SPEC SHEETSHSDC Signal Transmitter (1-output)
Features:

SHS (1-input 1-output) converts DC voltage/current into isolated DC
voltage/current.

Functions: (Can be changed via the Setting Software) Sensor correction (Input value correction)
 Normal/Reverse mode
 Filter time constant Input and output types

Model: SHS - ① ② - 0 - ④

Model name
Input 1Output 1
Power supply
OptionPower Supply

DC voltage

DC current① INPUT 1A0A1A2A3A4A5A6A7A8A9V0V1V2V3V4V5V6V7V8V94 to 20mA (Built-in 50Ω shunt resistor)
4 to 20mA (250Ω shunt resistor)
4 to 20mA (50Ω shunt resistor)
0 to 20mA (250Ω shunt resistor)
0 to 16mA (62.5Ω shunt resistor)
2 to 10mA (250Ω shunt resistor)
0 to 10mA (100Ω shunt resistor)
1 to 5mA (100Ω shunt resistor)
0 to 1mA (1000Ω shunt resistor)
10 to 50mA (10Ω shunt resistor)
0 to 10mV (Input resistance 1MΩ)
0 to 50mV (Input resistance 1MΩ)
0 to 60mV (Input resistance 1MΩ)
0 to 100mV (Input resistance 1MΩ)
0 to 1V (Input resistance 1MΩ)
0 to 5V (Input resistance 1MΩ)
1 to 5V (Input resistance 1MΩ)
-5 to 5V (Input resistance 1MΩ)
0 to 10V (Input resistance 1MΩ)
-10 to 10V (Input resistance 1MΩ)0100 to 240V AC 50/60Hz④ Option
0No option needed

1

Multi-rotation trimmer

2

Moisture-proof treatment

3

Multi-rotation trimmer + Moisture-proof treatment

DC Voltage

DC Current② OUTPUT 1
12
3
45A
BCD
EFG

4 to 20mA (allowable load resistance 750Ω max.)
0 to 20mA (allowable load resistance 750Ω max.)※10 to 16mA (allowable load resistance 900Ω max.)※1
2 to 10mA (allowable load resistance 1500Ω max.)
0 to 10mA (allowable load resistance 1500Ω max.)※1
0 to 10mV (allowable load resistance 10kΩ min.)※2
0 to 100mV (allowable load resistance 100kΩ min.)※2
0 to 1V (allowable load resistance 1000Ω min.)※2
0 to 5V (allowable load resistance 5000Ω min.)※2
1 to 5V (allowable load resistance 5000Ω min.)0 to 10V (allowable load resistance 10kΩ min.)※2-5 to 5V (allowable load resistance 10kΩ min.)※1: 0mA or less: Out of base accuracy.
※2: 0V or less: Out of base accuracy.

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

SPEC SHEET
Performance

Base accuracy (at 25℃)
Temperature coefficient
Response time
Insulation resistanceDielectric strength

General Specifications
Input
Zero adjustment range
Power supply
Power consumption
Operating temperature, humidity
Storage temperature
Material
Mounting method
External dimensions
Weight±0.1% of each input span
± 0.015 %/℃ (0 to 10mV output: ±0.02%/℃)
0.5 sec. max. (0→90%)
100 MΩ minimum, at 500V DC
2.0kV AC for 1 minute4 to 20mA, 0 to 20mA, 0 to 16mA, 2 to 10mA, 0 to 10mA, 1 to 5mA, 0 to 1mA,
10 to 50mA DC
0 to 10mV, 0 to 50mV, 0 to 60mV, 0 to 100mV, 0 to 1V, 0 to 5V, 1 to 5V, -5 to 5V,
DC voltage
0 to 10V, -10 to 10V DC
Span adjustment range
95 to 105% (Adjustable from front panel.)-5 to 5% (Adjustable from front panel.)
100 to 240V AC 50/60Hz
Allowable voltage range
85 to 264V ACApprox. 9 VA max.
-10 to 55℃ (Non-condensing, No icing), 35 to 85%RH (Non-condensing)-10 to 60℃
Case: Flame-resistant resin, Black color, Panel: Polycarbonate
DIN rail22.5(W) x 89(H) x 70(D)mm (without socket)
Approx. 76 g (without socket)
DC current

Terminal Arrangement

Circuit Configuration

Power supply voltage
100 to 240V ACOutput
DC current input
DC voltage input

PWR ⑬ - ⑭
OUT ⑨ - ⑫
A ①-④
V ①-④(8P Socket)

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp