Darwin Technology
The easy way to connect

SmartWire Darwin communication system
Connect don´t wire
For the manufacturer of machinery and installations, nothing is more important thanfinding the balance between maximum functionality and optimal costs. Designed forfurther development, SmartWire-Darwin is a communication system for industrial control
equipment in control panels and in the periphery: from control, protection and switchingto actuation, operation and monitoring.
A technology that will win you profits, now and in the future.
SmartWire-Darwin greatly reduces wiring expenses and helps save costs: from design
through construction and commissioning, up to expansions. SmartWire-Darwin relieson the proven Eaton Moeller industrial control equipment and enables these devices tocommunicate.
• Planning and engineering efficiently• Connecting error-free• Fast commissioning• Convenient operation• Maintenance with direct diagnostics• Simple expansion

Steuern

Schützen

SchaltenBedienen &Beobachten

Antreiben

Information about SmartWire-Darwin
is available in the Online Manual on www.moeller.net/support:
SmartWire Darwin: System (AWB2723-1617de)
SmartWire Darwin: Gateways (AWB2723-1612de)
SmartWire Darwin: Stations (AWB2723-1613de)
SmartWire Darwin products in this catalogue:
Chap. 1 - SmartWire Darwin - the complete range
Chap. 2 - RMQ-Titan pilot devices, RMQ connections
Chap. 5 - contactors, contactor modules
Chap. 7 - motor-protective circuit-breaker
Chap. 9 - soft starter, DS7
Chap. 17 - NZM circuit-breaker to 1600 A, interface module2010 CA08103002Z-EN   www.eaton.com

SmartWire-Darwin communication system (SWD)

SmartWire-Darwin System
Description

1/2

System overview

1/4

SWD Gateways, I/O modules, power feed modules
Ordering

1/6

SWD connections at RMQ-Titan pilot devices
System overview

1/8

Ordering

1/10

SWD modules to connect contactors and motor starters.
System overview

1/12

Ordering

1/14

SWD-capable Soft starter DS7
System overview

1/15

Ordering

1/15

SWD interface module for NZM circuit-breakers
System overview

1/16

Ordering

1/16

SWD accessories
Ordering

1/17

Engineering
Power-/current consumption of the SWD stations

1/19

Technical data
SWD gateways, Powerfeed modules

1/20

SWD I/O modules

1/22

SWD connections at RMQ-Titan pilot devices

1/24

SWD modules to connect contactors, motor starters and circuit breaker NZM.

1/26

SWD accessories

1/28

Dimensions
SWD modules and RMQ connections

1/30

Accessories

1/31

1/2

Darwin Technology
SmartWire-Darwin System

Description
SmartWire-Darwin System

SmartWire-Darwin.

Secures your know-how.
SmartWire-Darwin significantly cuts your wiring requirements and helps you save costs across the entire value chain from design through construction, programming,
commissioning to extending your system.
Utilizing Eaton’s industrial switchgear, SmartWire-Darwin is based on tried-and-tested technology. SmartWire-Darwin makes Eaton industrial switchgear
communications-enabled.

any PLCYour user program remains intact
Incorporating the SmartWire-Darwin gateway in
the Eaton PLC program is also easy. Only the PLC
configuration needs to be modified—the user
program remains unchanged making the transition
to SmartWire-Darwin, including PLC programming
quick and easy.
Your software expertise is safe!

SmartWire-Darwin in the STEP 7 PLC configuration

SmartWire-Darwin in the easySoft-CoDeSys PLC configuration2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/3

SmartWire-Darwin System

Planning and ordering help (SWD?Assist)• Easy generation of applications with the SmartWire-Darwin System• Integrated function for the generation of ordering lists• Integrated plausibility check• Online functionality– Simple preliminary commissioning of SmartWire-Darwin inputs and outputs and function testing– Easy diagnostics of SmartWire-Darwin slaves• Download– Free download under
http://downloadcenter.moeller.net
Planning a SmartWire-Darwin string is quick and easy with
the SWD-Assist software

SmartWire-Darwin System

2010 CA08103002Z-EN

www.eaton.com

1/4

Darwin Technology
SmartWire-Darwin System

System overview
4
6
6
3
8
2

5
7

1
1

16
12

13

15

10

9
11
11

6

14

6
6
6

6

20

19

22

19

18

22

21
21

19

3
6

3

6
6

17

23

25

3

32
24

24

33

Darwin Technologywww.moe

SWD-Ass ist

ller.net/darwin

V1.0 0Planning tool
product rangefor the SmartWire-Dar

win

26

28

27

25

20

22

28
13

22

15

31

11
14

29
6

3

4

2010 CA08103002Z-EN

www.eaton.com

6

6

3

30

Darwin Technology

1/5

Gateways, I/O modules, power feed modules
Sub-D data plug, 9 pole1

SmartWire-Darwin
gateways2

SmartWire-Darwin
blade terminal 8 pole3

SmartWire-Darwin
ribbon cable, 8 pole4

SmartWire-Darwin
input/output modules

5

SmartWire-Darwin
device plug 8 pole6

SmartWire-Darwin
connection for NZM

7

NZM circuit-breakers

8

SmartWire-Darwin
contactor module

9

SmartWire-Darwin
powerfeed module

17

RMQ-Titan surface
mounting enclosure

25

DILM contactors

10

18

11

SmartWire-Darwin
card for function elements,base fixing

26

SmartWire-Darwin
contactor module with
Manual-0-Automatic switch

SmartWire-Darwin
LED elements,
front fixing
RMQ-Titan mounting
adapter for front mounting

19

SmartWire-Darwin
LED elements for base fixing

27

Motor protective circuit
breakers

12
RMQ-Titan indicator light

20

28

MSC motor starters

13

21

SmartWire-Darwin
PKE modules

14

SmartWire-Darwinfunction elements forfront fixing

SmartWire-Darwin
Function elements for basefixing29

22

PKE motor starters withelectronic motor protection

15

SmartWire-Darwin
operating elements

SmartWire-Darwin
adapter for flat/roundcable for top-hat rail
mounting

SmartWire-Darwin
control panel cable adapter
for flat to round cable

23

SmartWire-Darwin
network termination for
8 pole ribbon cable

30

SmartWire-Darwin
plug connectors

24

DS7 soft starters

31

SmartWire-Darwinplanning and ordering aid,
SWD-Assist

32

SmartWire-Darwin
round cable, 8 pole33

DS7 soft starter with PKE
electronic motor protection

16

Features
SmartWire-Darwin gateway

SmartWire-Darwin
input/output module

Power feeder module

Planning and ordering help
(SWD-Assist)• Connection of SmartWire-Darwin
to fieldbus.
• Supports the PROFIBUS-DP and
CANopen fieldbuses.
• Provides of the supply voltage for
the SmartWire-Darwin slaves.
• Supplies the control voltage for the
motor starters or contactors.
• Configuration button for automatic
addressing of the SmartWireDarwin slaves.
• Support of up to 99 SmartWireDarwin slaves.
• Connection of the SmartWireDarwin ribbon cable via blade
terminal.

• Connection to SmartWire-Darwin
ribbon cable via device plug.
• Integration of other switching
devices without integrated SmartWire-Darwin technology.
• Variant with 8 digital inputs, or
4 digital inputs and 4 non-isolatedtransistor outputs, or 4 digital
inputs and 2 relay outputs 250 V AC.
• SmartWire-Darwin diagnostics
LED for signalling of the communication status of the module.

• Connection to SmartWire-Darwin
ribbon cable via blade terminal.
• Provides of the supply voltage for
the SmartWire-Darwin slaves.
• Control voltage feeder for the
motor starters and contactors.
• Formation of emergency-stop
groups.

• Easy generation of applications
with the SmartWire-Darwin
system.
• Integrated function for thegeneration of ordering lists.
• Integrated plausibility check.
• Online functionality– Simple preliminary commissioning of SmartWire-Darwin inputs
and outputs and function testing.
– Easy diagnostics of SmartWireDarwin slaves• .
• Free download under
http://downloadcenter.moeller.net

Gateways, I/O modules, power feed modules

2010 CA08103002Z-EN

www.eaton.com

1/6

Darwin Technology
Gateways, I/O modules, power feed modules
HPL01006EN

Ordering
Description

Part no.
Article no.

