 cycles, IEC 60068-2-6

0.075 mm (10 - 57 Hz), 10 cycles, IEC 60068-2-6

Shock resistance, shock duration 11 ms

g

15, IEC 60068-2-27 (3 shocks)

15, IEC 60068-2-27 (3 shocks)

Installation altitudemMax. 2000 m a.m.s.l., observe derating above this1)Max. 2000 m a.m.s.l., observe derating above this1)

Protection type

IP20

IP20

FixingScrew-on

Screw-on

Mounted position

Any

Any

e

Vibration

GW4... with transformer
28
27
26
25
24
23
22
21
20
0

1

Input voltage
Rated value

V AC

400

Range

V AC

Taps ± 5% 380, 400, 420

400

400

400

Rated input current for phase

A

0.24

0.46

0.65

0.9

No-load losses

W

5

14.2

13.9

Short-circuit losses

W

19.6

28.6

V DC

24

24

400

230

230

230

230

230

230

230

230

1.8

0.45

0.8

1.2

1.4

25.5

38.2

7.6

9

12.8

10.2

44.2

59

55.5

15.5

29.7

32.7

35

24

24

24

24

24

24

24

Output voltage
Rated value
Tolerance
Tolerance

See current/voltage characteristic

See current/voltage characteristic

–

–

–

–

–

–

–

–

–

Ripple

%

≦3

≦3

≦3

≦3

≦3

≦5

≦5

≦5

≦5

Output current (rated value)

A

5

10

15

20

30

3

5

8

10

Output current range at 55 °C

A

0-5

0 - 100 - 150 - 200 - 30

0-3

0-5

0-8

0 - 10Solidmm2

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

0.5 - 4

Flexible with ferrule

mm2

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

0.5 - 2.5

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Screw terminals

Terminal capacity

Connections
Dimensions
Width

mm

125

155

155

190

190

85

85

106

121

Height

mm

73

82

97

105

115

90

98

100

105

Depth

mm

140

170

170

225

240

122

135

151

169

Weight

kg

2.4

4.4

5.8

7.6

11.2

2

2.5

3.65

4.45

Protection
Input voltageu1V

3 x 400

3 x 400

3 x 400

3 x 400

3 x 400

230

230

230

230

Input current

I1

A

0.24

0.46

0.65

0.9

1.8

0.45

0.8

1.2

1.4

PKZM0-0,25

PKZM0-0,63

PKZM0-1

PKZM0-1

PKZM0-2,5

PKZM0-0,63

PKZM0-1

PKZM0-1,6

PKZM0-1,6

0.24

0.46

0.65

0.9

1.8

0.45

0.8

1.2

1.4

FAZ

FAZ-S1/1

FAZ-S1/1

FAZ-S1/1

FAZ-S1/1

FAZ-S2/1

FAZ-S1/1

FAZ-S1/1

FAZ-S2/1

FAZ-S2/1

Short-circuit protection only

●

●

–

–

–

●

–

–

–

Circuit-breaker
PKZ
Current setting

A

Miniature circuit-breaker (MCB)

1) Derating

Notes

From +44 to +55 °C: linear deratingfrom 100 % to 93 %2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

14/134 Automation products

Mains power supply units

Mains power supply units

SN3-050-BU8

SN3-100-BV8

SN3-200-BV8

SN3-050-EU8

SN3-100-EU8

SN3-200-EU8

GeneralStandards

EN 61204, 73/23/EWG, 89/336/EWG, EN 50178, EN 60950, UL 60950, UL 508, SELV (EN 60950)

Protection type
Enclosure

IP20

IP20

IP20

IP20

IP20

IP20

Terminals

IP20

IP20

IP20

IP20

IP20

IP20

Protection classAccording to EN 61140, Class 1

Mounting

DIN rail (IEC/EN 60715), snap fixing

Mounted position

Horizontal

Horizontal

Horizontal

Horizontal

Horizontal

Horizontal

Heat dissipation

W

Normally ≦ 15

Normally ≦ 29

Normally ≦ 58

Normally ≦ 15

Normally ≦ 29

Normally ≦ 58

Efficiency

%

≧ 88

≧ 88

≧ 88

≧ 88

≧ 88

≧ 88

Width

mm

57

90

200

57

90

200

Height

mm

130

130

130

130

130

130

Depth

mm

130

130

130

130

130

130

Weight

kg

0.96

1.07

2.83

0.96

1.07

2.83

Minimum distance to adjacent devicesmmHorizontal 10, vertical 80

Dimensions

Terminal capacity
Only operate plug-in terminals off load.
Input circuit
Flexible with ferrulemm2

