eay control relay
MFD-Titan multi-function display
The control relays eay500/700/800 and the multifunction display MFD Titan offer
all the technical possibilities needed to realize applications in industrial and manualapplications as well as in machinery or apparatus construction.

eay500
Functions such as multifunction relays, current pulse switches, counters, analog value
comparators, week and year time switches +++ Stand-alone device +++ Optimal for smaller
applications +++ Connectable to Ethernet

eay700
Complete functional scope of an eay500 +++ Local and remote extension options for flexible
applications +++ Connectable to current bus systems or Ethernet
eay800
Complete functional scope of an eay700 +++ Numerous additional functions such as
PID controller, arithmetic functions, value scaling, fast counter (5 kHz) +++ To perform
comprehensive control tasks +++ Digital and analog expandability +++ Integrated
communication through eayNet +++ Connectable to current bus systems or Ethernet

MFD-Titan
Combines control function of an eay800 with convenient visualization +++Display, control, regulation and communication with one device +++ E/A modules for direct
temperature sensing +++ Digital and analog expandability +++ Communication througheayNet possible +++ Connectable to current bus systems or Ethernet
2010 CA08103002Z-EN   www.eaton.com

eay control relay, MFD-Titan multi-function display

Control relay eay

MFD-Titan Multi-function display

Technical overview

System overview

Control relay, multi-function display

12/3

MFD-Titan Multi‐function‐displaySystem overview
Control relays eay500, eay700

Ordering
12/4

Ordering
Basic deviceseay500

12/6

eay700

12/7

I/O expansions

12/8

Coupling module

12/8

Bus modules

12/8

Ethernet gateway

12/8

Power supply unit/CPU module

12/22

Power supply unit/communication module

12/23

Input/output modules

12/24

I/O expansions

12/25

Coupling module

12/25

Bus modules

12/26

Ethernet gateway

12/26
12/27

12/9
Control relay, multi-function display
12/12

Technical data

Ordering

Basic devices, Expansion Devices

Basic deviceseay800

12/22

Accessories

System overview
Control relay eay800

Display/keypad

Expansion Devices

Expansion Devices

Accessories

12/20

12/14

Expansion Devices

eay...12/30

eay...DA...

12/31

eay…AB...

12/32

eay...DC...

12/33

eay…AC...

12/35

I/O expansions

12/15

Coupling module

12/15

Bus modules

12/16

Display/operating unit, CPU, communication modules 12/36

Ethernet gateway

12/16

Input/output modules

12/16

Basic devices, Expansion Devices
Transistor outputs

12/42

Relay outputs

12/44

Bus modules

12/45

Ethernet coupling unit, upstream device

12/47

Switched-mode power supply units

12/49

Dimensions
75

16.25

45

90

M4

110

16.25

102

Accessories

12/39

4.5
107.5

47.5
56.5
58

Basic device, expansion units, display/operating unit

12/51

Central processing unit, communication module,
inputs/outputs modules

12/52

Accessories

12/53

12/2

Control relays, multi-function display
Notes

Notes

2010 CA08103002Z-EN

www.eaton.com

Control relays, multi-function display

12/3

Technical overview

Technical overview
FunctionsTechnical overview

easy500/700

easy800

MFD-...CP8...

Counter functions

Counter relay(up, down counting)
Frequency counters
High-Speed counter
Incremental counters
Hour meter

16 (0 to 32000)

32 ( g231)

32 ( g231)

Weekly timer (4 channels per timer,
each channel offers one On/Off time)
Year time switch
Set cycle time
Timing relay

8

32

8
–
16
(0.01 s … 99 h 59 min)32
1
1
32 (0.005 s … 2³² min), On-delayed and/or off-delayed(optionally random switching), pulse shaping, flashing

Program sequencing functions

Jump
Conditional jump
Master reset

8
–
3

32
32
32

32
32
32

Maths functions

Analog value comparator

16

32

32

Arithmetic–

32 (ADD, SUB, MUL, DIV)

32 (ADD, SUB, MUL, DIV)PID controller
PT1 signal smoothing filter
Value scaling
Numerical converter
Pulse output
Pulse width modulation
Value limit

–
–
–
–
–
–
–

32
32
32
32
2
2
32

32
32
32
32
–
2
32

Block comparison
Block transfer
Boolean operation

–
–
–

32
32
32 (AND, OR, NOT)

32
32

Comparator
Data function block
Data multiplexer
Shift register
Table function

16
–
–
–
–

32
32
32
32
32

32
32
–
32
32

Communication functions

Get value from the NET
Put value on the NET
Bit output via NET
Bit input via NET
Diagnostic alarm
Serial protocol
Synchronize clock via NET

–
–
–
–
–
–
–

32
32
32
32
9
32
1

32
32
32
32
9
–
1

Text functions

Text display(can be edited via software)
Static text
Message text
Screen menu
Running text
Rolling text

16 x (4 x 12 characters)

32 x (4 x 16 characters)

YesTime functions

Memory functions

Value entry functions

Value display functions

Date and time information
Year time switch entry
Latching pushbutton
Button field
Timing relay value entry
Value entry
Week clock inputEnter counter value/reference value/OT

2 (max. 1 kHz)4 (max. 5 kHz)4 (max. 3 kHz)2 (max. 1 kHz)4 (max. 5 kHz)4 (max. 3 kHz)–2 (max. 3 kHz)2 (max. 3 kHz)4 (operating hours value is stored super-retentively (e.g also with program change)

32 (AND, OR, NOT)

Yes
Yes
Yes
Yes
Yes

Yes

Yes

Yes

Yes

Bit display
Message bitmap
Bargraph
Numerical value
Timing relay value display
Actual values
Date and time

32

Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes

Yes
Yes

Yes
Yes

Yes
Yes

2010 CA08103002Z-EN

www.eaton.com

12/4

Control relays
500, 700

System overview
500, 700

1

3
4
3

1

2
5

6

7

2

8

POW

BUS

POWER
COM-ERR

ERR
MS

ADR

NS

11
12

10

9

11

10

2010 CA08103002Z-EN

www.eaton.com

Control relays

12/5

500, 700
Basic devices
500

Remote text display
1

700
Expandable: Digital inputs/outputs
and bus systems AS-Interface,
CANopen, PROFIBUS-DP, DeviceNet
12 V DC = easy...DA...
24 V DC = easy...DC...
24 V AC = easy...AB...
100 - 240 V AC = easy...AC...
12 digital inputs
4 usable as analog inputs(DA, DC or AB versions)
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
Display and keypad optional
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/7

EASY202-RE

Consists of:

Display/operating unit MFD-80(-B)
Power supply unit/communication module MFD(-AC)-CP4-500

Stand-alone
12 V DC = easy...DA...
24 V DC = easy...DC...
24 V AC = easy...AB...
100 - 240 V AC = easy...AC...
8 digital inputs
2 usable as analog inputs(DA, DC or AB versions)
4 relay outputs (max. 10 A, UL) or
4 transistor outputs
Display and keypad optional
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/6

Output expansion

33Including connection cable(5 m, can be cut to length) for
easy500/700
24 V DC = MFD-CP4-500
100 - 240 V AC = MFD-AC-CP4-500
Spring-loaded terminals￫ Page 12/16

I/O expansions
EASY410...

Ethernet gateway

2

EASY209-SE

4

24 V DC
Serial interface easyRelay toEthernet￫ Page 12/16

10

24 V DC
6 digital inputs
4 relay outputs (max. 10 A, UL) or
4 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

EASY6...

Bus modules
EASY204-DP

9

2 relay outputs (max. 10 A, UL)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

5

PROFIBUS-DP slave connection,
24 V DC￫ Page 12/16

11

24 V DC
12 digital inputs
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

Coupling module
EASY205-ASI

6

AS-Interface connection as slave￫ Page 12/16

EASY221-CO

EASY200-EASY

7

CANopen connection, 24 V DC
￫ Page 12/16

EASY222-DN

8

12

For remote connection of a digital
I/O expansion through two-poleconnection cable (max. 30 m);e.g. NYM 3 × 1.5 mm2
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

DeviceNet connection, 24 V DC
￫ Page 12/16

2010 CA08103002Z-EN

www.eaton.com

12/6

Control relays

500/700

Basic devices
HPL12006EN

Ordering
500/700Basic devices

SupplyvoltagePart no.
Article no.

√

24 V AC

1 off

–

√

24 V AC–√–

100 - 240 V AC

4

–

√

√

100 - 240 V AC

–

4

–

–

√

100 - 240 V AC

8

2

4

–

√

√

12 V DC

8

2

4

–

–

√

12 V DC

8

2

4

–

√

–

24 V DC

8

2

4

–

√

√

24 V DC

8

2

4

–

–

√

24 V DC

8

2

–

4

√

√

24 V DC

8

2

–

4

–

√

24 V DCEASY512-AB-RC
274101
EASY512-AB-RCX
274102
EASY512-AC-R
274103
EASY512-AC-RC
274104
EASY512-AC-RCX
274105
EASY512-DA-RC
274106
EASY512-DA-RCX
274107
EASY512-DC-R
274108
EASY512-DC-RC
274109EASY512-DC-RCX
274110EASY512-DC-TC
274111
EASY512-DC-TCX
274112
EASY-COMBINATION-*1)
257823

1 off

Inputs

Outputs

Other features

DigitalOf which
can beused asanalogRelays 10 A
(UL)Transistor

Display +keypadRealtime
clock

8

2

4

–

√

8

2

4

–

8

–

4

8

–

8

Price
See price
list

Std. pack500
Stand alone

Customized inscription, user program• Customized inscription of easy control relay trough labeling software
Labeleditor or• Supply of easy control relay programmed with user program
Notes

Procedure and ordering example for Labeleditor inscription software
Individually inscribe your device in 4 stages:– Download the inscription software: www.moeller.net/support, keyword:“Labeleditor”– Creation of label template (menu-guided in the software)– Send the label template to the factory by email.
The email address is automatically set for the selected product by the
program. When your template is sent, the Labeleditor issues a file namesuch as “EASY_12345.zip”. This file name is part of the article to beordered (see Ordering examples).
– Send order to the Eaton office or the electrical wholesalers.
Ordering example 
EASY719-DC-RC with “Company logo”:
1 x EASY-COMBINATION-*
1 x EASY719-DC-RC
1 x the file name “EASY_xxxxx.zip” issued by the Labeleditor

4
5

2

2

6

Power

easy 500

7
82010 CA08103002Z-EN

2, 6

www.eaton.com

6

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -1) UL/CSA certification not required

3

1

Information relevant for export to North America

Accessories
1 Ethernet gateway
2 Connection cable
3 Power supply unit/communication
4 Display/keypad
5 Programming software
6 PC programming cable
7 Switched-mode power supply unit
8 Memory card

Page
￫ Page 12/16￫ Page 12/27￫ Page 12/23￫ Page 12/16￫ Page 12/9
￫ Page 12/9
￫ Page 12/10￫ Page 12/9

500/700

Control relays

12/7

Basic devices
HPL12007EN
500/700Basic devices

InputsDigitalOutputs
Of which
can beused asanalogRelays 10 A
(UL)

Other features
Transistor

Display +keypadReal-time
clock

SupplyvoltagePart no.
Article no.

Price
See price
list

Std. pack700
Expandable: Digital inputs/outputs and bus systems AS-Interface, CANopen, PROFIBUS-DP, DeviceNet
12
4
6
–
√
√
24 V AC

DEL

ESC

12

4

6

–

–

√

24 V AC

12

–

6

–

√

√

100 - 240 V AC

12

–

6

–

–

√

100 - 240 V AC

12

4

6

–

√

√

12 V DC

12

4

6

–

–

√

12 V DC

12

4

6

–

√

√

24 V DC

12

4

6

–

–

√

24 V DC

12

4

–

8

√

√

24 V DC

12

4

–

8

–

√

24 V DC

ALT

OK

EASY719-AB-RC
274113
EASY719-AB-RCX
274114
EASY719-AC-RC
274115
EASY719-AC-RCX
274116
EASY719-DA-RC
274117
EASY719-DA-RCX
274118
EASY719-DC-RC
274119EASY719-DC-RCX
274120EASY721-DC-TC
274121EASY721-DC-TCX
274122

1 off

EASY-COMBINATION-*1)
257823

1 off

Customized inscription, user program• Customized inscription of easy control relay trough labeling software Labeleditor or• Supply of easy control relay programmed with user program
Notes

Procedure and ordering example for Labeleditor inscription software
Individually inscribe your device in 4 stages:– Download the inscription software: www.moeller.net/support,
keyword: “Labeleditor”– Creation of label template (menu-guided in the software)– Send the label template to the factory by email.
The email address is automatically set for the selected product by the
program.
When your template is sent, the Labeleditor issues a file name such
as “EASY_12345.zip”.
This file name is part of the article to be ordered (see Ordering
examples).
– Send order to the Eaton office or the electrical wholesalers.
Ordering example 
EASY719-DC-RC with “Company logo”:
1 x EASY-COMBINATION-*
1 x EASY719-DC-RC
1 x the file name “EASY_xxxxx.zip” issued by the Labeleditor

1

3
4
5

2

2

Power

6
easy 700

6

Information relevant for export to North America
Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -1) UL/CSA certification not required

Accessories
1 Ethernet gateway
2 Connection cable
3 Power supply unit/communication module
4 Display/keypad
5 Programming software
6 PC programming cable
7 Switched-mode power supply unit
8 Memory card
9 Inputs/outputs expansion
10 output expansion, bus module, coupling module

Page￫ Page 12/16￫ Page 12/27￫ Page 12/23￫ Page 12/16￫ Page 12/9
￫ Page 12/9
￫ Page 12/10￫ Page 12/9
￫ Page 12/15￫ Page 12/16

Power

9

7

2, 6
9

Power

8

10

2010 CA08103002Z-EN

www.eaton.com

12/8

Control relays

500/700

Expansion devices
HPL12008EN
Expansion devices500/700

SupplyvoltagePart no.
Article no.

–100 - 240 V AC

8

24 V DCEASY618-AC-RE
212314
EASY620-DC-TE
212313

Inputs

Outputs

DigitalRelay
10 A (UL)

Transistor

6
–

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

I/O expansions
Can be used through easyLink
12
12
Power

12

6

–

24 V DC–2–

24 V DCUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

EASY618-DC-RE
232112
EASY202-RE1)
232186

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
6

4–

24 V DC

6–

4

24 V DCEASY410-DC-RE
114293
EASY410-DC-TE
114294NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01
UL Listed, CSA certified
IEC: IP20,
UL/CSA Type: Request filed
for UL and CSA
IEC: IP20,
UL/CSA Type: -Coupling module
Can be used through easyLink
For remote connection of a digital I/O expansion
up to 30 m.

EASY200-EASY
212315

1 off

Bus modules
Can be used through easyLink
AS-Interface

Slave
4 inputs,
4 outputs,
4 parameter bits
Addresses
available 0 to 31
Slave
Addresses
available
1 to 126–

EASY205-ASI
22159824 V DCEASY204-DP
212316

CANopenAddresses
available
1 to 127

24 V DCEASY221-CO
233539DeviceNet

Addresses
available
0 to 63

24 V DCEASY222-DN
23354024 V DCEASY209-SE
101520PROFIBUSDP

1 off

Ethernet gateway
Serial interface easyRelay or
MFD-...CP8/CP10... to Ethernet,
for connecting to easyOPC
server, easySoft, or easyCom

Notes1) Not for use in combination with basic unit EASY719-DA-...