Price
See price list

Std. pack

SWD gateways
Gateway to the connection to the fieldbus and for supplying the SmartWire-Darwin (SWD) slaves and switchgear.
EU5C-SWD-DP
116308

1 off

EU5C-SWD-CAN
116307

1 off

EU5E-SWD-8DX
116381
EU5E-SWD-4D4D
116382
EU5E-SWD-4D2R
116383

1 off

For additional control voltage supply of the motor starters and contactors.
For the formation of emergency-stop groups for the motor starters and contactors.

EU5C-SWD-PF1-1
1163091 off

For the supply of other SWD slaves.
For additional control voltage supply of the motor starters and contactors.
For the formation of emergency-stop groups for the motor starters and contactors.

EU5C-SWD-PF2-1
116380

1 off

Connection to PROFIBUS-DP as slave.
Automatic baud rate detection from 9.6 kBit/s to 12 Mbit/s.
Address range 1 - 126.
9 pole SUB-D socket.
Connection of up to 58 SWD slaves.
Connection to CANopen as slave.
Automatic baud rate detection from 10 kBit/s to 1 Mbit/s.
Address range 1 - 32.
9 pole SUB-D plug.
Connection of up to 99 SWD slaves.

SWD I/O modules
SmartWire-Darwin slaves for the connection of digital I/O signals.
Digital module with 8 digital inputs 24 V DC
Digital module with 4 digital inputs 24 V DC and 4 transistor outputs 24 V DC/0.5 A
Digital module with 4 digital inputs 24 V DC and 2 relay outputs 250 V AC

SWD powerfeed module

Information relevant for export to North America
NA Certification

Request filed for UL and CSA
UL/CSA approval applied for2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/7

Notes
Notes

2010 CA08103002Z-EN

www.eaton.com

1/8

Darwin Technology
SWD RMQ connections

SWD RMQ connections

5
5
2

3
6

1

12
13

7
2
40
8
14

39

5

4

Darwin Technologywww.moeller.net/da

SWD-Ass ist

rwin

V1.0 0Planning toolfor
product range the SmartWire-Dar

win

9
10

38

11

27
37

11

30

36
11

26

35

15

34
25
33
31
24
32

16

30

17
23

29
21

21

20
22

18

28
20

19
18

21
19

2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/9

SWD RMQ connections
RMQ-Titan, 4-way selector
switch ￫ Chapter 2

1

RMQ-Titan, label with label
mount for 4-way selector
switch and joystick￫ Chapter 2

2

SWD front mounting adapter
for 2 × M22-SWD-K22￫ Page 1/11

3

RMQ-Titan, front mounting
adapter with three mounting
locations ￫ Page 1/11

4

SWD function elementwith 3 positions for front
mounting ￫ Features

5

SWD LED element for front
mounting ￫ Features

6

SWD function elementwith 2 positions for front
mounting ￫ Features

7

SWD function element with
2 positions and LED for front
mounting ￫ Features

8

SWD function element with
3 positions and LED for front
mounting ￫ Features

9

Link for SWD device plugs￫ Features

10

Features
SWD-RMQ connection for front
fixing ￫ Page 1/10
• Adaptation with standard adapter
M22-A or M22-SWD-A4 for 4-way
selector switch/pushbutton andjoystick.
• Combination with standard pilot
devices of the RMQ-Titan M22
serie.
• Types with one or two change overcontacts and with/without
integrated LED element.
• LED elements in four colors.
• SmartWire-Darwin diagnostics
LED for signalling of the communication status of the function
element.
• Connection to SmartWire-Darwin
ribbon cable with device plug.
.

RMQ-Titan, M22 contact
elements for front mounting￫ Chapter 2

11

RMQ-Titan, M22 contact
elements with base fixing￫ Chapter 2

21

SWD device plug
￫ Page 1/17

12

Link for SWD PCB￫ Page 1/11

22

SWD ribbon cable￫ Page 1/17

13

SWD function element with
3 positions and LED for basefixing ￫ Features

23

SWD-Assist, Planning andordering help ￫ Features

14
24

RMQ-Titan, surface
mounting enclosure￫ Chapter 2

15

SWD function element with
3 positions for base fixing￫ Features

25

SWD PCB for surface
mounting enclosure￫ Features

16

SWD function element with
2 positions and LED for basefixing ￫ Features

26

Cable gland for SWD roundcable ￫ Chapter 2

17

SWD function element with
2 positions for base fixing￫ Features
SWD LED element for basefixing ￫ Features

SWD bulkhead plug/socket
RJ45 with prefabricatedsignal cables ￫ Features

18

SWD socket/plug for roundcable ￫ Features

19

SWD round cable￫ Page 1/18

20

RMQ-Titan, insert labels￫ Chapter 2

30

RMQ-Titan, label mountfor double actuator pushbuttons ￫ Chapter 2

31

RMQ-Titan, indicator light￫ Chapter 2

32

RMQ-Titan, key-operated
actuator ￫ Chapter 2

33

RMQ-Titan, selector switch
actuator ￫ Chapter 2

34

RMQ-Titan, button plates/
button lenses ￫ Chapter 2

35

RMQ-Titan, pushbutton
actuators ￫ Chapter 2

36

27

RMQ-Titan, label mounts￫ Chapter 2

37

RMQ-Titan, bezels￫ Chapter 2

28

RMQ-Titan, emergency stop
pushbuttons (for safety
circuits use only standard
contacts M22) ￫ Chapter 2

38

RMQ-Titan, double
actuators ￫ Chapter 2

29
RMQ-Titan, joystick￫ Chapter 2

39

RMQ-Titan, 4-way
pushbutton ￫ Chapter 2

40

Link for device plug
￫ Page 1/11

SWD RMQ connection for base fixing￫ Page 1/10

Planning and ordering help
(SWD Assist)• Connection to SmartWire-Darwin
device plug.
• Suitable for bridging adapted
external SmartWire-Darwin device
plugs (e.g. as placeholders).

• For use with SWD PCB, RMQ-Titan
surface mounting enclosure and
RMQ-Titan M22 control circuit
devices.
• Types with one or two change overcontacts and with/without
integrated LED element.
• LED elements in four colors.
• SmartWire-Darwin diagnostics
LED for signalling of the communication status of the function
element.

• Easy generation of applications
with the SmartWire-Darwin
system.
• Integrated function for thegeneration of ordering lists.
• Integrated plausibility check.
• Online functionality:– Simple preliminary commissioning of SmartWire-Darwin inputs
and outputs and function testing.
– Easy diagnostics of SmartWireDarwin slaves.
• Free download under
http://downloadcenter.moeller.net

Surface mounting enclosure with
PCB ￫ Page 1/11
• Connection of SmartWire-Darwinfunction elements for base fixing.
• Type with 1, 2, 3, 4 and 6 slots.
• Bridging of free slots with link forbase fixing.
• Integrated connectable network
terminator.

Housing bushing socket￫ Page 1/18
• Use for RMQ-Titan M22 surface
mounting enclosure or control
panel.
• Type plug/socket.
• Prefabricated signal cable withferrules for connection to PCB forsurface mounting enclosure.

SWD RMQ connections

2010 CA08103002Z-EN

www.eaton.com

1/10

Darwin Technology
SWD RMQ connections
HPL01010EN

Ordering
Number ofcontacts

Circuit symbol

Contact travel
diagram in connection
with front element

Configuration

Color LED

Part no.
Article no.

Price
See pricelist

1without LED

M22-SWD-K11
11596420 offwithout LED

M22-SWD-K22
11596510 offwithout LED

M22-SWD-KC11
11599520 offwithout LED

M22-SWD-KC22
115996

10 off

M22-SWD-K11LED-W
115972
M22-SWD-K11LED-B
115973
M22-SWD-K11LED-G
115974
M22-SWD-K11LED-R
11597520 off

M22-SWD-K22LED-W
115978
M22-SWD-K22LED-B
115979
M22-SWD-K22LED-G
115980
M22-SWD-K22LED-R
11598110 off

M22-SWD-K11LEDC-W
116003
M22-SWD-K11LEDC-B
116004
M22-SWD-K11LEDC-G
116005
M22-SWD-K11LEDC-R
11600620 off

M22-SWD-K22LEDC-W
116009
M22-SWD-K22LEDC-B
116010
M22-SWD-K22LEDC-G
116011
M22-SWD-K22LEDC-R
11601210 offStd. pack

Function elements
Front fixing
1 change overcontact
0 1.2

2.8

1
2.8

3

6

2

5

5.5

2 change overcontacts
0 1.2

4

4

3

6

2

5

5.5

Base fixing
1 change overcontact
0 1.2

2.8

2.8

3

1

2

3

1

1

3

2

5.5

2 change overcontacts
0 1.2

2

5.5

Front fixing
1 change overcontact
0 1.2

2.8

1
2.8

6

5

5.5

2 change overcontacts
0 1.2

4

4

3

6

2

5

5.5

Base fixing
1 change overcontact
0 1.2

2.8

Notes

2.8

3

1

2

3

1

5.5

2 change overcontacts
0 1.2

2

5.5

SWD function elements can be combined with RMQ-Titan operating elements M22... ￫ Chapter “Control circuit devices”
Information relevant for export to North America
NA Certification

Request filed for UL and CSA
UL/CSA approval applied for2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/11

SWD contactor modules, SWD PKE module
HPL010111EN
Configuration

Color
LED

Part no.
Article no.

