Worldwide Locations
U.S.A
Sumitomo Machinery Corporation of America(SMA)
4200 Holland Blvd. Chesapeake, VA 23323, U.S.A.
TEL (1)757-485-3355 FAX (1)757-485-7490
CanadaSM Cyclo of Canada, Ltd. (SMC)
1453 Cornwall Road, Oakville, Canada ON L6J 7T5
TEL (1)905-469-1050 FAX (1)905-469-1055
MexicoSM Cyclo de Mexico, S.A. de C.V. (SMME)
Av. Desarrollo 541, Col. Finsa, Guadalupe,
Nuevo León, México, CP67132
TEL (52)81-8144-5130 FAX (52)81-8144-5130
BrazilSumitomo Industrias Pesadas do Brasil Ltda.
(SHIB)
Rodovia do Acucar (SP-075) Km 26
Itu, Sao Paulo, Brasil
TEL (55)11-4886-1000 FAX (55)11-4886-1000
Chile
SM-Cyclo de Chile Ltda. (SMCH)
Camino Lo Echevers 550, Bodegas 5 y 6,
Quilicura, Región Metropolitana, Chile
TEL (56)2-892-7000
FAX (56)2-892-7001
Argentina
SM-Cyclo de Argentina S.A. (SMAR)
Ing Delpini 2230, B1615KGB Grand Bourg,
Malvinas Argentinas, Buenos Aires, Argentina
TEL (54)3327-45-4095 FAX (54)3327-45-4099
GuatemalaSM Cyclo de Guatemala Ensambladora, Ltda.
(SMGT)
Parque Industrial Unisur, 0 Calle B 19-50 Zona 3,
Bodega D-1 Delta Bárcenas en Villa Nueva, Guatemala
TEL (502)6648-0500 FAX (502)6631-9171
Colombia
SM Cyclo Colombia, S.A.S. (SMCO)
Parque Industrial Celta, Km 7.0 Autopista Medellín,
Costado Occidental, Funza, Cundinamarca, Colombia
TEL (57)1-826-9766
Peru
SM Cyclo de Perú, S.A.C (SMPE)
Jr. Monte Rosa 255, Oficina 702, Lima,
Santiago de Surco, PerúTEL (51)1-713-0342
FAX (51)1-715-0223
Germany
Sumitomo (SHI) Cyclo Drive Germany GmbH
(SCG)
Cyclostraße 92, 85229 Markt Indersdorf, Germany
TEL (49)8136-66-0
FAX (49)8136-5771

Austria
Sumitomo (SHI) Cyclo Drive Germany GmbH(SCG)SCG Branch Austria Office
Gruentalerstraße 30A, 4020 Linz, Austria
TEL (43)732-330958 FAX (43)732-331978

Korea
Sumitomo (SHI) Cyclo Drive Korea, Ltd. (SCK)Royal Bldg. 19 Rm. 913, 5 Saemunan-ro 5-Gil Jongro-Gu
Seoul, Korea 03173
TEL (82)2-730-0151
FAX (82)2-730-0156

Belgium
Hansen Industrial Transmissions NV (HIT)
Leonardo da Vincilaan 1, Edegem, Belgium
TEL (32)34-50-12-11 FAX (32)34-50-12-20

TaiwanTatung SM-Cyclo Co., Ltd. (TSC)
22 Chungshan N. Road 3rd., Sec. Taipei, Taiwan 104,
R.O.C.
TEL (886)2-2595-7275 FAX (886)2-2595-5594

FranceSM-Cyclo France SAS (SMFR)
8 Avenue Christian Doppler, 77700 Serris, France
TEL (33)164171717
FAX (33)164171718
Italy
SM-Cyclo Italy Srl (SMIT)
Via dell' Artigianato 23, 20010 Cornaredo (MI), Italy
TEL (39)293-481101 FAX (39)293-481103
Spain
SM-Cyclo Iberia, S.L.U. (SMIB)
C/Gran Vía Nº 63 Bis, Planta 1, Departamento 1B
48011 Bilbao–Vizcaya, SpainTEL (34)9448-05389 FAX (34)9448-01550
United Kingdom
SM-Cyclo UK Ltd. (SMUK)Unit 29, Bergen Way, Sutton Fields Industrial Estate,
Kingston upon Hull, HU7 0YQ, East Yorkshire,
United Kingdom
TEL (44)1482-790340 FAX (44)1482-790321
TurkeySM Cyclo Turkey Güç Aktarım Sis. Tic. Ltd. Sti.
(SMTR)
Barbaros Mh. Çiğdem Sk. Ağaoğlu, Office Mrk. No:1 Kat:4 D.18
Ataşehir, İstanbul, Turkey
TEL (90)216-250-6069 FAX (90)216-250-5556
India
Sumi-Cyclo Drive India Private Limited (SDI)
Gat No. 186, Raisoni Industrial Park, Alandi Markal Road,
Fulgaon-Pune, Maharashtra, India
TEL (91)96-0774-5353
China
Sumitomo (SHI) Cyclo Drive China, Ltd. (SCT)
11F, SMEG Plaza, No. 1386 Hongqiao Road,
Changning District, Shanghai, China （P.C. 200336）
TEL (86)21-3462-7877 FAX (86)21-3462-7922
Hong Kong
SM-Cyclo of Hong Kong Co., Ltd. (SMHK)
Rm 1301, CEO Tower, 77 Wing Hong Street,
Cheung Sha Wan, Kowloon, Hong Kong
TEL (852)2460-1881 FAX (852)2460-1882

Singapore
Sumitomo (SHI) Cyclo Drive Asia Pacific Pte.
Ltd. (SCA)
15 Kwong Min Road, Singapore 628718
TEL (65)6591-7800
FAX (65)6863-4238
Philippines
Sumitomo (SHI) Cyclo Drive Asia Pacific Pte. Ltd.
Philippines Branch Office (SMPH)
C4 & C5 Buildings Granville Industrial Complex, Carmona,
Cavite 4116, Philippines
TEL (63)2-584-4921
FAX (63)2-584-4922
Vietnam
SM-Cyclo (Vietnam) Co., Ltd. (SMVN)
Factory 2B, Lot K1-2-5, Road No. 2-3-5A,
Le Minh Xuan Industrial Park, Binh Chanh Dist.,
HCMC, Vietnam
TEL (84)8-3766-3709 FAX (84)8-3766-3710