Cannot be used on the EASY200‐EASY coupling module2010 CA08103002Z-EN

www.eaton.com

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508; CSA C22.2
No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20,
UL/CSA Type: -500/700

Control relays

12/9

Accessories
HPL12009EN
Accessories500/700

Supplyvoltage

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Remote text display
Display/keypad
Monochrome display 132 × 64 pixels with switchable
backlight
IP65, removable silver front frameWith keypad, with Moeller company logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29
With keypad, without Moeller company
logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29

Without keypad, with Moeller company
logotype
Without keypad,
without Moeller company logotype
NEMA 4xPower supply unit/communication modules
IP20, can be combined with display/operating unit MFD-80... asremote text display
24 V DC
With connection cable(5 m, can be cut to length)
100 - 240 V AC With connection cable(5 m, can be cut to length)
24 V DC
Without connection cable

MFD-80-B
265251
MFD-80-B-X
284905

MFD-80265250
MFD-80-X
284904

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, in combination
with MFD-XM-80: UL/CSA
Type 4X
IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, UL/CSA Type 4X

MFD-CP4-500
274094MFD-AC-CP4-500
286823
MFD-CP4
280888MFD-AC-CP4
286822

1 off

Menu selection in 13 languages
Operating systems: Windows 2000 SP4,
Windows XP SP3,
Windows Vista (32 Bit), Windows 7 (32 Bit)

EASY-SOFT-BASIC
284545
EASY-SOFT-PRO
266040

1 off

UL/CSA certification not required

SUB-D, 9 pole, serial, 2 m

EASY-PC-CAB
2024091 off

Product Standards

USB, 2 m

EASY-USB-CAB
1079261 off

For connecting the MFD(-AC)-CP4 or
EASY209-SE with easy500/easy700,
5 m, can be cut to length

MFD-CP4-500CAB5
280886

1 off

32-kB module

EASY-M-32K
270884

1 off

DeutschAWB2528-1508D
278499AWB2528-1508GB
278500

1 off

100 - 240 V AC

Without connection cable

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Programming software

Programming cable

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Connecting cables

Memory cards

Manuals

English1 off2010 CA08103002Z-EN

www.eaton.com

12/10Control relays

500/700

Accessories
HPL12010EN
Accessories500/700

Supplyvoltage

Description

For use withPart no.
Article no.

With plug-in power
supply unit
100 - 240 V AC/
24 V DC
With plug-in power
supply unit
120 V AC/24 V DC,
plug for North
AmericaWith plug-in power
supply unit
100 - 240 V AC/
24 V DCeasy500-DC

EASY412-DC-SIM
212318easy500-DC

EASY412-DC-SIM-NA
222566easy700-DC
easy800-DC
EC4P

EASY800-DC-SIM
256278Price
See price
list

Std. pack

Information relevant for export to North America

Input/output simulators
24 V DC

24 V DC

24 V DC

1 off

Accessories

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

EASY200-POW
229424

1 off

Product Standards

EASY400-POW
212319

1 off

EASY430-POW
110940EASY500-POW
110941

1 off

EASY600-POW
2623991 off

Switched-mode power supply units
Primary-switched mode, stabilized
Rated input voltage:
50/60 Hz: 100 - 240 V
Rated output voltage:
24 V/12 V DC
Rated output current:
0.35 A/20 mA
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual
ripple): 24 V DC (± 3 %)Rated output current:
1.25 A
Power

Power

2010 CA08103002Z-EN

Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual
ripple): 24 V DC (± 3 %)Rated output current: 2.5 A
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual
ripple): 24 V DC (± 3 %)Rated output current: 4.2 A

www.eaton.com

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 107.1-01;
CE marking
E300415
NMTR, NMTR7
UL report applies to both US
and Canada
3211-87, 3211-07
UL Listed, certified by UL for
use in Canada
IEC: IP20, UL/CSA Type: -500/700

Control relays

12/11

Accessories
HPL12011EN
Accessories500/700

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

BallastTo increase the AC input current
6 channels, cable length up to 100 m

EASY256-HCI
231168UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see TechnicalData;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -PROFIBUS-DP data cable
ZB4-900-KB1
206983100 m

Pins, 9 pole
Cable entry, angled 90°
Metallized insulated housing
Maximum transfer rate 12 MBit/s
Integrated switch (accessible fromthe outside) for the bus terminating
resistors
Terminal block for two cable entries,
with straight or 90° angled cable entry,
as required

ZB4-209-DS2
206982
ZB4-209-DS3
217820

1 off

Bus connector plug between base unit
and expansion unit/bus module

EASY-LINK-DS
221607

1 off

UL/CSA certification not required

ZB4-101-GF1
061360

9 off

UL/CSA certification not required

M22-TA
226161

1 off

Product Standards

Twisted pair, without plug, 2-core,2 x 0.64 mm²(only suitable for fixed wiring)
100 m

PROFIBUS-DP bus connector plug

1 off

Connection plug

Fixing bracket
For screw fixing to mounting plate
3 fixing brackets
per easy400, 500, 600, 700, 800, EC4P,
ES4P
2 fixing brackets per easy200
3 fixing brackets per,
MFD...-CP8/CP10…

Telescopic clip
With 35mm top-hat rail to IEC/EN 60715
for adjusting the mounting depth whenrear mounting in CI-K… enclosures andcabinets.
Stepless adjustment via scale from75 – 115 mm.
Screw and snap fastening

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN 60947-5; UL 508;
CSA-C22.2 No. 14-05;
CSA-C22.2 No. 94-91;
CE marking
E29184NKCR
0125283211-03
UL Listed, CSA certified

Top-hat rail adapter for inspection flap window
12 mm x 66 mm x 82 mm
Mounting on hinged inspection
window, for front fitting of devices.
Complete set, consisting of 2 brackets
and 4 screws

SKF-HA
233782

1 off

UL/CSA certification not required

94 mm x 77 mm x 25 mm (4 space units)
For use with easy500
130 mm x 77 mm x 25 mm (6 space units)
For use with EASY700, EASY800, EC4P,
ES4P

SKF-FF4
233780SKF-FF6
233781

1 off

UL/CSA certification not required

Inspection window

1 off

800Basic devices2010 CA08103002Z-EN

www.eaton.com

12/12Control relays

800

Basic devices

System overview

2
3

1
2

1

T
AL

L
DE

C
ES

OK

15
15

4

5

6

7

POW

BUS

MS
NS

14
14

10
11

9, 12

8

10

12

2010 CA08103002Z-EN

www.eaton.com

800

Control relays

12/13

800

Basic device
800

Output expansion
1

Expandable: Digital and analog inputs/
outputs and bus systems AS-Interface,
CANopen, PROFIBUS-DP, DeviceNet
Bus system easyNet on board
24 V DC = easy...DC...
100 - 240 V AC = easy...AC...
12 digital inputs
4 usable as analog inputs (DC versions)
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
1 analog output, optional on DC
versions
Display and keypad optional
Bolt-on and top-hat rail mounting
Screw terminals
Technical overview￫ Page 12/14

EASY406-DC-ME

2
2

3

EASY411-DC-ME

EC4P

13

Safety control relays
Safety
ES4P

14￫ Page 13/5

924 V DC
1 digital input
6 analog inputs (2 × 0–10 V, 2 × 0–20
mA and 2 × Pt100; voltage inputs(0–10 V) can optionally be used asdigital inputs
2 transistor outputs/
2 analog outputs (0–10 V)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

EASY6...

Compact PLC Control

Multi-function display
MFD-Titan

15￫ Page 12/22

10

24 V DC
12 digital inputs
6 relay outputs (max. 10 A, UL) or
8 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

24 V DC
Serial interface easyRelay toEthernet￫ Page 12/16

Bus modules
4

PROFIBUS DP connection as slave,
24 V DC￫ Page 12/16
5

AS-Interface connection as slave￫ Page 12/16

EASY221-CO

11￫ Page 14/64

2 analog inputs (2 × 0–10 V, 2 × 0 – 20
mA, or 2 × x Pt100; voltage inputs canbe combined in any arrangement
Voltage inputs (0 – 10 V) can
optionally be used as digital inputs
2 transistor outputs
1 analog output (0 - 10 V)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

Ethernet gateway

EASY205-ASI

924 V DC
1 digital input

Including connection cable(5 m, can be cut to length) for
easy800
24 V DC = MFD-CP4-800
100 - 240 V AC = MFD-AC-CP4-800
Spring-loaded terminals￫Page 12/16

EASY204-DP4

EASY200-EASY
For remote connection of a digital
I/O expansion through two-poleconnection cable (max. 30 m);e.g. NYM 3 × 1.5 mm²
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

I/O expansions

Consists of:

EASY209-SE

8

2 relay outputs (max. 10 A, UL)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

Remote text display

Display/operating unit MFD-80(-B)
Power supply/communication
moduleEASY202-RE

Coupling module

EASY410...

12

24 V DC
6 digital inputs
4 relay outputs (max. 10 A, UL) or
4 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

6

CANopen connection, 24 V DC
￫ Page 12/16

EASY222-DN

7DeviceNet connection, 24 V DC
￫ Page 12/16

2010 CA08103002Z-EN

www.eaton.com

12/14Control relays

800

Basic devices
HPL12014EN

Ordering
800Basic devices

Inputs

Outputs

DigitalOf which
can beused asanalogOther features

Relay
10 A (UL)

Transistor

Analog

Display +keypadReal-time
clock

SupplyvoltagePart no.
Article no.

Price
See price
list

Std. pack800
Expandable: Digital and analog inputs/outputs and bus systems AS-Interface, CANopen, PROFIBUS-DP, DeviceNet
Bus system easyNet on board
Individual laser inscription possible with EASY-COMBINATION-*￫ Page 12/6

easyNet on board
12

–

6

–

–

√

√

100 - 240 V AC

12

–

6

–

–

–

√

100 - 240 V AC

12

4

6

–

–

√

√

24 V DC

12

4

6

–

–

–

√

24 V DC

12

4

6

–

1

√

√

24 V DC

12

4

6

–

1

–

√

24 V DC

12

4

–

8

–

√

√

24 V DC

12

4

–

8

–

–

√

24 V DC

12

4

–

8

1

√

√

24 V DC

12

4

–

8

1

–

√

24 V DCEASY819-AC-RC
256267
EASY819-AC-RCX
256268
EASY819-DC-RC
256269EASY819-DC-RCX
256270EASY820-DC-RC
256271EASY820-DC-RCX
256272
EASY821-DC-TC
256273
EASY821-DC-TCX
256274
EASY822-DC-TC
256275
EASY822-DC-TCX
256276

1 off

Information relevant for export to North America
Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data; UL 508; CSA C22.2 No. 142-M1987; CSA C22.2 No. 213-M1987; CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -

5

3

1

4

2

2

6

6

11

easyNetPowereasy 800

7

Power

9

8
9

2, 6

Power

12
8

10

2010 CA08103002Z-EN

MFD Titan

easy 800

2, 6

www.eaton.com

Accessories
1 Ethernet gateway
2 Connection cable
3 Power supply unit/communication
module4 Display/keypad
5 Programming software
6 PC programming cable
7 Switched-mode power supply unit
8 Memory card
9 Inputs/outputs expansion
10 output expansion units, bus module,
coupling module
11 easyNet
12 Multi-function display MFD-Titan

Page￫ Page 12/16￫ Page 12/27￫ Page 12/23￫ Page 12/16￫ Page 12/9
￫ Page 12/9
￫ Page 12/10￫ Page 12/9
￫ Page 12/15￫ Page 12/16￫ Page 12/18￫ Page 12/22

800

Control relays

12/15

Expansion devices
HPL12015EN
800Expansion devices

Inputs

Outputs

DigitalRelay
10 A (UL)

Transistor

6

–

–

8

SupplyvoltagePart no.
Article no.

Price
See
price list

100 - 240 V
AC
24 V DCEASY618-AC-RE
212314
EASY620-DC-TE
212313

Std. pack

Information relevant for export to North America

1 off

Product Standards

I/O expansions
Can be used through easyLink
12
12
Power

12

6

–

24 V DC–2–

24 V DCUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

EASY618-DC-RE
232112
EASY202-RE1)
232186

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
6

4–

24 V DC

6–

4

24 V DCEASY410-DC-RE
114293
EASY410-DC-TE
114294NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987; CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: Request filed
for UL and CSA
IEC: IP20,
UL/CSA Type: -Coupling module
Can be used through easyLink
For remote connection of a digital I/O
expansion up to 30 m.

EASY200-EASY
212315

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

InputsDigital / analog

Supply voltage

Part no.
Article no.

1

24 V DC2

24 V DCEASY406-DC-ME
114295
EASY411-DC-ME116567

Outputs
Of whichusable as
digital

Relays
10 A (UL)

Transistor

Analog

1 / 2 2)2–

2

1 / 6 3)

2–

2

IEC/EN see Technical Data;
UL 508; CE marking;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -

Price
See
price list

Std. pack

I/O expansions
Can be used through easyLink

Notes1) Not for use in combination with EASY719-DA-…basic unit

Information relevant for export to North America

Cannot be used on the EASY200‐EASY coupling module2) 2 × 0 - 10 V, 2 × 0 - 20 mA, 2 × RTD (2/3-wire connection);any combination
Voltage inputs (0–10 V) can optionally be used as digital inputs
3) 2 x 0 - 10 V, 2 x 0 - 20 mA, 2 x Pt100 (2/3 wire connection);
Voltage inputs (0–10 V) can optionally be used as digital inputs

NA Certification
Degree of Protection

1 off
1 off

Request filed for UL and CSA
IEC: IP20,
UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

12/16

Control relays

800

Expansion units, accessories
HPL12016EN
800Expansion units, accessories

SupplyvoltagePart no.
Article no.

Slave
4 inputs, 4 outputs,
4 parameter bits
Addresses
available
0 to 31
Slave
Addresses
available
1 to 126–

EASY205-ASI
22159824 V DCEASY204-DP
212316

CANopenAddresses
available
1 to 127

24 V DCEASY221-CO
233539DeviceNet

Addresses
available
0 to 63

24 V DCEASY222-DN
23354024 V DCEASY209-SE
101520

1 off

With keypad, with Moeller company logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29
With keypad, without Moeller company
logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29

MFD-80-B
265251

1 off

MFD-80-B-X
284905

1 off

Without keypad, with Moeller company
logotype
Without keypad,
without Moeller company logotype
NEMA 4xMFD-80265250
MFD-80-X
284904

1 off

Description

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Bus modules
Can be used through easyLink
AS-Interface

PROFIBUSDPUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see TechnicalData;
UL 508; CE marking;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Ethernet gateway
Serial interface easyRelay or
MFD-...CP8/CP10... to Ethernet,
for connecting to easyOPC server,
easySoft, or easyCom

Remote text display
Display/keypad
Monochrome display 132 × 64 pixels with switchable backlight
IP65, removable silver front frame
Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, in combination
with MFD-XM-80: UL/CSA
Type 4X
IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, UL/CSA Type 4X

Power supply unit/communication modules
IP20, can be combined with display/operating unit MFD-80... asremote text display
Product Standards
With connection cable(5 m, can be cut to length)
With connection cable(5 m, can be cut to length)
Without connection cable

24 V DC

Without connection cable

100 - 240 V AC

2010 CA08103002Z-EN

www.eaton.com

24 V DC
100 - 240 V AC

MFD-CP4-800
274095
MFD-AC-CP4-800
286824
MFD-CP4
280888MFD-AC-CP4
286822

1 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -800

Control relays

12/17

Accessories
HPL12017EN
800Accessories

Part no.
Article no.

Std. pack

Information relevant for export to North America

EASY-SOFT-PRO
266040

1 off

UL/CSA certification not required

Sub-D, 9 pole, serial, 2 m

EASY800-PC-CAB
256277

1 off

Product Standards

USB, 2 m

EASY800-USB-CAB
106408

1 off

Configurable modem, printer andprogramming cable, possible
transfer rate 56 kbaud,
9 pole Sub-D plug (plug + socket
for assembly by user)

EASY800-MO-CAB
286079

1 off

MFD-CP4-800-CAB5
280887

1 off

Description

Price
See price
list

Programming software
Menu selection in 13 languages
Operating systems: Windows 2000
SP4, Windows XP SP3,
Windows Vista (32 Bit),
Windows 7 (32 Bit)

Programming cable

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN see Technical Data; UL 508;
CSA C22.2 No. 142-M1987; CSA C22.2
No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified

Modem cable

Connecting cables
For connecting MFD(-AC)-CP4
with easy800/MFD-..-CP8/CP10...
5 m, can be cut to length

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data; UL 508;
CSA C22.2 No. 142-M1987; CSA C22.2
No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Memory cards
EASY-M-256K
256279256-kB module

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data; UL 508;
CSA C22.2 No. 142-M1987; CSA C22.2
No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -800Accessories

Supply voltage

Description

For use withPart no.
Article no.