Price
See price
list

Std. pack

Information relevant forexport to North America

NA Certification
Request filed for UL
and CSAUL/CSA approval
applied for.

LED elements
Front fixing
1

1

1

1

4

4

4

4

3

3

3

3

6

6

6

6

2

2

2

2

5

M22-SWD-LED-W
11596620 off

5

M22-SWD-LED-B
11596720 off

5

M22-SWD-LED-G
11596820 off

5

M22-SWD-LED-R
11596920 offBase fixing

2

3

1

M22-SWD-LEDC-W
11599720 off

2

3

1

M22-SWD-LEDC-B
11599820 off

2

3

1

M22-SWD-LEDC-G
11599920 off

2

3

1

M22-SWD-LEDC-R
11600020 off

1

3

2

M22-A
21637450 off

5

UL/CSA certification not
required

M22-A-GVP
216375500 off

5

UL/CSA certification not
required

M22-SWD-A4
116016

10 off

NA Certification
Request filed for UL
and CSAUL/CSA approval
applied for.

M22-SWD-I1-LP01
115990
M22-SWD-I2-LP01
115991
M22-SWD-I3-LP01
115992
M22-SWD-I4-LP01
115993
M22-SWD-I6-LP01
115994

1 off

NA Certification
Request filed for UL
and CSAUL/CSA approval
applied for.

M22-SWD-SEL8-10
1166985 off

NA Certification
Request filed for UL
and CSAUL/CSA approval
applied for.

Fixing adapters
Front fixing
For 1 function element
M22-SWD-K… or LED element
M22-SWD-LED…
In addition 1 or 2 contact elements
M22-K.. possible.
Sequence number on fixing
adapter.

1

For 2 function elements
M22-SWD-K22...
For use with M22-WR4,-WRJ4, -D4 in conjunction
with M22-(SWD)-K

4

4

1

3

6

6

4

2

2

3

Printed circuit boards

OUT

IN

PCBs for surface mounting enclosure M22-I.. for mounting base function elements
M22-SWD...K.
Integrated, connectable SWD network terminator
Number of mounting locations:
1

OFF

ON

2
3
4
6

1 off
1 off
1 off
1 off

Link
Bridging of open mounting locations on M22-SWD-I...-LP01 PCB
Base fixing
NA Certification
Request filed for UL
and CSAUL/CSA approval
applied for.

Notes
SWD LED elements can be combined with RMQ-Titan indication elements M22... ￫ Chapter "Control circuit devices"
SWD contactor modules, SWD PKE module2010 CA08103002Z-EN

www.eaton.com

1/12

Darwin Technology
SWD contactor modules, SWD PKE module

System overview

1

2
3

6

Darwin Technologywww.moeller.net/darwin

4

SWD-Assist

5

V1.0 0Planning toolfor
product range the SmartWire-Dar
win

1
7

2

8

3
9

10

4

4
11

12

13
14

15
16

4

10

MSC-DEA networkable PKEbased motor starters up to
7 kW ￫ Features1

Network terminator￫ Page 1/17

5

MSC-D DOL starters basedon PKZM0 up to 7 kW
￫ Chapter 8

Planning and ordering help,
SWD assist ￫ Features

6

2

7

MSC-R reversing starters
based on PKZM0 up to 7 kW
￫ Chapter 8

3

MSC-DEA networkable PKEbased motor starters up to
15 kW ￫ Features

8

SWD ribbon cable￫ Page 1/17

4

MSC-D DOL starters basedon PKZM0 up to 15 kW￫ Chapter 82010 CA08103002Z-EN

www.eaton.com

MSC-R reversing starters
based on PKZM0 up
to 15 kW ￫ Chapter 89Modules SWD PKE modules￫ Features

13

SWD device plug
￫ Page 1/17

10

SWD contactor module withmanual/auto functionality￫ Features

14

Power feeder module￫ Features

11

SWD contactor module￫ Features

15

SWD input/output modulewith relay outputs￫ Features

12

Link for device plug
￫ Page 1/17

16

Darwin Technology

1/13

SWD contactor modules, SWD PKE module
Features

SWD contactor modules, SWD PKE module

MSC-DEA networkable PKE-based
motor starter ￫ Chapter 8• Plug & play-capable motor starter
combi-nation up to 15 kW, consisting of
PKE basic unit, contactor DILM and
PKE trip block PKE-XTUA.
• Exchangeable trip blocks for cover ofcurrent ranges.
• Wide-range overload protection
ratio 4:1.
• Adjustable time-lag classes(CLASS 5, 10, 15, 20) for different
tripping characteristics.
• Networkable via SWD PKE module.
Powerfeed module ￫ Page 1/6• Provision of SmartWire-Darwin supply
voltage.
• Provision of 24 V DC supply voltage foractivating the contactors.
• Formation of emergency-stop groups.

SWD PKE module ￫ Page 1/14
• Pluggable onto contactors in thexStart range.
• Suitable for motor starters MSC-DEA…(24 V DC) or DILM(C)7 -DILM(C)32 in
combination with PKE12/32 and trip
block PKE-XTUA-…
• Use of the standard switchgear of thexStart range.
• Use of the standard accessories in thexStart range.
• Integrated mechanical contactor
switching state indication.
• Integrated contactor switching statescanning.
• Transmission of PKE-specific data
(switch position PKE, relative motor
current, thermal motor image, trip indications (overload, short-circuit,…),type PKE trip block, set value of overload release and time-lag class).
• Communication cable (PKE32-COM)for connection to PKE trip blockincluded as standard.
• Contactor actuation.
• Selectable ZMR functionality(contactor opening on overload).
• SWD diagnostics LED for signallingthe communication status of themodules and signalling of the switch
command via SmartWire-Darwin.
• Manual/Auto functionality for
automatic or manual switching onof the connected contactor.
• Connection to SmartWire-Darwin
ribbon cable via device plug.

SWD contactor module ￫ Page 1/14
• Pluggable onto contactors in thexStart range.
• Suitable for contactors DILM7 DILM38(24VDC), DILMC7…DILMC32 (24 VDC),
DILA DILMP20 DILMP45 (24 VDC
RDC24) or motor starter MSC…(24 VDC).
• Use of the standard switchgear of thexStart range.
• Use of the standard accessories in thexStart range.
• Suitable for contactor combinations
with PKZ or with Z overload relays.
• Integrated switch position scanning.
• Integrated mechanical switch positionindication.
• Contactor actuation.
• SWD diagnostics LED for signallingthe communication status of themodules and signalling of the switch
command via SmartWire-Darwin.
• Two digital inputs for scanning floating
contacts, such as motor-protective
circuit-breaker auxiliary contacts.
• For DIL-SWD-32-002 built-in Manual/
Auto functionality for automatic or
manual switching on of the connectedcontactor.
• Connection to SmartWire-Darwin
ribbon cable via device plug.

Link for device plug ￫ Page 1/17
• Connection to SmartWire-Darwin
device plug.
• Suitable for the bridging of alreadyadapted device plugs (e.g. as aplaceholder).
Planning and ordering help (SWD assist)• Easy generation of applications with
the SmartWire-Darwin system.
• Integrated function for the generationof ordering lists.
• Integrated plausibility check.
• Online functionality.
– Simple preliminary commissioningof SmartWire-Darwin inputs andoutputs and function testing.
– Simple diagnostics of SmartWireDarwin slaves.
• Free download under
http://downloadcenter.moeller.net
Safety engineering• Emergency-stop disconnection
to IEC/EN 954-1, switching category 3;
EN ISO 13849-1 PL d; IEC 62061 SIL 2• Central switch off of the control
voltage at the gateway or power
feeder module.
• Combination with safety-related
switchgears possible.

