取扱説明書

ペーパーレスレコーダ
通信機能(RS485 MODBUS/イーサネット)
形式：GR200

GR2CJ2 2010.01

注）MODBUSⓇは，AEG Schneider Automation International 社の商標または登録商標です。
注）PC-9801 シリーズは，日本電気株式会社の商標または登録商標です。
注）N88-日本語 BASIC は，日本電気株式会社の商標または登録商標です。
注）MS-DOS は，Microsoft Corporation の商標または登録商標です。

ご注意
1. 免責事項
本書の内容は，将来予告なしに変更される事があります。
本書の内容につきましては，正確さを期するため万全の注意を払っておりますが，本書中の誤記や，情報の抜け，あるいは情報の使用に起因する結果生じた間接障害を含むいかなる損害に対しても，弊社は責任をおいかねますので，あらかじめご了承ください。

目次

1. 通信機能について ····················································································································1
1.1 概

要 ·······························································································································1

1.2 MODBUS スレーブ通信機能の概要(RS-485 ｲﾝﾀｰﾌｪｲｽ)································································1
1.3 イーサネット通信機能の概要·································································································2
2. 仕様 ································································································································3

2.1 通信仕様 ····························································································································3
3. 接

続 ································································································································4

3.1 通信端子割付 ······················································································································4
3.2 接

続 ····························································································································5

4. 通信条件設定 ··························································································································6
4.1 設定項目 ····························································································································6
4.2 設定操作方法 ······················································································································7
5. MODBUS 通信プロトコル ·········································································································8
5.1 概

要 ····························································································································8

5.2 メッセージの構成················································································································95.3 スレーブの応答················································································································· 11
5.4 ファンクションコード········································································································ 12
5.5 エラーチェックコード（CRC-16）の算出·············································································· 13
5.6 伝送制御手順 ···················································································································· 15
5.7 FIX 処理 ·························································································································· 17
6. メッセージの詳細 ·················································································································· 18
6.1 ワードデータの読出し［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：03H］ ········································································· 18
6.2 読出し専用ワードデータの読出し［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：04H］ ·························································· 20
6.3 連続ワードデータの書込み［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：10H］ ··································································· 22
7. アドレスマップ と データ形式 ································································································ 24
7.1 データ形式 ······················································································································· 24
7.2 アドレスマップ················································································································· 25
7.3 アドレスマップの補足説明·································································································· 41
8. サンプルプログラム ··············································································································· 51
9. イーサネット通信機能 ············································································································ 56
9.1 LAN ボード仕様 ················································································································ 56
9.2 接続先 ····························································································································· 56
9.3 接続 ································································································································ 56
9.4 イーサネット通信条件設定·································································································· 58
9.5 イーサネット通信条件設定操作方法······················································································ 58
10. FTP サーバ機能 ··················································································································· 59
10.1 FTP サーバ機能説明 ········································································································· 59
10.2 FTP サーバ機能設定 ········································································································· 61
10.3 FTP サーバ機能設定操作方法 ····························································································· 62－i－10.4 FTP サーバ操作方法 ········································································································· 63
11. Web サーバ機能···················································································································· 64
11.1 Web サーバ機能説明 ········································································································· 64
11.2 Web サーバ機能設定 ········································································································· 64
11.3 Web サーバ機能設定操作方法 ····························································································· 64
11.4 Web サーバ操作方法 ········································································································· 65
11.5 Web モニタ画面 ··············································································································· 65
12. E-mail 送信機能 ··················································································································· 68
12.1 E-mail 送信機能説明 ········································································································ 68
12.2 E-mail 機能設定 ·············································································································· 68
12.3 E-mail 機能設定操作方法··································································································· 69
12.4 E-mail の送信テスト操作方法····························································································· 72
12.5 E-mail 送信内容··············································································································· 72
13. MODBUS TCP/IP 機能 ········································································································· 74
13.1 MODBUS TCP/IP 機能説明 ······························································································· 74
13.2 MODBUS TCP/IP 機能設定 ······························································································· 74
13.3 MODBUS TCP/IP 機能設定操作方法 ··················································································· 74
13.4 MODBUS TCP/IP 通信プロトコル ······················································································ 75
14. トラブルシューティング ······································································································· 77

－ii－

1.
1.1 概

通信機能について

要

本機は RS-485 インターフェイスによる通信機能（オプション）と イーサネットインターフェイスによる通信機能（オプション）を備えております。

1.2 MODBUS スレーブ通信機能の概要(RS-485 ｲﾝﾀｰﾌｪｲｽ)
MODBUS スレーブ通信の詳しい使用方法については，第２章～第８章を参照してください。
・ＭＯＤＢＵＳスレーブ通信機能は，上位コンピュータ，プログラマブルコントローラ，

グラフィッ

クパネル等とのデータ送受信が可能です。
・通信システムは，マスタとスレーブから構成されます。1 台のマスタに対し，最大 31 台のスレーブ（本機）を接続可能です。
但し，マスタが一度に通信可能なスレーブは 1 台なので，各スレーブにて設定する「MODBUS ス
テーション No.」によって通信相手を特定します。
・マスタとスレーブが通信を行うためには送受信データのフォーマットが一致している必要があります。
本機では，MODBUS プロトコルによって通信データのフォーマットを定めています。
・パーソナルコンピュータ等，RS-232C インターフェイスを持つ機器をマスタとする時は，RS-232C⇔ RS-485 変換器を使用してください。
［RS-232C ⇔ RS-485 変換器］
（推奨品）
型番:K3SC-10（絶縁タイプ）／(株)オムロン－1－

注）RS-232C ⇔ RS-485 変換器をご使用の際には，変換器 ⇔ マスタ間のケーブル接続にご注意く
ださい。ケーブル接続が間違っていると正常に通信ができません。
また，通信コンバータの通信設定（ボーレート，パリティなど）がある場合には，設定にご注意ください。

1.3 イーサネット通信機能の概要
イーサネット通信機能の詳しい使用方法については，第 10 章~第 11 章を参照してください。
・イーサネット通信機能として，以下の機能がご使用できます。
①

ＦＴＰサーバ機能
パソコンのブラウザ（Internet Explorer Ver.6）や DOS プロンプトを使用してペーパーレスレ
コーダのコンパクトフラッシュに記録されているファイルを取りだすことが出来ます。

②

Web サーバ機能
パソコンのブラウザ（Internet Explorer Ver.6）でペーパーレスレコーダの測定値やイベント情報を確認することが出来ます。

③

E-mail 送信機能
警報発生時や一定周期で E-mail を送信することが出来ます。

④

MODBUS TCP/IP 機能
MODBUS TCP/IP 通信により，上位コンピュータ，プログラマブルコントローラ，グラフィッ
クパネル等とのデータ送受信が可能です。

注）Internet Explorer 以外のブラウザ、例えば、Netscape は、ご使用になれません。

－2－

2.

仕

様

2.1 通信仕様
項 目
電気的仕様
通信方式
同期方式
接続形態
最大接続台数
通信距離
通信速度
データ形式

伝送コード
誤り検出
絶縁

仕 様
EIA RS-485 準拠
2 線式 半 2 重
調歩同期
1：N
31 台
最大 500m（総延長）9600bps，19200bps
データ長
8 ビット
ストップビット 1 ビット
パリティ無し，偶数，奇数（選択可能）
HEX 値（MODBUS RTU モード）
CRC-16
通信部とアースは機能絶縁（耐圧 AC500V）

－3－

3.

接

続

警告
感電防止及び故障防止のため，全ての配線が終了するまで，通電しないでください。

3.1 通信端子割付
信号名
TRX2 －TRX1 ＋

通信用端子－4－

3.2 接続・ケーブルは，シールド付ツイストペア線をご使用ください。
・ケーブルの総延長は，最大 500m です。1 回線にマスターを 1 台，本機を最大で 31 台接続する事ができます。
・回線の両端は，100（1/2W 以上）の終端抵抗によって終端してください。
・ケーブルのシールドは，マスター側で一箇所で接地してください。
・本機へ印加されるノイズレベルが，1000V を超える事が予想される場所に設置してご使用になる場合，
下図の様に，ホスト側にノイズフィルタをご使用になる事をお勧め致します。
推奨ノイズフィルタ:ZRAC2203-11 / TDK

マスター（PC など）RS-232CRS-485

ノイズフィルタ－5－

通信ケーブルGR200

4.

通信条件設定マスターと本機が正しく通信を行う為には，以下の設定が必要です。
・マスターと本機すべての通信条件設定が同一である事。
・1 回線に接続されている，すべての本機に異なった「MODBUS ステーション No.」が設定されている事。（同一の「MODBUS ステーション No.」に設定されているものがない事）

4.1 設定項目
表に設定パラメータを示します。前面キー操作により設定してください。
項目
ステーション No.

1

受け渡し時の値

伝送速度
パリティ設定19200bps
奇数

データ長
ストップビット

8 ビット
1 ビット

設定値の範囲
0～255(0：通信機能停止)
9600bps，19200bps
なし：パリティなし
奇数：奇数パリティ
偶数：偶数パリティ
固定(変更不可)
固定(変更不可)－6－

備考
異なる値を各機器に設定します。
同じ通信条件をマスターおよびすべての機器に設定します。

4.2 設定操作方法
通信条件の設定操作方法を，下記の例により，説明します。
例）偶数パリティ，ステーション No.10 に設定します。
キー操作
SEL

表示
トレンド表示パラメータ設定

∨

本体設定

ENT
∨
ENT
ENT
∨

∨
＜
∨
＜
∨

設定値記憶
通信設定
通信設定
数値入力画面
10
MODUBUS
ステーション No.
MODUBUS 通信速度
9600
MODUBUS パリティ
偶数
フロント通信機能

DISP

設定記憶選択画面

ENT

設定記憶確認画面

ENT
電源 OFF
電源 ON

トレンド表示－トレンド表示ENT

意味
運転状態（トレンド表示）
SEL キーを押すとパラメータ設定画面が表示されます。
∨キーを 2 回押して本体設定を選択します。
（キーを押しすぎた場合は∧キーで戻ります。）
ENT キーを押して設定値記憶を選択します。
∨キーを 7 回押して通信設定を選択します
ENT キーを押すと通信設定画面が表示されます。
ENT キーを押すと数値入力画面が表示されます。
＜＞∧∨キーを使って数値を 10 に変更します。
ENT キーを押すとステーション No.が決定します。
∨キーを押して通信速度を選択します。
＜キーを押して 9600 を選択します。
∨キーを押して MODUBUS パリティを選択します。
＜キーを押して偶数を選択します。
∨キーを押してフロント通信を選択します。
DISP キーを押すと設定を記憶するか否かを選択する画面が表示されます。
ENT キーを押すと設定を記憶します。
（確認画面が表示されます。）
トレンド画面が表示されます。
電源を落とします。
電源を入れ直すと設定が完了します。

－7－

5.
5.1 概

MODBUS 通信プロトコル

要

MODBUS プロトコルによる通信システムでは，常に「マスタから通信を開始し，スレーブがそれに応答する」という形態をとります。
伝送の手順は，以下のようになります。
1） マスタはスレーブに対して，指令メッセージを送信する。
2） スレーブは，受信したメッセージに含まれているステーション No.が自局 No.と一致するか調べる。
3） 一致した場合，指令を実行し，応答メッセージを返送する。
4） 一致しない場合は，受信した指令メッセージを捨て，次の指令メッセージを待ちます。
a） 指令メッセージ中のステーション No.が自局 No.と一致した場合
マスタ→スレーブ

指令メッセージ

マスタ←スレーブ

応答メッセージ

回線上のデータb） 指令メッセージ中のステーション No.が自局 No.と一致しない場合
マスタ→スレーブ

指令メッセージ（応答しない）マスタ←スレーブ

回線上のデータ5） 安全の為，応答メッセージの確認を行い，無応答，エラー発生などの場合は，３回以上のリト
ライをかける構造としてください。
マスタは，指令メッセージ中のステーション No.の指定を行う事により，同一回線上に接続されている，複数のスレーブに対し，個別に通信を行うことができます。

－8－5.2 メッセージの構成
指令メッセージおよび応答メッセージは，ステーション No.，ファンクションコード，データ部，及びエラーチェックコードの 4 つの部分から構成され，この順序で送信します。
ステーション No.（1 バイト）
ファンクションコード（1 バイト）
データ部（2～133 バイト）
エラーチェックコード（CRC-16）（2 バイト）
図5-1 メッセージの構成
以下に，各部分について説明します。

(1) ステーション No.
スレーブの指定番号です。パラメータ「MODBUS ステーション No.」に設定した値と一致したス
レーブのみが指令を処理します。
パラメータ「MODBUS ステーション No.」の設定についての詳細は，4章を参照ください。

(2) ファンクションコード
スレーブに実行させたい機能を指定するためのコードです。
詳細は5.4節を参照ください。

(3) データ部
ファンクションコードを実行するために必要なデータです。データ部の構成は，ファンクション
コードにより異なります。詳細は6章を参照ください。
記録計内のデータは，レジスタ番号が割付けられており，通信にてデータを使用する為には，このレジスタ番号を指定します。
尚，メッセージ上で伝送される，レジスタ番号は，相対アドレスで行います。
相対アドレスの算出は下式にて行います。

相対アドレス = レジスタ番号 の下4桁 －1例えば，あるファンクションコードにて指定するレジスタ番号=40003 の場合，
相対アドレス =（40003 の下 4 桁）－1
= 0002がメッセージ上で使用されます。

－9－

(4) エラーチェックコード
信号伝送での過程でのメッセージの誤り（ビットの変化）を検出するためのコードです。
MODBUS プロトコル（RTU モード）では，CRC-16（Cycric Redundancy Check:周期冗長検査）を使用します。
CRC 算出方法については，5.5節を参照ください。

－10－5.3 スレーブの応答(1) 正常時の応答
スレーブは，それぞれのメッセージに対応した応答メッセージを作成し，返信します。この場合のメッセージの構成も5.2項に示すものと同一です。
データ部の内容はファンクションコードによって異なります。詳細は6章を参照ください。

(2) 異常時の応答
指令メッセージの内容に伝送エラー以外の不具合（実在しないファンクションコードの指定など）があった場合，スレーブはその指令を実行せずに，エラー応答メッセージを作成して返信します。
エラー応答メッセージの構成は，図 5-2に示す通りで，ファンクションコードには，指令メッセー
ジのファンクションコードに 80H を加えた値を使用します。
エラーコードは表 5-1に示します。
ステーション No.
ファンクションコード + 80H
エラーコードエラーチェック（CRC-16）
図5-2 エラー応答メッセージ

表5-1 エラーコード
エラーコード内容
01H
ファンクション・コード不良

02H

03H

説明
実在しないファンクション・コードが指定されました。
ファンクション・コードを確認してください。
レジスタに対するアドレス不 指定したファンクション・コードで使用できな
良い，レジスタ番号の相対アドレスが指定されています。
レジスタの個数不良
個数の指定が大き過ぎる為，レジスタ番号が存在しない領域まで，指定されています。

(3) 無応答
スレーブは以下の場合，指令メッセージを無視し，応答も返しません。
・指令メッセージに指定されたステーション No.と，スレーブに設定されたステーション No.が一致しないとき・エラーチェックコードが一致しないとき，又は伝送エラー（パリティエラー等）を検出したとき。
・メッセージ構成データの間隔が 24 ビットタイム以上空いたとき。
（5.6 伝送制御手順 参照）
・スレーブのステーション No.設定=0 のとき。