Price
See pricelistWith plug-in power supply unit
100 - 240 V AC/
24 V DCeasy700-DC
easy800-DC
EC4P

EASY800-DC-SIM
256278

1 off

AWB2528-1423D
261371AWB2528-1423GB
262671

1 off

Std. pack

Input/output simulator
24 V DC

ManualUser manual, German
User manual, English

2010 CA08103002Z-EN

1 off

www.eaton.com

12/18Control relays

800

Accessories
HPL12018EN
800Accessories

For use withPart no.
Article no.

Length: 0.3 m

easyNetLength: 0.8 m

easyNetLength: 1.5 m

easyNetDescription

Price
See price
list

Std. pack

Information relevant for export to North America

EASY-NT-30
256283
EASY-NT-80
256284EASY-NT-150
256285

1 off

Product Standards

Network connection cables

Bus termination resistor

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -8 pole, RJ45, 124 ΩConnection to PIN 1 andPIN 2easyNet

EASY-NT-R
256281

2 off

4 x 0.14 mm², twisted pair,
AWG 26
Length: 100 m

easyNet

EASY-NT-CAB
256286

1 off

UL File No.
UL CCN
NA Certification
Degree of Protection

E135462
NRAQ
UL Listed
IEC: IP 20, UL/CSA Type: -easyNet

EASY-NT-RJ45
25628010 offProduct Standards

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Data cableBus connector plug
8 pole, RJ45UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Crimping tool
For RJ45 plug

EASY-NT-CAB
EASY-NT-RJ45

EASY-RJ45-TOOL
256282

1 off

MFD-800-CAB5
266041

1 off

Point-to-point connection cable
Serial interface forconnecting MFD-…-CP8/
CP10... to easy800 or
MFD-…-CP8/CP10..., 5 m,
can be cut to length

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Switched-mode power supply units
Primary-switched mode, stabilized

Rated input voltage:
50/60 Hz: 100 - 240 V
Rated output voltage:
24 V/12 V DC
Rated output current:
0.35 A/20 mA
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple): 24 V
DC (± 3 %)Rated output current:
1.25 A

Power

Power

Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple): 24 V
DC (± 3 %)Rated output current: 2.5 A
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple): 24 V
DC (± 3 %)Rated output current: 4.2 A

800Accessories

2010 CA08103002Z-EN

www.eaton.com

EASY200-POW
229424

1 off

EASY400-POW
212319

1 off

EASY430-POW
110940EASY500-POW
110941

1 off

EASY600-POW
2623991 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 107.1-01;
CE marking
E300415
NMTR, NMTR7
UL report applies to both
US and Canada
3211-87, 3211-07
UL Listed, certified by UL
for use in Canada
IEC: IP20, UL/CSA Type: -800

Control relays

12/19

Accessories
HPL12019EN
800Accessories

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

BallastTo increase the AC input current
6 channels, cable length up to
100 m

EASY256-HCI
231168UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -PROFIBUS-DP data cable
ZB4-900-KB1
206983100 m

Pins, 9 pole
Cable entry, angled 90°
Metallized insulated housing
Maximum transfer rate 12 Mbits/s
Integrated plug, accessible fromoutside, for bus terminating
resistors
Terminal block for two cable
entries, with straight or 90° angled
cable entry, as required

ZB4-209-DS2
206982
ZB4-209-DS3
217820

1 off

Bus connector plug between
base unit and expansion unit/bus
moduleEASY-LINK-DS
221607

1 off

UL/CSA certification not required

ZB4-101-GF1
061360

9 off

UL/CSA certification not required

M22-TA
226161

1 off

Product Standards

Twisted pair, without plug, 2-core,2 x 0.64 mm²(only suitable for fixed wiring)
100 m

PROFIBUS-DP bus connector plug

1 off

Connection plug

Fixing bracket
For screw fixing to mounting plate
3 fixing brackets
per easy400, 500, 600, 700, 800,
EC4P, ES4P
2 fixing brackets per easy200
3 fixing brackets per
MFD...-CP8/CP10-…

Telescopic clip
With 35 mm top-hat rail to
IEC/EN 60715 for mounting
depth compensation when rear
mounting in CI-K… enclosuresand cabinets.
Stepless adjustment via scalefrom 75 – 115 mm.
Screw and snap fastening

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN 60947-5; UL 508; CSAC22.2 No. 14-05; CSA-C22.2 No.
94-91; CE marking
E29184NKCR
0125283211-03
UL Listed, CSA certified

Top-hat rail adapter for inspection flap window
12 mm x 66 mm x 82 mm
Mounting on hinged inspection
window, for front fitting of devices.
Complete set, consisting of
2 brackets and 4 screws

SKF-HA
233782

1 off

UL/CSA certification not required

130 mm x 77 mm x 25 mm (6 space
units)For use with EASY700, EASY800,
EC4P, ES4P

SKF-FF6
233781

1 off

UL/CSA certification not required

Inspection window

MFD-Titan

2010 CA08103002Z-EN

www.eaton.com

12/20Multi-function display

MFD-Titan

System overview

1
2

1

14

3

4

5

6

POW

BUS

MS

13

NS

13

9
11

8, 10

7
12
9

10

2010 CA08103002Z-EN

www.eaton.com

MFD-Titan

Multi-function display

12/21

Display/operating unit, power supply unit/CPU module
MFD-Titan

Bus modules
EASY204-DP

The multi-function display MFD-Titan
can be used in the following
combinations:Power supply unit/CPU
Power supply unit/CPU + I/O modules
Power supply unit/CPU + display andoperating unit
Power supply unit/CPU + display andoperating unit + I/O modules￫ Page 12/22

I/O modules

EASY221-CO

EASY222-DN

1

EASY202-RE

10

24 V DC
6 digital inputs
4 relay outputs (max. 10 A,UL)
or 4 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

Coupling module
EASY200-EASY

Output expansion
7

2 relay outputs (max. 10 A, UL)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

11

For remote connection of a digital
I/O expansion through two-poleconnection cable (max. 30 m);e.g. NYM 3 × 1.5 mm²￫ Page 12/15

Compact PLC Control
EC4P

I/O expansions

12￫ Page 14/64
1

1

24 V DC
Monochrome display
132 × 64 pixels
With or without keypad
Custom laser labeling possible￫ Page 12/16

2

8

24 V DC
1 digital input
2 analog inputs(2 × 0–10 V, 2 × 0–20 mA, 2 × RTD);
any combination
Voltage inputs (0–10 V) can optionallybe used as digital inputs
2 transistor outputs
1 analog output (0 - 10 V)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

EASY411-DC-ME

Ethernet gateway
EASY209-SE

6

DeviceNet connection, 24 V DC
￫ Page 12/16

24 V DC
100 - 240 V AC
Bus system easyNet optionally
on-board￫ Page 12/22

24 V DC
Serial interface, PSU/CPU module to
Ethernet￫ Page 12/16

4

AS-Interface connection as slave￫ Page 12/16

EASY406-DC-ME

Display/keypad

EASY410...

1

EASY205-ASI

9

5

CANopen connection, 24 V DC
￫ Page 12/16

24 V DC
6 digital inputs
2 of which usable as analog inputs
2 Pt 100 or 2 Ni1000 RTD inputs
4 transistor outputs
1 Analog output, optional
Spring-loaded terminals￫ Page 12/24

Power supply unit/CPU module

3

PROFIBUS DP connection as slave,
24 V DC￫ Page 12/16

24 V DC
100 - 240 V AC
12 digital inputs
4 usable as analog inputs(DC versions)
4 relay outputs (max. 10 A,UL)
or 4 transistor outputs
1 analog output,
optional on DC versions
Spring-loaded terminals￫ Page 12/24

I/O modules with temperature
measuring

EASY6...
24 V DC
12 digital inputs
6 relay outputs (max. 10 A,UL)or 8 transistor outputs
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

Safety control relays
Safety
ES4P

13￫ Page 13/5

Control relays 800
EASY8…

14￫ Page 12/14
8

24 V DC
1 digital input
6 analog inputs(2 x 0 - 10 V, 2 x 0 - 20 mA, 2 x Pt100);
Voltage inputs (0–10 V) can optionallybe used as digital inputs
2 transistor outputs/
2 Analog outputs (0 - 10 V)
Bolt-on and top-hat rail mounting
Screw terminals￫ Page 12/15

MFD-TitanDisplay/operating unit, power supply unit/CPU module2010 CA08103002Z-EN

www.eaton.com

12/22Multi-function display

MFD-Titan

Display/operating units, CPU, communication modules
HPL12022EN

Ordering
Supplyvoltage

Description

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

Product Standards

Display/keypad
Monochrome display 132 × 64 pixels with switchable backlight
IP65, removable silver front frameWith keypad, with Moeller company
logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29
With keypad, without Moeller company
logotype
NEMA 4x in conjunction with MFD-XM-80
protective diaphragm ￫ 12/29

MFD-80-B
265251

1 off

MFD-80-B-X
284905

1 off

Without keypad, with Moeller
company logotype NEMA 4x
Without keypad,
without Moeller company logotype
NEMA 4xMFD-80265250
MFD-80-X
284904

1 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, in combination
with MFD-XM-80: UL/CSA
Type 4X
IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP65, UL/CSA Type 4X

MFD-TitanDisplay/operating units, CPU, communication modules

Power supply unit/CPU module
Can be combined with display and control unit MFD-80-..
and I/O module; expandable: Digital and analog inputs/outputs
and bus systems
AS-Interface, CANopen, PROFIBUS-DP, DeviceNet;bus system easyNet optional on-board IP20
Spring-loaded terminals
Supplyvoltage
100 - 240 V AC Program andscreen memory,with easyNet
100 - 240 V AC Program andscreen memory,
without easyNet
24 V DC
Program andscreen memory,
without easyNet
24 V DC
Program andscreen memory,with easyNet
24 V DC

24 V DC

1) Note2010 CA08103002Z-EN

Dual program andscreen memory as
MFD-...-CP8...,
without easyNet
Dual program andscreen memory as
MFD-...-CP8...,with easyNet

1) For availability please inquire

www.eaton.com

MFD-AC-CP8-NT
274092

1 off

MFD-AC-CP8-ME
274091

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

MFD-CP8-ME
267164
MFD-CP8-NT
265253
MFD-CP10-ME 1)
133801

1 off

MFD-CP10-NT 1)
133800

1 off

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -MFD-Titan

Multi-function display

12/23

Communication modules
HPL12023EN
MFD-TitanCommunication modules

Supplyvoltage

Description

Part no.
Article no.

For usewithPrice
See price
list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards

1 off

UL/CSA certification not required

Power supply unit/communication modules
IP20, can be combined with display/operating unit MFD-80...
as remote text display
24 V DC
With connection
easy500
cable
easy700(5 m, can be cut tolength)24 V DC
With connection
easy800
cable
EC4P(5 m, can be cut toES4P
length)100 - 240 V AC With connection
easy500
cable
easy700(5 m, can be cut tolength)100 - 240 V AC With connection
easy800
cable
EC4P(5 m, can be cut toES4P
length)24 V DC
Without connection
cable
100 - 240 V AC Without connection
cable

MFD-CP4-500
274094

MFD-CP4-800
274095

MFD-AC-CP4-500
286823

MFD-AC-CP4-800
286824

IEC/EN see
Technical Data;
UL 508; CSA C22.2
No. 142-M1987;
CSA C22.2 No. 213M1987;
CE marking
UL File No.
E135462
UL CCNNRAQ
CSA File No.
012528CSA Class No.
2252-01 + 2258-02
NA Certification
UL Listed,
CSA certified
Degree of Protection IEC: IP20,
UL/CSA Type: -MFD-CP4
280888MFD-AC-CP4
286822Customized inscription, user program
MFD-80-...
MFDMFD-CP8... COMBINATION-*
MFD-CP10... 265260• Customized inscription of multi-function display withlabeling software Labeleditor or• Supply of multi-function display programmed with user
program
Notes

Procedure and ordering example for Labeleditor inscription software
Individually inscribe your device in 4 stages:– Download the inscription software: www.moeller.net/support, keyword: “Labeleditor”– Creation of label template (menu-guided in the software)– Send the label template to the factory by email. The email address is automatically set for the selected product by the program. When yourtemplate is sent, the Labeleditor issues a file name such as “EASY_12345.zip”. This file name is part of the article to be ordered (see Ordering
examples).
– Send order to the Eaton office or the electrical wholesalers.
Ordering example: MFD-Titan
MFD-80-B multi-function display with “company name”:
1 x MFD-COMBINATION-*
1 x MFD-80-B
1 x the file name “MFD_xxxxx.zip” issued by the Labeleditor

Accessories
1 Ethernet gateway
2 Connection cable
3 Programming software
4 PC programming cable
5 Inputs/outputs expansion
6 output expansion, bus module,
coupling module
7 Display/keypad
8 Power supply unit/CPU module
9 I/O module
10 Memory card
11 easyNet
12 Switched-mode power supply unit

3
1

4

2

4

11

easyNet10Page￫ Page 12/16￫ Page 12/27￫ Page 12/9
￫ Page 12/9
￫ Page 12/15￫ Page 12/16￫ Page 12/16￫ Page 12/23￫ Page 12/17￫ Page 12/9
￫ Page 12/18￫ Page 12/10

MFD Titan
easy 800

5

Power

9
6

7

8

2, 4
10

9

8

12

5

2010 CA08103002Z-EN

www.eaton.com

12/24Multi-function display

MFD-Titan

I/O modules
HPL12024EN
MFD-TitanI/O modules

Power supply

DigitalOf which
can beused asanalog

Pt100

Relays 10
A (UL)

Transistor

AnalogTemperature
range

Part no.
Article no.

MFD-CP8...
MFD-CP10...
MFD-CP8...
MFD-CP10...
MFD-CP8...
MFD-CP10...
MFD-CP8...
MFD-CP10...

12

4

–

4

–

–

–

1 off

12

4

–

–

4

–

–

12

4

–

4

–

1

–

12

4

–

–

4

1

–

MFD-R16265254
MFD-T16265255
MFD-RA17265364
MFD-TA17265256

MFD-ACCP8...

12

–

–

4

–

–

–

MFD-AC-R16
274093

1 off

6

2

2

–

4

–

MFD-TP12-PT-A
106042

1 off

6

2

2

–

4

–

2

–

–

4

–

6

2

2

–

4

1

MFD-TP12-PT-B
106043
MFD-TP12-NI-A
106044
MFD-TAP13-PT-A
106045

1 off

6

6

2

2

–

4

1

2

–

–

4

1

MFD-TAP13-PT-B
106046
MFD-TAP13-NI-A
1060471 off

6-40…+90 °C
0…+250 °C
0…+400 °C-200…+200 °C
0…+850 °C-40…+90 °C
0…+250 °C-40…+90 °C
0…+250 °C
0…+400 °C-200…+200 °C
0…+850 °C-40…+90 °C
0…+250 °C

For use with

Inputs

OutputsPrice
See price list

Std. packI/O modules
IP20, spring-loaded terminals

24 V DC
24 V DC
24 V DC
24 V DC
100 - 240 V DC

1 off
1 off
1 off

I/O module with temperature measuring
IP20, spring-loaded terminals
Temperature range configurable

24 V DC

MFD-CP8...
as of device
version 08,
MFD-CP10...

Information relevant for export to North America
Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection2010 CA08103002Z-EN

IEC/EN see Technical Data; UL 508; CSA C22.2 No. 142-M1987; CSA C22.2 No. 213-M1987; CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -www.eaton.com

1 off
1 off

1 off

MFD-Titan

Multi-function display

12/25

Expansion devices
HPL12025EN
MFD-TitanExpansion devices

Inputs

Outputs

DigitalRelay
10 A (UL)

Transistor

6

–

–

8

SupplyvoltagePart no.
Article no.

Price
See
price list

100 - 240 V
AC
24 V DCEASY618-AC-RE
212314
EASY620-DC-TE
212313

Std. pack

Information relevant for export to North America

1 off

Product Standards

I/O expansions
Can be used through easyLink
12
12
Power

12

6

–

24 V DC–2–

24 V DCUL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

EASY618-DC-RE
232112
EASY202-RE1)
232186

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
6

4–

24 V DC

6–

4

24 V DCEASY410-DC-RE
114293
EASY410-DC-TE
114294NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987; CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: Request filed
for UL and CSA
IEC: IP20,
UL/CSA Type: -Coupling module
Can be used through easyLink
EASY200-EASY
212315For remoteconnection ofa digital I/O
expansion up
to 30 m.

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

InputsDigital / Analog

SupplyvoltagePart no.
Article no.

1

24 V DC2

24 V DCEASY406-DC-ME
114295
EASY411-DC-ME116567

Outputs
Of whichusable as
digital

Relay 10 A
(UL)Transistor

Analog

1 / 22)2–

2

1 / 63)

2–

2

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ, NRAQ70125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -

Price
See
price list

Std. pack

I/O expansions
Can be used through easyLink

Notes1) Not for use in combination with basic unit EASY719-DA-...

1 off
1 off

Information relevant for export to North America

Cannot be used on the EASY200‐EASY coupling module2) 2 × 0 - 10 V, 2 × 0 - 20 mA, 2 × RTD (2/3-wire connection);any combination
Voltage inputs (0–10 V) can optionally be used as digital inputs
3) 2 x 0 - 10 V, 2 x 0 - 20 mA, 2 x Pt100 (2/3 wire connection);
Voltage inputs (0 –10 V) can optionally be used as digital inputs

NA Certification
Degree of Protection

Request filed for UL and CSA
IEC: IP20,
UL/CSA Type: -2010 CA08103002Z-EN

www.eaton.com

12/26

Multi-function display

MFD-Titan

Expansion devices
HPL12026EN
MFD-TitanExpansion devices

SupplyvoltagePart no.
Article no.

Slave
4 inputs,
4 outputs,
4 parameter bits
Addresses
available
0 to 31
Slave
Addresses
available
1 to 126–

EASY205-ASI
22159824 V DCEASY204-DP
212316

CANopenAddresses
available
1 to 127

24 V DCEASY221-CO
233539DeviceNet

Addresses
available
0 to 63

24 V DCEASY222-DN
23354024 V DCEASY209-SE
101520Description

Price
See price
list

Std. pack

Information relevant for export toNorth America

1 off

Product Standards

Bus modules
Can be used through easyLink
AS-Interface

PROFIBUSDP

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
UL File No.
E135462
UL CCN
NRAQ, NRAQ7
CSA File No.
012528CSA Class No.
2252-01 + 2258-02
NA Certification
UL Listed, CSA certified
Degree of ProtectionIEC: IP20, UL/CSA Type: -Ethernet gateway
Serial interface easyRelay or
MFD-...CP8/CP10... to Ethernet,
for connection to easyOPC
server, easySoft, or easyCom

1 off

MFD-TitanAccessoriesMFD-TitanAccessories

Description

For use withPart no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

Programming software
Menu selection in 13 languages
Operating systems: Windows 2000 SP4,
Windows XP SP3,
Windows Vista (32-bit), Windows 7 (32-bit)

EASY-SOFT-PRO
266040

1 off

EASY800-PC-CAB
256277

1 off

Programming cable
SUB-D, 9 pole, serial, 2 m

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
USB, 2 m

EASY800-USB-CAB
106408

1 off

Configurable modem, printer and programming
cable, possible transfer rate 56 kbaud,
9 pole Sub-D plug (plug + socket for selfconnection)

EASY800-MO-CAB
2860791 off

Modem cable

Connecting cables

2010 CA08103002Z-EN

www.eaton.com

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142M1987; CSA C22.2 No.
213-M1987; CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified

MFD-Titan

Multi-function display

12/27

Accessories
HPL12027EN
Description

For use withFor connecting the MFD(-AC)-CP4 or EASY209-SE witheasy500/easy700,
5 m, can be cut to length
For connecting the MFD(-AC)-CP4 or EASY209-SE witheasy800/MFD-..-CP8/CP10...,5 m, can be cut to length

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

MFD-CP4-500-CAB5
280886

1 off

Product Standards

MFD-CP4-800-CAB5
280887

1 off

EASY-M-256K
256279EASY-M-512K1)
1349691 off

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142M1987; CSA C22.2 No.
213-M1987; CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Memory cards
256-kB module

MFD-…-CP8

512-kB module

MFD-CP10...

Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142M1987; CSA C22.2 No.
213-M1987; CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Manuals
German

MFD-Titan

English

MFD-Titan

AWB2528-1480D
267187AWB2528-1480GB
267188

1 off

EASY-NT-30
256283
EASY-NT-80
256284EASY-NT-150
256285

1 off

1 off

Network connection cables
Length: 0.3 m

easyNetLength: 0.8 m

easyNetLength: 1.5 m

easyNetProduct Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical
Data; UL 508;
CSA C22.2 No. 142M1987; CSA C22.2 No.
213-M1987; CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -UL File No.
UL CCN
NA Certification
Degree of Protection

E135462
NRAQ
UL Listed
IEC: IP 20, UL/CSA Type: -

1 off
1 off

Bus termination resistor
8 pole, RJ45, 124 ΩConnection to PIN 1 and PIN 2

easyNet

EASY-NT-R
256281

2 off

4 x 0.14 mm², twisted pair,
AWG 26
Length: 100 m

easyNet

EASY-NT-CAB
256286

1 off

Data cableNote1) For availability please inquire

MFD-TitanAccessories

Description

For use withPart no.
Article no.

8 pole, RJ45

easyNet

EASY-NT-RJ45
256280Price
See price
list

Std. pack

Information relevant for export to North America

10 offProduct Standards

Bus connector plug

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987;
CE marking
E135462
NRAQ
0125282258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Crimping tool–

For RJ45 plug

EASY-NTCABEASY-NTRJ45

EASY-RJ45-TOOL
256282

1 off2010 CA08103002Z-EN

www.eaton.com

12/28Multi-function display

MFD-Titan

Accessories
HPL12028EN
Description

For use withPart no.
Article no.

easy800
MFD-…-CP8

MFD-800-CAB5
266041Price
See price
list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Point-to-point connection cable
Serial interface
for connecting
MFD-…-CP8/CP10... toeasy800 or
MFD-…-CP8/CP10...,5 m, can be cut tolengthDescription

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

Part no.
Article no.

Price
See pricelist

IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -Std. pack

Information relevant for export to North America

EASY200-POW
229424

1 off

Product Standards

EASY400-POW
212319

1 off

EASY430-POW
110940EASY500-POW
110941

1 off

EASY600-POW
2623991 off

Switched-mode power supply units
Primary-switched mode, stabilized
Rated input voltage:
50/60 Hz: 100 - 240 V
Rated output voltage:
24 V/12 V DC
Rated output current:
0.35 A/20 mA
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple):
24 V DC (± 3 %)Rated output current:
1.25 A

Power

Power

Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple):
24 V DC (± 3 %)Rated output current: 2.5 A
Rated input voltage:
50/60 Hz: 100 - 240 V AC
Rated output voltage (residual ripple):
24 V DC (± 3 %)Rated output current: 4.2 A

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection
Product Standards

1 off
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01 + 2258-02
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 107.1-01;
CE marking
E300415
NMTR, NMTR7
UL report applies to both US andCanada3211-87, 3211-07
UL Listed, certified by UL for use
in Canada
IEC: IP20, UL/CSA Type: -BallastTo increase the AC input current
6 channels, cable length up to 100 m

EASY256-HCI
231168

1 off

Product Standards

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

IEC/EN see Technical Data;
UL 508;CSA C22.2 No. 142-M1987;
CSA C22.2 No. 213-M1987;
CE marking
E135462
NRAQ
0125282252-01
UL Listed, CSA certified
IEC: IP20, UL/CSA Type: -MFD-Titan

Multi-function display

12/29

Accessories
HPL12029EN
MFD-TitanAccessories

Description

For use withPart no.
Article no.

Price
See price
list

Std. pack

Information relevant for export to North America

PROFIBUS-DP data cable
ZB4-900-KB1
206983100 m

Pins, 9 pole
Cable entry, angled 90°
Metallised insulated housing
Maximum transfer rate 12 MBit/s
Integrated switch (accessible from theoutside) for the bus terminating resistors
Terminal block for two cable entries,
with straight or 90° angled cable entry, as
required

ZB4-209-DS2
206982
ZB4-209-DS3
217820

1 off

Bus connector plug between base unit andexpansion unit/bus module

EASY-LINK-DS
221607

1 off

UL/CSA certification not required

ZB4-101-GF1
061360

9 off

UL/CSA certification not required

M22-TA
226161

1 off

Product Standards

Twisted pair, without plug, 2-core,2 x 0.64 mm²(only suitable for fixed wiring)
100 m

PROFIBUS-DP bus connector plug

1 off

Connection plug

Fixing bracket
For screw fixing to mounting plate
3 fixing brackets
per easy400, 500, 600, 700, 800, EC4P, ES4P
2 fixing brackets per easy200
3 fixing brackets per MFD...-CP8/CP10…

Telescopic clip
With 35mm top-hat rail to IEC/EN 60715 formounting depth compensation when rear
mounting in CI-K… enclosures and cabinets.
Stepless adjustment via scale from75 – 115 mm.
Screw and snap fastening

UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification

IEC/EN 60947-5; UL 508;
CSA-C22.2 No. 14-05;
CSA-C22.2 No. 94-91;
CE marking
E29184NKCR
0125283211-03
UL Listed, CSA certified

Mounting rail to IEC/EN 60715
Mounting rail with cutout specifically for MFD...-CP8/CP10… for fixing
easy expansion units (2 space units)
Length: 142.5 mm
easy200

MFD-TS-144
274090

1 off

UL/CSA certification not requiredProtective coverTransparent
Protection against
accidental actuation
sealable
Application without front
framesMFD-80…

MFD-XS-80
2652591 off

Product Standards IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987; CE marking
UL File No.
E135462
UL CCNNRAQ
CSA File No.
012528CSA Class No.
2252-01 + 2258-02
NA Certification
UL Listed, CSA certified

Transparent version forharsh environmental
conditions and applicationin the food industry
For increasing the degree ofprotection to NEMA 4X for
MFD-80-B

MFD-80…

MFD-XM-80
265258

1 off

Product Standards IEC/EN see Technical Data;
UL 508; CSA C22.2 No. 142M1987; CSA C22.2 No. 213M1987; CE marking
UL File No.
E135462
UL CCNNRAQ
CSA File No.
012528CSA Class No.
2252-01 + 2258-02
NA Certification
UL Listed, CSA certified
Degree of ProtectionIEC: IP65, UL/CSA Type 4X

Protective diaphragm2010 CA08103002Z-EN

www.eaton.com

12/30Control relays

...

Basic devices, expansion devices
...Basic devices, expansion devices

Technical data

EASY200-EASY
EASY202-RE

EASY4…-DC-…E

EASY6...

EASY512-…

EASY8..-…
EASY7…

GeneralStandards

EN 55011, EN 55022, IEC/EN 61000-4, IEC 60068-2-6, IEC 60068-2-27

Dimensions (W x H x D)

mm

Weightkg

35.5 x 90 x 58
(2 space units)
0.07

Mounting

71.5 x 90 x 58
(4 space units)
0.2

107.5 x 90 x 58
(6 space units)
0.3

107.5 x 90 x 72
(6 space units)
0.3

Top-hat rail IEC/EN 60715, 35 mm or screw fixing using fixing brackets ZB4-101-GF1(accessories).

Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

Max. tightening torque

Nm

0.6

°C

-25…55, low temperatures to IEC 60068-2-1, high temperatures to IEC 60068-2-2

Ambient climatic conditions
Operating ambient temperature
Condensation

Prevent condensation by means of suitable measures

LCD display (clearly legible)°C

0 - 550 - 550 - 550 - 55Storage°C-40 - 70

-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 955 - 955 - 955 - 95Air pressure (in operation)hPa

795 - 1080

795 - 1080

795 - 1080

795 - 1080

IP20

IP20

IP20

IP20

Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

57 - 150

57 - 150

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Drop height

Shocks

18

18

18

18

mm

50

50

50

50

Free fall, packaged (IEC/EN 60068-2-32)

m

1

1

1

1

II/2

II/2

II/2

II/2

Mounting position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree
Electrostatic discharge (ESD), to IEC EN 61000-4-2
Air discharge

kV

8

8

8

8

Contact discharge

kV

6

6

6

6

V/m

10

10

10

10

Electromagnetic fields (RFI), to IEC EN 61000-4-2
Radio interference suppression

EN 55011 Class B, EN 55022 Class B

Burst to IEC/EN 61000-4-4
Supply cables

kV

2

2

2

2

Signal cables

kV

2

2

2

2

kV

2 (supply cables, symmetrical, EASY…AC)Power pulses (surge), to IEC/EN 61000-4-5

kV

0.5 (supply cables, symmetrical, EASY…DC)

Radiated RFI, to IEC/EN 61000-4-6

V

10

10

10

EN 50178

EN 50178

Power pulses (surge), to IEC/EN 61000-4-5

10Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

EN 50178

Back-up/accuracy of the real-time clock
–

–

1)

–

1)

1)

s/day

–

–

Normally ± 5(± 0.5 h⁄Year)–

Normally ± 5(± 0.5 h⁄Year)

Normally ± 5(± 0.5 h⁄Year)Accuracy of timing relay (of value)

%

–

–

±1

± 0.02± 0.02

Resolution

Range “S”

ms

–

–

10

10

5

Range “M:S”

s

–

–

1

1

1

Range “H:M”

min

–

–

1

–

1000000(106)

1000000(106)

10000000 (1010)(read/write cycles)

Back-up time
Accuracy of the real-time clock at 55 °C
Repetition accuracy of timing relays

Retentive memory

1

Write cycles of the retentive memory (minimum)

–

Notes

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D
1)a2010 CA08103002Z-EN

www.eaton.com

200
180
160
140
120
100
80
60
40
20
0

① Back-up time (hours)② Service life (years)

25°C
55°C

0

1

2 3

4

5

6

7

8

9

10 11 12 13 14 15 16 17 18 19 20b...DA...

Control relays

12/31

Basic devices
...DA...Basic devices

EASY512-DA-…

EASY719-DA-…

Power supply
Rated operational voltage

V

12 DC (-15/+30%)

12 DC (-15/+30%)

Permissible range

Ue

V DC

10.2…15.6

10.2…15.6

Ripple%≦5≦5Input current
At rated voltage

mA

Normally 140

Normally 200

Voltage dips (IEC/EN 61131-2)

ms

10

10

Heat dissipation

W

Normally 2

Normally 3.5

Number812

Inputs can be used as analog inputs

2 (I7, I8)

4 (I7, I8, I11, I12)

Status display

LCD display (if provided)

LCD display (if provided)

Digital inputs 12 V DC

Potential isolation
From power supply

No

No

Between digital inputs

No

No

From the outputs

Yes

Yes

Rated operating voltage

Ue

V DC

12

12

On signal ”0”

Ue

V DC

4 (I1 - I8)

4 (I1 - I12)

On signal ”1”

Ue

V DC

8 (I1 - I8)

8 (I1 - I12)

Input current on signal "1"
I1 to I6mA

3.3 (at 12 V DC)

3.3 (at 12 V DC)

I7, I8, I11, I12mA

1.1 (at 12 V DC)

1.1 (At 12 V DC)

I9 to I10mA–

3.3 (at 12 V DC)

Debounce ON

ms

20

20

Debounce OFF

ms

Normally 0.3 (I1 - I6), 0.35 (I7, I8)

Normally 0.3 (I1 - I6, I9, I10), 0.35 (I7, I8, I11, I12)

Debounce ON

ms

20

20

Debounce OFF

ms

Normally 0.3 (I1 - I6), 0.15 (I7, I8)

Normally 0.4 (I1 - I6, I9, I10), 0.35 (I7, I8, I11, I12)

m

100

100

Frequency counters

2 (I3, I4)

2 (I3, I4)

High-speed counter inputs

2 (I1, I2)

2 (I1, I2)<1<1

SquareSquare< 30< 30

2 (I7, I8)

4 (I7, I8, I11, I12)

Delay time from 0 to 1

Delay time from 1 to 0

Cable length (unshielded)

Maximum counter frequency

kHz

Pulse shape
Cable length shieldedmAnalog inputs
NumberPotential isolation
From power supply

No

No

From the digital inputs

No

No

From the outputs

Yes

Yes

Between the inputs

NoNo

DC voltage

DC voltage

Input type
Signal range

V DC

0 - 100 - 10Resolution, analog

V

0.01

0.01

Resolution, digital

V

0.01

0.01

Resolution

Bit

10 (value 1 - 1023)

10 (value 0 - 1023)

Input impedance

kΩ

11.2

11.2

Two EASY devices

%

±3

±3

Within a single device%± 2, (I7, I8, I11, I12) ± 0.12 V± 2, (I7, I8, I11, I12) ± 0.12 V

Conversion time analog/digitalms

Input current

mA

Input delay ON: 20;
Input delay OFF: each cycle time
<1

Input delay ON: 20;
Input delay OFF: each cycle time
<1

Cable length shielded

m

< 30

< 30

Accuracy of actual value

Relay outputs￫ See technical data, relay outputs

Notes

For additional Technical Data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8…
￫ AWB2528-1423D

2010 CA08103002Z-EN

www.eaton.com

12/32Control relays

...AB...