0.2…2.5 (22…14 AWG)

Flexible without ferrulemm2

0.2…2.5 (22…14 AWG)

Solid

mm2

0.2…2.5 (22…14 AWG)

Flexible with ferrule

mm2

0.12…2.5 (26…14 AWG)

Flexible without ferrule

mm2

0.12…2.5 (26…14 AWG)

Solid

mm2

0.12…2.5 (26…14 AWG)

Ambient temperature, operation°C-25 - +70

Ambient temperature, full load°C

0 - +60 (without derating)Ambient temperature, storage°C-40 - +85

2.5 … 10
(14 … 8 AWG)
0.5 … 10
(20 … 8 AWG)
0.5 … 16
(22 … 6 AWG)

0.2…2.5 (22…14 AWG)

2.5 … 10
(14 … 8 AWG)
0.5 … 10
(20 … 8 AWG)
0.5 … 16
(22 … 6 AWG)

0.12…2.5 (26…14 AWG)

-25 - +70

-25 - +70

-25 - +70

-25 - +70

-40 - +85

-40 - +85

-40 - +85

-40 - +85

0.2…2.5 (22…14 AWG)
0.2…2.5 (22…14 AWG)

2.5 … 10
(14 … 8 AWG)
0.5 … 10
(20 … 8 AWG)
0.5 … 16
(22 … 6 AWG)

Output circuit

0.12…2.5 (26…14 AWG)
0.12…2.5 (26…14 AWG)

2.5 … 10
(14 … 8 AWG)
0.5 … 10
(20 … 8 AWG)
0.5 … 16
(22 … 6 AWG)

Environmental data
-25 - +70
-40 - +85

Climatic proofing

According to IEC 60068-2-3, 93% at +40 °C, non-condensing

Pollution degree

According to EN 50178; 2

Climate class (IEC)

According to EN 60721; 3K3

Vibration resistance (IEC/EN 60068-2-6)

1…57 Hz, amplitude ±0.075 mm; 57…100 Hz, 5 g

Shock resistance (IEC 60068-2-27)

30 g all directions

Insulation voltage
Inputs/outputs

3 kV AC (type test), 1.2 kV AC (routine test)

Input

1.5 kV AC (type test), 1.2 kV AC (routine test)

Output350 V AC (routine test)

Electromagnetic compatibility (EMC)
Interference immunity

EN 61000-6-2

ESD

According to EN 61000-4-2, Level 4-8 kV/15 kV

RFI

According to EN 61000-4-3, Level 3-10 V/m

Burst

According to EN 61000-4-4, Level 4-4 kV

Surge

According to EN 61000-4-5, Level 4-2 kV symmetrical, level 3-3 kV asymmetrical

Conducted HF

According to EN 61000-4-6, Level 3-10 V

Emitted interference

EN 61000-6-3

Electromagnetic fields

According to EN 55022, Class B

Conducted HF

According to EN 55022, Class B

2010 CA08103002Z-EN

www.eaton.com

Mains power supply units

Automation products 14/135

SN3-050-BU8

SN3-100-BV8

SN3-200-BV8

SN3-050-EU8

SN3-100-EU8

SN3-200-EU8

Input circuit
Rated input voltage

V

110 …240 AC––

110 …240 AC

110 …240 AC

110 …240 AC

Switch position 110V–

110 … 120 AC

110 … 120 AC

–

–

–

Switch position 230

V–

220 … 240 AC

220 … 240 AC

–

–

–

Primary voltage rangeV

85 … 264 AC––

85 …264 AC

85 …264 AC

85 …264 AC

Input voltage range1)

