PROGRAMMABLE CONTROLLER

PCA1INSTRUCTION MANUALPreface
Thank you for purchasing our programmable controller PCA1. This manual contains instructions for themounting, functions, operations and notes when operating the PCA1. To prevent accidents arising from themisuse of this controller, please ensure the operator receives this manual
Abbreviations used in this manual
Abbreviation
PV
SV
MV
OUT1
OUT2
AT

Term
Process variable
Desired value
Manipulated variable
Control output OUT1
Control output OUT2
Auto-tuning

Characters used in this manual ( : No character is indicated)
Indication
Number, /

-1

0

1

2

3

4

5

6

7

8

9

B

C

D

E

F

G

H

I

J

K

L

P

Q

R

S

T

U

V

W

X

Y

Z

IndicationA

Alphabet

M

Indication
Alphabet

N

O

Notes

• This instrument should be used in accordance with the specifications described in the manual.
If it is not used according to the specifications, it may malfunction or cause a fire.
• Be sure to follow the warnings, cautions and notices. If they are not observed, serious injury or malfunction
may occur.
• The contents of this instruction manual are subject to change without notice.
• Care has been taken to ensure that the contents of this instruction manual are correct, but if there are any
doubts, mistakes or questions, please inform our sales department.
• This instrument is designed to be installed through the control panel. If it is not, measures must be taken to
ensure that the operator cannot touch power terminals or other high voltage sections.
• Any unauthorized transfer or copying of this document, in part or in whole, is prohibited.
• Shinko Technos Co., Ltd. is not liable for any damage or secondary damage(s) incurred as a result of using
this product, including any indirect damage.

- 2 -Safety Precautions (Be sure to read these precautions before using our products.)

The safety precautions are classified into categories: “Warning” and “Caution”. Depending on circumstances,
procedures indicated by
Caution may result in serious consequences, so be sure to follow the directions
for usage.
which may lead to dangerous conditions and cause death or serious
Warning Procedures
injury, if not carried out properly.

CautionProcedures which may lead to dangerous conditions and cause superficial tomedium injury or physical damage or may degrade or damage the product, if not
carried out properly.

Warning• To prevent an electrical shock or fire, only Shinko or other qualified service personnel may handle theinner assembly.
• To prevent an electrical shock, fire or damage to the instrument, parts replacement may only beundertaken by Shinko or other qualified service personnel.

Safety Precautions• To ensure safe and correct use, thoroughly read and understand this manual before using this instrument.
• This instrument is intended to be used for industrial machinery, machine tools and measuring equipment. Verify
correct usage after purpose-of-use consultation with our agency or main office. (Never use this instrument for
medical purposes with which human lives are involved.)• External protection devices such as protective equipment against excessive temperature rise, etc. must be
installed, as malfunction of this product could result in serious damage to the system or injury to personnel.
Proper periodic maintenance is also required.
• This instrument must be used under the conditions and environment described in this manual. Shinko TechnosCo., Ltd. does not accept liability for any injury, loss of life or damage occurring due to the instrument being used
under conditions not otherwise stated in this manual.

Caution with Respect to Export Trade Control Ordinance
To avoid this instrument from being used as a component in, or as being utilized in the manufacture of
weapons of mass destruction (i.e. military applications, military equipment, etc.), please investigate theend users and the final use of this instrument. In the case of resale, ensure that this instrument is notillegally exported.

1. Installation Precautions
CautionThis instrument is intended to be used under the following environmental conditions(IEC61010-1): Overvoltage category , Pollution degree 2
Ensure the mounting location corresponds to the following conditions:• A minimum of dust, and an absence of corrosive gases• No flammable, explosive gases• No mechanical vibrations or shocks• No exposure to direct sunlight, an ambient temperature of 0 to 50 (32 to 122 ) that does not change
rapidly, and no icing• An ambient non-condensing humidity of 35 to 85 %RH• No large capacity electromagnetic switches or cables through which large current is flowing.
• No water, oil, chemicals or the vapors of these substances can come into direct contact with the unit.
• Please note that the ambient temperature of this unit – not the ambient temperature of the control panel– must not exceed 50 (122 ) if mounted through the face of a control panel, otherwise the life of theelectronic components (especially electrolytic capacitors) may be shortened.

Note: Avoid setting this instrument directly on or near flammable material even though the caseof this instrument is made of flame-resistant resin.
- 3 -2. Wiring Precautions
Caution• Do not leave wire remnants in the instrument, as they could cause a fire or malfunction.
• Use the solderless terminal with an insulation sleeve in which the M3 screw fits when wiring the
instrument.
• The terminal block of this instrument is designed to be wired from the left side. The lead wire must be
inserted from the left side of the terminal, and fastened with the terminal screw.
• Tighten the terminal screw using the specified torque. If excessive force is applied to the screw whentightening, the terminal screw or case may be damaged.
• Do not pull or bend the lead wire on the terminal side when wiring or after wiring, as it could cause
malfunction.
• This instrument does not have a built-in power switch, circuit breaker and fuse. It is necessary to installa power switch, circuit breaker and fuse near the controller.
(Recommended fuse: Time-lag fuse, rated voltage 250 V AC, rated current 2 A)
• For the grounding wire, use a thick wire (1.25 - 2.0 mm2).
• For a 24 V AC/DC power source, do not confuse polarity when using direct current (DC).
• Do not apply a commercial power source to the sensor which is connected to the input terminal nor
allow the power source to come into contact with the sensor.
• Use a thermocouple and compensating lead wire according to the sensor input specifications of thiscontroller.
• Use the 3-wire RTD according to the sensor input specifications of this controller.
• For DC voltage input, (+) side input terminal number of 0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC differsfrom that of 0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC, 0 to 1 V DC.
Terminal Number⑯ and ⑲⑱ and ⑲

DC Voltage Input
0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC
0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC,
0 to 100 mV DC, 0 to 1 V DC

• When using a relay contact output type, externally use a relay according to the capacity of the load toprotect the built-in relay contact.
• When wiring, keep input wires (thermocouple, RTD, etc.) away from AC power sources or load wires.

3. Operation and Maintenance Precautions
Caution• It is recommended that AT be performed on the trial run.
• When connecting USB communication cable (CMB-001) to the console connector, connect the cable
after power is turned OFF.
• Never turn the power ON or OFF, while USB communication cable (CMB-001) is connected to theconsole connector.
• Do not touch live terminals. This may cause electrical shock or problems in operation.
• Turn the power supply to the instrument OFF before retightening the terminal or cleaning.
Working on or touching the terminal with the power switched ON may result in severe injury or death
due to electrical shock.
• Use a soft, dry cloth when cleaning the instrument.
(Alcohol based substances may tarnish or deface the unit.)• As the display section is vulnerable, be careful not to put pressure on, scratch or strike it with a hard
object.
- 4 -Contents

1. Model ...................................................................................................................................................
7
1.1 Model.............................................................................................................................................
7
1.2 How to Read the Model Label .......................................................................................................
8
2. Name and Functions of Controller....................................................................................................
9
3. Mounting to the Control Panel ......................................................................................................... 12
3.1 External Dimensions (Scale: mm) ................................................................................................ 12
3.2 Panel Cutout (Scale: mm) ............................................................................................................. 12
3.3 Mounting to, and Removal from, the Control Panel ....................................................................... 13
3.3.1 Mounting the Unit .................................................................................................................. 13
3.3.2 Removing the Unit ................................................................................................................. 13
4. Wiring ................................................................................................................................................ 14
4.1 Terminal Arrangement ................................................................................................................... 15
4.2 Lead Wire Solderless Terminal ...................................................................................................... 16
4.3 Wiring ............................................................................................................................................ 16
4.3.1 Grounding .............................................................................................................................. 16
4.3.2 Power Supply ........................................................................................................................ 16
4.3.3 Control Output OUT1 and OUT2 ........................................................................................... 16
4.3.4 Input....................................................................................................................................... 17
4.3.5 Event Output EV1, EV2, EV3 and EV4 .................................................................................. 18
4.3.6 Event Input ............................................................................................................................ 18
4.3.7 External Operation Input ........................................................................................................ 19
4.3.8 Serial Communication............................................................................................................ 20
4.3.9 Transmission Output .............................................................................................................. 22
4.3.10 Time Signal Output .............................................................................................................. 23
5. Outline of Key Operation and Explanation of Groups .................................................................... 24
5.1 Outline of Key Operation ............................................................................................................... 24
5.1.1 Block Setting Group ............................................................................................................... 26
5.1.2 Engineering Setting Group .................................................................................................... 27
5.2 Explanation of Groups ................................................................................................................... 28
6. Basic Operating Procedure after Power ON and Setting Examples .............................................. 30
6.1 Basic Operating Procedure after Power ON .................................................................................. 30
6.2 Initial Setting, Program Pattern Setting and Block Setting ............................................................. 31
7. Setting Items ....................................................................................................................................... 43
7.1 Pattern Setting Group .................................................................................................................... 43
7.2 Block Setting Group....................................................................................................................... 47
7.2.1 PID Block Setting Group ........................................................................................................ 48
7.2.2 Time Signal Block Setting Group ........................................................................................... 50
7.2.3 Wait Block Setting Group ....................................................................................................... 52
7.2.4 Alarm Block Setting Group..................................................................................................... 54
7.2.5 Output Block Setting Group ................................................................................................... 58
7.3 Repetitions and Pattern Link Setting Group .................................................................................. 60
7.4 AT Perform Group .......................................................................................................................... 62
7.5 Engineering Setting Group ............................................................................................................ 64
7.5.1 Input Parameter Setting Group .............................................................................................. 66
7.5.2 Output Parameter Setting Group ........................................................................................... 69
7.5.3 Event Output Parameter Setting Group ................................................................................. 72
7.5.4 SV Limit Setting Group .......................................................................................................... 83
7.5.5 Transmission Output Parameter Setting Group ..................................................................... 84
7.5.6 Communication Parameter Setting Group ............................................................................. 85
7.5.7 Other Parameters Setting Group ........................................................................................... 87
7.6 Auto/Manual Control Switch Group ............................................................................................... 94
7.7 Clearing the Setting Data .............................................................................................................. 95
8. Operation ............................................................................................................................................ 96
8.1 Performing Program Control .......................................................................................................... 96
8.1.1 Performing Program Control .................................................................................................. 96
8.1.2 Stopping Program Control ..................................................................................................... 101- 5 -8.1.3 Suspending Program Control (Hold Function) ....................................................................... 102
8.1.4 Advancing Program Step (Advance Function) ...................................................................... 103
8.1.5 Returning to Previous Program Step (Return-to-Previous Function) ..................................... 104
8.1.6 Speeding up Program Step Time (Step Time Speed-up Function) ........................................ 105
8.1.7 Changing Program Step SV and Step Time .......................................................................... 106
8.1.8 Ending Program (Pattern End Function) ................................................................................ 107
8.2 Performing Fixed Value Control ..................................................................................................... 108
8.2.1 Performing Fixed Value Control ............................................................................................. 108
8.2.2 Finishing Fixed Value Control ................................................................................................ 110
8.3 Switching Auto/Manual Control ...................................................................................................... 111
8.3.1 Switching to Manual Control .................................................................................................. 112
8.3.2 Switching to Automatic Control .............................................................................................. 113
8.4 Switching the SV/MV/TIME Display ............................................................................................... 114
8.5 Performing AT ................................................................................................................................ 115
8.5.1 Notice when Performing AT ................................................................................................... 115
8.5.2 AT Action ................................................................................................................................ 117
8.5.3 Performing AT ........................................................................................................................ 118
9. Action Explanation ............................................................................................................................. 119
9.1 OUT1 Action .................................................................................................................................. 119
9.2 OUT1 ON/OFF Control Action ....................................................................................................... 120
9.3 OUT2 (Heating/Cooling Control) Action ......................................................................................... 121
9.4 OUT2 (Heating/Cooling Control) Action (When Setting Dead Band) ........................................... 122
9.5 OUT2 (Heating/Cooling Control) Action (When Setting Overlap Band) ....................................... 123
9.6 Alarm Action .................................................................................................................................. 124
9.7 Pattern End Output ........................................................................................................................ 126
10. Specifications ................................................................................................................................... 127
10.1 Standard Specifications ............................................................................................................... 127
10.2 Optional Specifications ................................................................................................................ 139
11. Troubleshooting ............................................................................................................................... 141
11.1 Indication ..................................................................................................................................... 141
11.2 Key Operation .............................................................................................................................. 143
11.3 Control ......................................................................................................................................... 144
12. Character Table ................................................................................................................................ 145
12.1 Group Selection ........................................................................................................................... 145
12.2 Pattern Setting Group .................................................................................................................. 146
12.3 Block Setting Group..................................................................................................................... 148
12.4 PID Block Setting Group.............................................................................................................. 149
12.5 Time Signal Block Setting Group ................................................................................................. 150
12.6 Wait Block Setting Group ............................................................................................................ 151
12.7 Alarlm Block Setting Group ......................................................................................................... 152
12.8 Output Block Setting Group ......................................................................................................... 154
12.9 Repetitions and Pattern Link Setting Group ................................................................................ 155
12.10 AT Perform Group ..................................................................................................................... 156
12.11 Engineering Setting Group ........................................................................................................ 157
12.12 Input Parameter Setting Group .................................................................................................. 158
12.13 Output Parameter Setting Group ............................................................................................... 160
12.14 Event Output Parameter Setting Group ..................................................................................... 161
12.15 SV Limit Setting Group .............................................................................................................. 166
12.16 Transmission Output Parameter Setting Group ......................................................................... 167
12.17 Communication Parameter Setting Group ................................................................................. 168
12.18 Other Parameters Setting Group ............................................................................................... 169
12.19 Auto/Manual Control Switch Group............................................................................................ 172
13. Making Program Pattern Table and Data Table .............................................................................. 173
13.1 Making Program Pattern Table .................................................................................................... 173
13.2 Making Data Table ....................................................................................................................... 175
PCA1 Key Operation Flowchart ............................................................................................................ 179- 6 -1. Model
1.1 Model
PCA1
Control output
OUT1

0R

Relay contact output

S

Non-contact voltage output

A

Direct current output

Power supply

0

100 to 240 V AC

voltage1

24 V AC/DC

Input

0

Multi-range (*1)
0

Option 1 (*2)

Option 1 not needed.

1

C

Serial communication RS-232C

2

C5

Serial communication RS-485

3

TS

Time signal output

4

C+TS

Serial communication RS-232C+Time signal output

5

C5+TS

Serial communication RS-485+Time signal output

0
Option 2 (*2)

Option 2 not needed.

1

TA

Transmission output (4 to 20 mA DC)

2TVTransmission output (0 to 1 V DC)

0

Option 3 (*2)

Option 3 not needed.

1

DR (*3)2

DS (*3)3

DA (*3)

Heating/Cooling control output OUT2
Relay contact output
Heating/Cooling control output OUT2
Non-contact voltage output
Heating/Cooling control output OUT2
Direct current output

Factory default values of Event output are shown below.
EV1 : Pattern end output
EV2 : No event
EV3 : Alarm output, High limit alarm
EV4 : Alarm output, Low limit alarm(*1) Thermocouple, RTD, Direct current or DC voltage can be selected by keypad.
(*2) Only one option can be selected from Option 1, Option 2 and Option 3 respectively.
(*3) If Heating/Cooling control (DR, DS or DA option) is ordered, Event output EV2 will be disabled.

- 7 -1.2 How to Read the Model Label
The model label is attached to the left side of the case.

①

②
③
④
⑤
⑧
⑥
⑨

⑦

⑩
(Fig. 1.2-1)
No.
①
②
③

Description
Terminal arrangement
Model
Option④⑤

Input
Control output,
Event output⑥

Power supply,Power consumption
Serial number
RoHS directive
UL recognized factory ID
Manufacturer

⑦
⑧
⑨
⑩

ExampleTerminal arrangement of PCA1R00-410 (*)
PCA1R00-410
C+TS (Serial communication RS-232C+Time signal
output)TA [Transmission output (4-20 mA DC)]
MULTI-RANGE (Multi-range input)
O1: 3 A 250 V AC (Control output OUT1)
EV1: 3 A 250 V AC (Event output EV1)
EV2: 3 A 250 V AC (Event output EV2)
EV3: 3 A 250 V AC (Event output EV3)
EV4: 3 A 250 V AC (Event output EV4)
100 to 240 V AC 50/60 Hz,
14 VA
No. 165F05000
RoHS directive compliant
SF: Fukuoka factory
SHINKO TECHNOS CO., LTD.

(*) Terminal arrangement diagram differs depending on the model.

- 8 -2. Name and Functions of Controller
①

②

③
⑤

④

⑥
⑦

⑩

⑧

⑪

⑨
⑫

⑯

⑬

⑰

⑭

⑱

⑮

⑲

⑳

(Fig. 2-1)

- 9 -

Action Indicators, Display
No.
Name
①
PV indicator②

PV Display③

SV indicator

MV indicator

TIME indicator④

SV/MV/TIME
Display⑤

PTN indicator⑥

PTN Display⑦

PROFILE indicator⑧

STEP indicator⑨

STEP Display⑩

Time unit indicator

Description
Backlight: Red/Green/Orange
Lit when PV is indicated in RUN mode.
Backlight: Red/Green/Orange
Indicates PV in RUN mode.
Indicates setting characters in setting mode.
Backlight: Green
Lit when SV is indicated on the SV/MV/TIME Display.
Retains indicator status at power OFF.
Backlight: Green
Lit when OUT1 MV is indicated on the SV/MV/TIME Display.
Flashes when OUT2 MV is indicated on the SV/MV/TIME Display.
Retains indicator status at power OFF.
Backlight: Green
Lit when TIME is indicated on the SV/MV/TIME Display.
Retains indicator status at power OFF.
Backlight: Green
Indicates SV, MV or TIME in RUN mode.
Retains display indication at power OFF.
Indicates the set values in setting mode.
Backlight: Orange
Lit when the pattern number is indicated.
Backlight: Orange
Indicates the pattern number.
If ‘Holding’ is selected in [Step SV Hold function when program ends],
flashes when program control ends.
Backlight: Green
When program control is performing, the indicator lights up depending on
the program setting as follows.
: Lit when step SV is rising.
: Lit when step SV is constant.
: Lit when step SV is falling.
Backlight: Orange
Lit when the step number is indicated.
Backlight: Orange
Indicates the step number.
The step number flashes during Wait action.
Indicates
during Manual control.
Backlight: Green
When the SV/MV/TIME Display indicates TIME, the following is shown
depending on the selection in [Step time unit].
M: Lit when ‘Hours:Minutes’ is selected in [Step time unit].
S: Lit when ‘Minutes:Seconds’ is selected in [Step time unit].

- 10 -

Action Indicator (Backlight: Orange)No.
Name
Description
Lit
when
control
outputOUT1
is ON.
⑪
OUT1
For direct current output type, flashes corresponding to the MV
in 125 ms cycles.
Lit when control output OUT2 (DR, DS or DA option) is ON.
OUT2
For direct current output type (DA option), flashes corresponding to the
MV in 125 ms cycles.
Lit when Event output EV1 is ON.
EVT1
Lit when Event output EV2 is ON.
EVT2
Lit when Event output EV3 is ON.
EVT3
Lit when Event output EV4 is ON.
EVT4
Lit when Manual control is performing.
MAN
Lit during Serial communication (C or C5 option) TX (transmitting) output.
T/R
Flashes during AT (Auto-tuning).
AT
Lit in AT standby when ‘Multi mode’ is selected in [AT mode].
LOCK
Lit when ‘Lock’ is selected in [Set value lock].
Lit during program control RUN.
RUN
Flashes during Fixed value control.
Flashes during program control HOLD.
HOLD
Key

No.
⑫

Name
RUN key⑬

PATTERN/UP key⑭

SET/RESET key⑮

STOP/MODE key⑯

ADVANCE/DOWN
key⑰

FAST key⑱

HOLD/ENTER
key⑲

DISPLAY/BACK MODE key

Console Connector
No.
Name
⑳
Consoleconnector

Description
Performs program control.
Cancels HOLD during Program control HOLD.
PATTERN key: Selects program pattern number.
UP key: Increases the numerical value in setting mode.
SET key: Moves to setting mode.
RESET key: Moves to RUN mode.
STOP key: Stops the program control, or cancels the pattern end output.
MODE key: Switches or selects setting mode.
ADVANCE key: During program control, interrupts performing step, andproceeds to the next step (ADVANCE function).
DOWN key: Decreases the numerical value in setting mode.
During program control, the step time progress is made 60 times faster.
In setting mode, the numerical value change is made faster.
HOLD key: During program control, time progress pauses, and control
continues with the SV at the given time (HOLD function).
ENTER key: Registers the setting data, and moves to the next setting
item.
DISPLAY key: Switches the indication on the SV/MV/TIME Display.
BACK MODE key: Moves back to the previous mode.

Description
By connecting the USB communication cable (CMB-001, sold separately),
the following operations can be conducted from an external computer,using the Console software SWC-PCA101M.
• Reading and setting of step SV, step time, PID and various set values• Reading of PV and action status• Function change- 11 -

3. Mounting to the Control Panel
3.1 External Dimensions (Scale: mm)
Terminal cover(sold separately)□91

Screw type mounting bracket

11.5

□96

98.5
104.5 (when terminal cover is used)(Fig. 3.1-1)
3.2 Panel Cutout (Scale: mm)

Caution130

92＋0.80

If horizontal close mounting is used for the controller, IP66 specification (Drip-proof/Dust-proof)
may be compromised, and all warranties will be invalidated.

n×96-3 ＋0.5
0Horizontal close mounting
n: Number of mounted units□92＋0.8
0(Fig. 3.2-1)- 12 -

106.2

Gasket3.3 Mounting to, and Removal from, the Control Panel

CautionAs the case of the PCA1 is made of resin, do not use excessive force while tightening
screws, or the mounting brackets or case could be damaged.
The torque should be 0.12 N•m.
3.3.1 Mounting the Unit
Mount the controller vertically to the flat, rigid panel to ensure it adheres to the Drip-proof/Dustproof specification (IP66).
CAUTION:
If the horizontal close mounting is used for the controller, IP66 specification (Drip-proof/Dust-proof)
may be compromised, and all warranties will be invalidated.
Mountable panel thickness: 1 to 8 mm(1) Insert the controller from the front side of the control panel. (Fig. 3.3.1-1)(2) Attach the mounting brackets by the slots at the top and bottom of the case, and secure thecontroller in place with the screws.
The torque should be 0.12 N•m.

Up

Down

(Fig. 3.3.1-1)
3.3.2 Removing the Unit
(1) Turn the power to the unit OFF, and disconnect all wires before removing the unit.
(2) Loosen the screws of the mounting brackets, and remove the mounting brackets.
(3) Pull the unit out from the front of the control panel.

- 13 -

4. Wiring
Warning
Turn the power supply to the instrument off before wiring or checking.
Working on or touching the terminal with the power switched on may result in severe injury
or death due to electrical shock.

