Preservation

Please send this operation manual to the final customer without fail.

Hot-air generator
Operation manual●Please read this without fail before use.
◆ This time, thank you very much for purchasing the hot-air generator.
◆ Please confirm whether the model, type, voltage and the order article are not wrong by the nameboard of this machine.

Please read Operation manual (Basis operation) regarding the operation of the hot-air generator.

1.Attention on use
2.Installation
3.Piping
4.Power supply
5.Maintenance inspection
6.Name of every part
7.Service terminal
8.Abnormal detection

TSK High pressure
TSK Hot-air generator
hot-air generator･ TSK-18･ TSK-22H4･ TSK-23 ･ 33
･ TSK-32H5･ TSK-42 ･ 52 ･ 52HT･ TSK-52H6･ TSK-56･ TSK-53H7･ TSK-62 ･ 72
･ TSK-62H8･ TSK-82･ TSK-72H9･ TSK-92 ･ 102･ TSK-82H10･ TSK-121
Platinum catalytic oxidation type deodorization device･ HJ-1.5

TAKETSUNA MANUFACTORY CO., LTD.

Contents
・・・・・・・・・・・・・・・・・・・

１

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

２

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

２

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

２

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

３

1.Attention on use
2.Installation
3.Piping※ Please confirm without fail before use.

4.Power supply

5.Maintenance inspection

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

４・５

7.Service terminal ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

６～８

6.Name of every partＴＳＫ－１８・２３・３３ ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

６

ＴＳＫ－２２Ｈ４・３２Ｈ５

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

６

ＴＳＫ－４２・５２・５２ＨＴ・５６・６２・７２・８２・９２・１０２・１２１、ＨＪ－１．５ ・・・・・・・・・・・

７

ＴＳＫ－５２Ｈ６・５３Ｈ７・６２Ｈ８・７２Ｈ９・８２Ｈ１０ ・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

７

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

８

Output situation of each output terminal

8.Abnormal detection

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・ ９～１４

8-1 Overheat

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

９

8-2 Temp. warning

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

１０・１１

8-3 Blower warning

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

１２・１３

8-4 Other warning

・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・・

１４

1.Attention on use※ Please confirm without fail before use.

For the hot-air generator is used without malfunctioning◆Important matters that demand special attention that became the cause of malfunction that occurred in the past isentered. Please inquire with the use method of your company.

● Please attach the demi-filter or CR-filter without fail to the suction side of the hotair generator.
● Please clean always the filter that is used or wire net of the hot-air generator inlet.
(Standard equipment) Heater inside is overheated by the clogging of the filter andthe hot-air generator may can not operate.

● Hot-air generator malfunctions when these adhered to the controller inside of the
hot-air generator in the case that dust, mine dust, floating objects that passelectricity of carbon fiber, oil, lampblack, oil mist, moisture, and vapor is included
to the atmosphere of the setting place of the hot-air generator.

● Hot-air generator can not use in corrosiveness of combustibility gas,
inflammability gas, plating, and atmosphere. Please consult us in the advance.

● Please turn ON the breaker (NFB) of the hot-air generator constantly. Please do
not turn ON/OFF as the operation switch. Electron devices of the inside aredamaged by serge voltage.

● Leakage of the hot-air is occured without fail on the characteristic of the flexible
hose in the case of the piping by the flexible hose to the outlet and inlet of hot-air
generator. Electron devices inside the operation panel are damaged by the hot-airof the high temp. that leaked flows backward to the hot-air generator inside. So,
please execute the glass tape for the air leakage prevention that was enclosed to theoutlet and inlet.

● Input terminal A1-A10 and output terminal B8-B10 is malfunctioned by thevoltage is applied. And, output terminal B1-B7 is malfunctioned by the voltage
more than the rating is applied.

● Please do not unite or wire that was adjoined the wiring of the service terminal
with the power supply line, high tone wave line. Electron devices of the inside aredamaged by noise.

● Please do not stopped the hot-air generator with the electromagnet contact device
that was established to the first side of the hot-air generator. Electron devices of
the inside are damaged by serge voltage .