V

100 … 350 DC––

100 … 350 DC

100 … 350 DC

100 … 350 DC

Switch position 110 V AC

V–

85 … 132 AC

85 … 132 AC

–

–

–

Switch position 230 V ACV–

184 … 264 AC

184 … 264 AC

–

–

–

Switch position 230 V DC

V–

220 … 350 DC

220 … 350 DC

–

–

–

Rated value

Hz

50/60

50/60

50/60

50/60

50/60

50/60

Range

Hz

47…63

47…63

47…63

47…63

47…63

47…63

At 110 … 240 V AC

A

–

–

At switch position 110 V ACA

Approx.
2.2 …1.2–

Approx.
5.5 …2.5
–

A

–

–

–

–

W

Normally 135

Approx.
9.0…8.0
Approx.
4.4…4.0
Normally 538

Approx.
3.5 …1.6–

At switch position 230 V AC

Approx.
4.2…4.0
Approx.
2.4…2.2
Normally 269

Approx.
2.2 …1.2–

Normally 135

Normally 269

Normally 538

Mains failure bridging durationms≦ 23 A /ca. 0.9 A2s
Normally ≧ 100≦ 40 A /ca. 1.8 A2s
Normally ≧ 50

≦ 70 A /ca. 8 A2s
Normally ≧ 50

≦ 23 A /ca. 0.9 A2s
Normally ≧ 100≦ 33 A /ca. 0.2 A2s
Normally ≧ 40

≦ 40 A /ca. 1.9 A2s
Normally ≧ 40

Start-up after mains voltage appliedms

Mains frequency

Current consumption

Input power
Inrush current limiter/i2t (cold start)

Normally ≧ 100

Normally ≧ 10

Normally ≧ 20

Normally ≧ 100

Normally ≧ 5Normally ≧ 370

Transient overvoltage protection

Varistors

Varistors

Varistors

Varistors

Varistors

Varistors

Internal input fuse(device protection, not accessible)
Leakage current to PE

4 AT

6.3 AT

12 AF

4 AT

6.3 AT

12 AF< 3.5 mA

< 3.5 mA

< 3.5 mA

< 3.5 mA

< 3.5 mA

< 3.5 mA

mA

Output circuit
L+, L+, L-, LRated output voltage

Proof against short-circuit, no-load and overload
V

24 DC

24 DC

24 DC

24 DC

24 DC

24 DC

Tolerance-1…+5 %

-1…+5 %

-1…+5 %

-1…+5 %

-1…+5 %

-1…+5 %

Output voltage setting range

Fixed 24 V DC

22…28 V DC; default setting 24 V ±0.5%

Rated output power

W

120

240

480

120

240

480

Rated output current Tu ≦ 60 °C

A

5

10

20

5

10

20

Peak output current (power reserves)
Tu ≦ 40 °C
Derating 60 °C ≦ Tu ≦ 70 °C

A

Normally ≦ 7.25

Normally ≦ 12.25

Normally ≦ 22.5

Normally ≦ 7.25

Normally ≦ 12.25

Normally ≦ 22.5

2.5 % for Kelvin temperature increase

Control deviation at
Load change 10…90 %, static

Normally±0.1 %±0.1 %±0.1 %±0.05 %

±0.05 %

±0.05 %

Load change 10…90 %, dynamic

Normally

±3 %

±3 %

±3 %

±3 %

±3 %

±3 %

Controller acting timemsNormally 1

Normally 1

Normally 1

Normally 1

Normally 1

Normally 1

Normally ±0.05 %Normally ±0.05 %Normally ±0.05 %Normally ±0.05 %Normally ±0.05 %Normally ±0.05 %Normally ≦ 30

Normally ≦ 5Normally ≦ 15

Normally ≦ 30

Normally ≦ 4Normally ≦ 12

Input voltage deviation ±10 %Rise time 10…90 %ms

Residual ripple and switching peaks

20 MHz normally < 50 mVss

Parallel connection capability

Yes, up to 5 devices for redundancy and for power increase, non symetrical current

Series connection capability

Yes, for voltage increase (max. 2 off)

Resistance to reverse feed

Yes, limited to Approx. 35 V AC

Power factor correction (PFC)No

Status indication

OUTPUT OK: LED green

Overload characteristics

Thermal protection

Response to short-circuitContinuously with current limitation

Current limitation at short-circuit

A

Approx. 11

Yes
Thermal protection
Approx. 19

Approx. 25

Short-circuit protection

Proof against sustained short circuit

Overload protection

Thermal protection

Capacitive load starting

Not restricted

Notes1) At ≧ 264 V DC, use suitable external fuse in addition

Approx. 11

Approx. 19

2010 CA08103002Z-EN

Approx. 25

www.eaton.com

14/136 Automation products

Mains power supply units

SN3-000-MMEU8GeneralStandards%

IEC 61204
73/23/EEC
89/336/EEC
EN 50178, EN 60950, UL 60950, UL 508
100

Dimensions (W x H x D)

mm

56.25 × 54 × 24 (in fitted state)