－11－

5.4 ファンクションコードMODBUS プロトコルでは，ファンクションコード別にレジスタ番号が割付けられており，各ファン
クションコードは，特定のレジスタ番号に対してのみ作用します。
この対応を，表 5-2に，ファンクション別のメッセージ長さを表 5-3に示します。
表5-2 ファンクションコードと対象アドレス の対応
ファンクションコード
機能
対象
No.
読出し(連続) 保持レジスタ
03H
読出し(連続) 入力レジスタ
04H
書込み･連続 保持レジスタ
10H

番号
4xxxx
3xxxx
4xxxx

レジスタ番号
内容
読出/書込 ワードデータ
読出
ワードデータ
読出/書込 ワードデータ

表5-3 ファンクションコードとメッセージ長さ
ファンクション
コード
03H
04H
10H

指定可能
データ数

内容

ワードデータの読出し
64 ワードワードデータ(読出専用)の読出し 64 ワード
連続ワードデータの書込み
64 ワード－12－[単位：byte]
指令メッセージ 応答メッセージ
最小
最大
最小
最大
8
8
11

8
8
137

7
7
8

133
133
8

5.5 エラーチェックコード（CRC-16）の算出
CRC-16 は 2 バイト（16 ビット）のエラーチェックコードです。計算範囲はメッセージ先頭（ステーション No.）からデータ部の最後尾までです。
スレーブは受信メッセージの CRC を計算し，受信した CRC コードと一致していなければ無応答となります。
CRC-16 の算出フローを図 5-3に示します。

スタート
FFFFH（16 進数）を CR に設定*変数の説明CR:CRC エラーチェックデータ（2 バイト）
I:コマンドメッセージの計算文字の桁
J:CR 計算回数の確認

I＝1 と設定

排他的論理和（XOR）が，CR と指定メッセー
ジの I 文字の 1 文字（1 バイト）ごとに実行され，その結果が CR に設定される。
J＝1 と設定

CR の 右 端 のビットは１か？

NO

YES
CR を 1 ビットだけ右寄せ後，A001H と排他的論理和（XOR）が実行され，その結果がCR に設定される。

CR を 1 ビットだけ右寄せする。

J を１加算NO

8 回の計算を終了
しましたか？
J>8YES
I を１加算NO

全文字の計算を終了しましたか？
I>全文字数YES
終了

図5-3 CRC-16 の算出フロー図－13－（ステーション No.，ファンクションコード
及びデータの順で計算を実行します。）
CR 計算結果が LOW 及び HIGH の順番でメッセージの終わりに加えられます。

－14－

5.6 伝送制御手順(1) マスタの通信方法
マスターは，以下の項目を守って通信を行ってください。
(1-1) 指令メッセージ送信前に，48 ビットタイム以上の空白状態を設ける。
(1-2) 1 つの指令メッセージの各バイト間隔は，24 ビットタイム未満で送信する。
(1-3) 指令メッセージ送信後，24 ビットタイム未満で，受信待機状態に入る。
(1-4) 応答メッセージ受信後，48 ビットタイム以上の空白状態を設け，次の指令メッセージを送信する。
［(1-1)と同義］(1-5) 安全の為，応答メッセージの確認を行い，無応答，エラー発生などの場合は，3 回以上のリトライをかける構造としてください。
注）上記の定義は，最悪値です。安全の為，2～3 倍のマージンを持って，マスタ側プログラムを作成する事を推奨致します。具体的には，9600bps では，空白状態(1-1)は，10ms 以上，バイト
間隔(1-2)，送信から受信への切り替え(1-3)は，1ms 以内になるようプログラムされる事を推奨致します。

(2) 説明1) フレームの検出
本通信システムは，2 線式 RS-485 インターフェースを使用している為，回線上の状態としては，
以下の 2 つの状態があります。
(a) 空白状態（回線上にデータがない状態）(b) 通信状態（回線上にデータが流れている状態）
回線上に接続されている機器は，最初に受信状態にあり，回線をモニタします。回線上に 24
ビットタイム以上の空白状態が現れた時，前のフレームの終了を検出し，次の 24 ビットタイム以
内に，受信待機状態に入ります。回線上にデータが現れると受信を開始し，再び 24 ビットタイム
以上の空白を検出した時に，そのフレームの終了を検出します。つまり，最初の 24 ビットタイム
以上の空白状態から，次に現れた 24 ビットタイム以上の空白状態までに，回線上に現れたデータ
を 1 フレーム（まとまったデータの塊）として，取り込みます。
したがって，1 つのフレーム（指令メッセージ）は，以下の事を守って送信する必要があります。
(1-1) 指令メッセージ送信前に，48 ビットタイム以上の空白状態を設ける。
(1-2) 1 つの指令メッセージの各バイト間隔は，24 ビットタイム未満で送信する。
2) 本機の応答
本機は，フレーム検出（24 ビットタイム以上の空白状態の検出）後，そのフレームを指令メッセージとして，処理を行います。指令メッセージが自局向けの場合，応答メッセージを返しますが，この処理時間は，約 300～500ms です。（指令メッセージの内容によって，この時間は，変化します。）よって，マスタは，指令メッセージ送信後，以下の事を守る必要があります。
(1-3) 指令メッセージ送信後，24 ビットタイム未満で，受信待機状態に入る。

－15－

5ms 以上の長さの間隔が必要（10ms 以上を推奨）
コントロール→GR200ステーション
GRGR200

POL1

POL2
最大 500ms

コントロール←GR200ステーション
GR200

POL1 応答データ

回線上のデータ
POL1

POL1 応答データ

－16－

POL2

5.7 FIX 処理（データ書き込み時の注意事項）
本機は，設定パラメータを保持する為に，内部に不揮発性メモリ（F-ROM）を持っています。不揮発性メモリに書き込まれたデータは，本機の電源を切っても消える事はありません。通信経由にて書き込みを行ったパラメータを本機の電源を切っても保持したい場合，FIX 処理を行う必要があります。
FIX 処理を行うと，内部メモリに格納されているパラメータが，不揮発性メモリへ書き込まれます。
図 5-4に，FIX の手順を示します。
注意）・ FIX 処理には，約 2 秒かかります。
・ FIX 中に GR200 の電源を切らないでください。不揮発性メモリのデータが壊れて，本機が使用できなくなる事があります。
・ FIX 処理中に前面からのパラメータ変更を行わないでください。メモリ異常の原因となります。
・ 不揮発性メモリ（F-ROM）は，書き込み回数に制限のあるデバイスです。本機が使用している不揮発性メモリの，書き換え保証回数は，最低 100,000 回です。FIX 処理は，設定パラメータを書き換えた時など，必要最小限の時のみ行ってください。定周期で行うなど，不必要に FIX 処理を行う事はやめてください。
FIX 始めファンクションコード : 03H
相対アドレス: 1387Hで FIX データを読み出す

No

FIX=0?
Yes

ファンクションコード : 10H
相対アドレス: 1387Hで FIX データに‘1’を書く

ファンクションコード : 03H
相対アドレス: 1387Hで FIX データを読み出す

No

FIX=0?
Yes
FIX 終了図5-4 FIX の手順

－17－

6.

メッセージの詳細

6.1 ワードデータの読出し［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：03H］
ファンクションコード 1 メッセージで読み出せる最大ワード数 相対ﾃﾞｰﾀｱﾄﾞﾚｽ レジスタ番号
03H

内 容
記憶可能
0000H－1386H 40001－44999
データ
記憶不可能
1387H－176FH 45000－46000
データ

64 ワード(1) メッセージの構成
指令メッセージの構成（バイト）応答メッセージの構成（バイト）ステーション No.
ステーション No.
ファンクションコード
ファンクションコード
読み出し
上位
読み出しバイト数
読み出しワード数×2
開始番号
下位
上位
最初のワード（相対アドレス）
データ内容
読み出し
上位
下位

 1～64
ワード数

下位
次のワード
上位
データ内容
CRC データ
下位
下位
上位
～
～
最後のワード
上位
データ内容
下位
下位
CRC データ
上位* 読み出しワードデータの並び
MSB
LSB
最初のワードデータ内容の上位バイト
最初のワードデータ内容の下位バイト
次のワードデータ内容の上位バイト
次のワードデータ内容の下位バイト～～
最後のワードデータ内容の上位バイト
最後のワードデータ内容の下位バイト(2) 機能説明
読み出し開始番号から読み出しワード数連続したワード情報を読み出します。スレーブは，読み出
しワードデータを上位バイト，下位バイトの順に送信します。

－18－

(3) メッセージ伝送
下記にステーション No.2 からチャネル 1 の表示範囲 MIN 値及び表示範囲 MAX 値を読み出す場
合を例示します。
チャネル 1 の表示範囲 MIN 値の相対アドレス：001BH（レジスタ番号 40028），データ数：02H
指令メッセージの構成（バイト）ステーション No.
02H
ファンクションコード
03H
読み出し
上位
00H
開始番号
下位
1BH
（相対アドレス）
読み出し
上位
00H
ビット数
下位
02H
下位
B4H
CRC データ
上位
3FH

応答メッセージの構成（バイト）ステーション No.
02H
ファンクションコード
03H
読み出しバイト数
04H
最初のワード
データ内容
次のワード
データ内容
CRC データ* 読出しデータの意味
チャネル 1 表示範囲 MIN 値

00

00H =

0

0F

A0H = 4000

（最初のワードデータ内容）
チャネル 1 表示範囲 MAX 値（次のワードデータ内容）
単位が°C で小数点位置が 1 の時
チャネル 1 表示範囲 MIN 値 =0.0°C

チャネル 1 表示範囲 MAX 値 = 400.0°C
Point

小数点の扱いについては，7.1節を参照ください。

－19－

上位

00H

下位
上位
下位
下位
上位

00H
0FH
A0H
CCH
BBH

6.2 読出し専用ワードデータの読出し［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：04H］
ファンクションコード 1 メッセージで読み出せる最大ワード数
04H

64 ワード相対アドレス

レジスタ番号

0000H－07CFH 30001－32000(1) メッセージの構成
指令メッセージの構成（バイト）応答メッセージの構成（バイト）ステーション No.
ステーション No.
ファンクションコード
ファンクションコード
読み出し開始番号 上位
読み出しバイト数
読み出しワード数×2（相対アドレス） 下位
最初のワード
上位
データ内容
読み出し
上位
下位

 1～64
ワード数
下位
次のワード
上位

データ内容
下位
下位
CRC データ
上位～～
最後のワード
上位
データ内容
下位
下位
CRC データ
上位* 読み出しワードデータの並び
MSB
LSB
最初のワードデータ内容の上位バイト
最初のワードデータ内容の下位バイト
次のワードデータ内容の上位バイト
次のワードデータ内容の下位バイト～～
最後のワードデータ内容の上位バイト
最後のワードデータ内容の下位バイト(2) 機能説明
読み出し開始番号から読み出しワード数連続したワード情報を読み出します。スレーブは，読み出
しワードデータを上位バイト，下位バイトの順に送信します。

－20－

(3) メッセージ伝送（例）
下記に，ステーション No.1 からチャネル 2 の測定値を読み出す場合を例示します。
チャネル 2 の測定値の相対アドレス：0065H（レジスタ番号 30102），データ数：01H
指令メッセージの構成（バイト）ステーション No.
01H
ファンクションコード
04H
読み出し開始番号 上位
00H（相対アドレス） 下位
65H
読み出し
上位
00H
ワード数
下位
01H
下位
21H
CRC データ
上位
D5H

応答メッセージの構成（バイト）ステーション No.
01H
ファンクションコード
04H
読み出しバイト数
02H
最初のワード
上位
01H
データ内容
下位
4FH
下位
F9H
CRC データ上位
54H* 読み出しデータの意味
チャネル 2 測定値

01 4FH = 335（最初のワードデータの内容）
単位が°C で小数点位置が 1 の時
チャネル 2 の測定値 = 33.5°C
Point

小数点の扱いについては，7.1節を参照してください。

－21－

6.3 連続ワードデータの書込み［ﾌｧﾝｸｼｮﾝｺｰﾄﾞ：10H］
ファンクションコード 1 メッセージで書き込める最大ワード数
64 ワード

10H

相対アドレス

レジスタ番号内 容
記憶可能
0000H－1386H 40001－44999
データ
記憶不可能
1387H－176FH 45000－46000
データ(1) メッセージの構成
指令メッセージの構成（バイト）ステーション No.
ファンクションコード
書き込み開始番号 上位（相対アドレス） 下位
書き込み
上位

 1～64
ワード数下位 書込ワード数×2


書き込みバイト数
最初の書き込み
ワードデータ
次の書き込みワードデータ応答メッセージの構成（バイト）ステーション No.
ファンクションコード
書き込み開始番号 上位（相対アドレス） 下位
書き込み
上位
ワード数
下位
下位
CRC データ
上位

上位
下位
上位
下位

～

～
最後の書き込み
ワードデータCRC データ

上位
下位
下位
上位

* 書き込みワードデータの並び
MSB
LSB
最初のワードデータ内容の上位バイト
最初のワードデータ内容の下位バイト
次のワードデータ内容の上位バイト
次のワードデータ内容の下位バイト～～
最後のワードデータ内容の上位バイト
最後のワードデータ内容の下位バイト(2) 機能説明
書き込み開始番号から書き込みワード数連続したワード情報を書き込みます。マスタは，書き込み
ワードデータを上位バイト，下位バイトの順に送信します。

－22－

(3) メッセージ伝送（例）
下記に，ステーション No.1 のチャネル 1 に差演算チャネル=チャネル 2，PV シフト値=20.0°C，
PV 傾き=110.0%を書き込む場合を例示します。
差演算チャネル=0002H（=2D：チャネル 2）
PV シフト値=00C8H（=200D）
PV 傾き=044CH（=1100D）
チャネル 1 の差演算チャネルの相対アドレス：0014H（レジスタ番号 40021），データ数：03H
指令メッセージの構成（バイト）ステーション No.
01H
ファンクションコード
10H
書き込み開始番号 上位
00H（相対アドレス） 下位
14H
書き込み
上位
00H
ワード数
下位
03H
書き込みバイト数
06H
最初の書き込み
上位
00H
ワードデータ下位
02H
次の書き込み上位
00H
ワードデータ下位
C8H
最後の書き込み
上位
04H
ワードデータ
下位
4CH
下位
5DH
CRC データ
上位
CBH
Point

応答メッセージの構成（バイト）ステーション No.
01H
ファンクションコード
10H
書き込み開始番号 上位
00H（相対アドレス） 下位
14H
書き込み
上位
00H
ワード数
下位
03H
下位
41H
CRC データ
上位
CDH

伝送データ中には小数点を含むことができないため，上記のように，“110.0”というデータは“1100”として伝送します。
各々のデータの伝送形式については，アドレスマップ（7章）を参照ください。

注意

FIX 中に次の書込み指令メッセージを送信しても，無応答となります。

－23－

7.