Caution• Do not leave wire remnants in the instrument, as they could cause a fire or malfunction.
• Use the solderless terminal with an insulation sleeve in which the M3 screw fits when wiring the
instrument.
• The terminal block of this instrument is designed to be wired from the left side. The lead wire must be
inserted from the left side of the terminal, and fastened with the terminal screw.
• Tighten the terminal screw using the specified torque. If excessive force is applied to the screw whentightening, the terminal screw or case may be damaged.
• Do not pull or bend the lead wire on the terminal side when wiring or after wiring, as it could cause
malfunction.
• This instrument does not have a built-in power switch, circuit breaker and fuse. It is necessary to installa power switch, circuit breaker and fuse near the controller.
(Recommended fuse: Time-lag fuse, rated voltage 250 V AC, rated current 2 A)
• For the grounding wire, use a thick wire (1.25 – 2.0 mm2).
• For a 24 V AC/DC power source, ensure polarity is correct when using direct current (DC).
• Do not apply a commercial power source to the sensor which is connected to the input terminal nor
allow the power source to come into contact with the sensor.
• Use a thermocouple and compensating lead wire according to the sensor input specifications of thiscontroller.
• Use the 3-wire RTD according to the sensor input specifications of this controller.
• For DC voltage input, (+) side input terminal number of 0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC differsfrom that of 0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC and 0 to 1 V DC.
Terminal Number⑯ and ⑲⑱ and ⑲

DC Voltage Input
0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC
0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC,
0 to 1 V DC

• When using a relay contact output type, externally use a relay according to the capacity of the load toprotect the built-in relay contact.
• When wiring, keep input wires (thermocouple, RTD, etc.) away from AC power sources or load wires.

- 14 -

4.1 Terminal Arrangement(Fig. 4.1-1)
Terminal Code
GND
PWR

O1
O2
EV1
EV2
EV3
EV4
EVENT INPUT
RS-485/RS-232C
TC
RTD
DC 1V≧DC 5V≦DC mA
TRANSMIT OUTPUTEXT OPERATION
T.SIGNAL OUTPUT

Description
GroundingPower supply 100 to 240 V AC or 24 V AC/DC
For a 24 V AC/DC power source, ensure polarity is correct when using direct
current (DC).
Control output OUT1
Control output OUT2 (DR, DS or DA option)
Event output EV1
Event output EV2
Event output EV3
Event output EV4
Event input
Serial communication RS-485 (C5 option) or RS-232C (C option)
Thermocouple input
RTD input
DC voltage input: 0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC,
0 to 100 mV DC, 0 to 1 V DC
DC voltage input: 0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC
Direct current input: 0 to 20 mA DC, 4 to 20 mA DC
Transmission output (TA or TV option)
External operation input: STOP, HOLD, ADV, RUN
Time signal output (TS option)- 15 -

4.2 Lead Wire Solderless Terminal
Use a solderless terminal with an insulation sleeve in which an M3 screw fits as shown below.
The torque should be 0.63 N•m.
SolderlessTightening
Manufacturer
Model
Terminal
TorqueNichifu Terminal Industries Co., Ltd.
TMEV1.25Y-3
Y-typeJapan Solderless Terminal MFG Co., Ltd.
VD1.25-B3A
0.63 N•m
Nichifu Terminal Industries Co., Ltd.
TMEV1.25-3
Ring-type
Japan Solderless Terminal MFG Co., Ltd.
V1.25-3
3.2 mm

5.8 mm Max.

5.8 mm Max.

3.2 mm(Fig. 4.2-1)
4.3 Wiring
For the terminal arrangement, refer to Section “4.1 Terminal Arrangement” (p.15).
4.3.1 Grounding
For the grounding wire, use a thick wire (1.25 to 2.0 mm2).

4.3.2 Power Supply
Power supply voltage is 100 to 240 V AC or 24 V AC/DC.
For a 24 V AC/DC, ensure polarity is correct when using direct current (DC).
ACDC

4.3.3 Control Output OUT1 and OUT2When Heating/Cooling control (DR, DS, DA option) is ordered, control output OUT2 is available.
Specifications of Control output OUT1 and OUT2 are shown below.
Control Output OUT1
Relay contact

Non-contact voltage(for SSR drive)
Direct current

1a 1bControl capacity: 3 A 250 V AC (resistive load),
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
12 V DC 15%
Max. 40 mA (short circuit protected)
4 to 20 mA DC
Load resistance: Max. 600- 16 -

Control Output OUT2
Relay contact(DR option)

Non-contact voltage(for SSR drive)(DS option)
Direct current(DA option)
Relay contact

1aControl capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
12 V DC 15%
Max. 40 mA (short circuit protected))
4 to 20 mA DC
Load resistance: Max. 600

Non-contact voltage,
Direct current

Number of Shinko SSR units when connected in parallel (for Non-contact voltage output):• SA-400 series: 5 units• SA-500 series: 2 units
4.3.4 Input
Input wirings are shown below.
For DC voltage input, (+) side input terminal number of 0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC
differs from that of 0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC, 0 to 1 V DC.
DC voltage input DC voltage input
0 to 10 mV DC
0 to 5 V DC
Thermocouple
Direct current-10 to 10 mV DC
1 to 5 V DC
RTD input
input
input
0 to 50 mV DC
0 to 10 V DC
0 to 100 mV DC
0 to 1 V DC

- 17 -

4.3.5 Event Output EV1, EV2, EV3 and EV4Specifications of Event output EV1, EV2, EV3 and EV4 are shown below.
Relay contact

Event output EV1

1a
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
Event output EV2

Event output EV3
Event output EV4

Event output EV3 and EV4 share one common terminal.
4.3.6 Event Input
Up to 4 points of Event input are available.
If Serial communication (C, C5 option) is ordered, up to 2 points of Event input are available.
Specifications of Event input are shown below.
Circuit current when closed
Approx. 16 mA
4 points of Event input

2 points of Event input

Level action is used to determine ON or OFF.
When power is turned ON, level action is engaged.
4 points of Event input: Pattern numbers 1 to 15 can be switched by ON (Closed) or OFF (Open)status of DI1 to DI4.
2 points of Event input: Pattern numbers 1 to 3 can be switched by ON (Closed) or OFF (Open)status of DI1 and DI2.
Pattern numbers selected by Event input have priority over pattern numbers selected by keypad
operation.
To select pattern numbers by keypad, make sure all Event inputs are in OFF (Open) status.

- 18 -

• 4 points of Event input DI1 to DI4 [ : ON (Closed) status]
PTN Display

*

1

2

3

4

5

6

7

8

9

10

11

12

13

14

15

DI1
DI2
DI3
DI4
* This pattern number is selected via the keypad.
• 2 points of Event input DI1 and DI2 [ : ON (Closed) status]
PTN Display

*

1

2

3

DI1
DI2
* This pattern number is selected via the keypad.
4.3.7 External Operation Input
4 points of External operation input are available.
Specifications of External operation input are shown below.
Circuit current when closed

Approx. 16 mA

Signal edge action is used to determine ON or OFF.
Signal rising edge action from OFF (Open) to ON (Closed) of External operation input is engaged,
and program control RUN, STOP, HOLD and ADVANCE are performed.
When power is turned ON, level action is engaged.
External
Operation Input
STOP
HOLD
ADV
RUN

External Operation Input Function
Stops the program control.
During program control, current performing step progress pauses.
During program control, interrupts performing step, and proceeds to thebeginning of the next step.
Performs program control.

- 19 -

4.3.8 Serial Communication
When the C or C5 option is ordered, Serial communication is available.
C option

C5 option(1) Serial Communication[Wiring Example]
When using USB communication cable CMC-001-1 (sold separately)
USB communication cable
CMC-001-1 (sold separately)

PCA1⑬ YA(-)⑭ YB(+)
⑮ SG

YA(-)
YB(+)
COM

Host computer
USB port
Shield wireFG

⑬ YA(-)⑭ YB(+)⑮ SG

Shield wireFG

⑬ YA(-)⑭ YB(+)⑮ SG(Fig. 4.3.8-1)
When using RS-232C communication line
RS-232C
TXD

3

RXD

2

⑬ TX
⑭ RX
⑮ COM

GND 5
DCD

1

DTR

4

DSR

6

RTS

7

CTS

8

RI

9

PCA1

Shield wireFG

Host computer
D-sub 9-pin connector(Fig. 4.3.8-2)- 20 -

When using communication converter IF-400 (sold separately)
TXD

3

RXD

2

GND 5
DCD

1

DTR

4

DSR

6

RTS

7

CTS

8

RI

9

Communication converter IF-400 (sold separately)
RS-232C
RS-4854
3
1
6

Shieldwire

PCA1⑬ YA(-)⑭ YB(+)⑮ SG

Shield wire

FG

FG

Host computer
D-sub 9-pin connector⑬ YA(-)⑭ YB(+)⑮ SG

Shield wire

CDM

FG

⑬ YA(-)⑭ YB(+)⑮ SG(Fig. 4.3.8-3)(2) SV Digital Transmission
If ‘SV digital transmission’ is selected in [Communication protocol], step SV can be digitallytransmitted to the Shinko indicating controllers with the communication function (C5 option).
Update cycle: 250 ms
Connection
Connect YA (-) to YA (-), YB (+) to YB (+), SG to SG terminal (of PCA1 and indicating
controllers with the communication function) respectively.
A maximum of 31 units can be connected.
[Wiring Example]
PCA1 and indicating controllers with the communication function
PCA1
YA(-)
YB(+)
SG

YA(-) ⑬
YB(+) ⑭
SG ⑮
Shieldwire

FG

Shield wire

FG

YA(-)
YB(+)
SG

Shield wire

FG

(Fig. 4.3.8-4)- 21 -

YA(-)
YB(+)
SG

Indicating
controllers with
communication
function(Max.31 units)

Shield wire
Connect only one end of the shield to the FG to avoid a ground loop. If both ends of the shieldwire are connected to the FG, the circuit will be closed, resulting in a ground loop.
This may cause noise.
Be sure to ground the FG.
Recommended cable: OTSC-VB 2PX0.5SQ (made by Onamba Co., Ltd.) or equivalent (Use atwisted pair cable.)
4.3.9 Transmission Output
If the TA, TV option is ordered, Transmission output is available.
Specifications of Transmission output are shown below.
Resolution
TA option
OutputTV option

Output accuracy
Response time

12000
4 to 20 mA DC
Load resistance: Max. 500
0 to 1 V DC
Load resistance: Min. 100 k
Within 0.3% of Transmission output span
400 ms + Input sampling period (0%90%)

Converting the value (PV, SV or MV transmission) to analog signal every 125 ms, outputs
the value in current or voltage. (Factory default: PV transmission)
Outputs Transmission output low limit value if Transmission output high limit and low limit
value are the same.
If SV or MV transmission is selected, 4 mA or 0 V will be output when program control stops(in Standby).

- 22 -

4.3.10 Time Signal Output
If the TS option is ordered, Time signal output is available.
Specifications of Time signal output are shown below.
Number of circuits
Open collector

8
Capacity: 24 V DC
Max. 50 mA

For the Time signal output, a maximum of 8 points (Time signal output TS1 to TS8) can be selected
for each step.
Time signal outputs TS1 to TS5 can be used as Status output as follows.
Time signal output TS1
Status (RUN) output
Time signal output TS2
Status (HOLD) output
Time signal output TS3
Status (WAIT) output
Time signal output TS4
Status (FAST) output
Time signal output TS5
Status (STOP) output
When program control is performing, outputs Time signal output TS1 to TS8 in accordance with thesettings (Time signal output OFF time, Time signal output ON time) of selected time signal block.

- 23 -

5. Outline of Key Operation and Explanation of Groups
5.1 Outline of Key Operation

Power ON+

RUN mode
Program control
RUN(*)(1 sec)+(3 sec)Data clear

Program control
Stop (in Standby)

Group selection mode
Pattern settinggroup

Setting patternnumberSetting items in thegroup

Block setting group(See Section 5.1.1)

PID block settinggroup

Setting items in thegroup

Output block settinggroup

Setting items in thegroup

Repetitions and patternlink setting group

Setting items in thegroup

AT Perform group

Setting items in thegroup

Engineering setting
group (See 5.1.2)

Input parametersetting group

Setting items in thegroup

Other parameters
setting group

Setting items in thegroup

Auto/Manual control
switch group(*): Select a pattern number with theAuto/Manual control
switchkey, and perform program control with the- 24 -

key.

Explanation of Mode
Mode
RUN modeGroup selection mode

Description
The unit enters the RUN mode when power is turned ON.
Resumes from Program control Stop (in Standby) or Program control RUN,
depending on the status of power OFF.
Indication differs depending on the status below.
Program control Stop PV, SV and PTN indicators light up.
(in Standby)
The PV Display indicates PV.
The PTN Display indicates the pattern number.
Other indicators and Displays are unlit.
Program control RUN PV, SV, PTN, STEP, PROFILE, Time unit andAction indicators are lit.
The PV Display indicates PV.
The SV/MV/TIME Display indicates SV, MV or TIME.
The PTN Display indicates the pattern number.
The STEP Display indicates the step number.
Selects a group from the following:
Pattern setting group, Block setting group, Repetitions and Pattern linksetting group, AT perform group, Engineering setting group,
Auto/Manual control switch group

Key Operation
Key Operation，

Description
If any key is pressed, the unit moves to the next item, illustrated by an arrow.
Press thekey until the desired setting item appears.
Returns to RUN mode from any mode.
Moves back to the previous mode (opposite to when theorkey
is pressed).
When theandkey are pressed at the same time, the mode
returns to the previous setting group as follows.

++

Block setting
group

+

+
(3 sec)+Alarm block
setting group+

EV4 alarm
value

Return-to-Previous Function
Ifandkeys are pressed at the same time during program control
RUN, interrupts performing step, and the unit moves back to the previous
step, and performs control.
However, if the elapsed time of the current step is less than 1 minute, theprogram control goes back to the beginning of the previous step. If theelapsed time in the current step is longer than 1 minute, the program
control goes back to the beginning of the current step.
The Return-to-Previous Function is disabled at Step 0 of started pattern,but moves back to the beginning of Step 0.
Program clearing function
When program control is stopped (in Standby), and if the
key ispressed for approximately 3 seconds at any item in pattern setting group,
data (for current step on the STEP Display and all the following steps) will
return to the default value.
Data clearing function
When program control is stopped (in Standby), and if the,andkeys are pressed simultaneously for 3 seconds, the PV Display
indicates, and all program data – except Input type, OUT1
proportional cycle, OUT2 proportional cycle – will return to the factory
default. It takes approx. 30 seconds for data clear.
- 25 -

5.1.1 Block Setting Group

Block setting group

PID block settinggroup

Setting items in thegroup

Time signal block
setting group

Setting items in thegroup

Wait block settinggroup

Setting items in thegroup

Alarm block setting
group (*)

Setting items in thegroup

Output block settinggroup

Setting items in thegroup(*) Appears when an Alarm type is selected in [Event output EV: Appears only when the option is ordered.

- 26 -

allocation].

5.1.2 Engineering Setting GroupEngineering setting

group

Input parametersetting group

Setting items in thegroup

Output parametersetting group

Setting items in thegroup

Event output parameter setting group

Setting items in thegroup

SV limit settinggroup

Setting items in thegroup

Transmission output

Setting items in thegroup

Communication parameter setting group

Setting items in thegroup

Other parameters
setting group

Setting items in thegroup: Appears only when the option is ordered.

- 27 -

5.2 Explanation of Groups
Press thekey in RUN mode. The unit moves to Pattern setting group in Group selection mode.
Select a group with thekey, and press the
key. Setting items in the group can be set.
If thekey is pressed in the Block setting group, the unit enters setting groups such as PID block,
Alarm block.
Select a group with thekey, and press the
key. Setting items in the group can be set.
If thekey is pressed in the Engineering setting group, the unit enters setting groups such as Input
parameter, Output parameter.
Select a group with thekey, and press the
key. Setting items in the group can be set.
Group
Pattern setting group

Block setting group

PID block setting
group

Time signal block
setting group(when the TS option isordered)
Wait block settinggroup
Alarm block settinggroup

Output block setting
group

Repetitions and Patternlink setting group
AT Perform group

PV Display

Contents
Selects the following items:
Setting pattern number, Step SV, Step time, PID blocknumber, Alarm block number, etc.
Selects the following setting groups:
PID block, Time signal block, Wait block, Alarm block,
Output block
Sets the following items of blocks 0 to 9:
OUT1 proportional band, Integral time, Derivative
time, ARW, OUT2 proportional band (when DR, DS
or DA option is ordered)
Sets the following items of blocks 0 to 15:
Time signal output OFF time,
Time signal output ON time
Sets Wait value of blocks 0 to 9.
Sets the following alarm values of blocks 0 to 9:
EV1 alarm value, EV2 alarm value, EV3 alarm value,
EV4 alarm value(Appears when an Alarm type is selected in [Event
output EV allocation].)Sets the following items of blocks 0 to 9:
OUT1 high limit, OUT1 low limit,
OUT2 high limit (when DR, DS or DA option is ordered),
OUT2 low limit (when DR, DS or DA option is ordered),
OUT1 rate-of-change
Sets the number of repetitions and pattern links.
Sets the following items:
AT mode, AT Perform/Cancel, AT bias.

- 28 -

GroupEngineering setting
group

Input parametersetting group
Output parametersetting group

Event output
parameter settinggroup

SV limit setting group
Transmission output
parameter setting
group (When TA or TV
option is ordered)Communication
parameter setting
group (When C or C5
option is ordered)
Other parameters
setting group
Auto/Manual control
switch group

PV Display

Contents
Selects the following setting groups:
Input parameter, Output parameter, Event output
parameter, SV limit, Transmission output parameter,
Communication parameter, Other parameters
Sets the following items:
Input type, Scaling high limit, Scaling low limit, Decimal
point place, Sensor correction, PV filter time constantSets the following items:
OUT1 proportional cycle, OUT1 ON/OFF hysteresis,
OUT2 proportional cycle (when DR, DS or DA option isordered), OUT2 cooling method (when DR, DS or DA
option is ordered), Direct/Reverse action, etc.
Sets the following items:
Event output EV1 allocation,
Event output EV2 allocation,
Event output EV3 allocation,
Event output EV4 allocation
Sets the following items:
SV high limit, SV low limit.
Sets the following items:
Transmission output type, Transmission output highlimit, Transmission output low limit
Sets the following items:
Communication protocol, Instrument number,Communication speed, Response delay time, etc.
Sets the following items:
Set value lock, Program start Auto/Manual,
Program control start type, Power restore action, etc.
Sets the following item:
Auto/Manual control switch.

- 29 -

6. Basic Operating Procedure after Power ON
and Setting Examples
6.1 Basic Operating Procedure after Power ON

Power ON
Initial setting
Input parameter(p.34)
Output parameter(p.35)

Set Input and Output parameters.

Event output
parameter (p.35)
Other parameters(p.36)

Set program control related data.

Program patternsetting
Pattern setting(pp.37 - 39)

Set program patterns.

Block setting
PID block(p.39)
Wait block(p.39)
Set each block data.
Alarm block(pp.39, 40)
Output block(p.41)

Test operation

Turn the load circuit power ON, andperform test operation.

AT Perform(pp.41, 42)

Selects AT mode, and performs AT.

RUN- 30 -

6.2 Initial Setting, Program Pattern Setting and Block Setting• Example of Initial Setting
Setting Group
Input parametersetting group
Output parametersetting group
Event output parametersetting group
Other parameters
setting group

Setting Item

Setting Example
K, -200 to 1370
1200
0
15 seconds
Reverse action
Process high alarm
Energized

Input type
Scaling high limit
Scaling low limit
OUT1 proportional cycle
Direct/Reverse action
Event output EV2 allocation
EV2 alarm Energized/
De-energized
Program start Auto/Manual
Program control start type
Power restore action
Step time unit
Step time indication
Step SV indication
Step SV Hold function when
program ends

• Example of Program Pattern Setting
Pattern 1
Step number0

Manual start
PV start
Continues after power isrestored
Hours:Minutes
Remaining time
SV corresponding to the steptime progress
Not holding

1

2

3

4

500
1:00
1
0
2
1

1000
0:40
2
1
1
0

1000
1:00
2
0
2
1

0
2:00
1
0
1
0

1000

500

0
Step SV
Step time
PID block number
Wait block number
Alarm block number
Output block number

500
0:30
1
1
1
0

(Fig. 6.2-1)- 31 -

Explanation of the Program Pattern
Step 0: After program control starts, control is performed so that SV gradually rises from 0
to 500 for 30 minutes.
Step 1: Control is performed to keep the SV at 500 for 1 hour.
Step 2: Control is performed so that SV gradually rises from 500 to 1000 for 40 minutes.
Step 3: Control is performed to keep the SV at 1000 for 1 hour.
Step 4: Control is performed so that SV gradually falls from 1000 to 0 for 2 hours.
• Example of Block Setting
How to set each block setting group
If program pattern is not set for a step, its block number becomes 0 (zero). We highly recommendthat you leave the factory default of Block 0 in each block setting group as they are, and set thevalues from Block 1.
Setting GroupPID block setting group(*1)

Wait block setting group
Alarm block setting
group (*2)

Output block settinggroup

Setting Item
Block 0 OUT1 proportional band
Block 0 integral time
Block 0 derivative time
Block 0 ARW
Block 1 OUT1 proportional band
Block 1 integral time
Block 1 derivative time
Block 1 ARWBlock 2 OUT1 proportional band
Block 2 integral time
Block 2 derivative time
Block 2 ARWBlock 0 Wait value
Block 1 Wait value
Block 0 EV2 alarm value
Block 0 EV3 alarm value
Block 0 EV4 alarm value
Block 1 EV2 alarm value
Block 1 EV3 alarm value
Block 1 EV4 alarm value
Block 2 EV2 alarm value
Block 2 EV3 alarm value
Block 2 EV4 alarm value
Block 0 OUT1 high limit
Block 0 OUT1 low limit
Block 1 OUT1 high limit
Block 1 OUT1 low limit

Setting Example
10200 seconds
50 seconds
50%
10
200 seconds
50 seconds
50%
10
200 seconds
50 seconds
50%
0 (*3)
10
0 (*4)
0 (*4)
0 (*4)
600
5
5
1100
10
10
100% (*5)
0% (*5)80%0%(*1) As PID constant are obtained by performing AT, values in the PID block setting group are factory default value.
(*2) As EV1 is used as Pattern end output, ‘EV1 alarm value’ setting item does not appear.
(*3) As ‘Block 0 Wait value’ is used as Wait Disabled, the Wait value is factory default value.
(*4) As Block 0 EV2, EV3 and EV4 alarm values are used as No alarm action, their values are factory default value.
(*5) As Block 0 OUT1 high limit and low limit are used as MV setting range for manual control, their values are factory
default value.

- 32 -

Operation method will be described based on the Initial setting, Program pattern setting and Blocksetting examples.
Indication of Setting Details
Input type
• Upper left: PV Display: Indicates setting characters.
• Lower left: SV/MV/TIME Display: Indicates setting values or selections.
• Right side: Indicates the setting item.

Key Operation for Setting• To increase or decrease the set value (numeric value), use theIf theor

key is pressed with theor

key simultaneously, makes the numeric valuechange faster.
To switch the selection items, use the• To register the setting data, use the•+means pressing the

key.

or
or
and

key.
key.
keys at the same time.