HF-430NEO Series
Analog Input/Output option
Model : P1-AG
Userʼs Guide

Malaysia
SM-Cyclo (Malaysia) Sdn. Bhd. (SMMA)
No.7C, Jalan Anggerik Mokara 31/56, Kota Kemuning,
Seksyen 31, 40460 Shah Alam, Selangor Darul Ehsan,
Malaysia
TEL (60)3-5121-0455 FAX (60)3-5121-0578
Indonesia
PT. SM-Cyclo Indonesia (SMID)
Jalan Sungkai Blok F 25 No. 09 K, Delta Silicon III,
Lippo Cikarang, Bekasi 17530, Indonesia
TEL (62)21-2961-2100 FAX (62)21-2961-2211
Thailand
SM-Cyclo (Thailand) Co., Ltd. (SMTH)
195 Empire Tower, Unit 2103-4, 21st Floor, South
Sathorn Road, Yannawa, Sathorn, Bangkok 10120,
ThailandTEL (66)2670-0998
FAX (66)2670-0999
Australia
Sumitomo (SHI) Hansen Australia Pty. Ltd.
(SHAU)
181 Power St, Glendenning, NSW 2761, Australia
TEL (61)2-9208-3000 FAX (61)2-9208-3050
Japan
Sumitomo Heavy Industries, Ltd. (SHI)
ThinkPark Tower, 1-1 Osaki 2-chome, Shinagawa-ku,
Tokyo 141-6025, JapanTEL (81)3-6737-2511 FAX (81)3-6866-5160

NOTICE

Specifications, dimensions, and other items are subject to change without prior notice.

Power Transmission & Controls Group
Headquarter ThinkPark Tower, 1-1 Osaki 2-chome, Shinagawa-ku, Tokyo 141-6025, Japan

No.DM3412E-1.0
EA10 Printed 2020.03

1. Make sure that this userʼs guide is delivered to the end userof inverter unit.
2. Read the instruction manual and userʼs guide before installing or
operating the inverter unit, and store it in a safe place for reference.

Userʼs Guide DM3412E-1

Copyright © 2020 Sumitomo Heavy Industries,Ltd. All rights reserved.
All rights reserved. No part of this publication may be reproduced, stored in a retrieval system, ortransmitted, in any form or by any means, mechanical, electronic, photocopying, recording, or otherwise,
without the prior written permission of Sumitomo. No patent liability is assumed with respect to the use of
the information contained herein. Moreover, because Sumitomo is constantly striving to improve its
high-quality products, the information contained in this manual is subject to change without notice. Every
precaution has been taken in the preparation of this manual. Sumitomo assumes no responsibility forerrors or omissions. Neither is any liability assumed for damages resulting from the use of the information
contained in this publication.

Introduction
Introduction
Thank you for purchasing the P1-AG: Analog Input/Output option for HF-430NEO series inverter.
This instruction manual describes how to handle and maintain the P1-AG. Please read this manual carefully
before using the P1-AG, and keep it handy for those who operate, maintain and inspect it.

■User's Guide(this document)
The User's Guide provides detailed information necessary for handling the product.
Please make sure to read User's Guide for proper use.
Always use the P1-AG strictly within the range described in the User's Guide and perform proper inspection
and maintenance to prevent failures or accidents.
The latest version of the User's guide can be obtained through our website.

■Handling the inverter HF-430NEO
For handling the HF-430NEO, please make sure to read its Instruction manual and User's Guide.

■For a proper use
Before using the inverter, please read carefully the HF-430NEO Instruction manual and User's Guide, theP1-AG User's Guide.
In Addition any personnel handling or performing maintenance of the product must read carefully the HF430NEO Instruction manual and User's Guide, the P1-AG User's Guide.
Before any attempt to install, operate, maintain or inspect this equipment, a complete understanding of theequipment specifications, safety instructions, precautions, handling and operation instructions is required.
Please follow all the specifications and instructions for a proper use. Additionally, periodically review the
HF-430NEO Instruction manual and User's Guide, the P1-AG User's Guide.

■Precautions
It is prohibited to reproduce or reform this document partially or totally in any form without the publisher's
permission.
The contents of the document are subject to change without prior notice.
Any handling, maintenance or operation method NOT described on the HF-430NEO Instruction manualand User's Guide, the P1-AG User's Guide is not covered by the product warranty.
Please DO NOT perform any procedure NOT described on the HF-430NEO or the P1-AG manuals since it
can be the cause of unexpected failures or accidents.
We are not responsible for any impact from operations regardless of unexpected failure or accident due tooperation or handling of the product in a manner not specified on the HF-430NEO Instruction manual andUser's Guide, the P1-AG User's Guide. We appreciate your understanding.
Note that, in case the HF-430NEO Instruction manual and User's Guide, the P1-AG User's Guide areenclosed, they should be delivered to the end user of the inverter. Also make sure to download and keep
accessible any other related guides or instruction manuals for the end user.

■Trademark
・CRIMPFOX® is a registered trademark of Phoenix Contact GmbH & Co. KG.
・ Any other brand names and product names mentioned in this guide are trademarks or registeredtrademarks of their respective owners.

S-1

Table of Contents
Table of Contents●●

Introduction.................................................... S-1
Table of Contents .......................................... S-2

Chapter 1 Safety Precautions
1.3 Symbol explanation ....................................... 1-2
1.4 Precautions ..................................................... 1-2

1.1 About this chapter ...................................... 1-1
1.2 Types of warnings ........................................... 1-1

Chapter 2 Overview
2.4 Guide objectives............................................. 2-1
2.5 Guide outline .................................................. 2-2

2.1 About this chapter.......................................... 2-1
2.2 Applicable devices ......................................... 2-1
2.3 Before reading this guide .............................. 2-1

Chapter 3 Preparing for operation
3.3 Name plate ...................................................... 3-1
3.4 Dimensions after installed ............................ 3-2

3.1 About this chapter.......................................... 3-1
3.2 P1-AG appearance and nomenclature........ 3-1

Chapter 4 Enclosed Items
4.3 Verification after the purchase..................... 4-1

4.1 About this chapter.......................................... 4-1
4.2 About the enclosed items ............................. 4-1

Chapter 5 Installation and wiring
5.3 Terminal block and wiring ............................ 5-4

5.1 About this chapter.......................................... 5-1
5.2 Installation ....................................................... 5-1

Chapter 6 Function of Analog Input/Output
6.3 List of parameters related to the P1-AG ..... 6-2

6.1 About this chapter.......................................... 6-1
6.2 Terminal connection ...................................... 6-1

Chapter 7 Troubleshooting
7.3 Inverter troubleshooting ............................... 7-1
7.4 Any other trouble ........................................... 7-3

7.1 About this chapter.......................................... 7-1
7.2 Self-diagnosis .................................................. 7-1

Chapter 8 Specifications
8.2 Device Specifications .................................... 8-1

8.1 About this chapter.......................................... 8-1● Warranty ............................................... App.1-1

S-2

Safety Precautions

Chapter 1

Chapter 1 Safety Precautions

1

1.1 About this chapter
This chapter contains the information about Safety precautions during the installation, wiring, operationand inspection.
Before installation, wiring, operation, inspection, or usage please read completely and fully understandthis guide.