アドレスマップ と データ形式

7.1 データ形式
7.1.1 伝送データ形式
本機で使用している MODBUS プロトコルは，RTU（Remote Terminal Unit）モードです。伝送されるデータは“数値”であり，ASCII コードではありません。

7.1.2 小数点の扱いについて
伝送データ上では，小数点は付加されません。小数点が付くデータについては，小数点位置あわせの処理（送信時は小数点除去，受信時は小数点付加）を行ってください。

7.1.3 入力異常時のデータについて
表示データが入力異常（オーバー，アンダー，バーンアウト，イジョウ）の時は測定値の読み出し
データは次のようになります。
表示データ
オーバー
アンダー
バーンアウトイジョウ

読み込みデータ
32767–32767–32768–32768

通信経由にて入力異常の検出は、アドレス 30131: 入力異常情報にて行うことが出来ます。

7.1.4 書き込みデータ範囲について
各パラメータにデータを書き込む場合，その書き込みデータは書き込みデータ設定範囲内となるようにしてください。GR200 は，設定範囲外データの書き込みも受け付けますが，この場合，GR200 本体の動作は保証されませんので，十分ご注意ください。

－24－

7.2 アドレスマップ
個別パラメータ機能・設定範囲についての詳細な内容は本体の取扱説明書を参照ください。
データタイプ

ロング：ロングデータ このアドレスのデータをロング単位で扱う。１データ／２アドレス
ワード：ワードデータ このアドレスのデータをワード単位で扱う。1 データ／1 アドレス
バイト：バイトデータ このアドレスのデータをバイト単位で扱う。最大 2 データ／1 アドレス
ビット：ビットデータ このアドレスのデータをビット単位で扱う。最大 16 データ／1 アドレス

7.2.1 ワードデータ[読出/書込]：ファンクションコード [ 03H，10H]
レジスタ
タイプ
番 号
4XXXX

メモリ内容

1，2 文字目

40001 バイト
40002 バイト
40003 バイト
40004 バイト
40005 バイト

タグ 1

読み出しデータ / 書き込みデータ 設定範囲

備

タグ 1 (8 文字）を ASCII コードにて設定する。

3，4 文字目
5，6 文字目
7，8 文字目
1，2 文字目

40006 バイト
タグ 2
3，4 文字目
40007 バイト
5，6 文字目
40008 バイト
7，8 文字目
40009 ワード
表示色
40010 ワード
入力種別
40011 ワード
入力フィルタ
40012 ワード単位
40013 ワード
スケーリング
40014 ワード
MIN
測定範囲
40015 ワードMAX
40016 ワード
MIN
工業値
40017 ワード CH 1
MAX
40018 ワード 設定
小数点位置
40019 ワード (64 ﾜｰﾄﾞ) 開平演算
40020 ワード
対数演算
40021 ワード
差演算チャネル
40022 ワード
PV シフト値
40023 ワード
PV 傾き
40024 ワード40025 ワード40026 ワード
記録動作
40027 ワード
記録タイプ
40028 ワード
MIN
表示範囲
40029 ワードMAX
40030 ワード40031 ワード
他チャネル入力チャネル
40032 ワード40033 ワード40034 ワード40035 ワード40036 ワード
F 値演算
40037 ワード
積算演算動作

タグ 2 (8 文字）を ASCII コードにて設定する。

1 ～ 14 ( 詳細は表 1 を参照)
0 ～ 40 (詳細は表 2 を参照)
0 ～ 900 (0 ～ 900 sec)
0 ～ 167 ( 詳細は表 3 を参照)
0:OFF，1:ON–1000 ～ 5500 ( 詳細は表 4 を参照)
–1000 ～ 5500 ( 詳細は表 4 を参照)
–32767 ～ 32767–32767 ～ 32767
0 ～ 4 (詳細は表 5 を参照)
0:OFF，1:ON
0:OFF，1:ON
0 ～30 (0:OFF，1 ～ 30:チャネル 1 ～ 30)–32767 ～ 32767
0 ～ 32767 (0.00 ～ 327.67%)

未使用

未使用
未使用
0:表示のみ，1:記録有り
0:最小最大，1:瞬時値，2:平均値–32767 ～ 32767 (詳細は表 6 を参照)
–32767 ～ 32767 (詳細は表 6 を参照)
未使用
0 ～ 29(チャネル 1 ～ 30)
未使用
未使用
未使用
未使用
0:OFF，1:ON
1:入力値の積算，2:カウンタ，3:時間測定

－25－

考

レジスタ
タイプ
番 号
40038 バイト

メモリ内容
1，2 文字目

積算用
40039 バイト
3，4 文字目
タグ
40040 バイト
5，6 文字目
40041 バイト
7，8 文字目
40042 ワード CH 1
積算用単位
40043 ワード 設定
積算下限カット値
40044 ワード (64 ﾜｰﾄﾞ) 積算除数
40045 ワード
積算タイプ
40046 ワード
外部入力
40047 ワード
積算単位時間
40048 ワード
積算リセット動作
40049 ワード
積算リセット入力
40050 ワード

読み出しデータ / 書き込みデータ 設定範囲
積算タグ (8 文字）を ASCII コードにて設定する。

0 ～ 167 (詳細は表 3 を参照)
–32767 ～ 32767 (詳細は表 6 を参照)
1 ～ 32767
0 ～ 15 (詳細は表 7 を参照)
0 ～ 81 (詳細は表 8 を参照)
0:/s，1:/min，2:/h，3:/day0:OFF，1:ON
0 ～ 130 (詳細は表 9 を参照)
未使用
未使用

～
40065 ワード CH2 設定

備

CH1 と同じ割付～
40129 ワード CH3 設定

CH1 と同じ割付～
40193 ワード CH4 設定

CH1 と同じ割付～
40257 ワード CH5 設定

CH1 と同じ割付～
40321 ワード CH6 設定

CH1 と同じ割付～
40385 ワード CH7 設定

CH1 と同じ割付～
40449 ワード CH8 設定

CH1 と同じ割付～
40513 ワード CH9 設定

CH1 と同じ割付～
40577 ワード CH10 設定

CH1 と同じ割付～
40641 ワード CH11 設定

CH1 と同じ割付～
40705 ワード CH12 設定

CH1 と同じ割付～
40769 ワード CH13 設定

CH1 と同じ割付～
40833 ワード CH14 設定

CH1 と同じ割付～
40897 ワード CH15 設定

CH1 と同じ割付～
40961 ワード CH16 設定

CH1 と同じ割付～
41025 ワード CH17 設定

CH1 と同じ割付～
41089 ワード CH18 設定

CH1 と同じ割付

～
41153

未使用

～
41921 ワード CH1 警報
警報種類
41922 ワード 設定
設定値
警報 No.1
41923 ワード (16 ﾜｰﾄﾞ)41924 ワード
出力リレー No.
41925 ワード
警報 No.2 警報種類
41926 ワード
設定値

0:OFF，1:H 警報，2:L 警報–32767 ～ 32767 (詳細は表 6 を参照)
未使用
0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)
0:OFF，1:H 警報，2:L 警報–32767 ～ 32767 (詳細は表 6 を参照)

－26－

考

レジスタ
タイプ
番 号
41927 ワード41928 ワード

メモリ内容

読み出しデータ / 書き込みデータ 設定範囲

備
未使用

出力リレー No.

0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)

－27－

考

レジスタ
タイプ
メモリ内容
番 号
41929 ワード
警報種類
41930 ワード
設定値
警報 No.3
41931 ワードCH1 警報41932 ワード
出力リレー No.
設定
41933 ワード
警報種類
(16 ﾜｰﾄﾞ)
41934 ワード
設定値
警報 No.4
41935 ワード41936 ワード
出力リレー No.
41937 ワード CH2 警報設定

読み出しデータ / 書き込みデータ 設定範囲

備

0:OFF，1:H 警報，2:L 警報–32767 ～ 32767 (詳細は表 6 を参照)
未使用
0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)
0:OFF，1:H 警報，2:L 警報–32767 ～ 32767 (詳細は表 6 を参照)
未使用
0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)
CH1 と同じ割付～
41953 ワード CH3 警報設定

CH1 と同じ割付～
41969 ワード CH4 警報設定

CH1 と同じ割付～
41985 ワード CH5 警報設定

CH1 と同じ割付～
42001 ワード CH6 警報設定

CH1 と同じ割付～
42017 ワード CH7 警報設定

CH1 と同じ割付～
42033 ワード CH8 警報設定

CH1 と同じ割付～
42049 ワード CH9 警報設定

CH1 と同じ割付～
42065 ワード CH10 警報設定

CH1 と同じ割付～
42081 ワード CH11 警報設定

CH1 と同じ割付～
42097 ワード CH12 警報設定

CH1 と同じ割付～
42113 ワード CH13 警報設定

CH1 と同じ割付～
42129 ワード CH14 警報設定

CH1 と同じ割付～
42145 ワード CH15 警報設定

CH1 と同じ割付～
42161 ワード CH16 警報設定

CH1 と同じ割付～
42177 ワード CH17 警報設定

CH1 と同じ割付～
42193 ワード CH18 警報設定

CH1 と同じ割付

～
42209

未使用

～
画面
1，2 文字目
グループ 142426 バイト 設定
3，4 文字目
42427 バイト (18 ﾜｰﾄﾞ)
5，6 文字目
42428 バイト
画面名称 7，8 文字目
42429 バイト
9，10 文字目
42430 バイト
11，12 文字目
42431 バイト
13，14 文字目
42432 バイト
15，16 文字目
42433 ワード
画面構成チャネル No.1
42434 ワード
画面構成チャネル No.2
42435 ワード
画面構成チャネル No.3
42436 ワード
画面構成チャネル No.4
42425 バイト

Display name (16文字) をASCIIコードにて設定する。

0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18

－28－

考

レジスタ
タイプ
番 号
42437 ワード

メモリ内容
画面構成チャネル No.5

読み出しデータ / 書き込みデータ 設定範囲
0:無し，1 ～ 18:ch1 ～ 18

－29－

備

考

レジスタ
タイプ
メモリ内容
番 号
42438 ワード
画面構成チャネル No.6
画面42439 ワード
画面構成チャネル No.7
グループ 142440 ワード
画面構成チャネル No.8
設定42441 ワード
画面構成チャネル No.9
(18 ﾜｰﾄﾞ)
42442 ワード
画面構成チャネル No.10
42443 ワード 画面グループ 2 設定

読み出しデータ / 書き込みデータ 設定範囲

備0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
0:無し，1 ～ 18:ch1 ～ 18
画面グループ 1 と同じ割付～
42461 ワード 画面グループ 3 設定

画面グループ 1 と同じ割付～
42479 ワード 画面グループ 4 設定

画面グループ 1 と同じ割付～
42497 ワード42498 ワード42499 ワード42500 ワード42501 ワード42502 ワード42503 ワード

未使用
トレンド表示方向
画面
カラーバーの表示内容
グループ 1
目盛表示
設定 2(5 ﾜｰﾄﾞ)
画面分割数
画面グループ 2 設定 2

0:縦，1:横0:チャネル No.，1:タグ No.，2:単位
0:OFF，1:ON
未使用
1 ～ 20
画面グループ 1 と同じ割付～
42508 ワード 画面グループ 3 設定 2

画面グループ 1 と同じ割付～
42513 ワード 画面グループ 4 設定 2

画面グループ 1 と同じ割付～
42518 ワード42519 ワード42520 ワード42521 ワード42522 ワード

画面
グループ 1設定 3(4 ﾜｰﾄﾞ) アナログメータ表示切換
画面グループ 2 設定 3

未使用
未使用
未使用
0:バーグラフ，1:アナログメーター
画面グループ 1 と同じ割付～
42526 ワード 画面グループ 3 設定 3

画面グループ 1 と同じ割付～
42530 ワード 画面グループ 4 設定 3

画面グループ 1 と同じ割付～
42534 ワード
～

未使用
未使用
未使用

42541
42542 ワード42543
42544 ワード42545 ワード42546 ワード42547 ワード42548 ワード42549 ワード42550 ワード42551 ワード42552 ワード42553 ワード42554 ワード42555 ワード42556 ワード42557 ワード42558 ワード42559 ワード42560 ワード42561 ワード

積算時間

0 ～ 9 (詳細は表 10 を参照)

積算基準日

1 ～ 31 ( 1 ～ 31 日)

未使用
未使用
未使用
積算外部入力H-P ,L-P 演算周期（分）AVG 演算周期（分）SUM 演算周期（分）
演算式１

演算
CH19
設定
(36 ワート)

演算式１

演算式１

演算式２

0 ～ 129 (詳細は表 8 を参照)
1 ～ 32767 (1 ～ 32767 分)
1 ～ 32767 (1 ～ 32767 分)
1 ～ 32767 (1 ～ 32767 分)
１番目の演算内容 ( 詳細は表 11 を参照 )引数１
引数２
２番目の演算内容
引数１
引数２
３番目の演算内容
引数１
引数２
１番目の演算内容
引数１

－30－

未使用

考

レジスタ
タイプ
メモリ内容
読み出しデータ / 書き込みデータ 設定範囲
番 号
42562 ワード
引数２
演算
ワード
CH19
42584 ワード演算式４
３番目の演算内容
設定
42585 ワード (36 ワート)
引数１42586 ワード
引数２42587 ワード 演算ＣＨ２０設定
演算ＣＨ１９と同じ割付

考

～

～

備

42623 ワード 演算ＣＨ２１設定～

演算ＣＨ１９と同じ割付

42659 ワード 演算ＣＨ２２設定～

演算ＣＨ１９と同じ割付

42695 ワード 演算ＣＨ２３設定～

演算ＣＨ１９と同じ割付

42731 ワード 演算ＣＨ２４設定～

演算ＣＨ１９と同じ割付

42767 ワード 演算ＣＨ２５設定～

演算ＣＨ１９と同じ割付

42803 ワード 演算ＣＨ２６設定～

演算ＣＨ１９と同じ割付

42839 ワード 演算ＣＨ２７設定～

演算ＣＨ１９と同じ割付

42875 ワード 演算ＣＨ２８設定～

演算ＣＨ１９と同じ割付

42911 ワード 演算ＣＨ２９設定～

演算ＣＨ１９と同じ割付

42947 ワード 演算ＣＨ３０設定～

演算ＣＨ１９と同じ割付
定数値
小数点位置

-32767 ～ 32767 ( 詳細は表 12 を参照 )
0～4

定数値
小数点位置

-32767 ～ 32767 ( 詳細は表 12 を参照 )0～4～42983 ワード
定数１42984 ワード43021 ワード
定数２０43022 ワード43023 ワード
～

未使用
未使用

43032 ワード43033 ワード43034 ワード43035 ワード43036 ワード43037 ワード43038 ワード43039 ワード43040 ワード43041 ワード43042 ワード43043 ワード43044 ワード43045 ワード43046 ワード43047 ワード43048 ワード43049 ワード43050 ワード43051 ワード43052 ワード

時刻設定

時刻セット要求
年
月日時分

1:時刻セット要求 (自動クリア）
1 ～ 99 ( 2001 ～ 2099 年)
1 ～ 12 ( 1 ～ 12 月)
1 ～ 31 ( 1 ～ 31 日)
0 ～ 23 ( 0 ～ 23 時)
0 ～ 59 ( 0 ～ 59 分)＊注意
記録中および積算中は絶対に時間を変更
しないでください。
未使用
未使用

表示更新周期

0 ～ 19 (詳細は表 13 を参照)

LCD 自動消灯時間
ファイル分割周期
CF カード FULL 時の警報出力設定
記録データのアスキー/バイナリ選択
基準温度
Z値
F 値演算
小数点位置

0 ～ 60 ( 0:常時点灯，1 ～ 60:1 ～ 60 分)
0 ～ 4 (詳細は表 14 を参照)
0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)
0:アスキー，1:バイナリ–2300 ～ 32767 (–230.0 ～ 3276.7°C)–2300 ～ 32767 (–230.0 ～ 3276.7°C)
0 ～ 4 (詳細は表 15 を参照)

リセット温度
バッテリ警報出力設定–2300 ～ 32767 (–230.0 ～ 3276.7°C)
0 ～ 28 (0:無し，1 ～ 28:DO1 ～ 28)

未使用

未使用

未使用

－31－

レジスタ
タイプ
メモリ内容
番 号
43053 ワード ファイル上書き機能
43054 ワード トレンド表示圧縮
43055 ワード43056 ワード 警報ヒステリシス
43057 ワード 警報ラッチ
43058 ワード MODBUS 通信ステーション No.
43059 ワード MODBUS 通信ボーレート
43060 ワード MODBUS パリティ
43061 ワード パラメータ設定用パスワード
43062 ワード ＣＦマネージャ用パスワード
43063 ワード 記録キー用パスワード
43064 ワード43065 ワード
43066 ワード43067 ワード トレンド画面背景色
43068 ワード ヒストリカル画面背景色

読み出しデータ / 書き込みデータ 設定範囲
0:OFF，1:ON
0:1/1, 1: 1/10,

2:1/30,3:1/60未使用

0 ～ 10000 ( 0.00 ～ 100.00%)
0:OFF，1:ON
0 ～ 255 ( 0:通信機能無し)
0:9600bps，1:19200bps
0:無し，1:奇数，2:偶数
0 ～ 9999
0 ～ 9999
0 ～ 9999
未使用
未使用
未使用
0 : 白, 1 : 黒
0 : 白, 1 : 黒
未使用～
43081 バイト
43082 バイト
43083 バイト
43084 バイト
43085 バイト
43086 バイト
43087 バイト
43088 バイト
43089 バイト
43090 バイト
43091 バイト
43092 バイト
43093 バイト
43094 バイト
43095 バイト
43096 バイト
43097 ワード43098 ワード43099 ワード43100 ワード43101 ワード43102 ワード43103 ワード

備

1，2 文字目

メッセージ (32文字) をASCIIコードにて設定する。

3，4 文字目
5，6 文字目
7，8 文字目
9，10 文字目
11，12 文字目
13，14 文字目
メッセー
15，16 文字目
ジ
17，18 文字目
メッセー
19，20 文字目
ジ
21，22 文字目
No.1
設定
23，24 文字目
(22 ﾜｰﾄﾞ)
25，26 文字目
27，28 文字目
29，30 文字目
31，32 文字目
未使用
未使用
メッセージタイミング
DI No.／警報チャネル
警報 No.