● The thunder serge that occurred by falling of a thunderbolt becomes a cause to thewrong action, damage, and fire accident of the hot-air generator. Please attach thearrester without fail and please perform the falling of a thunderbolt measure in thecase that the hot-air generator is used in the place where receives the influence offalling of a thunderbolt.

● Please use the commercial power supply (50/60Hz) that has the sine wave-like tothe power supply of the hot-air generator. Please do not use the power supply thathas the distortion wave including a high tone wave from the frequency
transformation device absolutely. Electron devices of the inside are damaged byhigh tone wave and noise.
－１－2. Installation① Please establish to the horizontal position.Pleaserefer to the photograph of the right about the around of
inclination. And, please establish to the horizontal
position about the right and left.
② Please fix it firmly as occasion demands.
③ Place where can not establish･Upper part of generation thing･ Neighborhood of combustible･ Place where back is stuck to wall etc.

･Place where height is more than 1000m･Outdoor, and place where is exposed to the storm･Place where air pressure is low･Place where ambients humidity is more than 85%R.H.
･Place where ambients temp. is more than 0 - +45ﾟC.
･ Place where acid and corrosiveness gas is floating･Place where has vibration･ Place where has floating objects that pass electricity (Carbon fiber etc.)･ Room where is tightly sealed and case inside ･Places of there are many dust

3. Piping① Please fix the piping to the outlet and inlet certainly.
Leakage of the hot-air is occured without fail on the characteristic of the flexible hose in
the case of the piping by the flexible hose to the outlet and inlet of hot-air generator.
Electron devices inside the operation panel are damaged by the hot-air of the high temp.
that leaked flows backward to the hot-air generator inside. So, please execute the glass
tape for the air leakage prevention that was enclosed to the outlet and inlet.

② Please pipe as thickly, short, and gradual curve as possible.
③ Please insulate sufficiently without fail to piping.
④ Please do not hang the pulling load to the outlet flange in the

Execution example of the glass tape forthe air leakage prevention

condition thate the hot-air generator with the outlet flange was fixed.

4. Power supply① Please ask the connection of the power supply and ground construction work to the electric repairing work technic② Please connect the power cord in accordance with R(Red), S(White), T(Black), and Ground(Green).
Power cord is not belonged TSK-121. So, please prepare separately.(Recommendation cord : Cab tire cable 100mm 2 )③ Please use the commercial power supply (50/60Hz) that has the sine wave-like to the power supply of the hot-air
generator. Please do not use the power supply that has the distortion wave including a high tone wave from thefrequency transformation device absolutely.
④ Please establish the exclusive use circuit. Please decide the capacity of the sensitivity current in accordancewith the following table in the case that the electric leakage circuit breaker is attached.
⑤ Please execute the ground construction work to prevent electric shock accident prevention. (Less than 300V : Dclass ground Less than 600V : C-class ground)
Attention

The voltage depression is occurred by too long wiring. So, please pay attention.

Attention

Please block the power supply without fail at the time of wiring and inspection. Please block the factory power supply without failbecause electricity is flowing to the control circuit even if the breaker (NFB) of the hot-air generator is turned OFF. You receive anelectric shock when work is conducted in the condition that the power supply is turned ON.

Attention

Please secure sufficient capacity in the case that the socket was established for connection. Socket may cause contact defectiveness,absence phase, generation, and malfunction by passing year change. So, please refrain from the use of the socket.

Attention

Hot-air generator is the device that is used in industry environment mainly. Radio wave obstacle may occur if this is used in residence
environment. User of this product must take the appropriate means for obstacle reduction.

Model
TSK-18・22・32
TSK-42・52・52HT・55, HJ-1.5
TSK-62・72・82
TSK-92・102・121

Rough standard of the sensitivity current of the electric leakage circuit

50mA
50mA
100mA
200mA

※ About 10 times of the early period leakage current are general as the sensitivity current of the electric leakage circuit breaker.

