Reference Topology HON02

Version 1.00.00

Reference Topology HON02
Honeywell Experion®PKS and PROFIBUS for
Chemical Industry

SD02062S/04/EN/01.17

1/12

Reference Topology HON02

SD02062S/04/EN/01.17

Version 1.00.00

2/12

Reference Topology HON02

Version 1.00.00

Table of Contents
123

Document Information ................................................................................................................. 4
1.1

Purpose and Scope ........................................................................................................................... 4

1.2

Document History ............................................................................................................................ 4

1.3

Related Documents .......................................................................................................................... 4

Target Market .............................................................................................................................. 4
2.1

Industry Application ......................................................................................................................... 4

2.2

Fieldbus Technology ........................................................................................................................ 4

Reference Topology ..................................................................................................................... 5
3.1

Overview .......................................................................................................................................... 5

3.2

Process Control System .................................................................................................................... 5

3.3

Asset Management System.............................................................................................................. 6

3.4

Field Network Infrastructure ............................................................................................................ 7

3.4.1

PROFIBUS DP Optical Ring Network ........................................................................................ 7

3.4.2

PROFIBUS DP Cable Type A Network ....................................................................................... 7

3.4.3

PROFIBUS DP/PA Coupling ...................................................................................................... 7

3.4.4

PROFIBUS PA Cable Type A Network ....................................................................................... 8

3.5

Field Devices..................................................................................................................................... 93.5.1

PROFIBUS DP devices ............................................................................................................... 9

3.5.2

PROFIBUS PA devices ............................................................................................................... 9SD02062S/04/EN/01.17

3/12

Reference Topology HON02

Version 1.00.00

1 Document Information
1.1 Purpose and ScopeThis document specifies the Open Integration Reference Topology HON02. All content of this document is
jointly developed, reviewed and released by Honeywell Process Solutions and Endress+Hauser as acommon deliverable of Open Integration.

1.2 Document History
This is version 1.00.00 of this document. Version history:
VersionReleased

Description

1.00.002017-12

Initial version

1.3 Related Documents
Please refer to related documents as listed below:
Document

Description

SD02063S/04/EN/01.17

Integration Tutorial HON02

SD02064S/04/EN/01.17

Integration Test Summary HON02

SD02065S/04/EN/01.17

List of Tested Devices and Versions HON02

2 Target Market
2.1 Industry Application
This reference topology is designed to serve applications in Chemical industry.

2.2 Fieldbus Technology
This reference topology is designed for instrumentation with PROFIBUS DP and PROFIBUS PA.

SD02062S/04/EN/01.17

4/12

Reference Topology HON02

Version 1.00.00

3 Reference Topology
3.1 Overview

3.2 Process Control System
The process control system part top left in the overview is provided by Honeywell Process Solutions:
The yellow and green switches establish a redundant Ethernet backbone for all Honeywell Experion®PKSservers, workstations and control units. Each control unit consists of at least two CF9 control firewall
modules and two C300 controller modules to provide level 1 redundancy. PGM modules serve to connect
to the underlying PROFIBUS DP/PA network. Core element on top of the system backbone is theExperion®PKS software for control engineering, complemented with Experion®FDM software for asset
management.

SD02062S/04/EN/01.17

5/12

Reference Topology HON02

Version 1.00.00

Reference hardware:

Experion®PKS

ArticleDescription

Processor: CC-PCF901

Control Firewall with 9 ports (CF9)

IOTA: CC-TCF901

Experion®PKS

Processor: CC-PCNT02

C300 Controller

IOTA: CC-TCNT01

Experion®PKS

Processor: CC-IP0101

PROFIBUS Gateway Module with 2 DP segments (PGM2)

IOTA: CC-TP0X01

3.3 Asset Management System
The asset management system part top right in the overview is provided by Endress+Hauser:
FieldCare or PAM Suite Servers and Clients may access the underlying PROFIBUS/DP/PA fieldbus network
either via system backbone and hardware of the control system, or independently via Fieldgate SFG500.
Reference hardware:

Fieldgate SFG500

ArticleDescription

SFG500Ethernet / PROFIBUS DP gateway

SFM500-A1

Asset Management Module for Fieldgate SFG500

Complementary to this, Endress+Hauser also supports integral means of Honeywell with device drivers forExperion®FDM.

