TI01677S/04/EN/01.22-00
71569912
2022-03-31

ProductsSolutions

ServicesTechnical Information
FieldGate SWG50
Functional WirelessHART gateway

Application
The FieldGate SWG50 is a gateway for WirelessHART networks. It enables
WirelessHART field devices to communicate with each other and manages network
security and connectivity. The FieldGate converts and stores data from wireless fielddevices in a format that is compatible with other systems. It has Ethernet interfaces
for connecting to host applications such as SCADA tools.
Your benefits• Easy commissioning and diagnosis of a self-organized WirelessHART network withup to 100 WirelessHART devices.
• Ideal for operations with limited space in the cabinet, since it is compact and canbe mounted on DIN rails.
• Flexible use of FieldGate in the hazardous areas of a plant.
• Seamless integration of field device information into higher-level systemapplications using standardized protocols such as Modbus TCP or HART-IP.

FieldGate SWG50

About this document
Symbols

Safety symbols
DANGER

This symbol alerts you to a dangerous situation. Failure to avoid this situation will result in serious orfatal injury.
WARNING

This symbol alerts you to a dangerous situation. Failure to avoid this situation can result in serious or
fatal injury.
CAUTION

This symbol alerts you to a dangerous situation. Failure to avoid this situation can result in minor or
medium injury.
NOTICE

This symbol contains information on procedures and other facts which do not result in personalinjury.
Symbols for certain types of information
SymbolMeaning
Permitted
Procedures, processes or actions that are permitted.
Preferred
Procedures, processes or actions that are preferred.
Forbidden
Procedures, processes or actions that are forbidden.
Tip
Indicates additional information.
Reference to documentationA

Reference to page
Reference to graphic

Visual inspection

Electrical symbols
SymbolMeaning
Direct current
Alternating current
Direct and alternating current
Ground connection
A grounded terminal which, as far as the operator is concerned, is grounded via agrounding system.
Protective earth (PE)Ground terminals that must be connected to ground prior to establishing any otherconnections.
The ground terminals are located on the interior and exterior of the device:• Interior ground terminal: protective earth is connected to the mains supply.
• Exterior ground terminal: device is connected to the plant grounding system.

2Endress+Hauser

FieldGate SWG50

Function and system design
Measuring system

The FieldGate SWG50 is a functional WirelessHART gateway. It comprises a network manager
application, a WirelessHART (access point) interface module and a gateway application. Up to 100
wireless or corded devices can be connected to the FieldGate SWG50. The application supplies datafrom the WirelessHART network via Modbus TCP or HART-IP. A CommDTM makes it possible toattach DTMs to connected devices.

System architecture12345 67869Netilion

WirelessHART

121110A0048719

1123456789101112Network connection

Example of WirelessHART network architecture with FieldGate SWG50
Endress+Hauser Field Xpert, e.g. SMTxx
Host application / FieldCare SFE500
Ethernet communication
FieldGate SWG50
FieldEdge SGC500
https Internet connection
Netilion CloudApplication Programming Interface (API)Internet browser-based Netilion Service app or user application
WirelessHART adapter SWA70 used as a repeater
HART field device with WirelessHART adapter SWA70
Encrypted wireless connection via WirelessHARTThe configuration of the FieldGate SWG50 is performed entirely via an embedded web server. The
web server is password-protected and uses only secure (HTTPS) connections.
It is possible to save the configuration settings of the gateway as a password-protected file on a PC.
It is also possible to upload the file to a device for easy commissioning of a replacement gateway.
The gateway firmware can be updated via the web server.
It is possible to restore the factory settings via the web server (or the button on the front of thegateway).

Endress+Hauser3

FieldGate SWG50

Communication and dataprocessing

HART IPThe gateway supports HART IP via TCP and UDP. Up to 10 socket connections can be established atthe same time.
Modbus TCP
The gateway supports Modbus TCP via Ethernet.

Input
Measuring range

Up to 250 m outdoors.
Up to 50 m indoors.
Depending on the type of antenna to be connected and the environment.

Type of input

WirelessHART communication interface (IEC 62591)

Input signal

Up to 100 WirelessHART-based devices can be connected. Process variables and device statusaccording to HART standard are transmitted by the field devices to the gateway in burst modes.

Operating frequency

2.4 GHz ISM band

Transmission power

10 dB

OutputOutput and input variants

Ethernet interface in RJ45 format, to which only twisted-pair cables with an impedance of 100 Ω canbe connected.
The maximum distance between units is based on Ethernet standards and is determined by theenvironment and the networks' compliance with these standards.

Output signal

HART-IP and MODBUS TCP communication interface

Transmission behavior

The transmission rate is 10, 100 or 1000 Mbps.

Power supply
Supply voltage

DC power input range: 10.8 to 30.5 VDC
Current outputs P1 and P2 are redundant and have reverse polarity protection.

Power consumption<7 W

Current consumption

290 mA at 24 VDC.

Electrical connection

Reference

Label

Plug type

Signal

Use

J1

1

RJ-45

10/100/1000-T

Ethernet connection

J2

2

RJ-45

10/100/1000-T

Ethernet connection

J3

3RJ-45

10/100/1000-T

Ethernet connection

4Endress+Hauser

FieldGate SWG50

Reference

Label

Plug type

SignalUse

J4

4RJ-45

10/100/1000-T

Ethernet connection

J5ANTRSMA2.4 GHz

Antenna connection

J6*Philips screw

J7Plug8-pin Combicon

Grounding of device
DC voltage

Power supply

PlugSignal

Marking

1DC++P1-2

DC-3DC+

4DC-

5N/A

NC

6N/A

NC

7N/A

NC

8N/A

NC

+P2-The holding force of the plug-in connector must be at least 15 N.