－２－

5. Maintenance inspection
Test button
This is such a test button that confirms whether the
breaker (NFB) of this machine operates normally at thetime of overheat. One time in a month, please continue topush the button for several seconds in operation
stoppage condition (Electricity is flowing). And, pleaseconfirm the illumination of the OVERHEAT lamp,
operation display of overheat P.9), and trip action of the
breaker (NFB) of this machine.
After confirmation, please turn OFF the source power
supply (factory power supply) and breaker (NFB) of thismachine at first. And please turn ON once again.

Test button

Individual inspection◆I recommend that is carried out the individual inspection in the case that the use period exceeded 10 years tohave this machine used more safely.
【Item of the individual inspection 】
・ Measurement of the insulation resistance value ・ Measurement of the heater current value ・ Increase
bundle inspection of each terminal unit ・ Foreign substance mixing inspection and cleaning inside thecontroller ・ Foreign substance mixing inspection and cleaning inside this machine and inlet ・ Actionof the electricity part and generation inspection ・ Other inspection by eyes
Please ask to the adjacent electricity businessman about the individual inspection.
Attention ： Please do not carry out the insulation resistance voltage test of this machine. (It gets finishedenforcement at the time of shipment.) It becomes the cause of malfunction.

－３－

6. Name of every part
Control panel (All machine type community)

⑭
⑬
⑫
⑨

⑪
⑦
⑧
①
②
③

⑩
⑤

⑥

④
⑲

⑱

⑮

⑯

⑰

① STOP switch⑩ TIMER display

This is the stop switch of blow operation and hot-air operation,and for the cancellation of timer operation.

Setting time of the timer is displayed. Time is reduced by time
counting.

② HOT-AIR switch⑪ HEATER lamp

Hot-air operation is started when the switch was pushed.

ON/OFF of the heater is displayed by illumination and flickering.

③ BLOW switch⑫ TEMP. ALM lamp

Blow operation is started when the switch was pushed.

④ ON TIMER switch

This is lighted within the range of the temp. alarm setting value inthe case that temp. alarm setting is input.

Time that the operation is started is set up when the switch was
pushed. Please push HOT-AIR switch after setting.

This is lighted when the operation condition was changed to the exte

⑬ EXT. CNTL lamp

⑤ OFF TIMER switch⑭ EXT. SENSOR lamp

Time that the operation is stopped is set up when the switch was
pushed. Please push HOT-AIR switch after setting.

This is lighted when the operation condition was changed to the exte

⑥ EXT. RUN switch
Hot-air generator is operated with the external operation signal and external
heater ON/OFF signal by the switch is continued to push (about 2 seconds).

⑦ PV display
Outlet temp. is displayed. Temp. of the external sensor is displayedby the operation condition is changed to the external sensor.

⑮ OVERHEAT lamp
This is lighted and the breaker (NFB) is become trip in the casethat the heater case inside became a abnormal high temp.

⑯ TEMP. WARN. lamp
Breaker (NFB) is become trip or bloe operation is become in thecase that discharge temp. became a high temp. or suction temp.
became over the permission temp. of the blower.

⑧ SV display⑰ BLOWER WARN. lamp

Setting temp. of the outlet is displayed. Setting temp. of the external sensor isdisplayed by the operation condition is changed to the external sensor.

This is lighted when the blower became the overload and operation stops.

⑨ AIR VOL CNTL display

Breaker (NFB) is become trip by the button is pushed.

Setting value of the air volume control (Frequency setting) is
displayed. (Only the inverter installation machine type)This is used in the case that the operation condition is changed.

