B-2339(2)Hardware Manual

SmartAXIS FT2J/1J

SAFETY PRECAUTIONSSAFETY PRECAUTIONS• Be certain to read this manual carefully before performing installation, wiring, or maintenance and inspection
works, or operating the SmartAXIS FT2J/1J (Hereinafter referred to as "SmartAXIS"). If the SmartAXIS is used in amanner not specified by the manufacturer, the protection provided by the equipment may be impaired.
• The SmartAXIS has been manufactured with careful regard to quality. However, if you intend to use this product inapplications where failure of this equipment may result in damage to property or injury, ensure that it used inconjunction with appropriate fail-safe backup equipment.
• Precautionary measure should be taken to avoid unauthorized access from the outside network to the SmartAXIS.
Please note that the Company shall not be liable for any loss, damage or other expenses incurred directly or
indirectly by unauthorized access, etc.
• In this manual, safety precautions are categorized depending on the severity as Warning or Caution:
Warning notices are used to emphasize that improper operation may cause severe
personal injury or death.
Caution notices are used where inattention might cause personal injury or damage toequipment.

• This product is not designed for use in applications requiring a high degree of reliability and safety, such as
applications for medical devices, nuclear power, railroads, aerospace, and automotive devices. This productshould not be used for such applications.
• Turn off the power of this product before installation, removal, wiring, maintenance, and inspection of thisproduct. Failure to turn power off may cause electrical shock or fire hazard.
• Special expertise is required to install, wire, configure, and operate this product. Person without such expertisemust not use this product.
• This product uses an LCD (liquid crystal display) as a display device. The liquid inside the LCD is harmful to theskin. If the LCD is broken and the liquid attaches to your skin or clothing, wash the liquid off using soap, andconsult a doctor immediately.
• An emergency circuit that uses emergency stop switch or an interlocking circuit must be configured outside ofthis product.
• Do not use touch switches for an emergency circuit or an interlocking circuit. If this product fails, serious injury
to operators and equipment damage may be caused.
• If relays or transistors in this product output circuits should fail, outputs may remain at on or off state. For
output signals which may cause serious accidents, configure monitor circuits outside this product.
• This product self-diagnostic function may detect internal circuit or program errors, stop programs, and turnoutputs off. Configure circuits so that the system containing this product is not jeopardized when outputs turnoff.
• In case this product is accidentally dropped or exposed to significant shock, stop using this product, check thisproduct for damage, and confirm that its various functions work safely and correctly.
• Connect SmartAXIS's FG wire to grounding resistance of 100 Ω or less. Otherwise, there is a risk of electric
shock or malfunction.
• The screen will not be visible if the backlight of this product burns out. However, the touch panel will remainfunctional. Thus, erroneous touch panel operation may occur while controlling the touch panel. Because such
erroneous operations could result in damage, the touch panel should not be used once the backlight is burnedout.

Preface-1

SmartAXIS Hardware ManualSAFETY PRECAUTIONS• Prevent this product from falling while moving or transporting, otherwise it may cause damage or malfunction tothis product as a result.
• Use the product within the environmental limits given in the catalog and this manual. Use of the product inhightemperature or high-humidity environments, or in locations where it is exposed to condensation, corrosive
gas, or large shock loads can create the risk of electrocution and fire.
• This product is designed for use in pollution degree 2. Use this product in environments of pollution degree 2.
(based on the IEC 60664-1 rating)• Install this product according to the this manual. Improper installation will result in falling, failure, electricalshock, fire hazard, or malfunction of this product.
• Prevent metal fragments or wire chips from dropping inside this product housing. Ingress of such fragments andchips may cause fire hazard, damage, and malfunction.
• Use a power supply of the rated value. Using a wrong power supply may cause fire hazard.
• The main unit uses “PS2” as DC power supply. (based on the IEC/EN 61131 rating)• Use wire of a proper size to meet the voltage and current requirements.
• When exporting this product to Europe, use an EN 60127 (IEC 60127) approved fuse on the power line outside
this product.
• When exporting this product to Europe, use an EU-approved circuit protector.
• Make sure of safety before starting and stopping this product. Incorrect operation of this product may cause
mechanical damage or accidents.
• This product cannot be directly connected to the communication lines (including public wireless LAN) of
telecommunication carriers (mobile communication companies, fixed-line communication companies, Internet
providers, etc.). When connecting this product to the Internet, be sure to connect via a device, such as a router.
• The touch panel of this product is made of glass, and will break if exposed to excessive shock. Take due carewhen handling it.
• When operating the touch panel in an environment where the ambient operating temperature exceeds 50°C,
there is a risk of getting burn injury. So please use heat-resistant gloves, touch pen, and such to prevent burninjury.
• The protective film attached to the display of this product is to protect the product from scratches duringtransportation. Please remove the protective film before use. If the display is used with protective film, the film
may become cloudy and stick to the display depending on the usage environment and may become
unremovable.
• Do not push hard or scratch the touch panel and protection sheet with a hard object like hand tool. Touch panel
and protection sheet can be easily damaged.
• Do not install this product in areas subjected to strong ultraviolet rays.
• Do not attempt to disassemble, repair or modify this product. This can create the risk of fire or electrocution.
• When disposing of this product, do so as an industrial waste.
• When using this product in a system that requires clock accuracy, set the time regularly.
• Do not switch off the power or pull out the USB flash drive while it is being accessed, as this may result in
destruction of the stored data. If the data on the USB flash drive is corrupted, format the USB flash drive.
• Turn off the power supply of this product before connecting or disconnecting USB devices other than USB
memory.

SmartAXIS Hardware Manual

Preface-2

Revision history

Revision history
September 2023:

First Edition

January 2024:

Second Edition

July 2024:

Third Edition

Caution• All rights in this manual belong to IDEC Corporation. It may not be reproduced, reprinted, sold, transferred orrented without our permission.
• The contents of this manual are subject to change without notice.
• Please contact your vendor or IDEC Corporation with any problems regarding the operation of this product.

Trademarks

WindO/I and SmartAXIS are registered trademarks of IDEC CORPORATION in JAPAN.
All other company names and product names used in this manual are trademarks of their respective owners.

Preface-3

SmartAXIS Hardware ManualRegarding Compatible Standards

Regarding Compatible Standards

The conforming standards supported by this product are as follows.
UL 121201 / CSA C22.2 No.213 (Under application)• This product is for indoor use only.
• Open type or panel mounted when installed in a Listed Type 4X "Indoor Use Only",Type 13 enclosure.
• The use of an SELV source.
• When wiring this product at the field, use copper conductors only.
Test item particulars
Type of item

Open Type/enclosed type when panel mounted in appropriate end enclosure

Description of equipment function

Control

Connection to mains supply

N/A connected to SELV source

Overvoltage Category

None

Pollution Degree

2

Environmental Conditions

Extended:

Temperature:-20 to +55ºC, see RATINGS section for detail.

Humidity:

10 to 95%RH (no condensation)

For use in wet locations

NO

Equipment mobility

Panel mounted

Operating Conditions

Continuous• This product is suitable for use in Class I, Division 2, Groups A, B, C, D or Non-Hazardous locations only.
• RATINGS:
Input: 24 Vde, SELV, LIM
Type Number
Power Consumption

FT2J-7U22*AF-B

FT1J-4F12RAG-*FT1J-4F14*AG-*

17W

13W

15W

Maximum Surrounding Air: -20 to +55ºC
Enclosure Type 4X Indoor Use only, Type 13• Temperature Code: T4A• Equipment to be installed in an environmentally suitable enclosure that requires the use of a tool to access.
• L'appareil FT2J/1J est convu pour etre utilise uniquement dans des emplacements de classe I, division 2, groupes
A, B, C, Dou non dangereux.
• Caracteristiques:
Entree: 24 Vde, Tres basse tension de securite (SELV), LIMITES
Nummer eingeben

FT2J-7U22*AF-B

FT1J-4F12RAG-*FT1J-4F14*AG-*

Energieverbrauch

17W

13W

15W

Air ambiant maximal: -20 a +55ºC
Boitiers de type 4X pour une utilisation interieure, de type 13.
• Code de temperature: T4A• L'appareil FT2J/1J doit etre installe dans un boitier adapte a l'environnement et uniquementaccessible a l'aide
d'outils.

SmartAXIS Hardware Manual

Preface-4

Preface

PrefaceThank you for purchasing the SmartAXIS manufactured by IDEC Corporation.
This manual describes the specifications of the SmartAXIS FT2J/1J, how to install it, and various functions.
Read this manual to ensure the correct understanding of the entire functions of this product.
IDEC Corporation makes the latest product manual PDFs available on our website at no additional cost. Please
download the latest product manual PDFs from our website.
Read the following materials as necessary for your particular application.
References

Content

SmartAXIS Hardware Manual(This document)

Describes the product specifications, installation and wiring instructions of
the FT2J/1J, optional items, and I/O cartridges.

WindO/I-NV4 User's Manual (PDF)

Describes the basic operations of the FT2J/1J, how to create the project
necessary for operation, and the various drawings and parts that make up
the project.

Ladder Programming Manual (PDF)

Describes basic operations for programming with ladders, monitoring
methods on the WindLDR, instruction lists, and details of each instruction.

WindO/I-NV4 External Device Setup Manual(PDF)

Describes the connection procedures and available device addresses forvarious communication including the Device Link Communication, O/I Link
communication, and DM Link communication.

Symbols Used in this ManualThis manual uses the following symbols to facilitate explanation.
Symbols……

Information that requires special attention. Failure to operate the product in accordancewith the information provided can lead to serious injury or damage.

……

Information relating to requests or material to reference in the use of a function……

Useful information relating to a function

YES

……

Screen buttons are indicated by bold text or by using the actual graphic icon.

****

……

Controls are indicated by bold text.

Preface-5

SmartAXIS Hardware ManualAbbreviations, Generic Terms, and Terminology Used in this Manual

Abbreviations, Generic Terms, and Terminology Used in this Manual
Item

Description

FT2J

The name is short for SmartAXIS FT2J-7U22*AF-B.

FT1J

The name is short for SmartAXIS FT1J-4F1**AG-*.

FT2J/1J

The format used to refer to FT2J and FT1J.

SmartAXIS

Generic term for integrated display controller FT2J/1J.

External Device

Generic term used to refer to a PLC or micro computer that is connected to andcommunicates with the main unit.

Device Address

Memory that is capable of storing values in unit of bits or words loaded on the main unit
and external device.

WindO/I-NV4

Integrated configuration software application for creating projects of the main unit.

Operating System

Software used to manage and control system software.

System Software

Software that performs basic control and management of the main unit.

Project

Data including image data required for operating the main unit, which is created with
WindO/I-NV4.

Internal Device

The generic term for internal device addressing on the main unit such as internal relays,
registers, etc.

SmartAXIS Hardware Manual

Preface-6

Contents

Contents
SAFETY PRECAUTIONS ................................................................................ Preface-1
Revision history ........................................................................................... Preface-3
Caution ....................................................................................................... Preface-3
Trademarks ................................................................................................. Preface-3
Regarding Compatible Standards .................................................................. Preface-4
Preface ....................................................................................................... Preface-5
Symbols Used in this Manual ........................................................................ Preface-5
Abbreviations, Generic Terms, and Terminology Used in this Manual ............... Preface-6

Chapter 1
1

2

Chapter 2
1

2Main Unit Specifications
FT2J .................................................................................................................... 1-1
1.1

Packing Content..............................................................................................1-1

1.2

Type Number..................................................................................................1-1

1.3

Part Names.....................................................................................................1-2

1.4

External Interfaces..........................................................................................1-3

1.5

Specifications................................................................................................ 1-11

1.6

Dimensions................................................................................................... 1-14

1.7

Installation ................................................................................................... 1-15

1.8

Wiring .......................................................................................................... 1-20

1.9

Maintenance and Inspection .......................................................................... 1-24

1.10

Software License Information......................................................................... 1-25

FT1J .................................................................................................................. 1-26
2.1

Packing Content............................................................................................ 1-26

2.2

Type Number................................................................................................ 1-27

2.3

Part Names................................................................................................... 1-28

2.4

External Interfaces........................................................................................ 1-29

2.5

Specifications................................................................................................ 1-37

2.6

Dimensions................................................................................................... 1-40

2.7

Installation ................................................................................................... 1-41

2.8

Wiring .......................................................................................................... 1-44

2.9

Maintenance and Inspection .......................................................................... 1-47

2.10

Software License Information......................................................................... 1-49

I/O Cartridge
Digital I/O Cartridge.............................................................................................. 2-1
1.1

Packing Content..............................................................................................2-1

1.2

Type Number..................................................................................................2-1

1.3

Part Names.....................................................................................................2-1

1.4

Specifications..................................................................................................2-2

1.5

Dimensions.....................................................................................................2-5

1.6

Install and remove ..........................................................................................2-5

1.7

Wiring ............................................................................................................2-6

Analog I/O Cartridge ............................................................................................. 2-7
2.1

Preface-7

Packing Content..............................................................................................2-7

SmartAXIS Hardware ManualContents

Chapter 3
12

Chapter 41

2.2

Type Number................................................................................................. 2-7

2.3

Part Names.................................................................................................... 2-8

2.4

Specifications ................................................................................................. 2-9

2.5

Dimensions ...................................................................................................2-13

2.6

Install and remove ........................................................................................2-13

2.7

Wiring ..........................................................................................................2-14

Options
Optional items.......................................................................................................3-1
1.1

FT2J.............................................................................................................. 3-1

1.2

FT1J.............................................................................................................. 3-2

Replacement Parts.................................................................................................3-3
2.1

FT2J.............................................................................................................. 3-3

2.2

FT1J.............................................................................................................. 3-3

Module Configuration Editor
Overview ..............................................................................................................4-1
1.1

2

3

4

Configuration & Functions ............................................................................... 4-1

Basic Operations....................................................................................................4-2
2.1

Open the Module Configuration Editor ............................................................. 4-2

2.2

Inserting I/O Cartridges .................................................................................. 4-2

2.3

Deleting I/O Cartridge .................................................................................... 4-4

2.4

Changing I/O Cartridge................................................................................... 4-5

Digital I/O Cartridge Settings..................................................................................4-6
3.1

I/O Assignments ............................................................................................ 4-6

3.2

Parameter Settings......................................................................................... 4-6

Analog I/O Cartridge Settings .................................................................................4-7
4.1

I/O Assignments ............................................................................................ 4-7

4.2

Parameter Settings......................................................................................... 4-7

SmartAXIS Hardware Manual

Preface-8

Contents

Preface-9

SmartAXIS Hardware Manual

Main Unit Specifications

Chapter 1

1.1

FT2J
Packing Content
Before installing the main unit, make sure that the model you have received is what you actually ordered, and noparts are damaged to accidents during shipping.
Product Name & Dimensions

Quantity

Description

1

Main unit

4-1

Removable terminal block 9-pin

1Removable terminal block 16-pin

1Removable terminal block 11-pin

2Attached to the main unit

FT2J

Mounting clips

Serial interface connector

Input terminal connector

Output terminal connector

Dummy cartridge

1.2

Type Number
LCD

7.0 inch wide
TFT Color

Bezel
Color

Black

Input Terminal Specification

Digital input (shared sink/source): 10
Analog input (shared digital sink input): 4

SmartAXIS Hardware Manual

Output Terminal
Specification

Type Number

Relay output: 8

FT2J-7U22RAF-B

Transistor sink output: 6
Analog output: 2

FT2J-7U22KAF-B

Transistor source output: 6
Analog output: 2

FT2J-7U22SAF-B

1-1

Main Unit Specifications

11

1 FT2J

1.3

Part Names
(2)

(3)

(13) (11) (14)
TOP

(5)

USB1

(6)

USB2

(7)

LAN

IN

RESET

Slot1

COM

(1)

No.

1-2

(8)

Name

(9)

(10)

(4)

Slot2

OUT

(12)

Description
Normal Operation
Operating system is booting. (Normal Operation)
Operating system is booting. (Boot mode)
Preparing to boot the operating system, running in boot mode.
Main unit is damaged.
Power is off.