Basic devices
...AB...Basic devices

EASY512-AB-…

EASY719-AB-…

Power supply
V

24 AC

24 AC

Permissible range

Rated operational voltage

Ue

V AC

20.4…26.4

20.4…26.4

Frequency

Hz50/60 (± 5%)50/60 (± 5%)mA

Normally 200

Normally 300

ms

20

20

VA

Normally 5

Normally 7

Input current
At 24 V AC 50/60 Hz
Voltage dips (IEC/EN 61131-2)
Heat dissipation
At 24 V AC
Digital inputs 24 V DC
Number812

Inputs can be used as analog inputs

2 (I7, I8)

4 (I7, I8, I11, I12)

Status display

LCD display (if provided)

LCD display (if provided)

Potential isolation
From power supply

No

No

Between digital inputs

No

No

From the outputs

Yes

Yes

Rated operational voltage

Ue

V

24 AC

24 AC

V AC

0-6

0-6

Ue

V

(I7, I8) > 7 AC, > 9.5 DC (I1 - I6) 14 - 26.4 AC

Hz

50 - 60(I7, I8, I11, I12) > 7 AC, > 9.5 DC (I1 - I6, I9, I10)
14 - 26.4 AC
50 - 60

Rated voltage L (sinusoidal)
On signal ”0”
On signal ”1”
Rated frequency
Input current on signal "1"
I1 to I6mA

4 (at 24 V AC, 50 Hz)

4 (at 24 V AC, 50 Hz)

I7, I8mA

2 (at 24 V AC, 50 Hz) 2 (at 24 V DC)

2 (at 24 V AC, 50 Hz) 2 (at 24 V DC)

I9, I10mA–

4 (At 24 V AC, 50 Hz)

I11, I12mA–

2 (at 24 V AC, 50 Hz) 2 (at 24 V DC)

Debounce ON, 50/60 Hz

ms

80⁄66⅔

80⁄66⅔

Debounce OFF, 50/60 Hz

ms

20⁄16⅔

20⁄16⅔

Maximum remote installation distance

m

40

40

I9, I10m–

Normally 40

2 (I7, I8)

4 (I7, I8, I11, I12)

Delay time (0 - 1/1 - 0) I1 - I12

Max. admissible cable length (per input)

Analog inputs
NumberPotential isolation
From power supply

No

No

From the digital inputs

No

No

From the outputs

Yes

Yes

Between the inputs

NoNo

DC voltage

DC voltage

Input type
Signal range

V DC

0 - 100 - 10Resolution, analog

V

0.01

0.01

Resolution, digital

V

0.01

0.01

Resolution

Bit

10 (value 1 - 1023)

10 (value 0 - 1023)

Input impedance

kΩ

11.2

11.2

Accuracy of actual value
Two EASY devices

%

±3

±3

Within a single device%± 2, (I7, I8) ± 0.12 V± 2, (I7, I8, I11, I12) ± 0.12 V

Conversion time analog/digitalms

Input current

mA

Input delay ON: 20;
Input delay OFF: each cycle time
<1

Input delay ON: 20;
Input delay OFF: each cycle time
<1

Cable length shielded

m

< 30

< 30

Relay outputs￫ See technical data, relay outputs

Notes

2010 CA08103002Z-EN

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D

www.eaton.com

...DC...

Control relays, multi-function display

12/33

Basic devices, expansion devices
...DC...Basic devices, expansion devices

EASY410-DC-RE
EASY410-DC-TE

EASY512-DC-…

EASY6..-DC-.E

EASY7..-DC-…

EASY7..-DC-…

EASY8..-DC-…

Power supply
Rated operational voltage

V

24 DC (-15/+20%)

Permissible range

Ue

V DC

20.4…28.8

20.4…28.8

20.4…28.8

20.4…28.8

20.4…28.8

20.4…28.8

Ripple

%

≦5

≦5

≦5

≦5

≦5

≦5

Input current
mA

Normally 140

Normally 80

Normally 140

Normally 140

Normally 140

Normally 140

Voltage dips (IEC/EN 61131-2)

At rated voltage

ms

10

10

10

10

10

10

Heat dissipation

W

Normally 3.5

Normally 2

Normally 3.4

Normally 3.5

Normally 3.5

Normally 3.4

Digital inputs 24 V DC
Number

6

8

12

12

12

12

Inputs can be used as analog inputs-

2 (I7, I8)–

4 (I7, I8, I11, I12)

4 (I7, I8, I11, I12)

4 (I7, I8, I11, I12)

Status display

LCD display (if provided)

Potential isolation
From power supply

No

No

No

No

No

No

Between digital inputs

No

No

No

No

No

No

From the outputs

Yes

Yes

Yes

Yes

Yes

Yes

–

–

–

–

–

Yes

From PC interface, memory card,easyNet, easyLink
Rated operating voltage

Ue

V DC

24

24

24

24

24

24

On signal ”0”

Ue

V DC

< 5 (R1 - R6)< 5 (I1 - I8)< 5 (I1 - I12,
R1 - R12)< 5 (I1 - I12,
R1 - R12)< 5 (I1 - I12,
R1 - R12)

On signal ”1”

Ue

V DC

> 15.0 (R1 - R6)> 15 (I1 - I6), > 8(I7, I8)–> 15.0 (I1 - I6, I9,
I10), > 8.0 (I7, I8,
I11, I12)> 15.0 (I1 - I6, I9,
I10), > 8.0 (I7, I8,
I11, I12)< 5 (I1 - I6, I9,
I10) < 8 (I7, I8,
I11, I12)> 15.0 (I1 - I6, I9,
I10), > 8.0 (I7, I8,
I11, I12)

R1 - R6 (R12)mA

3.3 (at 24 V DC)–

3.3 (at 24 V DC)

–

–

–

I1 to I6mA–

3.3 (at 24 V DC)–

3.3 (at 24 V DC)

3.3 (at 24 V DC)

3.3 (at 24 V DC)

I7, I8mA–

2.2 (at 24 V DC)–

2.2 (at 24 V DC)

2.2 (at 24 V DC)

2.2 (at 24 V DC)

I9, I10

mA

–

–

–

3.3 (at 24 V DC)

3.3 (at 24 V DC)

3.3 (at 24 V DC)

I11, I12

mA

–

–

–

2.2 (at 24 V DC)

2.2 (at 24 V DC)

2.2 (at 24 V DC)

Debounce ON

ms

20

20

20

20

20

20

Debounce OFF

ms

Normally 0.25
(R1 - R6)

Normally 0.25
(I1 - I8)

Normally 0.25
(R1 - R12)

Normally 0.25
(I1 - I12)

Normally 0.25
(I1 - I12)

Normally 0.1(I1 - I4), normally0.25 (I5 - I12)

Input current on signal "1"

Delay time from 0 to 1

Delay time from 1 to 0
Debounce ON

ms

20

20

20

20

20

20

Debounce OFF

ms

–

–

–

–

–

Cable length (unshielded)

m

100

100

100

100

100

Normally 0.1(I1 - I4), normally
0.4 (I5, I6, I9, I12),
normally 0.2 (I7,
I8, I11, I12)100–

2 (I3, I4)–

2 (I3, I4)

2 (I3, I4)

4 (I1, I2, I3, I4)

–

<1

–

<1

<1

<5

–

Square–SquareSquareSquare

–

–

–

–

–

2 (I1 + I2, I3 + I4)

–

≦1

–

≦1

≦1

≦3

Pulse shape

–

–

–

–

–

SquareCounter inputs I1 and I2, I3 and I4

–

–

–

–

–

2

Signal offset

–

–

–

–

–

90°

Mark-to-space ratio

–

–

–

–

–

1:1

Frequency counters
NumberCounter frequency

kHz

Pulse shape
Incremental counters
NumberCounter frequency

kHz

High-speed counter inputs–

2 (I1, I2)–

2 (I1, I2)

2 (I1, I2)

4 (I1, I2, I3, I4)

Cable length, shielded

Number
m

–

< 20

–

< 20

< 20

< 20

Counter frequency

kHz

–

<1

–

<1

<1

<5

–

Square–SquareSquareSquare

–

100

100

100

100

100

Pulse shape
Cable length (unshielded)mTransistor outputs￫ See technical data, relay outputs￫ See technical data, transistor outputs

Notes

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D

Relay outputs

2010 CA08103002Z-EN

www.eaton.com

12/34Control relays, multi-function display

...DC...

Basic devices, expansion devices
...DC...Basic devices, expansion devices

EASY406…-DC-ME

EASY411-DC-ME

EASY512-DC-…

EASY7..-DC-…

EASY8..-DC-…

2

6

2 (I7, I8)

4 (I7, I8, I11, I12)

4 (I7, I8, I11, I12)

Analog inputs
NumberPotential isolation
From power supply

No

No

No

No

No

From the digital inputs

No

No

No

No

No

From the outputs

No

No

Yes

Yes

Yes

Yes

Yes

No

No

Yes

From PC interface, memory card,easyNet, easyLink
Input type

DC voltage

DC voltage

DC voltage

DC voltage

DC voltage

Signal range

V DC

0 - 100 - 100 - 100 - 100 - 10Resolution, analog

V

–

–

0.01

0.01

0.01

Resolution, digital

V

–

–

0.01

0.01

0.01

Resolution

Bit

10 (value 0 - 1023)

Input impedance

kΩ

11.2

11.2

11.2

11.2

11.2

±3

±3

Accuracy of actual value
Two EASY devices

%

±3

±3

±3

Within a single device

%

<±3%

<±3%

Conversion time analog/digital

ms

800

800

Input current

mA

<1

<1

± 2, (I7, I8, I11, I12)
± 2, (I7, I8, I11, I12)
± 0.12 V± 0.12 V
Input delay ON: 20; input delay OFF: every
cycle time<1
<1

± 2, (I7, I8, I11, I12)
± 0.12 V
Each CPU
cycle<1

Cable length shielded

m

< 10

< 10

< 30

< 30

< 30

1

2

–

–

1

Analog outputs
NumberPotential isolation
From power supply

No

No

No

No

No

From the digital inputs

No

No

No

No

No

From the digital outputs

No

No

No

No

Yes

easyLink

Yes

Yes

No

No

Yes

DC voltage

DC voltage––

DC voltage

Output type
Signal range
Signal range min. voltage

V

0

0

–

–

0

Signal range max. voltage

V

10

10

–

–

10

A

0.01

0.01

–

–

0.01

Load resistance

1 kΩ

1 kΩ

–

–

1 kΩ

Overload and short-circuit protection

Yes

Yes

–

–

Yes

Max. output current

Resolution, analog

V DC

0.01

0.01

–

–

0.01

Resolution, digitalBit

10 (value 0 - 1023)

10 (value 0 - 1023)––

Recovery time

μs

–

–

–

–

10, (value:0 – 1023)
100-25 °C - 55 °C

%

2

2

–

–

2

25C

%

1

1

–

–

1

ms

200

200

Input delay ON: 20; input delay OFF:every cycle time

Each CPU
cycle

Number––––Max. 8––––1000 Kbit/s, 6 m
500 Kbit/s, 25 m
250 Kbit/s, 60 m
125 Kbit/s, 125 m
50 Kbit/s, 300 m
20 Kbit/s, 700 m
10 Kbit/s, 1000 m

Accuracy

Conversion time analog/digital
Network easyNet
Stations
Data transfer rate/distance

Potential isolation
Of the 2 additional inputs

–

–

–

–

Yes

Potential isolation

–

–

–

–

Yes

Electrical isolation between inputs andinternal power supply
Potential isolation

–

–

–

–

Yes

–

–

–

–

Yes

Bus termination (first and last station)

–

–

–

–

Yes

Terminal type

–

–

–

–

RJ45, 8 pole

Notes

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D

2010 CA08103002Z-EN

www.eaton.com

...AC...

Control relays, multi-function display

12/35

Basic devices, expansion devices
...AC...Basic devices, expansion devices

EASY512-AC-R..

EASY618-AC-RE

EASY719-AC-RC.

EASY819-AC-RC.

Power supplyV

100/110/115/120/230/240 AC (+10/-15 %)Permissible range

Rated operational voltage

Ue

V AC

85…26485…26485…26485…264Frequency

Hz50/60 (± 5%)50/60 (± 5%)50/60 (± 5%)50/60 (± 5%)

Input current
At 115/120 V AC 60 Hz

mA

Normally 40

Normally 70

Normally 70

Normally 70

At 230/240 V AC 50 Hz

mA

Normally 20

Normally 35

Normally 35

Normally 35

Voltage dips (IEC/EN 61131-2)

ms

20

20

20

20

At 115/120 V AC

VA

Normally 5

Normally 10

Normally 10

Normally 10

At 115/230 V AC

VA

Normally 5

Normally 10

Normally 10

Normally 10

Number

8

12

12

12

Status display

LCD display (if provided)

Heat dissipation

Digital inputs 115/230 V AC

Potential isolation
From power supply

No

No

No

No

Between digital inputs

No

No

No

No

From the outputs

Yes

Yes

Yes

Yes

Potential isolation

–

–

–

Yes

Rated voltage L (sinusoidal)
On signal ”0”V AC

0 - 400 - 400 - 400 - 40On signal ”1”

V AC

79 - 264

79 - 264

79 - 264

79 - 264

Hz

50 - 60

50 - 60

50 - 60

50 - 60

6 x 0.25 (at 115 V AC,
60 Hz)6 x 0.5(at 230 V AC, 50 Hz)
2 x 4 (at 115 V AC,
60 Hz)2 x 6(at 230 V AC, 50 Hz)
4 x 0.25 (at 115 V AC,
60 Hz)4 x 0.5(at 230 V AC, 50 Hz)

6 x 0.25 (at 115 V AC,
60 Hz)6 x 0.5(at 230 V AC, 50 Hz)
2 x 4 (at 115 V AC,
60 Hz)2 x 6(at 230 V AC, 50 Hz)
4 x 0.25 (at 115 V AC,
60 Hz)4 x 0.5(at 230 V AC, 50 Hz)

Rated frequency
Input current on signal "1"
R1 to R12mA

I1 to I6

mA

I7, I8mA

I9 to I12mA

12 x 0.25 (at 115 V AC,
60 Hz)12 x 0.5(at 230 V AC, 50 Hz)
6 x 0.25 (at 115 V AC,
60 Hz)6 x 0.5(at 230 V AC, 50 Hz)
2 x 4 (at 115 V AC,
60 Hz)2 x 6(at 230 V AC, 50 Hz)

Delay time
Delay time (0 - 1/1 - 0) I1 - I6, I9 - I12,
R1 - R12
Debounce ON, 50/60 Hz

ms

80⁄66⅔

80⁄66⅔

80⁄66⅔

80⁄66⅔

Debounce OFF, 50/60 Hz

ms

20⁄16⅔

20⁄16⅔

20⁄16⅔

20⁄16⅔

Debounce ON, 50/60 Hz

ms

160⁄15080⁄66⅔

80⁄66⅔

120⁄100

Debounce OFF, 50/60 Hz

ms

100⁄100

20⁄16⅔

20⁄16⅔

40⁄33⅔

Debounce ON, 50/60 Hz

ms

80⁄66⅔

80⁄66⅔

80⁄66⅔

80⁄66⅔

Debounce OFF, 50/60 Hz

ms

20⁄16⅔

20⁄16⅔

20⁄16⅔

20⁄16⅔

Delay time I7, I8 (1 - 0)

Delay time I7, I8 (0 - 1)

Max. admissible cable length (per input)
R1 to R12m–

Normally 40––

I1 to I6m

Normally 40

Normally 40

Normally 40

Normally 60

I7, I8m

Normally 100

Normally 100

Normally 100

Normally 100

I9 to I12m–

Normally 40

Normally 40

Normally 60

Relay outputs
Notes￫ See technical data, relay outputs
For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D

2010 CA08103002Z-EN

www.eaton.com

12/36

Control relays, multi-function display

MFD-80, MFD-(AC)-CP...