0 ～ 2 (詳細は表 16 を参照)
0 ～ 9/ 0～29 (詳細は表 16 を参照)
0 ～ 3 (詳細は表 16 を参照)
未使用
メッセージ No.1 と同じ割付

43125 ワード メッセージ No.3 設定

メッセージ No.1 と同じ割付～

メッセージ No.2 設定～
43147 ワード メッセージ No.4 設定

メッセージ No.1 と同じ割付～
43169 ワード メッセージ No.5 設定

メッセージ No.1 と同じ割付～
43191 ワード メッセージ No.6 設定

メッセージ No.1 と同じ割付～
43213 ワード メッセージ No.7 設定

メッセージ No.1 と同じ割付～
43235 ワード メッセージ No.8 設定

メッセージ No.1 と同じ割付～
43257 ワード メッセージ No.9 設定

メッセージ No.1 と同じ割付

～

－32－

考

レジスタ
タイプ
メモリ内容
番 号
43279 ワード メッセージ No.10 設定

読み出しデータ / 書き込みデータ 設定範囲

備

メッセージ No.1 と同じ割付～
43301 バイト
43302 バイト
43303 バイト
43304 バイト 単位 No.1 設定
43305 バイト
43306 バイト
43307 バイト
43308 バイト 単位 No.2 設定

1，2 文字目
3，4 文字目
5，6 文字目
7 文字目

単位 No.1 と同じ割付～
43315 バイト 単位 No.3 設定

単位 No.1 と同じ割付～
43322 バイト 単位 No.4 設定

単位 No.1 と同じ割付～
43329 バイト 単位 No.5 設定

単位 No.1 と同じ割付～
43336 バイト 単位 No.6 設定

単位 No.1 と同じ割付～
43343 バイト 単位 No.7 設定

単位 No.1 と同じ割付～
43350 バイト 単位 No.8 設定

単位 No.1 と同じ割付～
43357 バイト 単位 No.9 設定

単位 No.1 と同じ割付～
43364 バイト 単位 No.10 設定

単位 No.1 と同じ割付～
43371 バイト 単位 No.11 設定

単位 No.1 と同じ割付～
43378 バイト 単位 No.12 設定

単位 No.1 と同じ割付～
43385 ワード
～

未使用
未使用

43496 ワード43497 ワード43498 ワード43499 ワード43500 ワード43501 ワード43502 ワード43503 ワード43504 ワード43505 ワード43506 ワード

DI 1 機能設定
DI 2 機能設定
DI 3 機能設定
DI 4 機能設定
DI 5 機能設定
DI 6 機能設定
DI 7 機能設定
DI 8 機能設定
DI 9 機能設定
DI 10 機能設定

0 ～ 5 ( 詳細は表 17 を参照)
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5
0 ～ 5

～

書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止

44001 バイト PILC データ
44002 バイト
44003 バイト
44004 バイト
44005 バイト
44006 バイト
44007 バイト
44008 バイト
44009 バイト
44010 バイト
44011 バイト

1，2 文字目
3，4 文字目
5，6 文字目
7，8 文字目
9，10 文字目
11，12 文字目
13，14 文字目
15，16 文字目
17，18 文字目
19，20 文字目
21，22 文字目

－33－

考

レジスタ
タイプ
番 号
44012 バイト
44013 バイト
44014 バイト
44015 バイト
PILC データ
44016 バイト
44017 バイト
44018 バイト
44019 バイト
44020 バイト
シリアル No.
44021 バイト
44022 バイト
44023 バイト
44024 バイト
44025 ワード

読み出しデータ / 書き込みデータ 設定範囲

メモリ内容
23，24 文字目
25，26 文字目
27，28 文字目
29，30 文字目
31，32 文字目
1，2 文字目
3，4 文字目
5，6 文字目
7，8 文字目
9，10 文字目
11，12 文字目
13，14 文字目
15，16 文字目

備

考

～

書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止
書込禁止

以下の 45000～45500 番地のデータは，本体に記録されません。
読み出しデータ / 書き込みデータ 設定範囲
未使用
1:リセット (自動クリア）
0:書き込み禁止無し，1:書き込み禁止( 詳細は表 18 を参照)
( 詳細は表 19 を参照)
1:リセット (自動クリア）
1:解除 (自動クリア）
書込禁止

チャネル１～１６ ( 詳細は表 20 を参照 )チャネル１７～３０
未使用
未使用

～
45061 ワード45062 ワード45063 ワード45064 ワード45065 ワード
45066 ワード45067 ワード45068 ワード45069 ワード45070 ワード45071 ワード45072 ワード考

1:記憶 (自動クリア）～
45051 ビット チャネル毎の45052 ビット 積算リセット要求
45053 ワード

備

～

レジスタ
タイプ
メモリ内容
番 号
45000 ワード 設定値の記憶要求
45001 ワード45002 ワード F 値リセット要求
45003 ワード CF カード書き込み禁止要求
45004 ビット 本体コントロールフラグ
45005 ビット メッセージ要求フラグ
45006 ワード 積算リセット要求フラグ
45007 ワード 警報ラッチ解除要求フラグ
45008 ワード

通信入力 1 : M01
通信入力 2 : M02
通信入力 3 : M03
通信入力 4 : M04
通信入力 5 : M05
通信入力 6 : M06
通信入力 7 : M07
通信入力 8 : M08
通信入力 9 : M09
通信入力 10 : M10
通信入力 11 : M11
通信入力 12 : M12

～

書込禁止

以下のアドレスデータは，本体に記憶されます。
レジスタ
タイプ
メモリ内容
番 号
45501 ワード45002 ワード E-mail 機能
45503 ワード FTP サーバ機能
45504 ワード FTP アクセス管理
45505 ワード Web サーバ機能

読み出しデータ / 書き込みデータ 設定範囲

備 考
未使用

0:OFF,
0:OFF,
0:OFF,
0:OFF,

1:ON
1:ON
1:ON
1:ON

－34－

レジスタ
タイプ
メモリ内容
番 号
45506 ワード45507 ワード45508 ワード MODBUS TCP/IP 機能
45509 ワード IP アドレス
１桁目の設定45510 ワード
２桁目の設定45511 ワード
３桁目の設定45512 ワード
４桁目の設定45513 ワード サブネットマスク １桁目の設定
45514 ワード
２桁目の設定45515 ワード
３桁目の設定45516 ワード
４桁目の設定45517 ワード デフォルト
１桁目の設定ゲートウェイ45518 ワード
２桁目の設定45519 ワード
３桁目の設定45520 ワード
４桁目の設定45521 ワード SMTP アドレス
１桁目の設定45522 ワード
２桁目の設定45523 ワード
３桁目の設定45524 ワード
４桁目の設定45525 バイト 送信元アドレス
1，2 文字目
45526 バイト
3，,4 文字目
45527 バイト
5，6 文字目
45528 バイト
7，8 文字目
45529 バイト
9，10 文字目
45530 バイト
11，12 文字目
45531 バイト
13，14 文字目
45532 バイト
15，16 文字目
45533 バイト
17，18 文字目
45534 バイト
19，20 文字目
45535 バイト
21，22 文字目
45536 バイト
23，24 文字目
45537 バイト
25，26 文字目
45538 バイト
27，28 文字目
45539 バイト
29，30 文字目
45540 バイト
31，32 文字目
45541 バイト
33，34 文字目
45542 バイト
35，36 文字目
45543 バイト
37，38 文字目
45544 バイト
39，40 文字目
45545 バイト
41，42 文字目
45546 バイト
43，44 文字目
45547 バイト
45，46 文字目
45548 バイト
47，48 文字目
45549 バイト
49，50 文字目
45550 バイト
51，52 文字目
45551 バイト
53，54 文字目
45552 バイト
55，56 文字目
45553 バイト
57，58 文字目
45554 バイト
59，60 文字目
45555 バイト
61，62 文字目
45556 バイト
63，64 文字目
45557 バイト 送信者名
1，2 文字目
45558 バイト
3，4 文字目
45559 バイト
5，6 文字目
45560 バイト
7，8 文字目

読み出しデータ / 書き込みデータ 設定範囲

備
未使用
未使用

0:OFF, 1:ON
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
0～255
アドレス(64 文字）を ASCII コードにて設定する。

送信者名(32 文字）を ASCII コードにて設定する。

－35－

考

読み出しデータ / 書き込みデータ 設定範囲

アドレス(64 文字）を ASCII コードにて設定する。

送信先アドレス１と同じ割付

～

レジスタ
タイプ
メモリ内容
番 号
45561 バイト
9，10 文字目
45562 バイト
11，12 文字目
45563 バイト
13，14 文字目
45564 バイト
15，16 文字目
45565 バイト
17，18 文字目
45566 バイト
19，20 文字目
45567 バイト
21，22 文字目
45568 バイト
23，24 文字目
45569 バイト
25，26 文字目
45570 バイト
27，28 文字目
45571 バイト
29，30 文字目
45572 バイト
31，32 文字目
45573 バイト 送信先アドレス１ 1，2 文字目
45574 バイト
3，4 文字目
45575 バイト
5，6 文字目
45576 バイト
7，8 文字目
45577 バイト
9，10 文字目
45578 バイト
11，12 文字目
45579 バイト
13，14 文字目
45580 バイト
15，16 文字目
45581 バイト
17，18 文字目
45582 バイト
19，20 文字目
45583 バイト
21，22 文字目
45584 バイト
23，24 文字目
45585 バイト
25，26 文字目
45586 バイト
27，28 文字目
45587 バイト
29，30 文字目
45588 バイト
31，32 文字目
45589 バイト
33，34 文字目
45590 バイト
35，36 文字目
45591 バイト
37，38 文字目
45592 バイト
39，40 文字目
45593 バイト
41，42 文字目
45594 バイト
43，44 文字目
45595 バイト
45，46 文字目
45596 バイト
47，48 文字目
45597 バイト
49，50 文字目
45598 バイト
51，52 文字目
45599 バイト
53，54 文字目
45600 バイト
55，56 文字目
45601 バイト
57，58 文字目
45602 バイト
59，60 文字目
45603 バイト
61，62 文字目
45604 バイト
63，64 文字目
45605 バイト 送信先アドレス 2

送信先アドレス１と同じ割付～

45637 バイト 送信先アドレス 3

送信先アドレス１と同じ割付～

45669 バイト 送信先アドレス 4

送信先アドレス１と同じ割付～

45701 バイト 送信先アドレス 5

送信先アドレス１と同じ割付～

45733 バイト 送信先アドレス 6

送信先アドレス１と同じ割付～

45765 バイト 送信先アドレス 7

－36－

備 考

読み出しデータ / 書き込みデータ 設定範囲

備

送信先アドレス１と同じ割付

～

レジスタ
タイプ
メモリ内容
番 号
45797 バイト 送信先アドレス 8

未使用
未使用

～

45829 ワード
ユーザ名(16 文字）を ASCII コードにて設定する。

ユーザ名(8 文字）を ASCII コードにて設定する。

0: 管理者,

1 : ゲスト
未使用

ユーザアカウント１と同じ割付～

45901 バイト ユーザ
ユーザ名
1，2 文字目
45902 バイト ｱｶｳﾝﾄ 1
3，,4 文字目
45903 バイト
5，6 文字目
45904 バイト
7，8 文字目
45905 バイト
9，10 文字目
45906 バイト
11，12 文字目
45907 バイト
13，14 文字目
45908 バイト
15，16 文字目
45909 バイト
ﾊﾟｽﾜｰﾄﾞ
1，2 文字目
45910 バイト
3，4 文字目
45911 バイト
5，6 文字目
45912 バイト
7，8 文字目
45913 ワード
ユーザレベル
45914 ワード45915 バイト ユーザアカウント 2

ユーザアカウント１と同じ割付～

45929 バイト ユーザアカウント 3

ユーザアカウント１と同じ割付～

45943 バイト ユーザアカウント 4

ユーザアカウント１と同じ割付～

45957 バイト ユーザアカウント 5

ユーザアカウント１と同じ割付～

45971 バイト ユーザアカウント 6

ユーザアカウント１と同じ割付～

45985 バイト ユーザアカウント 7

ユーザアカウント１と同じ割付～

45999 バイト ユーザアカウント 8

未使用
未使用

～

46013 ワード46101 バイト E-mail46102 バイト トリガー
46103 バイト 設定 146104 バイト
46105 バイト
46106 バイト
46107 バイト
46108 バイト
46109 バイト
46110 バイト
46111 バイト
46112 バイト
46113 バイト
46114 バイト
46115 バイト
46116 バイト
46117 バイト
46118 バイト
46119 バイト
46120 バイト
46121 バイト
46122 バイト

タイトル 1，2 文字目
3，4 文字目
5，6 文字目
7，8 文字目
9，10 文字目
11，12 文字目
13，14 文字目
15，16 文字目
17，18 文字目
19，20 文字目
21，22 文字目
23，24 文字目
25，26 文字目
27，28 文字目
29，30 文字目
31，32 文字目
ﾃｷｽﾄ 1
1，2 文字目
3，4 文字目
5，6 文字目
7，8 文字目
9，10 文字目
11，12 文字目

タイトル(32 文字）を ASCII コードにて設定する。

テキスト１(32 文字）を ASCII コードにて設定する。

－37－

考

読み出しデータ / 書き込みデータ 設定範囲

備 考

テキスト１(32 文字）を ASCII コードにて設定する。

(詳細は表 21 を参照)