SWD input/output modules ￫ Page 1/6• Digital module with four 24 V DC digital
inputs and two relay outputs for
actuating contactors DILM40-DILM72.
• Connection to SmartWire-Darwin
through device plug.

Design note
“The number of motor starters or DILM contactors that can be connected is dependent upon the power consumption of the magnet systems per SmartWire Darwin line.
To increase the number of SmartWire-Darwin modules that can be connected power feeder modules can be used.”

24 V DCDILM(C)7, DILA DILM(C)9DILM(C)15

DILM(C)17

DILM(C)25

3

DILM(C)12,
DILMP20
4.5

Pick-up power[W]
Holding power
[W]

3
3

12

DILM(C)32,
DILMP32
12

DILM38,
DILMP45
12

4.5

12

3

4.5

4.5

0.5

0.5

0.5

05

2010 CA08103002Z-EN

www.eaton.com

1/14

Darwin Technology
SWD contactor modules, SWD PKE module
HPL01014EN

Ordering
SWD contactor modules, SWD PKE module

Description

For use withPart no.
Article no.

Price
See pricelist

DILM(C)7… DILM(C)32
DILM38DILA
MSC-D(E)-...(24VDC)

DIL-SWD-32-001
118560

5 off

DILM(C)7… DILM(C)32
DILM38DILA
MSC-D(E)-...(24VDC)

DIL-SWD-32-002
118561

5 off

DILM(C)7… DILM(C)32
MSC-DEA

PKE-SWD-32
126895

4 off

Std. pack

SWD contactor modules1)
SmartWire-Darwin module for surface-mounting on contactors.
Per contactor 1 module.
Two digital inputs for floating contacts.
1 electrical interlock for the surface mounting of reversing starters.
Messages: contactor switch status, status of the digital inputs 1 and 2.
Commands: contactor actuation

Two digital inputs for floating contacts.
1 electrical interlock for the surface mounting of reversing starters.
1-0-A switch for manual or automatic operation.
Messages: contactor switch status, status of the digital inputs 1 and 2,
switch position 1-0-A switch.
Commands: contactor actuation

SWD PKE module1)2)
SmartWire-Darwin module for connection of motor starter combination, model “extended”
24 V DC (MSC-DEA-…) up to 15 kW.
One module per contactor and PKE.
Surface-mounting to contactors.
Interface for connection of PKE trip block PKE-XTUA-…
Connecting cable between module and trip block PKE-XTUA-…
included as standard.
1 electrical interlock for the surface mounting of reversing starters.
1-0-A switch for manual or automatic operation.
Selectable overload relay function (ZMR) for disconnecting thecontactor on overload.
Messages:- Switch position contactor/PKE/1-0-A switch- Motor current in %- Thermal motor image in %- Trip-indicating auxiliary contact (overload, short-circuit,...)- Set value of overload release- Set value of time lag (CLASS), type of trip block
Commands: contactor actuation, activation of overload relay function
(ZMR)
Notes

1)

• Take into account the max. current consumption of the contactor coils per SmartWire-Darwin line.
• A2 connections must not be bridged.
• Wiring sets DILM 12-XRL and PKZM0-XRM12 cannot be used.
• Connection terminals for electrical interlocking are not suitable for safety technology.
2) • Additional SWD contactor module required fir actuation of reversing starter.
Information relevant for export to North America
NA Certification

Request filed for UL and CSA
UL/CSA approval applied for2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/15

Soft starters
HPL01015EN

System overview
Soft starters

DS7 smartWire-Darwin soft starters

1 Short description

SWD ribbon cable2

SWD device plug

3

1

3
2

The DS7-…-D soft starters are designed forconnection to SmartWire-Darwin. These
two-phase-controlled soft starters control
three-phase motors for applications with normal
operating frequency in the 4 to 200 A rating
range (1.5 to 110 kW at 400 V mains voltage).
Due to Eaton’s special control method the true
running behavior of a DS7 can be compared withthat of three-phase soft starters.
SmartWire-Darwin provides a direct connection
to the DS7 without control signal wiring. ThroughSmartWire-Darwin the PLC transmits all control
signals directly to the soft starter. The device
data are available for processing in the master
controller without any additional requirements.
The connection with SmartWire-Darwin is fast,easy, inexpensive and convenient.
Note:
For further details see section “Soft starters”

Ordering
Rated
operational
currentof the soft
starter
Ie

Assigned motor rating

A

400 V

480 V

460 V

P

P

P

kW

HP

HP

Part no.
Article no.

Price
See
price list

Std. pack

Information relevant for export to North America

1 off

Product Standards

Soft starters
Soft starters for three-phase loads, mains supply voltage
230–480 V AC (50/60 Hz)
Rated control circuit voltage Uc: 24 V DC SmartWire-Darwin
4
1.5
2
2
7

3

3

3

9

4

5

5

12

5.5

7.5

7.5

16

7.5

10

10

24

11

15

15

32

15

20

20

41

22

30

30

55

30

40

40

70

37

50

50

81

45

60

60

100

55

75

75

135

75

100

100

160

90

125

125

200

110

150

150

DS7-34DSX004N0-D
134943
DS7-34DSX007N0-D
134945
DS7-34DSX009N0-D
134946
DS7-34DSX012N0-D
134947DS7-34DSX016N0-D
134948
DS7-34DSX024N0-D
134949DS7-34DSX032N0-D
134950Suitable forMax. Voltage Rating
Degree of Protection

IEC/EN 60947-4-2;
GB 14048.6; UL 508;
CSA-C22.2 No 0-M91;
CSA-C22.2 No 14-05
CE marking
Request filed for UL and
CSA
Branch circuits
480 V
IP20; UL/CSA Part no. 1

2010 CA08103002Z-EN

www.eaton.com

NA Certification

DS7-34DSX041N0-D
134952
DS7-34DSX055N0-D
134953
DS7-34DSX070N0-D
134954
DS7-34DSX081N0-D
134955
DS7-34DSX100N0-D
134956
DS7-34DSX135N0-D
134957DS7-34DSX160N0-D
134958
DS7-34DSX200N0-D
134959

1/16

Darwin Technology
SWD interface for NZM circuit-breakers
HPL01016EN

System overview
SWD interface for NZM circuit-breakers

4

SmartWire-Darwin
NZM circuit-breakers

1 Short description

Connection cable from NZM
to NZMX-SWD-704

2

NZM interface forSmart-Wire-Darwin

3

SWD ribbon cable

4

SWD device plug

5

5
1

3

2

The NZM interface module implements
the data connection between circuitbreakers NZM2/3/4 with electronic
release and SmartWire-Darwin. It transmits the following digital status data:• On-Off-Tripped• Load warnings• Reason for last trip
• Actual currents, the switch type andthe current settings of the rotary coding
switches.
The switch can also be operated with aremote operator.
Note:
For further details see section“NZM circuit-breakers”.

2

Ordering
Description

Part no.
Article no.

Price
See price
list

Std.
pack

Notes

1 off

A connection cable to thecircuit-breaker is included
as standard.

NZM interface to SmartWire-Darwin
The module implements the data connection between the NZM2/3/4
with electronic release and the SmartWire-Darwin.
The following data is transmitted:• Digital status data (ON/OFF/TRIPPED)• Load warnings• Reason for last trip
• The actual currents• The switch type• The current settings of the rotary coding switches
The switch can also be operated with a remote operator.
• Two digital inputs for the switch status• Two transistor outputs for remote operation• Retentive memory for energy data (kWh)Energy data is transmitted through digital input (S0) from an externalenergy measuring module NZN...-XMC-SO.

2010 CA08103002Z-EN

www.eaton.com

NZM-XSWD-704
135530Darwin Technology

1/17

Accessories
HPL01017EN
Accessories

Std. pack

Information relevant for export
to North America

SWD4-100LF8-24
116026
SWD4-3LF8-24-2S
116027
SWD4-5LF8-24-2S
116028
SWD4-10LF8-24-2S
1160291 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

SWD4-8SF2-5
11602210 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

Link for device plug SWD4-8SF2-5

SWD4-SEL8-10
116021

5 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for8 pole blade terminal for connection to
gateway, power feeder module, coupling, network
termination

SWD4-8MF2
11602310 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

Coupling for 8 pole blade terminal

SWD4-8SFF2-5
116024

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

Network terminator for 8 pole ribbon cable

SWD4-RC8-10
116020

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied forCable adapter for flat cable (plug) toround cable (terminal)

SWD4-8FRF-10
121377

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

SWD4-SFL8-20
121380
SWD4-SML8-20
121381

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

Description

Part no.
Article no.

