HIGH/LOW SELECTOR SAASINSTRUCTION MANUALPreface
Thank you for purchasing the High/Low Selector SAAS.
This manual contains instructions for the mounting, functions, operations and notes when
operating the SAAS. To prevent accidents arising from the misuse of this instrument, please
ensure the operator receives this manual.

Notes• This instrument should be used in accordance with the specifications described in the manual.
If it is not used according to the specifications, it may malfunction or cause a fire.
• Be sure to follow the warnings, cautions and notices. If they are not observed, serious injury
or malfunction may occur.
• Specifications of the SAAS and the contents of this instruction manual are subject to change
without notice.
• Care has been taken to ensure that the contents of this instruction manual are correct, but if there
are any doubts, mistakes or questions, please inform our sales department.
• This instrument is designed to be installed on a DIN rail. If it is not, measures must be taken to
ensure that the operator does not touch power terminals or other high voltage sections.
• Any unauthorized transfer or copying of this document, in part or in whole, is prohibited.
• Shinko Technos CO., LTD. is not liable for any damage or secondary damage(s) incurred as aresult of using this product, including any indirect damage.
SAFETY PRECAUTIONS (Be sure to read these precautions before using our products.)
The safety precautions are classified into categories: “Warning” and “Caution”.
Depending on circumstances, procedures indicated by
Caution may cause serious
results, so be sure to follow the directions for usage.
which may lead to dangerous conditions andWarning Procedurescause death or serious injury, if not carried out properly.

CautionProcedures which may lead to dangerous conditions and cause
superficial to medium injury or physical damage or may
degrade or damage the product, if not carried out properly.

Warning• To prevent an electric shock or fire, only Shinko or other qualified service personnel may
handle the inner assembly.
• To prevent an electric shock, fire or damage to the instrument, parts replacement may only
be undertaken by Shinko or other qualified service personnel.

Safety precautions• To ensure safe and correct use, thoroughly read and understand this manual before using this
instrument.
• This instrument is intended to be used for industrial machinery, machine tools and measuring
equipment. Verify correct usage after consulting purpose of use with our agency or main office.
(Never use this instrument for medical purposes with which human lives are involved.)• External protection devices such as protection equipment against excessive temperature rise, etc.
must be installed, as malfunction of this product could result in serious damage to the system or
injury to personnel. Also proper periodic maintenance is required.
• This instrument must be used under the conditions and environment described in this manual.
Shinko Technos Co., Ltd. does not accept liability for any injury, loss of life or damage occurring
due to the instrument being used under conditions not otherwise stated in this manual.
Caution with respect to Export Trade Control Ordinance
To avoid this instrument from being used as a component in, or as being utilized in the manufactureof weapons of mass destruction (i.e. military applications, military equipment, etc.), please
investigate the end users and the final use of this instrument.
In the case of resale, ensure that this instrument is not illegally exported.
2

1. Installation precautions

CautionThis instrument is intended to be used under the following environmental conditions(IEC61010-1): Overvoltage category , Pollution degree 2
Ensure the mounting location corresponds to the following conditions:• A minimum of dust, and an absence of corrosive gases• No flammable, explosive gases• No mechanical vibrations or shocks• No exposure to direct sunlight, an ambient temperature of -5 to 55 (23 to 131 )that does not change rapidly, and no icing• An ambient non-condensing humidity of 35 to 85%RH• No large capacity electromagnetic switches or cables through which large current is flowing• No water, oil or chemicals or where the vapors of these substances can come into
direct contact with the unit
• When installing this unit within a control panel, take note that ambient temperature ofthis unit must not exceed 55 (131 ). Otherwise the life of electronic components(especially electrolytic capacitor) may be shortened.
Note: Avoid setting this instrument directly on or near flammable material even though
the case of this instrument is made of flame-resistant resin.