0:OFF, 1:ON
(詳細は表 22 を参照)
未使用
E-mail トリガー１と同じ割付

～

レジスタ
タイプ
メモリ内容
番 号
46123 バイト
13，14 文字目
46124 バイト
15，16 文字目
46125 バイト
17，18 文字目
46126 バイト
19，20 文字目
46127 バイト
21，22 文字目
46128 バイト
23，24 文字目
46129 バイト
25，26 文字目
46130 バイト
27，28 文字目
46131 バイト
29，30 文字目
46132 バイト
31，32 文字目
46133 バイト
ﾃｷｽﾄ 2
1，2 文字目
46134 バイト
3，4 文字目
46135 バイト
5，6 文字目
46136 バイト
7，8 文字目
46137 バイト
9，10 文字目
46138 バイト
11，12 文字目
46139 バイト
13，14 文字目
46140 バイト
15，16 文字目
46141 バイト
17，18 文字目
46142 バイト
19，20 文字目
46143 バイト
21，22 文字目
46144 バイト
23，24 文字目
46145 バイト
25，26 文字目
46146 バイト
27，28 文字目
46147 バイト
29，30 文字目
46148 バイト
31，32 文字目
46149 ワード
トリガータイミング
46150 ワード
トリガータイミング引数 146151 ワード
トリガータイミング引数 246152 ワード
ＰＶ値 有り無し
46153 ワード
送信先アドレス№
46154 ワード46155 バイト E-mail トリガー設定 2

E-mail トリガー１と同じ割付～

46209 バイト E-mail トリガー設定 3

E-mail トリガー１と同じ割付～

46263 バイト E-mail トリガー設定 4

E-mail トリガー１と同じ割付～

46317 バイト E-mail トリガー設定 5

E-mail トリガー１と同じ割付～

46371 バイト E-mail トリガー設定 6

E-mail トリガー１と同じ割付～

46425 バイト E-mail トリガー設定 7

E-mail トリガー１と同じ割付～

46479 バイト E-mail トリガー設定 8

E-mail トリガー１と同じ割付～

46533 バイト E-mail トリガー設定 9

E-mail トリガー１と同じ割付～

46587 バイト E-mail トリガー設定 10

未使用
未使用
未使用

～

46641 ワード
47000 ワード 最終アドレス－38－

7.2.2 ワードデータ[読出]：ファンクションコード[04H]
レジスタ
タイプ
メモリ内容
番 号
3XXXX
30001 ビット システム情報
30002 ビット
30003 ビット
DO1 ～ 16
DO 出力情報
30004 ビット
DO17 ～ 28
30005 ビット
30006 ビット DI 情報

読み出しデータ備( 詳細は表 23 を参照)
未使用
( 詳細は表 24 を参照)
未使用
( 詳細は表 25 を参照)～

未使用
0 ～ 1000 (0.00 ～ 100.0%,100.0%：メモリ FULL)

30086 ワード メモリカード利用～
30093 ビット
30094 ビット
30095 ビット 警報出力情報
30096 ビット
30097 ビット
30098 ビット
30099 ビット
30100 ビット30101 ワード30102 ワード30103 ワード
測定値

CH 1 ～ 4
CH 5 ～ 8
CH 9 ～ 12
CH 13 ～ 16
CH 17 ～ 18

( 詳細は表 26 を参照)

CH 1
CH 2
CH 3

–32767 ～ 32767 （ 小数点無し )–32767 ～ 32767 （ 小数点無し )–32767 ～ 32767 （ 小数点無し )30117 ワード30118 ワード

CH 17
CH 18

–32767 ～ 32767 （ 小数点無し )–32767 ～ 32767 （ 小数点無し )30131 ワードCH 1

0:正常入力，1:ﾊﾞｰﾝｱｳﾄ，2:ｵｰﾊﾞｰ，3:ｱﾝﾀﾞｰ，4:電圧異常30132 ワード
入力異常情報30133 ワード

CH 2
CH 3

未使用
未使用
未使用

～
～

未使用

～
30148 ワード

CH 18
未使用

～
30161 ロング 積算値
30162 ロング
30163 ロング
30164 ロング

CH1
CH1
CH2
CH2

–999999999 ～ 999999999（小数点無し)

CH18
CH18

–999999999 ～ 999999999（小数点無し)

CH1
CH1
CH2
CH2

グリニッジ時間

CH18
CH18

グリニッジ時間

CH1
CH1
CH2
CH2

グリニッジ時間

CH18

グリニッジ時間–999999999 ～ 999999999（小数点無し)～
30195 ロング
30196 ロング

未使用～
30221 ロング 積算開始時間
30222 ロング
30223 ロング
30224 ロング

グリニッジ時間～
30255 ロング
30256 ロング

未使用～
30281 ロング 積算終了時間
30282 ロング
30283 ロング
30284 ロング

グリニッジ時間～
30315 ロング

－39－

考

レジスタ
タイプ
番 号
30316 ロング

メモリ内容

読み出しデータ

備

CH18

～

未使用

30341 ロング 前回の積算値
30342 ロング
30343 ロング
30344 ロング

CH1
CH1
CH2
CH2

–999999999 ～ 999999999（小数点無し)

CH18
CH18

–999999999 ～ 999999999（小数点無し)–999999999 ～ 999999999（小数点無し)～～

30375 ロング
30376 ロング

30401 ロング 前回の積算開始時間 CH1CH130402 ロング
CH230403 ロング
CH230404 ロング

グリニッジ時間グリニッジ時間

～
CH18
CH18

30435 ロング
30436 ロング

グリニッジ時間～

未使用

30461 ロング 前回の積算終了時間 CH1CH130462 ロング
CH230463 ロング
CH230464 ロング

グリニッジ時間

CH18
CH18

グリニッジ時間グリニッジ時間～

30495 ロング
30496 ロング
30497 ロング
～

未使用
未使用
未使用

32000 ワード 最終アドレス

注）・（書込禁止）の領域は，データを書き込まないでください。
・データが割り付けていない領域にデータを書き込む場合は，0 を書き込んでください。

－40－

考

7.3 アドレスマップの補足説明
表 1 表示色コード
データ
1
2
3
4
5
6
7
8
9
10
11
12
13
14

色
赤
青
紫
緑
水色
黄
灰色
藍色
檜皮
菖蒲
常盤
浅葱
鶯
銀鼠

表 2 入力種別コード
データ
0
1
2
3
4
5
6
7
8
9
10
11
12
20
21
30
31
32
33
40

入力種別
スキップ
K 熱電対
E 熱電対
J 熱電対
T 熱電対
R 熱電対
S 熱電対
B 熱電対
N 熱電対
W 熱電対
L 熱電対
U 熱電対
PN 熱電対
Pt100
JPt100
50mV
500mV
1-5V
0-5V
他チャネル入力

スキップ

初期小数点位置
0

熱電対

1

測温抵抗体

1

直流電圧

2
1
3

他チャネル入力0*入力種別を変更して小数点位置が変化する場合は，小数点位置も初期化してください。

－41－

表 3 単位コード
データ
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16
17
データ
90
91
92
93
94
95
96
97
98
99
100
101
102
103
104
105
106
107

単位
°C
°F
%RH
vol%

t/d
kg/d
g/d
m3/d
l/d
t/h
kg/h
g/h
m3/h
l/h

単位
mN
N
N･m
J
kJ
mm/s
mm/min
mm/h
m/s
m/min
m/h
rps
rpm
rph
m/s2
rad/s
km/h

データ
18
19
20
21
22
23
24
25
26
27
28
29
30
31
32
33
34
35

単位
t/min
kg/ming/min
m3/min
l/min
t/s
kg/s
g/s
m3/s
l/s

データ
108
109
110
111
112
113
114
115
116
117
118
119
120
121
122
123
124
125

単位
us
ms
s
min
h
day
mV
V
kV
uA
mA
A
Hz
dB
W
kW
VA
kVA

mbar
bar
N/mm2
N/m2

データ
36
37
38
39
40
41
42
43
44
45
46
47
48
49
50
51
52
53

単位
MPa
Pa
KPa
Mpa

mm
cm
m

ml
L
kl
mm3
cm3
m3

データ
126
127
128
129
130
131
132
133
134
135
136
137
138
139
140
141
142
143

単位
Var
kVar
uS/cm
uF
F
C
mH
H
m ohm
ohm
k ohm
M ohm
lx
cd
lm
cd/m2

データ
54
55
56
57
58
59
60
61
62
63
64
65
66
67
68
69
70
71

単位
mm2
cm2
m2
g
kg
t
g/cm3
kg/cm3
g/m3
kg/m3

データ
144
145
146
147
148
149
150
151
152
153
154
155
156
157
158
159
160
161

単位
uSv/h
mSv/h
nGy/h
uGy/h
um

*Unit1～12 :単位作成画面で作成した単位が選択されます。
表 4 測定範囲の設定範囲
入力種別
50mV
500mV
1-5V
0-5V

設定範囲
–1000 ～ 5500 (–10.00 ～ 55.00mV)–100 ～ 5500 (–10.0 ～ 550.0mV)
500 ～ 5500 (0.500 ～ 5.500V)–100 ～ 5500 (–0.100 ～ 5.500V)

表 5 小数点位置コード
小数点位置データ
0
1
2
3
4

設定範囲
–32767 ～ 32767–3276.7 ～ 3276.7–327.67 ～ 327.67–32.767 ～ 32.767–3.2767 ～ 3.2767

－42－

g/l
kg/l
g/ml

Pa･s
mPa･s

*Unit 1
*Unit 2
*Unit 3
*Unit 4
*Unit 5
*Unit 6

データ
72
73
74
75
76
77
78
79
80
81
82
83
84
85
86
87
88
89

単位
ppm
ppmNH3
ppmSO2
ppmH2S
ppmCO
ppmO2
ppmNOx
ppb
pH
mol
%
%H2
%CO2
%He
%Ar
%O2
%NaCl
%CO

データ
162
163
164
165
166
167

単位
*Unit 7
*Unit 8
*Unit 9*Unit 10
*Unit 11
*Unit 12

表 6 表示範囲等の設定範囲
・F 値演算 OFF の場合
入力種別 熱電対，測温抵抗体タイプ°C (摂氏)°F (華氏)

入力種別

表示範囲
警報 No.1～4 設定値
積算カット値

表示範囲
警報 No.1～4 設定値
積算カット値

K 熱電対
E 熱電対
J 熱電対
T 熱電対
R 熱電対
S 熱電対
B 熱電対
N 熱電対
W 熱電対
L 熱電対
U 熱電対
PN 熱電対
Pt100
JPt100–2300 ～ 14000 (–230.0 ～ 1400.0°C)–2300 ～ 8300 (–230.0 ～ 830.0°C)–2300 ～ 11300 (–230.0 ～ 1130.0°C)–2300 ～ 4300 (–230.0 ～ 430.0°C)–300 ～ 17900 (–30.0 ～ 1790.0°C)–300 ～ 17900 (–30.0 ～ 1790.0°C)
3700 ～ 17900 (370.0 ～ 1790.0°C)–300 ～ 13300 (–30.0 ～ 1330.0°C)–300 ～ 17900 (–30.0 ～ 1790.0°C)–2300 ～ 9300 (–230.0 ～ 930.0°C)–2300 ～ 4300 (–230.0 ～ 430.0°C)–300 ～ 13300 (–30.0 ～ 1330.0°C)–2300 ～ 6300 (–230.0 ～ 630.0°C)–2300 ～ 6300 (–230.0 ～ 630.0°C)–3820 ～ 25520 (–382.0 ～ 2552.0°F)–3820 ～ 15260 (–382.0 ～ 1526.0°F)–3820 ～ 20660 (–382.0 ～ 2066.0°F)–3820 ～ 8060 (–382.0 ～ 806.0°F)–220 ～ 32540 (–22.0 ～ 3254.0°F)–220 ～ 32540 (–22.0 ～ 3254.0°F)
6980 ～ 32540 (698.0 ～ 3254.0°F)–220 ～ 24260 (–22.0 ～ 2426.0°F)–220 ～ 32540 (–22.0 ～ 3254.0°F)–3820 ～ 17060 (–382.0 ～ 1706.0°F)–3820 ～ 8060 (–382.0 ～ 806.0°F)–220 ～ 24260 (–22.0 ～ 2426.0°F)–3820 ～ 11660 (–382.0 ～ 1166.0°F)–3820 ～ 11660 (–382.0 ～ 1166.0°F)

入力種別 電圧タイプ
スケーリング OFF
表示範囲
警報 No.1～4 設定値
積算カット値

入力種別
50mV–1000 ～ 5500 (–10.00 ～ 55.00mV)

500mV–100 ～ 5500 (–10.0 ～ 550.0mV)

1-5V

500 ～ 5500 (0.500 ～ 5.500V)

0-5V–100 ～ 5500 (–0.100 ～ 5.500V)・F 値演算 ON の場合

入力種別

表示範囲
警報 No.1～4 設定値
積算カット値

全種–32767 ～ 32767 (詳細は表 15 を参照)

表 7 積算タイプコード
データ
0
1
3
6
15

スケーリング ON
表示範囲
警報 No.1～4 設定値
積算カット値

積算タイプ
日報
月報
年報
外部入力
OFF

－43－

–32767 ～ 32767 (詳細は表 5 を参照)

表 8 外部入力コード
データ
0
1
2
3
4
5
6
7
8
9

入力
DI 1
DI 2
DI 3
DI 4
DI 5
DI 6
DI 7
DI 8
DI 9
DI 10

データ
10
11
12
13
14

入力
CH 1 警報 No.1
CH 1 警報 No.2
CH 1 警報 No.3
CH 1 警報 No.4
CH 2 警報 No.1

126
127
128
129

CH30 警報 No.1
CH30 警報 No.2
CH30 警報 No.3
CH30 警報 No.4

11
12
13
14
15

入力
CH 1 警報 No.1
CH 1 警 No.2
CH 1 警報 No.3
CH 1 警報 No.4
CH 2 警報 No.1

127
128
129
130

CH30 警報 No.1
CH30 警報 No.2
CH30 警報 No.3
CH30 警報 No.4

表 9 積算時間コード
0
1
2
3
4

入力
無し
DI 1
DI 2
DI 3
DI 4

5

DI 5

6
7
8
9
10

DI 6
DI 7
DI 8
DI 9
DI 10

データ

… …

データ

表 10 積算時間コード
データ
0
1
2
3
4
5
6
7
8
9

積算時間
10 分
20 分
30 分
1 時間
2 時間
3 時間
4 時間
6 時間
12 時間
24 時間

－44－

表 11 演算式コード

演算内容 = 四則演算データ ＋ 関数データ × 256
データ 関数データ
データ
四則演算データ
0

無し

0

演算式終了

1

ABS

1

+ ( １番目の演算式に設定してください。)

2

POW

2

-

3

SQR

3

*

4

LOG

4

/

5

LN

6

EXP

7

RH

8

MAX

9

MIN

10

H-P

11

L-P

12

AVG

13

SUM

引数１，２ ＝ 引数タイプ × ２５６ ＋ データ№

データ

引数タイプ

引数の設定囲0

チャネル測定値

0 ～ 29 (チャネル 1 ～ 30 : C01 ～ C30 )1

チャネル積算値

0 ～ 29 (チャネル積算 1 ～ 30 : T01 ～ T30 )2

ディジタル入力

0 ～ 9 (DI1 ～ 10 : D01 ～ D10 )

3

通信入力

0 ～ 11(通信入力 1 ～ 12 : M01 ～ M12)4

定数

0 ～ 19 (定数 1 ～ 20 : K01 ～ K20 )

5

演算式１～３の結果

0 ～ 2 (演算式の結果 1 ～ 3 : B01 ～ B03 )例）チャネル１９の演算式１に “POW(C01, T02)*K03” を設定する場合、以下の値を設定してください。
アドレス

データ
42551
42552
42553
42554
42555
42556
42557
42558
42559

513
0
257
3
1026
0
0
0
0

表 12 定数データ
小数点位置
0
1
2
3
4

表示
(+)POW
C01
T02
*
K03
(無し)
(終了)
(無し)
(無し)

