BA02046S/00/EN/04.24-00
71654358
2024-03-01

Products

Solutions

Services

Operating Instructions
FieldPort SWA50
Intelligent WirelessHART adapter for HART measuring
instruments

Revision history

FieldPort SWA50

Revision history

2

Product
versionOperatingInstructions

ChangesComments

1.00.XX

BA02046S/04/EN/
01.20

–

Initial version

1.00.XX

BA02046S/04/EN/
02.21

Supply voltage
Burst

Corrections

1.00.XX

BA02046S/04/EN/
03.21

Alignment
Range
Note on status signal
Notes and references"Diagnostics" section

Amendments and changes

1.01.XX

BA02046S/04/EN/
04.24

Following sections:• Range• Operation options• Commissioning• Description of SmartBlue app for
SWA50• Description of DTM for SWA50• Updating the firmware• Diagnostics• Menu overview

Additions and changes basedon• New SWA50 firmware
incl. MSD
• Changeover of Field Xpert
operation from MSD to
DTM

Endress+Hauser

FieldPort SWA50

Table of contents

Table of contents
5.7

Post-mounting check . . . . . . . . . . . . . . . . . . . 28

6

Electrical connection . . . . . . . . . . . . . . 29

6.1
6.2
6.3
6.4

6.9

Supply voltage . . . . . . . . . . . . . . . . . . . . . . . .
Cable specification . . . . . . . . . . . . . . . . . . . . .
Terminal assignment . . . . . . . . . . . . . . . . . . .
Stripping in the case of a cable gland forshielded cable . . . . . . . . . . . . . . . . . . . . . . . .
2-wire HART field device with passive current
output . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .
4-wire HART field device with passive current
output . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .
4-wire HART field device with active current
output . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .
FieldPort SWA50 without HART field device(repeater) . . . . . . . . . . . . . . . . . . . . . . . . . . .
Post-connection check . . . . . . . . . . . . . . . . . .

7

Operation options . . . . . . . . . . . . . . . . . 34

7.1
7.2
7.3
7.4
7.5

Overview of operation options . . . . . . . . . . . .
Operation via SmartBlue app . . . . . . . . . . . . .
Operation via Field Xpert . . . . . . . . . . . . . . . .
Operation via FieldCare . . . . . . . . . . . . . . . . .
Local operation via Field Xpert or FieldCare . .

Product description . . . . . . . . . . . . . . . . 10

8Commissioning . . . . . . . . . . . . . . . . . . . . 36

3.1
3.2

Function . . . . . . . . . . . . . . . . . . . . . . . . . . . . 10
System architecture of FieldPort SWA50
WirelessHART version . . . . . . . . . . . . . . . . . . 11

8.1
8.2

4

Incoming acceptance and productidentification . . . . . . . . . . . . . . . . . . . . . 12

4.1
4.2
4.3

Incoming acceptance . . . . . . . . . . . . . . . . . . . 12
Product identification . . . . . . . . . . . . . . . . . . . 12
4.2.1 Nameplate . . . . . . . . . . . . . . . . . . . . 12
4.2.2 Manufacturer's address . . . . . . . . . . . 12
Storage and transport . . . . . . . . . . . . . . . . . . 12

Overview of operation options . . . . . . . . . . . . 36
Requirements . . . . . . . . . . . . . . . . . . . . . . . . 36
8.2.1 Requirements of the FieldPort
SWA50 . . . . . . . . . . . . . . . . . . . . . . . 36
8.2.2 Information required forcommissioning . . . . . . . . . . . . . . . . . 36
8.2.3 Points to check before
commissioning . . . . . . . . . . . . . . . . . 36
8.2.4 Initial password . . . . . . . . . . . . . . . . . 37
Putting the FieldPort SWA50 into operation . . 37
8.3.1 Commissioning via SmartBlue app . . . 37
8.3.2 Commissioning via Field Xpert . . . . . . 40
8.3.3 Commissioning via FieldCare . . . . . . . 42

5

Mounting . . . . . . . . . . . . . . . . . . . . . . . . . 13

5.1
5.2
5.3

Mounting instructions . . . . . . . . . . . . . . . . . . 13
Range . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 13
Mounting options . . . . . . . . . . . . . . . . . . . . . 14
5.3.1 "Direct mounting" version . . . . . . . . . . 14
5.3.2 "Remote mounting" version . . . . . . . . 15
Mounting the "direct mounting" version . . . . . 15
Mounting the "remote mounting" version . . . . 21
Installing the FieldPort SWA50 withmounting bracket . . . . . . . . . . . . . . . . . . . . . 25
5.6.1 Mounting and alignment options . . . . 25
5.6.2 Dimensions . . . . . . . . . . . . . . . . . . . . 26
5.6.3 Installing the mounting bracket andFieldPort SWA50 . . . . . . . . . . . . . . . 27

1

About this document . . . . . . . . . . . . . . . . 5

1.1
1.2

1.3
1.4
1.5
1.6

Purpose of this document . . . . . . . . . . . . . . . . . 5
Symbols . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 5
1.2.1 Safety symbols . . . . . . . . . . . . . . . . . . 5
1.2.2 Symbols forcertain types of information . . . . . . . . . 5
1.2.3 Symbols in graphics . . . . . . . . . . . . . . . 6
1.2.4 Electrical symbols . . . . . . . . . . . . . . . . 6
1.2.5 SmartBlue app icons . . . . . . . . . . . . . . 6
Terms and abbreviations . . . . . . . . . . . . . . . . . 6
Valid versions . . . . . . . . . . . . . . . . . . . . . . . . . 7
Documentation . . . . . . . . . . . . . . . . . . . . . . . . 7
Registered trademarks . . . . . . . . . . . . . . . . . . 7

2

Basic safety instructions . . . . . . . . . . . . 8

6.8

2.1
2.2
2.3
2.4
2.5
2.6
2.7

Requirements for personnel . . . . . . . . . . . . . . . 8
Designated use . . . . . . . . . . . . . . . . . . . . . . . . 8
Workplace safety . . . . . . . . . . . . . . . . . . . . . . . 8
Operational safety . . . . . . . . . . . . . . . . . . . . . . 8
Product safety . . . . . . . . . . . . . . . . . . . . . . . . . 8
IT security . . . . . . . . . . . . . . . . . . . . . . . . . . . . 9
Device-specific IT security . . . . . . . . . . . . . . . . . 9
2.7.1 Access via Bluetooth® wirelesstechnology . . . . . . . . . . . . . . . . . . . . . 9

3

5.4
5.5
5.6

Endress+Hauser

6.5
6.6
6.7

8.3

29
29
30
30
31
31
31
32
33

34
34
34
34
34

9

Operation . . . . . . . . . . . . . . . . . . . . . . . . . 43

9.1
9.2

Hardware locking . . . . . . . . . . . . . . . . . . . . . . 43
LEDs . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 43

10

Description of SmartBlue app for
SWA50 . . . . . . . . . . . . . . . . . . . . . . . . . . . 44

10.1 Menu overview (Navigation) . . . . . . . . . . . . . 44
10.2 "Device information" page . . . . . . . . . . . . . . . . 44
10.3 "Diagnostics: WirelessHART" page . . . . . . . . . . 47
10.4 "Diagnostics: FieldPort SWA50" page . . . . . . . 47
10.5 "Diagnostics: Field device" page . . . . . . . . . . . . 48

3

Table of contents

10.6

10.7

10.8

10.9

FieldPort SWA50"Application: FieldPort SWA50" page . . . . . . . 50
10.6.1 "Measured values" page (FieldPort
SWA50) . . . . . . . . . . . . . . . . . . . . . . 50
10.6.2 "HART info" page (FieldPort SWA50) . 50
"Application: Field device" page . . . . . . . . . . . . 51
10.7.1 "Measured values" page (Field
device) . . . . . . . . . . . . . . . . . . . . . . . 51
10.7.2 "HART info" page (Field device) . . . . . 51
"System: FieldPort SWA50" page . . . . . . . . . . . 52
10.8.1 "Device management" page (FieldPort
SWA50) . . . . . . . . . . . . . . . . . . . . . . 52
10.8.2 "Connectivity" page (FieldPort
SWA50) . . . . . . . . . . . . . . . . . . . . . . 52
10.8.3 "Burst period configuration" page
(FieldPort SWA50) . . . . . . . . . . . . . . 54
10.8.4 "Geolocation" page
(FieldPort SWA50) . . . . . . . . . . . . . . 55
10.8.5 "Information" page
(FieldPort SWA50) . . . . . . . . . . . . . . 55
"System: Field device" page . . . . . . . . . . . . . . . 56
10.9.1 "Device management" page (Field
device) . . . . . . . . . . . . . . . . . . . . . . . 56
10.9.2 "Information" page (Field device) . . . . 56

11

Description of DTM for SWA50 . . . . . 57

11.1
11.2
11.3
11.4
11.5
11.6

Identification . . . . . . . . . . . . . . . . . . . . . . . . . 57
Wireless Communication . . . . . . . . . . . . . . . . 58
Wired Communication . . . . . . . . . . . . . . . . . . 61
Device Variable Mapping . . . . . . . . . . . . . . . . 62
Burst Mode . . . . . . . . . . . . . . . . . . . . . . . . . . 64
Event Notification . . . . . . . . . . . . . . . . . . . . . 67

12

Diagnostics . . . . . . . . . . . . . . . . . . . . . . . 73

12.1
12.2
12.3
12.4
12.5

Calling up diagnostics . . . . . . . . . . . . . . . . . . 73
Identification . . . . . . . . . . . . . . . . . . . . . . . . . 73
Wireless Communication . . . . . . . . . . . . . . . . 74
Wired Communication . . . . . . . . . . . . . . . . . . 75
Health Status . . . . . . . . . . . . . . . . . . . . . . . . . 75
12.5.1 NAMUR NE 107 . . . . . . . . . . . . . . . . 76
12.5.2 ASM . . . . . . . . . . . . . . . . . . . . . . . . . 76
12.5.3 HART . . . . . . . . . . . . . . . . . . . . . . . . 77

13

Other DTM functions . . . . . . . . . . . . . . 78

13.1

Lock / Unlock . . . . . . . . . . . . . . . . . . . . . . . .

14

Diagnostics and troubleshooting . . . 80

16.2

Disposal . . . . . . . . . . . . . . . . . . . . . . . . . . . .

86

17

Accessories . . . . . . . . . . . . . . . . . . . . . . . 87

18

Technical data . . . . . . . . . . . . . . . . . . . . 88

19

Appendix . . . . . . . . . . . . . . . . . . . . . . . . . 89

19.1

Menu overview (SmartBlue app navigation) . . 89
19.1.1 FieldPort SWA50 withWirelessHART . . . . . . . . . . . . . . . . . 89

78

14.1 Diagnostics . . . . . . . . . . . . . . . . . . . . . . . . . . 80
14.2 Troubleshooting . . . . . . . . . . . . . . . . . . . . . . 81

15

Maintenance . . . . . . . . . . . . . . . . . . . . . . 83

15.1 General maintenance . . . . . . . . . . . . . . . . . . . 83
15.2 Updating the firmware . . . . . . . . . . . . . . . . . . 83

16

Repair . . . . . . . . . . . . . . . . . . . . . . . . . . . . 86

16.1

General notes . . . . . . . . . . . . . . . . . . . . . . . .

4

86Endress+Hauser

FieldPort SWA50

About this document

1

About this document

1.1

Purpose of this document

These Operating Instructions contain all the information that is required in the various
phases of the life cycle of the device: from product identification, incoming acceptance andstorage, to mounting, connection, operation and commissioning through totroubleshooting, maintenance and disposal.

1.2

Symbols

1.2.1

Safety symbols

DANGER

This symbol alerts you to a dangerous situation. Failure to avoid this situation will result inserious or fatal injury.
WARNING

This symbol alerts you to a dangerous situation. Failure to avoid this situation can result inserious or fatal injury.
CAUTION

This symbol alerts you to a dangerous situation. Failure to avoid this situation can result inminor or medium injury.
NOTICE

This symbol contains information on procedures and other facts which do not result inpersonal injury.

1.2.2

Symbols for certain types of information
SymbolMeaning
Permitted
Procedures, processes or actions that are permitted.
Preferred
Procedures, processes or actions that are preferred.
Forbidden
Procedures, processes or actions that are forbidden.
Tip
Indicates additional information.
Reference to documentationA

Reference to page
Reference to graphic
Notice or individual step to be observed

1. , 2. , 3. …

Series of steps
Result of a step
Help in the event of a problem
Visual inspection

Endress+Hauser

5About this document

FieldPort SWA50

1.2.3

Symbols in graphics

SymbolMeaning

SymbolMeaning

1, 2, 3,...

Item numbers

1. , 2. , 3. …

Series of steps

A, B, C, ...

Views
Hazardous area

1.2.4

A-A, B-B, C-C, ...

.

Sections
Safe area (non-hazardous area)

Electrical symbols
SymbolMeaning
Direct current
Alternating current
Direct current and alternating current
Ground connection
A grounded terminal which, as far as the operator is concerned, is grounded via agrounding system.
Potential equalization connection (PE: protective earth)Ground terminals that must be connected to ground prior to establishing any otherconnections.
The ground terminals are located on the interior and exterior of the device:• Interior ground terminal: potential equalization is connected to the supply network.
• Exterior ground terminal: device is connected to the plant grounding system.

1.2.5
Icon

SmartBlue app icons
Meaning
SmartBlue
Accessible field devices
Home
Menu
Settings

1.3

Terms and abbreviations

Term

Description

DeviceCare

Universal configuration software for Endress+Hauser HART, PROFIBUS, FOUNDATION
Fieldbus and Ethernet field devices

DTM

Device Type Manager

FieldCare

Scalable software tool for device configuration and integrated plant asset management
solutions

Loop-powered adapter Loop-powered adapter

6

Endress+Hauser

FieldPort SWA50

About this document

1.4

Valid versions

Component

VersionSoftwareV1.01.xx

HardwareV1.00.xx

1.5

Documentation

Current documentation such as Operating Instructions, certificates and approvals for the
product are available at www.endress.com on the relevant product page:1.

Select the product using the filters and search field.

2.

Open the product page.

3.

Select Downloads.