• To return to RUN mode from any setting group, press the
The unit can return to RUN mode from any setting item.

- 33 -

key.

Basic Procedure

Setting Details

Power ON

Power ON

RUN mode [Program control Stop (inStandby)]

RUN mode

Pattern setting group(4 times)
Engineering setting group

Input parameter setting
group

Input parameter setting group

Input typeor
K -200 to 1370

Scaling high limit
or
1200

Scaling low limit
or0+
Input parameter setting group- 34 -

Output parametersetting group

Output parameter setting group

OUT1 proportional cycleor
15 seconds(Multiple times)
Direct/Reverse actionor
Reverse action+
Output parameter setting group

Event output parametersetting group

Event output parameter setting group(Twice)Event output EV2 allocation
orProcess high alarm(3 times)
EV2 alarm Energized/De-energizedorEnergized+
Event output parameter setting group(Multiple times)- 35 -

Other parameters
setting group

Other parameters setting group(Twice)Program start Auto/Manualor
Manual start(Twice)Program control start typeorPV start

Power restore action
orContinues after power is restored.

Step time unit
or
Hours: Minutes

Step time indicationorRemaining time

Step SV indicationor- 36 -

SV corresponding to the step time progress(Twice)Step SV Hold function when program endsorNot holding+(Twice)Engineering setting group(Twice)Pattern setting group

Pattern setting group

Setting pattern numberor1

Step 0 Step SVor500

Step 0 Step time
or

0:30

Step 0 PID block numberor- 37 -

1

Step 0 Wait block numberor1

Step 0 Alarm block numberor1

Step 0 Output block numberor0

Step 1 Step SVor500

Step 1 Step timeor
1:00

Step 1 PID block numberor- 38 -

1

Set items up to ‘Step 4 output block number’in the same way.

Step 4 output block number+
Pattern setting group

Block setting group

PID block setting group

PID block setting group

At this stage, setting items in the PID block setting
group do not need to be set, as PID constants are
obtained by performing AT.

Wait block setting group

Wait block settinggroup(Twice)Block 1 Wait value
or
10+
Wait block setting group

Alarm block settinggroup

Alarm block setting group(4 times)
Block 1 EV2 alarm valueor- 39 -

600

Block 1 EV3 alarm value
or5

Block 1 EV4 alarm value
or5

Block 2 EV2 alarm value
or
1100

Block 2 EV3 alarm valueor10

Block 2 EV4 alarm value
or
10+
Alarm block setting group- 40 -

Output block settinggroup

Output block setting group(Multiple times)
Block 1 OUT1 high limitor80%

Block 1 OUT1 low limitor0%

At this stage, settings are complete.

RUN mode

RUN mode [Program control Stop (inStandby)]Pattern number to perform
Select Pattern 1 with the
key.
Turn the load circuit power ON,
and start test operation.
Test operation

Test operation (Program control RUN).
As an example, perform AT at Step 1 where
the step SV is constant.
By pressing thekey, the unit moves to
Step 1.

Pattern setting group(3 times)
AT Perform

AT Perform group- 41 -

AT modeorNormal mode

AT Perform/Cancelor
AT Perform

RUN mode
The AT indicator flashes while AT is
performing.
The AT indicator turns off after AT finishes.
Perform AT at Steps 2 or 3 for which PID
block number 2 is selected in the same way.
Program control STOP

Program control complete
After program control is finished, pattern end
output is turned ON, flashing.
If thekey is pressed for 1 second,
pattern end output turns off, and the unit
returns to Standby status.

RUN mode (in standby)

RUN mode [Program control Stop (inStandby)]

RUN

Program control starts (Program control
RUN).

- 42 -

7. Setting Items
Caution• When connecting USB communication cable (CMB-001) to the console connector, connect thecable after power is turned OFF.
• Never turn the power ON or OFF, while USB communication cable (CMB-001) is connected tothe console connector.
The following groups will be described:
Pattern setting group, Block setting group, Repetitions and Pattern link setting group,
AT perform group, Engineering setting group, Auto/Manual control switch group
How to register the Setting Data
• To increase or decrease the set value (numeric value), use theorkey.
If theor
key is pressed with the
key simultaneously, makes the numeric value change
faster.
To switch the selection items, use theorkey.
• To register the setting data, use theorkey.
7.1 Pattern Setting GroupIn the Pattern setting group, the following setting items can be set:
Setting pattern number, Step SV, Step time, PID block number, Alarm block number, etc.
• To enter Pattern Setting Group
Press thekey in RUN mode. The PV Display indicates, and the unit enters Patternsetting group in Group selection mode.
Press thekey in the Pattern setting group. The PV Display indicates, and the unit
enters ‘Setting pattern number’.
• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display indicates the setting pattern number, and the PV Display indicates setting
characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display indicates the setting step number, and the SV/MV/TIME Display
indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range (or selection item).
PTN Display

PV Display

Setting item, function, setting range (or selection item)

Step 0 step SV• Sets Step 0 step SV.
• Setting range:
SV low limit to SV high limit
STEP Display

SV/MV/TIME Display- 43 -

Setting items in the Pattern setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Setting pattern number• Selects the setting pattern number.
• Selection item:
0 to 15
Step 0 step SV• Sets Step 0 step SV.
Step SV is the value at the end of the step.
• Setting range:
SV low limit to SV high limit
Step 0 step time
• Sets Step 0 step time.
Step time is the processing time of the step.
• Setting range:, 0:00 to 99:59 Time unit follows the selection in [Step time unit].
If thekey is pressed at 0:00,
will be set.
Whenis set, Fixed value control will be performed using step SV
at Step 0.
Step 0 PID block number• Selects PID block number used for Step 0.
• Selection item:
0 to 9
Step 0 Time signal 1 block number• Selects Time signal 1 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS1 is selected in [Time signal output TS1/Status (RUN) output].

Step 0 Time signal 2 block number• Selects Time signal 2 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS2 is selected in [Time signal output TS2/Status (HOLD) output].

Step 0 Time signal 3 block number• Selects Time signal 3 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS3 is selected in [Time signal output TS3/Status (WAIT) output].

- 44 -

Character,
Factory Default

Setting Item, Function, Setting Range
Step 0 Time signal 4 block number• Selects Time signal 4 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS4 is selected in [Time signal output TS4/Status (FAST) output].

Step 0 Time signal 5 block number• Selects Time signal 5 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS5 is selected in [Time signal output TS5/Status (STOP) output].

Step 0 Time signal 6 block number• Selects Time signal 6 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Time signal 7 block number• Selects Time signal 7 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Time signal 8 block number• Selects Time signal 8 block number used for Step 0.
Selects any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
• Selection item:
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Wait block number• Selects a Wait block number used for Step 0.
• Selection item:
0 to 9
Step 0 Alarm block number• Selects an Alarm block number used for Step 0.
• Selection item:
0 to 9- 45 -

Character,
Factory Default

Setting Item, Function, Setting Range
Step 0 Output block number• Selects an Output block number used for Step 0.
• Selection item:
0 to 9
Step 1 step SV• Sets Step 1 step SV.
• Setting range:
SV low limit to SV high limit
Repeat the above settings up to ‘Step 15 Output block number’,in the same way if necessary.
Step 15 Output block number• Selects an Output block number used for Step 15.
• Selection item:
0 to 9At this stage, settings of Pattern setting group are complete.
andkeys are pressed at the same time, the unit returns to Group selection mode.
If theBy pressing thekey, the unit returns to RUN mode.

- 46 -

7.2 Block Setting GroupIn the Block setting group, the following block setting groups are included:
PID block setting group, Time signal block setting group, Wait block setting group, Alarm block setting
group, Output block setting group
About settings in each block setting group
If program pattern is not set for a step, its block number becomes 0 (zero). We highly recommend thatyou leave the factory default values of Block 0 in each block setting group as they are, and set thevalues from Block 1.
• To enter the Block setting group
Press thein RUN mode, and press
key (in that order). The PV Display indicates,
and the unit enters the Block setting group in Group selection mode.
Press thein the Block setting group. The PV Display indicates, and the unit enters PID
block setting group.
Every time thekey is pressed, the block setting groups are switched as shown below.
By pressing the
key at each block setting group, the unit moves to the setting items in the group.

PID block setting group

Setting items in the group

Time signal block setting group (*1)

Setting items in the group

Wait block setting group

Setting items in the group

Alarm block setting group (*2)

Setting items in the group

Output block setting group

Setting items in the group(*1) Available when Time signal output (TS option) is ordered.
(*2) Available when 001 to 012 (Alarm output) is selected in [Event output EV

allocation].

• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range (or selection item).
PTN Display

PV Display

Setting item, function, setting range (or selection item)

Block 0 OUT1 proportional band
• Sets Block 0 OUT1 proportional band.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to input span
STEP Display

SV/MV/TIME Display- 47 -( )7.2.1 PID Block Setting GroupIn PID block setting group, the following can be set for blocks 0 to 9:
OUT1 proportional band, Integral time, Derivative time, ARW and OUT2 proportional band (DR,DS or DA option)
Refer to recommended usage of block numbers as follows:
Block 0: For Fixed value control
Block 1: For low temperature program control
Block 2: For medium temperature program control
Block 3: For high temperature program control
Setting items in the PID block setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 OUT1 proportional band
• Sets Block 0 OUT1 proportional band.
When set to 0 or 0.0, OUT1 becomes ON/OFF control.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to input span ( )Thermocouple, RTD input with decimal point: 0.0 to input span ( )DC voltage, current input: 0.0 to 1000.0%
Block 0 integral time
• Sets Block 0 integral time.
Setting the value to 0 disables the function.
• Setting range:
0 to 3600 seconds
Block 0 derivative time
• Sets Block 0 derivative time.
Setting the value to 0 disables the function.
• Setting range:
0 to 1800 seconds
Block 0 ARW• Sets Block 0 ARW.
• Setting range:
0 to 100%
Block 0 OUT2 proportional band
• Sets Block 0 OUT2 proportional band.
OUT2 proportional band: Multiplied value of OUT1 proportional band
OUT2 proportional band is calculated as follows.
OUT2 proportional band = OUT1 proportional band x Multiplication factor
When set to 0.0, OUT2 becomes ON/OFF control.
When OUT1 proportional band is set to 0 or 0.0, OUT2 becomes ON/OFF
control.
• Setting range:
0.0 to 10.0 times (Multiplied value of Block 0 OUT1 proportional band)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

- 48 -

Character,
Factory Default

Setting Item, Function, Setting Range
Block 1 OUT1 proportional band
• Sets Block 1 OUT1 proportional band.
When set to 0 or 0.0, OUT1 becomes ON/OFF control.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to input span ( )Thermocouple, RTD input with decimal point: 0.0 to input span ( )DC voltage, current input: 0.0 to 1000.0%
Repeat the above settings up to ‘Block 9 OUT2 proportional band’,in the same way if necessary.
Block 9 OUT2 proportional band
• Sets Block 9 OUT2 proportional band.
OUT2 proportional band: Multiplied value of OUT1 proportional band
OUT2 proportional band is calculated as follows.
OUT2 proportional band = OUT1 proportional band x Multiplication factor
When set to 0.0, OUT2 becomes ON/OFF control.
When OUT1 proportional band is set to 0 or 0.0, OUT2 becomes ON/OFF
control.
• Setting range:
0.0 to 10.0 times (Multiplied value of Block 9 OUT1 proportional band)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

At this stage, settings of PID block setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Block setting group.
By pressing thekey, the unit returns to RUN mode.

- 49 -

7.2.2 Time Signal Block Setting GroupIn Time signal block setting group, the following can be set for blocks 0 to 15:
Time signal output OFF time, Time signal output ON time
• Time signal output function
Time signal output OFF time and Time signal output ON time are set within each step time, andoutputs them during Program control RUN.
A maximum of 8 points of Time signal output can be set for each step.
To use the Time signal output function, set the Time signal block number (for which Time signal
output OFF time and Time signal output ON time have been set) for each step.
Up to 16 Time signal blocks can be set.
• Program pattern setting example
Pattern 1
Step number
0

1

500

0
Step SV
Step time (Hours:Minutes)
PID block numberTime signal 1
block number
ON
OFFTime signal 2
block number
ON
OFFTime signal 3
block number
ON
OFFTime signal 4
block number
ON
OFF

500
0:30
1
0

500
1:00
1
1

①

2

2

②

1

2

③

1

1

Output block number

01• Time signal block setting example
Time signal block number
012

Output OFF time
(Hours:Minutes)
0:00
0:20
0:00

Output ON time
(Hours:Minutes)
0:00
0:30
0:30

① Time signal output operates in a sequence of Time signal output OFF time and then Timesignal output ON time.
The Time signal output automatically turns OFF when Time signal output ON time expires
within a step.
- 50 -

② If ON time is the same value as the step time, the Time signal output will turn OFF fora brief moment while Step numbers change.
Therefore, set the Time signal output ON time longer than the step time so that Time signal
output may turn ON even when steps changes.
③ When ON time is not the same value as the step time, from the point where steps move tothe next step, the Time signal output operates following the Time signal output OFF or ON
time of the next step, regardless of the Time signal output settings of the previous step.
Setting items in the Time signal block setting group are shown below.
Available when Time signal output (TS option) is ordered.
Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 Time signal output OFF time
• Sets Block 0 Time signal output OFF time.
• Setting range:
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Block 0 Time signal output ON time
• Sets Block 0 Time signal output ON time.
• Setting range:
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Block 1 Time signal output OFF time
• Sets Block 1 Time signal output OFF time.
• Setting range:
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Repeat the above settings up to ‘Block 15 Time signal output ON time’,in the same way if necessary.
Block 15 Time signal output ON time
• Sets Block 15 Time signal output ON time.
• Setting range:
00:00 to 99:59 Time unit follows the selection in [Step time unit].

At this stage, settings of Time signal block setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Block setting group.
By pressing thekey, the unit returns to RUN mode.

- 51 -

7.2.3 Wait Block Setting GroupIn Wait block setting group, Wait value can be set for blocks 0 to 9.
• Wait function
During Program control RUN, the program does not proceed to the next step until the deviation
between PV and SV enters SV Wait value at the end of step.
When the Wait function is activated, the STEP Display flashes.
• Explanation of Wait function• Program pattern rising stepSV

Wait value 10
T

T

500
490

Time
When PV becomes 490 , the Wait function is cancelled, proceeding to the next step.
As PV is not in the range of [SV－Wait value], the Wait function is activated, and the unit
does not proceed to the next step. The STEP Display flashes during Wait function.

• Program pattern falling stepSV

Wait value 10
T

T

510
500

Time
When PV becomes 510 , Wait function is cancelled, proceeding to the next step.
As PV is not in the range of [SV+Wait value], the Wait function is activated, and theunit does not proceed to the next step. The STEP Display flashes during Wait function.
Program pattern
PV
Program pattern which is delayed by T due to Wait function• How to cancel the Wait function
Press theor
key to cancel the Wait function.
Use External operation input [ADV] or [STOP] to cancel the Wait function as well.

- 52 -

Setting items in the Wait block setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 Wait value• Sets Block 0 Wait value.
When set to 0 or 0.0, the Wait function is disabled.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal point
follows the selection.)
Block 1 Wait value• Sets Block 1 Wait value.
When set to 0 or 0.0, the Wait function is disabled.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal point
follows the selection.)
Repeat the above settings up to ‘Block 9 Wait value’,in the same way if necessary.
Block 9 Wait value• Sets Block 9 Wait value.
When set to 0 or 0.0, the Wait function will be disabled.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal
point follows the selection.)

At this stage, settings of Wait block setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Block setting group.
By pressing thekey, the unit returns to RUN mode.

- 53 -

7.2.4 Alarm Block Setting GroupIn Alarm block setting group, the following can be set for blocks 0 to 9:
EV1 alarm value, EV2 alarm value, EV3 alarm value, EV4 alarm value• Alarm output
EV1 alarm output actions are shown below.
The same applies to EV2, EV3 and EV4 alarm output.
• High limit alarm• High limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value

SV-EV1 value+EV1 value+EV1 value

SV

Alarm output is in standby.
(Fig. 7.2.4-1)(Fig. 7.2.4-2)• Low limit alarm• Low limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value-EV1 value

SV +EV1 value

SV +EV1 value

Alarm output is in standby.
(Fig. 7.2.4-3)(Fig. 7.2.4-4)• High/Low limits alarm• High/Low limits with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueSV

EV1 valueEV1 valueSV

EV1 value

Alarm output is in standby.
(Fig. 7.2.4-5)(Fig. 7.2.4-6)- 54 -

• High/Low limit range alarm• High/Low limit range with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

SV EV1 value

SV EV1 value

Alarm output is in standby.
(Fig. 7.2.4-7)• Process high alarm(Fig. 7.2.4-8)• Process high with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.
(Fig. 7.2.4-9)(Fig. 7.2.4-10)• Process low alarm• Process low with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.
(Fig. 7.2.4-11)(Fig. 7.2.4-12)

For the alarm types (High limit alarm, High/Low limits alarm, Process high alarm), alarm output isactivated when the indication is overscale, and the standby function is released for the alarms withstandby function.
For the alarm types (Low limit alarm, High/Low limits alarm, Process low alarm), alarm output isactivated when the indication is underscale, and the standby function is released for the alarmswith standby function.
When the alarm action De-energized is selected, the output ON/OFF status acts conversely to thealarm action described above. (The Event indicators act the same as the action Energized.)
Event indicators
Event output

Energized

De-energized

Light
ON

Light
OFF
- 55 -

Setting items in the Alarm block setting group are shown below.
When 001 to 012 (Alarm output) is selected in [Event output EV allocation], the following will appear.
Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 EV1 alarm value• Sets Block 0 EV1 alarm value.
• Setting range:Type
No alarm action
High limit alarm

Setting Range– (Input span) to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

High limit withstandby alarm
Low limit alarm– (Input span) to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)– (Input span) to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

Low limit withstandby alarm
High/Low limits
alarm
High/Low limits
with standby alarm
High/Low limit
range alarm
High/Low limit
range with standby
Process high alarm
Process high withstandby alarm
Process low alarm
Process low withstandby alarm– (Input span) to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action is disabled when set to 0 or 0.0.)

Input range low limit to Input range high limit (*2)
Input range low limit to Input range high limit (*2)
Input range low limit to Input range high limit (*2)
Input range low limit to Input range high limit (*2)(*1) For DC voltage, current input, the input span is the same as the scaling span.
(*2) For DC voltage, current input, input range low (or high) limit value is the same as scaling low (orhigh) limit value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV1 allocation],

Block 0 EV2 alarm value• Sets Block 0 EV2 alarm value.
• Setting range:
Same as that of Block 0 EV1 alarm value.
Available when 001 to 012 (Alarm output) is selected in [Event output EV2 allocation].

Block 0 EV3 alarm value• Sets Block 0 EV3 alarm value.
• Setting range:
Same as that of Block 0 EV1 alarm value.
Available when 001 to 012 (Alarm output) is selected in [Event output EV3 allocation].

- 56 -

Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 EV4 alarm value• Sets Block 0 EV4 alarm value.
• Setting range:
Same as that of Block 0 EV1 alarm value.
Available when 001 to 012 (Alarm output) is selected in [Event output EV4 allocation].

Block 1 EV1 alarm value• Sets Block 1 EV1 alarm value.
• Setting range:
Same as that of Block 0 EV1 alarm value.
Available when 001 to 012 (Alarm output) is selected in [Event output EV1 allocation].

Repeat the above settings up to ‘Block 9 EV4 alarm value’,in the same way if necessary.
Block 9 EV4 alarm value• Sets Block 9 EV4 alarm value.
• Setting range:
Same as that of Block 0 EV1 alarm value.
Available when 001 to 012 (Alarm output) is selected in [Event output EV4 allocation].

At this stage, settings of Alarm block setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Block setting group.
By pressing thekey, the unit returns to RUN mode.

- 57 -

7.2.5 Output Block Setting GroupIn Output block setting group, the following can be set for blocks 0 to 9:
OUT1 high limit, OUT1 low limit, OUT2 high limit (DR, DS or DA option), OUT2 low limit (DR, DS or
DA option), OUT1 rate-of-change
Setting items in the Output block setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Block 0 OUT1 high limit• Sets Block 0 OUT1 high limit.
• Setting range:
OUT1 low limit to 100% (For direct current output: OUT1 low limit to 105%)
Block 0 OUT1 low limit• Sets Block 0 OUT1 low limit.
• Setting range:
0% to OUT1 high limit (For direct current output: -5% to OUT1 high limit)
Block 0 OUT2 high limit• Sets Block 0 OUT2 high limit.
• Setting range:
OUT2 low limit to 100% (For direct current output: OUT2 low limit to 105%)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Block 0 OUT2 low limit• Sets Block 0 OUT2 low limit.
• Setting range:
0% to OUT2 high limit. (For direct current output: -5% to OUT2 high limit)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Block 0 OUT1 rate-of-change• Sets Block 0 OUT1 rate-of-change (changing value of OUT1 MV for 1
second)Setting the value to 0 disables this function.
[OUT1 rate-of-change]
For Heating control, if PV is lower than SV, OUT1 MV changes as shown in(Fig. 7.2.5-1).
If OUT1 rate-of-change is set, OUT1 MV can be changed by the rate-ofchange (Fig. 7.2.5-2).
This control is suitable for high temperature heaters (for which slow
temperature rise is required, and used at approx. 1500 to 1800 ) which areeasily burnt out from turning on electricity rapidly.
ON (100%)

OFF (0%)(Fig. 7.2.5-1)- 58 -

100 %/sec

20 %/sec

10 %/sec

ON (100%)

OFF (0%)
1 sec

5 sec

10 sec(Fig. 7.2.5-2)• Setting range:
0 to 100 %/Second
Block 1 OUT1 high limit• Sets Block 1 OUT1 high limit.
• Setting range:
OUT1 low limit to 100% (For direct current output: OUT1 low limit to 105%)
Repeat the above settings up to ‘Block 9 OUT1 rate-of-change’,in the same way if necessary.
Block 9 OUT1 rate-of-change• Sets Block 9 OUT1 rate-of-change (changing value of OUT1 MV for 1
second).
Setting the value to 0 disables this function.
• Setting range:
0 to 100 %/second
At this stage, settings of Output block setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Block setting group.
By pressing thekey, the unit returns to RUN mode.