内容
四則演算データ : "+" (1)+関数データ : "POW"(2 * 256)
引数タイプ : チャネル測定値(0 * 256) + データ№ : 1 (0)引数タイプ : チャネル積算値(1 * 256) + データ№ : 2 (1)
四則演算データ : "*" (3)+関数データ : 無し (0 * 256)
引数タイプ : 定数(4 * 256) + データ№ : 3 (2)定数範囲-32767 ～ 32767-3276.7 ～ 3276.7-327.67 ～ 327.67-32.767 ～ 32.767-3.2767 ～ 3.2767－45－

表 13 表示更新周期
データ
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16
17
18
19

更新周期
1秒
2秒
3秒
5秒
10 秒
20 秒
30 秒
1分
2分
3分
5分
10 分
20 分
30 分
1時
2時
3時
4時
6時
12 時

表 14 ファイル分割周期コード
データ
0
1
2
3
4

ファイル分割周期
分割しない
１時間
１日
１週間
１ヶ月

表 15 F 値演算小数点位置
小数点位置
0
1
2
3
4

F 値演算 ON の場合–32767 ～ 32767–3276.7 ～ 3276.7–327.67 ～ 327.67–32.767 ～ 32.767–3.2767 ～ 3.2767

表 16 メッセージタイミングデータ
メッセージタイミングの内容により，意味が違います。
データ
0
1
2
3
4

メッセージタイミング無し
DI ON
DI OFF
警報発生
警報解除

DI No.／警報チャネル無し
0 ～ 9 ( DI1 ～ 10)
0 ～ 9 ( DI1 ～ 10)
0 ～ 17 ( CH 1 ～ 18 )0 ～ 17 ( CH 1 ～ 18 )－46－

警報 No.
無し
無し
無し
0 ～ 3 ( 警報 No.1 ～ 4 )0 ～ 3 ( 警報 No.1 ～ 4 )表 17 DI 機能設定
データ
0
1
2
3
4
5

DI 機能
無効
記録開始/停止
F 値演算リセット
積算開始/停止
積算リセット
画面点灯

表 18 本体コントロールフラグ
ビット
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15

内容
記録開始/停止
未使用
積算開始/停止
画面点灯
未使用
未使用
未使用
未使用
未使用
未使用
未使用
未使用
未使用
未使用
未使用
未使用

ライトデータ
0:記録停止，1:記録開始
0:積算停止，1:積算開始
0:変化無し，1:画面点灯

表 19 メッセージ要求フラグ
ビット
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15

内容
メッセージ No.1 要求
メッセージ No.2 要求
メッセージ No.3 要求
メッセージ No.4 要求
メッセージ No.5 要求
メッセージ No.6 要求
メッセージ No.7 要求
メッセージ No.8 要求
メッセージ No.9 要求
メッセージ No.10 要求
未使用
未使用
未使用
未使用
未使用
未使用

ライトデータ0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求
0:変化無し，1:メッセージ要求－47－

表 20 チャネルごとの積算リセット要求
書き込みデータ ０：変化無し，１：積算リセット要求
Bit

Address 45051

Address 45052

0

チャネル１

チャネル１７1

チャネル２

チャネル１８2

チャネル３

チャネル１９3

チャネル４

チャネル２０4

チャネル５

チャネル２１5

チャネル６チャネル２２6チャネル７チャネル２３7

チャネル８チャネル２４8チャネル９チャネル２５9

チャネル１０チャネル２６10

チャネル１１

チャネル２７11

チャネル１２チャネル２８12

チャネル１３

チャネル２９13

チャネル１４

チャネル３０14

チャネル１５

未使用

15

チャネル１６

未使用

表 21 E-mail トリガータイミングデータ
E-mail トリガータイミングの内容により，引数１と引数２の意味が違います。
データ
0
1
2
3
4
5

トリガータイミング無し
DI ON
DI OFF
警報発生
警報解除
本体異常警報

6

定周期

引数 1
無し
0 ～ 29 ( DI1 ～ 30)
0 ～ 29 ( DI1 ～ 30)
0 ～ 17 ( ﾁｬﾈﾙ 1 ～ 18 )0 ～ 17 ( ﾁｬﾈﾙ 1 ～ 18 )0 ～ 3
0: 全警報 OR 出力
1: 全警告 OR 出力
2: バッテリ無し
3: メモリカードフル
0 ～ 6
0: 1 時間
時間周期 1: 2 時間
2: 3 時間
3: 4 時間
4: 6 時間
5: 12 時間
6: 1 日

引数 2
無し
無し
無し
0 ～ 3 ( 警報 No.1 ～ 4 )0 ～ 3 ( 警報 No.1 ～ 4 )無し

0 ～ 23(基準時間 0:00 ～ 23:00 )表 22 送信先アドレス№
ビット
0
1
2
3
4
5
6
7
8
9

内容
E-mail アドレス No.1
E-mail アドレス No.2
E-mail アドレス No.3
E-mail アドレス No.4
E-mail アドレス No.5
E-mail アドレス No.6
E-mail アドレス No.7
E-mail アドレス No.8
未使用
未使用

データ
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス
0: 受信しない, 1: 受信するアドレス

－48－

10

未使用

11
12
13
14
15

未使用
未使用
未使用
未使用
未使用

表 23 システム情報
ビット
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15

内容
記録動作状態
CF 容量有り無し状態
ﾁｬﾈﾙ警報有り無し状態
未使用
未使用
画面状態
未使用
積算動作状態
バッテリ状態
未使用
CF 有り無し情報
未使用
未使用
未使用
未使用
未使用

リードデータ
0:停止中，1:記録中
0:容量有り，1:容量無し
0:無し，1:有り

0:点灯，1:消灯
0:停止中，1:積算中
0:バッテリ有り，1:バッテリ無し
0:無し，1:有り

表 24 DO 出力情報
ビット
0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15

アドレス 30003
内容DO 1 情報DO 2 情報DO 3 情報DO 4 情報DO 5 情報DO 6 情報DO 7 情報DO 8 情報DO 9 情報
DO 10 情報DO 11 情報DO 12 情報DO 13 情報DO 14 情報
DO 15 情報DO 16 情報

リードデータ
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON

表 25 DI 情報
ビット
0
1
2
3
4
5
6

内容
DI 1 情報DI 2 情報DI 3 情報DI 4 情報DI 5 情報DI 6 情報DI 7 情報

リードデータ
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON－49－

アドレス 30004
内容
DO 17 情報DO 18 情報DO 19 情報
DO 20 情報
DO 21 情報
DO 22 情報
DO 23 情報
DO 24 情報
DO 25 情報
DO 26 情報DO 27 情報DO 28 情報
未使用
未使用
未使用
未使用

リードデータ
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON
0:OFF，1:ON

7

DI 8 情報

0:OFF，1:ON

8

DI 9 情報

0:OFF，1:ON

9
10
11
12
13
14
15

DI 10 情報
未使用
未使用
未使用
未使用
未使用
未使用

0:OFF，1:ON

表 26 警報出力情報
全データ
0:警報 OFF, 1:ON
ビット

アドレス 30093

アドレス 30094

アドレス 30095

アドレス 30096

アドレス 30097

アドレス 30098

アドレス 30099

アドレス 30100

0

CH 1 警報 No.1

CH 5 警報 No.1

CH 9 警報 No.1

CH 13 警報 No.1

CH 17 警報 No.1

CH 21 警報 No.1

CH 25 警報 No.1

CH 29 警報 No.1

1

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

2

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.33

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

4

CH 2 警報 No.1

CH 10 警報 No.1

CH 14 警報 No.1

CH 18 警報 No.1

CH 22 警報 No.1

CH 26 警報 No.1

CH 30 警報 No.1

5

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

6

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

7

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

8

CH 3 警報 No.1

CH 11 警報 No.1

CH 15 警報 No.1

CH 19 警報 No.1

CH 23 警報 No.1

CH 27 警報 No.1

未使用

9

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

未使用

10

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

未使用

11

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

未使用

12

CH 4 警報 No.1

CH 12 警報 No.1

CH 16 警報 No.1

CH 20 警報 No.1

CH 24 警報 No.1

CH 28 警報 No.1

未使用

13

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

警報 No.2

未使用

14

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

警報 No.3

未使用

15

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

警報 No.4

未使用

CH 6 警報 No.1

CH 7 警報 No.1

CH 8 警報 No.1

－50－

8.

サンプルプログラム

本章では，PC-9801*1 及び互換機の N88-日本語 BASIC*2 にて動作する，データ読出し／書込みサンプ
ルプログラムを示します。
尚，ここで示すプログラムは，お客様のプログラム作成の際の参考として頂くためであり，全ての動作を保証するものではありません。
プログラム実行前に，下記要領で通信条件についてご確認ください。
・通信速度（ボーレート）:
MS-DOS*3 の SWITCH コマンド，及び SPEED コマンドで本機にあわせてください。
SWITCH コマンド及び SPEED コマンドについては，MS-DOS のリファレンスマニュアルを参照ください。
・ データ長，ストップビット，パリティ:
本プログラム内で設定します。本機との条件をあわせてください。
注）PC-9801 は日本電気株式会社の商標または登録商標です。
注）N88-日本語 BASIC は日本電気株式会社の商標または登録商標です。
注）MS-DOS は Microsoft Corporation の商標または登録商標です。

－51－

(a) データ読出し例
動作説明：チャネル 1～9 の測定値を 1 度に読出します。
（読み出しのみ可能領域からの読み出し）使用するファンクションコード

：04H

読み出し開始レジスタ番号：30101

読み出しワード数：91000 '------------------------------------------------------1010 '連続ワード読出し
SAMPLE PROGRAM
1020 '------------------------------------------------------1030 '
1040 '
1050 '
1060 CLS
1070 DIM CC(255)1080 '
1100 '-------------- 送信データ設定値 ----------------------1110 CC(1)=&H01'ステーションNo. = 11120 CC(2)=&H04'ファンクションコード
= 04H1130 CC(3)=&H00'レジスタ番号30101の相対アドレス(0064H)の上位バイト
1140 CC(4)=&H64'レジスタ番号30101の相対アドレス(0064H)の下位バイト
1150 CC(5)=&H00'読み出しワード数(0009H)の上位バイト
1160 CC(6)=&H09'読み出しワード数(0009H)の下位バイト
1170 COUNT=61200 '
1210 '------------- 送信データのCRCコード計算 -------------1220 GOSUB *CRC.CALC
1230 CC(7)=CRC.L'CRC演算結果の下位バイト→メッセージでの上位バイト
1240 CC(8)=CRC.H'CRC演算結果の上位バイト→メッセージでの下位バイト
1250 COUNT=COUNT+2
1300 '
1310 '------------- データ送信 ----------------------------1320 PRINT "送信データ > ";1330 OPEN "COM1:O81NN" AS #1'奇数パリティ･･･ "O81NN"
1340'偶数パリティの時 ･･･ "E81NN"
1350'パリティ無しの時 ･･･ "N81NN"
1360 FOR I=1 TO COUNT
1370
PRINT #1,CHR$(CC(I));'通信ポートに書込み
1380
PRINT RIGHT$("0"+HEX$(CC(I)),2);" "; '画面に表示
1390 NEXT I
1400 '
1410 FOR I=O TO 300000 :NEXT I'インターバル時間
1500 '
1510 '------------- データ受信 ---------------------------1520 PRINT
1530 LENGTH=LOC(1)'受信バッファにあるデータ数
1540 IF LENGTH=0 THEN PRINT "No answer" :END
1550 PRINT "受信データ < ";1560 FOR I=1 TO LENGTH
1570
X$=INPUT$(1,#1)'受信バッファからデータ取り込み
1580
CC(I)=ASC(X$)'数値化して格納
1590
PRINT RIGHT$("0"+HEX$(CC(I)),2);" "; '画面に表示
1600 NEXT I
1610 CLOSE #1
1620 COUNT=LENGTH-2
1630 GOSUB *CRC.CALC
1700 '
1710 '------------- 通信エラー確認 -----------------------－52－

1720 PRINT
1730 CRC.L$=RIGHT$("0"+HEX$(CRC.L),2)
1740 CRC.H$=RIGHT$("0"+HEX$(CRC.H),2)
1750 PRINT "CRC calculation = ";CRC.L$;" ";CRC.H$
1760 IF CC(LENGTH-1)<>CRC.L THEN GOTO *ER.MESSAGE
1770 IF CC(LENGTH)<>CRC.H THEN GOTO *ER.MESSAGE
1780 GOTO *PRT.RESULT
1790 *ER.MESSAGE
1800 PRINT "Communication error"
1810 END
1900 '
1910 '------------- 結果の表示 --------------------------1920 *PRT.RESULT
1930 '単位がmＶで小数点位置が1の時
1940 PRINT
1950 CH1$=HEX$(CC(4))+RIGHT$("0"+HEX$(CC(5)),2)'2byte → 1word
1960 CH2$=HEX$(CC(6))+RIGHT$("0"+HEX$(CC(7)),2)'2byte → 1word
1970 CH3$=HEX$(CC(8))+RIGHT$("0"+HEX$(CC(9)),2)'2byte → 1word
1980 CH4$=HEX$(CC(10))+RIGHT$("0"+HEX$(CC(11)),2) '2byte → 1word
1990 CH5$=HEX$(CC(12))+RIGHT$("0"+HEX$(CC(13)),2) '2byte → 1word
2000 CH6$=HEX$(CC(14))+RIGHT$("0"+HEX$(CC(15)),2) '2byte → 1word
2010 CH7$=HEX$(CC(16))+RIGHT$("0"+HEX$(CC(17)),2) '2byte → 1word
2020 CH8$=HEX$(CC(18))+RIGHT$("0"+HEX$(CC(19)),2) '2byte → 1word
2030 CH9$=HEX$(CC(20))+RIGHT$("0"+HEX$(CC(21)),2) '2byte → 1word
2040 PRINT "CH1 =";VAL("&H"+CH1$)/10;"mV"'小数点以下1桁
2050 PRINT "CH2 =";VAL("&H"+CH2$)/10;"mV"'小数点以下1桁
2060 PRINT "CH3 =";VAL("&H"+CH3$)/10;"mV"'小数点以下1桁2070 PRINT "CH4 =";VAL("&H"+CH4$)/10;"mV"'小数点以下1桁
2080 PRINT "CH5 =";VAL("&H"+CH5$)/10;"mV"'小数点以下1桁
2090 PRINT "CH6 =";VAL("&H"+CH6$)/10;"mV"'小数点以下1桁
2100 PRINT "CH7 =";VAL("&H"+CH7$)/10;"mV"'小数点以下1桁
2110 PRINT "CH8 =";VAL("&H"+CH8$)/10;"mV"'小数点以下1桁
2120 PRINT "CH9 =";VAL("&H"+CH9$)/10;"mV"'小数点以下1桁
2130 END
3000 '
3010 '------------ CRC 計算 -----------------------------3020 *CRC.CALC'内容はCRC算出フロー参照
3030 CR=&HFFFF
3040 FOR I=1 TO COUNT
3050
CR=CR XOR CC(I)3060
FOR J=1 TO 8
3070
CT=CR AND &H1
3080
IF CR<0 THEN CH=1 ELSE CH=0:GOTO *CRC.CALC.10
3090
CR=CR AND &H7FFF
3100*CRC.CALC.10
3110
CR=INT(CR/2)
3120
IF CH=1 THEN CR=CR OR &H4000
3130
IF CT=1 THEN CR=CR XOR &HA001
3140
NEXT J
3150 NEXT I
3160 CRC.L=CR AND &HFF
'CRC計算下位バイト
3170 CRC.H=((CR AND &HFF00)/256 AND &HFF)'CRC計算上位バイト
3180 RETURN－53－