⑱ PUSH TO TEST buttom⑲ MODE switch－４－

ＭＯＤＥＬ ： ＴＳＫ－５２
Heatproof blower (Hot-air circulation type)
HandleHot-air outlet
Outlet temp. sensor(Thermocouple JISK)

Power cord
Breaker (NFB)

Control panel
Service terminal

ＭＯＤＥＬ ： ＴＳＫ－５２Ｈ６
Silent coverAir filter

Vortex blower (Inclusion)

Remote operation switch (with cord 6m)

Air volume control dumper

Hot-air outlet(Male type ferrule)
Outlet temp. sensor(Thermocouple JISK)Free casterBreaker (NFB)
Control panel

Reverse phase lamp
Pressure abnormal alarm buzzer

Pressure sensor

Service terminal－５－Power cord

7. Service terminal●Service terminal of the input and output is equipped to all types. Please use as occasion demands.

【Type that is used 】 ＴＳＫ－１８・２３・３３、ＴＳＫ－２２Ｈ４・３２Ｈ５
ＲＣ：Connector for connection of Remote controller
This is the connector for connection of remote cable in the case thatthe remote controller of the option is used.

Ｅ.Ｓ+
Ｅ.Ｓ-

：External sensor input terminal
Please connect the terminal of the external sensor.
( Ｋ+→Ｅ.Ｓ+、Ｋ-→Ｅ.Ｓ- Tightening torque : 0.5N ･ m)

《Input terminal 》
Mini terminal (Application electric wire Shield wire AWG24 - 16
Peel length 7 - 9mm) Tightening torque : 0.4N ･ m
Necessary tool : No.1 Plus driver or 3mm Minus driver

Ｅ.Ｃ+
Ｅ.Ｃ-

：External temp. control input terminal
This is used in the case that temp. is controlled by other temp.
controllers. Please input SSR drive reverse action output(DC11 - 24V). At this time, please use the temp. controller ofthis machine as outlet temp. upper limiter.

Ｅ.Ｒ：External operation input terminal
This is used in the case that the hot-air generator is operated by
the outside signal. Input is for the contact output. (Terminal
voltage is less than DC15V 3.5mA.)

Ｅ.Ｈ：External heater input terminal
This is used in the case that the heaterr is turned ON/OFF by theoutside signal. Input is for the contact output. (Terminal voltage
is less than DC15V 3.5mA.)

ＣＯＭ ：Input common terminal
This is common for the external operation input terminal E.R andexternal heater input terminal E.H.
※ Terminal voltage of the external operation input terminal E.R and external heater
input terminal E.H is less than DC15V 3.5mA. Please prepare the relay that has thecontact capacity that can open and close this voltage.

※ Please change the external operation mode by pushing the EXT. RUN switch of thismachine in the case that the external operation input and external heater input is used.

《Output terminal 》 Contact capacity is less than DC30V 80mA. (Unvoltage point of contact signal output)
Mini terminal (Application electric wire Shield wire AWG24 - 16 Peel length 7 - 9mm) Tightening torque : 0.4N ･ m
Necessary tool : No.1 Plus driver or 3mm Minus driver

ＢＬＷ
ＨＯＴ
Ｔ.Ｗ.
Ｔ.Ａ
ＢＷ.
ＯＶＨ
ＣＯＭ

：Blow output terminal：Hot-air output terminal：Temp. warning output terminal：Temp. alarm output terminal：Blower warning output terminal：Overheat output terminal：Output common terminal

This terminal becomes ON when the blower is operating.
This terminal becomes ON when the hot-air is operating.
This terminal becomes ON at the time of the temp. warning.
This terminal becomes ON when the temp. alarm was output.
This terminal becomes ON at the time of the blower warning.
This terminal becomes ON at the time of overheat.

※ Protection circuit is not installed to unvoltage contact output. So, please do not connect the induction load (solenoid valve and conductor etc.).

Attention ：Please wire after the power supply is blocked without fail in the case that the service terminal is used.
You receive an electric shock if you wired in the condition which electricity is flowing. And, please attacha terminal cover without fail after wiring.
Attention ：Please do not unite or wire that was adjoined the wiring of the service terminal with the power supply
line, high tone wave line.
－６－【Type that is used 】 ＴＳＫ－４２・５２・５２ＨＴ・５６・６２・７２・８２・９２・１０２・１２１ ＨＪ－１．５
ＴＳＫ－５２Ｈ６・５３Ｈ７・６２Ｈ８・７２Ｈ９・８２H１０《Input terminal 》
Ａ１

M3 20P The upper row of the terminal Tightening torque : 0.5N ･ m：External operation ON/OFF terminal
This is used in the case that the hot-air generator is operated by the outside
signal. Input is for the contact output. (Terminal voltage is less than DC24V

Ａ２：External heater ON/OFF terminal
This is used in the case that the heaterr is turned ON/OFF by the outside signal.
Input is for the contact output. (Terminal voltage is less than DC24V 7mA.)