- 59 -

7.3 Repetitions and Pattern Link Setting GroupIn Repetitions and pattern link setting group, the following can be set:
Number of repetitions, Pattern link
Pattern numbers 0 to 15 can be linked to the next pattern. Only pattern numbers in numerical order canbe linked. For Pattern 15, Pattern 0 can be linked.
Randomly selected pattern numbers (Pattern 0 and Pattern 3) cannot be linked.
Number of repetitions for Pattern numbers 0 to 15: 0 to 9999 times.
For repetitions of linked pattern, the whole linked pattern will be repeated as many times as set in “starting
pattern number”.
(e.g.) If patterns 1 and 2 are linked, and if the number of repetitions of pattern 1 is set to 2 times,
the whole linked pattern (Patterns 1 and 2) will be repeated twice.
• To enter Repetitions and Pattern link setting group
Press thekey once in RUN mode, and press the
key twice. The PV Display indicates, and the unit enters the Repetitions and Pattern link setting group.
Press thekey in the Repetitions and Pattern link setting group. The PV Display indicates, and the unit enters ‘Repetitions for pattern 0’.
• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display indicates the setting pattern number, and the PV Display indicates setting
characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range.
PTN Display

PV Display

Setting item, function, setting range (or selection item)

Repetitions for Pattern 0• Sets the number of repetitions of pattern 0.
• Setting range:
0 to 9999 times
STEP Display

SV/MV/TIME Display

Setting items in the Repetitions and Pattern link setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Repetitions for pattern 0• Sets the number of repetitions of pattern 0.
• Setting range:
0 to 9999 times
Pattern link between pattern 0 and pattern 1• Selects Pattern link Enabled/Disabled for pattern 0 and pattern 1.
• Selection item:: Pattern link Disabled: Pattern link Enabled- 60 -

Character,
Factory Default

Setting Item, Function, Setting Range
Repetitions for Pattern 1• Sets the number of repetitions of Pattern 1.
• Setting range:
0 to 9999 times
Repeat the above settings up to ‘Pattern link between pattern 15 and pattern 0’,
in the same way if necessary.
Pattern link between pattern 15 and pattern 0• Selects Pattern link Enabled/Disabled for pattern 15 and pattern 0.
• Selection item:: Pattern link Disabled: Pattern link Enabled

At this stage, settings of “Repetitions and pattern link setting group” are complete.
If theandkeys are pressed at the same time, the unit returns to Group selection mode.
By pressing thekey, the unit returns to RUN mode.

- 61 -

7.4 AT Perform GroupIn AT Perform group, the following can be set:
AT mode, AT Perform/Cancel, AT bias
• To enter AT Perform group
Press thekey once in RUN mode, and press the
key 3 times. The PV Display indicates, and the unit enters the AT Perform group.
Press thein the AT Perform group. The PV Display indicates, and the unit enters ‘ATmode’.
• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range.
PTN Display

PV Display

Setting item, function, setting range (or selection item)

AT mode• Selects AT mode.
• Selection item:: Normal mode
STEP Display

SV/MV/TIME Display

Setting items in the AT Perform group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
AT mode• Selects AT mode.
Multi mode is enabled only during program control.
• Selection item:: Normal mode
When AT Perform is selected in [AT Perform/Cancel], AT starts
immediately.
: Multi mode
AT is automatically performed at the point where 90% of
progressed step time has elapsed.
If there are the same PID block numbers in one pattern, the AT is
performed only for the first step.
AT Perform/Cancel• Selects AT Perform/Cancel.
AT continues to perform when input errors (overscale, underscale) occur.
AT will be forced to stop if it has not been completed within 4 hours.
• Selection item:: AT Cancel: AT Perform- 62 -

Character,
Factory Default

Setting Item, Function, Setting Range
AT bias• Sets bias value for the AT. (See p.117)
AT point is automatically determined by the deviation between PV and SV.
AT bias setting is available for Fixed value control.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 50 (0 to 100 )Thermocouple, RTD input with decimal point: 0.0 to 50.0 (0.0 to 100.0 )At this stage, settings of AT Perform group are complete.
If theandkeys are pressed at the same time, the unit returns to Group selection mode.
By pressing thekey, the unit returns to RUN mode.

- 63 -

7.5 Engineering Setting GroupIn Engineering setting group, the following setting groups are included:
Input parameter setting group, Output parameter setting group, Event output parameter setting group,
SV limit setting group, Transmission output parameter setting group, Communication parametersetting group, Other parameters setting group• To Enter the Engineering Setting Group
Press thekey once in RUN mode, and press thekey 4 times. The PV Display indicates, and the unit enters the Engineering setting group.
Press thekey in the Engineering setting group. The PV Display indicates, and theunit enters Input parameter setting group in the Engineering setting group.
Each time thekey is pressed, the Engineering setting group is switched as follows.
By pressing the
key at each setting group, the unit moves to its setting items in the group.

Input parameter setting group

Setting items in the group

Output parameter setting group

Setting items in the group

Event output parameter setting group

Setting items in the group

SV limit setting group

Setting items in the group

Setting items in the group

Communication parameter setting group (*2)

Setting items in the group

Other parameters setting group

Setting items in the group(*1) Available when Transmission output (TA or TV option) is ordered.
(*2) Available when Serial communication (C or C5 option) is ordered.

- 64 -

• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range.

PTN Display

PV Display

Setting item, function, setting range (or selection item)

Input type
• Selects the input type.
• Selection item:
K -200 to 1370
STEP Display

SV/MV/TIME Display- 65 -

7.5.1 Input Parameter Setting GroupIn Input parameter setting group, the following can be set:
Input type, Scaling high limit, Scaling low limit, Sensor correction, PV filter time constant, etc.
Setting items in the Input parameter setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Input type
• Selects an input type.
If input type is changed, the following items revert to the factory default:
Scaling high limit, Scaling low limit, Sensor correction, SV high limit,
SV low limit, Transmission output high limit (except MV transmission),Transmission output low limit (except MV transmission), Step SV when
program control starts, PV color range, Loop break alarm time, Loop breakalarm span, AT bias
• Selection item:: K -200 to 1370
: K -200.0 to 400.0: J -200 to 1000
: R 0 to 1760
: S 0 to 1760
: B 0 to 1820
: E -200 to 800: T -200.0 to 400.0: N -200 to 1300
: PL0 to 1390
: C(W/Re5-26) 0 to 2315
: Pt100 -200.0 to 850.0: JPt100 -200.0 to 500.0: Pt100 -200 to 850: JPt100 -200 to 500: Pt100 -100.0 to 100.0: Pt100 -100.0 to 500.0: K -328 to 2498
: K -328.0 to 752.0: J -328 to 1832
: R 32 to 3200
: S 32 to 3200
: B 32 to 3308
: E -328 to 1472
: T -328.0 to 752.0: N -328 to 2372
: PL32 to 2534
: C(W/Re5-26) 32 to 4199
: Pt100 -328.0 to 1562.0: JPt100 -328.0 to 932.0: Pt100 -328 to 1562
: JPt100 -328 to 932- 66 -

Character,
Factory Default

Setting Item, Function, Setting Range: Pt100 -148.0 to 212.0: Pt100 -148.0 to 932.0: 4 to 20 mA DC -2000 to 10000: 0 to 20 mA DC -2000 to 10000: 0 to 10 mV DC -2000 to 10000: -10 to 10 mV DC -2000 to 10000: 0 to 50 mV DC -2000 to 10000: 0 to 100 mV DC -2000 to 10000: 0 to 1 V DC -2000 to 10000: 0 to 5 V DC -2000 to 10000: 1 to 5 V DC -2000 to 10000: 0 to 10 V DC -2000 to 10000
Scaling high limit• Sets scaling high limit value.
• Setting range:
Scaling low limit value to Input range high limit value
Scaling low limit• Sets scaling low limit value.
• Setting range:
Input range low limit value to Scaling high limit value
Decimal point place• Selects decimal point place.
• Selection item:: No decimal point: 1 digit after decimal point: 2 digits after decimal point: 3 digits after decimal point: 4 digits after decimal point
Available for DC voltage and current inputs.
Sensor correction• Sets sensor correction value.
[Sensor correction function]
When a sensor cannot be set at the exact location where control is desired, thesensor-measured temperature may deviate from the temperature in thecontrolled location. When using multiple indicating controllers, sometimes themeasured temperatures do not concur due to differences in sensor accuracy ordispersion of load capacities. In such a case, the control can be set at the desired
temperature by adjusting the input value of sensors. However, it is effective
within the input rated range regardless of the sensor correction value.
PV after sensor correction= Current PV + (Sensor correction value)• Setting range:
Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of the decimal point
follows the selection.)- 67 -

Character,
Factory Default

Setting Item, Function, Setting Range
PV filter time constant• Sets PV filter time constant.
If the value is set too high, it affects control results due to the delay of
response.
[PV filter time constant]
This is a filter function on the software, which has the same effect as a CR
filter. By calculating first-order lag of PV, this suppresses input fluctuation
caused by noise.
When the input value changes as shown in (Fig. 7.5.1-1), this function
makes the input change slowly, as shown in (Fig. 7.5.1-2).
T (PV filter time constant) is the time when input change reaches 63% of thedesired PV.
100%
63%

T

(Fig. 7.5.1-1)(Fig. 7.5.1-2)• Setting range:
0.0 to 100.0 seconds
At this stage, settings of Input parameter setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 68 -

7.5.2 Output Parameter Setting GroupIn Output parameter setting group, the following can be set:
OUT1 proportional cycle, OUT1 ON/OFF hysteresis, OUT2 proportional cycle (DR, DS or DA
option), OUT2 cooling method (DR, DS or DA option), Direct/Reverse action, etc.
Setting items in the Output parameter setting group are shown below.
Character,
Factory Default• Relay contact
output: 30 sec• Non-contact
voltage output:
3 sec

Setting Item, Function, Setting Range
OUT1 proportional cycle• Sets OUT1 proportional cycle.
• Setting range:
1 to 120 seconds
Available when control output OUT1 is Relay contact output or Non-contact voltage
output.

OUT1 ON/OFF hysteresis• Sets OUT1 ON/OFF hysteresis.

Hysteresis
ON

OFF
OUT1
hysteresis

SV(Fig. 7.5.2-1)• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point follows
the selection.)• DR: 30 sec• DS: 3 sec

OUT2 proportional cycle• Sets OUT2 proportional cycle.
• Setting range:
1 to 120 seconds
Available when Heating/Cooling control (DR or DS option) is ordered.

OUT2 cooling method• Selects OUT2 cooling method.
OUT2 proportional band

Air cooling
Oil cooling
Water coolingSV(Fig. 7.5.2-2)- 69 -

Character,
Factory Default

Setting Item, Function, Setting Range• Selection item:: Air cooling (Linear characteristics): Oil cooling (1.5th power of the linear characteristics): Water cooling (2nd power of the linear characteristics)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

OUT2 ON/OFF hysteresis• Sets OUT2 ON/OFF hysteresis.

Hysteresis
ON

OFF
SV

OUT2 hysteresis(Fig. 7.5.2-3)• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point follows
the selection.)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Overlap/Dead band
• Sets the overlap band or dead band for OUT1 and OUT2.
+ Set value: Dead band
– Set value: Overlap band
[Overlap band]
OUT1 proportional band
OUT2 proportional band

Overlap band
ON

ON
OUT1

OUT2

OFF

OFF
SV

(Fig. 7.5.2-4)- 70 -

Character,
Factory Default

Setting Item, Function, Setting Range[Dead band]
OUT1 proportional band

OUT2 proportional band

Dead band
ON

ON
OUT1

OUT2

OFF

OFF
SV

(Fig. 7.5.2-5)• Setting range:
Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of the decimal point
follows the selection.)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Direct/Reverse action• Selects either Reverse (Heating) or Direct (Cooling) control action.
• Selection item:: Reverse action: Direct action
At this stage, settings of Output parameter setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 71 -

7.5.3 Event Output Parameter Setting GroupIn Event output parameter setting group, the following can be set:
Event output EV1 allocation, Event output EV2 allocation,
Event output EV3 allocation, Event output EV4 allocation
In Event output (EV1 to EV4) allocation, the following can be selected:
Alarm output, Pattern end output, Loop break alarm, Output during AT
Factory default values for EV1, EV2, EV and EV4:
EV1: Pattern end output
EV2: No event
EV3: Alarm output, High limit alarm
EV4: Alarm output, Low limit alarm
Alarm output actions are shown below.
• High limit alarm• High limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value

SV-EV1 value+EV1 value+EV1 value

SV

Alarm output is in standby.
(Fig. 7.5.3-1)(Fig. 7.5.3-2)• Low limit alarm• Low limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value-EV1 value

SV +EV1 value

SV +EV1 value

Alarm output is in standby.
(Fig. 7.5.3-3)(Fig. 7.5.3-4)• High/Low limits alarm• High/Low limits with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueSV

EV1 valueEV1 valueSV

EV1 value

Alarm output is in standby.
(Fig. 7.5.3-5)(Fig. 7.5.3-6)- 72 -

• High/Low limit range alarm• High/Low limit range with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

SV EV1 value

SV EV1 value

Alarm output is in standby.
(Fig. 7.5.3-7)• Process high alarm(Fig. 7.5.3-8)• Process high with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.
(Fig. 7.5.3-9)(Fig. 7.5.3-10)• Process low alarm• Process low with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.
(Fig. 7.5.3-11)(Fig. 7.5.3-12)

For the alarm types (High limit alarm, High/Low limits alarm, Process high alarm), alarm output isactivated when the indication is overscale, and the standby function is released for the alarms withstandby function.
For the alarm types (Low limit alarm, High/Low limits alarm, Process low alarm), alarm output isactivated when the indication is underscale, and the standby function is released for the alarmswith standby function.
When the alarm action De-energized is selected, the output ON/OFF status acts conversely to thealarm action described above. (The Event indicators act the same as the action Energized.)
Event indicators
Event output

Energized

De-energized

Light
ON

Light
OFF
- 73 -

Setting items in the Event output parameter setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Event output EV1 allocation• Selects Event output EV1 from the Event Output Allocation Table below.
For Alarm output, the alarm value is set by deviation from the SV(excluding Process alarm), and if the input goes outside the range, the Alarm
output is turned ON (turned OFF for High/Low limit range alarm).
When De-energized action is selected, the output is activated conversely.
Pattern end output turns ON after program control ends.
Loop break alarm output turns ON after detecting actuator trouble (heaterburnout, heater adhesion) or sensor burnout.
‘Output during AT’ turns ON during AT.
• Selection item:[Event Output Allocation Table]
Selection
Event Output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits with standby
alarm
Alarm output, High/Low limit range alarm
Alarm output, High/Low limit range withstandby alarm
Alarm output, Process high alarm
Alarm output, Process high with standby
alarm
Alarm output, Process low alarm
Alarm output, Process low with standby
alarm
Pattern end output
Loop break alarm output
Output during AT
Turns ON during AT.
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event output.
When 013 to 015 is selected, each output is common to multiple event outputs.

EV1 alarm hysteresis• Sets EV1 alarm hysteresis.
• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV1 allocation].

EV1 alarm delay time
• Sets EV1 alarm action delay time.
When setting time has elapsed after PV enters the alarm output range, thealarm is activated.
• Setting range:
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV1 allocation].

- 74 -

Character,
Factory Default

Setting Item, Function, Setting Range
EV1 alarm Energized/De-energized• Selects Energized/De-energized status for EV1 alarm.
When Energized is selected, Event output EV1 is conductive (ON) while theEV1 indicator is lit. Event output EV1 is not conductive (OFF) while the EV1
indicator is not lit.
When De-energized is selected, Event output EV1 is not conductive (OFF)while the EV1 indicator is lit. Event output EV1 is conductive (ON) while theEV1 indicator is not lit.
High limit alarm (Energized)

High limit alarm (De-energized)
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
SV

+EV1 value(Fig. 7.5.3-13)

SV+EV1 value(Fig. 7.5.3-14)• Selection item:: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV1 allocation].

Loop break alarm time
• Sets the time to assess the Loop break alarm.
[Loop break alarm]
When the control action is Reverse (Heating) control:
If the PV does not reach the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not drop to the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
When the control action is Direct (Cooling) control:
If the PV does not drop to the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not reach the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
• Setting range:
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV1
allocation].

- 75 -

Character,
Factory Default

Setting Item, Function, Setting Range
Loop break alarm band
• Sets the band to assess the Loop break alarm.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point follows
the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV1
allocation].

Event output EV2 allocation• Selects Event output EV2 from the Event Output Allocation Table below.
For Alarm output, the alarm value is set bydeviation from the SV(excluding Process alarm), and if the input goes outside the range, the Alarm
output is turned ON (turned OFF for High/Low limit range alarm).
When De-energized action is selected, the output is activated conversely.
Pattern end output turns ON after program control ends.
Loop break alarm output turns ON after detecting actuator trouble (heaterburnout, heater adhesion) or sensor burnout.
‘Output during AT’ turns ON during AT.
• Selection item:[Event Output Allocation Table]
Selection
Event Output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits with standby
alarm
Alarm output, High/Low limit range alarm
Alarm output, High/Low limit range withstandby alarm
Alarm output, Process high alarm
Alarm output, Process high with standby
alarm
Alarm output, Process low alarm
Alarm output, Process low with standby
alarm
Pattern end output
Loop break alarm output
Output during AT
Turns ON during AT.
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event output.
When 013 to 015 is selected, each output is common to multiple event outputs.

EV2 alarm hysteresis• Sets EV2 alarm hysteresis.
• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV2 allocation].

- 76 -

Character,
Factory Default

Setting Item, Function, Setting Range
EV2 alarm delay time
• Sets EV2 alarm action delay time.
When setting time has elapsed after PV enters the alarm output range, thealarm is activated.
• Setting range:
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV2 allocation].

EV2 alarm Energized/De-energized• Selects Energized/De-energized status for EV2 alarm.
When Energized is selected, Event output EV2 is conductive (ON) while theEV2 indicator is lit. Event output EV2 is not conductive (OFF) while the EV2
indicator is not lit.
When De-energized is selected, Event output EV2 is not conductive (OFF)while the EV2 indicator is lit. Event output EV2 is conductive (ON) while theEV2 indicator is not lit.
High limit alarm (Energized)

High limit alarm (De-energized)
EV2 hysteresis

EV2 hysteresis
ON

ON

OFF

OFF
SV

+EV2 value(Fig. 7.5.3-15)

SV+EV2 value(Fig. 7.5.3-16)• Selection item:: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV2 allocation].

Loop break alarm time
• Sets the time to assess the Loop break alarm.
[About Loop break alarm]
When the control action is Reverse (Heating) control:
If the PV does not reach the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not drop to the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
When the control action is Direct (Cooling) control:
If the PV does not drop to the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not reach the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
• Setting range:
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV2
allocation].

- 77 -

Character,
Factory Default

Setting Item, Function, Setting Range
Loop break alarm band
• Sets the band to assess the Loop break alarm.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point follows
the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV2
allocation].

Event output EV3 allocation• Selects Event output EV3 from the Event Output Allocation Table below.
For Alarm output, the alarm value is set bydeviation from the SV(excluding Process alarm), and if the input goes outside the range, the Alarm
output is turned ON (turned OFF for High/Low limit range alarm).
When De-energized action is selected, the output is activated conversely.
Pattern end output turns ON after program control ends.
Loop break alarm output turns ON after detecting actuator trouble (heaterburnout, heater adhesion) or sensor burnout.
‘Output during AT’ turns ON during AT.
• Selection item:[Event Output Allocation Table]
Selection
Event Output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits with standby
alarm
Alarm output, High/Low limit range alarm
Alarm output, High/Low limit range withstandby alarm
Alarm output, Process high alarm
Alarm output, Process high with standby
alarm
Alarm output, Process low alarm
Alarm output, Process low with standby
alarm
Pattern end output
Loop break alarm output
Turns ON during AT.
Output during AT
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event output.
When 013 to 015 is selected, each output is common to multiple event outputs.

EV3 alarm hysteresis• Sets EV3 alarm hysteresis.
• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV3 allocation].

- 78 -

Character,
Factory Default

Setting Item, Function, Setting Range
EV3 alarm delay time
• Sets EV3 alarm action delay time.
When setting time has elapsed after PV enters the alarm output range, thealarm is activated.
• Setting range:
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV3 allocation]

EV3 alarm Energized/De-energized• Selects Energized/De-energized status for EV3 alarm.
When Energized is selected, Event output EV3 is conductive (ON) while theEV3 indicator is lit. Event output EV3 is not conductive (OFF) while the EV3
indicator is not lit.
When De-energized is selected, Event output EV3 is not conductive (OFF)while the EV3 indicator is lit. Event output EV3 is conductive (ON) while theEV3 indicator is not lit.
High limit alarm (Energized)

High limit alarm (De-energized)
EV3 hysteresis

EV3 hysteresis
ON

ON

OFF

OFF
SV

+EV3 value(Fig. 7.5.3-17)

SV+EV3 value(Fig. 7.5.3-18)• Selection item:: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV3 allocation].

Loop break alarm time
• Sets the time to assess the Loop break alarm.
[About Loop break alarm]
When the control action is Reverse (Heating) control:
If the PV does not reach the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not drop to the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
When the control action is Direct (Cooling) control:
If the PV does not drop to the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not reach the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
• Setting range:
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV3
allocation].

- 79 -

Character,
Factory Default

Setting Item, Function, Setting Range
Loop break alarm band
• Sets the band to assess the Loop break alarm.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point follows
the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV3
allocation].

Event output EV4 allocation• Selects Event output EV4 from the Event Output Allocation Table below.
For Alarm output, the alarm value is set by deviation from the SV(excluding Process alarm), and if the input goes outside the range, the Alarm
output is turned ON (turned OFF for High/Low limit range alarm).
When De-energized action is selected, the output is activated conversely.
Pattern end output turns ON after program control ends.
Loop break alarm output turns ON after detecting actuator trouble (heaterburnout, heater adhesion) or sensor burnout.
‘Output during AT’ turns ON during AT.
• Selection item:[Event Output Allocation Table]
Selection
Event output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits
with standby alarm
Alarm output, High/Low limit range alarm
Alarm output, High/Low limit range withstandby alarm
Alarm output, Process high alarm
Alarm output, Process high with standby
alarm
Alarm output, Process low alarm
Alarm output, Process low with standby
alarm
Pattern end output
Loop break alarm output
Turns ON during AT.
Output during AT
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event output.
When 013 to 015 is selected, each output is common to multiple event outputs.

EV4 alarm hysteresis• Sets EV4 alarm hysteresis.
• Setting range:
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV4 allocation].

- 80 -

Character,
Factory Default

Setting Item, Function, Setting Range
EV4 alarm delay time
• Sets EV4 alarm action delay time.
When setting time has elapsed after PV enters the alarm output range, thealarm is activated.
• Setting range:
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV4 allocation].

EV4 alarm Energized/De-energized• Selects Energized/De-energized status for EV4 alarm.
When Energized is selected, Event output EV4 is conductive (ON) while theEV4 indicator is lit. Event output EV4 is not conductive (OFF) while the EV4
indicator is not lit.
When De-energized is selected, Event output EV4 is not conductive (OFF)while the EV4 indicator is lit. Event output EV4 is conductive (ON) while theEV4 indicator is not lit.
High limit alarm (Energized)

High limit alarm (De-energized)
EV4 hysteresis

EV4 hysteresis
ON

ON

OFF

OFF
SV

+EV4 value(Fig. 7.5.3-19)

SV+EV4 value(Fig. 7.5.3-20)• Selection item:: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV4 allocation].

