MONITOR

MONITORPart Number:

GBB15Description
The GBB15 is a self-contained unit with on-board temperature and humidity/dew-point sensors. It has an input capacity offour external sensors.
The GBB15 allows users to keep an eye on remote conditions from a secure web interface and receive SNMP, Email, and text
message alert notifications when user-adjustable thresholds are exceeded.
The web interface provides an overview of environmental measurements with real time sensor data. No software required securely access the graphical user interface from a web browser. All measurements are logged allowing users to collect data
for trending and capacity management. The GBB15 offers flexible access rights and security settings with up to three accessaccount levels. It offers secure access through the web and supports HTTP and HTTPS protocols. Up to 50 customizable
alarms can be configured with alarm escalations per sensor.
Up to four digital sensors can be connected using a standard splitter. A variety of optional plug-and-play sensors are available
for use with the GBB15 including but not limited to, temperature, humidity, airflow, power usage and more.
The GBB15 is a compact solution weighing less than half a pound and sized to fit in a 1U space at 5.25"L x 1.75"H x 1.5”W,
which is perfect for tight installments. With an operating range of -25° to 80° Celsius (-13° to 176° F), the GBB15 can beused to monitor temperature, humidity and other environmental parameters in a variety of applications including IT, telecom,healthcare, food supply and others.

SNMP, Email & SMS Alerts
Trigger escalating alarms if temperature or humidity fall outside of specified parameters via SNMP (v1, v2c), email and SMSmessages (e-mail to SMS gateway). For example, specify an email notification to one or more users at 70° F, add anotherlayer of personnel to the email alarm at 80° F, add your third party contractor at 85° F. Users may specify up to 50 alarms perunit.

Interface Network IP Cameras
The Web page interfaces up to four IP cameras (not included), allowing you a quick view of remote conditions, especially
useful in event of alarm.

No Software Required
The GBB15 is simple to install and use, requiring noTemperature, Humidity/
special software other than a standard Web Browser.
Dewpoint, Airflow
The GBB15 connects to an Ethernet Network with astandard RJ45 connector and sends data in standard
TCP/IP packets. It is easily configured with a simple
menu using a Web Browser and can be password
protected with 3 access account level types: Administrator,
Temperature
Control, View Only. From within an Intranet or over theInternet, the user can securely access the monitor byentering its IP address.

6 VDC(optional on
GBB15POE)

MONITORMONITORPart Number:

GBB15Specifications:ElectricalMINMAX

Input Voltage

6VDC

18VDCEnvironmentalMIN

MAX

Operating Temperature-13 °F

176 °F

Humidity (non-condensing)

5%

95%

Dew Point-47 °F174 °F

Physical Dimensions (Measured)Width1.72” (44mm)

Length5.22” (133mm)

Height1.29” (33mm)

GBB15 weight

2.3oz (66g)

Accuracy (Typical)
Temperature+/-0.5°C (20°C to 80°C)

Relative Humidity+/-2% (20% to 80%)

Dew Point+/- 2.5°C (-44 °C to 79 °C)

Network
Ethernet Link Speed

10/100 Mbps; Full Duplex,
RJ45 Receptacles

Protocols

HTTP, HTTPS(SSL/TLS) SMTP/POP3, ICMP, DHCP, TCP/IP,NTP, Syslog

Data Formats

HTML, SNMP, CSV/Plain Text,JSON, XML

Warranty

3 years from date of purchase

Approvals
RoHS

Compliant

C-TickCompliantCE

Compliant: EN55022 &EN55024

FCC

Compliant: Class A, Part 15

Please note the information contained herein is for informational purposes only. Technical claims listed depend on a series of technical assumptions. Your
experience with these products may differ if you operate the products in an environment, which is different from the technical assumptions. Geist reserves
the right to modify these specifications without prior notice. Geist makes no warranties, express or implied, on the information contained in this document.

Geist Americas

Geist Europe

Geist Asia

Geist Asia

1821 Yolande AveLincoln, NE 68521 USA
1.800.432.3219 or
1.402.474.3400
www.geistglobal.com

Unit 1, The Monarch Centre,
Ventrue Way,
Priorswood, Taunton,Somerset, TA2 8DE UK+44 (0) 1823 275100
www.geisteurope.com

China
Tiley Plaza, Unit #2808,
No. 199 Haide 3 Road
Nanshan Shenzhen
Guangdong Province China
Postal Code: 518000
Tel: +86.755.86639505
www.geistglobal.com

Hong Kong
Tel: +852 90361927
Email: salesasia@geistglobal.com
www.geistglobal.com

Geist DCiM
2290 E Prospect Rd.
Fort Collins, CO 80525
1.877.449.4150