Ａ３：Input common terminal
This is common for the external operation ON/OFF terminal A1 and external
heater ON/OFF terminal A2.

Ａ４・Ａ５ ：External temp. control input terminal
This is used in the case that temp. is controlled by other temp. controllers. Please
input SSR drive reverse action output (DC11 - 24V). At this time, please use thetemp. controller of this machine as outlet temp. upper limiter. (Ａ４→＋、Ａ５→－)

Ａ６・Ａ７ ：External sensor input terminal
Please connect the terminal of the external sensor. (Ｋ+→Ａ６、Ｋ-→Ａ７ )※Terminal voltage of the external operation ON/OFF terminal A1 and external heater
ON/OFF terminal A2 is less than DC24V 7mA. Please prepare the relay that has thecontact capacity that can open and close this voltage.
※Please change the external operation mode by pushing the EXT. RUN switch of thismachine in the case that the external operation ON/OFF and external heater ON/OFF isused.
A8･A9･A10 ：Terminal for connection of Remote controller

This is the terminal for connection of remote cable in the case that the remotecontroller of the option is used. (For communication of the remote controller)《Output terminal 》 M3 20P The Lower berth of the terminal Tightening torque : 0.5N ･ mContact capacity is less than DC30V 80mA. (Unvoltage point of contact signal output)

Ｂ１：Blow output terminal
This terminal becomes ON when the blower is operating.

Ｂ２：Hot-air output terminal
This terminal becomes ON when the hot-air is operating.

Ｂ３：Temp. warning output terminal
This terminal becomes ON at the time of the temp. warning.

Ｂ４：Temp. alarm output terminal
This terminal becomes ON when the temp. alarm was output.

Ｂ５：Blower warning output terminal
This terminal becomes ON at the time of the blower warning.

Ｂ６：Overheat output terminal
This terminal becomes ON at the time of overheat.

Ｂ７：Output common terminal

B8･B9・B10 ：Terminal for connection of Remote controller

This is the terminal for connection of remote cable in the case that the remote controller of the option is used. (Forpower supply of the remote controller)※Voltage DC24V has occurred to the remote controller power supply terminal B9-B10. Please never short-circuit. Hot-air
generator malfunctions without fail if short-circuits.

Attention ：Please wire after the power supply is blocked without fail in the case that the service terminal is used.
You receive an electric shock if you wired in the condition which electricity is flowing. And, please attacha terminal cover without fail after wiring.
Attention ：Please do not unite or wire that was adjoined the wiring of the service terminal with the power supply
line, high tone wave line.
－７－

Output situation of each output terminal
ＴＳＫ－１８・２３・３３、ＴＳＫ－２２Ｈ４・３２Ｈ５
Output terminal
Action of the hot-air generator

Usually stop
Blow operation
Hot-air operation
Cooling operation
Temp. alarm output
Overheat
Overheat sensor barnout
In the case that the discharge temp.
upper limit is exceeded
In the case that the suction temp.
upper limit is exceeded
Outlet sensor barnout
Inlet sensor barnout ※１
Inlet sensor barnout ※２
Inside temp. warning of the hot-air
generator
Inside SSC temp. warning of the
hot-air generator
Blower warning
External sensor barnout
Reverse connection of each temp.
sensor/Minus temp. detection
Opposite phase warning (Only H-type)

Blower warning Overheat output
terminal
output terminal
ＢＷ.
ＯＶＨ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＮ

Blow output
terminal
ＢＬＷ
ＯＦＦ
ＯＮ
ＯＮ
ＯＮ
ＯＮ
ＯＦＦ
ＯＦＦ

Heater output
terminal
ＨＯＴ
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＦＦ

Temp. warning
output terminal
Ｔ.Ｗ.
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ

Temp. alarm
output terminal
Ｔ.Ａ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＮ
ＯＮ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＮ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ

ＯＮ
ＯＦＦ

ＯＦＦ
ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

※ 1 C type : At the time of the inlet sensor barnout of TSK-18 - 33.
※ 2 H type : At the time of the inlet sensor barnout of TSK-22H4 - 32H5.