1.2 Types of warnings
In this guide, the safety precautions as well as residual risks are categorized by degree of risk as“Danger”, “Warning” and“Caution”.
The definition of each category is described below.

DangerThis category warns the user that in case of an incorrect or improper handling, it leads to a dangerous
situation that have a high risk of causing death, serious injuries and/or major property damage.

Warning
This category warns the user that in case of an incorrect or improper handling, it leads to a dangerous
situation that may cause death, serious injuries and/or major property damage.

CautionThis category warns the user that in case of an incorrect or improper handling, it leads to a dangerous
situation that may cause physical injuries and/or property damage.

However, any content labeled with “ Caution” and depending on the case, might have a possibility ofleading to a highly dangerous situation.
It is extremely important that you follow the instructions and warnings.
Furthermore, content labeled with “ ”must be followed and paid special attention.

1-1

Safety Precautions

Chapter 1
1.3 Symbol explanation

In this guide, there are some explanatory notes using different symbols. Please pay attention to thiscontent and keep in mind itsinformation.
Symbol definition
When handling this product, this symbol indicates danger, warning or caution about
ignition, electric shock, high temperature or other dangers.
Inside or near thesymbol, the specific content will be shown.

This symbol indicates “General hazard not specified, be cautious”.

This symbol indicates “Electric shock hazard”.
This symbol indicates prohibited actions“Actions that should not be done” when handling
this device.
This symbol indicates actions that must be done based on the instructions.

1.4 Precautions
1.4.1 Please be careful!

Danger・If handled incorrectly or improperly, it might cause death, serious physical injuries, or damage tothe inverter, motor or even the entire system.
CautionDo・Before installation, wiring, operation, inspection, or usage please read and fully understand thisguide and other references.

・There will be additional warnings about hazards and failure causes in other chapters.
Caution・Before installation, wiring, operation, inspection, or usage please read and fully understand thisguide.
Do・In order to explain this device details the illustrations in this guide might show this device without
covers.
CautionDo・Before operating this device please return all the covers to the original position, and follow all thenecessary regulations and instructions written in this guide.

1-2

Safety Precautions

Chapter 1
1.4.2 Precautions during the installation！

Danger● Risk of Fire!
Fire・DO NOT place inflammable objects nearby
Hazard・DO NOT let scraps of wire, welding sputtering, irons scraps or other objects get inside the device.
・Avoid installing this device in places with high temperature, high humidity, Condensation-prone

Prohibited conditions, dusty conditions, corrosive gas, explosive gas, flammable gas, grinding fluid mist,hydrogen sulfide or salt damage prone conditions. Additionally, it is recommended to install thisdevice in ventilated room not exposed to direct sunlight.
Do● Risk of Injury!
Injury・DO NOT install or operate products with damage or missing parts.
Prohibited● Risk of an Inverter failure!
Failure ・This device is a precision equipment, DO NOT drop it, or give it a strong shock.

・DO NOT get on (step on) or place heavy objects on this device.
・When handling the object, avoid places prone to static electricity(like carpets).

Do・Since the human body can get charged with static electricity, as a safety measure please toucha safe metallic surface before handling this device.

1.4.3 Precautions during the wiring!

Danger● Risk of an electric shock and/or fire!
Electric ・Be sure to ground the inverter.
shock ・Entrust the wiring work only to a qualified electrician.
and Fire
hazard ・Before the wiring work make sure to turn off the power supply and wait for more than 10 or 15
minutes depending on the inverter model.＊Confirm that the charge lamp is OFF and the DC voltage between terminals P and N is 45 V orDo
less.
＊For HF4322-5A5 to HF4322-022, HF4324-5A5 to HF4324-022 models the wait time is 10 minutes.
For HF4322-030 to HF4322-055, HF4324-030 to HF4324-055 models the wait time is 15 minutes.

Failure● Risk of inverter failure!
・DO NOT pull any wire after wiring.

Prohibited

1-3

Safety Precautions

Chapter 1● Risk of an electric shock and/or injury!
Electric
shock ・Perform the wiring only after installing the inverter.
andinjuryDo

Warning● Risk of an electric shock and/or injury!
Electric
shock ・DO NOT operate/switch any of the switches from the 4 pole DIP switch on this device.＊andWhen this device is shipped all switches are turned off.
injury・If any of the switches from the 4 pole DIP switch is operated/switched, this device will not work
as intended and it might be the cause of failure.
・Please handle the cables properly and DO NOT let them get damaged. Using damaged cables willDo
not only interfere with the correct operation of this device but also might be the cause of a system
failure.
＊ 4 pole DIP switch is implemented on the board exposed from the case of this product.

● Risk of Fire!
Fire
hazard ・Please tighten the screws and bolts with the specified torque.

Do(Please refer to the inverter user's guide)
・Verify that none of the screws and bolts are loose.
・Make sure that the inverter and this device are fixed together with the securing screw.
・Make sure that the connectors are properly fixed.

1.4.4 Precautions during operation and trial operation!

Danger● Risk of an electric shock or fire!
Electric
・DO NOT touch the inside of this device, check the signal, do any wiring or plug/unplug theshock
and Fire connectors while it energized.
hazard・DO NOT insert any sick or rod like objects inside this device while it is energized.

Prohibited● Risk of an injury and/or fire!
Injuryand Fire・DO NOT touch the inside of this device or the inverter while they are energized.
hazardProhibited

1-4

Safety Precautions

Chapter 1● Risk of an electric shock!
Electric・Make sure to fasten all the screws of this device before turning it on. DO NOT detach this device
shock

while it is energized or the inverter capacitors are still charged.
・Additionally DO NOT touch the inside of the inverter while the inverter capacitors are still charged.
・DO NOT touch this device with wet hands.

Prohibited

Warning● Risk of an injury and/or device damage!
Injury or・By using this device it becomes easier to change the settings and the output frequency of thedeviceinverter. When changing the settings or the output frequency of the inverter please make sure
Damagethat it is within the supported range by the gear motor and/or the equipment.
・In case this device is being used to make the inverter produce high frequency outputs for a motor
or other equipment, make sure with the respective manufacturer that the motor or the equipment
can tolerate the high frequency output given by the inverter.
Do・During operation verify the motor rotation direction, and that there are no irregular sounds orvibrations.

1.4.5 Precautions during Maintenance/ Inspection!

Danger● Risk of an electric shock!
Electric
shock ・Before the wiring work make sure to turn off the power supply and wait for more than 10 or 15

Do

minutes depending on the inverter model.＊(Confirm that the charge lamp is OFF and the DC voltage between terminals P and N is 45 Vor less.)

・Entrust the maintenance, inspection and/or part replacement only to a specialized personnel.
(Be sure to remove wristwatches and metal accessories, e.g., bracelets, before maintenance andProhibited
inspection work and use insulated tools for the work).