(1)

POWER LED

Green (lit):
Green (flash):Orange (lit):
Orange (flash):
Red (lit):
Not lit :(2)

Display

TFT color LCD(3)Touch Panel

PCAP touchscreen (Projected capacitive)(4)

Serial Interface (COM)

RS232C, RS422/485 Connector: Terminal Block 9-pin (Push-in type)
Maximum cable length: 15m (RS232C), 1200m (RS422/485)(5)

USB Interface (USB1)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(6)

USB Interface (USB2)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(7)

Ethernet Interface (LAN)IEEE802.3u 10BASE-T/100BASE-TX Connector: RJ-45(With Auto MDI/MDI-X function)
Maximum cable length: 100m

(8)Power Supply Terminal

Connector: Terminal Block 3-pin (Push-in type)(9)

Mounting Clip Position

4 places(10)

RESET Switch

Tact switch(11)

Input Terminal (IN)

Connector:

Removable terminal block 16-pin (Push-in type)
Digital input (shared sink/source) (I0 to I7, I10, I11)
Analog input (shared digital sink input) (I12 to I15)

Connector:

Removable terminal block 11-pin (Push-in type)
Relay Output (Q0 to Q7)
Transistor sink output (Q0 to Q5), Analog output (AQ0, AQ1)
Transistor source output (Q0 to Q5), Analog output (AQ0, AQ1)

(11)

Output Terminal (OUT)(13)

Cartridge Slot (Slot1)

Slots for connecting the following I/O cartridges. For details about the cartridges,
refer to Chapter 2 “I/O Cartridge” on page 2-1.

(14)

Cartridge Slot (Slot2)

Digital I/O cartridge:
Analog I/O cartridge:

FC6A-PN4, FC6A-PTK4, FC6A-PTS4
FC6A-PJ2A, FC6A-PJ2CP, FC6A-PK2AV, FC6A-PK2AW

SmartAXIS Hardware Manual

1 FT2J

1.4

1External Interfaces• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) when connecting a DC power

supply to the Input and Output terminals.
● Serial Interface (COM)Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Interface Specification

RS232C, RS422/485

Connector

Removable terminal block 9-pin

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

S3TL-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

No.1

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

No.9

No.

Name

I/O

Function

1

SD

OUT

Send Data

2

RD

IN

Receive Data

3

RS

OUT

Request to Send

4

CS

IN

Clear to Send

5

SG

―

Signal Ground

6

SDA

OUT

Send Data (+)

7

SDB

OUT

Send Data (-)

8

RDA

IN

Receive Data (+)

9

RDB

IN

Receive Data (-)

Communication type

RS232C

RS422/485*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

SmartAXIS Hardware Manual

1-3

Main Unit Specifications• Make sure to turn off the power to the FT2J before wiring each interface.
• The serial interface (COM) can be used as the RS232C and RS422/485 interfaces at same time.
• Use the SELV (Safety Extra-Low Voltage) circuit to connect the Serial, USB and Ethernet interfaces.

1 FT2J
Using RS422/485 interface
FT2J is not equipped with terminating resistor. Insert a terminating resistor of an appropriate value (about 100 to 120
Ohm, 1/2 W minimum) between terminal number 8 (RDA) and terminal number 9 (RDB), if necessary.
TOP
USB1

IN

USB2
LAN

RESET

Slot1

COM

Terminal Number 8 (RDA)

Slot2

OUT

Terminal Number 9 (RDB)

For inserting and removing wires, refer to “1.8 Wiring” on page 1-20.
● Input Terminal (IN)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Connector

Removable terminal block 16-pin (Push-in type)

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

S3TL-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

Input Points

14

Rated Input Voltage

24V DC

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

Input Voltage Range

0 to 28.8V DC

Effect of Improper
Input Connection

No damage
However, if high voltage is applied that exceeds the operating input voltage range, there isa risk of permanent damage.

*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

1-4

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

SmartAXIS Hardware Manual

1 FT2J

1

Digital Input
Shared sink/source

Input Points(Terminal Number/Common Line Name)

10 points in 1 common line
(I0 to I7, I10, I11 / COM0 terminal)

Rated Input Current
Input Impedance
Turn ON Time
Input Delay Time
Turn OFF Time

I0 to I5

4 mA/point (at 24V DC)

I6, I7, I10, I11

5 mA/point (at 24V DC)

I0 to I5

5.6 kΩ

I6, I7, I10, I11

4.3 kΩ

I0 to I5

25 μs maximum + software filter setting

I6, I7, I10, I11

100 μs maximum + software filter setting

I0 to I5

25 μs maximum + software filter setting

I6, I7, I10, I11

100 μs maximum + software filter setting

Main Unit Specifications

Input Circuit Type

Between Input Terminal and Internal
Photocoupler isolated
Circuit

Isolation

Between Input Terminals

Not isolated

Input TypeType1 (IEC 61131-2)

External Load for I/O Interconnection

Not isolated

Signal Determination Method

StaticEffect of Improper Input Connection

Even if wiring for sink or source connection is incorrect, nodamages are caused.
However, if high voltage is applied that exceeds the operating
input voltage range, there is a risk of permanent damage.

Cable Length in compliance with electromagnetic immunity 3 m■ Operating Ranges
I0 to I5

I6, I7, I10, I11

Voltage

Voltage28.8 V28.8 VON Area

ON Area

24 V

24 V

15 V

15 V

Transition
Area

Transition
Area
5V

5V

OFF Area

OFF AreaCurrent

0.5 mA

2.2 mA

3.8 mA

Current

4.7 mA

0.9 mA

3.2 mA

5.3 mA

6.4 mA■ Input Equivalent Circuit
I0 to I5

I6, I7, I10, I11
5.6 kΩ

Input

COM0

SmartAXIS Hardware Manual

Internal Circuit

COM0Internal Circuit

4.3 KΩ
Input

1-5

1 FT2J
Analog Input (shared digital sink input)
Input Electrical Characteristic*1

Voltage

Input Points(Terminal Number/Common Line Name)

4 points in 1 common line
(I12 to I15/ COM1(-) terminal)

Input Range

0 to 10V DC

4 to 20 mA

Input Impedance

78kΩ

250kΩ

Digital Resolution

4096 (12 bit)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

AD Conversion

Input Error

Optional range*2: -32768 to 32767
Sampling time

5 msec max.

Sample Repetition Time

5 msec max.

Total Input Delay Time

6 msec + 1 scan time

Type of Input

Single-ended

Operation Mode

Self-scan

Conversion Method

SAR

Maximum Error at 25°C

±3.0% of full scale

Temperature Coefficient±0.04% of full scale/°C

Maximum Error±5.0% of full scale

Status Display

Noise Resistance

Device Monitor screen (LCD display)
Maximum Temporary Deviation during
Electrical Noise Tests±5.0% of full scale

Input Filter

Yes

Recommended Cable for Noise
Immunity

Shielded cable

Calibration to Maintain Rated Accuracy

Not possible

Maximum Permanent Allowed Overload (No Damage)

28.8V DC

Overload Status (Outside Input Range) Detection

Detectable

Isolation

Used as Digital Input

Between Input Terminal and Internal
Circuit

Not isolated

Between Input Terminals

Not isolated

Digital Input Type— (IEC 61131-2 digital input type is not supported)

Input Threshold

ON voltage: 15V min.

ON current: 0.20 mA min.

OFF voltage: 5V max.

OFF current: 0.06 mA max.

*1 Can be set by application software.
*2 This function is used the analog value converting it to the specified range.

1-6

Current

SmartAXIS Hardware Manual

1 FT2J

1■ Operating Ranges

Main Unit Specifications

I12 to I15
Voltage28.8 VON Area
24 V

15 V

Transition
Area
5V

OFF AreaCurrent
0.06mA

0.2mA

0.3mA

0.37mA■ Input Equivalent Circuit
I12 to I15

56kΩ
Input circuit
120kΩ
22kΩ

130kΩ

0V

Internal Circuit

24V DC

0V

Pulse Intput
The maximum input frequency varies based on the input terminal and function.
Input Terminal

I0

I1

I2

I3

I4

I5

Adding counter

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzUp/down selection reversible
counter

20 kHz

-

-

-

-

-

Dual-pulse reversible counter

20 kHz

20 kHz----2-edge count

10 kHz

10 kHz----4-edge count

5 kHz

5 kHz

-

-

-

-

Catch input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzInterrupt input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHz--

20 kHz

20 kHz

20 kHz-High-speed counter
Function*1

Frequency measurement*1 Can be set by application software.

SmartAXIS Hardware Manual

1-7

1 FT2J● Output Terminal (OUT)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Connector

Removable terminal block 11-pin (Push-in type)

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

S3TL-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

Relay Output
Type Number

FT2J-7U22RAF-B

Output Points (Terminal Number)

8 (Q0 to Q7)

Output Type1a contact

Maximum Load Current

1

2 A max.

1 common line

7 A max.

Minimum Switching Load

1 mA, 5V DC (reference value)

Initial Contact Resistance

30 mΩ max.

Electrical Life

100,000 operations min.
(rated resistive load 1,800 operations/hour)

Mechanical Life

20,000,000 operations min. (no load 18,000 operations/hour)

Rated Load

240V AC 2 A, 30V DC 2 A
Between Output Terminal andInternal Circuit

Withstand Voltage

Between Output Terminals(COM2 and COM3)

Status Display

2,300V AC 5 mA, 1 minuteDevice Monitor screen (LCD display)

When the output voltage of FT2J-7U22RAF-B exceeds 200V AC, please connect COM2 and COM3 to single
power source.

Output Delay
ON

Input to Relay
OFF
ON

Output Relay StatusOFF

OFF Bounce: 6 ms maximum
OFF Delay: 10 ms maximum
ON Bounce: 6 ms maximum
ON Delay:
6 ms maximum*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

1-8

SmartAXIS Hardware Manual

1 FT2J

1

Transistor Output
FT2J-7U22KAF-B

FT2J-7U22SAF-B

Output Circuit TypeSink output

Source output

Output Points

6 (Q0 to Q5)

Rated Load Voltage

24V DCOperating Input Voltage Range

20.4 to 28.8 DC

Maximum Load Current

1

0.5 A

1 common line

3A

Voltage Drop (ON Voltage)

1V max. (Voltage between COM and output terminal when ON)

Maximum Inrush Current

1 A max.

Leakage Current

0.1 mA max.

Main Unit Specifications

Type Number

L/R=10 ms (28.8V DC, 1 Hz)

Inductive Load

100 mA max., 24V DC

External Current Draw

V(+) terminal supply power

Isolation

Photocoupler isolated

Status Display

Device Monitor screen (LCD display)COM2(+) terminal supply power■ Output Equivalent Circuit
FT2J-7U22KAF-B

FT2J-7U22SAF-B
COM2(+)

OutputInternal Circuit

Internal Circuit

V(+)

COM2(-)

SmartAXIS Hardware Manual

OutputV(-)

1-9

1 FT2J
Analog Output
Type Number

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Output Electrical Characteristic*1

Voltage

Output Points (Terminal Number/Common Line Name)

2 / 1 common line (AQ0, AQ1 / COM3(-) terminal)

Output Range
Output LoadDA Conversion

Output Error

Data

Noise Resistance

Current

0 to 10V DC

4 to 20 mA DC

Impedance

2 kΩ or higher

500 Ω or lower

Load Type

Resistive load

Scan Time

1 scanSettling time

1 ms or lower

Total Output System Transfer Time

1 ms + 1 scan time

Maximum Error at 25°C

±0.3% of full scale

Temperature Coefficient±0.02% of full scale/℃

Reproducibility after Stabilization Time

±0.4% of full scale

Non-linearity±0.01% of full scale

Output Ripple

30 mV maximum

Overshoot0%*2

Maximum Error±1.0% of full scale

Digital Resolution

4,096 (12 bits)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

Monotonicity

Yes

Current Loop OpenNot detectable

Maximum Temporary Deviation during
Electrical Noise Tests±5.0% or less of full scale

Optional range*3: -32768 to 32767

Recommended Cable for Noise Immunity

Shielded cable

Effect of Improper Output Connection

No damageCalibration to Maintain Rated Accuracy

Not possible■ Output Equivalent Circuit+

Analog Signal
Analog Output
Element–

Switching Signal

Pulse Output
Type Number

FT2J-7U22KAF-B

FT2J-7U22SAF-B

Output Points

4 (Q0 to Q3)

Maximum output pulse frequency

20kHz

PWM output

Duty cycle: 0.1 to 100.0 (increments of 0.1%)
Output pulse frequency: 30 to 1000 (increments of 1Hz)
When the pulse OFF time is shorter than 25μs, the pulse ON ratio is adjusted so that
the OFF time is 25us and output the signal.
When the pulse ON time is shorter than 25μs, the pulse OFF ratio is adjusted so that
the ON time is 25us and output the signal.

*1 Can be set by application software.
*2 Overshoot may occur at light loads. The occurrence of overshoot can be controlled by inserting damping resistance into
the circuit. A general guide for the damping resistance value is about 150 Ω including the input line impedance for thedestination.
*3 This function is used the analog value converting it to the specified range.

1-10

SmartAXIS Hardware Manual

1 FT2J

1.5

1Specifications

Safety Standards

UL61010-1, UL61010-2-201, CSA C22.2 No.61010-2-201 (c-UL), UL121201,
CSA C22.2 No.61010-1-12 (c-UL), CSA C22.2 No.213 (c-UL)

EMC Standards

IEC/EN 61131-2■ Environmental Specifications
Ambient Operating Temperature-20 to +55°C*1 (no freezing)Ambient Operating Humidity

10 to 95% RH (no condensation)

Ambient Storage Temperature-20 to +70°C (no freezing)Ambient Storage Humidity

10 to 95% RH (no condensation)

Altitude

0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport

Pollution Degree2

Corrosion Immunity

Free from corrosive gases■ Electrical Specifications
Rated Voltage

24V DCPower Consumption

17W maximum

Not using the USB1 and USB2
interfaces, the IN and OUT terminals,
and the Slot1 and Slot2 slots.
When Backlight OFF

5W maximum
3W maximum

Power Voltage Range

20.4 to 28.8V DC

Allowable Momentary Power Interruption

10 ms maximum (Power supply voltage: 24.0V DC to 28.8V DC)
5 ms maximum (Power supply voltage: 20.4V DC to 24.0V DC)

Inrush Current

40 A maximum

Dielectric Withstand Voltage

500V AC, 5 mA, 1 minute (between power and earth terminals)
500 V AC, 5 mA, 1 minute (between input and earth terminals)
2300 V AC, 5 mA, 1 minute (between relay output and earth terminals)
500 V AC, 5 mA, 1 minute (between transistor output and earth terminals)
500 V AC, 5 mA, 1 minute (between power and input terminals)
500 V AC, 5 mA, 1 minute (between power and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between power and relay output terminals)
500 V AC, 5 mA, 1 minute (between input and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between input and relay output terminals)■ Construction Specifications
Type Number

FT2J-7U22RAF-B

FT2J-7U22KAF-B, FT2J-7U22SAF-B

5 to 8.4Hz amplitude 3.5mm,
Vibration Resistance

Shock Resistance

8.4 to 150Hz acceleration 9.8m/s2
10 times on each of three mutually perpendicular axes
(IEC 61131-2)
98m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)

147m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)*1 For details about the restrictions due to the ambient operating temperature, refer to “Restrictions due to mounting
orientation” on page 1-17.

SmartAXIS Hardware Manual

1-11

Main Unit Specifications■ Applicable Standards

1 FT2J■ Function Specifications

Display

Touch PanelLCD Type*2

TFT color LCD

Display Colors

65,536

Effective Display Area

154.08 (W) × 85.92 (H) mm

Display Resolution

800 (W) × 480 (H) dots

Dot pitch

0.1926 (W) x 0.179 (H) mm

View angle

Left/Right/Top: 80°, Bottom: 60°

Brightness of LCD only

500 cd/m2

Brightness Adjustment

48 levels

Backlight

LED (white)

Backlight Life*3

Approx. 50,000 hours (The time until brightness becomes 50% of the initial value)

Switch Type

Projected Capacitive

Multiple Operations

Possible (2-point touch)User Memory

Approx. 24 MB

Backup time of the real-time clock(Ambient Operating Temperature at
25°C)

Min. 20 days*5

Backup Data

Keep by a largecapacity capacitor

Clock Data

Save to non-volatilememoryLog data, HMI Keep Relays, HMI Keep Registers, Internal Relays, Shift Registers,
Counters, Data Registers

Buzzer output

Single tone (tone length is adjustable)

Degree of Protection

Panel thickness is 1mm or more and less than 1.6mm: IP65F (IEC 60529)
Panel thickness is 1.6mm or more and 5mm or less: IP66F, IP67F (IEC 60529),
TYPE 4X (indoor use only),
TYPE 13Weight (approx.)

600g

*4

*2 Please be aware that small black and bright dots might show up on LCD Screen: it is not a failure or malfunction.
*3 The life of the LCD itself at an ambient operating temperature of 25°C. This is not a guaranteed value. The actual life
depends on the environment and conditions of use.
*4 It is a protection structure for the operating surface of HMI, which is attached to a panel. Although protection structure
suffices every test conditions, it does not guarantee to operate under all of the environmental condition.
As for IP65F/IP66F/IP67F oilproof structure, it suffices oilproof test conditions. Conditions are listed in the document thatcomes with Japanese Industrial Standard JIS C 0920.
Protection structure do not gurantee usage under long exposure to oil or usage of oil that is not prescribed in the
document. Please test/check beforehand to avoid trouble.
IP ratings are not applicable to UL certification.
*5 If the power interruption period exceeds the Backup time of the real-time clock, the error message "Initialize clock data"
will be displayed when the power is turned on, and the clock data will be initialized to 00:00:00 on January 1, 2000.

1-12

SmartAXIS Hardware Manual

1 FT2J

1■ EMC Specifications

Electrostatic Discharge

Contact: ±6kV
Air: ±8kVElectromagnetic Field

10V/m (80M to 1000MHz)
3V/m (1.4G to 2.0GHz)
3V/m (2.0G to 2.7GHz)
3V/m (2.7G to 6.0GHz)
80% AM (1kHz)

Fast Transient Burst

Power: ±2kV
Communication cable: ±1kV

Surge Immunity±500V (between +24V and 0V)±500V (between +24V and FE, 0 and FE)

Conducted Radio
Frequency Immunity

10V (Power, Communication cable) (150k to 80MHz)
80% AM (1kHz)

SmartAXIS Hardware Manual

Main Unit Specifications

Radiated Emission

Class A: 10m
40dBµV/m quasi-peak (30M to 230MHz)
47dBµV/m quasi-peak (230M to 1GHz)Class A: 3m
76dBµV/m (Peak), 56dBµV/m (AVG) (1G to 3GHz)
80dBµV/m (Peak), 60dBµV/m (AVG) (3G to 6GHz)

1-13

1 FT2J

1.6

Dimensions
Unit: mm
35.7

186.0

35.3

6.0

128.0

118.2

32.9

176.2

<Cable Attached Dimensions>
56

176.2

TOP
USB1

IN

118.2

USB2
LAN

RESET

Slot1

COM

Depending on the type of connection cable used the dimensions shown above will change.
The dimensions given here are representative values and are intended for reference only.

1-14

SmartAXIS Hardware Manual

Slot2

OUT

1 FT2JMark A<QR code>
See instr.
Manual.

1.7

Installation● Operating Environment
For designed performance and safety of the FT2J, do not install the FT2J in the following environments:• Where dust, briny air, or iron powder exist.
• Where oil or chemical splashes for a long time.
• Where space is filled with oil mist.
• Where direct sunlight falls on the FT2J.
• Where strong ultraviolet rays fall on the FT2J.
• Where corrosive or combustible gasses exist.
• Where shocks or vibrations are transmitted.
• Where condensation occurs due to rapid temperature change.
• Where high-voltage or arc-generating equipment (electromagnetic contactors or circuit protectors) exists in close
proximity.
● Ambient Temperature• Allow sufficient space for ventilation, and install the equipment away from heat sources.
• Allow at least 100mm between the FT2J and walls or other equipment.
• Do not install the FT2J where the ambient temperature exceeds the rated ambient operating temperature range.
When mounting the FT2J in such locations, provide a forced air-cooling fan or air-conditioner to keep the ambient
temperature within the rated temperature range.
• The FT2J is designed to install on a vertical plane so that natural air-cooling is provided. If you install it using anyother orientation, use forced-air cooling, or lower the ambient operating temperature.
● About Derating
The FT2J suppresses the temperature rise inside the product by reducing the backlight brightness when the ambient
operating temperature becomes high.
The relationship between the ambient operating temperature and brightness is as follows.
Brightness

USB1, USB2: Not in use
IN, OUT, Slot1, Slot2: In Use

100%

USB1, USB2: Not in use
IN, OUT: In Use
Slot1, Slot2: Not in use

10%
0%
-20℃

Ambient Operating Temperature
45℃

50℃

55℃

Brightness reduction occurs depending on the usage of the USB interface, IN, OUT, and cartridge slots.
Depending on each product the values shown above will change. The values given here are representative values areintended for reference only.

SmartAXIS Hardware Manual

1-15

1Main Unit Specifications● About the printed contents of the main unit
"Mark A" indicates that you can refer to the instruction sheet by using the QR code. For details about Conductormaterial and wire size, refer to “1.4 External Interfaces” on page 1-3 and “1.8 Wiring” on page 1-20.

1 FT2J● Installation• Make a panel cut-out on the panel with the dimensions shown below.
Unit: mm

B

A
A

118.6

B
+1.0
0

176.6

Panel Thickness+1.00

1.0 to 5.0• Use the attached mounting clips to tighten the screws evenly to mount panel: screws must be applied on total offour places with the specified torque 0.5 to 0.6N∙m.
Panel
Mounting Clip

Mounting Clip

• Mount the main unit on a rigid panel.
• Do not tighten with excessive force, otherwise the main unit may warp the display, or impair the waterproof
characteristics.
• If the mounting clips are tightened obliquely to the panel, the main unit may fall off the panel.
• When installing the main unit into a panel cut-out, make sure that the gasket is not twisted. Especially when reinstalling, take special care because any twists in the gasket will impair the waterproof characteristics. Also, if
the gasket comes off the main unit, align the convex part of the gasket with the concave part of the front case,and then insert the gasket fully into the gasket mounting groove without twisting it.
Concave part (Front case)Gasket mounting groove

Convex part (Gasket)

1-16

SmartAXIS Hardware Manual

1 FT2J

Orientation

LandscapeVerticalPortrait (Clockwise)

Ambient Operating Temperature: Output current limitation of
USB interface-20 to +45℃: 1000 mA+45 to +50℃: 500 mA+50 to +55℃: 150 mA-20 to +40℃: 1000 mA+40 to +55℃: 150 mA

Portrait (Counter Clockwise)

Landscape (Rotate 180°)-20 to +50℃: 500 mA+50 to +55℃: 150 mA

Horizontal• When installing the FT2J in a diagonal, the limitations are same as a horizontal.
• Confirm the visibility of the display in a final installation.
• When mounting in Landscape (Rotate 180 degrees) or Horizontal orientation, it is not possible to use theUSB interface with an output current that exceeds 500mA.
• Cartridge slots (Slot1, Slot2) cannot be used in the following cases.
- Orientation is in Vertical - Portrait (Clockwise) or - Portrait (Counter Clockwise) and the ambient
operating temperature is +50 to +55℃.
- Orientation is in Horizontal and the ambient operating temperature is +45 to +55℃.
• The analog I/O cartridge FC6A-PK2AW cannot be used when the orientation is in Horizontal and theambient operating temperature is +40 to +45°C.
For details about how to install the cartridge, refer to Chapter 2 “1.6 Install and remove” on page 2-5 or Chapter 2“2.6 Install and remove” on page 2-13.

SmartAXIS Hardware Manual

1-17

1Main Unit Specifications● Restrictions due to mounting orientation
The FT2J is designed to install on a vertical landscape. The ambient operating temperature and the output current of
the USB interface (total of USB1 and USB2) are limited as shown in the table below.

1 FT2J
By reducing the input voltage and input utilization (simultaneous ON ratio: a%) of I0 to I7, I10 and I11, use within
the ambient operating temperature range appropriate for the mounting orientation.
Type No.

FT2J-7U22RAF-B
Input Voltage
28.8V

Landscape

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
45℃
Ambient
OperatingTemperature
40℃

24.0V

0V
0%

60%

Ambient Operating
Input Voltage Temperature
55℃
28.8V

Input Voltage

0V

Ambient Operating
Temperature
55℃

28.8V

Portrait(Clockwise)

Ambient
OperatingTemperature
35℃

24.0V

Input utilization
80% 100% (a%)

0%

40%

60%

Input utilization
80% 100% (a%)

Ambient Operating
Temperature
50℃
Ambient Operating
Temperature
40℃

24.0V

0V
0%

20%

Input Voltage

40%

60%

Input utilization
100% (a%)

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
50℃

28.8V

Portrait(Counter
Clockwise)

Ambient Operating
Temperature
35℃
24.0V

0V
0%

20%

40%

28.8V

Ambient Operating
Temperature
40℃
24.0V

0V
0%

60%

Input Voltage

Ambient Operating
Temperature
55℃

28.8V

Horizontal

Input utilization
100% (a%)
Ambient Operating
Temperature
45℃
Ambient Operating
Temperature
35℃

24.0V

0V
0%

1-18

Input utilization
100% (a%)

Ambient
Operating Temperature
55℃

Input Voltage

Landscape(Rotate 180°)

60%

20%

40%

60%

SmartAXIS Hardware Manual

Ambient Operating
Temperature
50℃
Ambient
OperatingTemperature
45℃

Input utilization
100% (a%)

1 FT2J
If in compliance with UL standards, please follow the diagram below to reduce the input voltage and input usage rate
(ON state ratio: a%) accordingly.
FT2J-7U22RAF-B
Input Voltage
28.8V

FT2J-7U22KAF-B, FT2J-7U22SAF-B

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
45℃

Input Voltage
28.8V

Ambient
OperatingTemperature
40℃

Landscape

0V
0%

60%

Ambient
OperatingTemperature
35℃

Input utilization
80% 100% (a%)

Input Voltage
28.8V

Ambient Operating Ambient Operating
Temperature
Temperature
50℃
Ambient
55℃
OperatingTemperature
45℃

0V
0%

40%

60%

Input utilization
80% 100% (a%)

Ambient Operating Ambient Operating
Temperature
Temperature
55℃
50℃
Ambient Operating
Temperature
40℃

Portrait(Clockwise)

0V
0%

20%

Input Voltage

60%

Ambient Operating
Temperature
55℃

28.8V

Input utilization
100% (a%)
Ambient Operating
Temperature
50℃
Ambient Operating
Temperature
35℃

Portrait(Counter
Clockwise)

Input utilization
100% (a%)

0V
0%

20%

40%

Ambient Operating
Temperature
55℃

Input Voltage
28.8V

Ambient Operating
Temperature
40℃

Landscape(Rotate 180°)

0%

60%

Input utilization
100% (a%)

Input Voltage

Ambient Operating
Temperature
55℃

Ambient Operating
Temperature
45℃

0V

28.8V
Ambient Operating
Temperature
35℃

Horizontal

0V
0%

20%

40%

SmartAXIS Hardware Manual

Input utilization
100% (a%)

1-19Main Unit Specifications

Type No.

1

1 FT2J

1.8

Wiring• Turn off the power supply before wiring.
• Make the wiring as short as possible and run all wires as far away as possible from high-voltage and largecurrent cables. Follow all the procedures and precautions when wiring the FT2J.
• Separate the FT2J power supply wiring from the power lines of I/O devices and motor equipment.
• Ground the functional earth terminal to make sure of correct operation.
• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) circuit for power supply.
• Use Copper Conductors Only.
● Terminal Arrangement and Wiring Examples
FT2J-7U22RAF-B
Sink Input Wiring Example*1

Sink Input Wiring Example
External
power supply
24V DCͪ
2-wireSensor
ͬ

I0

I1

I2

I3

I4

I5

I6

I7

I10

External
power supply
24V DCͪͪͬͬ

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output deviceͪͬExternal
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/ͬcurrent output device
2-wire ͬͪͬSensor
ͪ
ͪ

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital / Analog IN

Digital IN

Ry. OUTPower supply terminal
ͪ

ͬ

COM
SD

SG

RDB

COM2 Q0

Q1

Q2

Q3

NC COM3 Q4

Q5

Q6

Q7

L

L

L

L

L

L

L

L

ͬ
ͪ

: Fuse*1 I12 to I15 cannot be used as source inputs.

1-20

SmartAXIS Hardware Manual

L : Load1 FT2J

1

FT2J-7U22KAF-B
Sink Input Wiring Example

External
power supply
24V DC
＋
2-wireSensor
−

I0

I1

I2

I3

I4

I5

I6

I7

I10

Main Unit Specifications

Sink Input Wiring Example*1

External
power supply
24V DC＋＋−−

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output device＋−
External
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/−current output device−
2-wire＋−Sensor
＋
＋

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital IN

Digital / Analog IN

Analog OUT

Tr. Sink OUTPower supply terminal
＋

−

COM
SD

SG

RDB

−

Q0

Q1

Q2

Q3

Q4

Q5

COM2 ＶCOM3
AQ0 AQ1(-) (+)
(-)

L

L

L

L

L

L

−
＋

＋

＋

−

Analog voltage/current input device
Analog Output Wiring Example: FuseL : Load*1 I12 to I15 cannot be used as source inputs.

SmartAXIS Hardware Manual

1-21

1 FT2JFT2J-7U22SAF-B
Sink Input Wiring Example *1

Sink Input Wiring Example
External
power supply
24V DC
＋
2-wireSensor
−

I0

I1

I2

I3

I4

I5

I6

I7

I10

External
power supply
24V DC＋＋−−

I11 COM0 I12

I13

I14

I15 COM1(-)

Analog voltage/current output device＋−
External
Analog Input Wiring Example
power supply
Source Input Wiring Example
24V DC
Analog voltage/−current output device
2-wire −＋−Sensor
＋
＋

I0

I1

I2

I3

I4

I5

I6

I7

I10

I11 COM0 I12 I13 I14 I15 COM1
(AI0) (AI1) (AI2) (AI3) (-)

Digital IN

Digital / Analog IN

Tr. Source OUTPower supply terminal＋−

Analog OUT

COM
SD

SG

RDB

−

Q0

Q1

Q2

Q3

Q4

Q5

L

L

L

L

L

L

COM2 ＶCOM3
AQ0 AQ1(-)(+) (-)

＋
−

＋

−
＋
Analog voltage/current input device
Analog Output Wiring Example: Fuse*1 I12 to I15 cannot be used as source inputs.

1-22

SmartAXIS Hardware Manual

L : Load1 FT2J

1+Power supply (24V DC)-

Power supply (0V)
Functional Earth (FE)• Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Applicable cable

AWG14 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

7 to 9 mm

Recommended ferrule

S3TL-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

AI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)● Caution when inserting and removing wires• When connecting a wire that has not been treated with a tip, such as a stranded wire, you can connect it byinserting the wire all the way in while pressing the pusher, and then releasing the pusher.
• When connecting wires with ferrules, connect the ferrules to the terminal block so that the long side is horizontal.
(See the figure below.)COM, IN, OUT
PusherPower Supply Terminal (Push button for removal)

OK

NG

OK

NG

• Do not pull out the wire without pressing the pusher. When pulling out the wire, use a flat blade screwdriver, etc.,
and pull the wire straight out while pressing the pusher with about 20 N of force.
• Be careful not to damage the push-in terminals. When pressing the pusher, do not apply more than 40N of force.

● Cautions for using the FT2J connected to a personal computer
When connecting the FT2J to a personal computer via the USB Interfaces, the FT2J or the personal computer may
break down depending on the conditions of the personal computer. Make sure of the following cautions, in order toprevent an accident.
• If the personal computer has a 3-pin power plug or power plug with a ground lead type, make sure to use a plug
socket including a ground input electrode or ground the earth lead, respectively.
• If the personal computer has a 2-pin power plug without ground lead, follow the procedure below when connect
the FT2J to the personal computer.
(1) Pull out the power plug of the personal computer from the AC outlet.
(2) Connect the FT2J to the personal computer.
(3) Insert the power plug of the personal computer into the AC outlet.

*1 Strip the sheath of the wire 7 to 9 mm from the end.
7 to 9 mm

SmartAXIS Hardware Manual

1-23

Main Unit Specifications● Power Supply Terminal• Pin assignment is shown in the following table.

1 FT2J● Recommended Tools
Tool Name
Normal type
Flat blade screwdriverWith insulated cover

Crimping tool
Stripping tool

1.9

Model Number (Order Number)

Manufacturer

SDS 0.4×2.5×75 (9009030000)

Weidmüller

S3TL-D04-25-75

IDEC

SDIS 0.4×2.5×75 (9008370000)

Weidmüller

S3TL-CR06D

IDEC

PZ6/5 (9011460000)

Weidmüller

S3TL-ST06IDEC

STRIPAX(9005000000)

Weidmüller

Maintenance and Inspection
Maintain and inspect the FT2J periodically to ensure the best performance. Do not disassemble, repair, or modify the
FT2J during inspection.
Maintenance andInspection Parts

Description

Display

Wipe any stain of the display using a soft cloth slightly dampened with neutral detergent or
alcoholic solvent. Do not use solvents such as thinner, ammonia, strong acid, and strong alkaline.

Terminals, Connectors

Check the terminals and connectors to make sure of no loose screws, incomplete insertion, ordisconnected lines.

Mounting Clips

Make sure that all mounting clips and screws are tightened sufficiently. If the mounting clips areloose, tighten the screw to the specified torque.

Backlight

The FT2J’s backlight cannot be replaced by the customer. When the backlight needs to be
replaced. Contact your vendor or IDEC Corporation.

● Maintenance Screen
When the following operation is performed during operation, the Maintenance Scree appears on the screen.
• Press the upper-left corner of the FT2J screen for three seconds or more.
If the Base Screen is switched before three seconds have elapsed, the load operation for the maintenance screen
will be canceled. Please press it again.
Press and hold3 or more seconds• Press the RESET switch on the back of the FT2J three times with a fine-tipped object.
TOP
IN

USB1

Fine-tipped object

USB2
LAN

RESET switch

RESET

COM

Slot1

Slot2

OUT

• The Maintenance Screen is not displayed in the System Mode.
• To display the maintenance screen, select the Enable Maintenance check box under the System tab in the
Project Settings dialog box. For details, refer to Chapter 4 "3.1 System Tab" in the WindO/I-NV4 User's
Manual.
• Do not touch the screen of the FT2J when operating the RESET switch.

1-24

SmartAXIS Hardware Manual

1 FT2J

1Main Unit Specifications● System ModeIn the System Mode, the FT2J can be changed to its initial settings and data can be initialized.
Press the System Mode at the top of the Maintenance Screen. The Top Page Screen appears.
Maintenance
System Mode
Device Monitor
Adjust Brightness
Ladder RUN/STOP● Adjusting the Brightness
The brightness of the FT2J display can be adjusted on the Adjust Brightness Screen.

1 Press the Adjust Brightness at the bottom of the Maintenance Screen. The Adjust Brightness Screen appears.
Maintenance
System Mode
Device Monitor
Adjust Brightness
Ladder RUN/STOP

2 Press the << and >> at the bottom the Adjust Brightness Screen to adjust the contrast to the optimal setting.
Maintenance

Adjust Brightness

3 Press the X to close the Adjust Brightness Screen.
To adjust the brightness in the System Mode, use the << and >> buttons located at the bottom of the Top
Page.

SYSTEM MODE TOP PAGE

Run

OfflineMain Menu

MAC Address 00:03:7B:20:00:77
Wired IP Address 192.168.1.150
2023/AUG/21/mon 06:46:34
SNTP

<<

EtherIP

BRIGHTNESS 31

ENG/JPN>>● Ladder RUN/STOP
Switch the ladder program between RUN and STOP by manipulating the value of the special internal relay M8000.
While the ladder program is STOP, the words “Ladder STOP” flashes at the bottom right of the screen.

1.10 Software License Information
This product contains various open source software in addition to the software owned by IDEC Corporation.
Information about open source software can be obtained from the QR code printed on the back of the FT2J.

SmartAXIS Hardware Manual

1-25

2 FT1J

2
2.1

FT1J
Packing Content
Before installing the main unit, make sure that the model you have received is what you actually ordered, and noparts are damaged to accidents during shipping.
Product Name & Dimensions

Quantity

Description

1

Main unit

2-

1

Removable terminal block 3-pin

1Removable terminal block 10-pin

1Removable terminal block 10-pin

1Removable terminal block 11-pin

2Attached to the main unit

FT1J

Mounting clips

Power supply terminal connector

Serial interface connector

Input terminal connector

Output terminal connector

Dummy cartridge

1-26

SmartAXIS Hardware Manual

2 FT1J

2.2

1Type Number
Bezel
Color

Black

4.3 inch wide
TFT Color

SilverInput Terminal Specification

Output Terminal
Specification

Type Number

Digital sink input: 6
Analog input (shared digital sink input): 2

Relay output: 4

FT1J-4F12RAG-B

Digital source input: 6
Analog input (shared digital sink input): 2

Transistor sink output: 4
Analog output: 2

FT1J-4F14KAG-B

Digital sink input: 6
Analog input (shared digital sink input): 2

Transistor source output: 4
Analog output: 2

FT1J-4F14SAG-B

Digital sink input: 6
Analog input (shared digital sink input): 2

Relay output: 4

FT1J-4F12RAG-S

Digital source input: 6
Analog input (shared digital sink input): 2

Transistor sink output: 4
Analog output: 2

FT1J-4F14KAG-S

Digital sink input: 6
Analog input (shared digital sink input): 2

Transistor source output: 4
Analog output: 2

FT1J-4F14SAG-S

SmartAXIS Hardware Manual

1-27

Main Unit SpecificationsLCD

2 FT1J

2.3

Part Names
(2)

(3)

(13)

(14)

(5)
(6)
(8)

(4)

(1)

(10)

(11)

(9)

(12)

(7)

No.

Name

Description
Normal Operation
Operating system is booting. (Normal Operation)
Operating system is booting. (Boot mode)
Preparing to boot the operating system, running in boot mode.
Main unit is damaged.
Power is off.

(1)

POWER LED

Green (lit):
Green (flash):Orange (lit):
Orange (flash):
Red (lit):
Not lit:(2)

Display

TFT color LCD(3)Touch Panel

PCAP touchscreen (Projected capacitive)(4)

Serial Interface (COM)

RS232C, RS422/485 Connector: Terminal Block 10-pin (Push-in type)
Maximum cable length: 15m (RS232C), 1200m (RS422/485)(5)

USB Interface (USB1)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(6)

USB Interface (USB2)

USB2.0 (Host) Connector: Type A Output current: 5V 500 mA(7)

Ethernet Interface (LAN)IEEE802.3u 10BASE-T/100BASE-TX Connector: RJ-45 (With Auto MDI/MDI-X function)
CAT 5 or higher, STP
Maximum cable length: 100m

(8)Power Supply Terminal

Connector (Main unit's accessories): Removable terminal block 3-pin (Push-in type)(9)

Mounting Clip Position

2 places(10) RESET Switch(11)

Input Terminal (IN)*1

Tact switch
Connector (Main unit's accessories):
Removable terminal block 10-pin (Push-in type)
Digital input (I0 to I5)
Analog input (shared digital sink input) (I12, I13)

(12) Output Terminal (OUT)*2

Connector (Main unit's accessories):
Removable terminal block 11-pin (Push-in type)
Relay Output (Q0 to Q3)
Transistor sink output (Q0 to Q3), Analog output (AQ0, AQ1)
Transistor source output (Q0 to Q3), Analog output (AQ0, AQ1)

(13) Cartridge Slot (Slot1)

Slots for connecting the following I/O cartridges. For details about the cartridges, refer to
Chapter 2 “I/O Cartridge” on page 2-1.

(14) Cartridge Slot (Slot2)

Digital I/O cartridge: FC6A-PN4, FC6A-PTK4, FC6A-PTS4
Analog I/O cartridge: FC6A-PJ2A, FC6A-PJ2CP, FC6A-PK2AV, FC6A-PK2AW*1 When using the optional terminal connector (FT9Z-XT10V), UL certification is not applicable. In addition, the tightening
torque is 1.7 lb-in (0.2 N∙m) when connecting cables.
*2 When using the optional terminal connector (FT9Z-XT11V), UL certification is not applicable. In addition, the tightening
torque is 1.7 lb-in (0.2 N∙m) when connecting cables.

1-28

SmartAXIS Hardware Manual

2 FT1J

2.4

1External Interfaces• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) when connecting a DC power

supply to the Input and Output terminals.
● Serial Interface (COM)Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Interface Specification

RS232C, RS422/485

Connector

Removable terminal block 10-pin

Applicable cable

AWG16 to 28

Conductor Type

Solid wire or Stranded wire

Wire Strip Length*1

8 to 9 mm

Recommended ferrule

S3TL-H025-12WJ
S3TL-H034-12WT
S3TL-H05-14WA
S3TL-H075-14WW(IDEC)

6

10

1

5

No.

Name

I/O

1

SD

OUT

Send Data

2

RD

IN

Receive Data

3

RS

OUT

Request to Send

4

CS

IN

Clear to Send

5

SG

-

Signal Ground

6

SDA

OUT

Send Data (+)

H0,25/12 HBL
H0,34/12 TK
H0,5/14 OR
H0,75/14 W(Weidmüller)

Function

7

SDB

OUT

Send Data (-)

8

RDA

IN

Receive Data (+)

9

RDB

IN

Receive Data (-)

10

SG

-

Signal GroundAI 0,25-8YE
AI 0,34-8TQ
AI 0,5-8WH
AI 0,75-8GY(Phoenix Contact)

Communication type

RS232C

RS422/485*1 Strip the sheath of the wire 8 to 9 mm from the end.
8 to 9 mm

SmartAXIS Hardware Manual

1-29

Main Unit Specifications• Make sure to turn off the power to the FT1J before wiring each interface.
• The serial interface (COM) can be used as the RS232C and RS422/485 interfaces at same time.
• Use the SELV (Safety Extra-Low Voltage) circuit to connect the Serial, USB and Ethernet interfaces.

2 FT1J
Using RS422/485 interface
FT1J is not equipped with terminating resistor. Insert a terminating resistor of an appropriate value (about 100 to 120
Ohm, 1/2 W minimum) between terminal number 8 (RDA) and terminal number 9 (RDB), if necessary.

Terminal Number 8 (RDA)
Terminal Number 9 (RDB)

For inserting and removing wires, refer to “2.8 Wiring” on page 1-44.
● Input Terminal (IN)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Product Name Intput terminal connector (Main unit's accessories)

Input terminal connector (Optional parts*1)

Connector

Removable terminal block 10-pin (Push-in type)

Removable terminal block 10-pin (Screw type)

Applicable
cable

AWG16 to 28

AWG14 to 28

Conductor
Type

Solid wire or Stranded wire

Wire Strip

8 to 9 mm

Length*2

6 to 7 mm

S3TL-H025-12WJ H0,25/12 HBL AI 0,25-8YE
S3TL-H025-12WJ H0,25/12 HBL AI 0,25-8YE
S3TL-H034-12WT H0,34/12 TK AI 0,34-8TQ
Recommended
S3TL-H034-12WT H0,34/12 TK AI 0,34-8TQ
S3TL-H05-14WA H0,5/14 OR
AI 0,5-8WH
ferruleS3TL-H05-14WA H0,5/14 OR
AI 0,5-8WH
S3TL-H075-14WW H0,75/14 W AI 0,75-8GY(IDEC)(Weidmüller) (Phoenix Contact)(IDEC)(Weidmüller) (Phoenix Contact)
Input Points

8

Rated Input
Voltage

24V DC

Input Voltage
Range

0 to 28.8V DC*1 FT9Z-XT10V (Right angle type)*2 Strip the sheath of the wire from the end.
Wire Strip Length

1-30

SmartAXIS Hardware Manual

2 FT1J

1Digital Input
FT1J-4F12RAG-*, FT1J-4F14SAG-*

FT1J-4F14KAG-*

Input Circuit TypeSink input

Source input

Input Points(Terminal Number)

6 points in 1 common line
(I0 to I5 / Power supply(-) terminal)

6 points in 1 common line
(I0 to I5 / Power supply(+) terminal)

Rated Input Current

I0 to I5

4.6 mA/point

5.2 mA/point

Input Impedance

I0 to I5

5.2 kΩ

4.7 kΩ

Input Delay Turn ON Time I0 to I5
TimeTurn OFF Time I0 to I5
Isolation

25 μs maximum + software filter setting
25 μs maximum + software filter setting

Between Input Terminal andInternal Circuit

Not isolated

Between Input Terminals

Not isolated

Input TypeType1 (IEC 61131-2)

External Load for I/O Interconnection

Not isolated

Signal Determination Method

StaticCable Length in compliance withelectromagnetic immunity

3m■ Operating Ranges
Sink Input (I0 to I5)

Source Input (I0 to I5)
Voltage

Voltage28.8 V28.8 VON Area

ON Area
24 V

24 V

15 V

15 V

Transition
Area

Transition
Area
5V

5V

OFF Area

OFF AreaCurrent

Current
2.9 mA

1.0 mA

4.6 mA-5.2 mA -6.2 mA-3.0 mA-1.0 mA

5.6 mA■ Input Equivalent Circuit
Source Input (I0 to I5)
24V DC

4.3kΩ
0.9kΩ

Internal Circuit

Input

24V DC

24V DC

4.7kΩ
Input

0V

47kΩ
10kΩ

Internal Circuit

Sink Input (I0 to I5)0V

SmartAXIS Hardware Manual

1-31

Main Unit Specifications

Type Number

2 FT1J
Analog Input (shared digital sink input)
Input Electrical Characteristic*1

Voltage

Input Points(Terminal Number/Common Line Name)

1 points in 1 common line
(I12, I13/COM0(-) terminal, COM1(-) terminal)

Input Range

0 to 10V DC

4 to 20 mA

Input Impedance

78kΩ

250kΩ

Digital Resolution

4096 (12 bit)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

AD Conversion

Input Error

Optional range*2: -32768 to 32767
Sampling time

5 msec max.

Sample Repetition Time

5 msec max.

Total Input Delay Time

6 msec + 1 scan time

Type of Input

Single-ended

Operation Mode

Self-scan

Conversion Method

SAR

Maximum Error at 25°C

±3.0% of full scale

Temperature Coefficient±0.04% of full scale/°C

Maximum Error±5.0% of full scale

Status Display

Noise Resistance

Device Monitor screen (LCD display)
Maximum Temporary Deviation during
Electrical Noise Tests±5.0% of full scale

Input Filter

Yes

Recommended Cable for Noise
Immunity

Shielded cable

Calibration to Maintain Rated Accuracy

Not possible

Maximum Permanent Allowed Overload (No Damage)

28.8V DC

Overload Status (Outside Input Range) Detection

Detectable

Isolation

Used as Digital Input

Between Input Terminal and Internal
Circuit

Not isolated

Between Input Terminals

Not isolated

Digital Input Type— (IEC 61131-2 digital input type is not supported)

Input Threshold

ON voltage: 15V min.

ON current: 0.20 mA min.

OFF voltage: 5V max.

OFF current: 0.06 mA max.

*1 Can be set by application software.
*2 This function is used the analog value converting it to the specified range.

1-32

Current

SmartAXIS Hardware Manual

2 FT1J

1■ Operating Ranges

Main Unit Specifications

I12, I13
Voltage28.8 VON Area
24 V

15 V

Transition
Area
5V

OFF AreaCurrent
0.06mA

0.2mA

0.3mA

0.37mA■ Input Equivalent Circuit
I12, I13

56kΩ
Input circuit
120kΩ
22kΩ

130kΩ

0V

Internal Circuit

24V DC

0V

Pulse Intput
The maximum input frequency varies based on the input terminal and function.
Input Terminal

I0

I1

I2

I3

I4

I5

Adding counter

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzUp/down selection reversible
counter

20 kHz

-

-

-

-

-

Dual-pulse reversible counter

20 kHz

20 kHz----2-edge count

10 kHz

10 kHz----4-edge count

5 kHz

5 kHz

-

-

-

-

Catch input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHzInterrupt input

20 kHz-

20 kHz

20 kHz

20 kHz

20 kHz--

20 kHz

20 kHz

20 kHz-High-speed counter
Function*1

Frequency measurement*1 Can be set by application software.