2. Wiring precautions

Caution• Do not leave bits of wire in the instrument, because they could cause a fire and malfunction.
• When wiring terminals, use ferrules with an insulation sleeve and crimping pliers madeby Phoenix Contact GMBH & CO. applicable to terminals.
• Tighten the terminal screw using the specified torque.
If excessive force is applied to the screw when tightening, the screw or case may bedamaged.
• This instrument has no built-in power switch, circuit breaker or fuse. It is necessary to
install them near the instrument.
(Recommended fuse: Time-lag fuse, rated voltage 250V AC, rated current 2A)• For wiring of AC power source, be sure to use exclusive terminals as described in thismanual. If AC power source is connected to incorrect terminals, the unit will burn out.
• For a 24V DC power source, do not confuse polarity when wiring.
• For DC voltage and current input, do not confuse polarity when wiring.
• Keep the input wire, power line and output wire away from one another.

3. Operation and maintenance precautions

Caution• Do not touch live terminals. This may cause electric shock or problems in operation.
• Turn the power supply to the instrument OFF when retightening the terminal andcleaning. Working or touching the terminal with the power switched ON may result insevere injury or death due to Electric Shock.
• Use a soft, dry cloth when cleaning the instrument.
(Alcohol based substances may tarnish or deface the unit.)• As the display section is vulnerable, do not strike or scratch it with a hard object orpress hard on it.
3Characters used in this manual
Indication
Number,

/

-1

0

1

2

3

4

5

6

7

8

9

A

B

C

D

E

F

G

H

I

J

K

L

M

N

O

P

Q

R

S

T

U

V

W

X

Y

Z

Indication
Alphabet
Indication
Alphabetmeans that no character is indicated (unlit) on the display.
---

CONTENTS ---1. ModelPage
1.1 Model ---------------------------------------------------------------------------- 5
1.2 How to read the model label ----------------------------------------------- 5
2. Name and functions of sections ------------------------------------ 5

3. Mounting

3.1 External dimensions (Scale: mm) ---------------------------------------- 6
3.2 Mounting and removal to/from the DIN rail ----------------------------- 6

4. Wiring

4.1 Recommended ferrules ----------------------------------------------------- 7
4.2 Terminal arrangement and circuit configuration ---------------------- 8
4.3 Wiring of terminals ----------------------------------------------------------- 8
4.3.1 Power source wiring ---------------------------------------------------- 8
4.3.2 Output wiring -------------------------------------------------------------- 8
4.3.3 Input wiring ---------------------------------------------------------------- 8
5. Operation flowchart ------------------------------------------------------- 9

6. Setup

6.1 Indication after power-on ------------------------------------------------- 10
6.2 Basic operation of setup --------------------------------------------------- 11
6.3 Setup of the unit ------------------------------------------------------------- 12
6.3.1 When using this unit as a signal conditioner -------------------- 13
6.3.2 When using the Reverse function ---------------------------------- 13
6.3.3 When using the 1st order lag filter function ---------------------- 13

7. Adjustment

7.1 Basic operation of adjustment ------------------------------------------- 14
7.2 Adjustment -------------------------------------------------------------------- 15

8. Operation

8.1 Indication after power-on -------------------------------------------------- 16
8.2 Operation ---------------------------------------------------------------------- 16
9. Specifications --------------------------------------------------------------- 18

10. Troubleshooting

10.1 Indication -------------------------------------------------------------------- 19
10.2 Key operation -------------------------------------------------------------- 19
10.3 Operation -------------------------------------------------------------------- 19
11. Character table ------------------------------------------------------------- 20

4

1. Model
1.1 Model

SA
Signal conditioner AS
01

Power supply

Series name: SA
High/Low selector
100 to 240V AC
24V AC/DC

1.2 How to read the model label
The model label is attached to the left side of the case.
Model
Input
OutputSerial number(Fig. 1.2-1)

2. Name and functions of sections
1 Power indicator (Green)

Lights when the power to the instrument is turned on.
2 Input display (Red)

1
2
3
6
4

7

5

8

(Fig.2.1)

