和文は裏面をご覧下さい。

INSTRUCTION MANUAL

Digital Indicating Controller

JCS-33A

JCS31JE6 2013.09
To prevent accidents arising from the misuse of this controller, please ensure the operator receives this manual.

Caution• This instrument should be used according to the specifications described in the manual.
If it is not used according to the specifications, it may malfunction or cause a fire.
• Be sure to follow the warnings, cautions and notices. Not doing so could cause serious injury and/or malfunction.
• Specifications of the JCS-33A and the contents of this instruction manual are subject to change without notice.
• Care has been taken to ensure that the contents of this instruction manual are correct, but if there are any doubts,
mistakes or questions, please inform our sales department.
• This instrument is designed to be installed through the face of a control panel. If it is not, measures must be taken
to ensure that the operator cannot touch power terminals or other high voltage sections.
• Any unauthorized transfer or copying of this document, in part or in whole, is prohibited.
• Shinko Technos CO., LTD. is not liable for any damage or secondary damage(s) incurred as a result of using thisproduct, including any indirect damage.
Safety precautions (Be sure to read these precautions before using our products.)
The safety precautions are classified into categories: “Warning” and “Caution”. Depending on circumstances,
procedures indicated by
Caution may cause serious results, so be sure to follow the directions for usage.
Warning
Procedures which may lead to dangerous conditions and cause death or serious injury, if not carried out properly.
Procedures which may lead to dangerous conditions and cause superficial to medium injury or
Cautionphysical damage or may degrade or damage the product, if not carried out properly.

Warning• To prevent an electric shock or fire, only Shinko or other qualified service personnel may handle the inner assembly.
• To prevent an electric shock, fire or damage to the instrument, parts replacement may only be undertaken by
Shinko or other qualified service personnel.

Safety Precautions• To ensure safe and correct use, thoroughly read and understand this manual before using this instrument.
• This instrument is intended to be used for industrial machinery, machine tools and measuring equipment. Verify
correct usage after purpose-of-use consultation with our agency or main office. (Never use this instrument for
medical purposes with which human lives are involved.)• External protection devices such as protective equipment against excessive temperature rise, etc. must be installed, as
malfunction of this product could result in serious damage to the system or injury to personnel. Also proper periodic
maintenance is required.
• This instrument must be used under the conditions and environment described in this manual. Shinko Technos Co., Ltd.
does not accept liability for any injury, loss of life or damage occurring due to the instrument being used under conditions
not otherwise stated in this manual.
Caution with respect to Export Trade Control Ordinance
To avoid this instrument from being used as a component in, or as being utilized in the manufacture of weapons ofmass destruction (i.e. military applications, military equipment, etc.), please investigate the end users and the final useof this instrument. In the case of resale, ensure that this instrument is not illegally exported.

1. Model1.1 Model

JCS–3 3Control action 3
A1
A

,
R
S
A

Series name: JCS-33A (W48 x H48 x D95mm)
PID
Alarm type can be selected by keypad.

*1

Relay contact: 1aControl output+2
Non-contact voltage (for SSR drive): 12 0V DC(OUT1)
DC current: 4 to 20mA DC
Input
M
Multi-range *2
100 to 240V AC (standard)
Supply voltage
1
24V AC/DC *3
A2
Alarm 2 (A2) *1
W (5A)CT rated current: 5AW (10A)CT rated current: 10A
Heater burnout alarm
W (20A)CT rated current: 20A
W (50A)CT rated current: 50A
Heating/Cooling
control,DT
Non-contact relay
OptionControl output (OUT2)
C5
Serial communication (RS-485)
SM
SV1/SV2 external selection
LA
Loop break alarm
BK
Color BlackTC
Terminal cover*1: Alarm types (9 types and No alarm action) and Energized/De-energized can be selected by keypad.
*2: Thermocouple, RTD, DC current, and DC voltage can be selected by keypad.
*3: Supply voltage 100 to 240V AC is standard. When ordering 24V AC/DC, enter “1” after the input code.
11.2 How to read the model label
Model labels are attached to thecase and the inner assembly.
For Heater burnout alarm output,
CT rated current is written in thebracket.

(1)
(2)
(3)

(Model label)
JCS-33A-R/M
A2
W(20A)(e.g.)
Relay contact output /Multi-range input
Alarm 2 (A2) output
Heater burnout alarm output (20A)No.

(1) Model (2) Option, supply voltage (“1” is entered only for 24V AC/DC)(3) Serial number

2. Name and functions(1) PV display

(1)
(2)
(3)
(4)

: Indicates the PV (process variable) or setting
characters in the setting mode with the red LED.
(2)
SV
display:
Indicates
the SV (desired value), MV (manipulated(5)
variable) or each set value in the setting modewith the green LED.
(6)(3) SV1 indicator : The green LED lights when SV1 is indicated on
the SV display.
(7)
(4)
SV2
indicator:
Theyellow LED lights when SV2 is indicated on(8)
the SV display.
(5) OUT1 indicator : When OUT1 is ON, the green LED lights.
(9)[For A/ type, it flashes corresponding to the(10)
MV (manipulated variable) in 250ms cycles.](6) OUT2 indicator : When OUT2 (DT option) is ON, the yellow LED
lights.
(7)
A1
indicator:
When
A1 output is ON, the red LED lights.
(11) (12) (13) (14)(8) EVT indicator : When Event output (A2, LA or W option) is ON,
the red LED lights.
(Fig. 2-1)
(9) AT indicator: When AT (auto-tuning) or auto-reset is
performing, the yellow LED flashes.
(10) TX/RX indicator : The yellow LED flashes during Serial communication output (transmitting).
(11) Increase Key ( ) : Increases the numeric value.
(12) Decrease Key ( ): Decreases the numeric value.
(13) Mode Key () : Selects the setting mode, or registers the set value.
(By pressing the Mode Key, the set value or selected value can be registered.)(14) OUT/OFF Key ( ) : Selects either Control output OFF function (Control output ON/OFF) or
Auto/Manual control switching. (To cancel the Control output OFF function,press the OUT/OFF Key again for approx. 1 second.)

NoticeWhen setting the specifications and functions of this controller, connect terminals 1 and 2 for power supply first,
then set them referring to Section “5. Settings” before performing “3. Mounting to the control panel” and “4. Wiring”.

