TECHNICAL DATA FOR THE XRGI® 25

Product Data Sheet, Date 18.06.2018

The XRGI® is a combined heat and power plant (CHP)
that works on the principle of cogeneration.
An XRGI® system consists of three main components:
the Power Unit, Q-Heat Distributor and the iQ-Control Panel.
In addition, you can also extend your XRGI® system with astorage tank with a capacity of 500, 800 or 1,000 litres for
optimum operation.

O R D E R I N G D ATA

Manufacturer

EC POWER

ModelXRGI® 25Article numberX250001

Modules

OUTPUTEFFICIENCIESH Y D R AU L I C

FUELSPower Unit, iQ25- Control Panel, Q70 Heat Distributor

50 %75 %Electrical output, modulatingkW

121824

Thermal Output

kW

333848

Power consumption, gas

kW48607750 %75 %100 %Power Modulation

Power Modulation
Electrical efficiency, LCV%

2530

31

Thermal efficiency, LCV%

686362

Total efficiency, LCV%

939393

Flow temperature, constant°C~ 85

Max. return temperature, variable°C

5-75

yes

Natural gas (all qualities), propane, butane°C

120

Emissions, NOxkg/MWhe+t<0.02

Emissions, COkg/MWhe+t<0.02Emissions, VOC

kg/MWhe+t<0.009POWER
CO N N E C T I O N

Voltage, 3 phase

V480

Frequency

Hz60

SERVICE

Service interval (operating hours)

Hours

4,000

E X H AU S T G A SDIMENSIONSAND WEIGHT

100 %Max. exhaust gas temperature

XRGI® 25 Power Unit

Q70-Heat Distributor

iQ25-Control Panel

Dimensions, W x H x Dmm

750 x 1,170 x 1,120

550 x 600 x 295

600 x 600 x 210

Footprint

m²0.84wall mounted

wall mounted

Weightkg

7504440

All values are net. Tolerance ±5 %. Specifications subject to change without notice.

W W W. E C P O W E R . E U

VERSION 1.0 2018

TECHNICAL DATA FOR THE XRGI® 25

Product Data Sheet, Date 18.06.2018

The XRGI® is a combined heat and power plant (CHP)
that works on the principle of cogeneration.
An XRGI® system consists of three main components:
the Power Unit, Q-Heat Distributor and the iQ-Control Panel.
In addition, you can also extend your XRGI® system with astorage tank with a capacity of 130, 210 or 260 gallons for
optimum operation.

O R D E R I N G D ATA

Manufacturer

EC POWER

ModelXRGI® 25Article number

X250001Modules

OUTPUT

50 %

75 %

kW

121824

Thermal Output

BTU/hr

112,000

129,000

163,000

Power consumption, gas

BTU/hr

163,000

204,000

262,000

50 %

75 %

100 %

Power Modulation
Electrical output, modulating

EFFICIENCIESH Y D R AU L I C

FUELS

E X H AU S T G A SPower Unit, iQ25- Control Panel, Q70 Heat Distributor

Power Modulation
Electrical efficiency, LCV%

253031

Thermal efficiency, LCV%

686362

Total efficiency, LCV%

939393

Flow temperature, constant°F~ 185

Max. return temperature, variable°F

41-167

yesNatural gas (all qualities), propane, butane°F

248

Emissions, NOx

lbs/MWhe+t<0.04

Max. exhaust gas temperature
Emissions, CO

lbs/MWhe+t<0.04

Emissions, VOC

lbs/MWhe+t

<0.02

POWER
CO N N E C T I O N

Voltage, 3 phaseV

480

Frequency

Hz60

SERVICE

Service interval (operating hours)

Hours

4,000

DIMENSIONSAND WEIGHT100 %XRGI® 25 Power Unit

Q70-Heat Distributor

iQ25-Control Panel

Dimensions, W x H x Din

29.5 x 44.1 x 46.1

21.6 x 23.6 x 11.6

23.6 x 23.6 x 8.3

Footprintsqft

9wall mounted

wall mountedWeightlbs

1500

9788

All values are net. Tolerance ±5 %. Specifications subject to change without notice.

W W W. E C P O W E R . E U

VERSION 1.0 2018