＊For HF4322-5A5 to HF4322-022, HF4324-5A5 to HF4324-022 models the wait time is 10 minutes.
For HF4322-030 to HF4322-055, HF4324-030 to HF4324-055 models the wait time is 15 minutes.

1-5

Safety Precautions

Chapter 1
1.4.6 Precautions for disposal!

Danger● Risk of an injury and/or an explosion!
・Outsource to a qualified industrial waste disposal contractor when discarding this device.
Injury andDisposing of this device on your own may result in the production of poisonous gas
explosion
hazard ・Contact your sales agent if you need to get this device fixed.

・A qualified waste disposer includes industrial waste collector/transporter and industrial waste
disposal operator. Follow all laws and decrees related to procedures of waste management andDopublic cleansing when disposing of this device.

1.4.7 Other Precautions

Danger● Risk of an injury, an electric shock and/or fire!
Electricshock
injuryand Fire
hazard・DO NOT modify this device.

Prohibited＊In addition to the precautions described above, there are other precautions described in the chapter 8of the inverter user's guide. Please read and follow those precautions as well.

1-6

Overview

Chapter 22Chapter 2 Overview
2.1 About this chapter

This chapter specifies the devices that this guide will describe. Additionally, it contains informationnecessary to clearly understand this guide, the objectives of this guide.

2.2 Applicable devices
The contents of this guide will apply to the P1-AG device. For information about the inverter please referto the HF-430NEO user's guide or the instruction manual.

2.3 Before reading this guideThis guide is aimed for people who purchase, handle, install or connect control equipment, design
systems or manage factories.
This guide units are based on the SI system.

2.4 Guide objectives
The objectives of this guide are:・explain how to wire and connect the device.
・explain how to set the necessary parameters.

2-1

Overview

Chapter 2
2.5 Guide outline
This guide has the following structure.

● The chapter 1: Safety Precautions"Safety Precautions" contains the safety instructions for installing, wiring, operating, maintaining andinspecting this device.

● The chapter 2: Overview"Overview" contains information necessary to clearly understand this guide.

● The chapter 3: P1-AG"About the P1-AG" contains the explanation about this device appearance and general features.

● The chapter 4: Enclosed Items"Enclosed Items" contains information about the items included with this device.

● The chapter 5: Installation and Wiring"Installation and Wiring" contains information for installing and wiring this device on the inverter.

● The chapter 6: Function of Analog Input/Output"Function of Analog Input/Output" contains the explanation of the inverter parameters that relate withthis device.

● Chapter 7: Troubleshooting"Troubleshooting" contains the explanation of inverter error (trip) status and its trouble shooting while
in use this device.

● Chapter 8: Specifications"Specifications" contains the specifications of this device.

2-2Chapter 3

P1-AG

3

Chapter 3 P1-AG
3.1 About this chapter

This chapter contains the explanation about this device external features and information on the nameplate.

3.2 P1-AG appearance and nomenclature
An external view of this device is shown below.
For installing this device, connectors and other parts refer to the chapter 5 "Installation and Wiring".

Input/Output terminal

FG Terminal
Name Plate (Bottom)

3.3 Name plate
The P1-AG name plate gives the following information.
Device model

P1-AG
Factory control number○○○○

Ver.▽▽▽＊＊＊＊＊＊＊△□□□□
Manufacture number (MFG No.)

3-1

VersionChapter 3

P1-AG

3.4 Dimensions after installed

96.5mmThe dimensions of this device after it is installed on the HF-430NEO are shown in the image below.
As shown on the image a part of this device will stand out from the HF-430NEO.
Please be cautious when installing the P1-AG.

HF-430NEO
Inverter

47 mm
HF-430NEO
Front surface
View from the right side of HF-430NEO

3-2

Chapter 4

Enclosed Items

4

Chapter 4 Enclosed Items
4.1 About this chapter
This chapter contains information about the items enclosed with the P1-AG.
Additionally, it is explained how to inspect and verify this product after its purchase.

4.2 About the enclosed items
・Enclosed items

P1-AG x1

Connector x1

User's guide x1

Name label x1

Contact your sales agent immediately in case there are defects or imperfections.

4.3 Verification after the purchase
4.3.1 Verification when unpacking
・Please verify the items written on the right when unpacking.
・In case there is any doubt or trouble with the product please contact your sales agent as soon as
possible.
Check that the items were not smashed or damaged during the delivery.

Check that
there is a P1-AG,
there is a connector,
there is a User's Guides,
there is a name label,when unpacking.

Please check again that your order match with the name plate of the device.

4-1

Installation and Wiring

Chapter 55Chapter 5 Installation and Wiring

5.1 About this chapter
This chapter contains information for installing and wiring this device on the HF-430NEO.
For information about the HF-430NEO installation, please refer to the HF-430NEO user's guide.
Additionally, when doing any work or operation, always follow the safety instructions and cautions givenin the chapter 1.

5.2 Installation
5.2.1 Installation
The P1-AG can be attached to any of the 3 option slots of HF-430NEO inverter.

It can be attached to either SLOT1, 2 or 3.

Option cassette connection slots
SLOT1
RJ45

KeypadUSB(micro-B)

5-1

SLOT2

SLOT3

Installation and Wiring

Chapter 55.2.2 How to install
For explanation purposes, it will be assumed that the P1-AG is going to be installed in the SLOT1.
(1) Remove the cover of the option cassette connection slot. Despite the removed cover will no longer
be needed, it is recommended to keep it in a safe place. However the screw that secured the cover
will be used to secure the P1-AG.

Option cassette connection slots
SLOT1

SLOT2

SLOT3

RJ45

Remove the screw and thenKeypadremove the cover.
The screw will be used later.

USB(micro-B)(2) Attach the P1-AG. The slots 2 and 3 have one more connection in the lower side.
However, the P1-AG will not need that connection.

Option cassette connection slots
SLOT1

SLOT2 SLOT3

RJ45

KeypadAttach the P1-AG to thisconnection.

USB(micro-B)

5-2

Installation and Wiring

Chapter 5(3) Secure the P1-AG with the screw removed in procedure (1).

Option cassette connection slots
SLOT1

SLOT2 SLOT3

RJ45

KeypadFasten the screw.

USB(micro-B)(4) Connect the FG terminal to functional ground.

Option cassette connection slots
SLOT1

SLOT2 SLOT3

RJ45

KeypadConnect to functional ground.