ＴＳＫ－４２・５２・５２ＨＴ・５６・６２・７２・８２・９２・１０２・１２１ ＨＪ－１．５
ＴＳＫ－５２Ｈ６・５３Ｈ７・６２Ｈ８・７２Ｈ９・８２Ｈ１０
Output terminal
Action of the hot-air generator

Usually stop
Blow operation
Hot-air operation
Cooling operation
Temp. alarm output
Overheat
Overheat sensor barnout
In the case that the discharge temp.
upper limit is exceeded
In the case that the suction temp.
upper limit is exceeded
Outlet sensor barnout
Inlet sensor barnout ※１
Inlet sensor barnout ※２
Inside temp. warning of the hot-air
generator
Inside SSC temp. warning of the
hot-air generator
Blower warning
Pressure warning
External sensor barnout
Reverse connection of each temp.
sensor/Minus temp. detection
Opposite phase warning (Only H-type)

Blower warning Overheat output
terminal
output terminal
Ｂ５
Ｂ６
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＮ

Blow output
terminal
Ｂ１
ＯＦＦ
ＯＮ
ＯＮ
ＯＮ
ＯＮ
ＯＦＦ
ＯＦＦ

Heater output
terminal
Ｂ２
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＦＦ

Temp. warning
output terminal
Ｂ３
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ

Temp. alarm
output terminal
Ｂ４
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＦＦ
ＯＮ
ＯＦＦ
ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＮ
ＯＮ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＮ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＮ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＮ
ＯＮ
ＯＦＦ

ＯＦＦ
ＯＦＦ
ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

ＯＦＦ

※ 1 C type : At the time of the inlet sensor barnout of TSK-42 - 121, HJ-1.5.
※ 2 H type : At the time of the inlet sensor barnout of TSK-52H6 - 82H10.
－８－

8. Abnormal detection◆Buzzer sounds at the same time as theabnormal display when abnormality was detected about TSK-42,52,52HT,
62,72, 82, 92, 102, 121, HJ-1.5, TSK-52H6, 53H7, 62H8, 72H9, 82H10. Even buzzer sound stops when abnormality
was canceled by the return method of each abnormality.

８－１ Overheat
Overheat is detected in the case that the inside of the heater case became an abnormal high temp. Or, barnout isdetected in the case that the overheat sensor for the temp. control inside the heater case snapped. And, the breaker(NFB) of this machine does trip and all the operation stop.
●At the time of overheat
Overheat lamp (Red) are lighted, and NFB is flickered to
PV dept. TCB to SV dept.
《Main cause 》

・ Clogging of the inlet wire net and filter
・ Lock of the blower motor by the mixing of the foreign
substance
・ Exhaust outlet of furnace etc. is not secured sufficiently
・ Resistance (pressure loss) of the outlet is big by theadjacency of object work
《Return method 》
Please remove the cause of overheat. And , source power
supply and the reaker of this machine are turned OFF atfirst and are turnd ON again after cooling sufficiently.

●At the time of overheat sensor barnout
Overheat lamp (Red) are flickered, and --- is flickered to
PV dept. TCB to SV dept.
《Main cause 》

・ Snapping of a wire of the overheat sensor
・ Snapping of a wire of overheat sensor wiring・ Miss of the overheat sensor wiring connector《Return method 》
Please turn OFF the first power supply and please order
the repair.

Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.

－９－８－２ Temp. warning
Hot-air generator is stopped or become blow operation when outlet and inlet temp. exceeded the upper limit, each sensor
becomes the barnout by snapping of a wire etc., or the inside temp. of the hot-air generator became warning too.