Ex documentation
All explosion-protection data are provided in separate Ex documentation. The relevant Ex
documentation is delivered with the Ex devices as standard.
If there is additional documentation for the device version, the documentation code ofthis supplementary documentation is specified on the nameplate.

1.6

Registered trademarks

HART®
Registered trademark of the FieldComm Group, Austin, Texas, USA
Bluetooth®
The Bluetooth® word mark and logos are registered trademarks owned by the Bluetooth
SIG, Inc. and any use of such marks by Endress+Hauser is under license. Other trademarks
and trade names are those of their respective owners.
Apple®
Apple, the Apple logo, iPhone, and iPod touch are trademarks of Apple Inc., registered in
the U.S. and other countries. App Store is a service mark of Apple Inc.
Android®
Android, Google Play and the Google Play logo are trademarks of Google Inc.

Endress+Hauser

7Basic safety instructions

FieldPort SWA50

2

Basic safety instructions

2.1

Requirements for personnel

The personnel for installation, commissioning, diagnostics and maintenance must meetthe following requirements:‣ Trained, qualified specialists: must have a relevant qualification for this specific roleand task and have been trained by Endress+Hauser. Experts at the Endress+Hauser
service organization.
‣ Personnel must be authorized by the plant owner/operator.
‣ Personnel must be familiar with regional and national regulations.
‣ Before starting work: personnel must read and understand the instructions in the
manual and supplementary documentation as well as the certificates (depending on
the application).
‣ Personnel must follow instructions and comply with general policies.
Operating personnel must meet the following requirements:‣ Personnel are instructed and authorized according to the requirements of the task by
the facility's owner-operator.

‣ Personnel follow the instructions in this manual.

2.2

Designated use

The FieldPort SWA50 is a loop-powered adapter that converts the HART signal of theconnected HART field device into a reliable and encrypted WirelessHART signal. The
FieldPort SWA50 can be retrofitted to all 2-wire or 4-wire HART field devices.
The Bluetooth signal may not be used to replace the wiring in the case of safety
applications with a control function.
Incorrect use
Non-designated use can compromise safety. The manufacturer is not liable for damage
caused by improper or non-designated use.

2.3

Workplace safety

When working on and with the device:‣ Wear the required personal protective equipment as per national regulations.

2.4

Operational safety

Risk of injury!

‣ Operate the device only if it is in proper technical condition, free from errors and faults.
‣ The operator is responsible for interference-free operation of the device.
Modifications to the device
Unauthorized modifications to the device are not permitted and can lead to unforeseeable
dangers:‣ If modifications are nevertheless required, consult with Endress+Hauser.

2.5

Product safety

This device is designed in accordance with good engineering practice to meet state-of-theart safety requirements, has been tested, and left the factory in a condition in which it issafe to operate.

8Endress+Hauser

FieldPort SWA50

Basic safety instructions

The device fulfills general safety requirements and legal requirements. It also complies
with the EU/EC directives listed in the device-specific EU Declaration of Conformity.
Endress+Hauser confirms this by affixing the CE mark to the device.

2.6

IT security

We only provide a warranty if the device is installed and used as described in the
Operating Instructions. The device is equipped with security mechanisms to protect itagainst any inadvertent changes to the device settings.
IT security measures in line with operators' security standards and designed to provide
additional protection for the device and device data transfer must be implemented by theoperators themselves.
For detailed information, see the Security Manual SD02984S(www.endress.com/SWA50)

2.7

Device-specific IT security

2.7.1

Access via Bluetooth® wireless technology

Signal transmission via Bluetooth® wireless technology uses a cryptographic
technique tested by Fraunhofer AISEC.
• Connection via Bluetooth® is not possible without specific Endress+Hauser devices or the
SmartBlue app.
• Only one point-to-point connection between one FieldPort SWA50 device and one
smartphone or tablet is established.
• The Bluetooth® wireless technology interface can be protected incrementally by meansof hardware locking. →  43
• The hardware locking cannot be disabled or bypassed using operating tools.

Endress+Hauser

9Product description

FieldPort SWA50

3

Product description

3.1

Function

The FieldPort SWA50 converts the HART signal of the connected HART field device into areliable and encrypted Bluetooth® or WirelessHart signal. The FieldPort SWA50 can be
retrofitted to all 2-wire or 4-wire HART field devices.
The following operating tools are available for the FieldPort SWA50:• The Endress+Hauser SmartBlue app for mobile devices• An Endress+Hauser Field Xpert SMTxx tablet PC• The Endress+Hauser FieldCare SFE500 field device configuration tool
Depending on the operating tool, the following functions are available:• Configuration of the FieldPort SWA50• Visualization of the measured values of the connected HART field device• Visualization of the current status of the FieldPort SWA50 and the connected HART
field device• Configuration of the connected HART field device
HART field devices can be connected to the Netilion Cloud via the FieldPort SWA50 and a
FieldEdge device.
Detailed information on Netilion Cloud: https://netilion.endress.com
The WirelessHART version of the FieldPort SWA50 can be integrated into a
WirelessHART network via the Endress+Hauser FieldGate SWG50 or via any compatible
WirelessHART gateway. More information is available from your Endress+Hauser salesorganization: www.addresses.endress.com.
NOTICE
Safety applications with control functions via WirelessHART signal
Undesirable behavior of safety application‣ Do not use a wireless signal such as WirelessHART in a safety application with acontrol function.

10

Endress+Hauser

FieldPort SWA50

Product description

3.2

System architecture of FieldPort SWA50
WirelessHART version
1

2

3

4

7

5 6

8

6

9

10

1

Netilion

WirelessHART

16

15

14

13

12

11
A0043239

Endress+Hauser

1

System architecture of SWA50 WirelessHART version

1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16

Endress+Hauser Field Xpert such as SMTxx
Host application / FieldCare SFE500
Ethernet communication
WirelessHART gateway, e.g. FieldGate SWG50
FieldEdge SGC500
https Internet connection
Netilion cloudApplication Programming Interface (API)Internet browser-based Netilion Service app or user application
Endress+HauserSmartBlue app
Encrypted wireless connection via Bluetooth®
HART field device with FieldPort SWA50, direct mounting
HART field device with WirelessHART adapter, e.g., SWA70
FieldPort SWA50 as repeater
Encrypted wireless connection via WirelessHARTHART field device with FieldPort SWA50, remote mounting

11Incoming acceptance and product identification

4

Incoming acceptance and productidentification

4.1

Incoming acceptanceFieldPort SWA50• Check the packaging for visible damage arising from transportation• Open the packaging carefully• Check the contents for visible damage• Check that the delivery is complete and nothing is missing• Retain all the accompanying documents
The device may not be put into operation if the contents are found to be damaged
beforehand. In this case, please contact your Endress+Hauser Sales Center:
www.addresses.endress.com
Return the device to Endress+Hauser in the original packaging where possible.
Scope of delivery• FieldPort SWA50• Cable glands as per ordered version• Optional: mounting bracket
Documentation included in delivery• Brief Operating Instructions• Depends on the version ordered: Safety Instructions

4.2

Product identification

4.2.1

Nameplate

The nameplate of the device is lasered onto the housing.
Additional information about the device is available as follows:• Enter the serial number specified on the nameplate into the Device Viewer(www.endress.com → Product tools → Access device specific information → Device
Viewer (from the serial number to device information and documentation) → Selectoption → Enter serial number): All information relating to the device is then displayed.
• Enter the serial number specified on the nameplate into theEndress+Hauser Operations App: All information relating to the device is then displayed.

4.2.2

Manufacturer's address

Endress+Hauser SE+Co. KG
Hauptstraße 179689 Maulburg
Germany
www.endress.com

4.3

Storage and transport• The components are packed in such a way that they are fully protected against shock
when in storage and during transportation.
• The permitted storage temperature is –40 to +85 °C (–40 to 185 °F).
• Store the components in the original packaging in a dry place.
• Where possible, only transport the components in the original packaging.

12

Endress+Hauser

FieldPort SWA50

Mounting

5

Mounting

5.1

Mounting instructions• Pay attention to the alignment and range. →  13
• Observe a distance of at least 6 cm from walls and pipes. Pay attention to the expansionof the Fresnel zone.
• Avoid mounting in close proximity to high-voltage devices.
• For a better connection, mount the FieldPort SWA50 in sight of a WirelessHART
network subscriber.
• Pay attention to the effect of vibrations at the mounting location.
We recommend that you protect the FieldPort SWA50 against precipitation anddirect sunlight. In order not to reduce signal quality, do not use a metal cover.
For detailed information on the vibration resistance, see the Technical Information for
the FieldPort SWA50 (TI01468S)

5.2

Range
The range depends on the alignment of the FieldPort SWA50, the mounting locationand the environmental conditions.
Since the antenna of the WirelessHART gateway is aligned vertically as a general rule,the ideal orientation for the FieldPort SWA50 is also vertical. If the antennas arealigned differently, this can greatly reduce the antenna range.

60°
40°
30°

120°
80°

100°

80°
30°
40°
30°

30°
80°
A0043409

2Different ranges depending on the position of the transmission window

BluetoothUp to 30 m (98 ft) without obstacles when FieldPort SWA50 is optimally aligned
WirelessHART• Up to 175 m (574 ft) without obstacles, between FieldGate SWG50 with 6 dBi antenna
and FieldPort SWA50, optimally aligned• Up to 75 m (246 ft) without obstacles, between FieldGate SWG50 with 2 dBi antenna
and FieldPort SWA50, optimally aligned• Up to 50 m (146 ft) without obstacles, between WirelessHART adapter SWA70 and
FieldPort SWA50, optimally aligned• Up to 25 m (82 ft) without obstacles, between two FieldPort SWA50 adapters, optimallyalignedEndress+Hauser

13

MountingFieldPort SWA50

5.3

Mounting options

5.3.1"Direct mounting" version
1

4
5

2

6
7

3

A0043241

3
1
2
3
4
5
6
7

Example of direct mounting
Cable
FieldPort SWA50 "direct mounting" version
HART field device
Bottom housing section
Transmission window
Design ring
Top housing section

Montage sequence for the "direct mounting" version: →  15

14

Endress+Hauser

FieldPort SWA50

Mounting

5.3.2"Remote mounting" version
1

2

4
5

3

6
7

A0043240

4
1
2
3
4
5
6
7

Example of remote mounting
HART field device
Cable
FieldPort SWA50 "remote mounting" version
Housing baseTransmission window
Design ring
Top housing section

For remote mounting, we recommend the optional mounting bracket →  25.
Alternatively, you can secure the remote version using pipe clips.
Mounting sequence for the "remote mounting" version: →  21

5.4

Mounting the "direct mounting" version

NOTICE
Damaged seals.
IP degree of protection is no longer guaranteed.
‣ Do not damage seals.
NOTICE
Supply voltage is present during installation.
Possible damage to the device.
‣ Switch off supply voltage prior to installation.
‣ Make sure the device is de-energized.
‣ Secure it against being switched back on.
Electrical connection: →  29
Tools required• Wrench AF24
• Wrench AF36

Endress+Hauser

15

MountingFieldPort SWA50

Mounting the FieldPort SWA50
1.

1.

2.

A0040564

2.

1.

2.
A0040565

3.

A0041512

4.

A0040500

16

Endress+Hauser

FieldPort SWA50

Mounting

5.

A0040502

6.

A0040501

Endress+Hauser

17

MountingFieldPort SWA50

7.
7 (0.28)
+ IN

+ IN

28 (1.10)+ OUT –+ IN -

7 (0.28)

A0041551

Ensure that the cores are of sufficient length to be connected in the field device. Do
not shorten the cores to the required length until you are connecting them in thefield device.
If you use a cable gland for a shielded cable, pay attention to the information on
stripping the wire →  30.
• Electrical connection for 2-wire HART field devices with passive current output:→  31• Electrical connection for 4-wire HART field devices with passive current output:→  31• Electrical connection for 4-wire HART field devices with active current output:→  31• Electrical connection for FieldPort SWA50 without HART field device: →  32
8.

A0041552

Tighten screws for strain relief. Torque: 0.4 Nm ± 0.04 Nm

18

Endress+Hauser

FieldPort SWA50

Mounting

9.

A0041553

Slide the electronic insert into the guide inside the housing.
10.
2.

1.

A0040506

For information regarding torque, see the field device documentation.
11.

A0041554

Ensure that the cores are of sufficient length to be connected in the field device.
Shorten the cores in the field device to the required length.

Endress+Hauser

19

MountingFieldPort SWA50

12.

2.

1.

A0040566

Do not tighten the top housing section yet, so that you are still able to rotate thebottom housing section.
13.

A0040568

Align the bottom housing section with the transmission window according to the
network architecture →  13.
To avoid wire breaks, rotate the bottom housing section by a maximum of ± 180°.
14.

A0040569

Tighten the top housing section so that the blue design ring can still be rotatedafterwards. Torque: 5 Nm ± 0.05 Nm

20

Endress+Hauser

FieldPort SWA50

Mounting

15.

A0040567

16. Perform commissioning →  36.

5.5

Mounting the "remote mounting" version

NOTICE
Damaged seal.
IP degree of protection is no longer guaranteed.
‣ Do not damage seal.
NOTICE
Supply voltage is present during installation.
Possible damage to the device.
‣ Switch off supply voltage prior to installation.
‣ Make sure the device is de-energized.
‣ Secure it against being switched back on.
For remote mounting, we recommend the optional mounting bracket. Alternatively,
you can secure the remote version using pipe clips.
Electrical connection: →  29
Tools required• Wrench AF27
• Wrench AF36
Mounting the FieldPort SWA50
1.

A0040498

Endress+Hauser

21

MountingFieldPort SWA50

2.

1.

2.
A0040499

3.

A0041512

4.

A0040500

5.

If you are mounting the FieldPort SWA50 using the optional mounting bracket,
follow the instructions in the "Mounting the mounting bracket and FieldPort SWA50"
section→  27.

6.

A0041513

22

Endress+Hauser

FieldPort SWA50

Mounting

7.

A0040503

8.

A00405019.
7 (0.22)
+ IN

+ IN

28 (1.10)+ OUT –+ IN -

7 (0.22)

A0040504

If you use a cable gland for a shielded cable, pay attention to the information on
stripping the wire →  30.
• Electrical connection for 2-wire HART field devices with passive current output:→  31• Electrical connection for 4-wire HART field devices with passive current output:→  31• Electrical connection for 4-wire HART field devices with active current output:→  31• Electrical connection for FieldPort SWA50 without HART field device: →  32

Endress+Hauser

23

MountingFieldPort SWA50

10.

A0040507

Tighten screws for strain relief. Torque: 0.4 Nm ± 0.04 Nm
11.

A0040508

Slide the electronic insert into the guide inside the housing.
12.

2.

1.
A0040509

Tighten the top housing section so that the blue design ring can still be rotatedafterwards. Torque: 5 Nm ± 0.05 Nm
13.

A004051024

Endress+Hauser

FieldPort SWA50

Mounting

14. Perform commissioning →  36.

5.6

Installing the FieldPort SWA50 with mounting
bracket5.6.1

Mounting and alignment options

The mounting bracket can be mounted as follows:• On pipes with a maximum diameter of 65 mm• On walls
The FieldPort can be aligned as follows using the support bracket:• Via the various mounting positions on the mounting bracket• By rotating the support bracket
Pay attention to the alignment and range →  13.

1

2

A0043411

Endress+Hauser

5

Alignment options via support bracket

1
2

Various mounting positions on support bracket
By rotating the support bracket

25

MountingFieldPort SWA50

5.6.2

Dimensions
165 (6.50)
87 (3.43)

Ø 65(Ø 2.56)

52 (2.05)

81 (3.19)

A0043313

40(1.75)

18 (0.71)

Dimensions of mounting bracket – pipe mounting

28 (1.10)

6

4.75 (0.19)
18 (0.71)

33(1.30)

78 (3.07)

103 (4.06)
A0043410

7

26

Dimensions of retaining bracket – wall mounting

Endress+Hauser

FieldPort SWA50

Mounting

5.6.3

Installing the mounting bracket and FieldPort SWA50
1 2

3

4

A0043312

8
1
2
3
4

FieldPort SWA50 mounted via optional mounting bracket
Hexagonal-headed bolt for securing and grounding
Support bracket
Mounting bracket
Round bracket

If you are mounting the FieldPort SWA50 using the mounting bracket, you must
remove the design ring between the top housing section and the bottom housing
section.
Tools required• Wrench AF10
• Allen key size 4
Installing the mounting bracket on a pipe

‣ Secure the mounting bracket to the pipe at the desired location. Torque: minimum
5 Nm

If you change the position of the support bracket on the mounting bracket, tighten thefour hexagonal-headed bolts with a torque of 4 Nm to 5 Nm.
Installing the mounting bracket on a wall

‣ Secure the support bracket to the wall at the desired location. The screws must be
suitable for the wall.

Mounting the FieldPort SWA50
Pay attention to the "Mounting the "remote mounting" version" section →  21.

Endress+Hauser

1.

Unscrew the cable glands of the FieldPort SWA50.

2.

Unscrew the top housing section.

3.

Remove the electronic insert from the housing.

4.

Remove the design ring from the bottom housing section.

5.

Slide the bottom housing section into the eyelet of the support bracket.

27

MountingFieldPort SWA50

6.

Carry out electrical connection for the FieldPort SWA50.

7.

Slide the electronic insert into the bottom housing section.

8.

Loosely screw on the top housing section.

9.

Align the bottom housing section with the transmission window of the FieldPort
SWA50 according to the network architecture. The transmission window is locatedunder the black plastic seal.

10. Tighten the top housing section. Torque: 5 Nm ± 0.05 Nm
11. Connect the protective ground to the hexagonal-headed bolt.
12. Tighten the hexagonal-headed bolt so that the FieldPort SWA50 is secured in themounting bracket.

5.7

Post-mounting check

Is the device undamaged (visual inspection)?



Does the device comply with the required specifications?



For example:• Ambient temperature• Humidity• Explosion protection

28

Are the screws that provide strain relief for the electronic insert tightened with the correct
torque?

Is the top housing section tightened with the correct torque?



Are all securing screws, such as those for the optional mounting bracket, firmly tightened?

Are the measuring point identification and labeling correct (visual inspection)?

Is the device aligned correctly with regard to the antenna range? →  13

Endress+Hauser

FieldPort SWA50

Electrical connection

6

Electrical connection

NOTICE
Short-circuit at OUT+ and OUT– terminals
Damage to device‣ Depending on the application, connect either the field device, PLC, transmitter orresistor to the OUT+ and OUT– terminals.
‣ Never short-circuit the OUT+ and OUT– terminals.

6.1

Supply voltage• Loop-powered 4 to 20 mA• 24 V DC (min. 4 V DC, max. 30 V DC): min. 3.6 mA loop current required for start-up• The supply voltage or the power unit must be tested to ensure it meets safety
requirements and the requirements for SELV, PELV or Class 2
Voltage drop
• If internal HART communication resistor is deactivated• 3.2 V in operation• < 3.8 V at start-up• If internal HART communication resistor is activated (270 Ohm)
• < 4.2 V at 3.6 mA loop current• < 9.3 V at 22.5 mA loop current
To select the supply voltage, pay attention to the voltage drop via the FieldPort
SWA50. The remaining voltage must be high enough to enable the start-up andoperation of the HART field device.

6.2

Cable specification

Use cables that are suitable for the anticipated minimum and maximum temperatures.
Observe grounding concept of the plant.
2 x 0.25 mm² to 2 x 1.5 mm²
You can use unshielded cable with or without ferrules and shielded cable with or without
ferrules.
If you select the "direct mounting" version and the "4-wire HART field device withactive current output and PLC or transmitter" electrical connection version, you can
use core cross-sections of 0.75 mm² at maximum. If larger core cross-sections are
required, we recommend remote mounting.

Endress+Hauser

29

Electrical connection

FieldPort SWA50

6.3

Terminal assignment
1+ IN -+ OUT –

21234

+ OUT –+ IN –

ON
OFF

A0040495

912

FieldPort SWA50 terminal assignment
Input terminal IN
Output terminal OUT

Application

Input terminal IN

Output terminal OUT

2-wire HART field device→  11,  31

Cable from supply voltage, PLC withactive current output or transmitterwith active current output

Cable to 2-wire HART field device

4-wire HART field device with
passive current output→  12,  31

Cable from supply voltage, PLC withactive current output or transmitterwith active current output

Cable to 4-wire HART field device

4-wire HART field device withactive current output→  31

Cable from 4-wire field device withactive 4 to 20 mA HART output

PLC or transmitter with passive
current output (optional),
alternatively wire bridge between
terminals OUT+ and OUT–

FieldPort SWA50 without fielddevice→  15,  33

Cable from supply voltage for FieldPort
SWA50

Resistor between terminals OUT+
and OUT–

6.4

Stripping in the case of a cable gland for shieldedcable

If you are using shielded cables and wish to connect the cable shield to the FieldPort
SWA50, you must use cable glands for shielded cable.
If you have ordered the "Brass M20 for shielded cable" option for the cable glands, you will
receive the following cable glands:• "Direct mounting" version: 1 cable gland for shielded cable• "Remote mounting" version: 2 cable glands for shielded cable
When mounting a cable gland for shielded cable, we recommend the following dimensions
for stripping. The dimensions for input terminal IN and output terminal OUT are different.

IN

5.5 (0.22)

OUT

7 (0.28)13(0.51)

28 (1.10)

7 (0.28)
28 (1.10)

5.5 (0.22)
18(0.71)
A0043665

 1030

Recommended dimensions for stripping in the case of cable glands for shielded cable for input terminal IN
and output terminal OUT

Endress+Hauser

FieldPort SWA50

Electrical connection• Sealing area (jacket):  4 to 6.5 mm (0.16 to 0.25 in)• Shielding: 2.5 to 6 mm (0.1 to 0.23 in)

6.5

2-wire HART field device with passive current output
Some grounding concepts require shielded cables. If connecting the cable shield to theFieldPort SWA50, you must use a cable gland for shielded cable. See ordering
information.

–

IN–

OUT–

–

+

IN+

OUT+

+

1

3

2

A0040494

 11
1
2
3

Electrical connection for 2-wire HART field devices with passive current output (optional grounding notshown)

Supply voltage (SELV, PELV or Class 2) or PLC with active current input or transmitter with active current
inputElectronic insert SWA50
2-wire field device 4 to 20 mA-HART

6.6

4-wire HART field device with passive current output
Some grounding concepts require shielded cables. If connecting the cable shield to theFieldPort SWA50, you must use a cable gland for shielded cable. See ordering
information.

1

–

IN–

OUT–

–

–

–

+

IN+

OUT+

+

+

+

2

3

4
A0040491

 12
1
2
3
4

Electrical connection for 4-wire HART field devices with passive current output (optional grounding notshown)

Supply voltage (SELV, PELV or Class 2) or PLC with active current input or transmitter with active current
inputElectronic insert SWA50
4-wire field device with passive 4 to 20 mA-HART output
Supply voltage for 4-wire field device

6.7

4-wire HART field device with active current output
Some grounding concepts require shielded cables. If connecting the cable shield to theFieldPort SWA50, you must use a cable gland for shielded cable. See ordering
information.

Endress+Hauser

31

Electrical connection

FieldPort SWA50

–

–

–

IN–

OUT–

–

+

+

+

IN+

OUT+

+

2

1

4

3

A0040492

 13
1
2
3
4

Electrical connection for 4-wire HART field devices with active current output (optional grounding notshown) – PLC or transmitter at OUT terminals

Supply voltage (SELV, PELV or Class 2) for 4-wire HART field device
4-wire field device with active 4 to 20 mA HART output
Electronic insert SWA50
PLC or transmitter with passive current input

1

–

–

–

IN–

OUT–

+

+

+

IN+

OUT+

2

3

4
A0045101

 14
1
2
3
4

Electrical connection for 4-wire HART field devices with active current output (optional grounding notshown) – resistor at OUT terminals

Supply voltage (SELV, PELV or Class 2) for 4-wire HART field device
4-wire field device with active 4 to 20 mA HART output
Electronic insert SWA50
Resistance 250 to 500 Ohm min. 250 mW between terminals OUT+ and OUT–

If you select the "direct mounting" version and the "4-wire HART field device withactive current output and PLC or transmitter" electrical connection version, you can
use core cross-sections of 0.75 mm² maximum. The wires that you insert into theshorter top housing section must be connected to the IN terminals opposite, and thewires that you insert into the longer bottom housing section must be connected to the
OUT terminals opposite. If larger core cross-sections are required, we recommend
remote mounting.

6.8

FieldPort SWA50 without HART field device(repeater)
Using this connection version, you can preconfigure the FieldPort SWA50 or use it asa repeater.

32

Endress+Hauser

FieldPort SWA50

Electrical connection

–

IN–

OUT–

+

IN+

OUT+

1

2

3
A0040493

 15
1
2
3

Supply voltage FieldPort SWA50, 20 to 30 VDC (SELV, PELV or Class 2)
Electronic insert SWA50
Resistance 1.5 kOhm and min. 0.5 W between terminals OUT+ and OUT–

6.9

Endress+Hauser

FieldPort SWA50 without HART field device (optional grounding not shown)

Post-connection check

Are the device and cable undamaged (visual check)?

Do the cables comply with the requirements?

Is the terminal assignment correct?



Have the cables been connected in such a way that no wires, insulation and / or cable shields
are jammed?

Is the supply voltage correct?

Is the FieldPort SWA50 grounded, if necessary?

33

Operation options

FieldPort SWA50

7

Operation options

7.1

Overview of operation options

You have the following operation options for the FieldPort SWA50:• The Endress+Hauser SmartBlue app for mobile devices• An Endress+Hauser Field Xpert SMTxx tablet PC• The Endress+Hauser FieldCare SFE500 field device configuration tool

7.2

Operation via SmartBlue app

The SmartBlue app for mobile devices is available in the Google Play Store and in theApple App Store.
An encrypted point-to-point connection is established between the FieldPort SWA50 andthe mobile device. It is only possible to connect the FieldPort SWA50 and the connected
HART field device via Bluetooth using the SmartBlue app. Configuration of the connected
HART field device is not possible via the SmartBlue app.

7.3

Operation via Field Xpert

You have the following operation options with a Field Xpert SMTxx:• Configuration via an encrypted point-to-point connection using Bluetooth• Remote configuration via WirelessHART using a WirelessHART gateway, the DTM for
the WirelessHART gateway and the DTM for the FieldPort SWA50• Local configuration using a modem and the DTM for the FieldPort SWA50
If a DTM is available for the HART field device, it is also possible to configure it via the
Field Xpert SMT. In the case of a Bluetooth connection, the HART commands are tunneled
via the Bluetooth channel.

7.4

Operation via FieldCare

You have the following operation options with FieldCare SFE500:• Remote configuration via WirelessHART using a WirelessHART gateway, the DTM for
the WirelessHART gateway and the DTM for the FieldPort SWA50• Local configuration using a modem and the DTM for the FieldPort SWA50
If a DTM is available for the HART field device, it is also possible to configure it via
FieldCare.

7.5

Local operation via Field Xpert or FieldCare

Local operation via Field Xpert or FieldCare takes place via a modem such as Commubox
FXA195.

34

Endress+Hauser

FieldPort SWA50

Operation options

1

2

3

+

IN+

OUT+

+

–

IN–

OUT–

–

4

6
5
A0055103

 16
1
2
3
4
5
6

Endress+Hauser

Connection example of the modem for local operation via Field Xpert SMTxx or FieldCare SFE500

Supply voltage or PLC with active current input or transmitter with active current input
Electronic insert SWA50 (internal communication resistor enabled)
2-wire field device 4 to 20 mA HART
Endress+Hauser Commubox FXA195 USB/HART modem
PC with FieldCare SFE500
Field Xpert SMT tablet PC

35

Commissioning

FieldPort SWA50

8Commissioning

8.1

Overview of operation options

You have the following options for commissioning the FieldPort SWA50:• The Endress+Hauser SmartBlue app for mobile devices and →  37
• An Endress+Hauser Field Xpert SMTxx tablet PC →  40
• The Endress+Hauser FieldCare SFE500 field device configuration tool →  42
Observe the requirements for commissioning: →  36

8.2

Requirements

8.2.1

Requirements of the FieldPort SWA50• The FieldPort SWA50 is electrically connected.
• Post-mounting check has been carried out →  28.
• Post-connection check has been carried out →  33.
• DIP switch 1 for Bluetooth communication must be set to ON →  43.
(Factory setting for DIP switch 1: ON)

8.2.2

Information required for commissioning

You will need the following information for commissioning:• HART device address of HART field device• Device tag of HART field device in Bluetooth network• Long tag for HART-6 and HART-7 field devices• (Short) tag for HART-5 field devices• Device tag of HART field device in WirelessHART network• Long tag for HART-6 and HART-7 field devices• HART message for HART-5 field devices
Each device tag in the WirelessHART network must be unique.

8.2.3

Points to check before commissioning

HART masterIn addition to the FieldPort SWA50, only one other HART master is permitted in the HART
loop. This other HART master and the FieldPort SWA50 may not be of the same mastertype. You can configure the master type either via the "HART master type" parameter or"Master Type".
HART communication resistor
For HART communication, you require either the internal HART communication resistor of
the FieldPort SWA50 or a HART communication resistor outside the FieldPort SWA50 in
the 4 to 20 mA loop.
Requirements for "internal HART communication resistor":
The "Internal" option is set for the "Communication resistor" parameter.
Requirements for "HART communication resistor outside the FieldPort SWA50":• The HART communication resistor of ≥ 250 Ohm is outside the FieldPort SWA50 in the
4 to 20 mA loop.
• The HART communication resistor must be wired in series between the "IN+" terminal of
the FieldPort SWA50 and the supply voltage, such as the PLC or active barrier.
• The "External" option is set for the "Communication resistor" parameter.

36

Endress+Hauser

FieldPort SWA50

Commissioning

8.2.4

Initial password

The initial password can be found on the nameplate.

8.3

Putting the FieldPort SWA50 into operation

8.3.1

Commissioning via SmartBlue app

Install the SmartBlue app
The SmartBlue app is available for download from the Google Play Store for mobile devices
with Android and from the Apple App Store for devices with iOS.

‣

Scan the QR code.
 The Google Play or App Store page is opened to download the SmartBlue app.
System requirements
Please see either the Google Play or App Store page for the system requirements of
the SmartBlue app.
Starting the SmartBlue app and logging in
1.

Endress+Hauser

Switch on the supply voltage for the FieldPort SWA50.

37

Commissioning

FieldPort SWA50

2.

Start the SmartBlue app on the smartphone or tablet.
 An overview of accessible devices is displayed.

 17
1
2
3
4

38

Reachable devices (live list)

Example of FieldPort SWA50 with Endress+Hauser HART field device, already connected to
SmartBlue app
Example of FieldPort SWA50 with HART field device of another manufacturer, already connected
to SmartBlue app
Example of FieldPort SWA50, not yet connected to SmartBlue app
Example of FieldPort SWA50 without HART field device, already connected to SmartBlue app

Endress+Hauser

FieldPort SWA50

Commissioning

3.

Select device from list.
 The "Login to device" page is displayed.

 18

Login

You can establish only one point-to-point connection between one FieldPort SWA50
and one smartphone or tablet.

‣ Log in. Enter admin as the user name and enter the initial password. The password canbe found on the nameplate.
 Once the connection has been established successfully, the "Device information"
page is displayed for the selected device. →  44
Change the password after logging in for the first time.
Checking and adjusting the HART configuration
Perform the following steps to ensure good communication between the FieldPort SWA50
and the connected HART field device.
• The parameters listed in this section can be found on the "HART Configuration"
page.
• Navigation: Root menu > System > FieldPort SWA50 > Connectivity > HART
configuration

Endress+Hauser

1.

Use the "HART address field device" parameter to check the HART address of the
HART field device and configure the address if necessary. The same HART address
must be used for the HART field device in the HART field device and in the FieldPort
SWA50. If the FieldPort SWA50 is to be used as a repeater, enter an address greaterthan 63 in the "HART address field device" parameter.

2.

Use the "Communication resistor" parameter to check the setting for the HART
communication resistor. If there is no HART communication resistor outside theFieldPort SWA50 in the 4 to 20 mA loop, you must enable the internal HART
communication resistor.

3.

Use the "HART master type" parameter to check the setting for an additional HART
master in the HART loop. In addition to the FieldPort SWA50, only one other HART
master is permitted in the HART loop. This other HART master and the FieldPort
SWA50 may not be of the same master type.

39

Commissioning

FieldPort SWA50

WirelessHART configuration
Perform the following steps to ensure good communication between the FieldPort SWA50
and the WirelessHART network.
• The parameters listed in this section can be found on the "WirelessHART
Configuration" page.
• Navigation: Root menu > System > FieldPort SWA50 > Connectivity >WirelessHART configuration• You can only edit the parameters if the "Do not attempt to join" option has been
selected for the "Join mode" parameter.
1.

Enter the ID number for the network via the "Network ID" parameter.

2.

Enter the network password via the "Join key" parameter.

3.

Connect to the network via the "Join mode" parameter. It can take up to 30 minutes toconnect to the WirelessHART network.

Burst mode
Burst modes are configured at the factory for the FieldPort SWA50. Use the "Burst period
configuration" page to configure the time periods for the burst modes or enable and disable
individual burst modes.

8.3.2

Commissioning via Field Xpert• For detailed information on operation with the Field Xpert SMT50, see BA02053S• For detailed information on operation with the Field Xpert SMT70, see BA01709S• For detailed information on operation with the Field Xpert SMT77, see BA01923S
Starting the Field Xpert and logging in

40

1.

Switch on the supply voltage for the FieldPort SWA50.

2.

Start the Field Xpert tablet PC. To do so, double-click Field Xpert on the start screen.
 The following view is displayed:3.

Tap the icon.
 A list of all available WIFI and Bluetooth devices appears.

Endress+Hauser

FieldPort SWA50

Commissioning

4.

Check whether the icon is enabled. If the icon is not enabled, tap the A list of all available Bluetooth devices appears.

 19
1
2
3

icon.

Reachable devices (live list)

Example of FieldPort SWA50 without HART field device, already connected to Field Xpert
Example of FieldPort SWA50, not yet connected to Field Xpert
Example of FieldPort SWA50 with Endress+Hauser HART field device, already connected to
Field Xpert

5.

Tap the icon next to the device that is to be configured.
 The Login dialog box appears.

6.

Log in. Enter admin as the user name and enter the initial password. The initial
password can be found on the nameplate.
 The "Online Parameterization" page of the SWA50 DTM is displayed.

Use theicon to open the DTM of the connected HART field device.

Change the password after logging in for the first time.

Endress+Hauser

41Commissioning

FieldPort SWA50

Checking and adjusting the HART configuration
Perform the following steps to ensure good communication between the FieldPort SWA50
and the connected HART field device.
• The parameters listed in this section can be found on the "Wired Communication"
page.
• Navigation: Online Parametrization > Wired Communication
1.

Use the "HART address field device" parameter to check the HART address of the
HART field device and configure the address if necessary. The same HART address
must be used for the HART field device in the HART field device and in the FieldPort
SWA50.

2.

Use the "Communication Resistor" parameter to check the setting for the HART
communication resistor. If there is no HART communication resistor outside theFieldPort SWA50 in the 4 to 20 mA loop, you must enable the internal HART
communication resistor.

3.

Use the "Master Type" parameter to check the setting for an additional HART masterin the HART loop. In addition to the FieldPort SWA50, only one other HART masteris permitted in the HART loop. This other HART master and the FieldPort SWA50
may not be of the same master type.

WirelessHART configuration
Perform the following steps to ensure good communication between the FieldPort SWA50
and the WirelessHART network.
• The parameters listed in this section can be found on the "Wireless Communication"
page.
• Navigation: Online Parametrization > Wireless Communication
1.

Enter the ID number for the network via the "Network Identification" parameter.

2.

Enter the network password via the "Join Key Part x of 4" parameter.

3.

Connect to the network via the "Join Mode" parameter. It can take up to 30 minutes toconnect to the WirelessHART network.

Burst Mode
Burst modes are configured at the factory for the FieldPort SWA50. You can configure theburst modes via the "Burst Mode" page.

8.3.3

Commissioning via FieldCare

1.

Enable the "Prefer FDT1.2.1 scanning" option in FieldCare. Path: FieldCare > Extras >Options > "Scanning" tab > " section Scan Result2.

Integrate the FieldPort SWA50 into a FieldCare project in accordance with the
Operating Instructions for FieldCare.

3.

Configure the FieldPort SWA50 →  57.
For detailed information on operation with FieldCare , see BA00065S

42

Endress+Hauser

FieldPort SWA50

Operation

9

Operation

9.1

Hardware locking

The DIP switches for hardware-locking are located on the electronic insert.
1234
ON
OFF

1234

+ OUT –+ IN –

ON
OFF

A0041784

 20

DIP switches for hardware-locking of functions

DIP switch

Function

Description

Factory setting

1

Bluetoothcommunication• ON: Communication via Bluetooth ispossible, e.g. via SmartBlue App andField Xpert.
• OFF: Communication via Bluetooth isnot possible.

ON

2

Firmware update• ON: You can carry out firmware updates.
• OFF: You cannot carry out firmware
updates.

ON

3

Configuration via
Bluetooth• ON: Configuration via Bluetooth ispossible, e.g. via SmartBlue App andField Xpert.
• OFF: Configuration via Bluetooth is notpossible.

ON

4

Reserve

–

–

9.2

LEDs

2 LEDs• Green: Flashes four times at start-up to indicate that the device is operational• Orange: Flashes every 2 seconds to indicate that a squawk function has been enabled
Activate the squawk function in the SmartBlue app using the "Identification" parameter→  43
The LEDs are located on the electronic insert and are not visible from the outside.

Endress+Hauser

43Description of SmartBlue app for SWA50

FieldPort SWA50

10Description of SmartBlue app for SWA50

10.1

Menu overview (Navigation)

Menu overview (Navigation): →  89

10.2

"Device information" pageThe following display options are possible for the "Device information" page:• FieldPort SWA50 with HART field device from Endress+Hauser• FieldPort SWA50 with HART field device from another manufacturer• FieldPort SWA50 without connected or accessible HART field device
Information about the serial number shown
The actual serial number is displayed for Endress+Hauser field devices with HART 6
and HART 7. A unique serial number is calculated for field devices from othermanufacturers and for Endress+Hauser field devices with HART 5. The calculated
serial number does not correspond to the actual serial number of the field device.
Information on the status signal indicated in the top line
When the Endress+Hauser field device is connected, the status signal displayed in the
top line is a combination of the status signal of the connected HART field device andthe status signal of the FieldPort SWA50.

44

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

 21
1
2
3
4
5
6
7

Endress+Hauser"Device information" view – Example of the SWA50 with Endress+Hauser HART field device

Combined status signal, consisting of the status for the SWA50 and the status of the connected HART fielddeviceInformation about the HART field device connected to the SWA50. Firmware version, order code and device
type are only displayed for Endress+Hauser field devices with HART 6 and HART 7.
Serial number. In the case of HART field devices, this is a unique number generated by the SWA50 consistingof Device type, Manufacturer ID and Device ID.
Status signal of the SWA50. If the status is not OK, the button for the "Diagnostics FieldPort SWA50" page isshown.
Status signal of the connected HART field device. If the status is not OK, the button for the "Diagnostics Field
device" page is shown.
Process values of HART field device
Product image of Endress+Hauser HART field device with SWA50

45

Description of SmartBlue app for SWA50

 22
1
2
3
4
5

4
5

46

"Device information" view – example for SWA50 with HART field device from another manufacturer

Information about the HART field device connected to the SWA50. Firmware version, order code, device typeand status are displayed only for Endress+Hauser field devices with HART 6 and HART 7.
Serial number. In the case of HART field devices from other manufacturers, this is a unique number generated
by the SWA50 consisting of Device type, Manufacturer ID and Device ID.
Status signal of the SWA50. If the status is not OK, the button for the "Diagnostics FieldPort SWA50" page isshown.
Output current of HART field device
Product image of HART field device from another manufacturer with SWA50

 23
1
2
3

FieldPort SWA50"Device information" view – example for SWA50 without connected or accessible HART field device

Status signal for SWA50
Information about the SWA50
Status signal of the SWA50. If the status is not OK, the button for the "Diagnostics FieldPort SWA50" page isshown.
Measured values of the SWA50. The output current 20 mA is always displayed in this case
Product image of SWA50, since HART field device is either not connected or not accessible

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

10.3"Diagnostics: WirelessHART" page

Navigation: Root menu > Diagnostics > WirelessHARTThis page displays FieldPort SWA50 information in conjunction with the WirelessHart
network which may be relevant for diagnostics.
Parameter

Description

Network ID

Shows the configured identification number of the SWA50 for the
WirelessHART network. The setting is made via the "WirelessHART
Configuration" page →  53.

Radio transmit powerShows the selected strength of the SWA50 radio signal. The setting is
made via the "WirelessHART Configuration" page →  53.
Possible notifications• 0 dBm• 10 dBm

Join mode

Shows the selected mode the SWA50 uses to connect to the network. The
setting is made via the "WirelessHART Configuration" page →  53.
Possible notifications• Do not attempt to join: Do not attempt to join
• Join now: Join now• Attempt to join on powerup or restart: Join on powerup or restart

Join status

Displays the current status while attempting to join.
Possible notifications• Network packets heard: Network packets received• ASN Acquired: ASN acquired• Synchronized to slot time: Time synchronized with the network.
• Advertisement heard: Advertising packet for sending received.
• Join requested: Join requested• Retrying join: Repeating attempt to join
• Join failed: Join failed• Authenticated: Authenticated• Network joined: Network connection established• Negotiating network properties: Negotiating network parameters• Normal operation commencing: Normal operation starts. Fully
connected.

Additional information

Shows additional information about the WirelessHart connection
Possible notifications• Join failed: Join failed• FieldPort does not have a join key: No join key was entered for the
SWA50.
• FieldPort not connected to WHART network: SWA50 is not connectedto the WirelessHART network• Bandwith allocation pending: Bandwidth request to the gateway
pending• Bandwith allocation denied: Bandwidth request to the gateway denied• Handheld configuration active: Handheld configuration active• No alternative path: No other path

"WirelessHART configuration"
buttonThe "WirelessHART configuration" page is opened →  53.