Loop break alarm time
• Sets the time to assess the Loop break alarm.
[About Loop break alarm]
When the control action is Reverse (Heating) control:
If the PV does not reach the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not drop to the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
When the control action is Direct (Cooling) control:
If the PV does not drop to the Loop break alarm band setting within the time
allotted to assess the Loop break alarm (after the MV has reached 100% or
the OUT1 high limit value), the alarm will be activated.
Likewise, if the PV does not reach the Loop break alarm band setting within
the time allotted to assess the Loop break alarm (after the MV has reached
0% or the OUT1 low limit value), the alarm will be activated.
• Setting range:
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV4
allocation].

- 81 -

Character,
Factory Default

Setting Item, Function, Setting Range
Loop break alarm band
• Sets the band to assess the Loop break alarm.
• Setting range:
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point follows
the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV4
allocation].

At this stage, settings of Event output parameter setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering
setting group.
By pressing thekey, the unit returns to RUN mode.

- 82 -

7.5.4 SV Limit Setting GroupIn SV limit setting group, the following can be set:SV high limit, SV low limit
Setting items in the SV limit setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
SV high limit• Sets SV high limit value.
• Setting range:
SV low limit to Scaling high limit
SV low limit• Sets SV low limit value.
• Setting range:
Scaling low limit to SV high limit

At this stage, settings of SV limit setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 83 -

7.5.5 Transmission Output Parameter Setting GroupIn Transmission output parameter setting group, the following can be set:
Transmission output type, Transmission output high limit, Transmission output low limit,
Setting items in the Transmission output parameter setting group are shown below.
Available when Transmission output (TA or TV option) are ordered.
Character,
Factory Default

Setting Item, Function, Setting Range
Transmission output type
• Selects transmission output type.
Converting the value (PV, SV or MV transmission) to analog signal
every 125 ms, outputs the value in current or voltage.
• Selection item:: PV transmission: SV transmission: MV transmission
Transmission output high limit• Sets the Transmission output high limit value.
This value correponds to 20 mA DC output or 1 V DC output.
If Transmission output high limit and low limit are set to the same value,
Transmission output low limit will be output.
If SV or MV transmission is selected, 4 mA DC or 0 V DC will be output
when program control stops (in Standby).
• Setting range:
When PV or SV transmission is selected:
Transmission output low limit to Input range high limit
When MV transmission is selected: Transmission output low limit to 105.0%
Transmission output low limit• Sets the Transmission output low limit value.
This value correponds to 4 mA DC output or 0 V DC output.
If Transmission output high limit and low limit are set to the same value,
Transmission output low limit will be output.
If SV or MV transmission is selected, 4 mA DC or 0 V DC will be output
when program control stops (in Standby).
• Setting range:
When PV or SV transmission is selected:
Input range low limit to Transmission output high limit
When MV transmission is selected: -5.0% to Transmission output high limit

At this stage, settings of Transmission output parameter setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 84 -

7.5.6 Communication Parameter Setting GroupIn Communication parameter setting group, the following can be set:Communication protocol, Instrument number, Communication speed, Response delay time, etc.
Setting items in the Communication parameter setting group are shown below.
Available when Serial communication (C or C5 option) are ordered.
Character,
Factory Default

Setting Item, Function, Setting Range
Communication protocol• Selects communication protocol.
• Selection item:: Shinko protocol: MODBUS ASCII: MODBUS RTU: SV digital transmission
Instrument number• Sets the instrument number.
The instrument numbers should be set one by one when multiple
instruments are connected in Serial communication, otherwise
communication is impossible.
• Setting range:
0 to 95
Communication speed• Selects a communication speed equal to that of the host computer.
• Selection item:: 9600 bps: 19200 bps: 38400 bps
Data bit/Parity• Selects data bit and parity, in accordance with the data bit and parity of thehost computer.
• Selection item:: 8 bits/No parity: 7 bits/No parity: 8 bits/Even: 7 bits/Even: 8 bits/Odd: 7 bits/Odd
Stop bit• Selects the stop bit, in accordance with the stop bit of the host computer.
• Selection item:: 1 bit: 2 bits- 85 -

Character,
Factory Default

Setting Item, Function, Setting Range
Response delay time
• Response from the controller can be delayed after receiving command fromthe host computer.
If Response delay time is changed via software communication, the changed
delay time will be reflected from that response data.
• Setting range:
0 to 1000 ms

At this stage, settings of Communication parameter setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 86 -

7.5.7 Other Parameters Setting GroupIn Other parameters setting group, the following can be set:Set value lock, Program start Auto/Manual, Program control start type, Power restore action, etc.
Setting items in the Other parameters setting group are shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Set value lock• Selects either Unlock or Lock.
• Selection item:: Unlock: Lock (None of the set values – except Set value lock – can bechanged.)
Program start Auto/Manual• Selects Program start Auto/Manual when power is turned ON.
• Selection item:: Manual start
When power is turned ON, and in Program control Stop (inStandby), and if the
key is pressed, the selected patternnumber program will be performed from Step 0.
: Automatic start
When power is turned ON, the selected pattern number
program will be automatically performed from Step 0.
Step SV when program control starts• Sets SV when program control starts.
• Setting range:
SV low limit to SV high limit
Program control start type
• Selects program control start type.
PV start, PVR start
100

25
Time
1:00
0:45
PV starting point
When program control starts, step SV isadvanced to the PV (25 ), then program
control starts.

(Fig. 7.5.7-1)- 87 -

Character,
Factory Default

Setting Item, Function, Setting Range
SV start
100

Time
1:00
Program control starts.
Program control starts from the step SV which has
been set in [Step SV when program control starts].

(Fig. 7.5.7-2)• Selection item:: PV start
Only when program control starts, the step SV is advanced to
the PV, then program control starts.
: PVR start
When program control starts and in pattern repeating, the step
SV is advanced to the PV, then program control starts.
: SV start
Program control starts from the step SV which has been set in[Step SV when program control starts].
Power restore action• Selects the program status if a power failure occurs mid-program and it isrestored.
• Selection item:: Stops after power is restored.
Stops program control, and returns to Standby status.
: Continues after power is restored.
Continues (Resumes) previous program control after power isrestored.
: Suspends after power is restored.
Suspends (on hold) current program control, and performs
control using the step SV from the point of suspension.
Pressing the
key cancels suspension, and Program
control resumes.

- 88 -

Character,
Factory Default

Setting Item, Function, Setting Range
Step time unit
• Selects the Step time unit.
• Selection item:: Hours:Minutes: Minutes:Seconds
Step time indication• During program control, selects step time indication typewhen the SV/MV/TIME Display is switched to TIME indication.
• Selection item:: Remaining time
Indicates remaining step time.
: Step time
Indicates step time which has been set.
Step SV indication• During program control, selects step SV indication typewhen the SV/MV/TIME Display is switched to SV indication.
• Selection item:: SV corresponding to the step time progress
Updates step SV corresponding to the step time progress.
: Step SV
Indicates the step SV which has been set during program
pattern setting.
Pattern end output time
• Sets Pattern end output time after program control is finished.
If Pattern end output is selected in [Event output EV allocation], patternend output is turned ON after program control is finished, and the
SV/MV/TIME Display flashes.
Setting the time to 0 (zero) seconds causes continuous output, until the
key is pressed for 1 second, or until the power is turned OFF.
By pressing the
key for 1 second, Pattern end output is turned OFF,and the unit returns to Program control Stop (in Standby).
When set to 1 to 10000 seconds: Pattern end output is automatically turned
OFF after Pattern end output time has elapsed, and the unit returns to
Program control Stop (in Standby).
• Setting range:
0 to 10000 seconds- 89 -

Character,
Factory Default

Setting Item, Function, Setting Range
Step SV Hold function when program ends
• When program control ends, selects either ‘Holding’ or ‘Not holding’ of theStep SV Hold function.
If ‘Holding’ is selected, the PTN Display flashes when program control ends,
and control performs using the step SV of the last step.
By pressing the
key for 1 second, the Step SV Hold function iscancelled, and the unit returns to Program control Stop (in Standby).
• How to set program pattern when ‘Holding’ is selected:
Set the last step value (of the program pattern in the Pattern setting group– except step time), to all steps which have not been set yet.
Set the step time to 0:00.
• Selection item:: Not Holding (of Step SV Hold function): Holding (of Step SV Hold function)
Time signal output TS1 / Status (RUN) output• Selects either Time signal output or Status (RUN) output for Time signal
output TS1.
• Selection item:: Time signal output TS1: Status (RUN) output
Available when Time signal output (TS option) is ordered.

Time signal output TS2 / Status (HOLD) output• Selects either Time signal output or Status (HOLD) output for Time signal
output TS2.
• Selection item:: Time signal output TS2: Status (HOLD) output
Available when Time signal output (TS option) is ordered.

Time signal output TS3 / Status (WAIT) output• Selects either Time signal output or Status (WAIT) output for Time signal
output TS3.
• Selection item:: Time signal output TS3: Status (WAIT) output
Available when Time signal output (TS option) is ordered.

Time signal output TS4 / Status (FAST) output• Selects either Time signal output or Status (FAST) output for Time signal
output TS4.
• Selection item:: Time signal output TS4: Status (FAST) output
Available when Time signal output (TS option) is ordered.

- 90 -

Character,
Factory Default

Setting Item, Function, Setting Range
Time signal output TS5 / Status (STOP) output• Selects either Time signal output or Status (STOP) output for Time signal
output TS5.
• Selection item:: Time signal output TS5: Status (STOP) output
Available when Time signal output (TS option) is ordered.

Overshoot suppression Enabled/Disabled• Selects overshoot suppression Enabled/Disabled.
• Selection item:: Disabled: Enabled
Overshoot suppression factor• Sets overshoot suppression factor.
[Overshoot suppression factor]
When overshoot or undershoot occurs at the step change point during
program control, if overshoot suppression factor is set, overshoot orundershoot can be suppressed at the step change point.
If overshoot occurs as 1 , makes the overshoot suppression factor larger.
When it takes time until control is stabilized as 2 , makes the factor smaller.
①
SV

②

Time

(Fig. 7.5.7-3)• Setting range:
0.1 to 10.0
Available when Enabled is selected in [Overshoot suppression Enabled/Disabled].

Output status when input errors occur• Selects output status when input errors (overshoot or undershoot) occur.
• Selection item:: Output OFF: Output ON
Available only for controllers using direct current and voltage inputs, and direct current
output.

Backlight selection• Selects the display to backlight.
• Selection item:: All are backlit.
: PV Display is backlit.

- 91 -

Character,
Factory Default

Setting Item, Function, Setting Range
PV color• Selects PV Display color.
• Selection item:: Green: Red: Orange: When any alarm (EV1 to EV4) is ON: GreenRed
When alarm is OFF: Green
When any alarm (EV1 to EV4) is ON: The PV color turns fromgreen to red continuously according to the alarm.
: When any alarm (EV1 to EV4) is ON: Orange
Red
When alarm is OFF: Orange
When any alarm (EV1 to EV4) is ON: The PV color turns fromorange to red continuously according to the alarm.
: PV color changes continuously.
PV color changes continuously according to the PV color range.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV+PV color range]: Red
PV color
PV color
range
range
Orange

Green

Green

Red

SV
(Fig. 7.5.7-4): PV color changes continuously + Any alarm (EV1 to EV4) is ON:
Red
PV color changes continuously according to the PV color range.
In addition, when any alarm (EV1 to EV4) is ON: PV color turns
red.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV+PV color range]: Red
Any alarm (EV1 to EV4) is ON: Red

OrangePV colorrange

PV color
range

Green

Green

Red
EV2 value(Low limit alarm)

Red
SV(Fig. 7.5.7-5)- 92 -

Red

EV1 value(High limit alarm)Character,
Factory Default

Setting Item, Function, Setting Range
PV color range• Sets PV color range depending on the user setting.
• Setting range:
Thermocouple, RTD input: 0.1 to 200.0 ( )DC voltage, current input: 1 to 2000 (The placement of the decimal point follows
the selection.)
Available when

(PV color changes continuously) or[PV colorchanges continuously + Any alarm (EV1 to EV4) is ON: Red] is selected in [PV color].

Backlight time
• Sets time to backlight.
Sets backlight time from no operation status until backlight is switched off.
When set to 0, the backlight remains ON.
Backlight relights by pressing any key while backlight is OFF.
• Setting range:
0 to 99 minutes
At this stage, settings of Other parameters setting group are complete.
If theandkeys are pressed at the same time, the unit returns to the Engineering setting
group.
By pressing thekey, the unit returns to RUN mode.

- 93 -

7.6 Auto/Manual Control Switch GroupIn Auto/Manual control switch group, Auto/Manual control can be switched.
• To Enter the Auto/Manual control switch group
Press thekey once in RUN mode, and press thekey 5 times. The PV Display indicates, and the unit enters the Auto/Manual control switch group in Group selection mode.
Press thekey in the Auto/Manual control switch group. The PV Display indicates,
and the unit enters ‘Auto/Manual control switch’.
• Explanation of Setting Item
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default.
Right side: Indicates the setting item, explanation of its function, and setting range.

PTN Display

PV Display

Setting item, function, setting range (or selection item)

Auto/Manual control switch• Switches automatic or manual control.
• Selection item:: Automatic control
STEP Display

SV/MV/TIME Display

Setting item in Auto/Manual control switch group is shown below.
Character,
Factory Default

Setting Item, Function, Setting Range
Auto/Manual control switch• Switches automatic or manual control.
If control action is switched from automatic to manual and vice versa,
balanceless-bumpless function works to prevent a sudden change in MV.
When control action is switched to manual control, the MAN and MV
indicators light up, the STEP Display indicates , and the SV/MV/TIME
Display indicates the manual MV.
Manual MV can be set with theorkey.
If control action is switched to automatic control, the SV/MV/TIME Display
shows SV.
• Selection item:: Auto (Automatic control): Manual (Manual control)

At this stage, settings of Auto/Manual control switch group are complete.
If theandkeys are pressed at the same time, the unit returns to Group selection mode.
By pressing thekey, the unit returns to RUN mode.

- 94 -

7.7 Clearing the Setting Data
There are 2 methods in data clearing.
• Program Clearing:
Program pattern data of the selected step and all the following steps within the program pattern will be
removed.
• Data Clearing:
All setting data – except Input type, OUT1 proportional cycle, OUT2 proportional cycle – will be cleared.
Once data is mistakenly cleared, data should be entered again. Cleared data cannot be restored.

Clearing methods are shown below.
• Program Clearing
When program control is stopped (in Standby), and if the
key is pressed for 3 seconds at any
items in Pattern setting group, program pattern data (for current step on the STEP Display and all thefollowing steps) will return to the factory default.
(e.g.)To clear the program pattern data of Pattern 1 Step 3 and all the following steps:
Keep pressing the
key for approx. 3 seconds at any setting items of Pattern 1 Step 3.
All data of Pattern 1 Steps 3 to 15 will be cleared.
All data of Pattern 1 Steps 0 to 2 will not be cleared.
All data of Pattern 0 and Patterns 2 to 15 will not be cleared either.
• Data Clearing
When program control is stopped (in Standby), and if the,andkeys are pressed forapprox. 3 seconds, the PV Display indicates, and all setting values – except Input type,
OUT1 proportional cycle, OUT2 proportional cycle – will return to the factory default. It takes
approximately 30 seconds for data clear.
After data clearing is compete,on the PV Display will disappear, and the unit will return toProgram control Stop (in Standby).

- 95 -

8. Operation
8.1 Performing Program Control
8.1.1 Performing Program Control(1) Before turning the power ON
Check Sections “3. Mounting to the Control Panel (pp.12, 13)” and “4. Wiring (p.14 to 23)” before
turning the power ON.
(2) After turning the power ON
Set necessary items after turning the power ON.
Refer to Sections “5. Outline of Key Operation and Explanation of Groups (pp.24 to 29)”, “6. BasicOperating Procedure after Power ON and Setting Examples (pp.30 to 42)” and “7. Setting Items(pp.43 to 95)”.
(3) Selecting a pattern number to perform
There are 2 methods for selecting a pattern number:
Using thekey, or using Event input
Pattern numbers selected by Event input have priority over pattern numbers selected by thekey.
To select pattern numbers by keypad, make sure all Event inputs are in OFF (Open) status.
• Using the
key
Select a pattern from 0 – 15 in Program control Stop (in Standby) with thekey.

• Using Event input
Select a pattern from 1 – 15, depending on Closed (ON) or Open (OFF) status of any terminal(Event input DI1 to DI4) and the COM terminal.
If Serial communication (C or C5 option) is ordered, only Event input DI1 and DI2 can be used.
Select a pattern from 1 – 3 by means of Closed (ON) or Open (OFF) status of any terminal(Event input DI1 or DI2) and the COM terminal.
To select a pattern from 4 – 15, press thekey.
Level action is used to determine ON or OFF.
When power is turned ON, level action is engaged.
Event Input DI1 to DI4:
Select a performing pattern by closing any one terminal (DI1 to DI4) and the COM terminal.
: Close any one terminal (DI1 – DI4) and the COM terminal.
(e.g.) To select pattern 7 to perform, close ⑪ & ⑮, close ⑫ & ⑮, and close ⑬ & ⑮.
(Table 8.1.1-1)
Pattern
No.
Terminal No.
⑪ DI1

*

1

2

3

4

5

6

⑫ DI2
⑬ DI3
⑭ DI4
* This pattern number is selected via the keypad.
- 96 -

7

8

9

10

11

12

13

14

15

Event Input DI1 and DI2:
Select a performing pattern by closing any one terminal (DI1 or DI2) and the COM terminal.
: Close DI1 or DI2 terminal and the COM terminal.
(e.g.) To select pattern 3 to perform, close ⑪ & ⑮, and close ⑫ & ⑮.
(Table 8.1.1-2)
Pattern
No.
Terminal No.
⑪ DI1

*

1

2

3

⑫ DI2
* This pattern number is selected via the keypad.
(4) Perform Program Control
Automatic or manual start can be selected to perform program control.
Factory default: Manual start
Manual start: When power is turned ON, and in Program control Stop (in Standby) status,
the program pattern selected at (3) performs from Step 0, by pressing the

key.

Automatic start: When power is turned ON, the program pattern selected at (3) is automatically
performed from Step 0.
For Manual start, there are 2 ways to start program control:
Using thekey, or using External operation input.
• Using the
key
Press thekey in Program control Stop (in Standby).
Program control starts.
• Using External operation input
Close terminals 26 (RUN) and 27 (COM) of External operation input.
Program control starts.
Within 0.1 sec

Controller action(RUN) and
Closed (ON)(COM)

(RUN) andOpen (OFF)(COM)

Program control RUN

0.1 sec minimum
Program control performs by detecting signal edge action
from OFF to ON of terminals(RUN) and(COM).

(Fig. 8.1.1-1)- 97 -

[Program control start type]
Program control start type can be selected in [Program control start type].
PV start:
Only when program control starts, step SV and step time are advanced to the PV,then program control starts.
However, if step SV at the time of program control start is higher than the PV (when PV startis initiated), then program control will start from the SV set in [Step SV when program control
starts].

100

25
Time
1:00
0:45
PV start point
When program control starts,
step SV is advanced to PV (25 ).

(Fig. 8.1.1-2)
PVR start:
When program control starts and in pattern repeating, the step SV and step time areadvanced to the PV, then the program control starts.
Action is the same as that of PV start. Refer to (Fig. 8.1.1-2).
SV start:
Program control starts from the SV set in [Step SV when program control starts].

100

Time
1:00
Program control starts.
Program control starts from the SV set in[Step SV when program control starts].

(Fig. 8.1.1-3)- 98 -

[Power Restore Action]
If power fails during program control, the controller can be operated depending on the selection
in [Power restore action].
Progressing time error when power is restored: 1 minute• Stops after power is restored:
After power is restored, stops program control, and returns to Standby mode.
• Continues after power is restored:
After power is restored, continues (Resumes) program control.
• Suspends after power is restored:
After power is restored, suspends (on hold) current program, and performs Fixed value
control using the step SV from the point of suspension.
Pressing the
key cancels suspension, and program control resumes.

- 99 -

[Wait function]
While program control is running, the program does not proceed to the next step
until the deviation between PV and SV enters SV Wait value at the end of step.
The STEP Display flashes while the Wait function is working.
Explanation of Wait function• When program pattern is rising:SV

Wait value 10
T

T

500
490

Time

If PV becomes 490 , the Wait function will be cancelled,
proceeding to the next step.
As PV is not in the range of [SV-Wait value], the unit
is in Wait status, and does not proceed to the next step.
The STEP Display flashes during Wait action.

(Fig. 8.1.1-4)• When program pattern is falling:SV

Wait value 10
T

T

510
500

Time
If PV becomes 510 , the Wait function will be cancelled,
proceeding to the next step.
As PV is not in the range of [SV + Wait value], the unit
is in Wait status, and does not proceed to the next step.
The STEP Display flashes during Wait action.
Program pattern
PV
Program pattern delayed by T due to the Wait function(Fig. 8.1.1-5)• How to cancel the Wait function
Cancel the Wait function by pressing the

or

key.

The Wait function can also be cancelled by External operation input [ADV] or [STOP].

- 100 -

8.1.2 Stopping Program Control
To stop program control, press the• Using thePress thekey, or use External operation input.

key
key for approximately 1 second during program control.

Program control will stop.
• Using External operation input
Close terminals 23 (STOP) and 27 (COM) of External operation input.
Program control will stop.
Within 0.1 sec

Controller action

Program control RUN(STOP) andClosed (ON)(COM)

(STOP) andOpen (OFF)(COM)
0.1 sec minimum
Program control stops by detecting signal edge action from OFF to
ON of terminals(STOP) and(COM).

(Fig. 8.1.2-1)- 101 -

8.1.3 Suspending Program Control (Hold Function)
During program control, progress of current step can be suspended (paused).
Pressing the
key cancels suspension, and program control resumes.
During manual control, suspension cannot be cancelled.
To suspend program control, there are 2 methods:
Using thekey, or using External operation input• Using the
key
Pressing the
key during program control.
Progress of current step is suspended, and then Fixed value control is performed
using the SV from the point of suspension.
The HOLD indicator flashes.
• Using External operation input
Close terminals 24 (HOLD) and 27 (COM) of External operation input.
Progress of current step is suspended, and then Fixed value control is performed
using the SV at the point of suspension.
The HOLD indicator flashes.
Within 0.1 sec

Controller action(HOLD) andClosed (ON)(COM)

(HOLD) andOpen (OFF)(COM)

Program control suspends

Program control RUN

0.1 sec minimum
Program control suspends by detecting signal edge action from
OFF to ON of terminals(HOLD) and(COM).

(Fig. 8.1.3-1)- 102 -

8.1.4 Advancing Program Step (Advance Function)
Interrupts current step while program control is running, and proceeds to the beginning of the next
step.
While the Wait function is working, the Wait function is cancelled, and proceeds to the beginning of
the next step.
To advance program step, there are 2 methods:
Using thekey, or using External operation input• Using thePress thekey
key during program control.