SmartAXIS Hardware Manual

1-33

2 FT1J● Output Terminal (OUT)
Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Product Name Output terminal connector (Main unit's accessories)

Output terminal connector (Optional parts*1)

Connector

Removable terminal block 11-pin (Push-in type)

Removable terminal block 11-pin (Screw type)

Applicable
cable

AWG16 to 28

AWG14 to 28

Conductor
Type

Solid wire or Stranded wire

Wire Strip

8 to 9 mm

Length*2

6 to 7 mm

S3TL-H025-12WJ H0,25/12 HBL AI 0,25-8YE
S3TL-H025-12WJ H0,25/12 HBL AI 0,25-8YE
S3TL-H034-12WT H0,34/12 TK AI 0,34-8TQ
Recommended
S3TL-H034-12WT H0,34/12 TK AI 0,34-8TQ
S3TL-H05-14WA H0,5/14 OR
AI 0,5-8WH
ferruleS3TL-H05-14WA H0,5/14 OR
AI 0,5-8WH
S3TL-H075-14WW H0,75/14 W AI 0,75-8GY(IDEC)(Weidmüller) (Phoenix Contact)(IDEC)(Weidmüller) (Phoenix Contact)

Relay Output
Type Number

FT1J-4F12RAG-*

Output Points (Terminal Number)

4 (Q0 to Q3)

Output Type1a contact

Maximum Load Current

1

2 A max.

1 common line

2 A max.

Minimum Switching Load

1 mA, 5V DC (reference value)

Initial Contact Resistance

30 mΩ max.

Electrical Life

100,000 operations min.
(rated resistive load 1,800 operations/hour)

Mechanical Life

20,000,000 operations min. (no load 18,000 operations/hour)

Rated Load
Withstand Voltage

240V AC 2 A, 30V DC 2 A
Between Output Terminal andInternal Circuit

2,300V AC 5 mA, 1 minuteBetween Output Terminals (COMs)
Status Display

Device Monitor screen (LCD display)

When the output voltage of FT1J-4F12RAG-* exceeds 200V AC, use adjacent COMs with a single powersource.
Output Delay
ON

Input to Relay
OFF

ON

Output Relay StatusOFF

OFF Bounce: 1 ms maximum
OFF Delay: 10 ms maximum
ON Bounce: 1 ms maximum
ON Delay: 10 ms maximum*1 FT9Z-XT11V (Right angle type)*2 Strip the sheath of the wire from the end.
Wire Strip Length

1-34

SmartAXIS Hardware Manual

2 FT1J

1Transistor Output
FT1J-4F14KAG-*

FT1J-4F14SAG-*

Output Circuit TypeSink output

Source output

Output Points

4 (Q0 to Q3)

Rated Load Voltage

24V DCOperating Input Voltage Range

20.4 to 28.8 DC

Maximum Load Current

1

0.5 A

1 common line

2A

Voltage Drop (ON Voltage)

1V max. (Voltage between COM and output terminal when ON)

Maximum Inrush Current

1 A max.

Leakage Current

0.1 mA max.

Main Unit Specifications

Type Number

L/R=10 ms (28.8V DC, 1 Hz)

Inductive Load

100 mA max., 24V DC

External Current Draw

V(+) terminal supply power

Isolation

Photocoupler isolated

Status Display

Device Monitor screen (LCD display)COM2(+) terminal supply power■ Output Equivalent Circuit
FT1J-4F14KAG-*

FT1J-4F14SAG-*
COM2(+)

OutputInternal Circuit

Internal Circuit

V(+)

COM2(-)

SmartAXIS Hardware Manual

OutputV(-)

1-35

2 FT1J
Analog Output
Type Number

FT1J-4F14*AG-*

Output Electrical Characteristic*1

Voltage

Output Points (Terminal Number/Common Line Name)

1 / 1 common line
(AQ0, AQ1/COM3(-) terminal, COM4(-) terminal)

Output Range

0 to 10V DC

4 to 20 mA DC

Impedance

2 kΩ or higher

500 Ω or lower

Load Type

Resistive load

Scan Time

1 scanSettling time

1 ms or lower

Total Output System Transfer Time

1 ms + 1 scan time

Maximum Error at 25°C

±0.3% of full scale

Temperature Coefficient±0.02% of full scale/℃

Reproducibility after Stabilization Time

±0.4% of full scale

Non-linearity±0.01% of full scale

Output Ripple

30 mV maximum

Overshoot0%*2

Maximum Error±1.0% of full scale

Digital Resolution

4,096 (12 bits)

Data TypeCan be set for each channel.
Binary data: 0 to 4095

Monotonicity

Yes

Current Loop OpenNot detectable

Maximum Temporary Deviation during
Electrical Noise Tests±5.0% or less of full scale

Recommended Cable for Noise Immunity

Shielded cable

Output LoadDA Conversion

Output Error

Data

Noise Resistance

Current

Optional range*3: -32768 to 32767

Effect of Improper Output Connection

No damageCalibration to Maintain Rated Accuracy

Not possible■ Output Equivalent Circuit+

Analog Signal
Analog Output
Element–

Switching Signal

Pulse Output
Type Number

FT1J-4F14*AG-*

Output Points

4 (Q0 to Q3)

Maximum output pulse frequency

20kHz

PWM output

Duty cycle: 0.1 to 100.0 (increments of 0.1%)
Output pulse frequency: 30 to 1000 (increments of 1Hz)
When the pulse OFF time is shorter than 25μs, the pulse ON ratio is adjusted so that
the OFF time is 25us and output the signal.
When the pulse ON time is shorter than 25μs, the pulse OFF ratio is adjusted so that
the ON time is 25us and output the signal.

*1 Can be set by application software.
*2 Overshoot may occur at light loads. The occurrence of overshoot can be controlled by inserting damping resistance into
the circuit. A general guide for the damping resistance value is about 150 Ω including the input line impedance for thedestination.
*3 This function is used the analog value converting it to the specified range.

1-36

SmartAXIS Hardware Manual

2 FT1J

2.5

1Specifications

Safety Standards

UL61010-1, UL61010-2-201, CSA C22.2 No.61010-2-201 (c-UL), UL121201,
CSA C22.2 No.61010-1-12 (c-UL), CSA C22.2 No.213 (c-UL)

EMC Standards

IEC/EN 61131-2■ Environmental Specifications
Ambient Operating Temperature-20 to +55°C*1 (no freezing)Ambient Operating Humidity

10 to 95% RH (no condensation)

Ambient Storage Temperature-20 to +70°C (no freezing)Ambient Storage Humidity

10 to 95% RH (no condensation)

Altitude

0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport

Pollution Degree2

Corrosion Immunity

Free from corrosive gases■ Electrical Specifications
Type Number

FT1J-4F12RAG-*

Rated Voltage

24V DCPower Consumption

13W maximum

Not using the USB1 and USB2
interfaces, the IN and OUT terminals,
and the Slot1 and Slot2 slots.
When Backlight OFF

FT1J-4F14*AG-*

15W maximum

5W maximum
3W maximum

Power Voltage Range

20.4 to 28.8V DC

Allowable Momentary Power Interruption

10 ms maximum (Power supply voltage: 24.0V DC to 28.8V DC)
5 ms maximum (Power supply voltage: 20.4V DC to 24.0V DC)

Inrush Current

40 A maximum

Dielectric Withstand Voltage

500V AC, 5 mA, 1 minute (between power and earth terminals)
500 V AC, 5 mA, 1 minute (between input and earth terminals)
2300 V AC, 5 mA, 1 minute (between relay output and earth terminals)
500 V AC, 5 mA, 1 minute (between transistor output and earth terminals)
500 V AC, 5 mA, 1 minute (between power and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between power and relay output terminals)
500 V AC, 5 mA, 1 minute (between input and transistor output terminals)
2300 V AC, 5 mA, 1 minute (between input and relay output terminals)■ Construction Specifications
Type Number

FT1J-4F12RAG-*FT1J-4F14*AG-*

5 to 8.4Hz amplitude 3.5mm,
Vibration Resistance

Shock Resistance

8.4 to 150Hz acceleration 9.8m/s2
10 times on each of three mutually perpendicular axes
(IEC 61131-2)
98m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)

147m/s2, 11ms (3 shocks on each of
three mutually perpendicular axes)(IEC 61131-2)*1 For details about the restrictions due to the ambient operating temperature, refer to “Restrictions due to mounting
orientation” on page 1-43.

SmartAXIS Hardware Manual

1-37

Main Unit Specifications■ Applicable Standards

2 FT1J■ Function Specifications

Display

Touch PanelLCD Type*2

TFT color LCD

Display Colors

16.77 M

Effective Display Area

95.04 (W) × 53.856 (H) mm

Display Resolution

480 (W) × 272 (H) dots

Dot pitch

0.198 (W) x 0.198 (H) mm

View angle

Top/Bottom/Left/Right: 80°

Brightness of LCD only

500 cd/m2

Brightness Adjustment

32 levels

Backlight

LED (white)

Backlight Life*3

Approx. 50,000 hours (The time until brightness becomes 50% of the initial value)

Switch Type

Projected Capacitive

Multiple Operations

Possible (2-point touch)User Memory

Approx. 24 MB

Backup time of the real-time clock(Ambient Operating Temperature at
25°C)

Typ. 20 days*5

Backup Data

Keep by a largecapacity capacitor

Clock Data

Save to non-volatilememoryLog data, HMI Keep Relays, HMI Keep Registers, Internal Relays, Shift Registers,
Counters, Data Registers

Buzzer output

Single tone (tone length is adjustable)

Degree of Protection

Panel thickness is 1mm or more and less than 1.6mm: IP65F (IEC 60529)
Panel thickness is 1.6mm or more and 5mm or less: IP66F, IP67F (IEC 60529),
TYPE 4X (indoor use only),
TYPE 13Weight (approx.)

320g

*4

*2 Please be aware that small black and bright dots might show up on LCD Screen: it is not a failure or malfunction.
*3 The life of the LCD itself at an ambient operating temperature of 25°C. This is not a guaranteed value. The actual life
depends on the environment and conditions of use.
*4 It is a protection structure for the operating surface of HMI, which is attached to a panel. Although protection structure
suffices every test conditions, it does not guarantee to operate under all of the environmental condition.
As for IP65F/IP66F/IP67F oilproof structure, it suffices oilproof test conditions. Conditions are listed in the document thatcomes with Japanese Industrial Standard JIS C 0920.
Protection structure do not gurantee usage under long exposure to oil or usage of oil that is not prescribed in the
document. Please test/check beforehand to avoid trouble.
IP ratings are not applicable to UL certification.
*5 If the power interruption period exceeds the Backup time of the real-time clock, the error message "Initialize clock data"
will be displayed when the power is turned on, and the clock data will be initialized to 00:00:00 on January 1, 2000.

1-38

SmartAXIS Hardware Manual

2 FT1J

1■ EMC Specifications

Electrostatic Discharge

Contact: ±6kV
Air: ±8kVElectromagnetic Field

10V/m (80M to 1000MHz)
3V/m (1.4G to 2.0GHz)
3V/m (2.0G to 2.7GHz)
3V/m (2.7G to 6.0GHz)
80% AM (1kHz)

Fast Transient Burst

Power: ±2kV
Communication cable: ±1kV

Surge Immunity±500V (between +24V and 0V)±500V (between +24V and FE, 0 and FE)

Conducted Radio
Frequency Immunity

10V (Power, Communication cable) (150k to 80MHz)
80% AM (1kHz)

SmartAXIS Hardware Manual

Main Unit Specifications

Radiated Emission

Class A: 10m
40dBµV/m quasi-peak (30M to 230MHz)
47dBµV/m quasi-peak (230M to 1GHz)Class A: 3m
76dBµV/m (Peak), 56dBµV/m (AVG) (1G to 3GHz)
80dBµV/m (Peak), 60dBµV/m (AVG) (3G to 6GHz)

1-39

2 FT1J

2.6

Dimensions
Unit: mm
8.7

53.5

5.4

86.5

75.5

123.8

112.8

<Cable Attached Dimensions>
112.8

46.6

75.5

61.4

Depending on the type of connection cable used the dimensions shown above will change.
The dimensions given here are representative values and are intended for reference only.

1-40

SmartAXIS Hardware Manual

2 FT1JMark A<QR code>
See instr.
Manual.

2.7

Installation● Operating Environment
For designed performance and safety of the FT1J, do not install the FT1J in the following environments:• Where dust, briny air, or iron powder exist.
• Where oil or chemical splashes for a long time.
• Where space is filled with oil mist.
• Where direct sunlight falls on the FT1J.
• Where strong ultraviolet rays fall on the FT1J.
• Where corrosive or combustible gasses exist.
• Where shocks or vibrations are transmitted.
• Where condensation occurs due to rapid temperature change.
• Where high-voltage or arc-generating equipment (electromagnetic contactors or circuit protectors) exists in close
proximity.
● Ambient Temperature• Allow sufficient space for ventilation, and install the equipment away from heat sources.
• Allow at least 100mm between the FT1J and walls or other equipment.
• Do not install the FT1J where the ambient temperature exceeds the rated ambient operating temperature range.
When mounting the FT1J in such locations, provide a forced air-cooling fan or air-conditioner to keep the ambient
temperature within the rated temperature range.
• The FT1J is designed to install on a vertical plane so that natural air-cooling is provided. If you install it using anyother orientation, use forced-air cooling, or lower the ambient operating temperature.
● About Derating
The FT1J suppresses the temperature rise inside the product by reducing the backlight brightness when the ambient
operating temperature becomes high.
The relationship between the ambient operating temperature and brightness is when installed on a vertical landscapeas follows.
Brightness
100%

FT1J-4F12RAG-*
Total of USB1 and USB2: 150mA
IN, OUT, Slot1, Slot2: In use

10%

FT1J-4F14*AG-*
Total of USB1 and USB2: 500mA
IN: In use
OUT: Analog output (AQ0, AQ1) of the main unit is not in use.
Slot1, Slot2: FC6A-PK2AW cannot be used.

0%
-20℃

Ambient Operating Temperature
50℃

55℃

Brightness reduction occurs depending on the usage of the USB interface, IN, OUT, and cartridge slots.
Depending on each product the values shown above will change. The values given here are representative values areintended for reference only.

SmartAXIS Hardware Manual

1-41

1Main Unit Specifications● About the printed contents of the main unit
"Mark A" indicates that you can refer to the instruction sheet by using the QR code. For details about Conductormaterial and wire size, refer to “2.4 External Interfaces” on page 1-29 and “2.8 Wiring” on page 1-44.

2 FT1J● Installation• Make a panel cut-out on the panel with the dimensions shown below.
Unit: mm

B

A
A

75.9

B
+1.0
0

113.2

Panel Thickness+1.00

1.0 to 5.0• Use the attached mounting clips to tighten the screws evenly to mount panel: screws must be applied on total of
two places with the specified torque 0.3 to 0.4 N∙m.
Panel
Mounting Clip

Mounting Clip

• Mount the FT1J on a rigid panel.
• Do not tighten with excessive force, otherwise the FT1J may warp the display, or impair the waterproof
characteristics.
• If the mounting clips are tightened obliquely to the panel, the FT1J may fall off the panel.
• When installing the FT1J into a panel cut-out, make sure that the gasket is not twisted. Especially when reinstalling, take special care because any twists in the gasket will impair the waterproof characteristics. Also, if
the gasket comes off the main unit, align the convex part of the gasket with the concave part of the front case,and then insert the gasket fully into the gasket mounting groove without twisting it.
Concave part (Front case)Gasket mounting groove

Convex part (Gasket)

1-42

SmartAXIS Hardware Manual

2 FT1J

Orientation

LandscapeVerticalPortrait (Clockwise)

Portrait (Counter Clockwise)

Ambient Operating Temperature: Output current limitation of
USB interface
FT1J-4F12RAG-*FT1J-4F14*AG-*-20℃ to +40℃ : 1000mA+40℃ to +45℃ : 500mA+45℃ to +55℃ : 150mA-20℃ to +40℃ : 1000mA+40℃ to +55℃ : 500mA-20℃ to +40℃ : 1000mA+40℃ to +45℃ : 500mA+45℃ to +50℃ : 150mA+50℃ to +55℃ : 0mA-20℃ to +40℃ : 1000mA+40℃ to +50℃ : 500mA+50℃ to +55℃ : 150mA-20℃ to +40℃ : 1000mA+40℃ to +45℃ : 500mA+45℃ to +55℃ : 150mA-20℃ to +40℃ : 1000mA+40℃ to +55℃ : 500mA-20℃ to +40℃ : 1000mA+40℃ to +45℃ : 500mA+45℃ to +50℃ : 150mA+50℃ to +55℃ : 0mA-20℃ to +40℃ : 1000mA+40℃ to +50℃ : 500mA+50℃ to +55℃ : 150mA

Landscape (Rotate 180°)

Horizontal• When installing the FT1J in a diagonal, the limitations are same as a horizontal.
• Confirm the visibility of the display in a final installation.
• Depending on the ambient operating temperature, the following parts cannot be used with the FT1J4F14*AG-*.
45℃ or higher: Analog I/O cartridge FC6A-PK2AW in cartridge slots (Slot1, Slot2)
50℃ or higher: Analog output (AQ0, AQ1) of output terminal (OUT)
For details about how to install the cartridge, refer to Chapter 2 “1.6 Install and remove” on page 2-5 or Chapter 2“2.6 Install and remove” on page 2-13.