"Burst period configuration" button

The "Burst period configuration" page is opened. →  54

10.4

"Diagnostics: FieldPort SWA50" page

Navigation: Root menu > Diagnostics > FieldPort SWA50

Endress+Hauser

47

Description of SmartBlue app for SWA50

FieldPort SWA50

This page displays information about the FieldPort SWA50 which may be relevant for
diagnostics.
Parameter

Description

Device tag

Shows the SWA50 device tag

Status signal FieldPort SWA50

Shows the current NAMUR NE 107 status of the SWA50
Possible notifications• OK• Failure (F): Failure (F)• Maintenance required (M): Maintenance required (M)• Out of specification (S): Not within specification (S)• Function check (C): Function check (C)• Not categorized: Not categorized

Actual diagnostics

Shows the diagnostic number with the highest priority currently.
→  80

Active diagnostics

Shows the associated diagnostic text for the diagnostic number displayedby the "Actual diagnostics" parameter

Additional device status

Shows other states of the SWA50
Possible notifications• Lowpower mode: Low power mode is enabled.
• Additional status for field device: Additional status information
available for the field device. See field device for this status
information.
• SWA50: WirelessHART off: WirelessHART is disabled (Do not attempt
to join).
• SWA50: do not scan for field device: No search takes place for aconnected field device for the SWA50• HART device configuration locked: HART device configuration is locked
for the SWA50.
• Connected field device changed: The configuration for the field device
connected to the SWA50 was changed.
• Block transfer pending: The block transfer is pending.
• DIP switch 2 ON: FW update enabled: DIP switch 2 is set to the ON
position. Firmware updates are possible.
• DIP switch 3 ON: Config via BT enabled: DIP switch 3 is set to the ON
position. Configuration via Bluetooth is possible, e.g. via the SmartBlue
app and Field Xpert.

"Connectivity" button

The "Connectivity" page is opened. →  52

"Diagnostics WirelessHART" button

The "Diagnostics" WirelessHART page is opened. →  47

Configuration counter

Shows the number of configuration changes for the SWA50

RebootShows the number of restarts of the SWA50

Operating time from restartShows the uptime of the SWA50 since the last restart

Received Bluetooth signal strength

Shows the current Bluetooth radio signal strength in dB

Reduce Bluetooth radio transmit
power

Indicates whether the Bluetooth output power of the SWA50 is reduced
or notPossible notifications
• Yes
• No

"Identification" button

Enable squawk function for 1 minute.
Response• SWA50: The orange LED flashes at intervals of 2 seconds.
• Feldgerät: Falls das Feldgerät die Squawk-Funktion unterstützt, wird
die Funktion am Feldgerät aktiviert.

10.5"Diagnostics: Field device" page

Navigation: Root menu > Diagnostics > Field device

48

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

This page displays information about the HART field device which may be relevant for
diagnostics.
The diagnostic information is displayed only for Endress+Hauser HART field devices.
Parameter

Description

Device tag

Shows the device tag of the HART field device

Device typeShows the device type of the HART field device in HEX format, e.g.
0x1128

Status signal field device

Shows the current NAMUR NE 107 status of the HART field device
depending on the information available from the HART field device. The
data base that makes up the device status varies depending on HART
standard 5, 6 or 7 and the generation of the field device.
Possible notifications• OK• Failure (F): Failure (F)• Maintenance required (M): Maintenance required (M)• Out of specification (S): Not within specification (S)• Function check (C): Function check (C)Actual diagnostics

Shows the internal service ID or the diagnostic number with the highest
priority depending on the device type.
The service ID is displayed in accordance with the LIT-18 specification.
The "Actual diagnostics" parameter is called up via the device-specific
HART command 231.

Device status

Shows currently pending information from the device status byte.
Possible notifications• Device malfunction (F): Device fault (F)• Configuration changed (OK): Configuration changed (OK)• More status available (OK): Additional status information available(OK)• Loop current fixed (OK): Fixed value for loop current (OK)• Loop current saturated (S): Loop current saturated (S)• Non-primary variable out of limits (S): Non-primary variable (SV, TV,
QV) outside limit values (S)• Primary variable out of limits (S): Primary variable (PV) outside limit
values (S)Extended device status

Shows currently pending information from the extended device status
byte.
Possible notifications• Maintenance required (M): Maintenance required (M)• Device variable alert (OK): One of the device variables is in the alarm or
warning state• Critical power failure (F): Critical condition of supply voltage (F)• Failure (F): Fault (F)• Out of specification (S): Not within specification (S)• Function check (C): Function check required (C)Standard Status 0

Shows additional device status information from the standard section of
HART command 48 (byte 8).
Requirement
HART field devices with HART 7 or higher
Possible notifications• Device variable simulation active (C): Simulation of device variables
active (C)• Non-volatile memory defect (F): Flash memory faulty (F)• Volatile memory defect (F): RAM faulty (F)• Watchdog reset executed (F): Watchdog restart (F)• Power supply conditions out of range (S): Supply voltage not within
specification (S)• Environmental conditions out of range (S): Ambient conditions notwithin specification (S)• Electronic defect (F): Electronics module faulty (F)• Device configuration locked (OK): Device configuration locked (OK)Endress+Hauser

49

Description of SmartBlue app for SWA50

FieldPort SWA50

Parameter

Description

Standard Status 1

Shows additional device status information from the standard section of
HART command 48 (byte 9).
Requirement
HART field devices with HART 7 or higher
Possible notifications• Status simulation active (OK): Device status simulation active (OK)• Discrete variable simulation active (C): Measured value simulation
active (C)• Event notification overflow (OK): Overflow of event notifications (OK)• Battery / power supply needs maintenance (M): Battery or power
supply needs maintenance (M)Configuration counter

Shows the number of configuration changes for the HART field device

10.6"Application: FieldPort SWA50" page

10.6.1"Measured values" page (FieldPort SWA50)

Navigation: Root menu > Application > FieldPort SWA50 > Measured values
This page shows the measured values of the FieldPort SWA50.
Parameter

Description

Primary variable (PV)Shows the primary variable of the SWA50
Factory setting
Temperature [°]Secondary variable (SV)Shows the secondary variable of the SWA50
Factory setting
Signal strength of best neighbor in the WirelessHART network [dB]

Tertiary variable (TV)Shows the tertiary variable of the SWA50
Factory setting
Signal strength of second-best neighbor in the WirelessHART network[dB]

Quanternary variable (QV)

Shows the quaternary variable of the SWA50
Factory setting
Field device loop current [mA]
If no field device is connected to the SWA50, 20 mA is always displayed.

10.6.2"HART info" page (FieldPort SWA50)

Navigation: Root menu > Application > FieldPort SWA50 > HART info
This page shows the HART information of the FieldPort SWA50.

50

Parameter

Description

Device typeShows the device type of the SWA50 in HEX format (0x11F3)

Manufacturer ID

Shows the manufacturer ID of the SWA50 in HEX format, 0x11 forEndress+Hauser

HART revision

Shows the HART version of the SWA50, e.g. 7

HART descriptor

Shows the description that was entered for the SWA50.

HART message

Shows the message that was entered for the SWA50. The message istransmitted via the HART protocol at the request of the master.

Device ID

Shows the device ID of the SWA50, e.g. 0x7A2F51

No. of preambles

Shows the number of preambles entered.

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

Parameter

Description

HART data code

Shows the date that was entered for the SWA50, e.g. 2020-03-31. The
date provides information about a specific event, for example, such as thelast configuration change.

Device revision

Shows the hardware revision of the SWA50

10.7"Application: Field device" page

10.7.1"Measured values" page (Field device)

Navigation: Root menu > Application > Field device > Measured values
This page shows the measured values of the HART field device that is connected to theFieldPort SWA50. If a HART field device is not connected or the HART field device cannot
be reached, this page shows the measured values of the FieldPort SWA50.
The measured values PV, SV, TV and QV are displayed for Endress+Hauser devices
only.
Parameter

Description

Output current

Shows the output current of the HART field device

Primary variable (PV)Shows the primary variable of the Endress+Hauser HART field device

Secondary variable (SV)Shows the secondary variable of the Endress+Hauser HART field device

Tertiary variable (TV)Shows the tertiary variable of the Endress+Hauser HART field device

Quanternary variable (QV)

Shows the quaternary variable of the Endress+Hauser HART field device

10.7.2"HART info" page (Field device)

Navigation: Root menu > Application > Field device > HART info
This page shows the HART information of the HART field device that is connected to theFieldPort SWA50.
The HART information is displayed for Endress+Hauser devices only.

Endress+Hauser

Parameter

Description

Device typeShows the device type of the HART field device in HEX format, e.g.
0x1128Manufacturer ID

Shows the manufacturer ID of the HART field device in HEX format, e.g.
0x11 for Endress+Hauser

HART revision

Shows the HART version of the HART field device, e.g. 7

HART descriptor

Shows the description that was entered for the field device.

HART message

Shows the message that was entered for the HART field device. The
message is transmitted via the HART protocol at the request of themaster.

Device ID

Shows the device ID of the HART field device, e.g. 0x7A2F51

No. of preambles

Shows the number of preambles entered.

HART data code

Shows the date that was entered for the HART field devices, e.g.
2020-03-31. The date provides information about a specific event suchas the last configuration change.

Device revision

Shows the hardware revision of the HART field device

51Description of SmartBlue app for SWA50

FieldPort SWA50

10.8"System: FieldPort SWA50" page

10.8.1"Device management" page (FieldPort SWA50)

Navigation: Root menu > System > FieldPort SWA50 > Device management
Parameter

Description

Device tag

Enter device tag for SWA50.

10.8.2"Connectivity" page (FieldPort SWA50)

Navigation: Root menu > System > FieldPort SWA50 > Connectivity"Bluetooth configuration" page
Navigation: Root menu > System > FieldPort SWA50 > Connectivity > Bluetoothconfiguration
Use this page to configure the Bluetooth connection and perform firmware updates for the
FieldPort SWA50.
Page

Description

Reduce radio transmit power

Enable and disable a reduction in the transmission power of the SWA50.
Options• Yes: The transmission power of the SWA50 is reduced.
• No: The transmission power of the SWA50 is not reduced.
Factory setting
No

Change Bluetooth password

Change password. To change it, you must enter the user name, thecurrent password and the new password.
Factory setting• User name: admin• The password can be found on the nameplate.

Firmware update→  83"HART configuration" page
Navigation: Root menu > System > FieldPort SWA50 > Connectivity > HART configuration
Use this page to configure the HART parameters for the FieldPort SWA50. In addition, you
can configure the HART address of the connected HART field device.
Parameter

Description

HART address field device

Configure the HART address of the HART field device.
User entry
0 to 255
Factory setting0
the SWA50 is to be used as a repeater, you must enter an address Ifgreaterthan 63. The status signals of the field device aresuppressed in this mode.

HART master type

Select HART master type.
Options• Primary master• Secondary master
Factory setting
Secondary master

52

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

Parameter

Description

Communication resistor

Select installation site of HART communication resistor.
Options• External: Use an external communication resistor provided by thecustomer onsite between the IN+ terminal and the supply voltage.
• Internal: Use an internal communication resistor of the SWA50.
Factory setting
External

HART address SWA50

Configure the HART address of the SWA50 for slave access to SWA50.
User entry
0 to 63
Factory setting
15"WirelessHART configuration" page
Navigation: Root menu > System > FieldPort SWA50 > Connectivity > WirelessHART
configuration
Use this page to configure the WirelessHART connection.
Parameter

Description

Network ID

Requirement
Join mode: Do not attempt to join
Description
Enter the identification number of the network to which the FieldPort
connects.
User entry
0 to 65535
Factory setting
1447

Join key

Requirement
Join mode: Do not attempt to join
Description
Enter the network password.
User entry
32 hexadecimal numbers
Factory setting
456E6472657373202B20486175736572

Radio transmit power

Requirement
Join mode: Do not attempt to join
Description
Enter strength of radio signal.
User entry
0 or 10 dBm
Factory setting
10 dBmAdditional information
National restriction to 0 dBm is possible, as in Japan for example

Endress+Hauser

53Description of SmartBlue app for SWA50

FieldPort SWA50

Parameter

Description

Join mode

Select the mode the FieldPort uses to connect to the network.
Options• Do not attempt to join: Do not attempt to join
• Join now: Join now• Attempt to join on powerup or restart: Join on powerup or restart

Join status

Displays the current status while attempting to join.
Possible notifications• Network packets heard: Network packets received• ASN Acquired: ASN acquired• Synchronized to slot time: Time synchronized with the network.
• Advertisement heard: Advertising packet for sending received.
• Join requested: Join requested• Retrying join: Repeating attempt to join
• Join failed: Join failed• Authenticated: Authenticated• Network joined: Network connection established• Negotiating network properties: Negotiating network parameters• Normal operation commencing: Normal operation starts. Fully
connected.

10.8.3"Burst period configuration" page (FieldPort SWA50)

Navigation: Root menu > System > FieldPort SWA50 > Burst period configuration
Use this page to configure the time periods for the burst modes or enable and disable
individual burst modes.
Burst modes for the FieldPort SWA50 – factory setting

54

Burst Mode

Factory setting

1

Every 5 minutes, the SWA50 transmits the process values of the field device according to
HART command 3

2

Every 5 minutes, the SWA50 transmits the diagnostic data of the field device according
to HART command 48

3

Not configured

4Every 5 minutes, the SWA50 transmits its own process values in accordance with HART
command 3

5

Every 5 minutes, the SWA50 transmits its own diagnostic data according to HART
command 48

Endress+Hauser

FieldPort SWA50

Description of SmartBlue app for SWA50

Parameter

Description

FieldPort SWA50 (Burst Mode 4, 5) Select the time period for burst mode 4 and 5.
Options• 1 min• 2 min• 5 min• Custom (via DTM): The time period set via the DTM is used.
Factory setting
5 min
Field device (Burst Mode 1, 2)

Select the time period for burst mode 1 and 2 or disable burst mode.
Options• Off: Disable burst mode.
• 8s• 16 s• 32 s• 1 min• 2 min• 5 min• Custom (via DTM): The time period set via the DTM is used.
Factory setting
5 min

Other (Burst Mode 3)

Select the time period for burst mode 3 and or disable burst mode.
Options• Off: Disable burst mode 3.
• Custom (via DTM): The time period set via the DTM is used.
Factory settingOff

10.8.4"Geolocation" page (FieldPort SWA50)

Navigation: Root menu > System > FieldPort SWA50 > Gelocation
Use this page to configure information on the position of the FieldPort SWA50.
Parameter

Description

Location description

Enter a description of the location (32 characters maximum).