(b) データ書込み例
動作説明：通信経由でステーション No.1 の警報ラッチを解除します。
（1 ワード書き込み）
使用するファンクションコード

：10H

書き込み開始レジスタ番号：45007

書き込みワード数：1

書き込みデータ：1（警報ラッチ解除）

1000 '------------------------------------------------------1010 '1ワード書込みSAMPLE PROGRAM
1020 '------------------------------------------------------1030 '
1040 '
1050 '
1060 CLS
1070 DIM CC(255)1080 '
1100 '-------------- 送信データ設定値 ----------------------1110 CC(1)=&H01'ステーションNo. = 11120 CC(2)=&H10'ファンクションコード = 10H
1130 CC(3)=&H13'レジスタ番号45007の相対アドレス(138EH)の上位バイト
1140 CC(4)=&H8E'レジスタ番号45007の相対アドレス(138EH)の下位バイト
1150 CC(5)=&H00'書き込みワード数(0001H)の上位バイト
1160 CC(6)=&H01'書き込みワード数(0001H)の下位バイト
1170 CC(7)=&H02'書き込みワード数* 21180 CC(8)=&H00'書き込みデータの上位バイト(0001H)
1190 CC(9)=&H01'書き込みデータの下位バイト(0001H)
1200 COUNT=91210 '------------- 送信データのCRCコード計算 -------------1220 GOSUB *CRC.CALC
1230 CC(10)=CRC.L'CRC計算結果の下位バイト -> メッセージにおける上位バイト
1240 CC(11)=CRC.H'CRC計算結果の上位バイト -> メッセージにおける下位バイト
1250 COUNT=COUNT+2
1300 '
1310 '------------- データ送信 ----------------------------1320 PRINT "送信データ > ";1330 OPEN "COM1:081NN" AS #1 '9600bps，奇数パリティ，データ長 8ビット，ストップビット 1ビット
1340 FOR I=1 TO COUNT
1350
PRINT #1,CHR$(CC(I));'伝送ポートにおける書き込み
1360
PRINT RIGHT$("0"+HEX$(CC(I)),2);" "; '画面上に表示
1370 NEXT I
1380 '
1390 FOR I=O TO 300000 :NEXT I'インターバル間隔
1500 '
1510 '------------- データ受信 ---------------------------1520 PRINT
1530 LENGTH=LOC(1)'受信バッファにおけるデータ数
1540 IF LENGTH=0 THEN PRINT "No answer" :END
1550 PRINT "受信データ < ";1560 FOR I=1 TO LENGTH
1570
X$=INPUT$(1,#1)'受信バッファからのデータ取り込み
1580
CC(I)=ASC(X$)'デジタル化および記憶
1590
PRINT RIGHT$("0"+HEX$(CC(I)),2);" "; '画面上に表示
1600 NEXT I
1610 CLOSE #1
1620 COUNT=LENGTH-2
1630 GOSUB *CRC.CALC'GOSUB *CRC.CALC
1700 '－54－

1710 '------------- 通信エラーのチェック ----------------------1720 PRINT
1730 CRC.L$=RIGHT$("0"+HEX$(CRC.L),2)
1740 CRC.H$=RIGHT$("0"+HEX$(CRC.H),2)
1750 PRINT "CRC calculation = ";CRC.L$;" ";CRC.H$
1760 IF CC(LENGTH-1)<>CRC.L THEN GOTO *ER.MESSAGE'GOTO *ER.MESSAGE
1770 IF CC(LENGTH)<>CRC.H THEN GOTO *ER.MESSAGE'GOTO *ER.MESSAGE
1780 GOTO *PRT.RESULT'GOTO *PRT.RESULT
1790 *ER.MESSAGE
1800 PRINT "Communication error"
1810 END
1900 '
1910 '------------- 結果表示 --------------------------1920 *PRT.RESULT
1930 PRINT
1940 PRINT "Completion of alarm latch clear"1950 END
3000 '
3010 '------------ CRC計算 -----------------------------3020 *CRC.CALC'内容については，CRC計算フローチャートを参照してください。
3030 CR=&HFFFF
3040 FOR I=1 TO COUNT
3050
CR=CR XOR CC(I)3060
FOR J=1 TO 8
3070
CT=CR AND &H1
3080
IF CR<0 THEN CH=1 ELSE CH=0:GOTO *CRC.CALC.10
3090
CR=CR AND &H7FFF
3100*CRC.CALC.10
3110
CR=INT(CR/2)
3120
IF CH=1 THEN CR=CR OR &H4000
3130
IF CT=1 THEN CR=CR XOR &HA001
3140
NEXT J
3150 NEXT I
3160 CRC.L=CR AND &HFF
'CRC計算の下位バイト
3170 CRC.H=((CR AND &HFF00)/256 AND &HFF)'CRC計算の上位バイト
3180 RETURN

－55－

9.

イーサネット通信機能

イーサネット通信として、FTP サーバ機能、Web サーバ機能、E-mail 送信機能、MODBUS TCP/IP機能を使用できます。
ペーパーレスレコーダをイーサネットに接続する場合、IP アドレスなどの設定が必要ですので、必ず貴社のシステム管理者にご相談ください。

9.1 LAN ボード仕様
項目仕様

10BASE-T

伝送速度

10Mbps

伝送方式

ベースバンド最大ネットワーク長または最大ノード間隔

500ｍ（カスケード４段）

最大セグメント長

100m（ノードと HUB 間）

接続ケーブル

UTP（シールド無ツイストペア）22-26AWG

プロトコル

TCP/IP

9.2 接続先9.3 接続イーサネットHUB
10 BASE-T
ストレートケーブル

ノードと HUB 間の距離

： 最長 100ｍ

ネットワーク最大ノード数：100 台－56－

推奨ケーブル：10BASE-T ツイストペアケーブル カテゴリー5－57－

9.4 イーサネット通信条件設定

ペーパーレスレコーダをイーサネットに接続する為，IP アドレス, サブネットマスク，デフォルト
ゲートウェイの設定を行います。
（設定する値については，貴社のシステム管理者に相談してください。）



通信条件設定項目
項目

工場出荷初期設定

IP アドレス

192.168.

1.

1

各桁 0 to 255

サブネットマスク255.255.255.

0

各桁 0 to 255

デフォルトゲートウェイ

0.

0. 0.

0

備考

設定値の範囲設定変更後は，電源を再投入してください。

各桁 0 to 255

9.5 イーサネット通信条件設定操作方法①

パラメータ設定画面で「本体設定」→「イーサネット通信設定」を選びます。「イーサネット通
信設定」画面が表示されます。

②「イーサネット通信設定１」を選択してください。以下の画面が表示されます。

③"IP アドレス"にカーソルを移動し，IP アドレス を設定してください。

④"サブネットマスク"にカーソルを移動し，サブネットマスク を設定してください。

⑤"デフォルトゲートウェイ"にカーソルを移動し，デフォルトゲートウェイ を設定してください。

－58－

10.
10.1

FTP サーバ機能

FTP サーバ機能説明ブラウザまたは DOS プロンプトを使用し，記録計のコンパクトフラッシュに記録されている記録
ファイルを取り出すことが出来ます。
 ブラウザまたはＤＯＳプロンプトを使用し、記録計の内部メモリに記録されている記録データを取り出すことが出来ます。
 ブラウザまたは DOS プロンプトを使用し，記録計のコンパクトフラッシュに記録されている記録
ファイルを削除することが出来ます。（管理者レベルのユーザのみ削除可能です。
）
 ブラウザまたは DOS プロンプトを使用し，記録計のコンパクトフラッシュに記録されている記録
ファイルの名前を変更することが出来ます。
（管理者レベルのユーザのみ変更可能です。）
 パソコンのブラウザは，Microsoft 製の Internet Explorer を使用してください。
 FTP サーバにログインできるユーザ名とパスワードを８人まで設定することが出来ます。
 FTP アクセス管理機能を OFF に設定した場合，共通ユーザ名"ftp"（パスワードなし）にて FTP
サーバにログインすることが出来ます。
 FTP サーバにログイン，ログオフした時，イーサネットログ画面にその情報が表示されます。
 FTP サーバには，同時に 1 ユーザしかログインできません。
 記録計の内部メモリの記録データは、本体の"記録データ形式"設定に関係なくバイナリ形式になります。
 ＦＴＰサーバのフォルダ構成は、下図のようになっています。
（注意） FTP 通信要求が 10 分間無かった場合，通信が自動的に切断されます。
 ファイルサイズの大きいファイルを取りだす時，ペーパレスレコーダの表示動作が遅くなる場合があります。
 FTP 通信にてペーパレスレコーダのコンパクトフラッシュにアクセスしている時，コンパクトフ
ラッシュを取り出さないでください。また，FTP サーバ機能を使用している場合，"メモリカード
取出し"画面にてコンパクトフラッシュのアクセスを禁止してから取り出してください。
 記録，積算中のファイルの削除および名前の変更は行わないでください。
 FTP サーバ内のファイル属性は，すべて隠しファイルでリードオンリー属性として表示されます。
 FTP サーバにログイン中にイーサネット通信を強制終了させた場合，10 分経過して通信が自動的に切断するまで，再度ログインできません。
 FTP 通信にてペーパレスレコーダのコンパクトフラッシュにファイルを書き込むことは出来ません。
 FTP 通信にてペーパレスレコーダのコンパクトフラッシュ内のファイル一覧を表示した時，ファイルの更新時間が実際の時間と違っている場合があります。

－59－

ＦＴＰサーバのフォルダ構成

－60－

10.2

FTP サーバ機能設定



FTP サーバ機能を使用する為，FTP サーバ機能の設定とアクセス認証設定を行います。
また，FTP サーバ機能を使用するユーザ名とパスワードの設定を行います。

FTP サーバ機能設定項目項目



工場出荷初期設定

設定値の範囲FTP サーバ機能

OFF

ON，OFFFTP アクセス管理

OFF

ON，OFF

備考
設定変更後は，電源を再投入してください。

ユーザアカウント設定項目
項目
ユーザ名（№1～8)

工場出荷初期設定(空白)

設定値の範囲16 文字まで設定可能

パスワード（№1～8)(空白)

8 文字まで設定可能

ユーザレベル（№1～8)

管理者

管理者，ゲスト

－61－

備考

10.3


FTP サーバ機能設定操作方法

FTP サーバ機能設定① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→「イーサネット通信設定２」を選択してください。以下の画面が表示されます。

②"FTP サーバ機能"にカーソルを移動し，FTP サーバ機能の ON/OFF を選択してください。ONを設定した場合，FTP サーバ機能を使用することが出来ます。

③"FTP アクセス管理"にカーソルを移動し，FTP アクセス管理機能の ON/OFF を選択してください。ON を設定した場合，FTP サーバにログインする時，パスワードの入力が必要になります。



ユーザ名設定① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→「ユーザアカウント設定」を選択してください。以下の画面が表示されます。

②

設定したいユーザ№を選択してください。

③

ユーザ名を 16 文字以内で設定してください。

④

パスワードを 8 文字以内で設定してください。

⑤

ユーザのアクセスレベルを "管理者"と"ゲスト"から選択してください。ゲストを設定した場合，
FTP サーバにログインしてもファイルを削除することは出来ません。

－62－

10.4


FTP サーバ操作方法

以下の手順で操作を行い，ペーパーレスレコーダにブラウザから接続してください。
① Ethernet 上のパソコンで Internet Explorer を起動してください。
②

アドレス欄に以下の様にペーパーレスレコーダのＩＰアドレスを入力してください。
FTP:// (ペーパーレスレコーダの IP アドレス)
ペーパーレスレコーダの IP アドレスが，192.168.1.2 の場合は，FTP://192.168.1.2 と入力します。

③

ユーザ名とパスワードの入力要求画面が表示されますので，ユーザ名とパスワードを入力してください。

④

ブラウザ上に”Ｓ００００００”と”ＭＥＭＯＲＹ”ディレクトリが表示されます。
コンパクトフラッシュ内の記録ファイルを表示したい場合は、"S000000"フォルダを選択してください。
内部メモリ内の記録データを表示したい場合は、"MEMORY"フォルダを選択してください。

⑤

ブラウザ上に記録されている記録ファイルが表示されます。

⑥

取り出したいファイルを選択し、パソコン内の任意のフォルダにコピーしてください。

⑦

コンパクトフラッシュを選択している場合、記録ファイルの削除も可能です。
削除したいファイルを選択し、ファイルを削除してください。

－63－

11.
11.1

Web サーバ機能

Web サーバ機能説明

 ペーパーレスレコーダの測定値やイベントログをパソコンのブラウザでモニタすることが出来ます。
 パソコンのブラウザは，Microsoft 製の Internet Explorer を使用してください。
（注意）

携帯電話のブラウザではモニタすることは出来ません。携帯電話からレコーダの Web サーバに接続した場合，最悪レコーダが停止する可能性が有りますので，携帯電話からはモニタしないでください。
ブラウザへの更新周期が 10 秒のため，通信状況によりエラーが発生する場合があります。その場
合は，ブラウザの更新ボタンを押していただくと再度パソコンの画面が表示されます。
ご使用しているブラウザの環境によっては，文字が正常に表示されない場合があります。
9 チャネル仕様のペーパーレスレコーダの場合，測定値表示画面のチャネル 10～18 の測定値に0.0℃と表示されます。





11.2

Web サーバ機能設定

Web サーバ機能を使用する為，Web サーバ機能の設定を行います。



設定項目
項目
Web サーバ機能

11.3①

工場出荷初期設定
OFF

設定値の範囲ON，OFF

備考
設定変更後は，電源を再投入してください。

Web サーバ機能設定操作方法
パラメータ設定画面で「本体設定」→「イーサネット通信設定」→「イーサネット通信設定 2」を選択してください。以下の画面が表示されます。

②"Web サーバ機能"にカーソルを移動し，Web サーバ機能の ON/OFF を選択してください。ONを設定した場合，Web サーバ機能を使用することが出来ます。

－64－

11.4


Web サーバ操作方法

以下の手順にて操作を行い，ペーパーレスレコーダにパソコンのブラウザから接続してください。
① イーサネットに接続しているパソコンで Internet Explorer を起動してください。
②

アドレス欄に以下の様にペーパーレスレコーダのＩＰアドレスを入力してください。
http:// (ペーパーレスレコーダの IP アドレス)
ペーパーレスレコーダの IP アドレスが，192.168.1.2 の場合は， http://192.168.1.2 と入力しま
す。

③

11.5


ブラウザ上にペーパーレスレコーダのモニタ画面が表示されます。

Web モニタ画面
ペーパーレスレコーダの Web サーバに接続し，以下の画面が表示されます。

①

Web モニタメニュー画面

－65－

②

測定値表示画面③

積算値表示画面－66－

④

イベントサマリ表示画面

－67－

12.
12.1



E-mail 送信機能

E-mail 送信機能説明

ペーパーレスレコーダから E-mail を送信することが出来ます。（受信は出来ません。）
以下の条件で E-mail を送信することが出来ます。
① 警報発生または解除した時②

外部入力(DI)が ON または OFF した時③本体に異常が発生した時（バッテリエンド，メモリカードフル，全てのチャネルの警報の内の 1
つの警報が発生した時）④

一定周期毎(1，2，3，4，6，12 時間，1 日の中から選択可能です。)

 E-mail 送信先は 8 つのアドレスまで登録することが出来ます。
 E-mail には，各チャネルの測定値を添付することが出来ます。
 E-mail トリガ設定画面で，E-mail の送信テストをすることが出来ます。
（注意） E-mail 送信要求は，最大 16 件までしか連続で送信することが出来ません。送信要求が 16 件を超えた場合は，送信されませんので，連続で送信要求が発生しないように設定してください。
 E-mail を送信するには，記録計をメールサーバに登録する必要があります。メールサーバへの登録は，貴社のシステム管理者に相談してください。
 メール送信に失敗した場合，そのメール送信要求は取り消されます。
 メールの送信が出来ても，送信先アドレスが間違っている等実際にはメールが届いていない場合がありますので，注意してください。
 E-mail トリガー設定で，メールの送信先アドレスを複数登録している場合，すべての送信が失敗しないとイーサネットログ画面に NG と表示されません。
 送信者名と E-mail タイトル，テキスト 1，テキスト 2 に半角カタカナは使用できません。
 E-mail に測定値を添付し、測定値の単位に半角カタカナを使用している場合、メールの文字化けが発生します。

12.2

E-mail 機能設定

 E-mail 機能を使用する為，E-mail 送受信アドレス設定と，E-mail 送信トリガ設定を行います。
（設定する値については，貴社のシステム管理者に相談してください。）
 E-mail 機能設定項目
項目
E-mail 機能

工場出荷初期設定
OFF

設定値の範囲ON，OFF

備考
設定変更後は，電源を再投入してください。

 E-mail 送受信アドレス設定項目
項目

工場出荷初期設定
0.