Current step is stopped, and the unit proceeds to the beginning of the next step.
Each time thekey is pressed, the unit proceeds to the next step.
• Using External operation input
Close terminals 25 (ADV) and 27 (COM) of External operation input.
Current step is stopped, and the unit proceeds to the beginning of the next step.
Each time terminals 25 (ADV) and 27 (COM) are open and closed, the unit proceeds to thenext step.
Within 0.1 sec

Controller action(ADV) and
Closed (ON)(COM)

(ADV) andOpen (OFF)(COM)

Program control RUN (Step 0)

Program control RUN (Step 1)

0.1 sec minimum
Program control advances by detecting signal edge action from
OFF to ON of terminals(ADV) and(COM).

(Fig. 8.1.4-1)- 103 -

8.1.5 Returning to Previous Program Step (Return-to-Previous Function)
Stops the current step in program control, and returns to the previous step.
If the elapsed time of the current step is less than 1 minute, the program control returns to thebeginning of the previous step.
If the elapsed time of the current step is longer than 1 minute, the program control returns to thebeginning of the current step.
When this function is executed at Step 0 of starting pattern, this function is disabled, but returns tothe beginning of Step 0.
To return to the previous step, press

andkeys (in that order) together.

Current step stops, and the unit returns to the previous step or the beginning of the current step.

- 104 -

8.1.6 Speeding up Program Step Time (Step Time Speed-up Function)
To make program step time progress faster, press thekey.
While thekey is pressed, the step time progress is made 60 times faster.
If the Wait function is set, this function will be disabled as the Wait function has priority.

- 105 -

8.1.7 Changing Program Step SV and Step Time
When step SV and step time are changed during program control, they will change as follows.
• When changing step SV from 500 to 700
SV
700
500

Changing point
Step number

0

Time
1

2

: Pattern before change: Pattern after change(Fig. 8.1.7-1)• When changing step time from 0:30 to 0:50
SV
0:50
0:30
Changing point

Time
Step number

10: Pattern before change: Pattern after change(Fig. 8.1.7-2)- 106 -

2

8.1.8 Ending Program (Pattern End Function)
If Pattern end output is selected in [Event output EV allocation], Pattern end output is turned ON.
after program control is finished, and the SV/MV/TIME Display flashes
By pressing the
key for approximately 1 second, Pattern end output is turned OFF, and the unit
returns to Program control Stop (in Standby).
If Pattern end output time is set, Pattern end output is automatically turned OFF after Pattern end
output time has expired. And the unit returns to Program control Stop (in Standby).
[Step SV Hold function when program ends]
If ‘Holding’ is selected in [Step SV Hold function when program ends], the PTN Display flashes when
program control ends, and control performs using the step SV of the last step.
By pressing the
key for approximately 1 second, this function will be cancelled, and the unit
returns to Program control Stop (in Standby).
If ‘Holding’ is selected in [Step SV Hold function when program ends] when program control ends,
the PTN Display flashes, and control is performed using the step SV of the last step.
If ‘Not Holding’ is selected in [Step SV Hold function when program ends] while Step SV Hold function
is working, the program will be forced to stop.
If Pattern end output is selected in [Event output EV allocation], Pattern end output is turned ON
after program control is finished, and the SV/MV/TIME Display flashes- 107 -.

8.2 Performing Fixed Value Control
8.2.1 Performing Fixed Value Control
Fixed value control (control action that indicating controllers are performing) is performed using theset step SV.
To perform Fixed value control, set the step time (of the desired step SV) to.
(e.g.) Set the step SV (of Pattern 0, Step 0) to 500 , and set the step time to
Press thekey. Fixed value control is performed at 500 .

.

(1) Before turning the power ON
Check Sections “3. Mounting to the Control Panel (pp.12, 13)” and “4. Wiring (pp.14 to 23)” before
turning the power ON.
(2) After turning the power ON
Set necessary items after turning the power ON.
Refer to Sections “5. Outline of Key Operation and Explanation of Groups (pp.24 to 29)”, “6. BasicOperating Procedure after Power ON and Setting Examples (pp.30 to 42)” and “7. Setting Items(pp.43 to 95)”.
To perform Fixed value control. set the step SV and step time for the desired pattern.
To set the step time, press the
key at 0:00.
will be selected.
Select the PID block number, Alarm block number and Output block number.
During Fixed value control, Time signal block number and Wait block number are disabled.
(3) Selecting a pattern number to perform
There are 2 methods for selecting a pattern number:
Using thekey, or using Event input
Pattern numbers selected by Event input have priority over pattern numbers selected by thekey.
To select pattern numbers by keypad, make sure all Event inputs are in OFF (Open) status.
• Using the
key
Select a pattern from 0 – 15 for which step time is set to(in Standby), using thekey.

at (2) in Program control Stop

• Using Event input
Select a pattern from 1 – 15 for which step time is set toat (2), depending on Closed(ON) or Open (OFF) status of any terminal (DI1 to DI4) and the COM terminal.
If Serial communication (C or C5 option) is ordered, only Event input DI1 and DI2 can be used.
Select a pattern from 1 – 3 for which step time is set toat (2), by means of Closed (ON)or Open (OFF) status of DI1 or DI2 terminal and the COM terminal.
To select a pattern from 4 – 15, press thekey.
Level action is used to determine ON or OFF.
When power is turned ON, level action is engaged.
Event Input DI1 to DI4:
Select a pattern for which step time is set toat (2), by closing any one terminal (DI1 –DI4) and the COM terminal.
: Close any one terminal (from DI1 – DI4) and the COM terminal.
(e.g.) To select Pattern 7 to perform, close ⑪ & ⑮, close ⑫ & ⑮, and close ⑬ & ⑮
respectively.
- 108 -

(Table 8.2.1-1)
Pattern
No.
Terminal No.
⑪ DI1

*

1

2

3

4

5

6

7

8

9

10

11

12

13

14

15

⑫ DI2
⑬ DI3
⑭ DI4
* This pattern number is selected via the keypad.
Event Input DI1 and DI2:
Select a pattern for which step time is set toat (2), by closing DI1 or DI2 terminal
and the COM terminal.
: Close DI1 or DI2 terminal and the COM terminal.
(e.g.) To select Pattern 3 to perform, close ⑪ & ⑮, and close ⑫ & ⑮ respectively.
(Table 8.2.1-2)
PatternNo.
*
1
2
3
Terminal No.
⑪ DI1
⑫ DI2
* This pattern number is selected via the keypad.
(4) Execute Fixed Value Control
There are 2 ways to execute Fixed value control:
Using thekey, or using External operation input
key.
• Using thePress thekey in Program control Stop (in Standby).
The step, for which step time is set toat (2), is held, andFixed value control is performed using step SV.
The RUN indicator flashes during Fixed value control.
• Using External operation input
Close terminals 26 (RUN) and 27 (COM) of External operation input.
The step, for which step time is set toat (2), is held, andFixed value control is performed using step SV.
The RUN indicator flashes during Fixed value control.
Within 0.1 sec

Controller action(RUN) and
Closed (ON)(COM)

(RUN) andOpen (OFF)(COM)

Fixed value control RUN

0.1 sec minimum
Fixed value control performs by detecting signal edge action
from OFF to ON of terminals(RUN) and(COM).

(Fig. 8.2.1-1)- 109 -

8.2.2 Finishing Fixed Value Control
There are 2 ways to finish Fixed value control:
Using thekey, or using External operation input• Using thePress thekey
key for approximately 1 second during Fixed value control.

Fixed value control will stop, and the unit will revert to Program control Stop (in Standby).
• Using External operation input
Close terminals 23 (STOP) and 27 (COM) of External operation input.
Fixed value control will stop, and the unit will revert to Program control Stop (in Standby).
Within 0.1 sec

Controller action(STOP) andClosed (ON)(COM)

(STOP) andOpen (OFF)(COM)

Fixed value control is finished.

Fixed value control RUN

0.1 sec minimum
Fixed value control is finished by detecting signal edge action
from OFF to ON of terminals(STOP) and(COM).

(Fig. 8.2.2-1)- 110 -

8.3 Switching Auto/Manual Control
Auto/Manual control can be selected in [Auto/Manual control switch] in the Auto/Manual control switchgroup.
If control action is switched from automatic to manual and vice versa, balanceless-bumpless function
works to prevent a sudden change in MV.
• When control action is switched from automatic to manual, the MV before switching will become thedefault value for the manual control.
• When control action is switched from manual to automatic, the MV before switching will become thedefault value for the automatic control.

- 111 -

8.3.1 Switching to Manual Control
To switch to Manual control, select “
the
key.

(Manual)” in [Auto/Manual control switch], and press

When control action is switched to manual, the MAN and MV indicators light up, the STEP Display
indicates , and the SV/MV/TIME Display indicates the MV.
To increase or decrease the MV, use theBy pressing theor
key andorkey.
keys at the same time, the MV change is made faster.

MV setting range:
When control action is switched to Manual during Program control Stop (in Standby):[Output block 0 OUT1 low limit] to [Output block 0 OUT1 high limit]
If D option is ordered: – [Output block 0 OUT2 high limit] to [Output block 0 OUT1 high limit][D

option (DR, DS, DA option): Heating/Cooling control output OUT2]When control action is switched to Manual during program control:[OUT1 low limit of running step output block number] to[OUT1 high limit of running step output block number]
If D option is ordered: – [OUT2 high limit of running step output block number] to[OUT1 high limit of running step output block number][D

option (DR, DS, DA option): Heating/Cooling control output OUT2]

Performs Manual control using the increased/decreased MV.
Basic Procedure

Setting Details

Power ON

Power ON

RUN mode

RUN mode [Program control Stop (in Standby)]

Pattern setting group(5 times)
Auto/Manual control switch group

Auto/Manual control
switch group

Auto/Manual control switch

Auto/Manual control switch
Manual control
Manual control
The MAN and MV indicators light, andthe STEP Display indicates .

Manual control

orManual control(e.g.) 30.0%- 112 -

8.3.2 Switching to Automatic Control
To switch to Automatic control, select “and press the
key.

(Automatic)” in [Auto/Manual control switch],

When control action is switched to automatic, the SV/MV/TIME Display shows SV.
Basic Procedure

Setting Details

Manual control

Manual control(e.g.) 30.0%

Pattern setting group(5 times)
Auto/Manual control switch group

Auto/Manual control
switch group

Auto/Manual control switch

Auto/Manual control switch
Automatic control

RUN mode- 113 -

8.4 Switching the SV/MV/TIME Display
To switch the SV/MV/TIME Display, use thekey.
Each time thekey is pressed, the display and indicators change as follows.
[Program control]

The SV indicator lights.

The SV/MV/TIME Display indicates step SV.

The MV indicator lights (OUT1).

The SV/MV/TIME Display indicates OUT1 MV.

The MV indicator flashes (OUT2).

The SV/MV/TIME Display indicates OUT2 MV.
When Heating/Cooling control (DR, DS or DA option)is ordered.

The TIME indicator lights.

The SV/MV/TIME Display indicates step time.

[Fixed value control]

The SV indicator lights.

The SV/MV/TIME Display indicates SV.

The MV indicator lights (OUT1).

The SV/MV/TIME Display indicates OUT1 MV.

The MV indicator flashes (OUT2).

The SV/MV/TIME Display indicates OUT2 MV.
When Heating/Cooling control (DR, DS or DA option)is ordered.

The TIME indicator lights.

The SV/MV/TIME Display indicates- 114 -.

8.5 Performing AT
8.5.1 Notice when Performing AT• Perform the AT during the trial run.
• AT will be disabled if(Lock) is selected in [Set value lock].
• During AT, none of the setting items – except [AT Perform/Cancel] – can be set.
• If AT is cancelled during the process, OUT1 proportional band, Integral time, Derivative time, ARW
and OUT2 proportional band will revert to the values before AT was performed.
AT will be forced to stop if it has not been completed within 4 hours.
OUT1 proportional band, Integral time, Derivative time, ARW and OUT2 proportional band will revert
to the values before AT was performed.
[Notice when performing AT during Program control RUN]
• If AT is performed, AT starts from the AT starting point, and step time does not progress until AT
finishes. After AT finishes, remaining step will be performed.
SV

T
T

T

T

T

Time
AT EndAT Start
T : Time delay due to AT: Program pattern before AT is performed.
: Program pattern after AT is performed.

(Fig. 8.5.1-1)- 115 -

• When(Normal mode) is selected in [AT mode], manually perform AT for every step which
has different PID block number.
• When(Multi mode) is selected in [AT mode], AT is automatically performed at A (a point
where 90% of step progress time has elapsed at each step).
However, when there are same PID block numbers within 1 pattern as shown in (Fig. 8.5.1-2):
PID block 1 is used for steps 0, 1 and 4.
PID block 2 is used for steps 2 and 3.
AT will be performed at steps 0 and 2.
AT will not be performed at steps 1, 3 and 4.
SV

A

A

Step number

0

1

2

3

4

PID block number

1

1

2

2

1

Time

AT starts at “A”.

(Fig. 8.5.1-2)
When AT is performed in Multi mode, the AT indicator lights in AT standby, and flashes while AT
is performing. After AT finishes at each step, the following values are automatically set for the
PID block selected for each step:
OUT1 proportional band, Integral time, Derivative time, ARW, OUT2 proportional band
During Fixed value control, the Multi mode is disabled.

- 116 -

8.5.2 AT Action
In order to set each value of P, I, D and ARW automatically, the AT process should be made to fluctuate
to obtain an optimal value.
For DC voltage, current inputs, the AT process will fluctuate around the SV for conditions of [A], [B] and[C] below.
One of 3 types of fluctuation below is automatically selected depending on the deviation between SV
and PV.
[A] If there is a large difference between the SV and PV as the temperature is rising
When AT bias is set to 20 , AT process will fluctuate at the temperature 20 lower than the SV.
(Abbreviation: Temp.: Temperature)
Temperature 20△

SV

lower than the SV(4)(1) Calculates PID constants.
(2) PID constants calculated(3) Controlled by the PID constants
set by AT.
(4)
Time

AT starting point
(1)

(2)

(3)

(Fig. 8.5.2-1)[B] When the control is stable
The AT process will fluctuate around the SV.

△

SV(1) Calculates PID constants.
(2) PID constants calculated(3) Controlled by the PID constants
set by AT.

Time

AT starting point
(1)

(2)

(3)

(Fig. 8.5.2-2)[C] If there is a large difference between the SV and PV as the temperature is falling
When AT bias is set to 20 , AT process will fluctuate at the temperature 20 higher than the SV.
Temperature 20△

SVhigher than the SV(1) Calculates PID constants.
(2) PID constants calculated(4)(3) Controlled by the PID constants
set by AT.
(4)
Time

AT starting point
(1)

(2)

(3)

(Fig. 8.5.2-3)- 117 -

8.5.3 Performing AT
To perform AT, selectAnd press the
key.

Basic Procedure(AT Perform) in [AT Perform/Cancel] in the AT Perform group.

Setting Details

RUN mode

Program control RUN

Pattern setting group(3 times)
AT Perform group

AT Perform group(Twice)AT Perform/Cancel.

AT Perform/Cancel
AT Perform

RUN mode

RUN mode (AT Perform)
The AT indicator flashes while AT is performing.

- 118 -

9. Action Explanation
9.1 OUT1 Action
Reverse (Heating) action

Direct (Cooling) action

Proportional band

Proportional band

ON

ON

OFF

OFF

Control action

SV

SV
Relay contact
outputNon-contact
voltage output

H④

H④

H④

H④

H④

H④

C⑤

C⑤

C⑤

C⑤

C⑤

C⑤

L⑥

L⑥

L ⑥

L⑥

L⑥

L⑥

+⑤

+⑤

+⑤

+⑤

12 V DC

12/0 V DC

0 V DC

0 V DC

Cycle action is performed
according to deviation.

-⑥

-⑥

-⑥

+⑤

20 mA DC

-⑥

-⑥

+⑤
0/12 V DC-⑥+⑤

12 V DC-⑥

Cycle action is performed
according to deviation.

Cycle action is performed
according to deviation.

+⑤
Direct current
output-⑥

Cycle action is performed
according to deviation.

+⑤+⑤

4 mA DC

4 mA DC

-⑥

-⑥

+⑤
-⑥

+⑤
20 mA DC-⑥

Changes continuously
according to deviation.

Changes continuously
according to deviation.

Indicator (OUT1)
Lit

Unlit

Unlit

: Turns ON (lit) or OFF (unlit).

- 119 -

Lit

9.2 OUT1 ON/OFF Control Action

Control action

Reverse (Heating) action

Direct (Cooling) action

Hysteresis

Hysteresis

ON

ON

OFF

OFF
SV

SV
Relay contact
outputNon-contact
voltage output
Direct current
output

H④

H④

H④

H④

C⑤

C⑤

C⑤

C⑤

L⑥

L⑥

L⑥

L⑥

+⑤

+⑤

+⑤

12 V DC

0 V DC

0 V DC

-⑥

-⑥

-⑥

+⑤
12 V DC

-⑥

+⑤

+⑤

+⑤

+⑤

20 mA DC

4 mA DC

4 mA DC

20 mA DC

-⑥

-⑥

-⑥

-⑥

Indicator (OUT1)
Lit

Unlit

Unlit

: Turns ON (lit) or OFF (unlit).

- 120 -

Lit

9.3 OUT2 (Heating/Cooling Control) Action
Heating P-band (Cooling P-band)
ON
Control action

ON
Cooling action

Heating action

OFF

OFF
SV
Relay contact output(OUT1)

H④

H④

H④

C⑤

C⑤

C⑤

L⑥

L⑥

L⑥

Cycle action is performed
according to deviation.

Non-contact
voltage output(OUT1)+⑤+⑤

12 V DC

12/0 V DC-⑥+⑤
0 V DC-⑥-⑥

Cycle action is performed
according to deviation.

Direct current output(OUT1)+⑤
20 mA DC

-⑥

+⑤

+⑤

4 mA DC

20 to 4 mA DC-⑥-⑥

Changes continuously
according to deviation.

Relay contact output(OUT2)

Non-contact
voltage output(OUT2)

⑦

⑦

⑦

⑧

⑧

⑧

+⑦

+⑦

+⑦

0 V DC-⑧

0/12 V DC-⑧

12 V DC-⑧

Cycle action is performed
according to deviation.

Direct current output(OUT2)+⑦+⑦

4 mA DC

4 to 20 mA DC

-⑧

-⑧

+⑦
20 mA DC-⑧

Changes continuously
according to deviation.

Indicator (OUT1)
Lit

Unlit

Unlit

Lit

Indicator (OUT2): Turns ON (lit) or OFF (unlit).
: Represents Heating control action.
: Represents Cooling control action.

- 121 -

9.4 OUT2 (Heating/Cooling Control) Action (When Setting Dead Band)
Heating P-band

Dead band(Cooling P-band)
ON
Cooling action

ON
Control action

Heating action

OFF

OFF
SV

Relay contact output(OUT1)

H④

H④

H④

C⑤

C⑤

C⑤

L⑥

L⑥

L⑥

Cycle action is performed
according to deviation.

+⑤
Non-contact
voltage output (OUT1)+⑤+⑤

12/0 V DC

12 V DC-⑥-⑥

0 V DC-⑥

Cycle action is performed
according to deviation.

+⑤
Direct current output(OUT1)

20 mA DC

-⑥

+⑤

+⑤

20 to 4 mA DC-⑥

4 mA DC-⑥

Changes continuously
according to deviation.

⑦
Relay contact output(OUT2)

⑧

⑦

⑦

⑧

⑧

Cycle action is performed
according to deviation.

+⑦
0 V DC

Non-contact
voltage output (OUT2)-⑧+⑦
0/12 V DC-⑧+⑦
12 V DC-⑧

Cycle action is performed
according to deviation.

+⑦
4 mA DC

Direct current output(OUT2)-⑧+⑦
4 to 20 mA DC-⑧+⑦
20 mA DC-⑧

Changes continuously
according to deviation.

Indicator (OUT1)
Lit

Unlit

Unlit

Lit

Indicator (OUT2): Turns ON (lit) or OFF (unlit).
: Represents Heating control action.
: Represents Cooling control action.

- 122 -

9.5 OUT2 (Heating/Cooling Control) Action (When Setting Overlap Band)
Heating P-band

Control action

Cooling P-band
Overlap
band

ON
Heating action

ON
Cooling action
OFF

OFF
SV

Relay contact output(OUT1)

H④

H④

H④

C⑤

C⑤

C⑤

L ⑥

L⑥

L ⑥

Cycle action is performed
according to deviation.

+⑤
Non-contact
voltage output (OUT1)

+⑤

+⑤

-⑥

-⑥

12/0 V DC

12 V DC-⑥

0 V DC

Cycle action is performed
according to deviation.

+⑤
Direct current output(OUT1)

20 mA DC

- ⑥

+⑤

+⑤

- ⑥

- ⑥

20 to 4 mA DC

4 mA DC

Changes continuously
according to deviation.

⑦
Relay contact output(OUT2)

⑧

⑦

⑦

⑧

⑧

Cycle action is performed
according to deviation.

+⑦

+⑦

+⑦

-⑧

-⑧

- ⑧

0/12 V DC

0 V DC

Non-contact
voltage output (OUT2)

12 V DC

Cycle action is performed
according to deviation.

+⑦

4 mA DC

Direct current output(OUT2)

- ⑧

+⑦

+⑦

- ⑧

- ⑧

4 to 20 mA DC

Changes continuously
according to deviation.

20 mA DC

Indicator (OUT1)
Lit

Unlit

Unlit

Lit

Indicator (OUT2): Turns ON (lit) or OFF (unlit).
: Represents Heating control action.
: Represents Cooling control action.

- 123 -

9.6 Alarm Action• High limit alarm• High limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value-EV1 value+EV1 value

SV

SV+EV1 value

Alarm output is in standby.

• Low limit alarm• Low limit with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
-EV1 value-EV1 value

SV +EV1 value

SV +EV1 value

Alarm output is in standby.

• High/Low limits alarm• High/Low limits with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueSV

EV1 valueEV1 valueSV

EV1 value

Alarm output is in standby.

• High/Low limit range alarm• High/Low limit range with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

SV EV1 value

SV EV1 value

Alarm output is in standby.

- 124 -

• Process high alarm• Process high with standby alarm

EV1 hysteresis

EV1 hysteresis

ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.
• Process low alarm• Process low with standby alarm
EV1 hysteresis

EV1 hysteresis
ON

ON

OFF

OFF
EV1 valueEV1 value

Alarm output is in standby.

EV1 value and EV1 hysteresis represent EV1 alarm value and EV1 alarm hysteresis respectively.
The same applies to EV2, EV3 and EV4.
EVT1 indicator: Lit when EV1 terminals 9 and 10 are ON, and unlit when they are OFF.
EVT2 indicator: Lit when EV2 terminals 7 and 8 are ON, and unlit when they are OFF.
EVT3 indicator: Lit when EV3 terminals 29 and 30 are ON, and unlit when they are OFF.
EVT4 indicator: Lit when EV4 terminals 28 and 30 are ON, and unlit when they are OFF.
For the alarm types (High limit alarm, High/Low limits alarm, Process high alarm), alarm output isactivated when the indication is overscale, and the standby function is released for the alarms with thestandby function.
For the alarm types (Low limit alarm, High/Low limits alarm, Process low alarm), alarm output isactivated when the indication is underscale, and the standby function is released for the alarms with thestandby function.
When the alarm action De-energized is selected, the output ON/OFF status acts conversely to the alarm
action described above.
(The Event indicators acts the same as the action Energized.)
Event indicators
Event output

Energized

De-energized

Light
ON

Light
OFF

- 125 -

9.7 Pattern End Output
Program control RUN

Pattern end output ON

ON

OFF

Press theProgram control ends

key for approx. 1 sec.