3. Mounting to the control panel
3.1 Site selection

CautionUse within the following temperature and humidity ranges.
Temperature: 0 to 50 (32 to 122 ), Humidity: 35 to 85%RH (No icing, non-condensing)If the JCS-33A is installed through the face of a control panel, the ambient temperature of the JCS-33A must be
kept to under 50 . Otherwise the life of electronic parts (especially electrolytic capacitors) of the JCS-33A will be
shortened.
This instrument is intended to be used under the following environmental conditions(IEC61010-1): Overvoltage category , Pollution degree 2
Ensure the mounting location corresponds to the following conditions:• A minimum of dust, and an absence of corrosive gases• No flammable, explosive gases• No mechanical vibrations or shocks• No exposure to direct sunlight, an ambient temperature of 0 to 50 (32 to 122 ) that does not change rapidly• An ambient non-condensing humidity of 35 to 85%RH• No large capacity electromagnetic switches or cables through which large current is flowing• No water, oil or chemicals or where the vapors of these substances can come into direct contact with thecontroller23.2 External dimensions (Scale: mm)

Terminal cover (TC option)

Screw type mounting bracket

44.5
59.7

Gasket

11.5

48

95
101 (When terminal cover is used)(Fig. 3.2-1)

45 +0.5075

45 +0.50

3.3 Panel cutout (Scale: mm)

n x 48-3 +0.50Lateral close mounting
n: Number of units mounted

Caution: If lateral close mounting is used for the controller,
IP66 specification (Drip-proof/Dust-proof) may becompromised, and all warranties will be invalidated.

45 +0.5
0(Fig. 3.3-1)
3.4 CT (Current transformer) external dimensions (Scale: mm)

CTL-6S (for 5A, 10A, 20A)

CTL-12-S36-10L1U (for 50A)

(Fig. 3.4-1)

3.5 Mounting

CautionAs the case is made of resin, do not use excessive force while screwing in the mounting bracket,
or the case or screw type mounting bracket could be damaged.
The torque should be 0.12N•m.
Mount the controller vertically to ensure
it adheres to the Drip-proof/Dust-proof
specification (IP66).
Mountable panel thickness: 1 to 8mm
Insert the controller from the front sideof the panel.
Attach the mounting brackets to theslots at the top and bottom of the case,and secure the controller in place withthe screws provided.

(Fig.3.5-1)
3

4. Wiring
Warning
Turn the power supply to the instrument off before wiring or checking.
Working on or touching the terminal with the power switched on may result in severe injury or
death due to Electric Shock.

• OUT1 : Control output 1• OUT2 : Control output 2• A1: Alarm 1 output• EVT : Event output (A2 output, Heater burnout
alarm output, Loop break alarm output)• CT: CT input• SV2: SV1/SV2 external selection• RS-485: Serial communication (RS-485)• TC: Thermocouple input• RTD : Resistance temperature detector input• DC: DC current, DC voltage input
For DC current input, a 50 shunt
resistor (sold separately) must beconnected between input terminals.
(Fig. 4-1)

Caution• The terminal block of the JCS-33A is designed to be wired from the left side.
The lead wire must be inserted from the left side of the terminal, and fastened by the terminal screw.
• Dotted lines show options.
• Use a thermocouple and compensating lead wire that correspond to the sensor input specification of thiscontroller.
• Use the 3-wire RTD which corresponds to the input specification of this controller.
• This instrument does not have a built-in power switch, circuit breaker or fuse.
Be sure to install a built-in power switch, circuit breaker or fuse near the controller.
(Recommended fuse: Time-lag fuse, rated voltage 250V AC, rated current 2A)• For a 24V AC/DC power source, do not confuse polarity when using direct current (DC).
• When using a relay contact output type, use a relay externally according to the capacity of the load toprotect the built-in relay contact.
• When wiring, keep input wires (thermocouple, RTD, etc.) away from AC sources or load wires.
• Do not apply a commercial power source to the sensor connected to the input terminal nor allow thepower source to come into contact with the sensor.

Solderlessterminal

Y-typeRing-type

Manufacturer
Nichifu Terminal Industries CO.,LTD.
Japan Solderless Terminal MFG CO.,LTD.
Nichifu Terminal Industries CO.,LTD.
Japan Solderless Terminal MFG CO.,LTD.

Model

TorqueTMEV1.25Y-3
VD1.25-B3A
TMEV1.25-3
V1.25-3

0.63N•m

Heater burnout alarm option(1) This alarm is not usable for detecting heater current
under phase control.
(2) Use the current transformer (CT) provided, and pass one
lead wire of the heater circuit into the hole of the CT.
(3) When wiring, keep the CT wire away from AC sources
or load wires to avoid external interference.

CT

3.2mm

(Fig. 4-2)

(11)
CT input terminal
(12)
Power
supply(Fig. 4-3)
Heater4

5.8mm or less 5.8mm or lessLead wire solderless terminal
Use a solderless terminal with an insulation sleeve in which an M3 screw fits as shown below.
The torque should be 0.63N•m.
3.2mm

5. Settings
5.1 Operation flowchart

Output MV (manipulated
variable) indication

Control output OFF [] or
Auto/Manual control switching

PV/SV display mode

(Approx. 1 sec)

(Approx. 3 sec)+
[Main setting mode][Sub setting mode]
SV1
AT/Auto-reset
[
]
[
]
SV2
[

]

+
+
(Approx. 3 sec)
(Approx. 3 sec)
[Auxiliary function setting mode 1] [Auxiliary function setting mode 2]
Set value lock
Input type[][]

OUT1 proportional band[]

SV high limit[]

Scaling high limit[]

A2 type[]

OUT2 proportional band[]

SV low limit[]

Scaling low limit[]

A1 Energized/De-energized[]Integral time[]Sensor correction[]

Decimal point place[]

A2 Energized/De-energized[]

Derivative time[]

Communication protocol[]

PV filter time constant[]A1 hysteresis
[
]

ARW
[

Instrument number[]

OUT1 high limit[]

A2 hysteresis[]

OUT1 proportional cycle[]

Communication speed[]

OUT1 low limit[]

A1 action delay timer[]

OUT2 proportional cycle[]

Parity[]OUT1 ON/OFF hysteresis[]

A2 action delay timer[]

A1 value[]

Stop bit[]

OUT2 action mode[]

Direct/Reverse action[]

A2 value[]

OUT2 high limit[]

AT bias[]Heater burnout alarm value[. ]OUT2 low limit[]

SVTC bias[]

Loop break alarm time[]

Overlap/Dead band[]SV2 indication[]

Loop break alarm span[]

OUT2 ON/OFF hysteresis[]

Output status when input abnormal[]

A1 type[]

OUT/OFF Key function[]][Explanation of thekey]•: If thekey is pressed, the set value is saved, and the controller proceeds to the next setting item.
• If thekey is pressed for approx. 3 sec, the controller reverts to the PV/SV display mode from any mode.
[Key operation]•+: Press thewhile pressing the
key.
•+(Approx. 3 sec) : Press thefor approx. 3 sec while holding down the•+(Approx. 3 sec) : Press thefor approx. 3 sec while holding down the• Dotted lines are optional, and they appear only when the options are added.
5

key.
key.