Price
See pricelist

Ribbon cable, 8 pole
For laying the SmartWire-Darwin network inside the control panel.
Length: 100 m

SWD4-8SF2

SWD4-8SF2 SWD4-8S

Length: 3 m
Prefabricated with 2 blade terminals SWD4-8MF2.
Length: 5 m
Prefabricated with 2 blade terminals SWD4-8MF2.
Length: 10 m
Prefabricated with 2 blade terminals SWD4-8MF2.

1 off
1 off
1 off

Device plug
Device plug for connecting SmartWire-Darwin slaves

Link
Bridging open mounting locations for device plugs

Blade terminal

Coupler

SWD4-8SFF2

-5

+ 15V

Network terminator

SWD4-RC8-1

0

+ 15V

1

2

3

4

5

6

7

8

Cable adapter+15 V

Switch cabinet bushingTransition from SWD ribbon cable to round cable, can be plugged-in on both sides.
Additional control voltage feeder for the motor starters and contactors.
Suitable for wall thickness up to 4 mm.
Protection type IP67, drill hole 18.5 mm.
Connection of ribbon cable with blade terminal SWD4-8MF2
8 poleConnection round cable via socket.
Connection round cable via plug.

1 off2010 CA08103002Z-EN

www.eaton.com

1/18

Darwin Technology
Accessories
HPL01018EN
Std. pack

Information relevant for export
to North America

SWD4-50LR8-24
116030

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

SWD4-SF8-20
116031

1 off

NA Certification
Request filed for UL and CSA
UL/CSA approval applied for

SWD4-SM8-20
116032

1 off

8 pole socket, straight

SWD4-SF8-67
116033

1 off

8 pole plug, straight

SWD4-SM8-67
1160341 off

8 pole socket, 90° angled

SWD4-SF8-67W
116035

1 off

8 pole plug, 90° angled

SWD4-SM8-67W
116036

1 off

Pliers for device plugs

SWD4-CRP-1
116025

1 off

Pliers for blade terminal

SWD4-CRP-2
1166991 off

Insert for toggle lever press of device plugs

SWD4-CRPAD-1
116700

1 off

Insert for toggle lever press of blade terminal

SWD4-CRPAD-2
116701

1 off

Description

Part no.
Article no.

Price
See pricelist

Round cable, 8 pole
For laying the SmartWire-Darwin network outside of the control panel.
Length: 50 m, HK-SO-Li2YY, 8 mm diameter

Housing bushing socket
Enclosure bushing for installation in surface mounting enclosure M22-I...
8 pole socket/plug, IP67, for connection to SWD4-S(M,F)-67...
8 prefabricated cables for connection to PCB M22-SWD-I...
8 pole socket, M20

8 pole plug, M20

Connectors for SWD round cables
NA Certification
Request filed for UL and CSA
UL/CSA approval applied forTools for plugs

2010 CA08103002Z-EN

www.eaton.com

UL/CSA certification not
requiredDarwin Technology

1/19

Current consumption SWD slaves
HPL01019EN
Current consumption SWD slaves

Engineering
Current consumption 15 V SWD supply voltage
Part no.

Article no.

M22-SWD-K11
M22-SWD-K22
M22-SWD-LED-W
M22-SWD-LED-B
M22-SWD-LED-G
M22-SWD-LED-R
M22-SWD-K11LED-W
M22-SWD-K11LED-B
M22-SWD-K11LED-G
M22-SWD-K11LED-R
M22-SWD-K22LED-W
M22-SWD-K22LED-B
M22-SWD-K22LED-G
M22-SWD-K22LED-R
M22-SWD-KC11
M22-SWD-KC22
M22-SWD-LEDC-W
M22-SWD-LEDC-B
M22-SWD-LEDC-G
M22-SWD-LEDC-R
M22-SWD-K11LEDC-W
M22-SWD-K11LEDC-B
M22-SWD-K11LEDC-G
M22-SWD-K11LEDC-R
M22-SWD-K22LEDC-W
M22-SWD-K22LEDC-B
M22-SWD-K22LEDC-G
M22-SWD-K22LEDC-R
DIL-SWD-32-001
DIL-SWD-32-002
PKE-SWD-32
EU5E-SWD-8DX
EU5E-SWD-4D4D
EU5E-SWD-4D2R
NZM-XSWD-704
M22-SWD-I1-LP01
M22-SWD-I2-LP01
M22-SWD-I3-LP01
M22-SWD-I4-LP01
M22-SWD-I6-LP01
SWD4-RC8-10

115964115965115966115967115968115969115972115973115974115975115978115979115980115981115995115996115997115998115999116000116003116004116005116006116009116010116011116012118560118561
126895116381116382116383135530115990115991115992115993115994116020Current consumption
mA
7
7
19
19
19
19
19
19
19
19
19
19
19
19
7
7
19
19
19
19
19
19
19
19
19
19
19
19
40
40
58
12
45
45
35
17
17
17
17
17
17

Notes

DIL-SWD-32-…

PKE-SWD-32

W
W
W

3
4.5
12

3
4.5
12

mA
mA
mA

125
188
500

125
188
500

W
W
W

3
4.5
0.5

3
4.5
0.5

mA
mA
mA

125
188
21

125
188
21

With terminating resistor switched on-

Power consumption/current consumption 24 V SWD control voltage UAUX
Pick-up powerfor DILM(C) 7-9, DILA
for DILM(C) 12-15, DILMP20
for DILM(C) 17-38, DILMP32-45
Pick-up current
for DILM(C) 7-9, DILA
for DILM(C) 12-15, DILMP20
for DILM(C) 17-38, DILMP32-45
Sealing powerfor DILM(C) 7-9, DILA
for DILM(C) 12-15, DILMP20
for DILM(C) 17-38, DILMP32-45
Sealing current
for DILM(C) 7-9, DILA
for DILM(C) 12-15, DILMP20
for DILM(C) 17-38, DILMP32-45
SWD gateways, power feeder modules

2010 CA08103002Z-EN

www.eaton.com

1/20

Darwin Technology
SWD gateways, power feeder modules

Technical data

EU5C-SWD-DP

EU5C-SWD-CAN

EU5C-SWD-PF1-1

EU5C-SWD-PF2-1

GeneralStandards
Dimensions (W x H x D)

mm

IEC/EN 61131-2
EN 50178
35 x 90 x 127

Weight

kg

0.16

0.16

0.11

0.17

Weight

g

–

–

–

–

35 x 90 x 124

Mounting

Top-hat rail IEC/EN 60715, 35 mm

Mounting position

VerticalAmbient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)

IP20

IP20

IP20

IP20

Vibrations (IEC/EN 61131-2:2008)
Constant amplitude 3.5 mm

Hz

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

Constant acceleration, 1 g

Hz

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

Shocks

9

9

9

9

mm

50

50

50

50

m

0.3

0.3

0.3

0.3

Overvoltage category

II

II

II

II

Pollution degree

2

2

2

2

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Electromagnetic compatibility (EMC)

Electrostatic discharge (IEC/EN 61131-2:2008)
Air discharge (Level 3)

kV

8

8

8

8

Contact discharge (Level 2)

kV

4

4

4

4

Electromagnetic fields (IEC/EN 61131-2:2008)
80-1000 MHz

V/m

10

10

10

10

1.4 - 2 GHz

V/m

3

3

3

3

2 - 2.7 GHz

V/m

1

1

1

1

Radio interference suppression (SmartWire-Darwin)

EN 55011 Class A

Burst (IEC/EN 61131-2:2008, Level 3)
Supply cables

kV

2

2

2

2

CAN/DP bus cable

kV

1

1

–

–

SmartWire-Darwin cables

kV

1

1

1

1

V

Supply cables 0.5 kV, CAN/DP bus cable 1 kV
10
10
10
10

10

°C

-25 … +55

-25 … +55

-25 … +55

Surge (IEC/EN 61131-2:2008, Level 1)
Supply cables/CAN/DP bus cable
Radiated RFI (IEC/EN 61131-2:2008, Level 3)
Ambient climatic conditions
Operating ambient temperature (IEC 60068-2)
Condensation-25 … +55