(Pattern end output is cancelled.)

If Pattern end output is selected in [Event output EV allocation], the Pattern end output turns ON.
after program control ends. The SV/MV/TIME Display flashes
By pressing the
key for approximately 1 second, the Pattern end output is turned OFF, andthe unit reverts to Program control Stop (in Standby).
If Pattern end output time is set, the Pattern end output automatically turns OFF after Pattern end
output time has expired, and the unit reverts to Program control Stop (in Standby).

- 126 -

10. Specifications
10.1 Standard Specifications
RatingRated scale

Input
K
J
R
S
B
E
T
N
PLC(W/Re5-26)
Pt100

JPt1004 to 20 mA
0 to 20 mA
0 to 10 mV-10 to 10 mV
0 to 50 mV
0 to 100 mV
0 to 1 V
0 to 5 V
1 to 5 V
0 to 10 V

Input Range-200 to 1370
-328 to 2498
-200.0 to 400.0-328.0 to 752.0-200 to 1000
-328 to 1832
0 to 1760
32 to 3200
0 to 1760
32 to 3200
0 to 1820
32 to 3308
-200 to 800-328 to 1472
-200.0 to 400.0-328.0 to 752.0-200 to 1300
-328 to 2372
0 to 1390
32 to 2534
0 to 2315
32 to 4199
-200.0 to 850.0-328.0 to 1562.0-100.0 to 100.0-148.0 to 212.0-100.0 to 500.0-148.0 to 932.0-200 to 850-328 to 1562
-200.0 to 500.0-328.0 to 932.0-200 to 500-328 to 932-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)-2000 to 10000 (*)(*) Scaling and decimal point place selection are possible.

- 127 -

Resolution
1 ( )0.1 ( )
1 ( )
1 ( )
1 ( )
1 ( )
1 ( )
0.1 ( )
1 ( )
1 ( )
1 ( )
0.1 ( )
0.1 ( )
0.1 ( )1 ( )
0.1 ( )
1 ( )
1
1
1
1
1
1
1
1
1
1

Input
Input

Thermocouple

K, J, R, S, B, E, T, N, PL- , C (W/Re5-26)
External resistance: 100
max.
However, for B input, External resistance: 40

max.

RTD

Pt100, JPt100 3-wire type
Allowable input lead wire resistance: 10
max. per wire
However, Pt100, -100.0 to 100.0 : 5
max. per wire

Direct current

0 to 20 mA DC, 4 to 20 mA DC
Input impedance: 50

DC voltage

Allowable input current: 100 mA max.
0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC,
0 to 1 V DC:
Input impedance: 1 M minimum
Allowable input voltage: 5 V DC max.
Allowable signal source resistance:
2 k max. (0 to 1 V DC)
200
max. (0 to 100 mV DC, 0 to 50 mV DC)
40
max. (-10 to 10 mV DC)
20max. (0 to 10 mV DC)
0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC:
Input impedance: 100 k minimum
Allowable input voltage: 15 V DC max.
Allowable signal source resistance: 100

Event
input
External
operation
input

Input points
Circuit current
when closed
Input points
Circuit current
when closed
Actionmax.

Max. 4 points (When C or C5 option is ordered: 2 points)
Approx. 16 mA
4 points (STOP, HOLD, ADV, RUN)
Approx. 16 mA
Signal edge action
When power is turned ON, level action is engaged.

- 128 -

Output
Control output Relay contact
OUT1
1a 1b
Non-contact
voltage(for SSR drive)
Direct current
Event output
EV1
Event output
EV2
Event output
EV3, EV4

Max. 40 mA (short circuit protected)
4 to 20 mA DC (Resolution: 12000)
Load resistance: Max. 600
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)

Relay contact
1aElectrical life: 100,000 cycles
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)

Relay contact
1aElectrical life: 100,000 cycles
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)

Number of
circuits(TS option)Opencollector
Control output Relay contact
OUT2
1a
option)Electrical life: 100,000 cycles
12 V DC 15%

Relay contact
1aTime signal
output(D

Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)(DR option)

Non-contact
voltage(For SSR drive)

Electrical life: 100,000 cycles
Event output EV3 and EV4 share one common terminal.
8
Capacity: 24 V DC
Max. 50 mA
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
12 V DC 15%
Max. 40 mA (short circuit protected)(DS option)

Direct current(DA option)

Transmission
output(T

Resolution
Outputoption)Outputaccuracy
Response time

4 to 20 mA DC (Resolution: 12000)
Load resistance: Max. 600
12000
TA: 4 to 20 mA DC (Load resistance: Max. 500 )TV: 0 to 1 V DC (Load resistance: Minimum 100 K )Within0.3% of Transmission output span
400 ms + Input sampling period (0%→90%)- 129 -Power supply
Power supply voltage

Power consumption
Circuit insulation
configuration

PCA1 00-

Model
Power supply
Allowable
voltagefluctuation
Approx.16 VA

PCA1 10-100 to 240 V AC, 50/60 Hz
85 to 264 V AC

24 V AC/DC, 50/60 Hz
20 to 28 V AC/DCPower supply

Control output OUT1

Event input(*)

Electrically insulated

Event output EV2(Control output OUT2)

Event output EV1

Event output EV3

Serial communication

Transmission output

Time signal output

Event output EV4

Input

GND

(Fig. 10.1-1)(*) When both OUT1 and OUT2 are a non-contact voltage output or direct current
output type, OUT1 is not electrically insulated from OUT2.

Dielectric strength

Insulation resistance: 10 M minimum, at 500 V DC
Between Power terminal – Ground (GND): 1.5 kV AC for 1 minuteBetween Input terminal – Ground (GND): 1.5 kV AC for 1 minuteBetween Input terminal – Power terminal: 1.5 kV AC for 1 minute

Recommended Environment
0 to 50
Ambient temperature
Ambient humidity
35 to 85 %RH (Non-condensing)Environmental specification RoHS directive compliant- 130 -

Performance
Base
Thermocouple
accuracy

Within 0.2% of each input span 1 digit
However, R, S input, 0 to 200 (32 to 392 ): Within 6 (12 )B input, 0 to 300 (32 to 572 ): Accuracy is not guaranteed.
K, J, E, T, N input, Less than 0 (32 ): Within 0.4% of input span
1 digitWithin 0.1% of each input span 1 digit
Within 0.2% of each input span 1 digit

RTD
Direct current,
DC voltage
1 at 0 to 50
Cold junction compensation Within
accuracy
Effect of ambient temperature Within 50 ppm/ of each input span
Input sampling period
125 ms
0.1% of setting time
Time indication accuracy
Setting accuracy
Time setting accuracy
Setting
Temperature
resolution
Time
General Structure
WeightExternal dimensions
Mounting
Case
Front panel
Drip-proof/Dust-proof
Display
PV Display

SV/MV/TIME
Display

PTN Display

STEP Display

Based on Basic accuracy and Cold junction compensation accuracy.
0.1% of setting time
Thermocouple, RTD input without decimal point: 1 ( )Thermocouple, RTD input with decimal point: 0.1 ( )DC voltage, current input: 1
1 minute or 1 second

Approx. 460 g
96 x 96 x 98.5 mm (W x H x D)
Flush (Applicable panel thickness: 1 to 8 mm)
Flame-resistant resin, Color: Black
Membrane sheet
IP66 for front panel only
Indicates PV in RUN mode.
Indicates setting characters in setting mode.
11-segments LCD display 5-digits Backlight Red/Green/Orange
Character size: 24.0 x 11.0 mm (H x W)
Indicates SV, MV or TIME in RUN mode.
Retains display indication when power is OFF.
Indicates the set values in setting mode.
11-segments LCD display 5-digits Backlight: Green
Character size: 14.0 x 7.0 mm (H x W)
Indicates the pattern number.
Flashes if ‘Holding’ is selected in [Step SV Hold function when programends], when program control ends.
11-segments LCD display 2-digits Backlight: Orange
Character size: 10.0 x 5.0 mm (H x W)
Indicates the step number.
Flashes during Wait action.
during Manual control.
Indicates
11-segments LCD display 2-digits Backlight: Orange
Character size: 10.0 x 5.0 mm (H x W)

- 131 -

Indicator

PV indicator
SV indicator

MV indicator

TIME indicator

PTN indicator
STEP indicator
PROFILE
indicator

Time unit
indicator

Action indicator

Lit when PV is indicated in RUN mode.
Backlight: Red/Green/Orange
Lit when SV is indicated on the SV/MV/TIME Display.
Retains display indication when power is OFF.
Backlight: Green
Lit when OUT1 MV is indicated on the SV/MV/TIME Display.
Flashes when OUT2 MV is indicated on the SV/MV/TIME Display.
Retains display indication when power is OFF.
Backlight: Green
Lit when TIME is indicated on the SV/MV/TIME Display.
Retains display indication when power is OFF.
Backlight: Green
Lit when the pattern number is indicated.
Backlight: Orange
Lit when the step number is indicated.
Backlight: Orange
During program control, the indicator lights up depending on the
program setting as follows.
: Lit when step SV is rising.
: Lit when step SV is constant.
: Lit when step SV is falling.
Unlit when Fixed value control is performing.
Backlight: Green
When the SV/MV/TIME Display indicates TIME, the following is shown
depending on the selection in [Step time unit].
M: Lit when ‘Hours:Minutes’ is selected in [Step time unit].
S: Lit when ‘Minutes:Seconds’ is selected in [Step time unit].
Backlight: Green
Backlight: Orange
OUT1 Lit when control output OUT1 is ON.
For direct current output type, flashes corresponding to the
MV in 125 ms cycles.
OUT2 Lit when control output OUT2 (DR, DS or DA option) is ON.
For direct current output type (DA option), flashes
corresponding to the MV in 125 ms cycles.
Lit when Event output EV1 is ON.
EVT1
Lit when Event output EV2 is ON.
EVT2
Lit when Event output EV3 is ON.
EVT3
Lit when Event output EV4 is ON.
EVT4
Lit when Manual control is performing.
MAN
T/R
AT
LOCK
RUN
HOLD

Lit during Serial communication (C or C5 option)
TX (transmitting) output.
Flashes during AT.
Lit in AT standby when ‘Multi mode’ is selected in [AT mode].
Lit when ‘Lock’ is selected in [Set value lock].
Lit during Program control RUN.
Flashes during Fixed value control.
Flashes during Program control HOLD.

- 132 -

Setting Structure
Function key

RUN key
PATTERN key
UP keyFAST key

ADVANCE key
DOWN key
SET key
RESET key
STOP key
MODE key
DISPLAY key
BACK MODE key
HOLD key
ENTER key
Program Performance
Number of patterns
Number of steps
Number of repetitions
Program time range
Wait value

Control PerformanceControl action
OUT1 proportional band(P)
Integral time (I)Derivative time (D)OUT1 proportional cycle
ARW
OUT1 ON/OFF
hysteresis
OUT1 high limit, low limit

Performs program control.
Cancels HOLD during Program control HOLD.
Selects program pattern number.
Increases the numeric value in setting mode.
During program control, the step time progress ismade 60 times faster.
In setting mode, the numeric value change ismade faster.
During program control, interrupts performing
step, and proceeds to the next step (Advancefunction).
Decreases the numeric value in setting mode.
Moves to setting mode.
Moves to RUN mode.
Stops the program control, or cancels the patternend output.
Switches or selects setting mode.
Switches the indication on the SV/MV/TIME
Display.
Moves back to the previous mode.
During program control, time progress pauses,
and control continues using the SV at the given
time (HOLD function).
Registers the setting data, and moves to the next
setting item.

16 (Linkable)
256 (16 steps/pattern)
0 to 9999 times (Repetitions disabled when set to 0)
0 to 99 hours 59 minutes/step, or 0 to 99 minutes 59 seconds/step(Whenis set: Fixed value control is performed using step SV.)
Thermocouple, RTD input without decimal point: (0 to 100) ( )Thermocouple, RTD input with decimal point:(0.0 to 100.0) ( )DC voltage, current input:(0 to 1000)(The placement of the decimal
point follows the selection.)(The Wait function is disabled when set to 0 or 0.0.)• PID control action (with AT function)• ON/OFF control action (When proportional band is set to 0 or 0.0.)
0 to Input span ( )DC voltage, current input: 0.0 to 1000.0%(ON/OFF control action when set to 0 or 0.0.)
0 to 3600 seconds (Setting the value to 0 disables the function.)
0 to 1800 seconds (Setting the value to 0 disables the function.)
1 to 120 seconds
0 to 100%
0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal
point follows the selection.)
0 to 100% (Direct current output: -5 to 105%)- 133 -

Standard Function
Wait function

Hold function

Advance function
Return-to-previous function

Repetitions and pattern linkfunction

Step time speed-up function

Program clearing

Power restore action

Pattern end function

During program control, the program does not proceed to the next step
until the deviation between PV and SV enters SV Wait value at the endof step.
The STEP Display flashes while the Wait function is working.
During program control, progress of current step can be suspended.
Pressing the
key cancels suspension, and program control
resumes.
During manual control, suspension cannot be cancelled.
Interrupts current step during program control, and proceeds to thebeginning of the next step.
Stops current perfroming step, and returns to the previous program
step. If the elapsed time of the current step is less than 1 minute, theprogram control returns to the beginning of the previous step.
If the elapsed time of the current step is longer than 1 minute, theprogram control returns to the beginning of the current step.
This function is disabled at Step 0 of started pattern, but returns to thebeginning of Step 0.
Patterns 0 to 15 can be linked to the next pattern. Only pattern numbers
in numerical order can be linked. For Pattern 15, Pattern 0 can belinked.
Number of repetitions for Patterns 0 to 15: 0 to 9999 times.
For repetitions of linked pattern, the whole linked pattern will be
repeated as many times as set in “starting pattern number”.
During program control, the step time progress is made 60 times faster
while thekey is pressed.
If the Wait function is set, the Wait function has priority.
When program control is stopped (in Standby), and if the
key ispressed for 3 seconds at any items in Pattern setting group, program
pattern data (for current step on the STEP Display and all the following
steps) will return to the factory default value.
If power fails during program control, the controller can be operated
depending on the selection in [Power restore action].
Stops after power is restored: Stops program control, and returns toStandby mode.
Continues after power is restored: Continues (Resumes) previous
program control after power is restored.
Suspends after power is restored: Suspends (on hold) current program
control, and performs control using the step SV from the point ofsuspension. Pressing the
key cancels suspension, andprogram control resumes.
Progressing time error when power is restored: 1 minute
If Pattern end output is selected in [Event output EV
allocation],
Pattern end output is turned ON after program control is finished, and.
the SV/MV/TIME Display flashes
By pressing the
key for approximately 1 second, Pattern end
output is turned OFF, and the unit returns to Program control Stop (inStandby). If Pattern end output time is set, Pattern end output is
automatically turned OFF after Pattern end output time has expired. The
unit returns to Program control Stop (in Standby).
- 134 -

Event output EV1
Event output EV2

Event outputs EV3, EV4

Alarm action

Set value
ActionAlarm hysteresis

OutputLoop break alarm

Loop break alarm time
Loop break alarm bandOutputEvent input

External operation input

Data clear function

Output turns ON or OFF, depending on Event condition selected in[Event output EV1 allocation].
Output turns ON or OFF, depending on Event condition selected in[Event output EV2 allocation].
Disabled if the D option is ordered.
Output turns ON or OFF, depending on Event condition which is selectedin [Event output EV3 allocation] or [Event output EV4 allocation].
Event output EV3 and EV4 share one common terminal.
High limit alarm, High limit with standby alarm, Low limit alarm, Low limit
with standby alarm, High/Low limits alarm, High/Low limits with standby
alarm, High/Low limit range alarm, High/Low limit range with standby
alarm, Process high alarm, Process high with standby alarm, Process
low alarm, Process low with standby alarm
Alarm Energized/De-energized action are applied to the above alarms,
totaling 24 alarm types. No alarm action can also be selected.
Factory default value: 0
ON/OFF action
0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal
point follows the selection.)
EV output for which Alarm output (001 to 012) is selected in [Event
output EV allocation].
When Loop break alarm is selected in [Event output EV allocation],
detects actuator trouble (heater burnout, heater adhesion) or sensor
burnout.
0 to 200 minutes
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 0 to 1500 (The placement of the decimal
point follows the selection.)
EV output for which Loop break alarm output (014) is selected in[Event output EV allocation].
Select a pattern from 1 – 15 depending on ON (Closed) or OFF (Open)status of any terminal (DI1 to DI4) and the COM terminal.
If Serial communication (C or C5 option) is ordered, only Event input
DI1 and DI2 can be used, and a pattern from 1 – 3 can be selected toperform.
Pattern numbers selected by Event input have priority over patternnumbers selected by thekey.
To select pattern numbers by keypad, make sure all Event inputs are in
OFF (Open) status.
Level action is used to determine ON or OFF.
When power is turned ON, level action is engaged.
By detecting signal edge action from OFF (Open) to ON (Closed),program control can be performed, stopped, held or advanced.
During Manual control, External operation input will be disabled.
Signal edge action is used to determine OFF or ON.
When power is turned ON, level action is engaged.
When program control is stopped (in Standby), and if the,andkeys are pressed for approx. 3 seconds, the PV Display indicates, and all setting values – except Input type, OUT1 proportional
cycle, OUT2 proportional cycle – will return to the default value. It takes
approximately 30 seconds for data clear.
- 135 -

Attached Function
Sensor correction

Set value lockAuto/Manual control
switchShifts the PV when the temperature at the controlling location does notmatch with the temperature at the sensor location. (Effective within the
input rating range regardless of the sensor correction value.)
Correction range: Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of the decimal
point follows the selection.)
Locks all set values – except Set value lock – to prevent setting errors.
Auto/Manual control can be selected in [Auto/Manual control switch] inAuto/Manual control switch group.
If control action is switched from automatic to manual and vice versa,
balanceless-bumpless function works to prevent a sudden change in MV.
When switched to manual control, the MAN and MV indicators light up,
the STEP Display indicates , and the SV/MV/TIME Display indicatesthe MV. To set the MV, use theorkey.
When switched to automatic control, the SV/MV/TIME Display shows SV.
When power is turned ON, automatic control is performed.
MV setting range:
When control action is switched to Manual during Program control Stop(in Standby):[Output block 0 OUT1 low limit] to [Output block 0 OUT1 high limit]
If D option is ordered:– [Output block 0 OUT2 high limit] to [Output block 0 OUT1 high limit]

When control action is switched to Manual during program control:[OUT1 low limit of running step output block number] to[OUT1 high limit of running step output block number]
If D option is ordered: – [OUT2 high limit of running step output blocknumber] to [OUT1 high limit of running step output block number]Power failure countermeasure The setting data is backed up in the non-volatile IC memory.
The CPU is monitored by a watchdog timer, and if an abnormal status
Self-diagnosis
occurs, the controller is switched to warm-up status, turning all outputs
OFF.
This detects the temperature at the connecting terminal between the
Automatic cold junction
thermocouple and the instrument, and always maintains it at the same statustemperature
as if the reference junction location temperature were at 0 (32 ).
compensation
If thermocouple or RTD input is burnt out, the PV display flashes
Burnout (Overscale), and OUT1, OUT2 are turned OFF (OUT1 low limit value fordirect current output). For Manual control, the preset MV is output.
Output Status
Input
OUT1
OUT2
error
Contents, Indication
DirectReverseDirectReverse(Cooling) action (Heating) action (Cooling) action (Heating) action
OverscaleOFF (4 mA) or
OFF (4 mA) or OFF or
OFF or
If PV exceeded indication OUT1 low limit
OUT1 low
OUT2 low
OUT2 low
range high limit:
value
limit value
limit value
limit value
flashes.
Underscale
OFF (4 mA) or
OFF (4 mA) or OFF or
OFF or
If PV has dropped below OUT1 low limit
OUT1 low
OUT2 low
OUT2 lowindication range low limit: value
limit value
limit value
limit value
flashes.
For Manual control, the preset MV is output.
DC input disconnection: If DC voltage or current input is disconnected, the following is
indicated depending on the input.
4 to 20 mA DC, 1 to 5 V DC input: The PV Display flashes.
0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 100 mV DC, 0 to 1 V DC input:
The PV Display flashes.
0 to 20 mA, 0 to 5 V DC, 0 to 10 V DC input:
The PV Display indicates the value corresponding with 0 mA DC or 0 V DC input.
- 136 -

Thermocouple input: [Input range low limit value – 50 (100 )] to[Input range high limit value + 50 (100 )]Indication range,
Control range

Warm-up indication

Consolecommunication

RTD input: [Input range low limit value – Input span x 1%] to[Input range high limit value + 50 (100 )]DC voltage, current input:[Scaling low limit value – Scaling span x 1%] to[Scaling high limit value + Scaling span x 10%]After the power supply to the instrument is turned on, the PV Display
indicates the input type, and the SV Display indicates input range highlimit value (for thermocouple, RTD input) or scaling high limit value (fordirect current and voltage input) for approximately 3 seconds.
By connecting the USB communication cable (CMB-001, soldseparately) to the console connector (*), the following operations can be
conducted from an external computer, using the Console software SWCPCA101M.
Console communication and Serial communication (C or C5 option)cannot be used together.
(1) Reading and setting of step SV, step time, PID and various set values(2) Reading of PV and action status(3) Function change
Communication interface: C-MOS level(*) Connect the USB communication cable (CMB-001) after power is turned OFF.
Never turn the power ON or OFF after connection.