Wire the power terminals only. After the power is turned on, the sensor input characters and temperature unit /are indicated on the PV display, and the input range high limit value is indicated on the SV display for approximately
3 seconds. (For DC current and voltage input, the scaling high limit value is indicated.) (Table 5.1-1)
During this time, all outputs and the LED indicators are in OFF status.
Control will then start, indicating PV (process variable) on the PV display and SV (desired value) on the SV display.
(While Control output OFF function is working,is indicated on the PV display.)(Table 5.1-1)
Sensor input
K
J
R
S
B
E
T
N
PLC (W/Re5-26)
Pt100
JPt100
Pt100
JPt1004 to 20mA DC
0 to 20mA DC
0 to 1V DC
0 to 5V DC
1 to 5V DC
0 to 10V DC

PV
display

SV display(Default)

Setting range

PVdisplay

SV display(Default)

Setting range–200 to 1370
–199.9 to 400.0–200 to 1000
0 to 1760
0 to 1760
0 to 1820–200 to 800–199.9 to 400.0–200 to 1300
0 to 1390
0 to 2315–199.9 to 850.0–199.9 to 500.0–200 to 850–200 to 500–320 to 2500
–199.9 to 750.0–320 to 1800
0 to 3200
0 to 3200
0 to 3300–320 to 1500
–199.9 to 750.0–320 to 2300
0 to 2500
0 to 4200–199.9 to 999.9–199.9 to 900.0–300 to1500–300 to 900–1999 to 9999

–1999 to 9999

5.2 Main setting mode
Character
Name, Function, Setting range
SV1• Sets SV1.
• Setting range: SV low limit to SV high limit value
SV2• Sets SV2.
• Available only when the SM option is applied.
• Setting range: SV low limit to SV high limit value

Default value
00

5.3 Sub setting mode
Character
Name, Function, Setting range
Default value
AT/Auto-reset• Selects AT (auto-tuning) Perform/Cancel or Auto-reset Perform/Cancel.
• If the AT is cancelled during the process, P, I, D and ARW values revert to the previous value
at which AT was performed.
• When AT has not finished 4 hours after starting, it is automatically cancelled.
• Auto-reset ends 4 minutes after starting. It cannot be released while performing this function.
•: AT/Auto-reset Cancel/: AT/Auto-reset Perform
OUT1 proportional band10
• Sets the proportional band for OUT1.
• OUT1 becomes ON/OFF control when set to 0 or 0.0.
• Setting range: 0 to 1000 (2000 ), 0.0 to 999.9 ( ) or 0.0 to 100.0%
OUT2 proportional band
1.0 times• Sets the proportional band for OUT2.
• OUT2 becomes ON/OFF control when OUT1 proportional band is set to 0 or 0.0.
• Not available if DT option is not added or if OUT1 is in ON/OFF control.
• Setting range: 0.0 to 10.0 times (multiplying factor to OUT1 proportional band)
6

. ,
XX.X
alternating
display

Integral time
200 seconds• Sets integral time for OUT1.
• Setting the value to 0 disables the function.
• Not available if OUT1 is in ON/OFF control.
• Auto-reset can be performed when PD is control action (I=0).
• Setting range: 0 to 1000 seconds
Derivative time
50 seconds• Sets derivative time for OUT1.
• Setting the value to 0 disables the function.
• Not available if OUT1 is in ON/OFF control.
• Setting range: 0 to 300 seconds
ARW
50%• Sets ARW for OUT1.
• Available only when PID is the control action.
• Setting range: 0 to 100%
OUT1 proportional cycle
30 seconds,
3 seconds• Sets proportional cycle for OUT1.
• Not available for DC current output type or if OUT1 is in ON/OFF control.
• Setting range: 1 to 120 seconds
OUT2 proportional cycle
3 seconds• Sets proportional cycle for OUT2.
• Not available if the DT option is not added or if OUT2 is in ON/OFF control.
• Setting range: 1 to 120 seconds
A1 value0• Sets A1 output action point.
Setting the value to 0 or 0.0 disables the function (except Process high and Process low alarm).
• Not available if No alarm action is selected during A1 type selection.
• Setting range: Refer to (Table 5.3-1).
A2 value0• Sets A2 output action point.
Setting the value to 0 or 0.0 disables the function (except Process high and Process low alarm).
• Not available if A2 option is not added or if No alarm action is selected during A2 type selection.
• Setting range: Refer to (Table 5.3-1).
Heater burnout alarm value
0.0A• Sets the heater current value for Heater burnout alarm.
• Upon returning to set limits, the alarm will stop.
• Available only when the W option is added.
• Rated current: 5A (0.0 to 5.0A),
10A (0.0 to 10.0A)
20A (0.0 to 20.0A), 50A (0.0 to 50.0A)
Loop break alarm time
0 minutes• Sets the time to assess the Loop break alarm.
• Available only when the LA option is added.
• Setting range: 0 to 200 minutes
Loop break alarm span0
• Sets the temperature to assess the Loop break alarm.
• Available only when the LA option is added.
• Setting range: 0 to 150 ( ), 0.0 to 150.0 ( ) or 0 to 1500

(Table 5.3-1)
Alarm typeHigh limit alarm
Low limit alarm
High/Low limits alarm
High/Low limit range alarm
Process high alarm
Process low alarmHigh limit alarm with standby
Low limit alarm with standby
High/Low limits alarm with standby

Setting range– (Input span) to input span ( )*1– (Input span) to input span ( )*10 to input span ( )*10 to input span ( )*1Input range low limit value to input range high limit value *2
Input range low limit value to input range high limit value *2– (Input span) to input span ( )*1– (Input span) to input span ( )*10 to input span ( )*1• When input has a decimal point, the negative low limit value is –199.9, and the positive high limit value is 999.9.
• All alarm actions except process alarm are the deviation setting from the SV (desired value).
*1: For DC input, the input span is the same as the scaling span.
*2: For DC input, input range low (or high) limit value is the same as scaling low (or high) limit value.
75.4 Auxiliary function setting mode 1
Character
Name, Function, Setting range
Default value
Set value lock
Unlock• Locks the set values to prevent setting errors.
The setting item to be locked depends on the selection.
• When Lock 1 or Lock 2 is selected, AT (auto-tuning) and Auto-reset cannot be carried out.
•
(Unlock): All set values can be changed.
(Lock 1): None of the set values can be changed.
(Lock 2): Only main setting mode can be changed.
(Lock 3): All set values except input type can be changed. However, they return to theirprevious value after power is turned off because they are not saved in the non-volatilememory. Be sure to select Lock 3 when changing the set value frequently via
communication function. (If the value set by the communication function is the same as
the value before the setting, the value will not be written in the non-volatile memory.)
Do not change any setting item in Auxiliary function setting mode 2. If any item in themode is changed, it will affect other setting items such as the SV and Alarm value.
SV high limit
Input range• Sets the SV (desired value) high limit value.
high limit value• Setting range: SV low limit to input range high limit value,or SV low limit to scaling high limit value
SV low limit
Input range• Sets the SV (desired value) low limit value.
low limit value• Setting range: Input range low limit to SV high limit value,or scaling low limit to SV high limit value
Sensor correction
0.0• Sets the correction value for the sensor.
• Setting range: –100.0 to 100.0 ( ), or –1000 to 1000
Communication protocol
Shinko protocol• Selects communication protocol.
• Available only when the C5 option is added.
•: Shinko protocol,: Modbus ASCII mode,: Modbus RTU mode
Instrument number0• Sets the instrument number individually to each instrument when communicatingby connecting plural instruments in Serial communication.
• Available only when C5 option is added.
• Setting range: 0 to 95
Communication speed
9600bps• Selects a communication speed equal to that of the host computer.
• Available only when C5 option is added.
•: 2400bps,: 4800bps,: 9600bps,: 19200bps
ParityEven parity• Selects the parity.
• Not available if the C5 option is not added or if Shinko protocol is selectedduring the Communication protocol selection.
•: No parity,: Even parity,: Odd parity
Stop bit1• Selects the stop bit.
• Not available if the C5 option is not added or if Shinko protocol is selectedduring the Communication protocol selection.
•: Stop bit 1,: Stop bit 2
5.5 Auxiliary function setting mode 2
Character