6 Input indicator

Indicates the input value selected during Input High/Low
selection, by comparing Input 1 with Input 2 value
in the Run mode.
Indicates setting (or adjustment) characters in the
Setup and Adjustment mode.
3 Output display (Green)
Indicates the output value (%) corresponding to the
input value selected during Input High/Low selection, bycomparing Input 1 with Input 2 value in the Run mode.
Indicates the set (or adjusted) value in the Setup andAdjustment mode.
4 Up key ()
Increases the numeric value, or switches the selection
items.
5 Down key ()
Decreases the numeric value, or switches the selection
items.

Lights when Input 1 is indicated on the Input display.
Flashes when Input 2 is indicated on the Input display.
7 Mode key ()
By holding down this key for approx. 3 seconds, the unit proceeds to the Adjustment mode.
Switches the setting mode, and registers the set (or selected) value.
8 Sub-mode key (Unmarked)
If the Mode key is pressed while holding down this key, the unit proceeds to the Setup mode.
5

3. Mounting
3.1 External dimensions (Scale: mm)

75

DIN rail

97
22.5

100

4

(Fig. 3.1-1)
3.2 Mounting and removal to/from the DIN rail

Caution• Mount the DIN rail horizontally.
• To remove this instrument, a flat blade screwdriver is required for pulling down
the lever.
Never turn the screwdriver when inserting it into the release lever.
If excessive power is applied to the lever, it may break.
• Be sure to use commercially available fastening plates at both ends of the unit
if it is in a position susceptible to vibration or shock.
Recommended fastening plate
Manufacturer
Omron Corporation
IDEC Corporation
Panasonic Electric Works Co., Ltd.

Model
End plate
PFP-M
Fastening plate BNL6
Fastening plate ATA4806

Mounting to the DIN rail (Fig. 3.2-1)• Hook 1 of the instrument on theupper side of the DIN rail.
• Making 1 part of the instrument
as a support, fit the lower part 2of the instrument to the DIN rail.
The unit will be completely fixed to
the DIN rail when a “Click” sound is heard.

12(Fig. 3.2-1)
6

Removal from the DIN rail (Fig.3.2-2)• Insert a flat blade screwdriver
into the release lever ( 1 ).
• Remove the instrument from the
DIN rail by pulling down the lever ( 2 ).

Release lever

2

1(Fig. 3.2-2)

4. Wiring
Warning
Turn the power supply to the instrument off before wiring.
Working or touching the terminal with the power switched on may result in severe
injury or death due to Electric Shock.

4.1 Recommended ferrules
When using ferrules, use the following recommended ferrules and crimping pliers made by
Phoenix Contact GMBH &CO. See (Table 4.1-1).
Take note that screw size and tightening torque differ depending on the terminal number.
(Table 4.1-1)
Terminal Terminal Ferrules withnumberscrew insulation sleeve
1 to 4
M2.6
AI 0.25-8 YE
AI 0.34-8 TQ
AI 0.5-8 WH
AI 0.75-8 GY
AI 1.0-8 RD
AI 1.5-8 BK
5 to 9M2.0
AI 0.25-8 YE
AI 0.34-8 TQ
AI 0.5-8 WH

Conductor
Tightening
Crimping pliers
cross sections
torque2
0.2 to 0.25mm
0.5 to 0.6N•m
CRIMPFOX2
ZA 3
0.25 to 0.34mm
20.34 to 0.5mm
CRIMPFOX
0.5 to 0.75mm2UD 60.75 to 1.0mm2
1.0 to 1.5mm2
0.2 to 0.25mm2 0.22 to 0.25N•m
0.25 to 0.34mm2
0.34 to 0.5mm2

7

4.2 Terminal arrangement and circuit configuration

Insulation circuit+

5

Input 1

-

6

3

Input

OutputcircuitCPU

circuitOutput
4

-

1

+

7

Input 2++8

Display/Setting key
circuitPower
circuit9Power supply
2-(Fig. 4.2-1)
4.3 Wiring of terminals

Caution• For 100 to 240V AC, if the AC power source is connected to incorrect terminals,
this instrument will burn out.
• For a 24V DC power source, do not confuse polarity when wiring.
4.3.1 Power source wiring
Use terminals 1 (+) and2 (-) for the power supply to the instrument.