USB(micro-B)

5-3

Installation and Wiring

Chapter 5
5.3 Terminal block and wiring

Terminal arrangement, symbols and specifications of P1-AG are shown the followings.
■Terminal arrangement

1
2
3
4
5
6
7
8
9
10
11
12
13

14
15
16
17
18
19
20
21
22
23
24
25
26

Vi4
Ii4
L
Si4
L
Vi5
Ii5
L
Si5
L
Vi6
L
L

Vo3
Io3
L
So3
L
Vo4
Io4
L
So4
L
Vo5
L
L

FG
■Terminal specifications
Terminal Name

Analog Input

Description

Electrical Characteristic

Vi4

Voltage input 4:
0 to 10V

Input impedance: 10kΩ(approximately)
Allowable range of input: -0.3 to 12V

Ii4

Current input 4:
0 to 20mA

Input impedance: 100Ω(approximately)
Allowable range of input: 0 to 24mA

Si4

Select input 4:
voltage or current

Shorted Si4 to L: Vi4 enabled(initial condition)
Opened Si4: Ii4 enabled

Vi5

Voltage input 5:
0 to 10V

Input impedance: 10kΩ(approximately)
Allowable range of input: -0.3 to 12V

Ii5

Current input 5:
0 to 20mA

Input impedance: 100Ω(approximately)
Allowable range of input: 0 to 24mA

Analog Input 5
SwitchSi5

Select input 5:
voltage or current

Shorted Si5 to L: Vi5 enabled(initial condition)
Opened Si5: Ii5 enabled

Analog Input
Terminal 6

Vi6

Voltage 6:-10 to 10V

Input impedance: 10kΩ(approximately),
allowable range of input: -12 to 12V

Vo3

Voltage output 3:
0 to 10V

Maximum output current: 2mA
Allowable range: 0 to 10V(±10% accuracy)

Io3

Current output 3:
0 to 20mA

Allowable load impedance: 250Ω or less
Allowable range : 0 to 20mA(±20% accuracy)

So3

Select output 3:
voltage or current

Shorted So3 to L: Vo3 enabled(initial condition)
Opened So3: Io3 enabled

Vo4

Voltage: 0 to 10V

Maximum output current: 2mA
Allowable range: 0 to 10V(±10% accuracy)

Io4

Current: 0 to 20mA

Allowable load impedance: 250Ω or less
Allowable range : 0 to 20mA(±20% accuracy)

Analog Output 4
SwitchSo4

Select output 4:
voltage or current

Shorted So4 to L: Vo4 enabled(initial condition)
Opened So4: Io4 enabled

Analog Output
Terminal 5

Vo5

Voltage output 5:-10 to 10V

Maximum output current: ±2mA
Allowable range: -10 to 10V(±10% accuracy)

Analog Input
Terminal 4
Analog Input 4
SwitchAnalog Input
Terminal 5

Analog Output
Terminal 3

Analog Output

SymbolAnalog Output 3
SwitchAnalog Output
Terminal 4

Input/Output Common

L

Reference potential(signal ground)

Functional GroundFG

Connect to the functional ground (the screw size: M3)

It cannot work the following terminal combinations simultaneously.
・Combination of Vi4 and Ii4 terminal ： Combination of Vi5 and Ii5 terminal
Besides, redundant terminals need to be opened, do not wire or connect them.
・Combination of Vo3 and Io3 terminal： Combination of Vo4 and Io4 terminal

5-4

Installation and Wiring

Chapter 5■Recommendation terminals
In order to make convenience to wiring and improve the connection, it's recommended to use the ferrule
terminals with the following specifications for signal wire.
Wire diameter

Ferrule terminal[mm2] (AWG)

model *1)L1[mm]

L2[mm]

φd[mm]

φD[mm]

0.25 (24)AI 0,25-10 YE

10.0

14.5

0.8

2.0

0.34 (22)AI 0,34-10 TQ

10.0

14.5

0.8

2.0

0.5 (20)

AI 0,5-10 WH

10.0

16.0

1.1

2.5

0.75 (18)AI 0,75-10 GY

10.0

16.0

1.3

3.4

*1) Manufacturer:
PHOENIX CONTACT GmbH & Co. KG
Crimping tool: CRIMPFOX® 6
Note that these specifications are different from the recommended ferrule terminals for the inverter.
■Wiring
Inserting the wire:①Inserting the ferrule terminal into the P1-AG connector. It will be easy to insert without any tools if use
the recommendation ferrule terminals. *2)*2) In case not using the recommendation ferrule terminal,
please insert it with a flat head screwdriver in the reverse
order of removal method.
Inserting wire

Pulling out the wire:①Pressing the grey part *3) on P1-AG connector with flat screwdriver（width 2.5mm or less） to open
the wire port.
②Pulling out the wire or the ferrule terminal while pressing the flat screwdriver.
③Pulling out the flat screwdriver.

Pressing the grey part *3)with flat screwdriver

Pulling out
the wire or
the ferrule terminal

Pulling out the flatscrewdriver*3) It is orange of the actual color that grey parton the connector.

■Detaching the connector
Pulling down the latch lever in the arrow direction as shown below, then pulling out the connector.

Pulling down the latch lever

Pulling out the connector

5-5Chapter 6

Functions of Analog Input/Output

Chapter 6

Function of Analog
Input/Output

6

6.1 About this chapter
This chapter contains the information about the inverter setting parameters related to this product.

6.2 Terminal connection
An example of terminal connection of P1-AG is as follows.

(+)

Vi4

Vo3

(-)

L

L

Analog Input 4 voltage

Analog Output 3 voltage
(+)

Vi5

Vo4

(-)

L

L

(±10V)
Analog Input 6 voltage
(0V)

Vi6

Vo5

L

L

Analog Input 5 voltage

Analog Output 4 voltage

Analog Output 5 voltage

P1-AG terminal block
(+)

Ii4

Io3

(-)

L

L

Analog Input 4 current
Analog Output 3 current
(+)

Ii5

Io4

(-)

L

L

Analog Input 5 current
Analog Output 4 current

Si4

So3

L

L

Si5

So4

L

L

Analog Output 3 switch

Analog Input 4 switch

Analog Input 5 switch

Analog Output 4 switch

FG・Wiring the P1-AG, make sure that use the twisted pair cable with shield. In case of improper wiring, theinverter may malfunction caused by external noise. Make sure that the shield is wired to L terminal or
Ground terminal of the inverter. Additionally, do not be multipoint ground.
・Make sure that length of wiring to P1-AG must be 20 m or less. In case the length is more than 20 m, theinverter may malfunction caused by external noise.
・Make sure of wiring the FG terminal to functional ground.