Display/operating units, CPU, communication modules

MFD-80, MFD-(AC)-CP...Display/operating units, CPU, communication modules

MFD-80..

MFD-CP4…

MFD-AC-CP4..

MFD-CP10..

MFD-AC-CP8..

MFD-CP8..

GeneralStandards

EN 61000-6-1/-2/-3/-4, IEC 60068-2-6, IEC 60068-2-27

Dimensions (W x H x D)

mm

Weightkg

Mounting

86.5 x 86.5 x 21.5 (withbuttons) 86.5 x 86.5 x 20
(without buttons)
0.13

75 x 58 x 36.2

107.5 x 90 x 30

107.5 x 90 x 30

0.16

0.14

0.14

2 x 22.5 mm, display
fastened using
2° threaded fixing
rings.
Wall thickness:without top-hat rail(CPU) 1 – 6 mmwith top-hat rail
1 – 4 mm

Plug-fitted to thedisplay fixing shaft

Fitted on the fixing
shaft of the display
or on top-hat rail
according to
IEC/EN 60715, 35 mm
deep (without display)

Fitted on the fixing
shaft of the display
or on top-hat
rail according to
IEC/EN 60715, 35 mm
deep (without display)

Terminal capacity
Solid

mm2

–

–

0.2⁄4 (AWG 24 - 12)

0.2⁄4 (AWG 24 - 12)

Flexible with ferrule

mm2

–

–

0.2⁄2.5 (AWG 24 - 12)

0.2⁄2.5 (AWG 24 - 12)

Flat-blade screwdriver

mm

–

–

3.5 x 0.6

3.5 x 0.6

Max. tightening torque

Nm

–

–

–

–

°C

-25 - 55, low temperatures to IEC 60068-2-1, high temperatures to IEC 60068-2-2

Ambient climatic conditions
Operating ambient temperature
Condensation

Prevent condensation by means of suitable measures

LCD display(clearly legible)
Storage°C-5 - 50°C-40 - 70

-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing(IEC/EN 60068-2-30)
Air pressure (in operation)%

5 - 955 - 955 - 955 - 95hPa

795 - 1080

795 - 1080

795 - 1080

795 - 1080

IP65

IP20

IP20

IP20

Ambient mechanical conditions
Protection type
(IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

57 - 150

57 - 150

Shocks

18

18

18

18

mm

50

50

50

50

m

1

1

1

1

Mechanical shock resistance (IEC/EN
60068-2-27) semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Free fall, packaged (IEC/EN 60068-2-32)
Mounting position

2010 CA08103002Z-EN

Drop
heightVertical or horizontal

www.eaton.com

MFD-80, MFD-(AC)-CP...

Control relays, multi-function display

12/37

Display/operating units, CPU, communication modules

MFD-80..

MFD-CP4…

MFD-AC-CP4..

MFD-CP10..

MFD-AC-CP8..

MFD-CP8..

Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree
Electrostatic discharge (ESD),
to IEC EN 61000-4-2
Air discharge
Contact discharge
Electromagnetic
fields (RFI),
to IEC EN 61000-4-2
Radio interference suppression

–

–

–

–

kV

8

8

8

8

kV

6

6

6

6

V/m

10

10

10

10

EN 55011 Class B, EN 55022 Class B

Burst to IEC/EN 61000-4-4
Supply cables

kV

2

2

2

2

Signal cables

kV

2

2

2

2

–

0.5

1

0.5

10

10

10

10

High-energy pulses (surge)(IEC/EN 61000-4-5, Level 2)
Supply cables, symmetrical
Radiated RFI,
to IEC/EN 61000-4-6

V

Insulation resistance
Clearance in air and creepage
distances
Insulation resistance

EN 50178, UL 508, CSA C22.2, No. 142
EN 50178

Back-up/accuracy of the real-time
clock
Back-up time

–

–

1)

1)

s/day

–

–

Normally ±5 s/day(±0.5 h⁄Year)

Normally ±5 s/day(±0.5 h⁄Year)

%

–

–

± 0.02± 0.02Range “S”

ms

–

–

5

5

Range “M:S”

s

–

–

1

1

Range “H:M”

min

–

–

1

1

–

–

1010
(read ⁄ write
cycles)1010(read ⁄ write
cycles)Accuracy of the real-time clock at
55 °C
Repetition accuracy of timing relays
Accuracy of timing relay(of value)
Resolution

Retentive memory
Write cycles of the retentive memory(minimum)Notes

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8… ￫ AWB2528-1423D
1)

a

200
180
160
140
120
100
80
60
40
20
0

① Backup time (hours)② Service life (years)

25°C
55°C

0

1

2 3

4

5

6

7

8

9

10 11 12 13 14 15 16 17 18 19 20b2010 CA08103002Z-EN

www.eaton.com

12/38Control relays, multi-function display

MFD-(AC)-CP...

CPU, communication modules

MFD-(AC)-CP...CPU, communication modules

MFD-CP4..

MFD-CP8..
MFD-CP10..

MFD-AC-CP4..
MFD-AC-CP8..

24 DC (-15⁄+20 %)24 DC (-15⁄+20 %)100/110/115/120//230/240 AC(+10/-15 %)85…264

Power supply
Rated operational voltage

Ue

Permissible range

V
V AC

Permissible range

V DC

20.4…28.8

20.4…28.8

Ripple

%

≦5

≦5

–

Frequency

Hz

–

–

50⁄60 (± 5%)

Input current
At 115/120 V AC 60 Hz

mA

–

–

Normally 90

At 230/240 V AC 50 Hz

mA

–

–

Normally 60

At 24 V DC

mA

Normally 185

Normally 200

–

ms

10

10

10

Voltage dips (IEC/EN 61131-2)
Heat dissipation
At 115/120 V AC

VA

–

–

Normally 11

At 230⁄240 V AC

VA

–

–

Normally 15

At 24 V DC

W

1.5

3.4

–

1

–

–

9.6 kBaud––19.2 kBaud––

Max. 5Max. 5Max. 5

From power supply

Yes

–

–

From the connected device

Yes

–

–

Spring-loaded terminals––

Max. 1Max. 8Max. 8–1000 Kbit/s, 6 m
500 Kbit/s, 25 m
250 Kbit/s, 40 m
125 Kbit/s, 125 m
50 Kbit/s, 300 m
20 Kbit/s, 700 m
10 Kbit/s, 1000 m

1000 Kbit/s, 6 m
500 Kbit/s, 25 m
250 Kbit/s, 40 m
125 Kbit/s, 125 m
50 Kbit/s, 300 m
20 Kbit/s, 700 m
10 Kbit/s, 1000 m

Point-to-point connection
Stations
Baud rate
easy500, easy700

MBit/seasy800, MFD, EC4P
Distancem

Potential isolation

Terminal type
Power pulses
Stations

NumberData transfer rate/distance

Potential isolation
From power supply

–

Yes

Yes

From the inputs

–

–

Yes

From the outputs

–

Yes

Yes

From PC interface, memory card, easyNet,
easyLink
Bus termination (first and last station)

–

Yes

Yes

–

Yes

Yes

Terminal type–

RJ45, 8 pole

RJ45, 8 pole2010 CA08103002Z-EN

www.eaton.com

MFD-(AC)-R..., MFD-T...

Control relays, multi-function display

12/39

I/O modules

MFD-(AC)-R..., MFD-T...I/O modules

MFD-R16
MFD-RA17

MFD-AC-R16

MFD-T16
MFD-TA17

MFD-T.P..

EN 61000-6-1/-2/-3/-4,
IEC/EN 61000-4,
IEC 60068-2-6,
IEC 60068-2-27
89 x 90 x 44

EN 61000-6-1/-2/-3/-4,
IEC/EN 61000-4,
IEC 60068-2-6,
IEC 60068-2-27
89 x 90 x 25 (built-in)

EN 61000-6-1/-2/-3/-4,
IEC 60068-2-6, IEC
60068-2-27

0.15

0.14

0.14

GeneralStandards

Dimensions (W x H x D)

mm

EN 61000-6-1/-2/-3/-4,
IEC/EN 61000-4,
IEC 60068-2-6,
IEC 60068-2-27
89 x 90 x 44

Weightkg

0.15

Mounting

89 x 90 x 25 (built-in)

Fitted into the power supply unit.

Terminal capacity
Solid

mm2

0.2⁄4 (AWG 24 - 12)

0.2⁄4 (AWG 24 - 12)

0.2⁄4 (AWG 24 - 12)

0.2⁄4 (AWG 24 - 12)

Flexible with ferrulemm2

0.2⁄2.5 (AWG 24 - 12)

0.2⁄2.5 (AWG 24 - 12)

0.2⁄2.5 (AWG 24 - 12)

0.2⁄2.5 (AWG 24 - 12)

Flat-blade screwdrivermm

3.5 x 0.6

3.5 x 0.6

3.5 x 0.6

3.5 x 0.6

Solid

mm2

–

–

–

–

Flexible with ferrule

mm2

–

–

–

–

Flat-blade screwdriver

mm

–

–

–

–

Solid

mm2

0.08⁄2.5 (AWG 28 - 12)

0.08⁄2.5 (AWG 28 - 12)

0.08⁄2.5 (AWG 28 - 12)

0.08⁄2.5 (AWG 28 - 12)

Flexible with ferrule

mm20.08⁄1.5 (AWG 28 - 12)

0.08⁄1.5 (AWG 28 - 12)

0.08⁄1.5 (AWG 28 - 12)

0.08⁄1.5 (AWG 28 - 12)°C-25 - 55, low temperatures to IEC 60068-2-1, high temperatures to IEC 60068-2-2Power supply

Data cable

Ambient climatic conditions
Operating ambient temperature
Condensation

Prevent condensation by means of suitable measures

LCD display (clearly legible)°C

Storage°C-40 - 70

-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing(IEC/EN 60068-2-30)
Air pressure (in operation)%

5 - 955 - 955 - 955 - 95hPa

795 - 1080

795 - 1080

795 - 1080

795 - 1080

Pollution degree

2

2

2

2

Protection type (IEC/EN 60529, EN50178,
VBG 4)
Vibrations (IEC/EN 60068-2-6)

IP20

IP20

IP20

IP20

Ambient mechanical conditions

Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

57 - 150

57 - 150

Shocks

18

18

18

18

mm

50

50

50

50

m

1

1

1

1

Mechanical shock resistance(IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Free fall, packaged (IEC/EN 60068-2-32)

DropheightMounting position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Electrostatic discharge (ESD),
to IEC EN 61000-4-2
Air discharge

kV

8

8

8

8

Contact discharge

kV

6

6

6

6

Electromagnetic fields (RFI),
to IEC EN 61000-4-2
Radio interference suppression

V/m

10

10

10

10

EN 55011 Class B, EN 55022 Class B

Burst to IEC/EN 61000-4-4
Supply cables

kV

2

2

2

2

Signal cables

kV

2

2

2

2

Power pulses (surge) (IEC/EN 61000-4-5)

kV

2 (supply cables,
symmetrical)

2 (supply cables,
symmetrical)

2 (supply cables,
symmetrical)

Power pulses (surge), to IEC/EN 61000-4-5

kV

0.5 (supply cables,
symmetrical)

0.5 (supply cables,
symmetrical)

0.5 (supply cables,
symmetrical)

Radiated RFI, to IEC/EN 61000-4-6

V

10

10

10

2 (supply cables
symmetrical,
MFD-AC-CP8..)
0.5 (supply cables,
symmetrical,
MFD-CP8..)
10

Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

MFD-(AC)-R..., MFD-TI/O modules

2010 CA08103002Z-EN

www.eaton.com

12/40Multi-function display

MFD-(AC)-R..., MFD-T

I/O modules

MFD-R16
MFD-RA17

MFD-T16
MFD-TA17

MFD-T...P...

Number12

12

6

Inputs can be used as analog inputs

4 (I7, I8, I11, I12)

4 (I7, I8, I11, I12)

2 (I11, I12)

From power supply

No

No

No

Between digital inputs

No

No

No

From the outputs

Yes

Yes

Yes

Yes

Yes

Yes

MFD-AC-R16

Digital inputs 24 V DC

Potential isolation

From PC interface, memory card,easy NET, easyLink
Rated operating voltage

Ue

V DC

24

24

24

On signal ”0”

Ue

V DC

On signal ”1”

Ue

V DC

< 5.0 (I1 - I6, I9 - I10),< 8 (I7, I8, I11, I12)
> 15.0 (I1 - I6, I9 - I10),> 8.0 (I7, I8, I11, I12)

< 5.0 (I1 - I6, I9 - I10),< 8 (I7, I8, I11, I12)
> 15.0 (I1 - I6, I9 - I10),> 8.0 (I7, I8, I11, I12)

< 5.0 (I1 - I4),
< 8.0 (I11, I12)
>15.0 (I1 - I4),
> 8.0 (I11, I12)

Input current on signal "1"
I1 to I6mA

3.3 (at 24 V DC)

3.3 (at 24 V DC)–

I1 to I4mA––

3.3 (at 24 V DC)

I7, I8mA

2.2 (at 24 V DC)

2.2 (at 24 V DC)–

I9, I10mA

3.3 (at 24 V DC)

3.3 (at 24 V DC)–

I11, I12mA

2.2 (at 24 V DC)

2.2 (at 24 V DC)

2.2 (at 24 V DC)

Debounce ON

ms

20

20

20

Debounce OFF

ms

Normally 0.1 (I1 - I4), normally 0.25 (I5 - I12)

Debounce ON

ms

20

20

20

Debounce OFFmsmNormally 0.1 (I1 - I4),
normally 0.4 (I5, I6, I9,
I10), normally 0.2(I7, I8, I11, I12)
100

Normally 0.1 (I1 - I4),
normally 0.2 (I11, I12)

Cable length (unshielded)

Normally 0.1 (I1 - I4),
normally 0.4 (I5, I6, I9,
I10), normally 0.2(I7, I8, I11, I12)100
4 (I1, I2, I3, I4)

4 (I1, I2, I3, I4)

4 (I1, I2, I3, I4)

<3

<3

<3

SquareSquareSquare2 (I1 + I2, I3 + I4)

2 (I1 + I2, I3 + I4)

2 (I1 + I2, I3 + I4)

≦3

≦3

≦3

Pulse shape

SquareSquareSquareSignal offset

90°

90°

90°

4 (I1, I2, I3, I4)

4 (I1, I2, I3, I4)

4 (I1, I2, I3, I4)

<3

<3

<3

SquareSquareSquare

< 20

< 20

< 20

Delay time from 0 to 1

Delay time from 1 to 0100

Frequency counters
NumberCounter frequency

kHz

Pulse shape
Incremental counters
NumberCounter frequency

kHz

High-speed counter inputs
NumberCounter frequency

kHz

Pulse shape
Cable length, shieldedmDigital inputs 115/230 V AC
NumberStatus display
Potential isolation
From power supply
Between digital inputs
From the outputs
From PC interface, memory card,easyNet, easyLink
Rated voltage L (sinusoidal)
On signal ”0”
On signal ”1”
Rated frequency
Input current on signal "1"
I1 to I12

Delay time
Delay time (0 - 1⁄1 - 0) I1 - I12, 50⁄60 Hz
Max. admissible cable length (per input)
I1 to I122010 CA08103002Z-EN

www.eaton.com

12
LCD display(if provided)
No
No
Yes
Yes

V AC
V AC
Hz

0 - 4079 - 264
50 - 60

mA

12 x 0.2 (at 115 V AC,
60 Hz), 12 x 0.5(at 230 V AC, 50 Hz)
10⁄100m

Normally 60

MFD-R..., MFD-T...