●When the outlet temp. exceeded the upper limit
TEMP. WARN. lamp (Red) is lighted and NFB is
flickered to PV dept. TCA to SV dept. And, the breaker(NFB) of this machine does trip and all the operation《Main cause 》
・Outlet temp. exceeded the upper limit at the time ofusing the external sensor
・Decrease of the air volume by the excessive pressure loss
・Decrease of the air volume by the clogging of the inlet filter《Return method 》
Please remove the cause of outlet temp. upper limit. And, source power supply and the reaker of this machine areturned OFF at first and are turnd ON again after coolingsufficiently.
●When the inlet temp. exceeded the upper limit
TEMP. WARN. lamp (Red) is lighted and present temp. islighted to PV dept. TCC is flickered to SV dept. And, It
becomes blow operation condition.
《Main cause 》
・When hot-air circulation temp. exceeded the upper limitof the suction gas temp. of the hot-air generator《Return method 》
Please disarm by pushing STOP switch after the temp. of
the inlet dropped.
※Blower warning occurs when suction temp. exceeded about the high pressure hot-air generator H type. (Please refer to Blower warning of P.12 8-3.)●At the time of the barnout of the outlet sensor
TEMP. WARN. lamp (Red) is lighted and --- is flickered
to PV dept. TCA to SV dept. And, the breaker (NFB) of
this machine does trip and all the operation stop.
《Main cause 》
・Snapping of a wire of the outlet sensor
・Snapping of a wire of the outlet sensor wiring
・Miss of the outlet sensor wiring connector《Return method 》
Please order the repair after turning OFF the first power
supply.

Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.
－１０－

●At the time of the barnout of the inlet sensor
TEMP. WARN. lamp (Red) is lighted and --- is flickered
to PV dept. TCC to SV dept. And, all the operation stop.

《Main cause 》
・Snapping of a wire of the inlet sensor
・Snapping of a wire of the inlet sensor wiring
・Miss of the inlet sensor wiring connector《Return method 》
Please order the repair after turning OFF the breakert(NFB) of the this machine.
※BLOWER WARN. lamp is lighted when inlet sensor became the barnpout about the high pressure hot-air generator H type.

●At the time of the inside temp. warning of the hot-air generator
TEMP. WARN. lamp (Red) is flickered and OH is
flickered to PV dept. ALM to SV dept. And, It becomes
blow operation condition.
《Main cause 》
・Establishment atmosphere temp. of the hot-air generator is high.

・Hot-air that leaked from the outlet flowed backward to
the contrlo panel inside.
・ Influence of the furnace radiation temp. at the time of
the furnace upper part establishment《Return method 》
Please stop operation by pushing STOP switch. And,please disarm by turning OFF the breaker (NFB) of thismachine after inside temp. of the hot-air generator●At the time of the inside SSC temp. warning of the hot-air generator (Only TSK-121 200V)
TEMP. WARN. lamp (Red) is flickered and SSC isflickered to PV dept. ALM to SV dept. And, It becomes
blow operation condition.
《Main cause 》
・Establishment atmosphere temp. of the hot-air generator is high.

・Hot-air that leaked from the outlet flowed backward to
the contrlo panel inside.
・ Influence of the furnace radiation temp. at the time of
the furnace upper part establishment《Return method 》
Please disarm by pushing STOP switch after inside temp.
of the hot-air generator dropped.
Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.
－１１－

８－３ Blower warning
All the operation of hot-air generator is stopped when the blower became overload, overcurrent, and lock. It is detectedwith barnout when inlet sensor of high pressure hot-air generator snapped, and all the operation is stopped.

●At the time of the blower warning (C type : TSK-18 - 121, H type : TSK-22H4 - 72H9 with inverter, TSK-82H10)
BLOWER WARN. lamp (Red) is lighted and INV isflickered to PV dept. ALM to SV dept.