4.3.2 Output wiring
Use terminals 3 (+) and4 (-) for the output wiring.

4.3.3 Input wiring
Use terminals 5 (+), 6 (-) for Input 1 wiring.
Use terminals 7 (-), 8 (+) for Input 2 wiring.
Connect shunt resistor (sold separately) between input terminals 5 (+), 6 (-)
and between 7 (-), 8 (+).
See (Table 4.3.3-1).
(Table 4.3.3-1)
Shunt resistor
Model
Specification
RES-S02-050
50
0.1%

Input
4 to 20mA DC

8

5. Operation flowchart
Power ONWarm-up indication (Approx. 3sec.)

Run mode

Hold down the
key for approx. 3sec.
Adjustment modeIN
Output zeroadjustment
OUT

IN
OUT

Press thekey.
Output span
adjustment
Press the

IN
OUT

IN
OUT

key.
IN
OUT

• To return from
Adjustment to Run
mode, press the
key for approx. 3sec.
From any setting item
in Adjustment mode, it
is possible to return to
Run mode.

Press thekey while holding
down the Sub-mode key.
Setup modeSet value lock

IN
OUT

IN
OUT

IN
OUT

IN
OUT

Press thekey.
Decimal point
place
Press thekey
Output 0%
value

IN

Press thekey.
Output 100%
value

IN

Press thekey.
Input 1 filter
time constantIN

Press thekey.
Input 1 sensor
correction

IN

Press thekey.
Input 2 filter
time constantIN

Press the

9

key.

OUT

OUT

OUT

Input 2 sensor
correction
Press thekey.
OutputNormal/Reverse
Press thekey.
Display
selection
Press thekey.
Indication time

OUT

Press thekey.
Input High/Low

OUT

Press thekey.

6. Setup
Setup should occur before using this unit, to set the Output 0% value, Output 100% value,
Output Normal/Reverse, Input High/Low, etc. according to the users’ conditions.
If the users’ specifications are the same as the default value of the instrument, or if setup
has already been completed, it is not necessary to set up the instrument. Proceed to
Section “7. Adjustment”.
(Table 6-1)
Setting item
Set value lock
Decimal point place
Output 0% value
Output 100% value
Input 1 filter time constant
Input 1 sensor correction
Input 2 filter time constant
Input 2 sensor correction
Output Normal/Reverse
Display selection
Indication time
Input High/Low

Default value
UnlockNo decimal point
-1999
9999
0.0 seconds
0
0.0 seconds
0
NormalInput/Output indication
00.00 (Continuous)
Input High (High input signal)

6.1 Indication after power-on
After power-on, warm-up status below (Fig. 6.1-1) is indicated for approx. 3sec.
Indicates the input type.
Indicateswhen default value is 4 to 20mA DC.
Lights after
power-on.
Indicates the output type.
Indicateswhen default value is 4 to 20mA DC.
(Fig. 6.1-1)
After that, the unit switches to the Run mode as shown below.
Indicates the input value selected during Input
High/Low selection, by comparing Input 1 with Input
2 value.
Indicateswhen nothing is connected to the
input terminals.

(Fig. 6.1-2)

Indicates the output value in a percentage form (%)
corresponding to the input value selected during Input
High/Low selection, by comparing Input 1 with Input 2
value.
Indicates(-10.0%) when nothing is connectedto the input terminals.
106.2 Basic operation of setup
Setup is conducted in the Setup mode.
To enter the Setup mode, press the
key while holding down the Sub-mode key in the
Run mode. (Fig. 6.2-1)
To set (select) each item, use theorkey, and register the value with the
key.
(Fig. 6.2-2)(1) Run mode

To enter the Setup mode, press theMode ( ) key while holding down the
Sub-mode key in the Run mode.
Mode key
Sub-mode key (Unmarked)(Fig. 6.2-1)(2) Setup mode

To proceed to each setting item andto register the set (or selected) value,please use this key.