Control relays, multi-function display

12/41

I/O modules
MFD-R..., MFD-T...I/O modules

MFD-R...
MFD-T...
Analog inputs
NumberPotential isolation
From power supply
From the digital inputs
From the outputs
From PC interface, memory card,easyNet, easyLink
Input type
Signal range
Resolution, analog
Resolution, digital
Resolution
Input impedance
Accuracy of actual value
Two MFD devices
Within a single device
Conversion time analog/digital
Input current
Cable length shielded

4 (I7, I8, I11, I12)
2 (I11, I12) for
MFD-T(A)P
No
No
Yes
Yes

V DC
V
V
Bit
kΩ

DC voltage
0 - 100.01
0.01
10 (value 0 - 1023)
11.2

%
%
ms
mA
m

±3
±2%
Each CPU cycle<1< 30

MFD-RA17
MFD-TA17

MFD-TAP

1

1

No
No
Yes
Yes

No
No
Yes
Yes

V DC
Bit

DC voltage
0 - 10
0.01
1
Yes
0.01
10 (value 0 - 1023)

V DC
μs

–
100

DC voltage
0 - 10
0.01
1
Yes
0.01
12 (value 0 - 4095)
at QA01, MD
0.1, 0.01, 0.001 at MD
100

%
%
ms

2
1
Each CPU cycle2
1Each CPU cycle

Analog outputs
NumberPotential isolation
From power supply
From the digital inputs
From the digital outputs
From PC interface, memory card,easyNet, easyLink
Output type
Signal range
Max. output current
Load resistanceOverload and short-circuit protection
Resolution, analog
Resolution, digital
Resolution, digital
Recovery time
Accuracy-25 °C - 55 °C
25CConversion time, analog/digital

V DC
A
kΩ

MFD-TP, MFD-TAP
Analog input temperature resistance Pt100 or Ni1000 sensors
NumberInput type resistance sensor
Platinum sensor Pt100 according to DIN EN 60751, IEC 751
Nickel sensor Ni1000 according to DIN 43760
Temperature range
Pt100, range A, selectable
Ni1000, range A, selectable
Pt100, range B
Potential isolation
From power supply
From the digital inputs
From the outputs
From PC interface, memory card, easyNet, easyLink
Resolution digital, scaling per sensor
With operands "IA" and "MD", selectable under scaling
With operand "MD", selectable under scaling
Measurement value resolution analog/digital
Measuring current
Damage limit (in the case of a wiring error)
Measurement method
Accuracy (without EMC interference)
Two MFD devices one above the otherPt100 RTD (offset error, linearity error, repetition accuracy,
temperature dependency of the device included)
Ni1000 RTD (offset error, linearity error, repetition accuracy,
temperature dependency of the device included)
Conversion time analog/digital
Without sampling time setting, selectable per sensor
With sampling time (adjustable), selectable per sensor
Additional measurement aids
Filtering (software), analog input signal smoothing (Pt1 characteristic),
only with set sampling time, selectable for each detector
Filter for suppression of certain frequencies and their multiples
Diagnostics
Card diagnostic
Wire break diagnostic per sensor
Wire break diagnostic per sensor
Below lower measurement range
Upper measuring range limit of sensor exceeded
Cable length shielded

2 x Pt 100 or 2 x Ni1000 (according to part no.)MFD-TP12-PT...
MFD-TP12-NI...
°C, (°F)°C, (°F)°C, (°F)-40 - +90, (-40 - 194); 0 - 250, (32 - 482); 0 - 400, (32 - 752)
-40 - +90, (-40 - 194); 0 - 250, (32 - 482)
-0 - +8500, (32 - 1562); -200 - 200, (-328 - 392)
No
No
Yes
Yes

Bit
°C, (°F)
Bit
mA

12 (0 - 4095)
1, 0.1, (1), (0.1)
Depending upon the scaling< 1.6
Apply external voltage
Two or three wire per sensor, selectable by connection of sensor%%

Normally 1; maximal 1.6 (Pt), 1.2 (Ni)
± 0.8 of measurement range%± 0,6 of measurement range

ms
ms

200
200 - 65535
YesHz

50, 60, 250, 500

m

Yes
Yes
Yes
Yes
Yes
< 10

2010 CA08103002Z-EN

www.eaton.com

12/42Control relays, multi-function display

...T..., MFD...T...

...T..., MFD...T...

Control relays, multi-function display

Basic devices, expansion devices

12/43

Basic devices, expansion devices

...T..., MFD...T...Basic devices, expansion devices

Transistor outputs
NumberRated operating voltage
Permissible range
RippleSupply current
On signal ”0”
On signal ”1”

Short-circuit tripping current for Ra ≦ 10 mΩ
Total short-circuit current
Peak short-circuit current
Thermal cutout
Max. operating frequency at constant resistive load
RL < 100 kΩ (dependent on program and load)
Parallel connection of outputs
With resistive load, inductive load with external
suppressor circuit, combination within a group
Number of outputs
Max. total current
Status indication of the outputs
Inductive load to EN 60947-5-1
Without external suppressor circuit
T0.95 = 1 ms, R = 48 Ω, L = 16 mH
Utilization factor
Duty factor
Max. operating frequency
f = 0.5 Hz (max. ED = 50 %)DC-13, T0.95 = 72 ms, R = 48 Ω, L = 1.15 H
Utilization factor
Duty factor
Max. operating frequency
f = 0.5 Hz (max. ED = 50 %)T0.95 = 15 ms, R = 48 Ω, L = 0.24 H
Utilization factor
Duty factor
Max. operating frequency
f = 0.5 Hz (max. ED = 50 %)With external suppressor circuit
Utilization factor
Duty factor
Max. switching frequency, max.
duty factor
Notes

2010 CA08103002Z-EN

EASY512-DC-T..

EASY410-DC-TE
EC4E-221-DT…

EASY620-DC-TE

EASY721-DC-T..

EASY8..-DC-T..

MFD-T..

Ue
Ue

V DC
V DC
%

2
24
20.4 - 28.8
≦54
24
20.4 - 28.8
≦54
24
20.4 - 28.8
≦58
24
20.4 - 28.8
≦58
24
20.4 - 28.8
≦58
24
20.4 - 28.8
≦54
24
20.4 - 28.8
≦5

Normally⁄max.
Normally⁄max.

mA

24V/2A

9/16

9/16

18/32

18/32

18/32

18/32

mA

12/22

12/22

12/22

24/44

24/44

24/44

24 /44

Protection against polarity reversal

Potential isolation
Potential isolation from power supply, inputs
From PC interface, memory card, easyNet, easyLink
From the inputs
Rated operational current on signal "1" DC
Lamp load without Rv
Residual current on signal "0" per channel
Max. output voltage
On "0" at external load < 10 MΩ
On “1” at Ie = 0.5 A
Short-circuit protection

EASY4…-DC-ME

Ie

A
W
mA
V
V

A
A
A
Ops/h

Max.
A

Yes (Caution: A short circuit will result if 0 V or GND is applied to the
outputs in the event that the supply voltage is connected to the wrong
poles.)Yes (Caution: A short circuit will result if 0 V or GND is applied to the outputs in the event that the supply voltage is connected to the wrong
poles.)

No
Yes
–
1
5
< 0.1

Yes
Yes
–
Max. 0.5
5
< 0.1

Yes
Yes
–
Max. 0.5
5
< 0.1

Yes
Yes
–
Max. 0.5
5
< 0.1

Yes
Yes
–
Max. 0.5
5
< 0.1

Yes
Yes
Yes
Max. 0.5
3 (Q1 - Q4) 5 (Q5 - Q8)
< 0.1

Yes
–
Yes
Max. 0.55 (Q1 - Q4)
< 0.1

2.5
U = Ue -1 V
Yes, thermal (analysis
via diagnostics input
R16)
1.4 ≦ Ie ≦ 4
8
16
Yes
40000

2.5
U = Ue -1 V
Yes, thermal (analysis
via diagnostics input
I16, I15; R15, R16)
0.7 ≦ Ie ≦ 2 per output
8
16
Yes
40000

2.5
U = Ue -1 V
Yes, thermal (analysis
via diagnostics input
R16)
0.7 ≦ Ie ≦ 2 per output
8
16
Yes
40000

2.5
U = Ue -1 V
Yes, thermal (analysis via
diagnostics input I16, I15; R15,
R16)
0.7 ≦ Ie ≦ 2
16
32
Yes
40000

2.5
U = Ue -1 V
Yes, thermal (analysis via
diagnostics input I16, I15; R15,
R16)
0.7 ≦ Ie ≦ 2 per output
16
32
Yes
40000

2.5
U = Ue -1 V
Yes, electronic (Q1 – Q4), thermal(Q5 – Q8), (analysis via diagnostics
input I16, I15)
0.7 ≦ Ie ≦ 2 per output
16
32
Yes
40000

2.5
U = Ue -1 V
Thermal (Q1 – Q4), (analysis via
diagnostics input I16)

Q1 and Q2Group 1: Q1 to Q4

Group 1: Q1 to Q4

Group 1: S1 - S4Group 1: Q1 to Q4
Group 1: Q1 to Q4
Group 2: S5 - S8Group 2: Q5 to Q8Group 2: Q5 to Q84442 (Attention! Outputs must be activated simultaneously and for the same duration)24
42 (Attention! Outputs must be activated simultaneously and for the same
duration)
LCD display (if provided)

0.7 ≦ Ie ≦ 2 per output
8
16
Yes
40000

Group 1: Q1 to Q4
4

LCD display (if provided)g% DF
Operations

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

g
% DF
Operations

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

g
% DF
Operations

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

0.25
100
1500

g
% DF
Operations

1
1
100
100
Depending on the suppressor circuit

1
100

1
1
100
100
Depending on the suppressor circuit

1
100

1
100

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8…
￫ AWB2528-1423D, MFD-Titan ￫AWB2528-1480D

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

12/44Control relays, multi-function display

...R..., MFD...R...

Basic devices, expansion devices
...R..., MFD...R...Basic devices, expansion devices

EASY202-RE

EASY410-DC-RE
EASY512-..-R..
MFD-R.. MFD-AC-R..

EASY618/719-..-R..
EASY8..-…-R…

Number2

4

6

Outputs in groups of

2

1

1

Parallel switching of outputs to increase performance

Not permissible

Not permissible

Not permissible

Protection of an output relay

Miniature circuit-breaker B16 or fuse 8 A (slow)

Relay outputs

Potential isolation
From power supply

Yes

Yes

Yes

From the inputs

Yes

Yes

Yes

Electrical isolation in groups

Yes

Yes

Yes

Safe isolation according to EN 50178

V AC

300

300

300

Basic insulation

V AC

600

600

600

x 106

10

10

10

Lifespan, mechanical

Operations

Contacts
Conventional thermal current (10 A UL)

A

8

8

8

Recommended for load: 12 V AC/DC

mA

> 500

> 500

> 500

Short-circuit proof p.f. = 1, characteristic B16 at 600 A

A

16

16

16

Short-circuit proof p.f. = 0.5 - 0.7; characteristic B16 at 900 A

A

16

16

16

Rated impulse withstand voltage Uimp contact coil

kV

6

6

6

Ue

V AC

250

250

250

Ui

V AC

250

250

250

Safe isolation to EN 50178 between coil and contact

V AC

300

300

300

Safe isolation to EN 50178 between two contacts

V AC

300

300

300

Rated operating voltage
Rated insulation voltage

Making capacity
AC-15, 230 V AC, 3 A

Operations

300000300000300000DC-13, 24 V DC, 5 A, 0.1 Hz

Operations

200000200000200000AC–-15, 250 V AC, 3 A (600 ops./h)Operations

300000300000300000DC-13, L/R ≦ 150 ms, 24 V DC, 1 A (500 S/h)Operations

2000002000002000001000 W at 230/240 V AC

Operations

25000

25000

25000

500 W at 115/120 V AC

Operations

25000

25000

25000

With upstream electrical device

Operations

25000

25000

25000

UncompensatedOperations

25000

25000

25000

Operations

25000

25000

25000

Breaking capacity

Filament bulb loadFluorescent lamp loadFluorescent lamp load 10 x 58 W at 230/240 V AC

Fluorescent lamp load 1 x 58 W at 230/240 V AC, conventionallycompensatedSwitching frequency
Mechanical operations

x 106

10

10

10

Switching frequency

Hz

10

10

10

Resistive load/lamp load

Hz

2

2

2

Inductive load

Hz

0.5

0.5

0.5

Continuous current at 240 V AC

A

10

10

10

Continuous current at 24 V DC

A

8

8

8

UL/CSAAC
Control circuit rating codes (utilization category)

B 300 Light Pilot Duty

Max. rated operational voltage

V AC

300

300

300

Max. thermal continuous current p.f. = 1 at B 300

A

5

5

5

Max. make/breakp.f. ≠ capacity 1 at B 300

VA

3600/360

3600/360

3600/360

DC
Control circuit rating codes (utilization category)

R 300 Light Pilot Duty

Max. rated operational voltage

V DC

300

300

300

Max. thermal continuous current at R 300

A

1

1

1

Max. make/break capacity
at R 300

VA

28/28

28/28

28/28

Notes

2010 CA08103002Z-EN

For additional technical data EASY5… and EASY7… ￫ AWB2528-1508D, EASY8…
￫ AWB2528-1423D, MFD ￫ AWB2528-1480D

www.eaton.com

...ASI/DP/CO/DN

Control relays, multi-function display

12/45

Bus modules
...ASI/DP/CO/DNBus modules

EASY205-ASI

EASY221-CO

EASY204-DP

EASY222-DN

EN 55011, EN 55022, IEC/EN 61000-4,
EN 50325
EN 55011, EN 55022, IEC/EN
61000-4, IEC 62026
35.5 x 90 x 58 (2 space units)
0.15

GeneralStandards

Dimensions (W x H x D)

mm

EN 55011, EN 55022, IEC/EN 61000-4,
IEC 62026
EN 55011, EN 55022, IEC/EN
61000-4, IEC 61158
35.5 x 90 x 58 (2 space units)

Weight

kg

0.12

0.15

Top-hat rail IEC/EN 60715, 35 mm or screw fixing using fixing brackets ZB4-101-GF1(accessories).