《Main cause 》
・Wear of the bearing
・Abnormal voltage (Voltage more than the rating)・Piping of many pressure loss
・Opening the use of an extremely narrow nozzle《Return method 》
Abnormality is displayed to the inverter that wasestablished inside. Please turn off the breaker of thismachine after the display contents are confirmed. And,please communicate the display contents.
●At the time of the blower warning (H type : TSK-22H4 - 72H9)
BLOWER WARN. lamp (Red) is lighted and THR is
flickered to PV dept. ALM to SV dept.

《Main cause 》
・Wear of the bearing
・Abnormal voltage (Voltage more than the rating)・Piping of many pressure loss
・Opening the use of an extremely narrow nozzle《Return method 》
Please remove the cause. And , source power supply andthe reaker of this machine are turned OFF at first andare turnd ON again after cooling sufficiently.
●At the time of the barnout of the outlet sensor (H type : TSK-22H4 - 82H10)
BLOWER WARN. lamp (Red) is lighted ,TEMP. WARN
lamp (Red) is flickered and BL is flickered to PV dept.
TCC to SV dept.
《Main cause 》
・Closing condition of discharge side piping
・Piping of very many pressure loss

《Return method 》
Please disarm by pushing STOP switch after removing
the cause.
Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.
－１２－

●At the time of pressure abnormality (Only type that the digital pressure sensor was installed : TSK-52H6 - 82H10)
Output 1 display lamp of the digital pressure sensor is lighted and warning sound sounds in the case that the airpressure on the side of the discharge exceeded the continus usable discharge pressure.
BLOWER WARN. lamp (Red) is flickered and all operation is
stopped when the condition that the air pressure on the side ofthe discharge exceeded the continus usable discharge max.
pressure continued for 10 minutes. Discharge and setting temp.
in the time are displayed to PV and SV dept.

《Main cause 》
・Piping of many pressure loss
・Opening the use of an extremely narrow nozzle
・Over srueezing of the air volume by the valve《Return method 》
Please disarm by pushing STOP switch if it can be
operated under the continus usable max. pressure after
the cause is removed.
Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.

－１３－

８－４ Other warning●At the time of the barnout of the external sensor
Hot-air generator is stopped when the external sensor became the barnout of snapping of a wire etc. in the casethat the temp. of the place that parted is controlled by using the external sensor of the option.
--- is flickered to PV dept. TC0 to SV dept. (EXT.
SENSOR lamp is being lighted.)《Main cause 》
・Snapping of a wire of the external sensor
・Snapping of a wire of the external sensor compensating wire・ Miss of the inlet sensor wiring terminal《Return method 》
Please disarm by pushing STOP switch after theconfirmation of the external sensor.

●Reverse connection by each sensor or detection of minus temp.
Hot-air generator is stopped at the time of the reverse connection of each temp. sensor (External sensor is included)or perception of -15 ﾟ C. (Onle inside temp. sensor is -5 ﾟ C.)--- R34 is flickered to PV dept. display of each sensor to
SV dept.
：ＴＣ０：ＴＣＡ
External sensor
Outlet sensor：ＴＣＣ
Overheat sensor ：ＴＣＢ
Inlet sensor
Inside temp. sensor ：ＴＣＭ
《Main cause 》
・Reverse connection of the external sensor
・Reverse connection by the wiring readjustment of each sensor

・Atmosphere temp. or suction temp. of minus《Return method 》
Please disarm by pushing STOP switch after theconfirmation of the external sensor or the improvementof the minus condition. Please order the repair about
except for reverse connection of the external sensor.
●At the time of opposite phase abnormality (H type : Only TSK-22H4 -82H10)
Hot-air generator can not be operated when the connection of the power supply wire became a reverse phase about
the high pressure hot-air generator TSK-H type.
Each display becomes to the display of turning ON the breaker (NFB) of this machine. And
Reverse phase lamp (Red) is lighted.
《Main cause 》
・Reverse phase connection of the power supply《Return method 》
Please replace any wire of the connection wire of thepower supply.
Attention : Please block the source power supply (factory power supply) without fail when the wiring is
confirmed and readjusted at the time of abnormal.
－１４－