To set (or select)each item, use
these keys.
(Fig. 6.2-2)

11

6.3 Setup of the unit
The following shows all setup items. Set up the unit referring to the explanation of each item.
DisplayName, Function, Setting range
Default value
IN
Unlock
Set value lock
Locks the set values to prevent setting errors.
OUT
Selection item:: Unlock: Lock (None of the set values and adjusted values can be changed.)IN
No decimal point
Decimal point place
Selects the decimal point place.
OUT
Selection item:: No decimal point: 1 digit after decimal point: 2 digits after decimal point: 3 digits after decimal point
IN-1999
Output 0% value
Sets the value (indicated on the Input display) at 0% output.
Setting range: -1999 to Output 100% value (The placement of the decimal
OUT
point follows the selection)
IN

OUT

IN

OUT

IN

OUT

IN

OUT

IN

OUT

IN

OUT

9999
Output 100% value
Sets the value (indicated on the Input display) at 100% output.
Setting range: Output 0% value to 9999 (The placement of the decimal
point follows the selection)
0.0 seconds
Input 1 filter time constantSets Input 1 filter time constant.
Reduces input fluctuation caused by noise.
Setting range: 0.0 to 10.0 seconds
0
Input 1 sensor correction
Sets Input 1 sensor correction value.
Input 1 value = Current Input 1 value + Input 1 sensor correction value
Setting range: -1000 to 1000 (The placement of the decimal point follows
the selection)
0.0 seconds
Input 2 filter time constantSets Input 2 filter time constant.
Reduces input fluctuation caused by noise.
Setting range: 0.0 to 10.0 seconds
0
Input 2 sensor correction
Sets Input 2 sensor correction value.
Input 2 value = Current Input 2 value + Input 2 sensor correction value
Setting range: -1000 to 1000 (The placement of the decimal point follows
the selection)
NormalOutput Normal/Reverse
Selects either Normal mode (0.0 to 100.0%) or Reverse mode (100.0 to0.0%) for output status.
Selection item:: Normal: Reverse
12

IN

OUT

IN

OUT

IN

OUT

Input/Output indication
Display selection
Selects an indication type on the display.
Selection item:: Input/Output indication: Input indication: Output indication: No indication (Only the power indicator is lit.)
00.00 (Continuous)
Indication time
Sets the indication time of the display after the final key operation.
Not available if No indication (Only the power indicator is lit) is selectedduring Display selection
After the indication time has elapsed, the displays go off (Only the power
indicator is lit.).
If power is turned on again, or if any of the keys,,
and theSub-mode key is pressed while displays are unlit, the displays will light again.
Setting range:
00.00: Continuous indication
00.01 (1 second) to 60.00 (60 minutes) [Minute.Second]
With Input1 and 2, if input value is overscale or underscale, the Indication
time setting function is disabled.
Input High
Input High/Low
Selects Input High or Low, by comparing Input 1 with Input 2 value.
Selection range:: Input High (High input signal): Input Low (Low input signal)

6.3.1 When using this unit as a standard High/Low selector
Set the filter time constant to 0.0 seconds, andset the Output Normal/Reverse selection to “Normal”.
6.3.2 When using the Reverse function
This function reverses the output (100 to 0%)that corresponds to the input (0 to 100%).
Set the Output Normal/Reverse selection to “Reverse”.
6.3.3 When using the first order lag filter function
The value is outputted by performing the firstorder lag computation using the filter time
constant “T”. (Fig. 6.3.3-1)
Set the filter time constant to a random value(0.0 to 10.0 seconds).