0. 0

設定値の範囲SMTP アドレス0.

送信元アドレス(空白)

64 文字まで設定可能

送信者名

(空白)

32 文字まで設定可能

送信先アドレス 1～8(空白)

64 文字まで設定可能

備考

各桁 0 to 255－68－

半角カタカナは使用できません。

 E-mail 送信トリガ設定項目
項目

(空白)

トリガータイミング

無し

設定値の範囲
備考
半角カタカナは使用できません。
32 文字まで設定可能
無し, DI ON, DI OFF,警
報発生,警報解除
本体異常警報，定周期ﾄﾘｶﾞｰﾀｲﾐﾝｸﾞ=DI ON, DI OFF
DI 1 ～ 10
ﾄﾘｶﾞｰﾀｲﾐﾝｸﾞ=警報発生, 警報解除
チャネル 1 ～ 18

DI No.

DI 1

警報チャネルチャネル 1

警報 No.

1

本体異常警報タイプ

警報 ON(全ﾁｬﾈﾙ OR)

時間周期

１時間

1～4
全警報 OR 出力, 全警告 ﾄﾘｶﾞｰﾀｲﾐﾝｸﾞ=本体異常警報
OR 出力,ﾊﾞｯﾃﾘ無し, ﾒﾓﾘ
ｶｰﾄﾞﾌﾙﾄﾘｶﾞｰﾀｲﾐﾝｸﾞ=定周期
1,2,3,4,6,12 時間, 1 日

基準時間

0:00

0:00 ～ 23:00

テキスト１

(空白)

32 文字まで設定可能

半角カタカナは使用できません。

テキスト２

(空白)

32 文字まで設定可能

半角カタカナは使用できません。

測定値添付

無し

有り，無し

送信先アドレス№

選択無し

送信先ｱﾄﾞﾚｽ 1～8 選択

12.3


工場出荷初期設定

タイトル

E-mail 機能設定操作方法

E-mail 機能設定
① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→「イーサネット通信設定 2」を選択してください。以下の画面が表示されます。

②"E-mail 機能"にカーソルを移動し，E-mail 機能の ON/OFF を選択してください。ON を設定した場合，E-mail 送信機能を使用することが出来ます。

－69－



E-mail 送受信アドレス設定① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→｢E-mail 設定１｣を選択してください。以下の画面が表示されます。

②"SMTP アドレス"にカーソルを移動し，メールサーバの IP アドレスを設定してください。

③"送信元アドレス"にカーソルを移動し，送信元メールアドレスを設定してください。

④"送信者名"にカーソルを移動し，メール送信者名を設定してください。

⑤

パラメータ設定画面で「本体設定」→「イーサネット通信設定」→｢E-mail 設定 2｣を選択してください。以下の画面が表示されます。

⑥"送信先アドレス" にカーソルを移動し，メールの送信先アドレスを８つまで設定してください。

－70－



E-mail 送信トリガー設定① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→｢E-mail トリガー設定」を選択してください。以下の画面が表示されます。

②

E-mail 送信タイミングを 10 パターンまで設定できます。設定したいトリガー№を選択してください。

③"タイトル"にカーソルを移動し，E-mail のタイトルを設定してください。

④"トリガータイミング" にカーソルを移動し，E-mail 送信タイミングを選択してください。

E-mail 送信タイミングとして，以下のいずれかを選択してください。
タイミングを選択すると，タイミングの種類毎に詳細設定項目が表示されますので，それらの項目も設定してください。
(1) DI ON, DI OFF
DI の ON/OFF により，E-mail を送信することが出来ます。
DI ON/OFF タイミングを選択すると使用する DI №の設定項目が表示されますので，判定に使用する DI №を設定してください。
(2) 警報発生，警報解除
警報の発生，解除情報により，E-mail を送信することが出来ます。
警報発生/解除タイミングを選択すると使用するチャネル№と警報№の設定項目が表示されます
ので，判定に使用するチャネル№と警報№を設定してください。

－71－

(3) 本体異常警報
本体異常警報の発生情報により，E-mail を送信することが出来ます。
本体異常警報を選択すると，使用する本体異常警報の情報設定項目が表示されますので，判定に使用する情報を選択してください。
(4) 定周期
一定周期で E-mail を送信することが出来ます。
定周期を選択すると，周期と基準時間の設定項目が表示されますので，E-mail を送信する周期と基準になる時間を設定してください。
⑤"テキスト 1","テキスト 2"にカーソルを移動し，E-mail の内容に記載するコメントを 2 行設定してください。

⑥"測定値添付有無" にカーソルを移動し，E-mail の内容に全チャネルの測定値を記載するかどうかを 設定してください。ON を設定した場合，E-mail に全チャネルの測定値が記載されます。

⑦"送信先アドレス№"にカーソルを移動し，E-maiｌを受信するアドレス№を選択してください。
ON を設定したアドレス№にメールが送信されます。

12.4
E-mail の送信テスト操作方法

以下の手順で操作を行い，ペーパレスレコーダのＥ－ｍａｉｌ送信テストを行うことが出来ます。
① パラメータ設定画面で「本体設定」→「イーサネット通信設定」→｢E-mail トリガー設定」を選択してください。
②

送信テストを行いたい E-mail トリガー設定№.を選択してください。

③"E-mail 送信テスト"にカーソルを移動し，[ENT]キーを押すと，メールの送信テストを行うことが出来ます。

12.5
E-mail 送信内容
ペーパレスレコーダは，以下のような内容の E-mail を送信します。
送信者名

E-mail タイトル
E-mail トリガータイミング＆送信時間
E-mail テキスト 1
E-mail テキスト 2
PV 値

－72－

－73－

13.
13.1


MODBUS TCP/IP 機能

MODBUS TCP/IP 機能説明
MODBUS TCP/IP プロトコルは，RS-485 インターフェースにて使用している MODBUS プロトコル(MODBUS RTU)をイーサネットインターフェース上でも使えるようにしたプロトコルです。
＊ＲＳ－４８５インターフェースの MODBUS プロトコル(MODBUS RTU)については，第 5～7章を参照してください。
MODBUS TCP/IP 通信は，ポート番号 502 で通信を行います。
MODBUS TCP/IP 機能を使用し，ペーパレス記録計の設定値の読出しや書込みが出来ます。




13.2




MODBUS TCP/IP 機能設定
MODBUS TCP/IP 機能を使用する為，MODBUS TCP/IP 機能の設定を行います。
通信する機器の判定用にステーション№を設定します。
設定項目
項目

工場出荷初期設定

設定値の範囲MODBUS TCP/IP

OFF

ON，OFFMODBUS ステーション NO.

1

0 ～ 255

13.3①

備考
設定変更後は，電源を再投入してください。
０の場合は，通信しません。

MODBUS TCP/IP 機能設定操作方法
パラメータ設定画面で「本体設定」→「イーサネット通信設定」→「イーサネット通信設定 2」を選択してください。以下の画面が表示されます。

②"MODBUS TCP/IP"にカーソルを移動し，MODBUS TCP/IP 機能の ON/OFF を選択してください。ON を設定した場合，MODBUS TCP/IP 機能を使用することが出来ます。

③

パラメータ設定画面で「本体設定」→「RS-485 通信設定」を選択してください。

④"MODBUS ステーション NO."にカーソルを移動し，ステーション№を設定してください。

－74－

13.4

MODBUS TCP/IP 通信プロトコル

MODBUS TCP/IP プ ロ ト コ ル に よ る 通 信 は ， RS-485 イ ン タ ー フ ェ ー ス に て 使 用 し て い る
MODBUS プロトコル(MODBUS RTU)と同じようにインターフェース上でも使えるようにしたプ
ロトコルです。
＊RS-485 インターフェースの MODBUS プロトコル(MODBUS RTU)については，第 5～7 章を参照してください。
 MODBUS TCP/IP 通信は，ポート番号 502 で通信を行います。
 MODBUS TCP/IP プロトコルで使用するメッセージはＭODBUS RTU で使用するメッセージから
エラーチェックコード（CRC-16)の２バイトを削除し，6 バイトのヘッダを追加したメッセージになります。
MODBUS RTU メッセージを MODBUS TCP/IP 用のメッセージに変換する場合は，以下のようになります。
M O D BU S R TUメ ッ セ ー ジ
M O D BU S T CP/I Pメ ッ セ ー ジ

ヘッダ

CRC

データ部
↓
データ部

 MODBUS TCP/IP メッセージのヘッダ部は，転送 ID，プロトコル ID，データ部の総バイト数で構成されます。
B y te No .
データの内容0
転 送 ID

データの意味

転 送 ID

1

プ ロ ト コ ル ID
データバイト数2プ ロ ト コ ル ID

3

4
データバイト数

5:指 令 メ ッ セ ー ジ と 同 じ 数 値 を 応 答 メ ッ セ ー ジ で返します。
: M OD B US T CP /IPの 場 合 は 、 0を 設 定 し ま す 。
:デ ー タ 部 の バ イ ト 数 で す 。

例えば、6.2 章(3)メッセージ伝送(例)を MODBUS TCP/IP メッセージに変換する場合は、以下のよ
うになります。
ステーション№１からチャネル 2 の測定値を読み出す場合
チャネル 2 の測定値の相対アドレス:0065H(レジスタ番号 30102），データ数：01H
指令メッセージの構成（バイト）
MODBUS RTU メッセージ（バイト）

MODBUS TCP/IP メッセージ（バイト）
ヘッダ

転送 ID
プロトコル ID
バイト数

データ部

CRC

ステーション No.

01H

ファンクションコード
読出し開始番号（相対アドレス）
読出しデータ数
CRC データ

上位

00H

下位

00H

上位

00H

下位

00H

上位

00H

下位

06H

ステーション No.

01H

04H

ファンクションコード

04H

上位

00H

読出し開始番号

上位

00H

下位

65H

（相対アドレス）

下位

65H

上位

00H

読出し

上位

00H

下位

01H

データ数

下位

01H

上位

21H

下位

D5H

データ部

－75－

応答メッセージの構成（バイト）
MODBUS RTU メッセージ（バイト）

MODBUS TCP/IP メッセージ（バイト）
ヘッダ

転送 ID
プロトコル ID
バイト数

ステーション No.

01H

ファンクションコード
読出しバイト数

データ部

00H

下位

00H

上位

00H

下位

00H

上位

00H

下位

05H

ステーション No.

01H

04H

ファンクションコード

04H

02H

読出しバイト数

02H

データ部

上位

01H

最初のワードデー

上位

01H

タの内容

下位

4FH

タ内容

下位

4FH

CRC データ

上位

F9H

下位

54H

最初のワードデー
CRC

上位

 通信異常時、以下のエラーコードが返信されます。
エラーコード02H

内容
ファンクション・コード
不良
レジスタに対するアドレ
ス不良

03H

レジスタの個数不良

04H

デバイスエラー

01H

説明
実在しないファンクション・コードが指定されました。
ファンクション・コードを確認してください。
指定したファンクション・コードで使用できない，レジスタ番号の相対アドレスが指定されています。
個数の指定が大き過ぎる為，レジスタ番号が存在しない領域まで，指定されています。
スレーブ機器との通信が失敗しました。スレーブ機器の通信仕様を確認してください。

－76－

14.

トラブルシューティング

通信ができない場合，下記の項目をご確認ください。
RS-485 MODBUS 通信の場合□

通信設定変更後に電源を再投入しましたか？

□

通信に関連する全ての機器の電源は入っていますか？

□

結線に間違いはありませんか？

□

接続台数，接続距離は仕様の範囲ですか？

□

マスタ（上位コンピュータ） と スレーブ（本機）間で通信条件の設定は一致していますか？
□

通信速度: □ 9600bps□ 19200bps: 8 ビット

□

データ長

□

ストップビット : 1 ビット

□

パリティ

: □ 奇数（odd）□ 偶数（even）□ なし（none）□

送受信信号のタイミングは，本書5.4項を満たしていますか？

□ マスタから送信先として指定しているステーション No.と，接続されている本機のステーション No.
設定は一致していますか？
□

同一の伝送ライン上に接続された機器同士で同じステーション No.を設定していませんか？

□

本機のステーション No.設定が 0 以外になっていますか？
0 の場合は通信機能は働きません。

□

本機の型式（GR200□□□□□-□□□

R□-□）12 桁目が R または W ですか？
W

イーサネット通信の場合（FTP,Web,E-mail､MODBUS TCP/IP 共通）□

通信設定変更後に電源を再投入しましたか？

□

通信に関する全ての機器の電源は入っていますか？

□

結線に間違いはありませんか？

□

接続台数，接続距離は仕様の範囲ですか？

□

通信条件は正しいですか？

□□IP アドレス□

サブネットマスク□

デフォルトゲートウェイ

本機の型式（GR200□□□□□-□□□

E□-□）１２桁目がＥまたはＷですか？
W

ＦＴＰサーバ機能の場合□

ユーザ名とパスワードとユーザレベルは正しいですか？

□

本体にコンパクトフラッシュは挿入されていますか？

－77－E-mail 送信機能の場合□□

通信条件は正しいですか？
□

SMTP アドレス□

送信元メールアドレス□

送信先メールアドレス

E-mail 送信条件は正しいですか？

MODBUS TCP/IP 通信機能の場合□ マスタから送信先として指定しているステーション No.と，接続されている本機のステーション No.
設定は一致していますか？
□

本機のステーション No.設定が 0 以外になっていますか？
0 の場合は通信機能は働きません。

－78－

本

社

大阪営業所

〒562-0035
大阪府箕面市船場東２丁目５番１号
TEL:(072)727-4571
FAX:(072)727-2993
URL:http://www.shinko-technos.co.jp〒562-0035
大阪府箕面市船場東２丁目５番１号
TEL:(072)727-3991
FAX:(072)727-2991
E-mail:sales@shinko-technos.co.jp

神奈川

TEL:(045)361-8270／FAX:(045)361-8271

静岡TEL:(054)282-4088／FAX:(054)282-4089

北陸TEL:(076)479-2410／FAX:(076)479-2411

京滋

TEL:(077)543-2882／FAX:(077)543-2882

兵庫

TEL:(079)439-1863／FAX:(079)439-1863

東京営業所〒332-0006
埼玉県川口市末広１丁目１３番１７号
TEL:(048)223-7121
FAX:(048)223-7120

広島

TEL:(082)231-7060／FAX:(082)234-4334

徳島

TEL:(0883)24-3570／FAX:(0883)24-3217

名古屋営業所〒460-0013
名古屋市中区上前津１丁目７番２号
TEL:(052)331-1106
FAX:(052)331-1109

福岡TEL:(0942)77-0403／FAX:(0942)77-3446