Mounting
Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

3.5 x 0.8

Max. tightening torque

Nm

0.6

0.6

°C

-25…55, low temperatures to IEC 60068-2-1, high temperatures to IEC 60068-2-2

Ambient climatic conditions
Operating ambient temperature

Prevent condensation by means of suitable measures

Condensation
Storage°C-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 955 - 95Air pressure (in operation)hPa

795 - 1080

795 - 1080

IP20

IP20

Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

Shocks

18

18

mm

50

50

m

1

1

Vertical or horizontal

Vertical or horizontal

II/2

II/2

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Mounting position
Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree
Electrostatic discharge (ESD), to IEC EN 61000-4-2
Air discharge

kV

8

8

Contact discharge

kV

6

6

10

10

Electromagnetic fields (IEC/EN 61000-4-3, RFI)

V/m

EN 55011 Class B, EN 55022 Class B

Radio interference suppression
Burst to IEC/EN 61000-4-4
AS-Interface cables

kV

2

–

Supply cables

kV

–

2

Signal cables

kV–

Power pulses (surge), to IEC/EN 61000-4-5

kV–

Radiated RFI, to IEC/EN 61000-4-6

V

10

2
0.5 (supply cables,
symmetrical)

0.5 (supply cables, symmetrical)
10

Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

EN 501782010 CA08103002Z-EN

www.eaton.com

12/46

Control relays, multi-function display

...ASI/DP/CO/DN

Bus modules

EASY205-ASI

EASY204-DP

EASY221-CO

EASY222-DN

26.5 - 31.6

24 (-15/+20 %)24 (-15/+20 %)24 (-15/+20 %)20.4…28.8

20.4…28.8

20.4…28.8

Power supply
Rated operational voltage

UeV

Permissible range

V DC

Total power consumption of the
AS interface
Ripple

mA

≦ 30

–

–

–

%

–

≦5

≦5

≦5

Max. current consumption (at 24 V DC)

mA–

Normally 200

Normally 200

Normally 200

Voltage dips (IEC/EN 61131-2)

ms

–

10

10

10

Heat dissipation at 24 V DC

W

–

4.8

4.8

4.8

AS-Interface
protection against polarity reversal
AS-Interface profile

Yes

–

–

–

7F (hex)–––

Slave address

0 - 31

Addressing unit interface

3.5 mm socket

–

–

–

Power supply

–

Yes

Yes

Yes

SupplyPower: green

RUN LED (RUN): green

LED display

Com Error: red

Power LED (POW):
green
LED PROFIBUS-DP(BUS): red

Module status LED(MS): green
Network status LED(NS): red/green

S1 → input 0
S2 → input 1
S3 → input 2
S4 → input 3
R1 ← outputs 0R2 ← outputs 1
R3 ← outputs 2
R4 ← outputs 3R5 ← PARAMETEROUTPUT 0
R6 ← PARAMETEROUTPUT 1
R7 ← PARAMETEROUTPUT 2
R8 ← PARAMETEROUTPUT 3––

Terminal type–

SUB-D 9 pole, socket

RJ45

Potential isolation–

Protection against polarity reversal

LED indicators

LED ERROR (ERR): red

I/O addresses
easy700/easy800 contact and coil
↔ AS-Interface–

Network

Function–

5 pole, pluggable screw
terminal
Between bus and power supply (simple), between bus and power supply andeasy base unit (safe isolation)
PROFIBUS-DP slave
CANopen slave
DeviceNet slave

Interface

–

RS485

CAN

CAN

Bus protocol

AS-Interface

PROFIBUS-DPCANopenDeviceNet

Baud rates–

Bus terminating resistors–

Automatic search up to
12 MBit⁄s
Can be connected via
plug

Bus addresses–

1 - 126 can beaddressed via easybase unit with display or
via EASY-SOFT

Automatic search up to
1 MBit⁄s
Separate external bus
termination
required (120 Ω)
1 - 127 can beaddressed via easy
basic units with display
or via easySoft

Automatic search up to
500 kBit⁄s
Separate external bus
termination
required (120 Ω)
0 - 63 can beaddressed via easy
basic units with display
or via easySoft

Cyclical–All data R1 - R16, S1 - S8

Acyclical–

Read⁄write, time, day, daylight saving time
All parameters of the EASY function relay

Services2010 CA08103002Z-EN

www.eaton.com

EASY209-SE, EASY256-HCI

Control relays, multi-function display

12/47

Ethernet coupling unit, upstream device
EASY209-SE, EASY256-HCIEthernet coupling unit, upstream device

EASY209-SE

EASY256-HCI

GeneralStandards

EN 55011, EN 55022, IEC/EN 61000-4, EN 50178

Dimensions (W x H x D)

mm

35.5 x 90 x 58 (2 space units)35.5 x 90 x 58 (2 space units)

Weight

kg

0.15

0.15

NumberTop-hat rail IEC/EN 60715, 35 mm or screw fixing using fixing brackets
ZB4-101-GF1 (accessories).
–
6

Current increase 115/230 V AC

mA

–

4/6

Delay time

ms

–

40/37

Cable length

m

–

100

Parallel switching of outputs to increase performance–

Type of resistance–Several possible (Off-delay extended
depending on the number of parallel
channels)
Capacitive

Mounting
Channels
Voltage range for Ue

0 - 264

Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

3.5 x 0.8

Max. tightening torque

Nm

0.6

0.6

Solid

mm2

0.25/1.5 (AWG 24/16)–

Flexible with ferrule

mm20.14/ 1 (AWG 26/17)–°C-25…55Storage°C-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 955 - 95Air pressure (in operation)hPa

795 - 1080

795 - 1080

IP20

IP20

Data cable

Ambient climatic conditions
Operating ambient temperature

Condensation-25…55, low temperatures to
IEC 60068-2-1, high temperatures to
IEC 60068-2-2
Prevent condensation by means of suitable measures

Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

Shocks

18

18

mm

50

50

m

1

1

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Mounting position

Vertical or horizontal

Electromagnetic compatibility (EMC)
Overvoltage category/pollution degree

II/2

II/2

Electrostatic discharge (ESD), to IEC EN 61000-4-2
Air discharge

kV

8

8

Contact discharge

kV

6

6

RS-232 line unshielded: 3,
shielded: 10
EN 55011 Class B, EN 55022 Class B

10Electromagnetic fields (IEC/EN 61000-4-3, RFI)

V/mRadio interference suppression
Burst to IEC/EN 61000-4-4
AS-Interface cables

kV

–

–

Supply cables

kV

2

–

Signal cables

kV

–

–

Ethernet interface cable

kV

2

–

COM interface cable

kV

2

–

Power pulses (surge), to IEC/EN 61000-4-5

kV

1 (supply cables, symmetrical)

Radiated RFI, to IEC/EN 61000-4-6

V

RS-232 line unshielded: 3,
shielded: 10

2 (supply cables, symmetrical,
EASY…DC)
10

Insulation resistance
Clearance in air and creepage distances

EN 50178, UL 508, CSA C22.2, No. 142

Insulation resistance

EN 50178

EN 501782010 CA08103002Z-EN

www.eaton.com

12/48Control relays, multi-function display

EASY209-SE, EASY256-HCI

Ethernet gateway
EASY209-SE, EASY256-HCIEthernet gateway

EASY209-SE
Power supplyV

24 (-15/+20 %)Permissible range

Rated operational voltage

Ue

V DC

20.4…28.8

Ripple%≦5

Max. current consumption (at 24 V DC)

mA

Normally 65

Voltage dips (IEC/EN 61131-2)

ms–

Heat dissipation at 24 V DC

W

1.7

Protection against polarity reversal
Power supply

Yes

LED indicators
SupplyFront-LED Power: ON

LED display

Front-LED COM active: flashes

RJ-45 socket, top

No Activity: OFF, Amber: Half Duplex, Green: Full Duplex

RJ-45 socket, bottom

No Link: OFF, Amber: 10 MBit/s, Green: 100 MBit/s

Gateway ready for operation–

Power supply SmartWire (contactor)–

Network Status (easyNet/CANopen)
Status SmartWire

–
LED

–

Reset

Front: per pushbuttons > 2s

Strain relief

By cable tie in fastener

Network
Terminal type–

Potential isolation–

Bus protocol–

Bus terminating resistors–

Bus addresses

Default settings Ethernet:
IP adress 0.0.0.0 SUBNET screen: 255.255.0.0 coupling unit
address 0.0.0.0 remote address 0.0.0.0

2010 CA08103002Z-EN

www.eaton.com

...POW

Control relays, multi-function display

12/49

Switched-mode power supply units
...POWSwitched-mode power supply unitsEASY200-POW

EASY400-POW

EASY500-POW

EASY600-POW

EASY430-POW
GeneralStandards

EN 55011, EN 55022, IEC/EN 61000-4, IEC 60068-2-6, IEC 60068-2-27, EN 61000-6-2

Dimensions (W x H x D)

mm

Weightkg

Mounting

35.5 x 90 x 58
(2 space units)
0.1

71.5 x 90 x 58
(4 space units)
0.25

71.5 x 90 x 58
(4 space units)
0.28

107.5 x 90 x 58
(6 space units)
0.3

Top-hat rail IEC/EN 60715, 35 mm or screw fixing using fixing brackets ZB4-101-GF1(accessories).

Terminal capacity
Solid

mm2

0.2 - 4 (AWG 22 - 12)

Flexible with ferrulemm2

0.2 - 2.5 (AWG 22 - 12)

Flat-blade screwdrivermm

3.5 x 0.8

3.5 x 0.8

3.5 x 0.8

3.5 x 0.8

Max. tightening torque

Nm

0.6

0.6

0.6

0.6

°C

-25…55, lowtemperatures to
IEC 60068-2-1,
high temperatures
to IEC 60068-2-2-25…55, lowtemperatures to
IEC 60068-2-1,
high temperatures
to IEC 60068-2-2-25 - 55, lowtemperatures to
IEC 60068-2-1,
high temperatures
to IEC 60068-2-2;-25 - 45 to UL/CSA
Prevent condensation by means of suitable measures-25…55, lowtemperatures to
IEC 60068-2-1,
high temperatures
to IEC 60068-2-2

Ambient climatic conditions
Operating ambient temperature

Condensation
Storage°C-40 - 70

-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 - 955 - 955 - 955 - 95Air pressure (in operation)hPa

795 - 1080

795 - 1080

795 - 1080

795 - 1080

Max. installation altitude above sea level,observe derating at higher altitudes

m

2000

2000

2000

2000

Pollution degree

2

2

2

2

Protection type (IEC/EN 60529, EN50178, VBG 4)

IP20

IP20

IP20

IP20

Ambient mechanical conditions

Vibrations (IEC/EN 60068-2-6)
Constant amplitude 0.15 mm

Hz

10 - 57

10 - 57

10 - 57

10 - 57

Constant acceleration, 2 g

Hz57 - 150

57 - 150

57 - 150

57 - 150

Shocks

18

18

18

18

mm

50

50

50

50

m

1

1

1

1

Vertical or
horizontal

Vertical or
horizontal

Horizontal,
terminals at top

Horizontal,
terminals at top

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Free fall, packaged (IEC/EN 60068-2-32)

DropheightMounting position
Electromagnetic compatibility (EMC)
Electrostatic discharge (ESD), to IEC EN 61000-4-2
Air discharge

kV

8

8

8

8

Contact discharge

kV

6

6

6

6

V/m

10

10

10

10

Electromagnetic fields (RFI), to IEC EN 61000-4-2

EN 55011 Class B; EN 55022 Class B, EN 50081-2 Class B

Radio interference suppression
Burst pulses (IEC/EN 61000-4-4, level 3)kV

2Power pulses (surge) (IEC/EN 61000-4-5)

kV

2 (supply cables, symmetrical)

Power pulses (surge) (IEC/EN 61000-4-5,
Level 2), 24 V
Radiated RFI, to IEC/EN 61000-4-6

kV

0.5 (output cables, symmetrical)

V

10Surge voltage (EN 50 178), 24 V

kV

6

2

2

2

10

10

10

6

6

6

Insulation resistance
Clearance in air and creepage distances

EN 50178

Insulation resistance

EN 50178

Protection class Uout to Uin

Class II to IEC 60536

Potential isolation primary/secondaryYes, SELV (VDE 0100 Part 410; IEC 60364-4-41, HD 384.4.41 S2) EN 60950, EN 50178

Input voltage
Rated input voltage AC

V

Protective switches AC
Rated input voltage DC

100/120/230/240 (-15/+10 %)FAZ-C1/1 or FAZ-B6/1

V

DC protective switches

85 - 264

85 - 264

85 - 264

85 - 264

FAZ-C2/1-DC

FAZ-C2/1-DC

FAZ-C2/1-DC

FAZ-C2/1-DC

Voltage range

V AC

85 - 264

85 - 264

85 - 264

85 - 264

Frequency range

Hz

47 - 63

47 - 63

47 - 63

47 - 63

Mains failure bridging 115/230 V (IEC/EN 61000-4-11)

ms> 10/> 20> 20/> 40> 20/> 40> 20/> 40

Fuse 115/230 V

A

1.5 slow

2/1 time delay

2/1 time delay

2/1 time delay

2010 CA08103002Z-EN

www.eaton.com

12/50Control relays, multi-function display

...POW

Switched-mode power supply unitsEASY200-POW

EASY400-POW

EASY500-POW

EASY600-POW

EASY430-POW
Rating data
Efficiency

%

> 80

> 83

> 85

> 85

Power consumption

W

Normally 7

Normally 35

Normally 70

Normally 115

Heat dissipation

W

Normally 1

Normally 5

Normally 10

Normally 18

Rated input current value 115/230 V ACA

Approx. 0.17/0.05

Approx. 0.6/0.3

Approx. 0.8/0.4

Approx. 1/0.5

Inrush current at 230 C 25 V

A

<5

< 18

< 30

< 30

Rated value

V DC

12

–

–

–

Tolerance

%

±4

–

–

–

Switching peaks

mVSS

<7

–

–

–

Effect of input voltage

%

±1

–

–

–

Effect with 25 – 100 % load change

%

±1

–

–

–

Rated value

V DC

24

24

24

24

Tolerance

%

±3

±3

±3

±3

Switching peaks 115/230

mVSS< 50/30

<5

<5

<5

Effect of input voltage

%

±1

±1

±1

±1

Effect with 25 – 100 % load change

%

±1

±2

±2

±2

–

–

Yes

Yes

Input current

Output voltage
12 V DC (reference voltage)

24 V DCCan be connected in parallel to increase power

Yes

Output current
12 V DC (reference voltage)
Output currentmA

0 - 20–––Effectiveness of current limitation

mA

20

–

–

–

Reduction of output voltage after
current limitation
Overload proof

V

< 12

–

–

–

Yes, by current
limitation permanently short-circuit
proof
Yes

–

–

–

–

–

–

Proof against sustained short circuit
24 V DC
Output currentA0 - 0.35

0 - 1.25

0 - 2.5

0 - 4.2

Effectiveness of current limitation

A

> 0.4

> 1.5

> 2.8

> 4.8

Reduction of output voltage after
current limitation
Overload proof

V

–

< 18

< 18

< 18

Yes, by current limitation

Proof against sustained short circuit

Yes, hickup-mode

Yes, hickup mode, approx. 2 Hz

Special load conditions
Lamp load, cold, 24 V DC

W

2

10

–

–

Base load present

W

1

5

–

–

Behavior in the event of emergency switch off in 24 V
circuit, switch off using contactor (contactor load,no damage)

W

6

30

–

–

V DC

24

24

24

24

Indication
Indication of output voltage(LED, continuous green light = OK)2010 CA08103002Z-EN

www.eaton.com

..., MFD-80...

Control relays, multi-function display

12/51

Basic devices, expansions, display/operating unit

Dimensions
..., MFD-80...Basic devices, expansions, display/operating uniteasy200

easy400
easy500

7.5

easy600
easy700

10.75

50

16.25

75

16.25

110

90

102

110

90

M4

102

110

90

102

M4

M4

7.5

107.5

35.75

35.5

71.5

easy200
easy400
easy500

easy800

easy600
easy700

16.25

75

16.25

110

90

102

45

45

M4

4.5
4.5

48.5
47.5

70.5

56.5

72

58

107.5

MFD-80

MFD-80-B

28.25

30

28.25

20

13.7

30

30

86.5

32

22.3

22.3 +0.4

17

MFD-80...

MFD-CP...

MFD-CP...

21.5

13.7

62
86.5

2010 CA08103002Z-EN

www.eaton.com

12/52Control relays, multi-function display

MFD...

Central processing unit, communication module, inputs/outputs modules

MFD...Central processing unit, communication module, inputs/outputs modules

MFD-R... , MFD-T... , MFD-AC-R16

90

90

MFD-CP... , MFD-AC-CP...

88.1

38.75

30 g0.2

16.25

75

38.75

19

25

4.5
29.5

16.25

107.5

58
75

107.5

88.2
20

43.2
33.7

2010 CA08103002Z-EN

www.eaton.com

86.5

86.5

MFD-80... + MFD-CP4

90

MFD-80... + MFD-CP... + MFD-R.../MFD-T...
MFD-80... + MFD-AC-CP... + MFD-AC-R16

29.3

36.2
65.5

MFD..., SKF...

Control relays, multi-function display

12/53

Accessories

MFD..., SKF...Accessories

Hinged inspection windows
SKF-FF4

SKF-FF6
16

76

76

16

25

94

25

130

Top-hat rail adapter for hinged inspection window
SKF-HA

66

48

11

82

Protective cover

MFD-XM-80

MFD-XS-80

88.5

95

Protective diaphragm

22.5

88.5

25

86.5

Mounting rail
MFD-TS-144

30 g0.2

35

23.75

24

60

38.75

142.5

2010 CA08103002Z-EN

www.eaton.com