6-1

Chapter 6

Functions of Analog Input/Output

6.3 List of parameters related to the P1-AG
The following table shows the inverter setting parameters related to this product. For information about
actual usage, please refer to the HF-430NEO User's guide.
■Parameter
CodeParameter name

Code

dA-60

Analog input/output status monitor

oE-14

Parameter name[Ai5] End value

dA-64

Analog input [Ai4] monitor

oE-15[Ai5] Start rate

dA-65

Analog input [Ai5] monitor

oE-16[Ai5] End rate

dA-66

Analog input [Ai6] monitor

oE-17[Ai5] Start point selection

dA-81

Option slot-1 statusoE-21[Ai6] Filter time constantdA-82

Option slot-2 statusoE-23[Ai6] Start valuedA-83

Option slot-3 statusoE-24[Ai6] End value

oE-25[Ai6] Start rateoE-26

[Ai6] End rateoE-28

[Ai4] Voltage/Current bias adjustment

db-21
db-22

Reserved

db-23
AA101

Main speed input source selection, 1st-motor

oE-29[Ai4] Voltage/Current gain adjustment

AA201

Main speed input source selection, 2nd-motor

oE-30[Ai5] Voltage/Current bias adjustment

AA102

Sub speed input source selection, 1st-motor

oE-31[Ai5] Voltage/Current gain adjustment

AA202

Sub speed input source selection, 2nd-motor

oE-32[Ai6] Voltage bias adjustment

Ad-01

Torque reference input source selection

oE-33[Ai6] Voltage gain adjustment

Ad-11

Torque bias input source selection

oE-35[Ai4] Window comparator upper limit

Ad-40

Speed limit input source selection at torque control

oE-36[Ai4] Window comparator lower limit

AH-07

PID1 set-point 1 input source selection

oE-37[Ai4] Window comparator hysteresis width

AH-42

PID1 set-point 2 input source selection

oE-38[Ai5] Window comparator upper limit

AH-46

PID1 set-point 3 input source selection

oE-39[Ai5] Window comparator lower limit

AH-51

PID1 feedback 1 input source selection

oE-40[Ai5] Window comparator hysteresis width

AH-52

PID1 feedback 2 input source selection

oE-41[Ai6] Window comparator upper limit

AH-53

PID1 feedback 3 input source selection

oE-42[Ai6] Window comparator lower limit

AH-70

PID1 feed-forward input source selection

oE-43[Ai6] Window comparator hysteresis width

AJ-07

PID2 set-point input source selection

oE-44[Ai4] Operation level at disconnection

AJ-12

PID2 feedback input source selection

oE-45[Ai4] Operation level selection at disconnection

AJ-27

PID3 set-point input source selection

oE-46[Ai5] Operation level at disconnection

AJ-32

PID3 feedback input source selection

oE-47[Ai5] Operation level selection at disconnection

AJ-47

PID4 set-point input source selection

oE-48[Ai6] Operation level at disconnection

AJ-52

PID4 feedback input source selection

oE-49[Ai6] Operation level selection at disconnection

bA101

Upper frequency limit source selection, 1st-motor

oE-50[Ao3] Output monitor selection

bA201

Upper frequency limit source selection, 2nd-motor

oE-51[Ao4] Output monitor selection

bA110

Torque limit selection, 1st-motor

oE-52[Ao5] Output monitor selection

bA210

Torque limit selection, 2nd-motor

oE-56[Ao3] Output filter time constant

CA-70

Speed command selection when [F-OP] is active.

oE-57[Ao3] Data type selection

CC-01

Output terminal [UPF] function

oE-58[Ao3] Bias adjustment

CC-02

Output terminal [DRV] function

oE-59[Ao3] Gain adjustment

CC-03

Output terminal [X1] function

oE-60

Adjustment mode [Ao3] output level

CC-04

Output terminal [X2] function

oE-61[Ao4] Output filter time constant

CC-05

Output terminal [X3] function

oE-62[Ao4] Data type selection

CC-06

Output terminal [RL] function

oE-63[Ao4] Bias adjustment

CC-07

Output terminal [FL] function

oE-64[Ao4] Gain adjustment

oA-10

Operation selection at an option error (SLOT-1)

oE-65

Adjustment mode [Ao4] output level

oA-20

Operation selection at an option error (SLOT-2)

oE-66[Ao5] Output filter time constantoA-30

Operation selection at an option error (SLOT-3)

oE-67[Ao5] Data type selection

oE-01[Ai4] Filter time constantoE-68[Ao5] Bias adjustment

oE-03[Ai4] Start value

oE-69[Ao5] Gain adjustment

oE-04[Ai4] End value

oE-70

Adjustment mode [Ao5] output leveloE-05[Ai4] Start rate

PA-22

Output selection for the current monitor

oE-06[Ai4] End rate

PA-24

Output selection for the DC voltage monitoroE-07[Ai4] Start point selection

PA-26

Output selection for the output voltage monitor

oE-11[Ai5] Filter time constant

PA-28

Output selection for the torque monitor

oE-13[Ai5] Start value

PA-30

Output selection for the frequency matching

6-2

Troubleshooting

Chapter 7

Chapter 7 Troubleshooting

7

7.1 About this chapter
This chapter contains the troubleshooting of cases such as errors detected by the protection function,
warnings given by the warning function, or some cases in which the device is not working properly.
When the device is not working properly or there is any trouble, read this chapter before trying to solve theproblem. Use the following sections as a reference when dealing with these situations.

7.2 Self-diagnosis
The inverter tripped.
It is displaying an error. → Refer to this guide page 7-1「7.3 Inverter troubleshooting」

Please contact your supplier.
Before contacting the technical service, please confirm the items on the right.
(1)Inverter model,(2)Inverter manufacture number (MFG No.)(3)Option device model (P1-AG)(4)P1-AG manufacture number (MFG No.)
(5)Date of purchase(6)Inquiry contents
For information about how to check the (1) and (2) refer to the HF-430NEO user's guide.
For information about how to check the (3) and (4) refer to the chapter 3 in this guide.

7.3 Inverter troubleshooting
In case the some error was detected by the inverter, it stops the motor (trip) and gives a notice with therespective error code. When the trip occurs, the inverter display shows following screen.
TRIP

NRDY

M1

H07

Occurring trip
Overload MTR
E005 15/12/24 22:10
Out Freq：0.50Hz
Current：49.71APN Voltage：274.1Vdc
Status1
：Stop
List

oFW

46.49Hz----The number of E005 in the above is an error code. Abnormality related to this device and its solutions areshown the following.

7-1

Troubleshooting

Chapter 7■Abnormality and its solutions related with this product.

E060 / E069
Option 1 Error 0 / 9
E070 / E079
Option 2 Error 0 / 9
E080 / E089
Option 3 Error 0 / 9
When a communication error occurring between the P1-AG and the inverter, the inverter trips with thosecodes.
In case the communication error detected by the P1-AG, "E060, E070, or E080" is shown as the error code.
Additionally, in case the communication error detected by the inverter, "E069, E079, or E089" is shown as
the error code.
Those error codes "E06*, E07*, or E08*" depend on the slot in which the P1-AG is attached.
Issue▶

An erroroccurred in thecommunication
between the
P1-AG and theinverter.