Prevent with suitable measures

Storage°C-40 - 70

-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 … 95

5 … 95

5 … 95

5 … 95

Rated operating voltage

V

24 DC -15% +20%

Input voltage residual ripple

%

≦5

≦5

≦5

≦5

Yes

Yes

Yes

Yes

3

3

3

3

Supply voltage UAux

Protection against polarity reversal
Max. current

Imax

A

If contactors with a total power consumption > 3 A are connected, a power feeder module
EU5C-SWD-PF1/2 has to be used.
no, external fuse FAZ Z3

Short-circuit rating
Heat dissipation

W

Potential isolation
Rated operating voltage of 24 V DC stations

2010 CA08103002Z-EN

www.eaton.com

V

Normally 1

Normally 1

Normally 1

Normally 1

No

No

No

No

Normally UAux - 0.2

Normally UAux - 0.2

Normally UAux - 0.2

Normally UAux - 0.2

Darwin Technology

1/21

SWD gateways, power feeder modules

EU5C-SWD-DP

EU5C-SWD-CAN

EU5C-SWD-PF1-1

EU5C-SWD-PF2-1

Supply voltage UPow
Supply voltage

V

24 DC -15 % + 20 %24 DC -15 % + 20 %–24 DC -15 % + 20 %Input voltage residual ripple

%

≦5

≦5

–

≦5

Yes

Yes

–

Yes

0.7

0.7

–

0.7

Yes

Yes

–

Yes

Protection against polarity reversal
Rated operational current

I

A

Overload proof
Inrush current and lengthA

12.5 A/6 ms

12.5 A/6 ms–

12.5 A/6 ms

Heat dissipation at 24 V DC

W

3.8

3.8

–

3.8

No

No

–

Yes

Potential isolation between UPow and 15 V
SmartWire-Darwin supply voltage
Bridging voltage dips

ms

10

10

–

10

Repeat rate

s

1

1

–

1

Status indicator

LED

Yes

Yes

–

Yes

Provision of SmartWire-Darwin supply voltage
Rated operational voltage

UeV

14.5 ± 3 %14.5 ± 3 %–14.5 ± 3 %Max. current

Imax

A

0.7

0.7

–

0.7

If SWD modules with a total power consumption > 0.7 A are connected, a power feeder
module EU5C-SWD-PF2 has to be used.
Yes
Yes
–
Yes

Short-circuit rating
Connection supply voltages
Terminal typePush-in terminals

Solid

mm2

0.2 - 1.5 (AWG 24 - 16)

Flexible with ferrule

mm20.25 - 1.5

0.25 - 1.5

0.25 - 1.5

0.25 - 1.5

SmartWire-Darwin network
Station type

SmartWire-Darwin master––

Number of SmartWire-Darwin slaves

58

99

–

–

125

125

–

–

Automatic

Automatic

–

–

–

–

Connections

SmartWire-Darwin master LED: green
Configuration LED: red
Plug, 8 pole

Plug connectors

Blade terminal SWD4-8MF2

2 blade terminals SWD4-8MF2

Function

PROFIBUS-DP slave

CANopen slave––

Bus protocol

PROFIBUS-DPCANopen––

Baud rate

Up to 12 MB

Up to 1 MB––

Baud rate detection

Automatic

Automatic––

Station address

2 … 125

2 … 32––

Address setting

DIP switches

DIP switches––

Two-colored red/green
Switchable via plugTwo-colored red/green
DIP switches

–

–

–

–

1 x SUB-D, 9 pole,socketYes

1 x SUB-D plug,
9 pole
Yes

–

–

–

–

Baud rate

kBd

Address setting
Status indicatorLED

2 x plug, 8 pole

Fieldbus interface

Status indication of fieldbus interface
Terminal resistor
Terminal type fieldbus
Potential isolationLED2010 CA08103002Z-EN

www.eaton.com

1/22

Darwin Technology
SWD input/output modules

SWD input/output modules

EU5E-SWD-8DX

EU5E-SWD-4D4D

EU5E-SWD-4D2R

0.1

0.11

GeneralStandards
Dimensions (W x H x D)

mm

IEC/EN 61131-2
EN 50178
35 x 90 x 101

Weightkg

0.1

Mounting

Top-hat rail IEC/EN 60715, 35 mm

Mounting position

VerticalAmbient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)

IP20

IP20

IP20

Vibrations (IEC/EN 61131-2:2008)
Constant amplitude 3.5 mm

Hz

5 … 8.4

5 … 8.4

5 … 8.4

Constant acceleration, 1 g

Hz

8.4 … 150

8.4 … 150

8.4 … 150

Shocks

9

9

9

mm

50

50

50

m

0.3

0.3

0.3

Overvoltage category

II

II

II

Pollution degree

2

2

2

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Electromagnetic compatibility (EMC)

Electrostatic discharge (IEC/EN 61131-2:2008)
Air discharge (Level 3)

kV

8

8

8

Contact discharge (Level 2)

kV

4

4

4

Electromagnetic fields (IEC/EN 61131-2:2008)
80-1000 MHz

V/m

10

10

10

1.4 - 2 GHz

V/m

3

3

3

2 - 2.7 GHz

V/m

1

1

1

Radio interference suppression (SmartWire-Darwin)

EN 55011 Class A

Burst (IEC/EN 61131-2:2008, Level 3)
Supply cables

kV

2

2

2

Signal cables

kV

1

1

1

SmartWire-Darwin cables

kV

1

1

1

–

Supply cables 0.5 kV

–

V

10

10

10

°C

-25 … +55

-25 … +55

-25 … +55

Surge (IEC/EN 61131-2:2008, Level 1)
Radiated RFI (IEC/EN 61131-2:2008, Level 3)
Ambient climatic conditions
Operating ambient temperature (IEC 60068-2)

Prevent with suitable measures

Condensation
Storage°C-40 - 70

-40 - 70

-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 … 95

5 … 95

5 … 95

SmartWire-Darwin network
Station type

SmartWire-Darwin station (slave)

Baud rate detection

Automatic

SmartWire-Darwin status

LED

Connection

Green
Plug, 8 pole
Connection plug: Device plug SWD4-8SF2-5￫ Page 19

Current consumption (15 V SWD supply)
Connection supply and I/OTerminal typePush-in terminals

Solid

mm2

0.2 - 1.5 (AWG 24 - 16)