SD02062S/04/EN/01.17

6/12

Reference Topology HON02

Version 1.00.00

3.4 Field Network Infrastructure
3.4.1 PROFIBUS DP Optical Ring Network
The PROFIBUS DP Optical Ring Network is optional for this reference topology, with limited impact tointegration tests. If applied, Honeywell Process Solutions and Endress+Hauser recommend using opticallink modules from R.STAHL for this reference topology.
Recommended hardware:MediaconverterArticle

Description

9186/15-12-11

Safe area/Zone 2 installation; RS485 / FO “op is”; ring

For optical network a multimode cable with ST-connectors (BFOC/2,5 plug) is required. Optical ring issuitable for installation of the optical network in a Zone 1 or Zone 2 environment.
3.4.2 PROFIBUS DP Cable Type A Network
The PROFIBUS DP Cable Type A Network is mandatory for this reference topology, with limited impact tointegration tests. Specific reference hardware for this part is not yet defined; recommendable hardware
may be listed here in future.
3.4.3 PROFIBUS DP/PA Coupling
The PROFIBUS DP/PA Coupling is mandatory for this reference topology, with decisive impact tointegration tests. Honeywell Process Solutions and Endress+Hauser recommend using the SK3 Power Hubfrom Pepperl+Fuchs for this reference topology.
Reference hardware:

SK3 Power HubArticle

Description

MB-FB-GT

Gateway motherboard

MBHC-FB-4.HSC

Fieldbus Power Hub Motherboard

HD2-GTR-4PA

Gateway module

HCD2-FBPS-1.500

Fieldbus Power Supply Module

HD2-DM-A

Diagnostic module

ACC-MB-HSK

Shielding/grounding kit

SD02062S/04/EN/01.17

7/12

Reference Topology HON02

Version 1.00.00

3.4.4 PROFIBUS PA Cable Type A Network
The PROFIBUS PA Cable Type A Network is mandatory for this reference topology, with limited impact tointegration tests. Honeywell Process Solutions and Endress+Hauser recommend equipment provided byPepperl+Fuchs and R.STAHL for this reference topology.
Recommended hardware:

Segment Protector

ArticleDescription

R2-SP-IC*

Fieldbus device coupler for safe area or Zone 2 application.
Optional 4, 6, 8 or 10 spurs.

Field Barrier

R4D0-FB-IA*

Fieldbus device coupler for Zone 1 application.
Optional 8, 10 or12 spurs. Compliant to FISCO and Entity concept.

ArticleDescriptionField Device Coupler
Zone 2 En n9410/34-*

Fieldbus device coupler for safe area or Zone 2 Ex n application.

Field Device Coupler
Zone 1 Ex i

9411/21-*

Optional 4, 8 or 12 spurs.

SD02062S/04/EN/01.17

Fieldbus device coupler for Zone 1 Ex i application.
Optional 4 or 8 spurs. Compliant to FISCO concept.

8/12

Reference Topology HON02

Version 1.00.00

3.5 Field Devices
Open Integration reference topologies always have to be tested versus a selection of most relevant fielddevices for the target market defined in chapter 2.1. This serves to verify that the system under test iscapable to handle a necessary variety of certified field devices. All field devices are fully compliant tostandards, but may be implemented versus different version of standards and each field device typically
implements only a subset of relevant compliant means.
This chapter defines only a basic set of mandatory field devices for verification of this reference topology,
as agreed by Honeywell Process Solutions and Endress+Hauser. For more details, please refer to latest listof tested devices and versions for this reference topology, referenced in chapter 1.3.
3.5.1 PROFIBUS DP devices
Reference hardware:
ArticleDescription

Device Type

Promass 83

83F

Coriolis Flow Transmitter

0x1529

Promag 53

53PElectromagnetic Flow Transmitter

0x1526

3.5.2 PROFIBUS PA devices
Reference hardware:
ArticleDescription

Omnigrad M

TR10+TMT84

Temperature Transmitter

0x1551

Cerabar S

PMC71

Absolute and Gauge Pressure Transmitter

0x1541

SD02062S/04/EN/01.17

Device Type

9/12

Reference Topology HON02

Version 1.00.00

Reference hardware:
ArticleDescription

Liquiphant

FTL51

Vibronic Point Level Detection

0x152BDeltabar S

PMD75

Differential Pressure Transmitter

0x1542

Micropilot

FMR51

Radar Level Transmitter

0x1559

Cerabar M

PMP51

Absolute and Gauge Pressure Transmitter

0x1553Gammapilot

FMG60

Radiometric Level and Density Transmitter

0x1548Prowirl 200

7F2B

Vortex Flow Transmitter

0x1564

Levelflex

FMP51

Guided Radar Level Transmitter

0x1558Liquiline M

CM42

Liquid Analyzer Transmitter

0x1543

CPS11D

Memosens Digital pH Sensor

0x1544

CYK10

Memosens Digital Data Cable

0x154B

SD02062S/04/EN/01.17

Device Type

10/12

Reference Topology HON02

SD02062S/04/EN/01.17

Version 1.00.00

11/12

Reference Topology HON02

Version 1.00.00

www.endress.com/open-integration

SD02062S/04/EN/01.17

12/12