SmartAXIS Hardware Manual

1-43

1Main Unit Specifications● Restrictions due to mounting orientation
The FT1J is designed to install on a vertical landscape. The ambient operating temperature and the output current of
the USB interface (total of USB1 and USB2) are limited as shown in the table below.

2 FT1J

2.8

Wiring• Turn off the power supply before wiring.
• Make the wiring as short as possible and run all wires as far away as possible from high-voltage and largecurrent cables. Follow all the procedures and precautions when wiring the FT1J.
• Separate the FT1J power supply wiring from the power lines of I/O devices and motor equipment.
• Ground the functional earth terminal to make sure of correct operation.
• Use the SELV (Safety Extra-Low Voltage) circuit and LIM (Limited Energy) circuit for power supply.
• Use Copper Conductors Only.
● Terminal Arrangement and Wiring Examples
FT1J-4F12RAG-B, FT1J-4F12RAG-S-

Power supply terminal

+

-

+

Digital IN

I0

I1

I2

I3

Digital / Analog IN

I42-wireSensor+I5(AI0) COM0 (AI1) COM1
I12 (-) I13 (-)+

Ry. OUT

Q0 COM2 NC

Q1 COM3 NC

Q2 COM4 NC

Q3 COM5

L

L

L

L

: FuseL : Load-

Analog voltage/current output
deviceAnalog Output Wiring Example

1-44

SmartAXIS Hardware Manual

2 FT1J

1

FT1J-4F14KAG-B, FT1J-4F14KAG-S

I0

I1

Main Unit Specifications-

Power supply terminal

+

-

+

Digital IN

I2

Tr. Sink OUT

Digital / Analog IN

I3I4(AI0) COM0 (AI1) COM1
I12 (-) I13 (-)

I5

+

+

2-wireSensor
-

Q0

Q1

Q2

Q3

L

L

L

L

COM2 Ｖ(-) (+)

Analog OUT
COM3
COM4
NC AQ0 (-) AQ1 (-)

- +

+

-

-

Analog voltage/current input
device+Analog voltage/current output
device-Analog voltage/current input
deviceAnalog Output Wiring Example

Analog Input Wiring Example: FuseL : Load

FT1J-4F14SAG-B, FT1J-4F14SAG-S-

Power supply terminal

+

-

+

Digital IN

I0

I1

I2

I3

Digital / Analog IN

I4I5

2-wireSensor+(AI0) COM0 (AI1) COM1
I12 (-) I13 (-)+

Tr. Source OUT

Q0

Q1

Q2

Q3

L

L

L

L

COM2 Ｖ(+) (-)

Analog OUT
COM3
COM4
NC AQ0 (-) AQ1 (-)+-

Analog voltage/current output
deviceAnalog Output Wiring Example- +-アナログ電圧/
Analogvoltage/
電流入力機器
current input
device+-Analog voltage/current input
deviceAnalog Input Wiring Example: FuseSmartAXIS Hardware Manual

L : Load

1-45

2 FT1J● Power Supply Terminal• Pin assignment is shown in the following table.

+

Power supply (24V DC)-

Power supply (0V)
Functional Earth (FE)• Use applicable cables for wiring and recommended ferrules (made by IDEC, Weidmüller or Phoenix Contact) as
follows.
Product NamePower supply terminal connector(Main unit's accessories)

Connector

Removable terminal block 3-pin (Push-in type)

Applicable
cable

AWG12 to 24

Conductor
Type

Solid wire or Stranded wire

Wire Strip
Length*2(Optional parts*1)

AWG12 to 26

10 to 11 mm

S3TL-H025-12WJ
S3TL-H034-12WT
Recommended
S3TL-H05-14WA
ferruleS3TL-H075-14WW(IDEC)

Power supply terminal connector

12 to 13 mm
S3TL-H025-12WJ H0,25/12 HBL AI 0,25-8YE
H0,25/12 HBL AI 0,25-8YE
S3TL-H034-12WT H0,34/12 TK AI 0,34-8TQ
H0,34/12 TK AI 0,34-8TQ
S3TL-H05-14WA H0,5/14 OR AI 0,5-8WH
AI 0,5-8WH
H0,5/14 OR
S3TL-H075-14WW H0,75/14 W AI 0,75-8GY
H0,75/14 W AI 0,75-8GY(Weidmüller) (Phoenix Contact)(Weidmüller) (Phoenix Contact) (IDEC)● Caution when inserting and removing wires• When connecting a wire that has not been treated with a tip, such as a stranded wire, you can connect it byinserting the wire all the way in while pressing the pusher, and then releasing the pusher.
• When connecting wires with ferrules, connect the ferrules to the terminal block so that the long side is horizontal.
(See the figure below.)
Power Supply Terminal, COM, IN, OUT
Pusher(Push button for removal)

OK

NG• Do not pull out the wire without pressing the pusher. When pulling out the wire, use a flat blade screwdriver, etc.,
and pull the wire straight out while pressing the pusher with about 20 N of force.
• Be careful not to damage the push-in terminals. When pressing the pusher, do not apply more than 40N of force.

*1 FT9Z-1X03V (Right angle type)*2 Strip the sheath of the wire from the end.
Wire Strip Length

1-46

SmartAXIS Hardware Manual

2 FT1J● Recommended Tools
Tool Name
Normal type
Flat blade screwdriverWith insulated cover

Crimping tool

Stripping tool

2.9

Model Number (Order Number)

Manufacturer

SDS 0.4×2.5×75 (9009030000)

Weidmüller

S3TL-D04-25-75

IDEC

SDIS 0.4×2.5×75 (9008370000)

Weidmüller

S3TL-CR04TS3TL-CR06D

IDEC

PZ6/5 (9011460000)

Weidmüller

S3TL-ST06IDEC

STRIPAX(9005000000)

Weidmüller

Maintenance and Inspection
Maintain and inspect the FT1J periodically to ensure the best performance. Do not disassemble, repair, or modify the
FT1J during inspection.
Maintenance andInspection Parts

Description

Display

Wipe any stain of the display using a soft cloth slightly dampened with neutral detergent or
alcoholic solvent. Do not use solvents such as thinner, ammonia, strong acid, and strong alkaline.

Terminals, Connectors

Check the terminals and connectors to make sure of no loose screws, incomplete insertion, ordisconnected lines.

Mounting Clips

Make sure that all mounting clips and screws are tightened sufficiently. If the mounting clips areloose, tighten the screw to the specified torque.

Backlight

The FT1J’s backlight cannot be replaced by the customer. When the backlight needs to be
replaced. Contact your vendor or IDEC Corporation.

SmartAXIS Hardware Manual

1-47

1Main Unit Specifications● Cautions for using the FT1J connected to a personal computer
When connecting the FT1J to a personal computer via the USB Interfaces, the FT1J or the personal computer may
break down depending on the conditions of the personal computer. Make sure of the following cautions, in order toprevent an accident.
• If the personal computer has a 3-pin power plug or power plug with a ground lead type, make sure to use a plug
socket including a ground input electrode or ground the earth lead, respectively.
• If the personal computer has a 2-pin power plug without ground lead, follow the procedure below when connect
the FT1J to the personal computer.
(1) Pull out the power plug of the personal computer from the AC outlet.
(2) Connect the FT1J to the personal computer.
(3) Insert the power plug of the personal computer into the AC outlet.

2 FT1J● Maintenance Screen
When the following operation is performed during operation, the Maintenance Screen appears on the screen.
• Press the upper-left corner of the FT1J screen for three seconds or more.
If the Base Screen is switched before three seconds have elapsed, the load operation for the maintenance screen
will be canceled. Please press it again.
Press and hold3 or more seconds• Press the RESET switch on the back of the FT1J three times with a fine-tipped object.

Fine-tipped object
RESET switch• The Maintenance Screen is not displayed in the System Mode.
• To display the maintenance screen, select the Enable Maintenance check box under the System tab in the
Project Settings dialog box. For details, refer to Chapter 4 "3.1 System Tab" in the WindO/I-NV4 User's
Manual.
• Do not touch the screen of the FT1J when operating the RESET switch.
● System ModeIn the System Mode, the FT1J can be changed to its initial settings and data can be initialized.
Press the System Mode at the top of the Maintenance Screen. The Top Page Screen appears.
Maintenance
System Mode
Device Monitor
Adjust Brightness
Ladder RUN/STOP

1-48

SmartAXIS Hardware Manual

2 FT1J

1

1 Press the Adjust Brightness at the bottom of the Maintenance Screen. The Adjust Brightness Screen appears.
Maintenance
System Mode
Device Monitor
Adjust Brightness
Ladder RUN/STOP

2 Press the << and >> at the bottom the Adjust Brightness Screen to adjust the contrast to the optimal setting.
Maintenance

Adjust Brightness

3 Press the X to close the Adjust Brightness Screen.
To adjust the brightness in the System Mode, use the << and >> buttons located at the bottom of the Top
Page.
SYSTEM MODE TOP PAGE

Run

OfflineMain Menu

MAC Address 00:03:7B:20:00:77
Wired IP Address 192.168.1.150

2023/AUG/21/mon 06:46:34

SNTP
<<

EtherIP

ENG/JPN
BRIGHTNESS 31>>● Ladder RUN/STOP
Switch the ladder program between RUN and STOP by manipulating the value of the special internal relay M8000.
While the ladder program is STOP, the words “Ladder STOP” flashes at the bottom right of the screen.

2.10 Software License Information
This product contains various open source software in addition to the software owned by IDEC Corporation.
Information about open source software can be obtained from the QR code printed on the back of the FT1J.

SmartAXIS Hardware Manual

1-49

Main Unit Specifications● Adjusting the Brightness
The brightness of the FT1J display can be adjusted on the Adjust Brightness Screen.

2 FT1J

1-50

SmartAXIS Hardware ManualChapter 2
1

I/O Cartridge
2

Digital I/O Cartridge

I/O Cartridge

Digital I/O cartridges are used to expand the digital inputs or digital outputs.
To use a digital I/O cartridge, it must be configured in the Module Configuration Editor. For the configuration
procedure, refer to Chapter 4 “Module Configuration Editor” on page 4-1.

1.1

Packing Content
Before installing the FT2J/1J, make sure that the model you have received is what you actually ordered, and no parts
are damaged to accidents during shipping.
Product Name & Dimensions

Quantity

Description

1

Cartridge

1Japanese, English

Digital I/O cartridge

Instruction Sheet

1.2

Type Number
Cartridge Type

1.3

I/O Points

Digital Input

Input: 4

Digital Output

Output: 4

Type

Type Number

DC input (shared sink/source)

FC6A-PN4Transistor sink output

FC6A-PTK4

Transistor source output

FC6A-PTS4

Part Names

(2)

(1)

No.

Name

(1)

Description(1)

Terminals

These terminals connect the cartridge to the power supply and to input or output devices.

(2)

Connector

This connector connects the cartridge to Cartridge Slot of the FT2J/1J.

SmartAXIS Hardware Manual

2-1

1 Digital I/O Cartridge

1.4

Specifications■ Environmental Specifications
Type Number

FC6A-PN4

FC6A-PTK4

Ambient Operating Temperature-10 to +55°C (no freezing)Ambient Operating Humidity

10 to 95% RH (no condensation)

Ambient Storage Temperature-25 to +70°C (no freezing)Ambient Storage Humidity

10 to 95% RH (no condensation)

Altitude

0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport

PC6A-PTS4■ Construction Specifications
Type Number

FC6A-PN4

FC6A-PTK4

PC6A-PTS4

5 to 8.4 Hz half amplitude 3.5 mm,

Vibration Resistance

8.4 to 150 Hz, acceleration 9.8 m/s2 (1 G),
each direction XYZ, 2 hours

Shock Resistance

147 m/s2 (15 G), 11 ms, XYZ, 3 axes, 6 directions, 3 times each

■ Function Specifications
Type Number

FC6A-PN4

FC6A-PTK4

Rated Voltage

5.0 V, 3.3 V (supplied from main unit)

Current Draw

5.0 V: 0 mA
3.3 V: 35 mA

Weight

15 g

PC6A-PTS4■ Digital Input Specifications
Type Number

FC6A-PN4

Rated Input Voltage

12/24V DC (shared sink/source)

Operating Input Voltage Range

0 to 28.8V DC

Rated Input Current

5 mA/1 point (when 24V DC)
2.5 mA/1 point (when 12V DC)

Terminal Arrangement

Refer to “Terminal Arrangement and Wiring Examples” on page 2-6.

Input Impedance

4.4 kΩ

Input Delay Time (24V DC)

2-2

Turn ON Time

0.5 msTurn OFF Time

0.5 ms

Input TypeType 1 (IEC 61131-2)

External Load for I/O Interconnection

Not isolated

Signal Determination Method

StaticEffect of Improper Input Connection

No damage
However, if high voltage is applied that exceeds the operating input
voltage range, there is a risk of permanent damage.

Cable Length in compliance withelectromagnetic immunity

3m

SmartAXIS Hardware Manual

1 Digital I/O Cartridge
Operating Ranges
The operating range of Type 1 (IEC 61131-2) DC input modules is as follows.

2

Voltage (V DC)

I/O Cartridge

28.8 V

24 V

ON Area

8.5 V

Transition Area
5V

OFF AreaCurrent (mA)
5.3 mA 6.4 mA

0.9 mA 1.7 mA

Input Equivalent Circuit
FC6A-PN4

COM

4.3KΩ

Internal Circuit

Input

SmartAXIS Hardware Manual

2-3

1 Digital I/O Cartridge■ Digital Output Specifications
Type Number

FC6A-PTK4

FC6A-PTS4

Output Circuit TypeTransistor sink output

Transistor source output

Output Points

4 (4 points in 1 common line)

Rated Load Voltage

12/24V DC

Operating Input Voltage Range

10.2 to 28.8V DC

Rated Load

0.1 A/1 point

Terminal Arrangement

Refer to “Terminal Arrangement and Wiring Examples” on page 2-6.

Voltage Drop (ON Voltage)

0.4 V or less, voltage between COM and output terminal when ON

Allowed Inrush Current

1 A maximum

Leakage Current

0.1 mA maximum

Clamping Voltage

50 V

Lamp Load

2.4 W maximum

Inductive Load

L/R = 10 ms (28.8V DC, 1 Hz)

Protection Operation

None

External Current Draw

100 mA maximum, 24V DC (+V terminal supply power)

Output Delay Time
(24V DC)

Turn ON Time450 μs maximum

Turn OFF Time450 μs maximum

Output Equivalent Circuit
FC6A-PTK4

FC6A-PTS4
COM（+）

OutputInternal Circuit

Internal Circuit

V
（+）

COM
（-）

2-4

SmartAXIS Hardware Manual

OutputV（-）

1 Digital I/O Cartridge

1.5

Dimensions
Unit: mm

44.6

I/O Cartridge

12.5

34.8

1.6

17.8

Install and remove

1 Insert two flathead screwdrivers into the screwdriver insertion slots in both locations of the main unit, and while
pushing the tabs of the dummy cartridge, remove the dummy cartridge straight off of the main unit.
Screwdriver insertion slot

Dummy cartridge

2

Screwdriverinsertion slot

2 Pay careful attention to the direction of the cartridge and attach it directly onto the main unit.

Cartridge

To remove the cartridge, perform the work detailed in step 1.
• Always install and remove the cartridges when the power is turned off.
• Attach the cartridge directly onto the unit. If the cartridge is attached when tilted, it may be damaged orcause communication problems.
• When not using cartridge, attach the dummy cartridge.