Flexible with ferrule

mm20.25 - 1.5

0.25 - 1.5

0.25 - 1.5

Minimum length 8 mm
24 V DC supply for output supply
Rated operational voltage

Ue

Input voltage residual ripple
Protection against polarity reversal

2010 CA08103002Z-EN

www.eaton.com

V–

24 DC -15 % / +20 %

–

%

–

≦5

–

–

Yes

–

Darwin Technology

1/23

SWD input/output modules

EU5E-SWD-8DX

EU5E-SWD-4D4D

EU5E-SWD-4D2R

8

4

4

Digital inputs
NumberInput current

mA

Normally 4 at 24 V DC

Voltage level to IEC/EN 61131-2
Limit value type 1

Low < 5 V DC; High > 15 V DC

Input delay
SmartWire-Darwin status

LED

High → Low typ. < 0.2 ms
Low → High typ. < 0.2 ms
Yellow

Digital semiconductor outputs–

4–

Output current

NumberA–

Normally 0.5 at 24 V DC–

Short-circuit tripping current

A–

Max. 1.2 over 3 ms

–

W

–

≦3

–

Overload proof–

Yes, with diagnostics–

Switching capacity–

EN 60947-5-1 utilization
category DC-13–

Number––2

Contact type––

Normally open contact

Utilization category AC-1, 250 V, 6 A––> 6 x 104

Utilization category AC-15, 250 V, 3 A––> 5 x 104

Utilization category DC-13, 24 V, 1 A––> 2 x 105

Lamp load

RLL

Relay outputs

Operations

Safe isolation according to EN 50178

V AC

–

–

230

Minimum load current

mA

–

–

100 mA , 12 V DC

Response/reset time

ms

–

–

5/2.5

Bounce duration

ms

–

–

Normally 1.5––

External 4 A gL/gG–

Yellow

Yellow

Short-circuit protection
Status display outputs

LED

Potential isolation
Inputs from SmartWire-Darwin

Yes

Yes

Yes

Semi-conductor outputs from SmartWire-Darwin

–

Yes

–

Semi-conductor outputs from inputs

–

No

–

Relays from SmartWire-Darwin

–

–

Yes

Relays from inputs

–

–

Yes

Relays from relays

–

–

Yes

2010 CA08103002Z-EN

www.eaton.com

1/24

Darwin Technology

Darwin Technology

SWD RMQ connections

1/25

SWD RMQ connections

SWD RMQ connections

M22-SWD-K11

M22-SWD-KC11

M22-SWD-LED-…

M22-SWD-LEDC-…

M22-SWD-K11-LED…

M22-SWD-K11LEDC-…

M22-SWD-K22

M22-SWD-KC22

M22-SWD-K22-LED…

M22-SWD-K22LEDC-…

IEC/EN 61131-2
EN 50178
12 x 45 x 37

IEC/EN 61131-2
EN 50178
10 x 42 x 45

IEC/EN 61131-2
EN 50178
10 x 45 x 42

IEC/EN 61131-2
EN 50178
12 x 42 x 45

IEC/EN 61131-2
EN 50178
12 x 45 x 42

IEC/EN 61131-2
EN 50178
17 x 42 x 39

IEC/EN 61131-2
EN 50178
17 x 45 x 37

IEC/EN 61131-2
EN 50178
17 x 42 x 45

IEC/EN 61131-2
EN 50178
17 x 45 x 42

GeneralStandards
Dimensions (W x H x D)

mm

IEC/EN 61131-2
EN 50178
12 x 42 x 39

Weight

g

10

10

10

10

10

10

14

14

14

14

Any

Any

Any

Any

Any

Any

Any

Any

Any

Any

IP20

IP20

IP20

IP20

IP20

IP20

IP20

IP20

IP20

IP20

Mounting position
Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 61131-2:2008)
Constant amplitude 3.5 mm

Hz

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

Constant acceleration, 1 g

Hz

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

Shocks

9

9

9

9

9

9

9

9

9

9

mm

50

50

50

50

50

50

50

50

50

50

m

0.3

0.3

0.3

0.3

0.3

0.3

0.3

0.3

0.3

0.3

Overvoltage category

Not applicableNot applicableNot applicableNot applicableNot applicableNot applicableNot applicableNot applicableNot applicableNot applicable

Pollution degree

2

2

2

2

2

2

2

2

2

2

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Electromagnetic compatibility (EMC)

Electrostatic discharge (IEC/EN 61131-2:2008)
Air discharge (Level 3)

kV

8

8

8

8

8

8

8

8

8

8

Contact discharge (Level 2)

kV

4

4

4

4

4

4

4

4

4

4

Electromagnetic fields (IEC/EN 61131-2:2008)
80-1000 MHz

V/m

10

10

10

10

10

10

10

10

10

10

1.4 - 2 GHz

V/m

3

3

3

3

3

3

3

3

3

3

2 - 2.7 GHz

V/m

1

1

1

1

1

1

1

1

1

1

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

Radio interference suppression (SmartWire-Darwin)
Burst (IEC/EN 61131-2:2008, Level 3)
Supply cables

kV

2

2

2

2

2

2

2

2

2

2

SmartWire-Darwin cables

kV

1

1

1

1

1

1

1

1

1

1

V

10

10

10

10

10

10

10

10

10

10

°C

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

-30 … +55

Radiated RFI (IEC/EN 61131-2:2008, Level 3)
Ambient climatic conditions
Operating ambient temperature (IEC 60068-2)
Condensation

Prevent with suitable measures

Prevent with suitable measures

Storage°C-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

-40 - 80

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

9 … 959 … 959 … 959 … 959 … 959 … 95

5 … 95

5 … 95

5 … 95

5 … 95

SmartWire-Darwin network
Station type

SmartWire-Darwin station (slave)

Number

–

–

–

–

–

–

–

–

–

–

Baud rate setting

Automatic

Automatic

Automatic

Automatic

Automatic

Automatic

Automatic

Automatic

Automatic

Automatic

Green

Green

Green

Green

Green

Green

Green

Green

Green

Green

Connections

Plug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 polePlug, 8 pole

Plug connectors

SWD4-8SF2-5

M22-SWD-I…LP

SWD4-8SF2-5

M22-SWD-I…LP

SWD4-8SF2-5

M22-SWD-I…LP

SWD4-8SF2-5

M22-SWD-I…LP

SWD4-8SF2-5

M22-SWD-I…LP

Number of insertion cycles

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

≥ 50

Current consumption (15 V SWD supply)￫ Page 19

1 changeover
contact
1 x 106

2 changeover
contacts
1 x 106

2 changeover
contacts
1 x 106

2 changeover
contacts
1 x 106

2 changeover
contacts
1 x 106

SmartWire-Darwin status

LED

SmartWire-Darwin station (slave)￫ Page 19

Function element
Contacts
Lifespan mechanical/electrical

LED display

Switchoperations

1 changeover
contact
1 x 106

–

–

–

–

1 changeover
contact
1 x 106

No

No

Yes

Yes

Yes

Yes

No

No

Yes

Yes

Diagnostics

Yes

Yes

No

No

Yes

Yes

Yes

Yes

Yes

Yes

FixingFront fixing

Base fixing

Front fixing

Base fixing

Front fixing

Base fixing

Front fixing

Base fixing

Front fixing

Base fixing

2010 CA08103002Z-EN

LED

1 changeover
contact
1 x 106

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

1/26

Darwin Technology
SWD DIL module, SWD PKE module, SWD NZM interface

SWD DIL module, SWD PKE module, SWD NZM interface

DIL-SWD-32-001

DIL-SWD-32-002

PKE-SWD-32

NZM-XSWD-704

GeneralStandards

Dimensions (W x H x D)

mm

IEC/EN 61131-2
EN 50178
IEC/EN 60947
45 x 38 x 76

45 x 38 x 76

45 x 38 x 76

35 x 90 x 101

Weight

kg

0.04

0.04

0.04

0.1

Mounting

on DILM7 … DILM38

on DILM7 … DILM38

on DILM7 … DILM32

Mounting position

as DILM7 … DILM38

as DILM7 … DILM38

as DILM … DILM32

Top-hat rail I
EC/EN 60715, 35 mm
Vertical

IP20

IP20

IP20

IP20

Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178,
VBG 4)
Vibrations (IEC/EN 61131-2:2008)
Constant amplitude 3.5 mm

Hz

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

Constant acceleration, 1 g

Hz

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

Shocks

9

9

9

9

mm

50

50

50

50

m

0.3

0.3

0.3

0.3

Overvoltage category

II

II

II

II

Pollution degree

2

2

2

2

Mechanical shock resistance(IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31

DropheightFree fall, packaged (IEC/EN 60068-2-32)
Electromagnetic compatibility (EMC)

Electrostatic discharge(IEC/EN 61131-2:2008)
Air discharge (Level 3)
Contact discharge (Level 2)
Electromagnetic fields(IEC/EN 61131-2:2008)
80 - 1000 MHz

kV

8

8

8

8

kV

4

4

4

4

V/m

10

10

10

10

1.4 - 2 GHz

V/m

3

3

3

3

2 - 2.7 GHz

V/m

1

1

1

1

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

EN 55011 Class A

Radio interference suppression(SmartWire-Darwin)
Burst (IEC/EN 61131-2:2008, Level 3)
Supply cables

kV

–

–

–

2

CAN/DP bus cable

kV

1

1

1

1

SmartWire-Darwin cables

kV

1

1

1

1

Radiated RFI (IEC/EN 61131-2:2008,
Level 3)

V

10

10

10

10

°C

-25 … +60

-25 … +60

-25 … +60

-25 … +55

Storage°C

Prevent with suitablemeasures-30 - 70

Prevent with suitablemeasures-30 - 70

Prevent with suitablemeasures-30 - 70

Prevent with suitablemeasures-40 - 70

Relative humidity, non-condensing(IEC/EN 60068-2-30)%

5 … 95

5 … 95

5 … 95

5 … 95

SmartWire-Darwin
station (slave)
Automatic

SmartWire-Darwin
station (slave)
Automatic

SmartWire-Darwin
station (slave)
Automatic

SmartWire-Darwin
station (slave)
Automatic

Ambient climatic conditions
Operating ambient temperature(IEC 60068-2)
Condensation

