JZ SERIESSOLID STATE RELAY
JZ series is a very reliable small semiconductor
switch for power conditioning of resistance load.
By Zero Cross Switching mode, we achieve on-offcontrol of alternating current from 100V to 240V
with low noise.
■FEATURES●Slim form with small space●Wide input voltage range of 5 to 24V DC.
Connection to SSR drive type controller and PLC
available.
●High reliability by protection circuit built-in.
●Very visible with LED display●DIN rail mounting parts are prepared

JZ1240-F0
JZ1220-F0
JZ1210-F0■MODELS■SPECIFICATIONSJZ12□□- □0

Rated operating voltage : 5 to 24V DC
Rated input current :7mA or less (at 25℃)
Rated voltage :100 to 240V AC
Non repetitive surge peak on :(state current)
150A (10A type)
220A (20A type)
440A (40A type)
Applied load :Resistive load
Operate time :1/2 of load power source cycle+1ms or lessRelease time :1/2 of load power source cycle+1ms or less
Output ON voltage drop : 1.6V (RMS) or less
Leakage current :10mA or less (at 200V AC)
Insulation resistance :100MΩ or more (at 500 V DC,between the input and load
terminals, and heat sink)Withstand voltage :3000V AC for 1 min(between the input and load
terminals, and heat sink)
Storage temperature :-20 to 60℃(with no icing or condensation)
Ambient temperature :-10 to 50℃(with no icing or condensation)*Please refer to "load current ambient temperature" for details
Ambient humidity :45 to 85%RH
Weight :10A --- 80g (configuration S)
260g (configuration F)
20A --- 100g (configuration S)
280g (configuration F)
40A --- 100g (configuration S)
380g (configuration F)

Rated current
10 ：10A
20 ：20A
40 ：40A
Configuration
S：Main unit
F：Main unit + heat sink
+ DIN rail mounting parts●Rated load power
JZ1210（10A） JZ1220（20A）JZ1240（40A）with heat sink

0.1 to 10A

0.1 to 20A

0.5 to 40A

without heat sink

0.1 to 4A

0.1 to 5A

0.5 to 6A*Depending on ambient temperature. Please refer to load currentambient temperature■ACCESSORIES●DIN rail mounting parts
Please use it without heat sink, and when DIN rail mountingparts is installed.
ModelSpec

WeightJZ911

Rated current 10/20A

10g

JZ912

Rated current 40A

20g

1PSE-364

■CONNECTION■THE LOAD CURRENT - AMBIENT TEMPERATURE《For connecting with the SSR drive type controller》●Single-phase circuit

1 unit
The high-density or gang mounting of 3 units
The high-density or gang mounting of 10 units

LoadLOAD

20A type, configuration F
30
20

8.5A

86

7.2A
6.8A

10A (1unit)
8.5A (3 units)
8A (10 units)420-2050
40
17A

1614A
13A

20A (1unit)
17A (3 units)
16A (10 units)

12840-20

2040 50 60
0Ambient temperature (℃)

40A type, configuration F

Load current (A)20
10Load current (A)Load current (A)10A type, configuration F

322432A
27.2A
25.6A

40A (1unit)
34A (3 units)

16

SSR drive type controllerex) LT830 series

32A (10 units)

LT830

8PVAT

INPUT

0-20

20
40 50 60
0Ambient temperature (℃)

OUT1OUT2SV

EV1

20 35 40 50 60
0
Ambient temperature (℃)

EV2●Three-phase circuit
10A type, configuration S(+ JZ911)

20A type, configuration S(+ JZ911)

3.4A

32.8A
2.7A

4A (1unit)
3.4A (3 units)
3.2A (10 units)

2
10-20

5
4.2A

45A (1unit)
4.2A (3 units)
4A (10 units)

32
10-20

20
40 50 60
0Ambient temperature (℃)

3.5A
3.4A

ST

LOAD

LOAD

INPUT

INPUT

Select it as follows
when using withthe three-phase circuit.
・When load current
is 5A or less.
→10A type(JZ1210-F0)・When load current
is 10A or less.
→20A type(JZ1220-F0)・When load current
is 20A or less.
→40A type(JZ1240-F0)

6Load current (A)

4Load current (A)Load current (A)765R

40A type, configuration S(+ JZ912)

5.1A

546A (1unit)
5.1A (3 units)
4.8A (10 units)

32
10-20

2040 50 60
0
Ambient temperature (℃)

4.3A
4A

2040 50 60
0
Ambient temperature (℃)

SSR drive type controllerex) LT830 series
LT830

PVAT
OUT1
OUT2

LoadSV

EV1
EV2■DIMENSIONS
10A/20A type
●Configuration S40A type

●Configuration S + JZ911●Configuration S●Configuration S + JZ912373030293784529LOAD
LOAD

LOAD

ＬＯＡＤ

5-24V DC

9080−
４40A＋
３４−ＩＮＰＵＴ

40A
5-24V DC

４−＋３INPUT

INPUT

2-M4＋３●Configuration F
1002-M510030ＩＮＰＵＴ

INPUT

INPUT

●Configuration F

２100-240V AC

Solid State Relay

5-24V DC

ＩＮＰＵＴ

ＩＮＰＵＴ

１２100-240V AC

Solid State Relay

90＋３ＬＯＡＤ

ＬＯＡＤ

１100２10A

80

5-24V DC47.5452963296388LOAD
LOAD

ＬＯＡＤ

１ＬＯＡＤ

２100-240V AC

Solid State Relay

２5-24V DC＋３809010010A−４40A
5-24V DC４−90100-240V AC

Solid State Relay

100１80−４100-240V AC80１Solid State Relay

10A47.5２

Solid State Relay

100100-240V AC

ＬＯＡＤ80１82945LOAD

29＋３ＩＮＰＵＴ

ＩＮＰＵＴ

INPUT

INPUT

2-M3.5

Unit : mm

2-M3.5

Unit : mmSpecifications subject to change without notice. Printed in Japan (I) 2009. 1032-8 KUMANO-CHO,ITABASHI-KU,TOKYO 173-8632
Telephone : +81-3-3956-2171
Facsimile : +81-3-3956-0915
E-mail : inter@chino.co.jp
Website : http://www.chino.co.jp/