Name, Function, Setting range
Default value
Input typeK (–200 to 1370 )• The input type can be selected from thermocouple (10 types), RTD (2 types), DC current(2 types) and DC voltage (4 types), and the unit / can be selected as well. (Table 5.1-1)• When changing the input from DC voltage to other inputs, remove the sensor
connected to this controller first, then change the input. If the input is changed withthe sensor connected, the input circuit may break.
Scaling high limit
9999• Sets scaling high limit value.
• Available only for DC input.
• Setting range: Scaling low limit value to input range high limit value
Scaling low limit–1999• Sets scaling low limit value.
• Available only for DC input.
• Setting range: Input range low limit value to scaling high limit value
8

Decimal point place
No decimal point• Selects decimal point place.
• Available only for DC input.
•: No decimal point: 1 digit after decimal point: 2 digits after decimal point: 3 digits after decimal point
PV filter time constant
0.0 seconds• Sets PV filter time constant. (If the value is set too large, it affects control results due tothe delay of response.)• Setting range: 0.0 to 10.0 seconds
OUT1 high limit
100%• Sets OUT1 high limit value.
• Not available if OUT1 is in ON/OFF control.
• Setting range: OUT1 low limit value to 100%
(DC current output type: OUT1 low limit value to 105%)
OUT1 low limit0%• Sets OUT1 low limit value.
Not available if OUT1 is in ON/OFF control.
• Setting range: 0% to OUT1 high limit value(DC current output type: –5% to OUT1 high limit value)
OUT1 ON/OFF hysteresis
1.0• Sets ON/OFF hysteresis for OUT1.
• Available only when OUT1 is in ON/OFF control.
• Setting range: 0.1 to 100.0 ( ), or 1 to 1000
OUT2 action mode
Air cooling• Selects OUT2 action from air, oil and water cooling.
• Not available if the DT option is not added or if OUT2 is in ON/OFF control.
•: Air cooling,: Oil cooling,: Water cooling
OUT2 high limit
100%• Sets OUT2 high limit value.
• Not available if the DT option is not added or if OUT2 is in ON/OFF control.
• Setting range: OUT2 low limit value to 100%
OUT2 low limit0%• Sets OUT2 low limit value.
• Not available if the DT option is not added or if OUT2 is in ON/OFF control.
• Setting range: 0% to OUT2 high limit value
Overlap band/Dead band0
• Sets the overlap band or dead band for OUT1 and OUT2.
+ set value: Dead band, – set value: Overlap band
• Available only when the DT option is added.
• Setting range: -100.0 to 100.0 ( ), or -1000 to 1000
OUT2 ON/OFF hysteresis
1.0• Sets ON/OFF hysteresis for OUT2.
• Available when the DT option is added and when OUT2 is in ON/OFF control.
• Setting range: 0.1 to 100.0 ( ), or 1 to 1000
A1 typeNo alarm action• Selects A1 action type.
Note: If an alarm type is changed, the alarm set value becomes 0 (0.0).
: No alarm action: Process high alarm: High limit alarm: Process low alarm: Low limit alarm: High limit alarm with standby: High/Low limits alarm: Low limit alarm with standby: High/Low limit range alarm: High/Low limits alarm with standby
A2 typeNo alarm action• Selects A2 action type.
Note: If an alarm type is changed, the alarm set value becomes 0 (0.0).
• Available only when A2 option is added.
• Types and action are the same as those of A1 type selection.
A1 action Energized/De-energized
Energized• Selects Energized/De-energized for A1.
• Not available if No alarm action is selected during A1 type selection.
•: Energized,: De-energized9

A2 action Energized/De-energized
Energized• Selects Energized/De-energized for A2.
• Not available if A2 option is not added or if No alarm action is selected during A2 type selection.
•: Energized,: De-energizedA1 hysteresis
1.0• Sets A1 hysteresis.
• Not available if No alarm action is selected during A1 type selection.
• Setting range: 0.1 to 100.0 ( ), or 1 to 1000
A2 hysteresis
1.0• Sets A2 hysteresis.
• Not available if A2 option is not added or if No alarm action is selected during A2 type selection.
• Setting range: 0.1 to 100.0 ( ), or 1 to 1000
A1 action delay timer
0 seconds• Sets A1 action delay timer.
When setting time has passed after the input enters the alarm output range, the alarm isactivated.
• Not available if No alarm action is selected during A1 type selection.
• Setting range: 0 to 9999 seconds
A2 action delay timer
0 seconds• Sets A2 action delay timer.
When setting time has passed after the input enters the alarm output range, the alarm isactivated.
• Not available if A2 option is not added or if No alarm action is selected during A2 type selection.
• Setting range: 0 to 9999 seconds
Direct/ Reverse action
Reverse (Heating)• Selects Reverse (Heating) or Direct (Cooling) control action.
action•: Reverse (Heating) action,: Direct (Cooling) action
AT bias20• Sets bias value during AT (auto-tuning).
• Not available for DC input.
• Setting range: 0 to 50 (0 to 100 ), or 0.0 to 50.0 (0.0 to100.0 )SVTC bias
0• Desired value (SV) adds SVTC bias value to the value received by the SVTC command.
• Available only when C5 option is added.
• Setting range: Converted value of 20% of the rated value or 20% of the scaling range
SV2 indication
Indication• Selects either Indication or No indication of SV2.
• Available only when the SM option is added.
•: Indication,: No indication
Output status when input abnormal
Outputs OFF (4mA) or OUT1
• Selects OUT1, OUT2 (DT option) status when DC input is(OUT2) low limit value.
overscale or underscale.
• Available only for DC current output with DC input.
•: Outputs OFF (4mA) or OUT1 (OUT2) low limit value.
: Outputs a value between OFF (4mA) and ON (20mA) or between OUT1 (OUT2)
low limit value and OUT1 (OUT2) high limit value, depending on a deviation.
OUT/OFF Key function
Control output OFF function• Selects the OUT/OFF Key function if it is used for Control output OFF function or
for Auto/Manual control switching.
•: Control output OFF function,: Auto/Manual control switching
Sensor correction function
This corrects the input value from the sensor. When a sensor cannot be set at a location where control isdesired, the sensor measured temperature may deviate from the temperature in the controlled location.
When controlling with plural controllers, sometimes the measured temperatures (PV) do not concur due todifferences in sensor accuracy or dispersion of load capacities.
In such a case, the control can be set at the desired temperature by adjusting the input value of sensors.
However, it is effective within the input rated range regardless of the sensor correction value.
PV after sensor correction = Current PV+ (Sensor correction value)
Alarm Energized/De-energized
When [alarm action Energized] is selected, the alarm output (between terminals 3-4, or 3-5) is conducted (ON) while
the alarm output indicator is lit. The alarm output is not conducted (OFF) while the alarm output indicator is not lit.
When [alarm action De-energized] is selected, the alarm output (between terminals 3-4, or 3-5) is notconducted (OFF) while the alarm output indicator is lit. The alarm output is conducted (ON) while the alarm
output indicator is not lit.
10High limit alarm (when Energized is set)
A1 hysteresis