"Take over data from mobile device"
buttonIf the mobile device has location information, you can adopt thisinformation by tapping on the button for the SWA50.

LongitudeEnter longitude [°].

LatitudeEnter latitude [°].

AltitudeEnter height [m].

10.8.5"Information" page (FieldPort SWA50)

Navigation: Root menu > System > FieldPort SWA50 > Information
This page displays information on the FieldPort SWA50.

Endress+Hauser

Parameter

Description

Wireless communication

Shows the connection type, such as "Bluetooth" or "WirelessHART"

Device nameShows the device name for the SWA50

Manufacturer

Shows the manufacturer, "Endress+Hauser" in this case

Serial number

Shows the serial number of the SWA50

Order code

Shows the order code

Extended order code 1

Shows the extended order code 1

Extended order code 2

Shows the extended order code 2

55

Description of SmartBlue app for SWA50

FieldPort SWA50

Parameter

Description

Extended order code 3

Shows the extended order code 3

Firmware version

Shows the active firmware version

Hardware version

Shows the active hardware version

10.9"System: Field device" page

Navigation: Root menu > System > Field device
The "Field device" page is available for Endress+Hauser devices only.

10.9.1"Device management" page (Field device)

Navigation: Root menu > System > Field device > Device management
Parameter

Description

Device tag

Shows the device tag of the HART field device

10.9.2"Information" page (Field device)

Navigation: Root menu > System > Field device > Information
This page shows information about the HART field device that is connected to theFieldPort SWA50.
This information is displayed for Endress+Hauser field devices with HART 6 andhigher.

56

Parameter

Description

Device nameShows the device name of the HART field device

Manufacturer

Shows the manufacturer of the HART field device

Serial number

Shows the serial number of the HART field device

Order code

Shows the order code of the HART field device

Extended order code 1

Shows the first part of the extended order code of the HART field device

Extended order code 2

Shows the second part of the extended order code of the HART fielddeviceExtended order code 3

Shows the third part of the extended order code of the HART field device

Firmware version

Shows the active firmware revision of the HART field device

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

11

Description of DTM for SWA50

11.1

Identification

Use this page to configure the parameters necessary to identify the FieldPort SWA50.
The factory settings are displayed in the relevant fields.
Navigation
Online parameterization > Identifcation"Identification" parameter description page
Parameter

Description

Long Tag

Requirement
Devices from HART version 6.0
Description
Enter a tag for the SWA50.
This parameter is used for unique identification of the SWA50 in the network andin the plant. The parameter is used to set the burst mode and the event
notification.
User entry
Max. 32 characters from the ISO Latin 1 character set
Factory setting
SWA50_"Serial Number" The tag must be unique in the WirelessHART network.
Device Tag

Description
Enter a tag for the SWA50.
User entry
Max. 8 characters from the packed ASCII character set
Factory setting–

Descriptor

Description
Enter the description for the SWA50, e.g. function or location.
User entry
Max. 16 characters from the packed ASCII character set
Factory setting
SWA50

Date CodeDescription
Enter the date of a specific event, such as the last change.
User entry
DD.MM.YYYY

Endress+Hauser

57Description of DTM for SWA50

FieldPort SWA50

Parameter

Description

Message

Description
Enter the message that can be used as desired.
User entry
Max. 32 characters from the packed ASCII character set
Factory setting
SWA50

Polling Address

Description
Enter the HART address of the SWA50 on the wired interface.
User entry
0 to 63
Factory setting
15
Additional information
Since the "Long Tag" parameter and the MAC address are used to identify the
SWA50 in the wireless network, you can assign the same device address todifferent SWA50 devices.

Serial Number

Description
Shows the serial number of the SWA50.

Ext. Order CodeDescription
Shows the detailed order number of the SWA50.

Order CodeDescription
Shows the order code of the SWA50.

Country CodeDescription
Select the country where the SWA50 is operated.
Factory setting
Germany
Additional information
The selected country controls the signal strength in accordance with national
restrictions and thus the possible settings for the "Radio Power" parameter.

You can use the following characters for parameters for which you should entercharacters from the packed ASCII character set: @ A B C D E F G H I J K L M N O P Q R
S T U V W X Y Z [ \ ] ^ _ SP ! " # $ % & ' ( ) * + , - . / 0 1 2 3 4 5 6 7 8 9 : ; < = > ?

11.2

Wireless Communication

Use this page to configure the parameters necessary to integrate the FieldPort SWA50
into a wireless network.
Navigation
Online parameterization > Wireless Communication

58

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

Configure wireless communication and establish connection
1.

Configure parameters in the Join section.

2.

Click on the >> button for the Execute Join parameter.
 The settings are downloaded and stored in the SWA50.
Use the "Join Status" parameter to follow the progress of the connection.

"Wireless Communication" parameter description page
Parameter

Description

Network Identification

Description
Enter the identification number of the network to which the SWA50 should
connect.
User entry
0 to 65535
Factory setting
1447

Wireless Operation Mode

Description
Shows the status while the connection is being established or of the existing
connection of the SWA50 to the network.
Possible notifications• Idle: Waiting• Active Search: Active search for neighbor• Negotiating: Connection parameters are being negotiated with network
manager• Quarantined: Denied by network manager and temporary exclusion fromnetwork• Operational: Connection established• Suspended: Permanent exclusion• Deep Sleep/Ultra-Low Power/Passive Search: SWA50 is inactive

Radio Power

Description
Select strength of radio signal.
Options• 0 dBm• 10 dBm
Factory setting
10 dBmEndress+Hauser

59Description of DTM for SWA50

FieldPort SWA50

Parameter

Description

Join Key Part 1 of 4

Description
Enter join key part 1 of 4.
User entry
8 hexadecimal numbers
Factory setting
456E6472

Join Key Part 2 of 4

Description
Enter join key part 2 of 4.
User entry
8 hexadecimal numbers
Factory setting
65737320

Join Key Part 3 of 4

Description
Enter join key part 3 of 4.
User entry
8 hexadecimal numbers
Factory setting
2B204861

Join Key Part 4 of 4

Description
Enter join key part 4 of 4.
User entry
8 hexadecimal numbers
Factory setting
75736572

Join Mode

Description
Select the event upon which the SWA50 connects to the network.
Options• Do not attempt to join: Do not establish a connection.
• Join now: A connection is established once you click on the >> button for the"Execute Join" parameter.
• Attempt to join immediately on power-up or reset: Establish connection directly
after a restart.
Factory setting
Do not attempt to join

Execute Join

Description
Click button to write the set parameters to the SWA50 and to use them.
Additional information
If the "Join now" option is selected for the "Join Mode" parameter, the SWA50
attempts to connect to the network.

Join Status

Description
Displays the current status while attempting to join.
Possible notifications• Network packets heard: Network packets received• ASN Acquired: ASN acquired• Synchronized to slot time: Time synchronized with the network• Advertisement heard: Advertising packet for sending received.
• Join requested: Join requested• Retrying join: Repeating attempt to join
• Join failed: Join failed• Authenticated: Authenticated• Network joined: Network connection established• Negotiating network properties: Negotiating network parameters• Normal operation commencing: Normal operation starts. Fully connected.

60

Total Number of
Neighbours

Description
Shows the number of neighboring WirelessHart devices to which a connection has
been established.

Number of Advertising
Packets Received

Description
Shows the number of advertising packets to join the network sent by neighboring
devices or WirelessHART gateways and received by the SWA50.

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

Parameter

Description

Number of Join Attempts

Description
Shows the number of connection attempts that the SWA50 made until theconnection was established.

Active Advertising ShedTime [hh:mm:ss]

Description
Enter the time for an active join request. During this time, the SWA50 attempts toenable other SWA50 devices to connect to the network faster. To enable thisparameter, click the >> button for the "Request Active Advertising" parameter.
User entry
HH:MM:SS
Factory setting
00:40:00

Request Active
Advertising

Description
Clicking the >> button enables the "Active Advertising Shed Time [hh:mm:ss]"parameter.

Number of Neighbours
Advertising

Description
Shows the number of neighbors transmitting advertising packets for sending.

11.3

Wired Communication

Use this page to configure the parameters required for HART communication between the
FieldPort SWA50 and the connected HART field device.
Navigation
Online parameterization > Wired Communication"Wired communication" parameter description page
Parameter

Description

Polling Address

Description
Shows the HART address of the SWA50.
Factory setting
15

Master Type

Description
Select the HART master type for the SWA50.
Options• Primary master• Secondary master
Factory setting
Secondary master
addition to the SWA50, only one other HART master is permitted in the InHART
loop. This other HART master and the SWA50 may not be of the same
master type.

Endress+Hauser

61Description of DTM for SWA50

FieldPort SWA50

Parameter

Description

Preambles

Description
Enter the number of preambles.
User entry
5 to 50
Factory setting
5

Retries

Description
Enter the number of attempts to establish communication between the SWA50
and the HART field device.
User entry
2 to 5
Factory setting
3

Communication resistor

Description
Select the installation location of the HART communication resistor.
Options• External: Use external and customer-supplied communication resistor. The
communication resistor must be ≥ 250 Ohm and wired in series between the "IN+" terminal of the SWA50 and the supply voltage, such as the PLC or active
barrier.
• Internal: Use an internal communication resistor of the SWA50.
Factory setting
External

HART Adress Field Device

Description
Enter the HART address of the HART field device.
User entry
0 to 63
Factory setting0

Field Device Database

11.4

Description
Shows the HART information of the HART field device that is connected to the
SWA50.

Device Variable Mapping

The FieldPort SWA50 can output the value and status of different variables. Use this page
to configure the four variables PV, SV, TV and QV that are displayed in the network.
Variables for selection
OptionDescription

Field Device Loop Current

Loop current of field device

RSL of Best Neighbour

Signal strength of neighbor with highest signal strength

RSL of Second Best Neighbour

Signal strength of neighbor with second-highest signal strength

Temperature

Current temperature measured by the SWA50

Navigation
Online parameterization > Device Variable Mapping

62

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50"Device Variable Mapping" parameter description page
Parameter

Description

Select Primary Variable

Description
Select the primary variable.
Options
See the "Variables for selection" table.
Factory setting
Temperature

Primary Variable Unit

Description
Select the unit for the primary variable.
Options
The options depend on the variable selected.
Factory setting°C

Select Secondary Variable

Description
Select the secondary variable.
Options
See the "Variables for selection" table.
Factory setting
RSL of Best Neighbour

Secondary Variable Unit

Description
Select the unit for the secondary variable.
Options
The options depend on the variable selected.
Factory setting
dBm

Select Tertiary Variable

Description
Select the tertiary variable.
Options
See the "Variables for selection" table.
Factory setting
RSL of Second Best Neighbour

Tertiary Variable Unit

Description
Select the unit for the tertiary variable.
Options
The options depend on the variable selected.
Factory setting
dBm

Endress+Hauser

63Description of DTM for SWA50

FieldPort SWA50

Parameter

Description

Select Quaternary
Variable

Description
Select the quaternary variable.
Options
See the "Variables for selection" table.
Factory setting
Field Device Loop Current

Quaternary Variable Unit

Description
Select the unit for the quaternary variable.
Options
The options depend on the variable selected.
Factory setting
mA

11.5

Burst Mode

General information
In burst mode, slave devices can periodically send information such as process values
without a request from the master.
The FieldPort SWA50 is responsible for requesting this information from the connected
HART field device and forwarding it to the WirelessHART gateway. In addition, theSWA50 can send its own process values, i.e. the device variables to the WirelessHART
gateway.
In a typical configuration, the four device variables are transmitted from the connected
HART field device to the WirelessHART gateway at regular intervals. You can use burst
command numbers 3 and 48 for this purpose. We recommend that you set the same time
period for both commands. The SWA50 wakes the HART field device, adopts the device
variables and transmits them at the configured interval.
We recommend configuring a second burst mode for the SWA50 so that the SWA50
information is also available for host applications in the WirelessHART gateway.
You can configure the device variables on the "Device Variable Mapping" page →  62.
• If FieldCare or another configuration tool communicates with the SWA50 via amodem such as the FXA 195, the sending of burst modes is interrupted.
• Some HART field devices are also able to send burst modes. In this case, we
recommend enabling the burst mode in the SWA50 only. The burst settings of the
SWA50 are not synchronized with the burst settings of the HART field device.
"Burst Mode" page and "Burst Mode 1" to "Burst Mode 5" pages
The "Burst Mode" page provides an overview of the burst modes that are configured. You
can define up to 5 different burst modes via the "Burst Mode 1" to "Burst Mode 5" pages.
You can also configure a burst mode in offline mode. This burst mode becomes effective assoon as the SWA50 connects to the network.
Navigation• Online parameterization > Application Settings > Burst Mode > Burst Mode 1• Online parameterization > Application Settings > Burst Mode > Burst Mode 2• Online parameterization > Application Settings > Burst Mode > Burst Mode ...
Burst modes for the FieldPort SWA50 – Factory setting

64

Burst Mode

Factory setting

1

Every 5 minutes, the SWA50 transmits the process values of the field device according to
HART command 3

2

Every 5 minutes, the SWA50 transmits the diagnostic data of the field device according
to HART command 48

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

Burst Mode

Factory setting3

Not configured

4Every 5 minutes, the SWA50 transmits its own process values in accordance with HART
command 3

5

Every 5 minutes, the SWA50 transmits its own diagnostic data according to HART
command 48

Configuring burst modes

Endress+Hauser

1.

Open the page for configuring a burst mode, e.g. Burst Mode 1 page.

2.

Select the On option for the Burst Mode Control Code parameter.
 The gray input fields become white. Entries can be made.

3.

Select either "SWA50" or the connected HART field device for the Device Index
parameter.

4.

In the Period parameter, enter the time period following which the SWA50 should
send the device variables.

5.

Select the number for the burst command in the Burst Command Number
parameter.

6.

Click the Apply button.
 The settings are downloaded and stored in the SWA50.

7.

Confirm prompt with OK.
 Once the SWA50 is connected to the network, the burst mode takes immediate
effect.
If the SWA50 is not connected to the network, a message is displayed. Select OK
to confirm the message. The burst mode becomes effective as soon as the
SWA50 connects to the network.