Input
Time
OutputT
13(Fig. 6.3.3-1)

Time7. Adjustment
Performs the output zero and span adjustments.
Connect an mV generator to Input 1 terminals of this instrument.
Do not connect anything to Input 2 terminals.
Connect a digital multimeter to output terminals.
Select ”High (High input signal)” during the Input High/Low selection.
7.1 Basic operation of adjustment
Adjustment can be conducted in the Adjustment mode.
To enter Adjustment mode, hold down the
key for approx. 3 seconds in the Run mode.
(Fig. 7.1-1)
For output adjustment, use theorkey, and register the value with the
key.
(Fig. 7.1-2)
To revert to the Run mode, press the
key again for approximately 3 seconds.
(1) Run mode

To enter Adjustment mode, pleasehold down the
key for approx.
3 seconds in the Run mode.

(Fig. 7.1-1)(2) Adjustment mode

To proceed to each item in the
Adjustment mode and to register
the adjusted value, please use
this key.

Please use thesekeys for adjustment.

(Fig. 7.1-2)

14

7.2 Adjustment
The following shows all adjustment items. Adjust values referring to explanation of each item below.
Display
IN

OUT

IN

OUT

Name, Function, Setting range
Default value
0.00%
Output zero adjustment
Adjusts output zero.
Input the value corresponding to 0% output, then adjust the value with theor
key while viewing the output value (on the digital multimeter).
Setting range: -5.00 to 5.00%
Effective range of adjustment: -5 to 5%
0.00%
Output span adjustment
Adjusts output span.
Input the value corresponding to 100% output, then adjust the value with theor
key while viewing the output value (on the digital multimeter).
Setting range: -5.00 to 5.00%
Effective range of adjustment is 95 to 105%.

15

8. Operation
8.1 Indication after power-on
After power-on, the following warm-up status is indicated for 3 seconds (Fig. 8.1-1).

Indicates the input type.
Indicateswhen default value is 4 to 20mA DC.

Lights after power-on.

Indicates the output type.
Indicateswhen default value is 4 to 20mA DC.
(Fig. 8.1-1)
8.2 Operation
The unit enters the Run mode as shown in (Fig. 8.2-1).
By comparing Input 1 with Input 2, the value selected during Input High/Low selection isindicated or outputted.
Input 1 is indicated on the Input display when the Input indicator is lit.
Input 2 is indicated on the Input display when the Input indicator is flashing.
Indicates the input value selected during Input
High/Low selection, by comparing Input 1 with Input 2
value.
Indicateswhen nothing is connected to the
input terminals.

Input indicator(Fig. 8.2-1)

Output value corresponding to the input value selectedduring Input High/Low selection (Input 1 and Input 2
are compared) is indicated in a percentage form (%).
Indicates(-10.0%) when nothing is connectedto the input terminals.

16• Indication when input value is -2000 or less
For the indication of -2000 or less (up to –10% output), the input value and the minus (-)
sign are indicated alternately.
(e.g.) Indication of -2000
IN
IN• Indication when input value is 10000 or more
For the indication of 10000 or more (up to 110% output), the lower 4 digits of input value
are flashing.
(e.g.) Indication of 10020
IN
Flashes.

• Underrange, Overrange and Sensor burnout alarm indication
Even if any selection is made during the Display selection, the following indications appear.
Underrange : "" flashes on the Input display.
Overrange : "" flashes on the Input display.

• Indication time setting
If indication time is set, the displays will go off after the indication time has elapsed.
(Only the power indicator is lit.)
If power is turned on again, or if any of the keys,,
and the Sub-mode key
is pressed while displays are unlit, the displays will light again.
With Input1 and 2, if input value is overscale or underscale, the Indication time
setting function is disabled.