SmartWire-Darwin network
Station type
Address setting
Status SmartWire-Darwin

Green/orange

Green/orange

Green/orange

Green

Connections

LED

Plug, 8 polePlug, 8 polePlug, 8 polePlug, 8 pole

Plug connectors

Device plug
SWD4-8SF2-5￫ Page 19

Device plug
SWD4-8SF2-5

Device plug
SWD4-8SF2-5

Device plug
SWD4-8SF2-5

Current consumption (15 V SWD supply)

2010 CA08103002Z-EN

www.eaton.com

Darwin Technology

1/27

SWD DIL module, SWD PKE module, SWD NZM interface

DIL-SWD-32-001

DIL-SWD-32-002

PKE-SWD-32

NZM-XSWD-704

Manual/automatic mode

No

Yes

Yes

–

Setting–

Rotary switch

Rotary switch

–

2

2

–

–

15

15

–

–

Self-supplied

Self-supplied

–

–

3

3

–

–

No

No

–

–

≦2.8

≦2.8

–

–

Push-in terminals

Push-in terminals–

Push-in terminals

Operation mode

Connection auxiliary contact
NumberRated voltage
Input current at 1 signal, typical

Ue

V DC
mA

Potential isolation
Cable lengthmTerminal type
Terminal capacity
Solid

mm2

0.2 - 1.5 (AWG 24 - 16)

0.2 - 1.5 (AWG 24 - 16)

0.2 - 1.5 (AWG 24 - 16)

0.2 - 1.5 (AWG 24 - 16)

Flexible with ferrule

mm20.25 - 1.5

0.25 - 1.5

0.25 - 1.5

0.25 - 1.5

Minimum length 8 mm

Minimum length 8 mm

Minimum length 8 mm

Minimum length 8 mm2010 CA08103002Z-EN

www.eaton.com

1/28

Darwin Technology

Darwin Technology

Accessories

1/29

Accessories

Accessories

Part no.

SWD4-RC8-10

SWD4-8SF2-5

SWD4-8SFF2-5

SWD4-SF8-20

SWD4-SM8-20

SWD4-8FRF-10

SWD4-SFL8-20

SWD4-SML8-20

IEC/EN 61131-2
EN 50178
15 x 36.5 x 17.5

IEC/EN 61131-2
EN 50178
48.5 x 34.5 x 10

IEC/EN 61131-2
EN 50178
24 x 26 x 162

IEC/EN 61131-2
EN 50178
24 x 26 x 170

IEC/EN 61131-2
EN 50178
35 x 90 x 35

IEC/EN 61131-2
EN 50178
35 x 83 x 40

IEC/EN 61131-2
EN 50178
35 x 83 x 46

GeneralStandards
Dimensions (W x H x D)

mm

IEC/EN 61131-2
EN 50178
48.5 x 34.5 x 10

Weight

kg

–

–

–

–

–

–

–

–

Weight

g

10

5.5

4.5

20

22.5

42

50

50

Any

Any

Any

Any

Any

Any

Any

Any

IP20

IP20

IP20

IP67

IP67

IP20

IP67

IP67

Mounting position
Ambient mechanical conditions
Protection type (IEC/EN 60529, EN50178, VBG 4)
Vibrations (IEC/EN 61131-2:2008)
Constant amplitude 3.5 mm

Hz

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

5 … 8.4

Constant acceleration, 1 g

Hz

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

8.4 … 150

Shocks

9

9

9

–

–

9

9

9

mm

50

–

–

–

–

–

–

–

m

0.3

–

–

–

–

–

–

–

Overvoltage category

II

–

–

–

–

–

–

–

Pollution degree

2

–

–

–

–

–

–

–

Mechanical shock resistance (IEC/EN 60068-2-27)
semi-sinusoidal 15 g/11 ms
Drop to IEC/EN 60068-2-31
Free fall, packaged (IEC/EN 60068-2-32)

DropheightElectromagnetic compatibility (EMC)

Electrostatic discharge (IEC/EN 61131-2:2008)
Air discharge (Level 3)

kV

8

–

8

–

–

8

8

8

Contact discharge (Level 2)

kV

4

–

4

–

–

4

4

4

Electromagnetic fields (IEC/EN 61131-2:2008)
80-1000 MHz

V/m

10

–

–

–

–

–

10

10

1.4 - 2 GHz

V/m

3

–

–

–

–

–

3

3

2 - 2.7 GHz

V/m

1

–

–

–

–

–

1

1

EN 55011 Class A

–

–

–

–

–

–

–

Radio interference suppression (SmartWire-Darwin)
Burst (IEC/EN 61131-2:2008, Level 3)
SmartWire-Darwin cables

kV

1

–

–

–

–

–

–

–

V

10

–

–

–

–

–

10

10

°C

-25 … +55

-25 … +55

-25 … +55

-25 … +55

-25 … +55

-25 … +55

-25 … +55

-25 … +55

Storage°C

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Prevent with suitablemeasures-40 - 70

Relative humidity, non-condensing (IEC/EN 60068-2-30)%

5 … 95

5 … 95

5 … 95

5 … 95

5 … 95

5 … 95

5 … 95

5 … 95SWD-InPlug, 8 pole

Plug connector

Plug, 8 pole–Plug, 8 polePlug, 8 polePlug, 8 polePlug, 8 pole

Number of insertion cycles

≥ 200

≥1

≥ 200

–

≥ 500

≥ 200

≥ 200

≥ 500

SWD-Out–

Socket, 8 polePlug, 8 pole

Socket, 8 pole–

Push-in terminals

Socket, 8 polePlug, 8 pole

Number of insertion cycles

–

≥ 200

≥ 200

≥ 500

–

–

≥ 500

≥ 200

Current consumption (15 V SWD supply)￫ Page 19

Radiated RFI (IEC/EN 61131-2:2008, Level 3)
Ambient climatic conditions
Operating ambient temperature (IEC 60068-2)
Condensation

Connection options

2010 CA08103002Z-EN

www.eaton.com￫ Page 192010 CA08103002Z-EN

www.eaton.com

1/30

Darwin Technology
SWD RMQ connections

Dimensions
SWD RMQ connections

SWD gateways, input/output module, power feed modules
EU5C-SWD-DP

90

EU5C-SWD-DP
EU5C-SWD-CAN
EU5E-SWD-...
EU5C-SWD-PF...

35

a
122
122
97
120

4.5
a

SWD contactor modules

38

DIL-SWD-32-001
DIL-SWD-32-002

45

53.1
72.3

SWD PKE module

39

PKE-SWD-32

45

61.1
80.6

Fixing adapter (front fixing) for 3-contact/LED elements

Function elements

M22-A-…

M22-SWD-K...
M22-SWD-LED…
M22-A
M22-SWD-A4

19.3

19.3
30

40

SWD soft starter DS7
DS7-34DSX
Dimension ￫ Chapter "Soft starter"

SWD interface for NZM circuit-breakers
Dimensions ￫ Chapter " NZM Circuit-breakers"

2010 CA08103002Z-EN

www.eaton.com

a

45

21.5

25.7

M22-SWD-A4

64

a
44
48

Darwin Technology

1/31

Accessories
Accessories

Network terminator

Coupler

SWD4-8SF2-5

SWD4-RC8-10

SWD4-8SFF2-5

14.9

25.9

25.9

10.15

Ø 24

3

3

24

151

12.5

SWD4-SFL8-20

4

12

14

14

M18 x 0.75

Switch cabinet bushing socket

SWD4-SM8-20
M18 x 0.75

Switch cabinet bushing plug

M20 x 1.5

SWD4-SF8-20
M20 x 1.5

Housing bushing socket

SWD4-SM8-20
Ø 24

Housing bushing plug

144

10.15

34.3

34.3

24

48.4

36.4

4

4

30

48.4

12.8

17.2

Device plug

82.4

82.4

4

21

35

21

Adapter for blade terminal to round cable

Plug connector for SWD round cables, straight

SWD4-8FRF-10

SWD4-SF8-67

o 18.5o 18.5

SWD4-SM8-67

45

M16 x 0.75

35

90

44.5

35

23.2
36

Plug connector for SWD round cables, angled
SWD4-SM8-67W
o 18
37.1

37.4

o 18

SWD4-SF8-67W

M16 x 0.75

20

20

M16 x 0.75

30.8

30.8
54

55

2010 CA08103002Z-EN

www.eaton.com