65

Description of DTM for SWA50

FieldPort SWA50"Burst Mode X" parameter description page
Parameter

Description

Burst Mode Control CodeDescription
Enabling and disabling burst mode.
Options• Off: Burst mode disabled. The input fields are grayed out and write-protected.
• On: Burst mode enabled. The input fields are white. Entries can be made.
Factory setting• Burst mode 1, 2, 4 and 5: On• Burst mode 3: Off

Device Index

Requirement
Burst Mode Control Code: On
Description
Select the device for which the burst mode is effective.
Options• SWA50• Connected field device
Factory setting
SWA50

Period [hh:mm:ss]

Requirement
Burst Mode Control Code: On
Description
Enter the time period after which the SWA50 sends the device variables to the
WirelessHART gateway.
User entry• 00:00:08• 00:00:16• 00:00:32• Any time possible from 00:01:00
Factory setting
05:00:00

Burst Command Number

Requirement
Burst Mode Control Code: On
Description
Select the burst command number. Description of burst command: See thefollowing tables. For additional information, see HART specification.
Selection/user entry• Device Index "SWA50": Select 3, 9 or 48 from a drop-down list
• Device Index "Connected field device": Enter 1, 2, 3, 9, 33 or 48
Factory setting
1
Additional information• You can configure any command for the connected field device. Refer to thespecific Operating Instructions for possible commands.
• If in doubt, use command 3 and 48.

Device Variable Code 0
toDevice Variable Code 7

Requirement• Burst Mode Control Code: On• Burst Command Number: 9 or 33
Description
Select the device variables that are transmitted with the burst mode.
Selection/user entry• Device Index "SWA50" : Device variable code from drop-down list
• Device Index "Connected field device": Enter device variable code.
Factory setting
250
Additional information
Refer to the documentation for the field device for the device variables of theconnected field device.

66

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

Description of burst commands for the SWA50
Burst command

Description

3

Transmits the value of the 4 to 20 mA signal and up to 4 predefined device
variables and their unit in each case. Device variables: →  62.

9

The Device Variable Code 0 to Device Variable Code 7 fields are enabled.
Transmits the value, unit and status of up to 8 device variables.

48

Transmits the additional device status.

Description of burst commands for the field device connected to the SWA50
Burst command

Description

1

Transmits the value and unit of the "Primary variable" (PV).

2Transmits the value of the 4 to 20 mA signal and the corresponding value as apercentage, e.g. 4 mA and 0 % or 12 mA and 50 %.

3

Transmits the value of the 4 to 20 mA signal and up to 4 predefined device
variables and their unit in each case. Device variables: PV, SV, TV and QV.

9The Device Variable Code 0 to Device Variable Code 7 fields are enabled.
Transmits the value, unit and status of up to 8 device variables.

33

The Device Variable Code 0 to Device Variable Code 3 fields are enabled.
Transmits the value and unit of up to 4 device variables.

48

Transmits the additional device status.

11.6

Event Notification

General information
The event notification is a special application similar to the burst mode (burst message).
An event notification is sent as soon as there are changes in the device configuration or
device status, irrespective of whether data are already being sent by burst modes. You can
use the status in the device status byte, the extended device status byte and in command
48 for the event notification. You can define a certain number of bits that trigger an event
notification.
Event notifications have a lower priority than burst modes (burst messages). The event
notifications are given a time stamp when a notification is triggered for the first time. You
can define up to 2 different event notifications.
"Event Notification Control Code" page and "Event Notification Control Code 1" and"Event Notification Control Code 2" pages
The "Event Notification Control Code" page provides an overview of which event
notifications are configured. You can define two different event notifications via the "Event
Notification Control Code 1" and "Event Notification Control Code 2" pages.
You can also configure event notifications in the offline mode. The event notifications takeeffect as soon as the FieldPort SWA50 connects to the network.
Navigation• Online parameterization > Application Settings > Event Notification > Event Notification1• Online parameterization > Application Settings > Event Notification > Event Notification
2

Endress+Hauser

67Description of DTM for SWA50

FieldPort SWA50

Configuring the event notification

68

1.

Open the page for configuring an event notification, e.g. Event Notification Control
Code 1 page.

2.

Select the On option in the "Event" tab for the Event Notification Control Codeparameter.
 The gray input fields become white. Entries can be made.

3.

Select either "SWA50" or the connected HART field device for the Device Index
parameter.

4.

Configure the remaining parameters in the "Event" tab.

5.

Activate the desired event notifications in the "Standard Event Mask" tab. To do so,select the check box in front of the particular event. Multiple notifications can beselected.

6.

Activate the desired event notifications in the "Device-Specific Event Mask" tab. To doso, select the check box in front of the particular event. Multiple notifications can beselected. Observe the Operating Instructions for the selected device in the "Device
Index" parameter.

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50

7.

Click the Apply button.
 The settings are downloaded and stored in the SWA50.

8.

Click the OK button.
 If the SWA50 is connected to the network, the event is monitored immediately.
If the SWA50 is not connected to the network, a message is displayed. Confirm
the message with OK. The event becomes effective as soon as the SWA50
connects to the network.

"Event Notification" parameter description, "Event" tabParameter

Description

Event Notification Control Description
Code
Enable and disable the event monitoring mode.
Options• Off: Event monitoring mode is disabled. The input fields are grayed out andwrite-protected.
• On: Event monitoring mode enabled. Entries can be made.
Factory setting
Off
Additional information
The event monitoring parameters are written to the SWA50 once you click the"Apply" button.
Device Index

Requirement
Event Notification Control Code: On
Description
Select the device for which the event monitoring parameters are active.
Options• SWA50• Connected field device
Factory setting
SWA50

Endress+Hauser

69Description of DTM for SWA50

FieldPort SWA50

Parameter

Description

Event Notification Retry
Time

Requirement
Event Notification Control Code: On
Description
Enter the time between two attempts to transmit the event notification.
Transmission is repeated until the SWA50 gets confirmation of receipt.
User entry• 00:00:01• 00:00:02• 00:00:04• 00:00:08• 00:00:16• 00:00:32• Any time possible from 00:01:00
Factory setting
00:30:00

Maximum Update Time

Requirement
Event Notification Control Code: On
Description
Enter the maximum time that is used if no event change occurs. If an event has notoccurred, the SWA50 sends an event notification after this time. If an event
notification occurs during this time, the timer is restarted.
User entry• 00:00:01• 00:00:02• 00:00:04• 00:00:08• 00:00:16• 00:00:32• Any time possible from 00:01:00
Factory setting
00:30:00

Event Debounce Interval

Requirement
Event Notification Control Code: On
Description
Enter the time specifying how long an event must last before the event notificationis sent.

Event Status

Requirement
Event Notification Control Code: On
Description
Indicates whether and which event notifications have been sent and are not yet
confirmed. If the check box is ticked, the event notification has been sent but not
yet confirmed.
Monitored events• Configuration changed• Device status• Additional status information available
Factory setting
All check boxes disabledFirst unACK Time

Requirement
Event Notification Control Code: On
Description
Indicates how long the event notification listed under the "Event Status" parameteris active.
Factory setting
00:00:00

70

Endress+Hauser

FieldPort SWA50

Description of DTM for SWA50"Event Notification" parameter description, "Standard Event Mask" tabParameter

Description

Device Status

Options• Primary variable out of limits: Primary variable (PV) outside limit values• Non-primary variable out of limits: Non-primary variable (SV, TV, QV) outside
limit values• Loop current saturated: Loop current saturated• Loop current fixed: Fixed value for loop current• More status available: Additional status information available• Cold start: Cold start• Configuration changed: Configuration changed• Device malfunction: Device fault

Extended Device Status

Options• Maintenance required: Maintenance required• One of the device variables is an Alarm or Warning State: One of the device
variables is in the alarm or warning state• Critical power failure: Critical condition of power supply• Power failure: Fault• Out of specification: Not within specification• Function check: Function check required

Loop Current Saturated

See DTM.

Loop Current FixedSee DTM.

Standardized Status 0

See DTM.

Standardized Status 1

Options• Device variable simulation active: Simulation of device variables active• Non volatile memory defect: Flash memory faulty• Volatile memory defect: RAM defective• Software malfunction: Software malfunction (watchdog restart)• Power supply conditions out of specification: Supply not within specification• Adapter temperature out of specification: Ambient conditions not within
specification• Adapter hardware is defect: Electronics defective• Device configuration locked: Device configuration lockedStandardized Status 2

See DTM.

Standardized Status 3

See DTM.

"Event-Notification" parameter description, "Device-Specific Event Mask" tabMonitoring of device-specific events• HART field device: See the Operating Instructions of the connected HART fielddevice• FieldPort SWA50: See the following table
Monitoring of standard events for FieldPort SWA50
For the troubleshooting measures, see the corresponding diagnostics number in the"Diagnostics" section →  80.

Endress+Hauser

Byte

Bit

Description

Diagnostic
number0

0

So far no attempt has been made to establish a connection.

901

1

The adapter is not connected to any wireless network.

506

2

No alternative path to a neighbor available.

507

3

The adapter does not have a join key.

505

4

The adapter was unable to establish a connection to thewireless network.

503

5

WirelessHART started.

904

6Bluetooth connection active.

900

71

Description of DTM for SWA50

FieldPort SWA50

Byte

1

2

3

4

5

72

Bit

Description

Diagnostic
number

7––0

The adapter cannot communicate with the field device.

504

1

Error HART modem (loop current)

803

2 to 4––

5

The adapter is in the configuration mode.

508

6

The adapter is looking for connected device.

903

7

–

–

0

The adapter hardware is faulty.

316

1

The adapter is performing a self-test.

202

2

The adapter temperature is outside the permitted range.

825

3

–

–

4

The number of write cycles to the flash memory has exceededa critical threshold.

314

5

The number of write cycles to the flash memory has exceeded
the maximum value.

315

6 to 7––0 to 5––

6

Burst or event notification without field device

500

7

–

–

0

Wired device has additional status information.

502

1

Wired device not working correctly.

501

2 to 7––0

Not used–1

DIP switch 1: Bluetooth communication enabled509

2

DIP switch 2: Firmware update enabled

510

3

DIP switch 3: Configuration via Bluetooth enabled

511

4

DIP switch 4: Reserve enabled

512

5

–

–

6

Wireless module started.

905

7

Energy saving mode (< 60° and < 4.0 mA)

906

Endress+Hauser

FieldPort SWA50

Diagnostics

12

Diagnostics

12.1

Calling up diagnostics

Call up diagnostics in Field Xpert‣ Select the Diagnosis menu in DTM functions.
 The "Diagnosis" window is opened.
Call up diagnostics in FieldCare
1.

Click on the SWA50 in the network view.

2.

Open the context menu.

3.

Select the Diagnosis menu.
 The "Diagnosis" window is opened.

12.2

Identification

Diese Seite zeigt Informationen zum FieldPort SWA50.
Navigation
Diagnosis > Identification

Parameterbeschreibung Seite "Identification"

Endress+Hauser

Parameter

Beschreibung

Long Tag

Zeigt die lange Zeichenkette, die für den SWA50 eingegebene wurde.
Der Parameter dient der eindeutigen Identifikation des SWA50 im Netzwerk undin der Anlage. Der Parameter wird zur Einstellung des Burst-Modus und derEreignisbenachrichtigung genutzt.

Device Tag

Zeigt den Geräte-TAG, der für den SWA50 eingegeben wurde.

Descriptor

Zeigt die Beschreibung, die für den SWA50 eingegebene wurde.
Der Parameter dient zur Beschreibung des SWA50 wie z.B. Funktion oder Standort.

Date CodeZeigt das Datum, das für den SWA50 eingegeben wurde.
Das Datum dient zur Kennzeichnung eines bestimmten Ereignisses wie z.B. derletzten Änderung.

73Diagnostics

FieldPort SWA50

Parameter

Beschreibung

Message

Zeigt die eingegebene Nachricht
Die Nachricht kann beliebig verwendet werden. Die Nachricht wird auf
Anforderung des Masters über das HART-Protokoll gesendet

Real Time Clock Time

Zeigt die Netzwerksystemzeit.

Real Time Clock Date

Zeigt das Netzwerksystemdatum.

Serial Number

Zeigt die Seriennummer des SWA50.

Device Revision

Zeigt die Geräte-Version des SWA50.

Software Revision

Zeigt die Software-Version des SWA50.

Hardware Revision

Zeigt die Hardware-Version des SWA50.

Universal Command
Revision

Zeigt die HART-Protokollversion, die der SWA50 unterstützt.

Ext. Order CodeZeigt die ausführliche Bestellnummer des SWA50.

Order CodeZeigt die Bestellnummer des SWA50.

ENP Version

Zeigt die Version des elektronischen Typenschilds des SWA50.

12.3

Wireless Communication

Diese Seite zeigt Informationen zum Betrieb des FieldPort SWA50. Die Informationen
werden alle fünf Minuten aktualisiert.
Navigation
Diagnosis > Wireless Communication

Parameterbeschreibung Seite "Wireless Communication"

74

Parameter

Beschreibung

Network Identification

Zeigt die Identifikationsnummer des Netzwerks, mit dem sich der SWA50
verbindet.

MAC

Zeigt die MAC-Adresse des SWA50 .

Nickname

Zeigt den Kurznamen des SWA50 für den internen Gebrauch im Netzwerk.

Endress+Hauser

FieldPort SWA50

Diagnostics

Parameter

Beschreibung

Total Number of
Neighbours

Zeigt die Anzahl der WirelessHART-Geräte, die in der Umgebung des SWA50
wurden und zu denen eine Verbindung besteht.

Wireless Health Status

Zeigt wichtige Parameter zur Netzwerk-Kommunikation• Index: Kennung des Nachbar-Geräts• Nickname: Kurzname des Nachbar-Geräts• Mean RSL dBm: Mittlere Signalstärke des Nachbars, seit dem der SWA50 eine
Verbindung zum Netzwerk aufgebaut hat• Packets Transmitted: Anzahl der Pakete, die von dem SWA50 versendet wurden,
seit dem eine Verbindung zum Netzwerk besteht• Failed Transmits: Anzahl der Pakete, die von dem SWA50 versendet wurden
und die ihren Bestimmungsort nach Wiederholungen nicht erreicht haben, seitdem eine Verbindung zum Netzwerk besteht• Packets Received: Anzahl der Pakete, die der SWA50 erhalten hat, seit dem eine
Verbindung zum Netzwerk besteht
Diese Parameter zeigen die Werte seit dem letzten erfolgreichen
Verbindungsaufbau des SWA50 mit dem WirelessHART-Netzwerks. Wird die
Verbindung unterbrochen, werden die Werte zurückgesetzt.