SmartAXIS Hardware Manual

2-5

1 Digital I/O Cartridge

1.7

Wiring• When connecting cables to the cartridges, the tightening torque is 0.2 N m.
• Insert a fuse that corresponds to the load.

● Terminal Arrangement and Wiring Examples
Digital Input
FC6A-PN4
L Load

+

PNP

+
−

10.2 to 28.8V DC−

2-wireSensor

+
−

−

NPN

2-wireSensor

+10.2 to 28.8V DCFuseDigital Output

L
−
+

2-6

L

L

L Load

L LoadFuseFuseL

L+−

SmartAXIS Hardware Manual

DC10.2 to 28.8V

L

FC6A-PTS4

DC10.2 to 28.8V

FC6A-PTK4L

L

2 Analog I/O Cartridge

2

Analog I/O Cartridge

2

Analog I/O cartridges are used to expand the analog inputs or analog outputs.

To use an analog I/O cartridge, it must be configured in the Module Configuration Editor. For the configuration
procedure, refer to Chapter 4 “Module Configuration Editor” on page 4-1 and Chapter 4 “4.2 Parameter Settings” onpage 4-7.

2.1

Packing Content
Before installing the FT2J/1J, make sure that the model you have received is what you actually ordered, and no parts
are damaged to accidents during shipping.
Product Name & Dimensions

Quantity

Description

1

Cartridge

1Japanese, English

Analog I/O Cartridge

Instruction Sheet

2.2

Type Number
Cartridge TypeI/O Points

Signal Type
Voltage input: 0 to 10 V
Current input: 0 to 20 mA, 4 to 20 mA

Analog input

Input: 2

Thermocouple input: K type, J type, R type, S type, B type,
E type, T type, N type, C typeType Number
FC6A-PJ2A

FC6A-PJ2CP

Resistance thermometer input: Pt100, Pt1000, Ni100, Ni1000
Analog output

Output: 2

Voltage output: 0 to 10 V

FC6A-PK2AV

Current output: 4 to 20 mA

FC6A-PK2AW

SmartAXIS Hardware Manual

2-7

I/O Cartridge

The analog data and analog status of the analog I/O cartridge is stored in special data registers. For details, refer to
Chapter 4 “Data” on page 4-9.

2 Analog I/O Cartridge

2.3

Part Names

(2)

(1)

No.

(1)

Name

Description(1)

Terminals

These terminals connect the cartridge to the power supply and to input or output devices.

(2)

Connector

This connector connects the cartridge to Cartridge Slot of the FT2J/1J.

● Description Location of Version Number
The analog I/O cartridge version number is printed on the side of the analog I/O cartridge in the location in thefollowing diagram.

LOT
No
MADE .14XS1
IN JA 2525
V100
PAN

LOT No.xxxxxxxxx
MADE IN JAPAN
V100

Version Number

2-8

SmartAXIS Hardware Manual

2 Analog I/O Cartridge

2.4

Specifications

2■ Environmental Specifications
FC6A-PJ2A

FC6A-PJ2CP

FC6A-PK2AV

Ambient Operating Temperature-10 to +55°C (no freezing)Ambient Operating Humidity

10 to 95% RH (no condensation)

Ambient Storage Temperature-25 to +70°C (no freezing)Ambient Storage Humidity

10 to 95% RH (no condensation)

Altitude

0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport

FC6A-PK2AWI/O Cartridge

Type Number■ Construction Specifications
Type Number

FC6A-PJ2A

FC6A-PJ2CP

FC6A-PK2AV

FC6A-PK2AW

5 to 8.4 Hz half amplitude 3.5 mm,

Vibration Resistance

8.4 to 150 Hz, acceleration 9.8 m/s2 (1 G),
each direction XYZ, 2 hours

Shock Resistance

147 m/s2 (15 G), 11 ms, XYZ, 3 axes, 6 directions, 3 times each

■ Function Specifications
Type Number

FC6A-PJ2A

FC6A-PJ2CP

Rated Voltage

5.0 V, 3.3 V (supplied from main unit)

Current Draw

5.0 V: 3.3 V: 30 mA

Weight15 g

SmartAXIS Hardware Manual

FC6A-PK2AV

FC6A-PK2AW

5.0 V: 70 mA
3.3 V: 30 mA

5.0 V: 185 mA
3.3 V: 30 mA

2-9

2 Analog I/O Cartridge■ Analog Input Specifications
Type Number

FC6A-PJ2A

Input Electrical Characteristic*1

Voltage

FC6A-PJ2CP
Current

Thermocouple

Resistancethermometer

4 to 20 mA
0 to 20 mA

K type: -200 to +1300 °C(-328 to +2372 °F)
J type: -200 to +1000 °C(-328 to +1832 °F)
R type: 0 to 1760 °C(32 to 3200 °F)
S type: 0 to 1760 °C(32 to 3200 °F)
B type: 0 to 1820 °C(32 to 3308 °F)
E type: -200 to +800 °C(-328 to +1472 °F)
T type: -200 to +400 °C(-328 to +752 °F)
N type: -200 to +1300 °C(-328 to +2372 °F)
C type: 0 to 2315 °C(32 to 4199 °F)

Pt100:-200 to +850 °C(-328 to 1562 'F)
Pt1000:-200 to +600 °C(-328 to 1112 'F)
Ni100:-60 to +180 °C(-76 to 356 'F)
Ni1000:-60 to +180 °C(-76 to 356 'F)

Input Range

0 to 10 V

Input Impedance

1 mΩ min. 250 Ω max.

1 mΩ min.

Allowable Conductor Resistance

-

-

-

10 Ω max.

Input Detection Current

-

-

-

1.0 mA max.
(TYP: 0.2 mA)

Sampling time

10 ms

250 msSampling Repetition Time 20 ms

500 msTotal Input Delay Time*2
AD
Conversion Type of Input

Sampling time + Sampling repetition time + 1 scan timeSingle-ended

Signal Type

Self-scan

Conversion Method

SAR±0.1% of full scale
Cold junction compensation
accuracy ±4.0°C or less

Input Error

Maximum Error at 25°C

±0.1% of full scale

Temperature Coefficient±0.02%/°C of full scale

Exceptions
R type, S type thermocouple error:±6.0°C (0 to 200°C range only)±0.1% of full scale
B type thermocouple error:
Not guaranteed(0 to 300°C range only)
K type, J type, E type, T type,
N type thermocouple error:±0.4% FS
(0°C or lower range only)*1 Can be set by application software.
*2 The total input delay time increases in proportion to the number of channels used.

2-10

SmartAXIS Hardware Manual

2 Analog I/O Cartridge

Type Number

FC6A-PJ2A

Input Electrical Characteristic*1

Voltage

FC6A-PJ2CP
Current

Thermocouple

Resistancethermometer

K type: 15000 (14bit)
J type: 12000 (14bit)
R type: 17600 (15bit)
S type: 17600 (15bit)
B type: 18200 (15bit)
E type: 10000 (14bit)
T type: 6000 (13bit)
N type: 15000 (14bit)
C type: 23150 (15bit)

Pt100:
10500 (14bit)
Pt1000:8000 (13bit)
Ni100:
2400 (12bit)
Ni1000:2400 (12bit)

4,096 increments (12bit)

Input Value per Step

4.88 μA
2.44 mV(0 to 20 mA) 0.1°C(0 to 10 V) 3.91 μA
0.18'F(4 to 20 mA)

Data

Data Type*3

Can be set for each channel.
Binary data: 0 to 4095

Monotonicity

Yes

Input Data Out of Range

Detectable*4

Optional range*3: -32768 to 32767

Recommended cable
Noise
Resistance Crosstalk

Pair shielded cable

Isolation

None

Pair cable

1 LSB max.

Effect When Input is Incorrectly Wired No Damage
Maximum Permanent Allowed Overload(No damage)*5

13 V

40 mA

13 V

Calibration to Maintain Rated Accuracy Not possible*1 Can be set by application software.
*3 This function converts analog value within a specified range and uses it.
Example: When the digital resolution is 12 bits and the input range is -10 to +10 V, -5V input is displayed as 1024 forthe analog value. However, if the Min. is set to -1000 and the Max. is set to 1000 for Optional range, -500 istreated as an input value.

Min. value Input value-1,000-500Max. value
1,000

Analog value
0
1,024
Input voltage value -10V -5V

4,095
10V

*4 Input data out of range is reflected in the status of the analog I/O cartridge.
*5 The maximum voltage or current value that can be input without damage.

SmartAXIS Hardware Manual

2-11

I/O Cartridge

Digital Resolution22 Analog I/O Cartridge

Input Equivalent Circuit
FC6A-PJ2A

FC6A-PJ2CP＋
Voltage Input

A ＋Input Circuit−

Input Circuit

B −

GND

Current Input

Multiplexer

Multiplexer

Voltage Supply

GND

GND

＋

GND

B’

Voltage Supply■ Analog Output Specifications
Type Number

FC6A-PK2AV

FC6A-PK2AW

Output Electrical Characteristic

Voltage

Current

Output Range

0 to 10 V

4 to 20 mA

Impedance

2 kΩ or higher

500 Ω or lower

Load Type

Resistive load

DA Conversion Time

40 ms maximum

Output Update Interval

20 ms

Total Output System Transfer
Time

DA conversion time + Output Update Interval + 1 scan time

Maximum Error at 25°C

±0.3% of full scale

Temperature Coefficient±0.02%/°C of full scale

Output Ripple

30 mV max.

Overshoot0%

Digital Resolution

4,096 increments (12bit)

Output Value per Step

2.44 mV (0 to 10 V)

3.91 µA (4 to 20 mA)

Data Type in Application

0 to 4095 (0 to 10 V)

0 to 4095 (4 to 20 mA)

Monotonicity

Yes

Output Load

DA
Conversion

Output Error

Data

Current Loop Open
Noise
Resistance

20 ms maximum-

Maximum Temporary Deviation
during Electrical Noise Tests±4.0% of full scale max.

Recommended Cable

Pair shielded cable

Crosstalk

1 LSB max.

Isolation

None

Effect of Improper Output Connection

No damageCalibration to Maintain Rated Accuracy

Not possible

Output Equivalent Circuit
FC6A-PK2AV, FC6A-PK2AW+

Analog Signal
Analog Output
Element
Switching Signal

–

*

2-12

SmartAXIS Hardware ManualNot detectable2 Analog I/O Cartridge

2.5

Dimensions
Unit: mm

44.6

I/O Cartridge

12.5

34.8

2.6

17.8

Install and remove

1 Insert two flathead screwdrivers into the screwdriver insertion slots in both locations of the main unit, and while
pushing the tabs of the dummy cartridge, remove the dummy cartridge straight off of the main unit.
Screwdriver insertion slot

Dummy cartridge

2

Screwdriverinsertion slot

2 Pay careful attention to the direction of the cartridge and attach it directly onto the main unit.

Cartridge

To remove the cartridge, perform the work detailed in step 1.
• Always install and remove the cartridges when the power is turned off.
• Attach the cartridge directly onto the unit. If the cartridge is attached when tilted, it may be damaged orcause communication problems.
• When not using cartridge, attach the dummy cartridge.

SmartAXIS Hardware Manual

2-13

2 Analog I/O Cartridge

2.7

Wiring• Do not connect a thermocouple to a hazardous voltage component (60V DC or peak 42.4 V or higher
component).
Always check the wiring before turning on the power. If the wiring is incorrect, the analog I/O cartridge may bedamaged. When there is a risk of malfunction due to noise, use a shielded cable for the wiring and connect bothends of the shield to the FG.
• When connecting cables to the cartridges, the tightening torque is 0.2 N m.

● Terminal Arrangement and Wiring Examples
Analog Input
FC6A-PJ2A

FC6A-PJ2CP

IN0
+

+

IN0

IN1
+

−

+

+

−

−

IN1

A

B

B’

A

B

B’

+

−

NC

+

−

NC

+

−

0 to 10V

0 to 20mA
4 to 20mA

Analog voltage
output device

Analog current
output device

B
B’
Pt / Ni

A

Resistance thermometer−+

Thermocouple

Analog Output
FC6A-PK2AV

FC6A-PK2AW

OUT0

2-14

+

−

+

−

OUT0

OUT1
NC

+

−

+

−

NC

NC

OUT1

−

+

−

+

NC

−

+

−

+

0 to 10V

0 to 10V

4 to 20mA

4 to 20mA

Analog voltage
input device

Analog voltage
input device

Analog current
input device

Analog current
input device

SmartAXIS Hardware ManualChapter 3
1
1.1

Options

Optional items

3

FT2J
Type Number

USB Panel-Mount Extension Cable

PLC Connection Cable

Surface Protection Film*1
UV Surface Protection Film

Options

Name

Description

HG9Z-XCE11

Extension cable for attaching to USB interface (Type-A)
Length: 1m

FC2A-KP1C

Connection cable for Serial interface (COM)(Compatible models: IDEC FC5A/4A MICROSmart)
Length: 2.4m
<Connector>
Main unit: Parted wire
External device: Mini DIN 8-pin

HG9Z-XC275

Connection cable for Serial interface (COM)(Compatible models: IDEC FC5A/4A MICROSmart)
Length: 5m<Connector>
Main unit: Parted wire
External device: Mini DIN 8-pin

FC6A-KC1C

Connection cable for Serial interface (COM)(Compatible models: IDEC F6A MICROSmart FC6A-C*****E only)
Length: 5m<Connector>
Main unit: Parted wire
External device: RJ45

HG9Z-2D7PN05 5 pcs/pack*2

FT9Z-2D7PN05

5 pcs/pack*1 No UV resistant.
*2 The protective sheet is UV resistant, however, resistance against direct sunlight in outdoor usage is not guaranteed.

SmartAXIS Hardware Manual

3-1

1 Optional items

1.2

FT1J
Name

Type Number

USB Panel-Mount Extension Cable

HG9Z-XCE11

Extension cable for attaching to USB interface (Type-A)
Length: 1m

FC2A-KP1C

Connection cable for Serial interface (COM)(Compatible models: IDEC FC5A/4A MICROSmart)
Length: 2.4m
<Connector>
Main unit: Parted wire
External device: Mini DIN 8-pin

HG9Z-XC275

Connection cable for Serial interface (COM)(Compatible models: IDEC FC5A/4A MICROSmart)
Length: 5m<Connector>
Main unit: Parted wire
External device: Mini DIN 8-pin

FC6A-KC1C

Connection cable for Serial interface (COM)(Compatible models: IDEC F6A MICROSmart FC6A-C*****E only)
Length: 5m<Connector>
Main unit: Parted wire
External device: RJ45

PLC Connection Cable

Description

Surface Protection Film*1

HG9Z-1E4PN05 5 pcs/pack

UV Surface Protection Film*2

FT9Z-1E4PN05

5 pcs/pack

FT9Z-1X03V

Terminal Block 3-pin (Right angle type, Push-in type)
Applicable cable: AWG12 to 26
Conductor type: Solid wire or Stranded wire
Wire strip length: 12 to 13 mm
Recommended ferrule:
S3TL-H025-12WJ, S3TL-H034-12WT, S3TL-H05-14WA,
S3TL-H075-14WW (IDEC)
H0,25/12 HBL, H0,34/12 TK, H0,5/14 OR, H0,75/14 W(Weidmüller)
AI 0,25-8YE, AI 0,34-8TQ, AI 0,5-8WH, AI 0,75-8GY(Phoenix Contact)

FT9Z-XT10V

Terminal Block 10-pin (Right angle type, Screw type)
Applicable cable: AWG14 to 28
Conductor type: Solid wire or Stranded wire
Wire strip length: 6 to 7 mm
Recommended ferrule:
S3TL-H025-12WJ, S3TL-H034-12WT, S3TL-H05-14WA (IDEC)
H0,25/12 HBL, H0,34/12 TK, H0,5/14 OR (Weidmüller)
AI 0,25-8YE, AI 0,34-8TQ, AI 0,5-8WH (Phoenix Contact)

FT9Z-XT11V

Terminal Block 11-pin (Right angle type, Screw type)
Applicable cable: AWG14 to 28
Conductor type: Solid wire or Stranded wire
Wire strip length: 6 to 7 mm
Recommended ferrule:
S3TL-H025-12WJ, S3TL-H034-12WT, S3TL-H05-14WA (IDEC)
H0,25/12 HBL, H0,34/12 TK, H0,5/14 OR (Weidmüller)
AI 0,25-8YE, AI 0,34-8TQ, AI 0,5-8WH (Phoenix Contact)

Power Supply Terminal Connector

Input Terminal Connector*3

Output Terminal Connector*3*1 No UV resistant.
*2 The protective sheet is UV resistant, however, resistance against direct sunlight in outdoor usage is not guaranteed.
*3 When using this connector, the main unit is not applicable with UL certification. In addition, use applicable cables andrecommended ferrules shown in the table for wiring to each terminal.