High limit alarm (when De-energized is set)
A1 hysteresis

ON
OFF

ON
OFF

SV
+A1 value(Fig. 5.5-1)

6. OperationSV+A1 value(Fig. 5.5-2)

After the unit is mounted to the control panel and wiring is completed, operate the unit following the procedures below.
(1) Switch power supply to the JCS-33A ON.
• For approx. 3 sec after the power is switched ON, the sensor input characters and the temperature unit /are indicated on the PV display, and input range high limit value is indicated on the SV display.
(For DC current and voltage input, scaling high limit value is indicated.) See (Table 5.1-1).
During this time, all outputs and LED indicators are in OFF status.
• Control will then start, indicating PV (process variable) on the PV display, and SV (desired value) on the SV
display.
• While the Control output OFF function is working,is indicated on the PV display.
(2) Input each set value. Refer to “5. Settings”.
(3) Turn the load circuit power ON.
Control action starts so as to keep the control target at the SV (desired value).

7. Action explanation
7.1 OUT1 action

Heating ( Reverse ) action

Cooling ( Direct ) action
Proportional band

Proportional band
ON

ON

Controlaction
OFF

OFF
SV

SV
Relay contact
output

6

6

6

7

7

7

Cycle action is performed according to deviation

Non- contact
voltage output+ 6+ 6
12 V DC
12/0V DC
7
7

6

6

6

7

7

7

Cycle action is performed according to deviation+6+6
0 V DC

0V DC

7

7

+6
+6
0/12 V DC
12 V DC
7
7

Cycle action is performed according to deviation Cycle action is performed according to deviation

DC current
outputIndicator( OUT1 ) Green

+ 6
+ 6
+6
20mA DC 20 to 4 mA DC
4mA DC
7
7
7

+ 6
+6
+6
4mA DC 4 to 20 mA DC
20 mA DC7
7
7

Changes continuously according to deviation

Changes continuously according to deviation

Unlit

Lit

Unlit

Lit

: Acts ON (lit) orOFF (unlit).

7.2 OUT1 ON/OFF control action
Heating ( Reverse ) action

Cooling (Direct) action

Hysteresis
ControlactionHysteresis

ON

ON

OFF

OFF
SV

Relay contact
outputNon- contact
voltage output
DC current
outputIndicator(OUT1) Green

SV

6

6

6

6

7

7

7

7

+ 6

+ 6

12V DC
7+ 6

20mA DC
7
Lit

+ 6

0V DC

+6

0V DC

12V DC

7

7

7

+ 6

+ 6

+6

4 mA DC
7Unlit

4 mA DC
7

Unlit

11

20mA DC
7
Lit: Acts ON (lit) orOFF (unlit).

7.3 EVT (Heater burnout alarm) actionON
OutputOFF

Alarm action

Heater burnout alarm value
Small
Large
Load current

3

3

5

5

Indicator
Lit

Unlit

7.4 Alarm action
High limit alarm
A1 hysteresis
Alarm
actionHigh/ Low limits alarm
A1 hysteresis

ON

ON

ON

OFF

OFF
-A1 value SV
SV +A1 value-A1 value+A1 value
High/Low limit range alarm
Process high alarm
A1 hysteresis
A1 hysteresis

OFF

ON

Alarm
actionOFF
A1 value SV
A1 valueHigh limit alarm with standby
A1 hysteresis
Alarm
actionLow limit alarm
A1 hysteresis

ON

ON

ON

OFF

OFF

A1 value
High/Low limits alarm with standby
A1 hysteresis

A1 value
Low limit alarm with standby
A1 hysteresis

ON

ON

OFF
-A1 value SV+A1 valueA1 valueA1 value
SV
Process low alarm
A1 hysteresis

OFF

OFF
-A1 valueSV

A1 value+A1 valueA1 valueSV: Standby functions.
A1 indicator lights when A1 output terminals 3 and 4 are connected, and goes off when they are disconnected.
7.5 OUT2 (Heating/Cooling control) action
Heating P- band

7.6 OUT2 (Heating/Cooling control) action(When setting Overlap band)( Cooling P- band)

ON

Cooling P-band( Coolingaction )HeatingactionControlactionOFF

Relay contact
output (OUT1)

Heating P- band

ON

OFF

SV

6

6

6

7

7

7

Overlap
band

ON
ControlactionON

Heatingaction( Coolingaction)OFF
Cycle action is performed according to deviation.

Non-contact
voltage output( OUT1)+6
12 V DC-7+6
12/0 V DC-7+6
0 V DC-7+620mA DC-7+6
20 to 4mA DC-7+6

DC current
output(OUT1)

Relay contact
output (OUT1)

6

6

6

7

7

7

Cycle action is performed according to deviation.
.

Cycle action is performed according to deviation.

Non- contact
relay output(OUT 2)4 mA DC-7

Changes continuously according to deviation .

Non- contact
relay output( OUT 2)

OFF
SV

3

3

3

5

5

5

3

3

3

5

5

5

Cycle action is performed according to deviation .

Cycle action is performed according to deviation .

Indicator(OUT1)Green

Lit

Unlit

Indicator(OUT2) Yellow

Unlit

Lit

Indicator(OUT1) Green

Lit

Unlit

Indicator(OUT 2)Yellow

Unlit

Lit

: Acts ON (lit) or OFF (unlit).
: Represents Heating control action.

: Acts ON (lit) or OFF (unlit).

: Represents Cooling control action.

: Represents Heating control action.
: Represents Cooling control action.
12

7.7 OUT2 (Heating/Cooling control) action (When setting Dead band)
Heating P- band

(Cooling P-band)

Dead band

ON

ON
ControlactionHeatingactionOFF

Relay contact
output (OUT1)

6

6

7

7

SV

( Coolingaction )OFF
6
7

Cycle action is performed according to deviation .