Possible cause▶

Possible solution

・The P1-AG is notcorrectly attached.

・Refer to the chapter 5.3 "Installation", attach the P1-AG
again.

・There is anintruding object inbetween the P1-AG
and the inverter
connector.

・Remove the intruding object.

E068 Option 1 Error 8
E078 Option 2 Error 8
E088 Option 3 Error 8
In case the P1-AG is attached to the unsupported inverter, "E068, E078, or E088" is shown as the error
code.
Those error codes "E06*, E07*, or E08*" depend on the slot in which the P1-AG is attached.
Issue▶
An erroroccurred assoon as theinverter
powered on.

Possible cause▶

・The P1-AG is
attached to theunsupported
inverter.

Possible solution

・Refer to the chapter 5.2 "Supported inverters", attach
the P1-AG to the supported inverter.

7-2

Troubleshooting

Chapter 7
7.4 Any other troubles

In case the P1-AG does not work properly without any error codes of the inverter, refer to the following
solutions.
Issue▶

The function of
analoginput/output
does not work
properly.

Possible cause▶

Possible solution

・The P1-AG is notcorrectly attached.

・When a communication error occurring between the P1AG and the inverter, the P1-AG outputs 0V or 0mA in
analog output terminals.
Refer to the chapter 5.3 "Installation", attach the P1-AG
again.

・There is something
wrong with thewiring.

・Refer to the chapter 5.4 "Terminal Block and Wiring",
wire the P1-AG again.

7-3

Chapter 8

Specifications

8

Chapter 8 Specifications
8.1 About this chapter
This chapter contains information about the P1-AG specifications.

8.2 Device specifications■Specifications
Item

Specification

Model

P1-AG

WeightAmbient operating temperature

Environment

170 g-10 to 50℃

Ambient operating humidity

20 to 90%RH

Storage temperature *1)-20 to 65℃

Vibration resistance

5.9 m/s2(0.6G), 10 to 55 Hz

Conformance to EMC andelectrical safety standards

IEC/EN61800-3
Second environment, Category C3
IEC/EN61800-5-1 SELV

Enclosure rating

IP00

Analog input

0 to 10 V voltage input: 2 terminals
0 to 20 mA current input: 2 terminals

Analog output

0 to 10 V voltage output: 2 terminals
0 to 20 mA current output: 2 terminals

No icing or condensation conditions.

-10 to 10 V voltage input: 1 terminal-10 to 10 V voltage output: one terminalInterface

Analog input/output switch

0 to 10 V voltage/0 to 20 mA current input:
2 terminals
0 to 10 V voltage/0 to 20 mA current output:
2 terminals

Analog ground common

Reference potential(signal ground): 12 terminals*1) "Storage temperature" is the temperature during transportation.
When handling analog input/output signals, you need to use appropriate power supply for P1-AG and its
peripherals.

8-1

Warranty
Warranty
Warranty
periodThe warranty shall be 18 months from date of shipment or 12 months after initial
operation, whichever is shorter.

Warranty
condition

In the event that any problem or damage to the Product arises during the “Warranty
Period” from defects in the Product whenever the Product is properly installed andcombined with the Buyer’s equipment or machines maintained as specified in themaintenance manual, and properly operated under the conditions described in the
catalog or as otherwise agreed upon in writing between the Seller and Buyer or its
customers; the Seller will provide, at its sole discretion, appropriate repair or replacementof the Product without charge at a designated facility, except as stipulated in the“Warranty Exclusions” as described below.
However, if the Product is installed or integrated into the Buyer’s equipment or machines,
the Seller shall not reimburse the cost of: removal or re-installation of the Product orother incidental costs related thereto, any lost opportunity, any profit loss or otherincidental or consequential losses or damages incurred by the Buyer or its customers.

Warranty
exclusion

Not withstanding the above warranty, the warranty as set forth herein shall not apply to
any problem or damage to the Product that is caused by:
1.Installation, connection, combination or integration of the Product in or to the otherequipment or machine that rendered by any person or entity other than the Seller.
2.Insufficient maintenance or improper operation by the Buyer or its customers such that
the Product is not maintained in accordance with the maintenance manual provided ordesignated by the Seller;
3.Improper use or operation of the Product by the Buyer or its customers that is not
informed to the Seller, including, without limitation, the Buyer’s or its customers’
operation of the Product not in conformity with the specifications;4.Any problem or damage on any equipment or machine to which the Product isinstalled, connected or combined or any specifications particular to the buyer or its
customers;
5.Any changes, modifications, improvements or alterations to the Product or thosefunctions that are rendered on the Product by any person or entity other than the
Seller;6.Any parts in the Product that are supplied or designated by the Buyer or its customers;
7.Earthquake, fire, flood, salt air, gas, lightning, acts of God or any other reasons beyond
the control of the Seller;
8.Normal wear and tear, or deterioration of the Product’s parts, such as the cooling fan
bearings;
9.Any other troubles, problems or damage to the Product that are not attributable to theSeller.

OthersThe Seller will not be responsibility for the installation and removal of the inverter. Any
inverter transportation cost shall be born by both Seller and Buyer.

App.1-1

Worldwide Locations
U.S.A
Sumitomo Machinery Corporation of America(SMA)
4200 Holland Blvd. Chesapeake, VA 23323, U.S.A.
TEL (1)757-485-3355 FAX (1)757-485-7490
CanadaSM Cyclo of Canada, Ltd. (SMC)
1453 Cornwall Road, Oakville, Canada ON L6J 7T5
TEL (1)905-469-1050 FAX (1)905-469-1055
MexicoSM Cyclo de Mexico, S.A. de C.V. (SMME)
Av. Desarrollo 541, Col. Finsa, Guadalupe,
Nuevo León, México, CP67132
TEL (52)81-8144-5130 FAX (52)81-8144-5130
BrazilSumitomo Industrias Pesadas do Brasil Ltda.
(SHIB)
Rodovia do Acucar (SP-075) Km 26
Itu, Sao Paulo, Brasil
TEL (55)11-4886-1000 FAX (55)11-4886-1000
Chile
SM-Cyclo de Chile Ltda. (SMCH)
Camino Lo Echevers 550, Bodegas 5 y 6,
Quilicura, Región Metropolitana, Chile
TEL (56)2-892-7000
FAX (56)2-892-7001
Argentina
SM-Cyclo de Argentina S.A. (SMAR)
Ing Delpini 2230, B1615KGB Grand Bourg,
Malvinas Argentinas, Buenos Aires, Argentina
TEL (54)3327-45-4095 FAX (54)3327-45-4099
GuatemalaSM Cyclo de Guatemala Ensambladora, Ltda.
(SMGT)
Parque Industrial Unisur, 0 Calle B 19-50 Zona 3,
Bodega D-1 Delta Bárcenas en Villa Nueva, Guatemala
TEL (502)6648-0500 FAX (502)6631-9171
Colombia
SM Cyclo Colombia, S.A.S. (SMCO)
Parque Industrial Celta, Km 7.0 Autopista Medellín,
Costado Occidental, Funza, Cundinamarca, Colombia
TEL (57)1-826-9766
Peru
SM Cyclo de Perú, S.A.C (SMPE)
Jr. Monte Rosa 255, Oficina 702, Lima,
Santiago de Surco, PerúTEL (51)1-713-0342
FAX (51)1-715-0223
Germany
Sumitomo (SHI) Cyclo Drive Germany GmbH
(SCG)
Cyclostraße 92, 85229 Markt Indersdorf, Germany
TEL (49)8136-66-0
FAX (49)8136-5771