3-2

SmartAXIS Hardware Manual

2 Replacement Parts2
2.1

Replacement Parts
FT2J
Name

Quantity

Description

Mounting clips

HG9Z-4K2PN04

4-

Serial interface connector

HG9Z-XT09P

1

Terminal Block 9-pin (Vertical type, Push-in type)

Input terminal connector

FT9Z-XT16P

1

Terminal Block 16-pin (Vertical type, Push-in type)Output terminal connector

FT9Z-XT11P

1

Terminal Block 11-pin (Vertical type, Push-in type)

FT1J
Name

Type Number

Quantity

Description

HG9Z-4K2PN04

4-Power supply terminal connector

FT9Z-1X03P

1Terminal Block 3-pin (Vertical type, Push-in type)

Serial interface connector

FT9Z-1T10P

1Terminal Block 10-pin (Vertical type, Push-in type)

Input terminal connector

FT9Z-XT10P

1

Terminal Block 10-pin (Vertical type, Push-in type)Output terminal connector

FT9Z-XT11P

1

Terminal Block 11-pin (Vertical type, Push-in type)

Mounting clips

SmartAXIS Hardware Manual

3-3

Options

2.2

3

Type Number2 Replacement Parts

3-4

SmartAXIS Hardware ManualChapter 4
1

Module Configuration Editor

Overview
This chapter describes the Module Configuration Editor to configure the settings for the I/O cartridge.

1.1

Configuration & Functions

4

This section describes the names and functions that make up Module Configuration Editor.

Preview Module Configuration: Previews the image of the FT2J/1J and I/O cartridges
set in the module configuration area. Click this button todisplay the Preview Module Configuration dialog box.
Cartridges List:

Displays a list of cartridges that can be connected to the FT2J/1J.

Parameter Setting Area:

Displays the parameters set for the object selected in the Module Configuration Area.
Configure: Configure each parameter of the cartridge. Click this button to display theconfiguration dialog box that corresponds to the cartridge.

Module Configuration Area

Parameter Setting Area

SmartAXIS Hardware Manual

Cartridges List

4-1

Module Configuration Editor

Module configuration area: Displays the configuration of connected cartridges.

2 Basic Operations2
2.1

Basic Operations
Open the Module Configuration Editor
On WindLDR, click Cartridges in PLCs group on Configuration tab.
The Module Configuration Editor is displayed.

2.2

Inserting I/O Cartridges

1 Select the cartridge to insert in the Cartridges List, and then drag and drop it to the cartridge slot in the
Module Configuration Area.
The cartridge is inserted into the main unit.

Cartridge Slot

4-2

SmartAXIS Hardware Manual

2 Basic Operations

2 Click the inserted cartridge, and then click Configure in the Parameter Setting Area.
The configuration dialog box that corresponds to the cartridge is displayed.

4
Module Configuration Editor

Inserted Cartridge

3 Configure the parameters for the cartridge in each configuration dialog box.

SmartAXIS Hardware Manual

4-3

2 Basic Operations

2.3

Deleting I/O Cartridge

1 Click to select the cartridge to remove in the module configuration area.

Module configuration area

Cartridge to remove

2 Right-click the selected cartridge and click Remove.
The selected cartridge is removed.

I/O Cartridge to delete

4-4

SmartAXIS Hardware Manual

2 Basic Operations

2.4

Changing I/O Cartridge

1 Select the cartridge to move in the module configuration area, and drag and drop it onto the destination.

4
Module Configuration Editor

Cartridge to move
When the I/O cartridge is changed, the device addresses change according to the target slot. The device
addresses in the project are not changed.

SmartAXIS Hardware Manual

4-5

3 Digital I/O Cartridge Settings

3
3.1

Digital I/O Cartridge Settings
I/O Assignments
Type

Digital Input

Digital Output

Cartridge Slot

Slot 1

Slot 2

Slot 1

Slot 2

Device Address

I20 to I23

I24 to I27

Q10 to Q13

Q14 to Q17

I0 to I15 and Q0 to Q7 are internal devices of the FT2J/1J. For details, refer to Chapter 35 "1.2 Control
Device Addresses" in the WindO/I-NV4 User's Manual.

3.2

Parameter Settings
To use the digital input cartridges, configures the parameters.
Configure the parameters according to your application on the Digital I/O Cartridge Settings dialog box displayed byclicking Configure in Parameter Setting Area. For details, refer to “Digital I/O Cartridge Settings dialog box”.

● Digital I/O Cartridge Settings dialog box
The slot number placed the cartridge being edited is displayed on the title bar.

■ Type Number
Displays the type number of the cartridge placed in the cartridge slot.
■ Input Filter Settings
The input filter is used to adjust the filter width according to the width of the input signal in order to decrease theeffects of input contact bounce and noise. For details, refer to Chapter 28 "3.12 Input Filter" in the WindO/I-NV4
User's Manual.
Specifies the filter value (0, 3 to 15) in 1 millisecond increments. However, when the value is 0, the analog input is notfiltered.

4-6

SmartAXIS Hardware Manual

4 Analog I/O Cartridge Settings

4
4.1

Analog I/O Cartridge Settings
I/O Assignments
Type

Analog input

Cartridge Slot

Slot 1

Analog output
Slot 2

Slot 1

4

Slot 2

IN0

IN1

IN0

IN1

OUT0

OUT1

OUT0

OUT1

Analog Number

AI4

AI5

AI6

AI7

AQ2

AQ3

AQ4

AQ5

• AI0 to AI3 are analog inputs of the FT2J/1J. For details, refer to Chapter 28 "3.13 Analog Inputs" in the
WindO/I-NV4 User's Manual.
• AQ0 and AQ1 are analog outputs of the FT2J/1J. For details, refer to Chapter 28 "3.14 Analog Outputs" inthe WindO/I-NV4 User's Manual.

4.2

Parameter Settings
To use the analog I/O cartridges, configures the parameters.
The parameters are set for each channel. Configure the parameters according to your application on the Analog I/O
Cartridge Settings dialog box displayed by clicking Configure in Parameter Setting Area. For details, refer to “Analog I/
O Cartridge Settings Dialog Box”.

● Analog I/O Cartridge Settings Dialog Box
The slot number placed the cartridge being edited is displayed on the title bar.

(Parameter Setting List)■ Type Number
Displays the type number of the cartridge placed in the cartridge slot.

SmartAXIS Hardware Manual

4-7

Module Configuration Editor

Channel4 Analog I/O Cartridge Settings■ (Parameter Setting List)
Channel:

Displays the analog inputs or analog outputs assignments. For details, refer to“4.1 I/O Assignments”
on page 4-7.

Filter (ms):The analog input of the analog input cartridge is filtered to reach approximately 99% of the analog
input at the specified time.
Specifies the filter value (0 to 50000) in 50 milliseconds increments. However, when the value is 0,
the analog input is not filtered.

• Even when the analog input varies rapidly, the filtered analog value can be made to vary smoothly by
setting the filter.
• Analog output cartridges cannot be filtered.
Example: 100ms is set.
100
Analog input data after filtering (%)

90

Reaches approximately
99% of the analog input
in the set time (100 ms).

80
70
60
50
40
30
20
10
0
-20

0

20

40

60

80

100

120

Elapsed time (ms)Signal Type : The signal type that can be set varies based on the analog I/O cartridge model.
FC6A-PJ2A:

0 to 10V DC, 0 to 20 mA DC, 4 to 20 mA DC

FC6A-PJ2CP:

Type K, Type J, Type R, Type S, Type B, Type E, Type T, Type N, Type C,
Pt100, Pt1000, Ni100, Ni1000

FC6A-PK2AV:

0 to 10V DC

FC6A-PK2AW:

4 to 20 mA DC

The performance and functionality of the analog I/O cartridge vary based on the version. For details
about the version number, refer to Chapter 2 “Description Location of Version Number” on page 2-8.
Data Format :Select the data format that handles analog values from the following.
Binary data:

Converts an analog value to a value in the range 0 to 4095.

Optional range:

Converts the analog values to the set minimum and maximum
value range. For details, refer to “Minimum, maximum values”
on page 4-9.

Celsius (°C), Fahrenheit (°F)*1: Linearly converts the input value of the temperature sensor
selected in Signal Type. For detail, refer to “Minimum, maximum
values” on page 4-9.

*1 Analog input cartridge only

4-8

SmartAXIS Hardware Manual

4 Analog I/O Cartridge Settings

Minimum, maximum values :The minimum and maximum that can be set vary based on the item selected using
Data Format.
Binary data

The minimum value is 0 and the maximum value is4095.

Optional range:-32768 to 32767

Celsius °C, Fahrenheit (°F)*1: These vary based on the item selected for Signal
Type. The minimum and maximum are as follows.
Celsius

Data :

Temperature(0.1°C)

Analog value

Temperature(0.1°F)

Analog value

Type K-200.0 to
1,300.0-2,000 to
13,000-328.0 to
2,3720.0-3,280 to
23,720Type J-200.0 to
1,000.0-2,000 to
10,000-328.0 to
1,832.0-3,280 to
18,320Type R

0.0 to 1,760.0

0 to 17,600

32.0 to 3,200.0

320 to 32,000Type S

0.0 to 1,760.0

0 to 17,600

32.0 to 3,200.0

320 to 32,000Type B

0.0 to 1,820.0

0 to 18,200

32.0 to 3,308.0

320 to 33,080

Type E-200.0 to 800.0 -2,000 to 8,000-328.0 to
1,472.0-3,280 to
14,720Type T-200.0 to 400.0 -2,000 to 4,000 -328.0 to 752.0 -3,280 to 7,520

Type N-200.0 to
1,300.0-2,000 to
13,000-328.0 to
2,372.0-3,280 to
23,720Type C

0.0 to 2,315.0

0 to 23,150

32.0 to 4,199.0

320 to 41,990

Pt100-200.0 to 850.0 -2,000 to 8,500-328.0 to
1,562.0-3,280 to
15,620Pt1000-200.0 to 600.0 -2,000 to 6,000-328.0 to
1,112.0-3,280 to
11,120Ni100-60.0 to 180.0-600 to 1,800-76.0 to 356.0-760 to 3,560

Ni1000-60.0 to 180.0-600 to 1,800-76.0 to 356.0-760 to 3,560

Displays the special data registers that store the analog value for the analog inputs or analog outputs of
the analog I/O cartridge. The values of device addresses are updated with each scan.
D8176:

Analog value of the analog I/O cartridge (Slot1) (AI4/AQ2)

D8177:

Analog value of the analog I/O cartridge (Slot1) (AI5/AQ3)

D8186:

Analog value of the analog I/O cartridge (Slot2) (AI6/AQ4)

D8187:

Analog value of the analog I/O cartridge (Slot2) (AI7/AQ5)• The values of special data registers for unused channels (analog output cartridges whose Signal Type isset to Unused or slots without analog I/O cartridges installed) are undefined.
• If the filter is enabled on an analog input, the filtered value is stored in the special data register.
• The values of special data registers to store analog values are updated regardless of whether the ladderprogram is stopped or running.

*1 Analog input cartridge only

SmartAXIS Hardware Manual

4-9

4Module Configuration Editor

Signal Type

Fahrenheit

4 Analog I/O Cartridge Settings

Status :Displays the special data registers that store the status of the analog inputs or analog outputs expanded
using analog I/O cartridges.
D8178:

Analog I/O cartridge status (Slot1) (AI4/AQ2)

D8179:

Analog I/O cartridge status (Slot1) (AI5/AQ3)

D8188:

Analog I/O cartridge status (Slot2) (AI6/AQ4)

D8189:

Analog I/O cartridge status (Slot2) (AI7/AQ5)

The values of special data registers to store the status of the analog inputs or analog outputs are updated in
the scan end processing.
Analog input
StatusDescription

Analogvalue

0Operating normally

Current
analog value

1

Converting data (after the power is turned on and after the project is
downloaded)

Undefined

2

Initializing

0

3, 4

Reserved―

Wiring fault (out of maximum range)
Voltage0 to 10 V
0 to 20 mA

5Signaltype

Current
4 to 20 mA

V100*1: 10.0 V or higher

V201*1 or later: 10.2 V or higher
V100*1: 20.0 mA or higher

V201*1 or later: 20.4 mA or higher
V100*1: 20.0 mA or higher

Maximumvalue

V201*1 or later: 20.32 mA or higher

Thermocouple
Resistancethermometer

Maximum value or higher

Wiring fault (out of minimum range, open current loop)
Voltage0 to 10 V
0 to 20 mA

6

Signaltype

Current
4 to 20 mA

V100*1: 0 V or lower

V201*1 or later: -0.2 V or lower
V100*1: 0 mA or lower

V201*1 or later: -0 mA or lower
V100*1: 4.0 mA or lower

Minimumvalue

V201*1 or later: 3.68 mA or lower

Thermocouple
Resistancethermometer

Minimum value or higher

7

Reserved (Analog I/O cartridge correction value error)

8

There is a difference in the configured content for the installed analog input
cartridge and the Module Configuration Editor.

Undefined

9

The analog input cartridge has not been installed.

Undefined

10 to
65535

Reserved――*1 Version Number of the analog input cartridge. The version number is printed on the side of the analog I/O cartridge. For
details, refer to Chapter 2 “Description Location of Version Number” on page 2-8.

4-10

SmartAXIS Hardware Manual

4 Analog I/O Cartridge Settings

Analog output
StatusDescription

Analog value
Current analog
value

0

Operating normally

1

Reserved―

2

Initializing

0 V / 4 mA

3Parameter setting error
Reserved―

8

There is a difference in the configured content for the installed
analog output cartridge and the Module Configuration Editor.

9

The analog output cartridge has not been installed.

10

The analog output cartridge has been installed, but Unused is
selected as Signal Type.

11 to 65535 Reserved

0 V / 4 mA―
0 V / 4 mA―

SmartAXIS Hardware Manual

4-11

4Module Configuration Editor

4 to 7

Analog value
immediately before
the error occurredAbout the Warranty of the products
1

Warranty Period
The warranty period for IDEC products shall be three (3) year after purchase or delivery to the specified location.
However, this shall not apply in cases where there is a different specification in the Catalogs or there is anotheragreement in place between you and IDEC.

2

Warranty scope
Should a failure occur in an IDEC product during the above warranty period for reasons attributable to IDEC, then
IDEC shall replace or repair that product, free of charge, at the purchase location/delivery location of the product, or
an IDEC service base. However, failures caused by the following reasons shall be deemed outside the scope of thiswarranty.
i.

The product was handled or used deviating from the conditions/environment listed in the Catalogsii.

The failure was caused by reasons other than an IDEC productiii.

Modification or repair was performed by a party other than IDECiv.

The failure was caused by a software program of a party other than IDECv.

The product was used outside of its original purposevi.

Replacement of maintenance parts, installation of accessories, or the like was not performed properly inaccordance with the user's manual and Catalogsvii. The failure could not have been predicted with the scientific and technical standards at the time when the
product was shipped from IDEC
viii. The failure was due to other causes not attributable to IDEC (including cases of force majeure such as natural
disasters and other disasters)*

Customers assume their own risk in programming products, Company will not be held liable for damages as aresult of improper programming.

Furthermore, the warranty described here refers to a warranty on the IDEC product as a unit, and damages inducedby the failure of an IDEC product are excluded from this warranty.

3Service scope
The prices of IDEC products do not include the cost of services, such as dispatching technicians. Therefore, separate
fees are required in the following cases.
(1) Instructions for installation/adjustment and accompaniment at test operation (including creating application
software and testing operation, etc.)(2) Maintenance inspections, adjustments, and repairs(3) Technical instructions and technical training(4) Product tests or inspections specified by you

Specifications and other descriptions in this manual are subject to change without notice.
Information in this manual is current as of July, 2024.
2023 IDEC Corporation, All Rights Reserved.
B-2339(2)