Non - contact
voltage output(OUT1)+6
12 V DC-7+6
12/ 0V DC-7+6

DC current
output (OUT1)+6
20 mA DC
-7

+6
20 to 4 mA DC-7+6

0 V DC-7

Cycle action is performed according to deviation.

4mA DC-7

Changes continuously according to deviation .

Non- contact
relay output(OUT 2 )

3

3

3

5

5

5

Cycle action is performed according to deviation .

Indicator(OUT1) Green

Lit

Unlit

Indicator(OUT2)Yellow

Unlit

Lit

: Acts ON (lit) orOFF (unlit).
: Represents Heating
control action.
: Represents Cooling
control action.

8. AT of this controller

In order to set each value of P, I, D and ARW automatically, the AT (auto-tuning) process should be made tofluctuate to obtain an optimal value. One of 3 types of fluctuation below is automatically selected.
For DC input, the AT process will fluctuate around the SV for conditions of (A), (B) and (C) below.
Sometimes the AT process will not fluctuate if AT is performed at or near room temperature.
Therefore AT might not finish normally.
(A) In the case of a large difference between the SV and PV (process variable) as the temperature is rising
When AT bias is set to 20 , the AT process will fluctuate at a temperature 20 lower than the SV.
Temperature 20 lower than the SV(1) Calculating PID constantSV(2) PID constant calculated(4)(3) Controlled by the PID constantset by AT (auto-tuning).
Temperature(4) AT bias value
Time

AT starting point
(1)

(2)

(3)

(B) When the control is stable
The AT process will fluctuate around the SV.
SV(1) Calculating PID constant(2) PID constant calculated(3) Controlled by the PID constantset by AT (auto-tuning).

TemperatureTime

AT starting point
(1)

(2)

(3)

(C) In the case of a large difference between the SV and PV (process variable) as the temperature is falling
When AT bias is set to 20 , the AT process will fluctuate at a temperature 20 higher than the SV.
Temperature 20 higher than the SV(1) Calculating PID constantTemperature(2) PID constant calculated(3) Controlled by the PID constant(4)
SV
set by AT (auto-tuning).
(4) AT bias value
Time

AT starting point
(1)

(2)

(3)

13

9. Specifications

9.1 Standard specifications
Mounting: FlushSetting: Input system using membrane sheet key
Display
PV display: Red LED 4 digits, character size 10.2 x 4.9 mm (H x W)
SV display: Green LED 4 digits, character size 8.8 x 4.9 mm (H x W)
Accuracy (Setting and Indication):
Thermocouple : Within 0.2% of each input span 1digit, or within 2 (4 ),whichever is greater
However R, S inputs, 0 to 200 (400 ): Within 6 (12 )B input, 0 to 300 (600 ): Accuracy is not guaranteed.
K, J, E, T, N inputs, less than 0 (32 ): Within 0.4% of each input span 1digit
RTD: Within 0.1% of each input span 1digit, orwithin 1 (2 ), whichever is greater
DC current: Within 0.2% of each input span 1digit
DC voltage: Within 0.2% of each input span 1digit
Input sampling period: 250ms
Input
Thermocouple : K, J, R, S, B, E, T, N, PL- , C(W/Re5-26) External resistance: 100 or less(However, B input: External resistance: 40 or less)
RTD: Pt100, JPt100, 3-wire system
Allowable input lead wire resistance (10 or less per wire)
DC current: 0 to 20mA DC, 4 to 20mA DC
Input impedance: 50 [50 shunt resistor (sold separately) must be
installed between input terminals.] Allowable input current: 50mA or less
DC voltage: 0 to 1V DC: Input impedance: 1M or more
Allowable input voltage: 5V DC or less
Allowable signal source resistance: 2k or less
: 0 to 5V DC, 1 to 5V DC, 0 to 10V DC: Input impedance: 100k or more
Allowable input voltage: 15V DC or less
Allowable signal source resistance: 100 or less
OUT1 output
Relay contact : 1a, Control capacity 3A 250V AC (resistive load)
1A 250V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
Non-contact voltage (For SSR drive): 12+20V DC, Maximum 40mA (short circuit protected)
DC current: 4 to 20mA DC, Load resistance: Maximum 550
A1 output
Action: ON/OFF action
Hysteresis: 0.1 to 100.0 ( ), or 1 to 1000
Output: Relay contact: 1aControl capacity: 3A 250V AC (resistive load)
Electrical life: 100,000 cycles
Control action
PID control (with AT function)
PI control: When derivative time is set to 0
PD control (with auto-reset function): When integral time is set to 0
P control (with auto-reset function): When derivative and integral times are set to 0
ON/OFF control: When proportional band is set to 0 or 0.0
OUT1 proportional band : 0 to 1000 (2000 ), 0.0 to 999.9 ( ) or 0.0 to 100.0%(ON/OFF control when set to 0 or 0.0)
Integral time
: 0 to 1000 sec (OFF when set to 0)
Derivative time
: 0 to 300 sec (OFF when set to 0)
OUT1 proportional cycle : 1 to 120 sec (Not available for DC current output type)
ARW: 0 to 100%
OUT1 ON/OFF hysteresis: 0.1 to 100.0 ( ), or 1 to 1000
OUT1 high limit: 0 to 100% (DC current output type: –5 to 105%)
OUT1 low limit: 0 to 100% (DC current output type: –5 to 105%)
Circuit insulation configuration
Electrically insulated

1
2
3
4
5

Power
r
supply

A1

11
12
13
14

CT
input
SV2

OUT1
13
Communication 14
15

CPU

Input

6
7
8
9
10

EVT(A2,LA,W) or OUT2 ( DT )When OUT1 is non-contact voltage output or DC current output, OUT1 is not insulated from Communication,
and OUT1 is not insulated from SV2. So an insulation test must not be carried out between them.
14

Insulation resistance : 10M or more, at 500V DC
Dielectric strength: 1.5kV AC for 1 minute between input terminal and power terminal
1.5kV AC for 1 minute between output terminal and power terminal
Supply voltage: 100 to 240V AC 50/60Hz, 24V AC/DC 50/60Hz
Allowable voltage fluctuation: 100 to 240V AC: 85 to 264V AC, 24V AC/DC: 20 to 28V AC/DCPower consumption : Approx. 8VA
Ambient temperature : 0 to 50 (32 to 122 )Ambient humidity: 35 to 85%RH (non-condensing)
Weight: Approx. 200g
External dimensions : 48 x 48 x 95mm (W x H x D)
Material: Flame-resistant resin (Case)
Color: Light gray (Case)
Drip-proof/Dust-proof : IP66 for the front panel
Attached functions: [Set value lock], [Sensor correction], [Auto/manual control switching],[Input error indication]
Output status
Output status
Contents and
OUT1
OUT2
when input
Indication
abnormal (*1)
Direct action
Reverse action
Direct action
Reverse action
Overscale
Measured value
has exceeded
Indication range
high limit value.
"" flashes.
Underscale
Measured value
has dropped below
Indication range low
limit value.
"" flashes.