Weightkg

0.065

Duty factor

Terminal capacity
Flexible with ferrulemm2

0.2…2.5 (22…14 AWG)

Flexible without ferrulemm2

0.2…2.5 (22…14 AWG)

Solid

mm2

0.2…4 (22…14 AWG)

Protection type
Enclosure

IP20

Terminals

IP20

Protection class2

Mounting

Snap-fitted to power supply unit

FixingSnap-fitting, tool-lessVibration resistance (IEC/EN 60068-2-6)

1…57 Hz, amplitude ±0.075 mm, 57…100 Hz, 5 g

Shock resistance (IEC 60068-2-27)

5 g all directions

Environmental data
Ambient temperature
Operation°C-25… +70

Storage°C-40 - +85

Climatic proofing

93% at +40°C According to IEC 60068-2-3, non-condensing

Climate class (IEC)3K3 According to EN 60721

Insulation voltage
Rated insulation voltage

Ui

V AC

Uimp

kV

4 According to IEC 664, VDE 0110

kV

2.5 AC (routine test)

Power supply/measuring circuit/relay outputs
Rated impulse withstand voltage between all insulated circuits
Test voltage between all circuits

250 According to IEC 60974-1, EN 50178, VDE 0160
Safe isolation According to EN 50178, EN 60950

Overvoltage category/pollution degree

According to EN 60950, Class 2

Input circuit
Rated input voltage

V

Primary voltage range

V

110…240 AC / 100…350 DC(supplied From the input circuit of the power supply)
70…264 AC

Primary voltage rangeV

80 … 350 DC

Input power

VA

2.5

Input power

W

1.5

REMOTE-OFF input
Floating
R ≦ 1 kΩ

Switching off
Switching on

R ≧ 10 kΩ

Input current

mA

Normally 1 (200 mA for 200 μs)

Cable lengthm

25

Measuring circuits
INPUT
Monitoring function

Undervoltage monitoring

Threshold values

85 V AC / 90 V DC

Accuracy/tolerance%

Measuring cycle, max.

-5 % for AC and DC
Normally -8 % for AC and -30 % for DC

Hysteresis relative to the threshold valuemsNormally ≦ 50

OUTPUT
Monitoring function

Undervoltage monitoring

Threshold values

20 V DC

Accuracy/tolerance%±1

Hysteresis relative to the threshold value%

Normally 5

Measuring cycle, max.

ms

Normally ≦ 102010 CA08103002Z-EN

www.eaton.com

Mains power supply units

Automation products 14/137

SN3-000-MMEU8
Output circuit
11-12/14, 21-22/24
Contacts

NumberOperating principle

2 x 1 relay (changeover contact)
Quiescent current principle
AgNi

Contact material
Rated voltage

V

250 According to VDE 0110, IEC 60947-1

Minimum switching voltage

V

24

Maximum switching voltage

V

250

Minimum switching voltage

mA

10

Maximum switching current

A

1

Rated operational current
AC-12 (resistive) 230 V

1A

AC-15 (inductive) 230 V

1A

DC-12 (resistive) 24 V

1A

DC-13 (inductive) 24 V

1A

Durability
Mechanical

30 x 106 operations

Electrical

0.1 x 106 operations

Short-circuit rating
NC contacts

A

gL

2

N/O contacts

A

gL

2

Operating state display
Input OK

LED lit green when relay “Input OK” picked up

Output OK

LED lit green when relay “Output OK” picked up

Remote OFF

LED lit green when relay “Remote OFF” input R ≦ 1kΩ

Notes

Data at Tu = 25 °C, UIN = 230 V AC and nominal values, when no others
are given

Dimensions
GD4-...

c + 51)aec + 51)g

GW4-...

b1

f

b1

b 51)

b1

b 51)

SN3-000-MMEU8

130

54

SN3-050
SN3-100
SN3-200

24

130

57

a

2010 CA08103002Z-EN

www.eaton.com