12.4

Wired Communication

Diese Seite zeigt Informationen zum HART-Feldgerät, das an dem FieldPort SWA50
angeschlossen ist.
Navigation
Diagnosis > Wired Communication

Parameterbeschreibung Seite "Wired Communication"
Parameter

Beschreibung

Number of Devices

Zeigt folgendes:• 0: Kein HART-Feldgerät ist am SWA50 angeschlossen.
• 1: Ein HART-Feldgerät ist am SWA50 angeschlossen.

Wired Communication
StatusZeigt wichtige Parameter zur Netzwerk-Kommunikation• Index: Kennung des angeschlossenen HART-Feldgeräts• Long Tag or Message: Long Tag des angeschlossenen HART-Feldgeräts• STX Count: Anzahl der Rückmeldungen, die der SWA50 von dem
angeschlossenen HART-Felgerät erhalten hat• ACK Count: Anzahl der Rückmeldungen von HART-Feldgeräten, die der SWA50
erhalten hat• BACK Count: Anzahl Burst-Modi

12.5

Health Status

Diese Seite zeigt Diagnoseinformationen für den FieldPort SWA50 gemäß folgenden
Richtlinien und folgender Spezifikation:• NAMUR-Richtlinie NE 107• ASM-Richtlinien• HART-Spezifikation
Endress+Hauser

75Diagnostics

FieldPort SWA50

12.5.1

NAMUR NE 107

Navigation
Diagnosis > Health Status > NAMUR

Mögliche Gerätestatus
GerätestatusÜbersetzung

Good

Gut

Failure (F)Ausfall

Maintenance required (M)Wartungsbedarf

Out Of Specification (S)Außerhalb der Spezifikation

Function Check (C)Funktionskontrolle

12.5.2ASM

Navigation
Diagnosis > Health Status > ASM

Mögliche Gerätestatus

76

GerätestatusÜbersetzung

Good

Gut

Faults in the sensor or actuator element

Fehler im Sensor oder in der Stelleinrichtung

Faults in the electronics

Fehler in der Elektronik

Installation faults, fault during start-up

Installationsfehler, Fehler während derInbetriebnahme

Faults due to process influence, faults due to noncompliance with specified operating conditions

Prozessfehler, Fehler wegen Nichtbeachtung
spezifischer BetriebsbedingungenEndress+Hauser

FieldPort SWA50

Diagnostics

12.5.3

HART

Navigation
Diagnose > Health Status > HART

Wenn ein Kontrollkästchen markiert ist, ist die Aussage zutreffend.
Mögliche Gerätestatus

Endress+Hauser

Parameter

Beschreibung

Configuration ChangeCounter

Zeigt die Anzahl der KonfigurationsänderungenConfiguration Changed
Flag

Zeigt eine Änderung in der Konfiguration seit der letzten Kommunikation

Reboot Counter

Zeigt die Anzahl der Neustarts des SWA50

Real Clock Time

Zeigt die Systemuhrzeit

77Other DTM functions

FieldPort SWA50

13

Other DTM functions

13.1

Lock / Unlock

Use this page to protect the FieldPort SWA50 against unauthorized access via the DTM. If
locking is enabled and DIP switch 3 is set to "On", configuration via Bluetooth is still
possible.
If the "The device is write-protected (Device configuration locked)" option is enabled in the"Standardized Status 0" section, DIP switch 3 is set to "Off" and configuration via Bluetooth
is not possible.

"Lock / Unlock" parameter description page
Parameter

Description

Lock Code

Select the type of locking for the DTM to the SWA50.
Options• Unlocked: The SWA50 is unprotected. All parameters can be changed.
• Lock Temporary: The SWA50 is locked. A restart of the SWA50 or a power
outage disables the lock.
• Lock Permanent: The SWA50 is permanently locked. A restart of the SWA50 ora power outage do not disable the lock. The lock can be lifted via the "Lock Code"parameter.
• Lock All: The SWA50 is permanently locked for all masters.
If you select another option for the "Lock Code" parameter, the new option takes
immediate effect.

Lock Status

Shows the current access status of the DTM to the SWA50.
If a check box is selected, the statement is true.
Possible notifications• Device Locked: SWA50 is locked• Lock is Permanent: Permanently locked• Locked by Primary Master (Reset if Secondary Master): The SWA50 was locked
by the primary master. To unlock the device, the secondary master must restart.
• Configuration cannot be changed: Configuration cannot be changed• Locked by Gateway: The SWA50 is locked by the gateway

78

Lock CodeLock Status

Unlocked–

Lock Temporary

Device Locked

Lock Permanent

Lock is Permanent

Lock All

Device Locked, Locked is permanent and Configuration can not be changed–

Locked by Primary Master (Reset if Secondary Master)
Locking was triggered by the primary master.

Endress+Hauser

FieldPort SWA50

Endress+Hauser

Other DTM functions

Lock CodeLock Status

Lock All

Configuration cannot be changed–

Locked by Gateway
Locking was triggered by a gateway.

79Diagnostics and troubleshooting

FieldPort SWA50

14

Diagnostics and troubleshooting

14.1

Diagnostics

If a diagnostic event has occurred, the status signal appears in Netilion together with thecorresponding symbol for the event level according to NAMUR NE 107.
• Failure (F)• Function check (C)• Out of specification (S)• Maintenance required (M)Diagnostic
numberShort text

Corrective measure

Statussignal202

Self-test active.

Wait until self-test is completed.

F

314

Critical number of write cycles tomemory reached.

• Make sure that no cyclic configuration
change is automatically sent to theFieldPort.
• Change the FieldPort.

M

315

The hardware of the FieldPort isdefective.

Change the FieldPort.

F

316

The hardware of the FieldPort isdefective.

Change the FieldPort.

F

500

Incorrect entry in the burst/event
table

–

M

501

HART field device not working
correctly.

Check the HART field device.

F

502

Additional status information for
HART field device

–

F

503

WirelessHART connection failed• Ensure that a wireless device is withinreach.
• Enter the correct join key.
• Enter the correct network ID.
• Ensure that the network is
WirelessHART-compatible.

F

504

FieldPort cannot communicate with
the HART field device• Connect the HART field device.
• Check the HART field device and wiring.
• Check the HART address of the HART
field device.
• Increase the Start-up time.

F

505

FieldPort does not have a join key.

Enter the join key.

C

506

FieldPort not connected to the
WirelessHART network.

• Check the Join Key and network ID andconnect FieldPort to the network.
• If FieldPort was already connected,
check the signal path.

C507

No alternative WirelessHART signal See the "Diagnostic number 507"
path available.
description below–

508

FieldPort is in the configuration
mode

–

–

509

DIP switch 1: Bluetoothcommunication enabled

–

–

510

DIP switch 2: Firmware update
enabled––Electronics

Configuration

80

Endress+Hauser

FieldPort SWA50

Diagnostics and troubleshooting

Diagnostic
numberShort text

Corrective measure

Statussignal511

DIP switch 3: Configuration via
Bluetooth enabled

–

–

512

DIP switch 4: Reserve

–

–

803

Loop current• Check wiring. The loop current must be
between 3.6 mA and 22.5 mA.
• Change HART field device.

F

825

Operating temperature• Check ambient temperature.
• Check process temperature.

S

900

Bluetooth connected to config.
device––901

No connection attempt started yet
via WirelessHARTEnter the Join Key and network ID andstart the join attempt.

–

903

FieldPort is looking for connected
device.

––904

WirelessHART stack started

–

–

905

Wireless module started

–

–

906

Power save mode––

Process

Diagnostic number 507
To secure communication to the WirelessHART gateway in a WirelessHART network, thegateway specifies that a subscriber may only communicate with one neighbor.
Proceed as follows if you suspect that multiple subscribers in the WirelessHART network
have only one neighbor:1.

Check the signal paths of the network subscribers in the WirelessHART gateway.

2.

If there are multiple network subscribers with only one neighbor, check thefunctionality of the subscribers and the signal paths between the subscribers.

3.

If necessary, mount a repeater in a suitable position.

14.2

Endress+Hauser

Troubleshooting

Fault

MeasureNo communication between HART
field device and FieldPort.

Check the settings of the HART parameters in the FieldPort.
• SmartBlue app:
Root menu > System > FieldPort SWA50 > Connectivity > HART
Configuration →  52
• Field Xpert and FieldCare:"Wired communication" page →  61

No Bluetooth communication
between FieldPort and the SmartBlue
app.

Check whether Bluetooth communication is enabled →  43.

No Bluetooth communication
between FieldPort and Field Xpert.

Check whether Bluetooth communication is enabled →  43.

81

Diagnostics and troubleshooting

Fault

MeasureNo process values of HART fielddevices of other manufacturers in the
SmartBlue app.

For third-party HART field devices, use the Field Xpert .

The FieldPort does not connect to the
WirelessHART network.

82

FieldPort SWA50

 For device variables, see Technical Information TI01468S• It can take several minutes to establish a connection.
• Check network identification and network access key of the FieldPortand the WirelessHART gateway. The FieldPort and WirelessHART
gateway must use the same network identification and network
access key.
• Check if the FieldPort is correctly installed.

Endress+Hauser

FieldPort SWA50

Maintenance

15

Maintenance

15.1

General maintenanceWe recommend periodic visual inspections of the device.

15.2

Updating the firmware

You can run firmware updates for the FieldPort SWA50 via the SmartBlue app.
Requirements• The smartphone battery is charged or the smartphone is connected to a power supply.
• The Bluetooth signal quality of the smartphone is sufficient.
• In the case of the FieldPort SWA50, DIP switch 2 must be set to ON →  43.
(Factory setting of DIP switch 2: ON)
NOTICE
Error during firmware update. The firmware update includes uploading the firmware
package and installing the new firmware.
Incorrect firmware installation‣ The supply voltage must be applied during the entire firmware update process.
‣ The loop current must be at least 10 mA during the entire firmware update process.
The firmware update includes uploading the firmware package and installing the newfirmware.
‣ Wait until the firmware update has finished. The firmware update takes approx. 10 to
20 minutes. If the FieldPort SWA50 is actively connected to a WirelessHART network,
the firmware download process takes longer.
At least 10 mA must be generated by the connected HART field device during thefirmware update. This can be achieved by simulating the current output at the HART
field device, for example. You can check the current value in the SmartBlue app on the"Device information" page. →  44
If a HART field device is not connected to the FieldPort SWA50 or if the HART fielddevice cannot be reached, it is presumed that the loop current is at least 10 mA. In
this case, the SmartBlue app shows 20 mA for the loop current.→  32

Endress+Hauser

1.

Copy update packages to the SmartBlue app.

2.

Open the Firmware update page. Navigation: Root menu > System > FieldPort
SWA50 > Connectivity > Bluetooth configuration3.

Select update package from the list of available packages.

83

Maintenance

FieldPort SWA50

 24

84

"Firmware update" page1

Example of a package

4.

Tap the Start update button to upload the firmware package to the FieldPort
SWA50. If the update cannot be uploaded, the error message "Internal firmware
update error" is displayed.

5.

Wait until the firmware package is uploaded. Uploading of the firmware package
takes approx. 5 to 10 minutes. The remaining time is displayed. If the FieldPort
SWA50 is actively connected to a WirelessHart network, the upload takes longer.
 Once the firmware package has been uploaded successfully, the following view isdisplayed:

6.

Make sure that a loop current of at least 10 mA is present during installation of the
new firmware.

Endress+Hauser

FieldPort SWA50

Maintenance7.

Tap either the Apply button or Later button.
 Apply button: Installation of the new firmware on the FieldPort SWA50 isinitiated immediately.
Later button: Installation of the new firmware is initiated the next time theFieldPort SWA50 is restarted.

8.

Wait for installation of the new firmware. During installation of the new firmware,
the FieldPort SWA50 or the connected field device disappears from the live list of theSmartBlue app. The device is not displayed in the live list until the firmware has beensuccessfully installed. The installation takes approx. 6 minutes.

9.

Connect the FieldPort SWA50 to the SmartBlue app again.

10. Use the "Firmware version" parameter to check whether the new firmware is
installed. →  55
If the firmware package is not fully uploaded or is not correctly installed, the FieldPort
SWA50 operates with the old firmware.

Endress+Hauser

85

Repair

FieldPort SWA50

16

Repair16.1

General notes

Repairs may only be performed by Endress+Hauser staff or by individuals authorized andtrained by Endress+Hauser.

16.2

Disposal

If required by the Directive 2012/19/EU on waste electrical and electronic equipment(WEEE), the product is marked with the depicted symbol in order to minimize thedisposal of WEEE as unsorted municipal waste. Do not dispose of products bearing thismarking as unsorted municipal waste. Instead, return them to Endress+Hauser for
disposal under the applicable conditions.

86

Endress+Hauser

FieldPort SWA50

Accessories

17

Accessories

Optional accessories:
Mounting bracket (order number: 71520242)
Detailed information about the accessories is available from your Endress+Hauser salesorganization: www.addresses.endress.com or on the product page

Endress+Hauser

87Technical data

FieldPort SWA50

18

Technical data
For detailed information on "technical data": see Technical Information TI01468S

88

Endress+Hauser

Endress+Hauser

Diagnostics

Root menu

SystemApplication

Device information

Reachable devices

Firmware update

Change Bluetooth
password

19.1
Menu overview (SmartBlue app navigation)

19.1.1
FieldPort SWA50 with WirelessHARTInformation1), 2)

WirelessHART config.

HART configuration

Bluetooth config.

Appendix

Device managem.1), 2)

Information

Geolocation

Burst period config.

Connectivity

Device management

HART Info1), 2)

Measured values 2)

HART Info

Measured values

19

Field device 1), 2)

FieldPort SWA50

Field device

2)

FieldPort SWA50

Field device 1), 2)

FieldPort SWA50

WirelessHART

FieldPort SWA50
Appendix

Pages and parameters that are marked with 1) are only shown for Endress+Hauser
devices.

Pages and parameters that are marked with 2) are displayed for a FieldPort to which afield device is connected.

A0043771

89

*71654358*
71654358

www.addresses.endress.com