Terminals

Ground ring or spade/fork tongue crimp connection to M3 cap screw and lockwasher on top surface
of device housing.

Cable entries

Screw terminals: 0.2 to 4 mm2 (solid wire), 0.2 to 2.5 mm2(stranded wire (AWG 24-14))

Performance characteristicsHardware• Marvel Dual Core ARM-7 with 1.2 GHz, supplemented by 1 GB DDR4-RAM and 4 GB MMC flashmemory• Supervisor processor• 4-port Ethernet switch• WirelessHART interface transceiver module• WirelessHART AP interface module (model M2140)• FCC-ID: SJC-M2140• IC-ID: 5863-M2140

Software

The gateway application includes an embedded web server, a Modbus TCP interface, a HART-IP
interface and logic functions for managing the device.

Installation
Mounting location

The device must be installed in a housing that has a minimum protection rating of IP54 as per
EN/IEC 60079-15. The device must be used only in areas with a maximum pollution degree of 2 asdefined in EN/IEC 60664-1. The device can be installed in Zone 2 hazardous areas. Routing andremote installation of the antenna must comply with the relevant site regulations when installed in
unclassified Zone 2 or Class I, Division 2 hazardous areas. Otherwise, the antenna must be installed
within the end-use housing .

Installation instructions

Endress+Hauser

5FieldGate SWG50

The FieldGate SWG50 is mounted on an NS 35 mounting rail. To prevent the device from slipping,end clamps must be mounted on both sides. The device can be mounted either horizontally orvertically. The modules are mounted on the mounting rail from left to right.

A0048928

2Special mountinginstructions

Mounting on a standard DIN rail

A remote antenna can be mounted outside a cabinet. If there is a risk of lightning, installlightning/EMP protection between the gateway and the remote antenna.

Environment
Ambient temperature range–40 to 70 °C

Storage temperature–40 to 85 °C

Relative humidity

10 to 90 % non-condensing

Operating heightmax. 3 048 m (10 000 ft)

Climate classas per IEC 60068-2-30 Db

Degree of protection

IP20

Vibration resistance

Sinusoidal vibration as per IEC 60068-2-6
10 to 60 Hz 0.070 (p-p mm) amplitude
60 to 150 Hz60 Hz to 150 Hz 5 g acceleration
1 octave/minuteShock resistanceHalf-sinusoidal shock as per IEC 60068-2-27
15 g Shock18 ms Pulse

Electromagnetic
compatibility (EMC)

6Compliance with EMC directive 2014/30/EU

Endress+Hauser

FieldGate SWG50

Mechanical construction

120

Design, dimensions

4590A0048886

3Views in mm

Dimensions

120 mm ⋅ 90 mm ⋅ 45 mm (4.72 in ⋅ 3.54 in ⋅ 1.77 in)

WeightMax. 500 g

Materials

Housing material: aluminum
Terminals for power supply: nylon

Operability
Web server

4Endress+Hauser

Web server

7FieldGate SWG50

LEDLED

Description

ST (multicolored)

flashing green: device initializing
flashing red: device restarting or troubleshooting
lit green: power supply/device is active

MESH (green)

Device connection:
ON: WirelessHART devices connected
OFF: no WirelessHART devices found or not connected

ERR (red)Error:
OFF: no errors
ON: internal error

Service interface

There are four Gigabit Ethernet ports with identical functionality, which act as an unmanagedswitch. Each port can be used to access the web server, HART IP or Modbus interfaces.

Reset button

The reset button restores the standard IP address and resets the FieldGate SWG50 to the factory
setting.

Certificates and approvals
The latest approvals for the product are available from www.endress.com:
1.

Select the product using the filters and search field.

2.

Open the product page.

3.

Select Downloads.
 A list of all approvals and declarations appears.

Ordering information
Detailed ordering information is available from your nearest sales organizationwww.addresses.endress.com or in the Product Configurator at www.endress.com:
1.

Select the product using the filters and search field.

2.

Open the product page.

3.

Select Configuration.
Product Configurator - the tool for individual product configuration• Up-to-the-minute configuration data
• Depending on the device: Direct input of measuring point-specific information such asmeasuring range or operating language• Automatic verification of exclusion criteria• Automatic creation of the order code and its breakdown in PDF or Excel output format• Ability to order directly in the Endress+Hauser Online ShopAccessories
The accessories currently available for the product can be selected at www.endress.com:

81.

Select the product using the filters and search field.

2.

Open the product page.

3.

Select Spare parts & Accessories.

Endress+Hauser

FieldGate SWG50

Documentation
Standard documentation

FieldGate SWG50 Operating Instructions BA02235S/04/EN

Registered trademarks
HART®, WirelessHART® is the registered trademark of the FieldComm Group, Austin, TX 78759,
USA.
All other brand and product names are trademarks or registered trademarks of the companies andorganizations in question.

Endress+Hauser

9*71569912*
71569912

www.addresses.endress.com