Austria
Sumitomo (SHI) Cyclo Drive Germany GmbH(SCG)SCG Branch Austria Office
Gruentalerstraße 30A, 4020 Linz, Austria
TEL (43)732-330958 FAX (43)732-331978

Korea
Sumitomo (SHI) Cyclo Drive Korea, Ltd. (SCK)Royal Bldg. 19 Rm. 913, 5 Saemunan-ro 5-Gil Jongro-Gu
Seoul, Korea 03173
TEL (82)2-730-0151
FAX (82)2-730-0156

Belgium
Hansen Industrial Transmissions NV (HIT)
Leonardo da Vincilaan 1, Edegem, Belgium
TEL (32)34-50-12-11 FAX (32)34-50-12-20

TaiwanTatung SM-Cyclo Co., Ltd. (TSC)
22 Chungshan N. Road 3rd., Sec. Taipei, Taiwan 104,
R.O.C.
TEL (886)2-2595-7275 FAX (886)2-2595-5594

FranceSM-Cyclo France SAS (SMFR)
8 Avenue Christian Doppler, 77700 Serris, France
TEL (33)164171717
FAX (33)164171718
Italy
SM-Cyclo Italy Srl (SMIT)
Via dell' Artigianato 23, 20010 Cornaredo (MI), Italy
TEL (39)293-481101 FAX (39)293-481103
Spain
SM-Cyclo Iberia, S.L.U. (SMIB)
C/Gran Vía Nº 63 Bis, Planta 1, Departamento 1B
48011 Bilbao–Vizcaya, SpainTEL (34)9448-05389 FAX (34)9448-01550
United Kingdom
SM-Cyclo UK Ltd. (SMUK)Unit 29, Bergen Way, Sutton Fields Industrial Estate,
Kingston upon Hull, HU7 0YQ, East Yorkshire,
United Kingdom
TEL (44)1482-790340 FAX (44)1482-790321
TurkeySM Cyclo Turkey Güç Aktarım Sis. Tic. Ltd. Sti.
(SMTR)
Barbaros Mh. Çiğdem Sk. Ağaoğlu, Office Mrk. No:1 Kat:4 D.18
Ataşehir, İstanbul, Turkey
TEL (90)216-250-6069 FAX (90)216-250-5556
India
Sumi-Cyclo Drive India Private Limited (SDI)
Gat No. 186, Raisoni Industrial Park, Alandi Markal Road,
Fulgaon-Pune, Maharashtra, India
TEL (91)96-0774-5353
China
Sumitomo (SHI) Cyclo Drive China, Ltd. (SCT)
11F, SMEG Plaza, No. 1386 Hongqiao Road,
Changning District, Shanghai, China （P.C. 200336）
TEL (86)21-3462-7877 FAX (86)21-3462-7922
Hong Kong
SM-Cyclo of Hong Kong Co., Ltd. (SMHK)
Rm 1301, CEO Tower, 77 Wing Hong Street,
Cheung Sha Wan, Kowloon, Hong Kong
TEL (852)2460-1881 FAX (852)2460-1882

Singapore
Sumitomo (SHI) Cyclo Drive Asia Pacific Pte.
Ltd. (SCA)
15 Kwong Min Road, Singapore 628718
TEL (65)6591-7800
FAX (65)6863-4238
Philippines
Sumitomo (SHI) Cyclo Drive Asia Pacific Pte. Ltd.
Philippines Branch Office (SMPH)
C4 & C5 Buildings Granville Industrial Complex, Carmona,
Cavite 4116, Philippines
TEL (63)2-584-4921
FAX (63)2-584-4922
Vietnam
SM-Cyclo (Vietnam) Co., Ltd. (SMVN)
Factory 2B, Lot K1-2-5, Road No. 2-3-5A,
Le Minh Xuan Industrial Park, Binh Chanh Dist.,
HCMC, Vietnam
TEL (84)8-3766-3709 FAX (84)8-3766-3710

HF-430NEO Series
Analog Input/Output option
Model : P1-AG
Userʼs Guide

Malaysia
SM-Cyclo (Malaysia) Sdn. Bhd. (SMMA)
No.7C, Jalan Anggerik Mokara 31/56, Kota Kemuning,
Seksyen 31, 40460 Shah Alam, Selangor Darul Ehsan,
Malaysia
TEL (60)3-5121-0455 FAX (60)3-5121-0578
Indonesia
PT. SM-Cyclo Indonesia (SMID)
Jalan Sungkai Blok F 25 No. 09 K, Delta Silicon III,
Lippo Cikarang, Bekasi 17530, Indonesia
TEL (62)21-2961-2100 FAX (62)21-2961-2211
Thailand
SM-Cyclo (Thailand) Co., Ltd. (SMTH)
195 Empire Tower, Unit 2103-4, 21st Floor, South
Sathorn Road, Yannawa, Sathorn, Bangkok 10120,
ThailandTEL (66)2670-0998
FAX (66)2670-0999
Australia
Sumitomo (SHI) Hansen Australia Pty. Ltd.
(SHAU)
181 Power St, Glendenning, NSW 2761, Australia
TEL (61)2-9208-3000 FAX (61)2-9208-3050
Japan
Sumitomo Heavy Industries, Ltd. (SHI)
ThinkPark Tower, 1-1 Osaki 2-chome, Shinagawa-ku,
Tokyo 141-6025, JapanTEL (81)3-6737-2511 FAX (81)3-6866-5160

NOTICE

Specifications, dimensions, and other items are subject to change without prior notice.

Power Transmission & Controls Group
Headquarter ThinkPark Tower, 1-1 Osaki 2-chome, Shinagawa-ku, Tokyo 141-6025, Japan

No.DM3412E-1.0
EA10 Printed 2020.03

1. Make sure that this userʼs guide is delivered to the end userof inverter unit.
2. Read the instruction manual and userʼs guide before installing or
operating the inverter unit, and store it in a safe place for reference.

Userʼs Guide DM3412E-1