17

9. Specifications
Input specifications
DC current
Output specifications
DC current

4 to 20mA DC (50shunt resistor)

4 to 20mA DC (Allowable load resistance: 700
Zero adjustment range: -5 to 5%
Span adjustment range: 95 to 105%or less)

Performance
Accuracy

Input: Within 0.1% (Common to Input 1 and Input 2)
Output: Within 0.1%
Display accuracy
Within Input accuracy 1 digit
Response time
0.5 seconds (typical) (090%)
Temperature coefficient 0.015%/
Insulation resistance
Input – Output – Power: 10M or more, at 500V DC
Dielectric strength
Input – Output – Power: 2.0kV AC for 1 minute

General structure
Case
Front panel
Setting
Display, indicator

Flame-resistant resin, Color: Light gray
Membrane sheet
Setting by the front keypad
Input display : 7 segments Red LED display 4 digits
Character size: 7.4 x 4.0mm (H x W)
Output display : 7 segments Green LED display 4 digits
Character size: 7.4 x 4.0mm (H x W)
Power indicator: Green LED
Input indicator : Green LED

Installation specifications
Power supply
100 to 240V AC 50/60Hz, 24V AC/DC 50/60Hz
Allowable voltage range 85 to 264V AC, 20 to 28V AC/DCPower consumption
Approx. 6VA
Ambient temperature -5 to 55 (23 to 131 )Ambient humidity
35 to 85%RH (Non-condensing)
WeightApprox. 120g
Mounting
DIN rail mounting
External dimensions
W22.5 x H75 x D100mm
Attached function• Power failure countermeasure:
The setting data is backed up in the non-volatile IC memory.
• Self-diagnosis:
The CPU is monitored by a watchdog timer, and if an abnormal status is found on the CPU,the unit is switched to warm-up status with all outputs off.

18

10. Troubleshooting
10.1 Indication
Problem
Input display is flashing"" or "

Presumed cause and solution• Check the input signal source.

".

The indication of the Input • Check whether the sensor correcting value is suitable.
display is irregular or
Set it to a suitable value.
unstable.
• There may be equipment that interferes with or makes
noise near the unit.
Keep equipment that interferes with or makes noiseaway from the unit.
10.2 Key operation
Problem
Setting or adjustment is
not possible.
10.3 Operation
Problem
Input value does notchange.

No output

Presumed cause and solution• “Lock” has been selected during Set value lock selection.
Select “Unlock”.

Presumed cause and solution• Check whether input and output wires are securely
connected to the Input/Output terminals of the instrument.
Ensure that input and output wires are securely connectedto the Input/Output terminals.
• Check whether the wiring of input and output is correct.
• Check whether Output 100% and Output 0% value havebeen set to suitable values.
• Check whether Output type and Output Normal/Reverse havebeen selected correctly during Output type and Output
Normal/Reverse selection.
Check the selected value.

1911. Character table
All setting items are indicated in the following tables.
Setup mode
Display
Setting item
Set value lock
Decimal point place
Output 0% value
Output 100% value
Input 1 filter time constant
Input 1 sensor correction
Input 2 filter time constant
Input 2 sensor correction
Output Normal/Reverse
Display selection
Indication time
Input High/Low
Adjustment mode
Display
Setting item
Output zero adjustment
Output span adjustment

Default value

Data

UnlockNo decimal point
-1999
9999
0.0 seconds
0
0.0 seconds
0
NormalInput/Output indication
00.00 (Continuous)
Input High (High input signal)

Default value

Data

0.00%
0.00%

******* Inquiry *******For any inquiry about this unit, please contact the vendor where youpurchased the unit or our agency after checking the following.
(e.g.)• Model ........................………. SAAS• Serial number ….................... No. xxxxxx
In addition to the above, please let us know the details of malfunction,
if any, and the operating conditions.

SHINKO TECHNOS CO.,LTD.
OVERSEAS DIVISION

Reg. Office : 2-5-1, Senbahigashi, Minoo, Osaka, JapanURL: http://www.shinko-technos.co.jp
Tel : 81-72-727-6100
E-mail: overseas@shinko-technos.co.jp
Fax: 81-72-727-7006
No.SA6E2 2009.04