Data Sheet FBUHFCWEN

Ultipleat® High Flow
Filter Elements
for fine particle removal from water
Ultipleat High Flow filter elements are designed forhigh particle removal efficiency of fine particulates fromwater applications.

Description
The Ultipleat High Flow filter elements utilize
polyethersulfone (PES) media with unique, laid-overpleat geometry. The Ultipleat High Flow element is alarge diameter, single open ended, pleated cartridge withan inside to outside flow pattern and a core-freeconstruction.
The filter’s unique laid-over pleat geometry, combinedwith its large diameter means fewer elements are
required for a given flow rate when compared tostandard diameter cartridges. Filter vessels arecorrespondingly smaller, resulting in lower capital andinstallation costs, as well as reduced operating costs.

Features and Benefits
FeaturesBenefits

Polyethersulfone membranewith no adhesives orsurfactants• Consistent filtrate quality• Highly stable structure• Media provides a typical 3 log
reduction of Giardia cysts andCryptosporidium oocysts• Process reliability

Pleated (laid-over pleatgeometry) media in a large
diameter cartridge format• 10 % water savings*• 30 % lower operating costs*• Lower capital and installation costs*• Reduced installation footprint*• Longer service life

Inside to outside flow
configuration• At element change-out, protects
filtrate from recontamination bytrapping particulates inside the cartridge*Typical when compared to standard cartridges used in test comparison.

Ultipleat High Flow Elements

OuterWrap
Drainage
Layer

FilterMedium

Support
Layer

Flow

Ultipleat filter element construction, showing uniform flow distribution

Quality• Cartridges produced in a controlled environment• Manufactured according to ISO 9001:2008 certified
Quality Management System

Food Contact Compliance
Please refer to the Pall website
http://www.pall.com/foodandbev for a Declaration ofCompliance to specific National Legislation and/orRegional Regulatory requirements for food contact use.

Materials of Construction
Filter Medium

Pre-filtration layer Pall proprietary melt
blown polypropylene media, Final filtration
layer Pall proprietary Supor® membrane(polyethersulfone)

Support mesh and outer wrap

Polypropylene

End Caps and Handle

Polypropylene (10 % glass fiber reinforced)

O-ring Seal

Ethylene Propylene Rubber

Technical Information
3Operating Characteristics in Compatible Fluids1

Sanitization

Maximum Differential Pressure

Max. Operating Temperature2

MethodTemperature

Cumulative Time

82 °C (180 °F)

Hot Water

85-90 °C (185-194 °F)

10 hours

320 ppm totalperoxides

20 °C (68 °F)

3.45 bard (50 psid) (forward direction)

Compatible fluids are defined as those which do not swell, soften or attack anyof the filter components.
2Not recommended where the temperature is cycled more than 10 °C (50 °F).
1

Measured under laboratory test conditions. Users should verify suitability
against their own conditions of use. Where indicated 10 minute sanitization
cycles were utilized.

3Ordering Information
This information is a guide to the part number structure and possible options.
For availability of specific options and housing details, please contact Pall.

Typical Flow Rates4

Element Part Number: HFU 6

Flow Rate (US gpm)

CAS010 JUW(1016 mm / 40" Element and 1524 mm / 60" Element)

Table 150100

150200

100

Example Part Number: HFU640CAS010JUW

CodeDescription

40

1016 mm (40”)

601524 mm (60”)

Outside to in flow is not recommended. Ultipleat High
Flow filter elements are designed for water flow rates
typically >10 m3/h (44 US gpm), please contact yourPall representative for product recommendations moresuitable to lower flow rates.

Differential Pressure (mbard)

Table 1: Nominal Length

801.2")

16mm(4010600.9")m4m(60152400.6

200.3

0

Differential Pressure (psid)

See bold reference codes in tables.

00153045Flow Rate (m /h)3

Typical initial clean media differential pressure (Δp) per 1016 mm (40”) and1524 mm (60”) cartridge for water at 20 °C (68 °F); viscosity 1 centipoise.
For assistance in filter assembly sizing and housing selection, contact yourPall representative.

4

Pall Food and Beverage

Visit us on the Web at www.pall.com/foodandbev

25 Harbor Park Drive
Port Washington, NY 11050+1 516 484 3600
telephone+1 866 905 7255
toll free US
foodandbeverage@pall.com

Pall Corporation has offices and plants throughout the world. For Pall representatives
in your area, please go to www.pall.com/contact

Portsmouth - UK
+44 (0)23 9230 2269 telephone+44 (0)23 9230 2509 fax

Please contact Pall Corporation to verify that the product conforms to your nationallegislation and/or regional regulatory requirements for water and food contact use.
Because of technological developments related to the products, systems, and/orservices described herein, the data and procedures are subject to change
without notice. Please consult your Pall representative or visit www.pall.com to verify
that this information remains valid. Products in this document may be covered by one
or more of the following patent numbers: EP 667,800; EP 982,061; EP 1,380,331; US
5,543,047; US 5,690,765; US 5,725,784; US 6,113,784; US 7,083,564; US 7,318,800.
© Copyright 2010, Pall Corporation. Pall,, Supor and Ultipleat are trademarks of PallCorporation. ® Indicates a trademark registered in the USA. Filtration. Separation. Solution.SM
is a service mark of Pall Corporation.

FBUHFCWEN

Created in the UK.

June 2010