SPEC SHEET

SGL

Linearizer (1-output)
Features:

SGL (1-input 1-output) converts DC voltage/current signal into isolated
DC voltage/current signal by connecting up to 25 points of input andoutput linearly. Indication displays are equipped.

Functions:Linearization up to 25 points,
Sensor correction (Input value correction)
Normal/Reverse modeFilter time constantManual mode
Input and output types can be changed.

Model: SGL - ① ② - ③ - ④

Model nameInput 1Output 1
Power supply
Option③ Power supply

DC voltage

DC current① INPUT 1A0A1A2A3A4A5A6A7A8A9V0V1V2V3V4V5V6V7V8V9

4 to 20mA (Built-in 50Ω shunt resistor)
4 to 20mA (250Ω shunt resistor)
4 to 20mA (50Ω shunt resistor)
0 to 20mA (250Ω shunt resistor)
0 to 16mA (62.5Ω shunt resistor)
2 to 10mA (250Ω shunt resistor)
0 to 10mA (100Ω shunt resistor)
1 to 5mA (100Ω shunt resistor)
0 to 1mA (1000Ω shunt resistor)
10 to 50mA (10Ω shunt resistor)
0 to 10mV (Input resistance 1MΩ)
0 to 50mV (Input resistance 1MΩ)
0 to 60mV (Input resistance 1MΩ)
0 to 100mV (Input resistance 1MΩ)
0 to 1V (Input resistance 1MΩ)
0 to 5V (Input resistance 1MΩ)
1 to 5V (Input resistance 1MΩ)
-5 to 5V (Input resistance 1MΩ)
0 to 10V (Input resistance 1MΩ)
-10 to 10V (Input resistance 1MΩ)0
1

100 to 240V AC 50/60Hz
24V AC/DC 50/60Hz
For SGLL (with serial communication function),
only [0: 100 to 240V AC] is selectable.

④ Option
0No option needed

1

Multi-rotation trimmer

2

Moisture-proof treatment

3

Multi-rotation trimmer + Moisture-proof treatment

DC Voltage

DC Current② OUTPUT 1
12345ABCDEFG

4 to 20mA (allowable load resistance 750Ω max.)
0 to 20mA (allowable load resistance 750Ω max.)※1
0 to 16mA (allowable load resistance 900Ω max.)※1
2 to 10mA (allowable load resistance 1500Ω max.)
0 to 10mA (allowable load resistance 1500Ω max.)※1
0 to 10mV (allowable load resistance 10kΩ min.)※2
0 to 100mV (allowable load resistance 100kΩ min.)※2
0 to 1V (allowable load resistance 1000Ω min.)※20 to 5V (allowable load resistance 5000Ω min.)※2
1 to 5V (allowable load resistance 5000Ω min.)0 to 10V (allowable load resistance 10kΩ min.)※2-5 to 5V (allowable load resistance 10kΩ min.)※1: 0mA or less: Out of base accuracy.
※2: 0V or less: Out of base accuracy.

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

SPEC SHEET
Performance

Base accuracy (at 25℃)
Display accuracy
Temperature coefficient
Response time
Insulation resistanceDielectric strength

General specifications
Input
Zero adjustment range
Power supply
Power consumption
Operating temperature, humidity
Storage temperature
Material
Mounting method
External dimensions
Weight±0.1% of each input span
Base accuracy ±1 digit±0.015%/℃ (0 to 10mV output:±0.02%/℃)
0.5 sec. max. (0→90%)
100MΩ minimum, at 500V DC
2.0kV AC for 1 minute4 to 20mA, 0 to 20mA, 0 to 16mA, 2 to 10mA, 0 to 10mA, 1 to 5mA, 0 to 1mA,
10 to 50mA DC
0 to 10mV, 0 to 50mV, 0 to 60mV, 0 to 100mV, 0 to 1V, 0 to 5V, 1 to 5V, -5 to 5V,DC voltage
0 to 10V, -10 to 10V DC-5 to 5% (Adjustable from front panel.)
Span adjustment range
95 to 105% (Adjustable from front panel.)
100 to 240V AC 50/60Hz
85 to 264V AC
Allowable voltage range
24V AC/DC 50/60Hz
20 to 28V AC/DC
100 to 240 V AC: Approx. 9 VA max. (SGLL: Approx. 10 VA max.)
24 V AC: Approx. 6 VA max.
24 V DC: Approx. 3 W max.
-10 to 55℃ (Non-condensing, No icing), 35 to 85%RH (Non-condensing)-10 to 60℃
Case: Flame-resistant resin, Black color, Panel: Polycarbonate
DIN rail22.5(W) x 89(H) x 70(D)mm (without socket)
Approx. 77g (without socket)
DC current

Measurement range

Terminal arrangement

Input code
Measurement range
Resolution
A01A11A21A3
1
A41A51
A61
A71A81
A91-1999 to 9999 ※V0
1
V1
1
V2
1
V3
1
V4
1
V5
1
V6
1
V7
1
V8
1
V91
※ Decimal point position change and scaling are possible.

OUT ⑨ - ⑫
A ①-④
V ①-④
RS-485

Power supply voltage

100 to 240V AC, 24V AC/DCOutput
DC current input
DC voltage input
Serial communication RS-485(For SGLL)(8P Socket)

Circuit configuration

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/

PWR ⑬ - ⑭

E-mail: overseas@shinko-technos.co.jp

20190507