ON (20mA) or
OUT1 highlimit value (*2) OFF (4mA) or
OUT1 low limit
OFF (4mA) or
value
OUT1 low
limit value
ON (20mA) or
OUT1 high limit
OFF (4mA) or
value (*2)
OUT1 low
OFF (4mA) or
limit value
OUT1 low limitvalue

OFF orOUT2 low limit
value

ON or
OUT2 high limit
value (*2)
OFF orOUT2 low limit
value

ON or
OUT2 high limit
value (*2)
OFF orOUT2 low limitvalue

OFF orOUT2 low limitvalue(*1) This is only available for DC input and when OUT1 is DC current output type.
If OUT1 is not DC current output, the output status will be the same one as whenis selectedduring “Output status when input abnormal”.
For manual control, the preset manipulated variable (MV) is outputted.
(*2) Outputs a value between OFF (4mA) and ON (20mA) or between OUT1 (or OUT2) low limit value
and OUT1 (or OUT2) high limit value, depending on deviation.
Thermocouple, RTD input
Input
Input range
Indication range
Control range–199.9 to 400.0–199.9 to 450.0–205.0 to 450.0
K, T–199.9 to 750.0–199.9 to 850.0–209.0 to 850.0–199.9 to 850.0–199.9 to 900.0–210.0 to 900.0–200 to 850–210 to 900–210 to 900
Pt100–199.9 to 999.9–199.9 to 999.9–211.0 to 1099.9–300 to 1500
–318 to 1600
–318 to 1600
–199.9 to 500.0–199.9 to 550.0–206.0 to 550.0–200 to 500–207 to 550–207 to 550
JPt100–199.9 to 900.0–199.9 to 999.9–211.0 to 999.9–300 to 900–312 to 1000
–312 to 1000
Indication range and Control range for thermocouple inputs other than the above:
Input range low limit value –50 (100 ) to Input range high limit value +50 (100 )DC input
Indication range: [Scaling low limit value–Scaling span x 1%] to [Scaling high limit value +Scaling span x 10%]
However, “” or “” flashes when a range of –1999 to 9999 is exceeded.
Control range: [Scaling low limit value–Scaling span x 1%] to [Scaling high limit value +Scaling span x 10%]DC input disconnection
When DC input is disconnected, the PV display flashes “” for 4 to 20mA DC and 1 to 5V DC inputs, and“” for 0 to 1V DC input.
For 0 to 20mA DC, 0 to 5V DC and 0 to 10V DC inputs, the PV display indicates the value corresponding with
0mA or 0V input.
15

[Burnout]
When the thermocouple or RTD input is burnt out, OUT1 and OUT2 are turned off (for DC current output
type, OUT1 low limit value, OUT2 low limit value) and the PV display flashes “”.
[Self-diagnosis]
The CPU is monitored by a watchdog timer, and if an abnormal status is found on the CPU, thecontroller is switched to warm-up status.
[Automatic cold junction temperature compensation] (Only thermocouple input type)This detects the temperature at the connecting terminal between the thermocouple and the instrument, andalways maintains it at the same status as if the reference junction location was at 0 (32 ).
[Power failure countermeasure]
The setting data is backed up in the non-volatile IC memory.
[Warm-up indication]
After the power supply to the instrument is turned on, the sensor input character and temperature unit
/ are indicated on the PV display and input range high limit value is indicated on the SV display for 3
seconds.
For DC current and voltage input, the scaling high limit value is indicated.
Accessories: Screw type mounting brackets: 1 set
Instruction manual: 1 copy
CT (Current transformer): CTL-6S: 1 piece (for rated current 5A, 10A, 20A)
CTL-12-S36-10L1U: 1 piece (for rated current 50A)
9.2 Optional specifications
Alarm 2 (A2) (Option code: A2)[A2], [W] and [LA] options utilize common output terminals.
Action: ON/OFF action
Hysteresis: 0.1 to 100.0 ( ), or 1 to 1000
Output: Relay contact: 1aControl capacity: 3A 250V AC (Resistive load)
Electrical life: 100,000 cycles
Loop break alarm (Option code: LA)
When MV (manipulated variable) is maximum or minimum and when the PV does not change as much as thepreset span within the Loop break alarm assessment time, the alarm is activated.
This also detects the breaking status on the loop such as heater burnout, sensor burnout or actuator trouble.
[LA], [A2] and [W] options utilize common output terminals.
Setting range : Loop break alarm time: 0 to 200 minutes
Loop break alarm span: 0 to 150 ( ), 0.0 to 150.0 ( ), 0 to 1500
Output: Relay contact: 1aControl capacity: 3A 250V AC (Resistive load)
Electrical life: 100,000 cycles
Heater burnout alarm (including sensor burnout alarm) (Option code: W)
Monitors heater current with CT (current transformer), and detects burnout.
This alarm is also activated when indication is overscale or underscale.
[W], [A2] and [LA] options utilize common output terminals.
This option cannot be applied to DC current output type.
Rated current : 5A [W(5A)], 10A [W(10A)], 20A [W(20A)], 50A [W(50A)] (Must be specified.)
Setting range : 5A [W(5A)] : 0.0 to 5.0A (Off when set to 0.0)
10A [W(10A)] : 0.0 to 10.0A (Off when set to 0.0)
20A [W(20A)] : 0.0 to 20.0A (Off when set to 0.0)
50A [W(50A)] : 0.0 to 50.0A (Off when set to 0.0)
Setting accuracy: Within 5% of the rated value
Action: ON/OFF action
Output: Relay contact: 1aControl capacity: 3A 250V AC (resistive load)
Electrical life: 100,000 cycles
Heating/Cooling control (Option code: DT)
The specification of Heating side is the same as that of OUT1.
OUT2 proportional band: 0.0 to 10.0 times OUT1 proportional band (ON/OFF control when set to 0.0)
OUT2 integral time
: The same as that of OUT1.
OUT2 derivative time : The same as that of OUT1.
OUT2 proportional cycle: 1 to 120 seconds
OUT2 high limit setting : 0 to 100%
OUT2 low limit setting : 0 to 100%
Overlap band/Dead band setting range:
Thermocouple, RTD input: –100.0 to 100.0 ( )DC current, DC voltage input: –1000 to 1000 (The placement of the decimal point follows the selection.)
Output: Non-contact relay output, 0.3A 250V AC
Cooling action mode selection:
One cooling action can be selected from Air cooling (linear characteristic), Oil cooling (1.5th powerof the linear characteristic) and Water cooling (2nd power of the linear characteristic) by keypad.
16

Serial communication (Option code: C5)
When this option is added, the [SM] option cannot be added.
The following operations can be carried out from an external computer.
(1) Reading and setting of the SV, PID values and each set value(2) Reading of the PV and action status (3) Function change
Cable length: Maximum communication distance: 1.2km
Cable resistance: Within 50 (Terminators are not necessary, but if used, use
120 or more on one side.)
Communication line
: EIA RS-485
Communication method: Half-duplex communication
Synchronization method: Start-stop synchronization
Communication speed: 2400, 4800, 9600, 19200bps (Selectable by keypad)
Parity: Even, Odd, No parity (Selectable by keypad)
Stop bit: 1, 2 (Selectable by keypad)
Communication protocol: Shinko protocol, Modbus RTU, Modbus ASCII (Selectable by keypad)
Number of units connectable : Maximum 31 units to 1 host computer
Communication error detection : Double detection by parity and checksum
Digital external setting: The SV from the programmable controllers (with the SVTC option) can bedigitally transmitted to the JCS-33A (with the C5 option).
(The Set value lock of the JCS-33A must be set to Lock 3.)
When the data from the programmable controllers is out of the SV high limit or low limit
value, the JCS-33A ignores the value, and performs the control with the previous value.
The control desired value adds SVTC bias value to the value received by the SVTC command.
SV1/SV2 external selection (Option code: SM)
SV1 or SV2 can be selected by the external contact.
When this option is added, the [C5] option cannot be added.
Contact Open between terminals 13-14 : SV1
Contact Closed between terminals 13-14 : SV2
Contact current: 6mA
Color Black (Option code: BK): Front panel frame and case: Black
Terminal cover (Option code: TC): Electrical shock protection terminal cover

10. Troubleshooting

If any malfunctions occur, refer to the following items after checking the power supply to the controller.
10.1 Indication
ProblemPresumed cause and solution• Control output OFF function is working.
The PV display is indicating
Press thekey for approx. 1 second to release the function.
[].
• Thermocouple, RTD or DC voltage (0 to 1V DC) is burnt out.
[
] is flashing on the PV
Change each sensor.
display.
How to check whether the sensor is burnt out[Thermocouple]
If the input terminals of the instrument are shorted, and if a value
around room temperature is indicated, the instrument is likely to be
operating normally, however, the sensor may be burnt out.
[RTD]
If approx. 100 of resistance is connected to the input terminals
between A-B of the instrument and between B-B is shorted, and if
approximate 0 (32 ) is indicated, the instrument is likely to be
operating normally, however, the sensor may be burnt out.
[DC voltage (0 to 1V DC)]If the input terminals of the instrument are shorted, and if a scaling low
limit value is indicated, the instrument is likely to be operating
normally, however, the signal wire may be disconnected.
• Check whether the input terminals of thermocouple, RTD or DC voltage(0 to 1V DC) are securely mounted to the instrument input terminals.
Connect the sensor terminals to the instrument input terminals securely.
• Check whether input signal source for DC voltage (1 to 5V DC) or DC[] is flashing on the PV
current (4 to 20mA DC) is disconnected.
display.
How to check whether the input signal wire is disconnected[DC voltage (1 to 5V DC)]If the input to the input terminals of the instrument is 1V DC and if a
scaling low limit value is indicated, the instrument is likely to be
operating normally, however, the signal wire may be disconnected.
[DC current (4 to 20mA DC)]If the input to the input terminals of the instrument is 4mA DC and if a
scaling low limit value is indicated, the instrument is likely to be
operating normally, however, the signal wire may be disconnected.
• Check whether input signal wire for DC voltage (1 to 5V DC) or DC current(4 to 20mA DC) is securely connected to the instrument input terminals.
• Check if polarity of thermocouple or compensating lead wire is correct.
• Check whether codes (A, B, B) of RTD match with the instrument terminals.
17

The PV display keeps
indicating the value which
was set during Scaling low
limit setting.

The indication of PV display isabnormal or unstable.

The PV display is indicating[].

• Check whether the input signal source for DC voltage (0 to 5V DC, 0 to
10V DC) and DC current (0 to 20mA DC) is disconnected.
How to check whether the input signal wire is disconnected[DC voltage (0 to 5V DC, 0 to 10V DC)]If the input to the input terminals of the instrument is 1V DC and if avalue corresponding to 1V DC is indicated, the instrument is likely to
be operating normally, however, the signal wire may be disconnected.
[DC current (0 to 20mA DC)]If the input to the input terminals of the instrument is 4mA DC and if
a value corresponding to 4mA DC is indicated, the instrument islikely to be operating normally, however, the signal wire may bedisconnected.
• Check whether the input lead wire terminals for DC voltage (0 to 5V DC,
0 to 10V DC) or DC current (0 to 20mA DC) are securely mounted to the
instrument input terminals.
• Check whether sensor input or temperature unit ( or ) is correct.
Select the sensor input and temperature unit ( or ) properly.
• Sensor correction value is unsuitable. Set it to a suitable value.
• Check whether the specification of the sensor is correct.
• AC leaks into the controller input circuit from the sensors.
Use an ungrounded type sensor.
• There may be equipment that interferes with or makes noise near thecontroller.
Keep equipment that interferes with or makes noise away from thecontroller.
• Internal memory is defective.
Contact our agency or us.

10.2 Key operation
ProblemPresumed cause and solution• Unable to set the SV (desired • Set value lock (Lock 1 or Lock 2) is selected.
value), P, I, D, proportional Release the lock selection.
cycle or alarm value.
• During AT or auto-reset.
• The values do not change by
Cancel AT if required.
,keys.
It takes approximately 4 minutes until auto-reset is finished.
The setting indication does not • SV high or low limit value in Auxiliary function setting mode 1 may be setchange in the input range
at the point where the value does not change.
even if the,keys areSet it to a suitable value while in Auxiliary function setting mode 1.
pressed, and new values areunable to be set.
10.3 Control
ProblemTemperature does not rise.

The control output remains in
an ON status.
The control output remains in
an OFF status.

Presumed cause and solution• Sensor is out of order. Replace the sensor.
• Check whether the Sensor or control output terminals are securely
mounted to the instrument input terminals.
Ensure that the sensor or control output terminals are mounted to the
instrument input terminals securely.
• Check whether the wiring of sensor or control output terminals is correct.
• OUT1 or OUT2 low limit value is set to 100% or higher in Auxiliary
function setting mode 2.
Set it to a suitable value.
• OUT1 or OUT2 high limit value is set to 0% or less in Auxiliary function
setting mode 2.
Set it to a suitable value.

• If you have any inquiries, please consult our agency or the vendor where you purchased the unit.

SHINKO TECHNOS CO., LTD.
OVERSEAS DIVISION

Head Office: 2-5-1, Senbahigashi, Minoo, Osaka, Japan
http://www.shinko-technos.co.jp
URL:
E-mail:overseas@shinko-technos.co.jp
18

Tel: +81-72-727-6100
Fax: +81-72-727-7006