PV color range
Setting

The PV Display color can be selected from 7 types as follows.
Function
PV Color
Green
Constantly Green
Red
Constantly Red
OrangeConstantly Orange
When any alarm
When alarm is OFF: Green(EV1 to EV4) is ON: When any alarm (EV1 to EV4) is ON: The PV color turns from
Green
Red
green to red continuously according to the alarm.
When any alarm
When alarm is OFF: Orange(EV1 to EV4) is ON: When any alarm (EV1 to EV4) is ON: The PV color turns from
OrangeRedorange to red continuously according to the alarm.
PV color changes
PV color changes continuously according to the PV color
continuously.
range.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV+PV color range]: Red

OrangePV colorrange

PV color
range

Green

Green

SV
(Fig. 10.1-2)- 137 -

Red

Setting

Function
PV color changes
continuously + Any
alarm (EV1 to EV4)
is ON: Red

PV Color
PV color changes continuously according to the PV color
range. In addition, when any alarm (EV1 to EV4) is ON: PV
color turns red.
PV color changes continuously according to the PV color
range.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV+PV color range]: Red
Any alarm (EV1 to EV4) is ON: Red

OrangePV colorrange

PV color
range

Green

Green

Red
EV2 value(Low limit alarm)

Red
SV(Fig. 10.1-3)- 138 -

Red

EV1 value(High limit alarm)10.2 Optional Specifications
Serial communication(C or C5 option)

Communication line
Communication method
Communication speed
Synchronization method
Communication protocol

Data bit/Parity

The following operations can be carried out from an external computer.
(1) Reading and setting of the step SV, step time, PID and various set
values(2) Reading of the PV and action status(3) Function change
EIA RS-232C (C option)
EIA RS-485 (C5 option)
Half-duplex communication
9600, 19200, 38400 bps (Selectable by keypad)
Start-stop synchronization
Shinko protocol / MODBUS ASCII / MODBUS RTU / SV digitaltransmission (Selectable by keypad)
Communication converter IF-400 is available for Shinko protocol and
MODBUS protocol.
Data bit: 7 or 8
Parity: Even, Odd, No parity (Selectable by keypad)

Stop bit
Data format

SV digital transmission

PCA1

1 or 2 (Selectable by keypad)
Communication
ShinkoMODBUS ASCIIMODBUS RTU
protocolProtocolStart bit1
1
1
Data bit7
7 or 88
SelectableEven
No parity(No parity, Odd)
(Even, Odd)
ParityEven
Selectable
Selectable
Stop bit1
1 or 2
1 or 2
Selectable
Selectable
If ‘SV digital transmission’ is selected in [Communication protocol],step SV can be digitally transmitted to Shinko indicating controllers
with the communication function (C5 option).
Update cycle: 250 ms
Indicating controllers with communication function (Max. 31 units)

YA (-) ⑬

YA (-)YA (-)YA (-)YB (+) ⑭

YB (+)YB (+)YB (+)

SG

SG

SG

SG ⑮

(Fig. 10.2-1)- 139 -

Time signal output(TS option)

Transmission output(TA, TV option)

Heating/Cooling control
output (DR, DS or DA option)
OUT2 proportional band(P)
Integral time (I)Derivative time (D)OUT2 proportional cycle
Overlap/Dead band

OUT2 ON/OFF
hysteresis
OUT2 high limit,
OUT2 low limit
OUT2 cooling method

Time signal output OFF time and Time signal output ON time are set
within each step time, and outputs them during Program control RUN.
To use the Time signal output function, set the Time signal blocknumber (for which Time signal output OFF time and Time signal output
ON time have been set) for each step.
Select any one number from a maximum of 16 Time signal blocks.
The same number can be selected as many times as desired.
A maximum of 8 points of Time signal output can be used for one step.
Time signal output can be used as a status output.
Time signal output TS1
Status (RUN) output
Time signal output TS2
Status (HOLD) output
Time signal output TS3
Status (WAIT) output
Time signal output TS4
Status (FAST) output
Time signal output TS5
Status (STOP) output
Converting the value (PV, SV or MV transmission) to analog signal
every 125 ms, outputs the value in current or voltage.
If Transmission output high limit and low limit value are the same,
Transmission output low limit value will be output.
If SV or MV transmission is selected, 4 mA or 0 V will be output when
program control stops (in Standby).
Performs Heating/Cooling control.
If the D option is ordered, Event output EV2 will be disabled.
0.0 to 10.0 times (Multiplied value of OUT1 proportional band)(ON/OFF control when set to 0.0)
0 to 3600 seconds (Setting to 0 disables the function.)(Same value as that of OUT1)
0 to 1800 seconds (Setting to 0 disables the function.)(Same value as that of OUT1)
1 to 120 seconds
Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of thedecimal point follows the selection.)
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal
point follows the selection.)
0 to 100% (DA: -5 to 105%)(1) Air cooling: Linear characteristics(2) Oil cooling: 1.5th power of the linear characteristics(3) Water cooling: 2nd power of the linear characteristics- 140 -

11. Troubleshooting
Warning
Turn the power supply to the instrument off before wiring or checking.
Working on or touching the terminal with the power switched on may result in severe injury
or death due to electrical shock.
The instrument must be grounded before turning the power ON.
If any malfunctions occur, refer to the following items after checking that power is being supplied tothe controller.
11.1 Indication
ProblemPossible Cause

The PV Display indicates.

Internal non-volatile IC memoryis defective.

The PV Display flashes.

PV has exceeded the Indication
range and Control range.
Burnout of thermocouple, RTD or
disconnection of DC voltage(0 to 10 mV DC, -10 to 10 mV DC,
0 to 50 mV DC, 0 to 100 mV DC,
0 to 1 V DC)

Check whether the input terminalsof thermocouple, RTD or DC voltage(0 to 10 mV DC, -10 to 10 mV DC,
0 to 50 mV DC, 0 to 100 mV DC,
0 to 1 V DC) are securely mounted
to the instrument input terminals.

- 141 -

SolutionIf the problem is not still solved after
the power is turned OFF and ON
again, contact our agency or us.
Check the input signal source.
Replace each sensor.
How to check whether the sensor
is burnt out[Thermocouple]
If the input terminals of the
instrument are shorted, and if avalue around room temperature isindicated, the instrument is likely to
be operating normally, however, thesensor may be burnt out.
[RTD]
If approx. 100
of resistance isconnected to the input terminals
between A-B of the instrument andbetween B-B is shorted, and if avalue around 0 (32 ) is indicated,
the instrument is likely to be
operating normally, however, thesensor may be burnt out.
[DC voltage (0 to 10 mV DC,-10 to 10 mV DC, 0 to 50 mV DC,
0 to 100 mV DC, 0 to 1 V DC)]If the input terminals of the
instrument are shorted, and a value
corresponding to 0 mV or 0 V isindicated, the instrument is likely to
be operating normally, however, thesignal wire may be disconnected.
Connect the sensor terminals to the
instrument input terminals securely.

ProblemPossible Cause

Solution

The PV Display flashes.

PV has dropped below the
Indication range and Control range.
Check whether input signal wire for
DC voltage (1 to 5 V DC) or direct
current (4 to 20 mA DC) is
disconnected.

Check the input signal source andwiring of input terminals.
How to check whether the input
signal wire is disconnected[DC voltage (1 to 5 V DC)]If the input to the input terminals of
the instrument is 1 V DC and if a
scaling low limit value is indicated,
the instrument is likely to be
operating normally, however, thesignal wire may be disconnected.
[Direct current (4 to 20 mA DC)]If the input to the input terminals of
the instrument is 4 mA DC and if a
scaling low limit value is indicated,
the instrument is likely to be
operating normally, however, thesignal wire may be disconnected.
Connect the input signal wire to theterminals of this instrument securely.

The PV Display keeps
indicating the value set in[Scaling low limit].

Check whether input signal wire for
DC voltage (1 to 5 V DC) or current (4to 20 mA DC) is securely connectedto the instrument input terminals.
Check if polarity of thermocouple orcompensating lead wire is correct.
Check whether codes (A, B, B) of RTD
agree with the instrument terminals.
Check whether the input signal wire
for DC voltage (0 to 5 V DC, 0 to 10
V DC) and direct current (0 to 20
mA DC) is disconnected.

Check whether the input terminals
for DC voltage (0 to 5 V DC, 0 to 10
V DC) or direct current (0 to 20 mADC) are securely connected to the
instrument input terminals.
- 142 -

Wire them correctly.

Check the input signal wires of DC
voltage (0 to 5 V DC, 0 to 10 V DC)
and direct current (0 to 20 mA DC).
How to check whether the input
signal wire is disconnected[DC voltage (0 to 5 V DC, 0 to 10 V DC)]If the input to the input terminal ofthis controller is 1 V DC, and if avalue (converted value from scaling
high, low limit setting) corresponding
to 1 V DC is indicated, the controller
is likely to be operating normally,
however, the input signal wire may
be disconnected.
[Direct current (0 to 20 mA DC)]If the input to the input terminal ofthis controller is 4 mA DC, and if avalue (converted value from scaling
high, low limit setting) corresponding
to 4 mA DC is indicated, thecontroller is likely to be operating
normally, however, the input signal
wire may be disconnected.
Connect the input terminals of DC
voltage and current to the input
terminals of this instrument
securely.

Problem
The indication of PV
Display is irregularor unstable.

11.2 Key Operation
ProblemNone of the set values(Step SV, step time,
OUT1 proportional band,
EV alarm value, etc.)
can be set.
The setting indication
does not change in the
input range, and newvalues are unable to be
set.
A performing patternnumber cannot be
selected by the
key.

Possible Cause
Solution
Select the input type andCheck whether sensor input or
temperature unit ( or ) is correct. temperature unit ( or ) correctly.
Sensor correction value is
Set it to a suitable value.
unsuitable.
Check whether the sensor
Use a sensor with appropriate
specifications are correct.
specifications.
AC leaks into the sensor circuit.
Use an ungrounded type sensor.
There may be equipment that
Keep the instrument clear of any
interferes with or makes noise near
potentially disruptive equipment.
the instrument.

Possible Cause‘Lock’ is selected in [Set value lock].
AT is performing.

Solution
Select ‘Unlock’ in [Set value lock].
Cancel the AT.

SV high or low limit value may be set
at the point where the value does
not change.

Set it to a suitable value.

A pattern number might be selectedby means of Event input.
The pattern number selected via
Event input has priority over apattern number selected by the
key.

Open the COM terminal andany one terminal of Event input (DI1to DI4).

- 143 -

11.3 Control
Problem
Even though program
control is executed, thecontrol is advanced andthe program is finishedsoon.
Step does not progress.

PV does not rise or fall.

The control output OUT1or OUT2 remains in an
ON status.
The control output OUT1or OUT2 remains in an
OFF status.
The step SV Holdfunction does not work.
The step SV Holdfunction does not work
even if ‘Holding’ isselected in [Step SV Holdfunction when programends].

Possible Cause
The step time of the performing
pattern number is set to 0.00.

SolutionSet the step time to a suitable value.

Program control is suspended (Holdfunction).
While program control issuspended, the HOLD indicator
flashes.
The Wait function is working.
If the Wait function is working, the
STEP Display flashes.

Press theSensor is out of order.
Check whether the sensor or control
output terminals are securely
mounted to the instrument input
terminals.
Check whether the wiring of sensor
or control output terminals iscorrect.
OUT1 or OUT2 low limit value is set
to 100% or higher.

key.

Suspension of control will becancelled, and program control will
resume.
Cancel the Wait function bypressing theorkey.
The Wait function will be cancelled,
and program control will continue.
Replace the sensor.
Ensure that the sensor or control
output terminals are mounted to the
instrument input terminals securely.
Wire them correctly.

Set it to a suitable value.

OUT1 or OUT2 high limit value is set
to 0% or less.

Set it to a suitable value.

‘Not holding’ is selected in [Step SV
Hold function when program ends].
There are steps which have notbeen set within the program pattern.

Select ‘Holding’ in [Step SV Holdfunction when program ends].
Set the last step values (of the
program pattern in the Patternsetting group – except step time),
to all steps which have not been set
yet.
Set the step time to 0:00.

- 144 -

12. Character Table
12.1 Group Selection
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates group name characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display and the SV/MV/TIME Display are unlit.
Right side: Indicates the group name.
Character,
Factory Default

Group Name
Pattern setting group
Block setting group
Repetitions and pattern link setting group
AT Perfrom group
Engineering setting group
Auto/Manual control switch group- 145 -

12.2 Pattern Setting Group
Upper left: PTN Display, PV Display
The PTN Display indicates the pattern number to set, and the PV Display indicatessetting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display indicates the step number to set, andthe SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range (or selection item).
Character,
Factory Default

Setting Item, Setting Range
Setting pattern number
0 to 15
Step 0 step SV
SV low limit to SV high limit
Step 0 step time
, 0:00 to 99:59 Time unit follows the selection in [Step time unit].
If thekey is pressed at 0:00,
is set.
Whenis set, Fixed value control is performed using step
SV at Step 0.
Step 0 PID block number
0 to 9
Step 0 Time signal 1 block number
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS1 is selected in [Time signal output TS1/Status (RUN) output].

Step 0 Time signal 2 block number
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS2 is selected in [Time signal output TS2/Status (HOLD) output].

Step 0 Time signal 3 block number
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS3 is selected in [Time signal output TS3/Status (WAIT) output].

Step 0 Time signal 4 block number
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS4 is selected in [Time signal output TS4/Status (FAST) output].

Step 0 Time signal 5 block number
0 to 15
Available when Time signal output (TS option) is ordered, and when Time signal
output TS5 is selected in [Time signal output TS5/Status (STOP) output].

Step 0 Time signal 6 block number
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Time signal 7 block number
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Time signal 8 block number
0 to 15
Available when Time signal output (TS option) is ordered.

Step 0 Wait block number
0 to 9- 146 -

Data

Character,
Factory Default

Setting Item, Setting Range
Step 0 Alarm block number
0 to 9
Step 0 Output block number
0 to 9
Step 1 step SV
SV low limit to SV high limit
Repeat the above settings up to ‘Step 15 Output block number’,in the same way if necessary.
Step 15 Output block number
0 to 9- 147 -

Data

12.3 Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates group name characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display and the SV/MV/TIME Display are unlit.
Right side: Indicates the group name.
Character,
Factory Default

Group Name
PID block setting group
Time signal block setting group (When the TS option is ordered)
Wait block setting group
Alarm block setting group
Output block setting group- 148 -

12.4 PID Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range

Data

Block 0 OUT1 proportional band
Thermocouple, RTD input without decimal point: 0 to input span ( )Thermocouple, RTD input with decimal point: 0.0 to input span ( )DC voltage, current input: 0.0 to 1000.0%
Block 0 integral time
0 to 3600 seconds
Block 0 derivative time
0 to 1800 seconds
Block 0 ARW
0 to 100%
Block 0 OUT2 proportional band
0.0 to 10.0 times (Multiplied value of Block 0 OUT1 proportional band)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Block 1 OUT1 proportional band
Thermocouple, RTD input without decimal point: 0 to input span
Thermocouple, RTD input with decimal point: 0.0 to input span
DC voltage, current input: 0.0 to 1000.0%

( )
( )

Repeat the above settings up to ‘Block 9 OUT2 proportional band’,in the same way if necessary.
Block 9 OUT2 proportional band
0.0 to 10.0 times (Multiplied value of Block 9 OUT1 proportional band)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

- 149 -

12.5 Time Signal Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Block 0 Time signal output OFF time
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Block 0 Time signal output ON time
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Block 1 Time signal output OFF time
00:00 to 99:59 Time unit follows the selection in [Step time unit].
Repeat the above settings up to ‘Block 15 Time signal output ON time’,in the same way if necessary.
Block 15 Time signal output ON time
00:00 to 99:59 Time unit follows the selection in [Step time unit].

- 150 -

Data

12.6 Wait Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Block 0 Wait value
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal
point follows the selection.)
Block 1 Wait value
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal
point follows the selection.)
Repeat the above settings up to ‘Block 9 Wait value’,in the same way if necessary.
Block 9 Wait value
Thermocouple, RTD input without decimal point: 0 to 100 ( )Thermocouple, RTD input with decimal point: 0.0 to 100.0 ( )DC voltage, current input: 0 to 1000 (The placement of the decimal
point follows the selection.)- 151 -

Data

12.7 Alarlm Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Block 0 EV1 alarm value
Type
No alarm action
High limit alarm

Setting Range– (Input span) to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

High limit with standby
alarm
Low limit alarm– (Input span) to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)– (Input span) to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

Low limit with standby
alarm
High/Low limits alarm– (Input span) to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

High/Low limits withstandby alarm
High/Low limit range
alarm
High/Low limit range
with standby alarm
Process high alarm

0 to Input span (*1)

Process high withstandby alarm
Process low alarm

Input range low limit to Input range high limit

Process low withstandby alarm

Input range low limit to Input range high limit(Alarm action will be disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

0 to Input span (*1)
(Alarm action will be disabled when set to 0 or 0.0.)

Input range low limit to Input range high limit
(*2)
(*2)

Input range low limit to Input range high limit
(*2)
(*2)

(*1) For DC voltage, current input, the input span is the same as the scaling span.
(*2) For DC voltage, current input, input range low (or high) limit value is the same as scalinglow (or high) limit value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV1
allocation].

Block 0 EV2 alarm value
Same as that of Block 0 EV1 alarm value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV2
allocation].

Block 0 EV3 alarm value
Same as that of Block 0 EV1 alarm value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV3
allocation].

Block 0 EV4 alarm value
Same as that of Block 0 EV1 alarm value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV4
allocation].

- 152 -

Data

Character,
Factory Default

Setting Item, Setting Range
Block 1 EV1 alarm value
Same as that of Block 0 EV1 alarm value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV1

allocation].

Repeat the above settings up to ‘Block 9 EV4 alarm value’,in the same way if necessary.
Block 9 EV4 alarm value
Same as that of Block 0 EV1 alarm value.

Available when 001 to 012 (Alarm output) is selected in [Event output EV4

allocation].

- 153 -

Data

12.8 Output Block Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Block 0 OUT1 high limit
OUT1 low limit to 100% (For direct current output: OUT1 low limit to105%)
Block 0 OUT1 low limit
0% to OUT1 high limit (For direct current output: -5% to OUT1 highlimit)
Block 0 OUT2 high limit
OUT2 low limit to 100% (For direct current output: OUT2 low limit to105%)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Block 0 OUT2 low limit
0% to OUT2 high limit. (For direct current output: -5% to OUT2 highlimit)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Block 0 OUT1 rate-of-change
0 to 100 %/second
Block 1 OUT1 high limit
OUT1 low limit to 100% (For direct current output: OUT1 low limit to105%)
Repeat the above settings up to ‘Block 9 OUT1 rate-of-change’,in the same way if necessary.
Block 9 OUT1 rate-of-change
0 to 100 %/second- 154 -

Data

12.9 Repetitions and Pattern Link Setting Group
Upper left: PTN Display, PV Display
The PTN Display indicates the setting pattern number, and the PV Display indicatessetting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Repetitions for Pattern 0
0 to 9999 times
Pattern link between pattern 0 and pattern 1: Pattern link Disabled: Pattern link Enabled
Repetitions for Pattern 1
0 to 9999 times
Repeat the above settings up to ‘Pattern link between pattern 15 andpattern 0’, in the same way if necessary.
Pattern link between pattern 15 and pattern 0: Pattern link Disabled: Pattern link Enabled- 155 -

Data

12.10 AT Perform Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
AT mode: Normal mode
When AT Perform is selected in [AT Perform/Cancel], AT
starts immediately.
: Multi mode

AT is automatically performed at the point where 90% of
progressed step time has elapsed.
If there are the same PID block numbers in one pattern,
the AT is performed only for the first step.
AT Perform/Cancel: AT Cancel: AT Perform
AT biasThermocouple, RTD input without decimal point: 0 to 50 (0 to 100 )Thermocouple, RTD input with decimal point: 0.0 to 50.0
(0.0 to 100.0 )- 156 -

Data

12.11 Engineering Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates group name characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display and the SV/MV/TIME Display are unlit.
Right side: Indicates the group name.
Character,
Factory Default

Group Name
Input parameter setting group
Output parameter setting group
Event output parameter setting group
SV limit setting group
Transmission output parameter setting group
Communication parameter setting group

Other parameters setting group- 157 -

12.12 Input Parameter Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Input type
: K -200 to 1370
: K -200.0 to 400.0: J -200 to 1000
: R 0 to 1760
: S 0 to 1760
: B 0 to 1820
: E -200 to 800: T -200.0 to 400.0: N -200 to 1300
: PL0 to 1390
: C(W/Re5-26) 0 to 2315
: Pt100 -200.0 to 850.0: JPt100 -200.0 to 500.0: Pt100 -200 to 850: JPt100 -200 to 500: Pt100 -100.0 to 100.0: Pt100 -100.0 to 500.0: K -328 to 2498
: K -328.0 to 752.0: J -328 to 1832
: R 32 to 3200
: S 32 to 3200
: B 32 to 3308
: E -328 to 1472
: T -328.0 to 752.0: N -328 to 2372
: PL32 to 2534
: C(W/Re5-26) 32 to 4199
: Pt100 -328.0 to 1562.0: JPt100 -328.0 to 932.0: Pt100 -328 to 1562
: JPt100 -328 to 932: Pt100 -148.0 to 212.0: Pt100 -148.0 to 932.0: 4 to 20 mA DC -2000 to 10000: 0 to 20 mA DC -2000 to 10000: 0 to 10 mV DC -2000 to 10000: -10 to 10 mV DC -2000 to 10000: 0 to 50 mV DC -2000 to 10000: 0 to 100 mV DC -2000 to 10000- 158 -

Data

Character,
Factory Default

Setting Item, Setting Range: 0 to 1 V DC -2000 to 10000: 0 to 5 V DC -2000 to 10000: 1 to 5 V DC -2000 to 10000: 0 to 10 V DC -2000 to 10000
Scaling high limit
Scaling low limit value to Input range high limit value
Scaling low limit
Input range low limit value to Scaling high limit value
Decimal point place: No decimal point: 1 digit after decimal point: 2 digits after decimal point: 3 digits after decimal point: 4 digits after decimal point
Available for DC voltage and current inputs.

Sensor correction
Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of the decimal
point follows the selection.)

PV filter time constant
0.0 to 100.0 seconds- 159 -

Data

12.13 Output Parameter Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default• Relay contact
output: 30 sec• Non-contact
voltage output:
3 sec

Setting Item, Setting Range
OUT1 proportional cycle
1 to 120 seconds
Available when control output OUT1 is Relay contact output or Non-contact
voltage output.

OUT1 ON/OFF hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)• DR: 30 sec• DS: 3 sec

OUT2 proportional cycle
1 to 120 sec
Available when Heating/Cooling control (DR or DS option) is ordered.

OUT2 cooling method: Air cooling (Linear characteristics): Oil cooling (1.5th power of the linear characteristics): Water cooling (2nd power of the linear characteristics)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

OUT2 ON/OFF hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Overlap/Dead band
Thermocouple, RTD input: -200.0 to 200.0 ( )DC voltage, current input: -2000 to 2000 (The placement of the decimal
point follows the selection.)
Available when Heating/Cooling control (DR, DS or DA option) is ordered.

Direct/Reverse action: Reverse action: Direct action- 160 -

Data

12.14 Event Output Parameter Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Event output EV1 allocation[Event Output Allocation Table]
Selection
Event output
No event
Alarm output, High limit alarm
Alarm output, High limit
with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit
with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits
with standby alarm
Alarm output, High/Low limit range
alarm
Alarm output, High/Low limit range
with standby alarm
Alarm output, Process high alarm
Alarm output, Process highwith standby alarm
Alarm output, Process low alarm
Alarm output, Process low
with standby alarm
Pattern end output
Loop break alarm output
Output during AT

Data

Remarks

Turns ON during AT.

When 001 to 012 (Alarm output) is selected, one alarm can be set to one event
output. When 013 to 015 is selected, each output is common to multiple event
outputs.
EV1 alarm hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV1
allocation].

EV1 alarm delay time
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV1
allocation].

EV1 alarm Energized/De-energized: Energized: De-energized

Available when 001 to 012 (Alarm output) is selected in [Event output EV1
allocation].

- 161 -

Character,
Factory Default

Setting Item, Setting Range
Loop break alarm time
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV1
allocation].

Loop break alarm band
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point
follows the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV1
allocation].

Event output EV2 allocation[Event Output Allocation Table]
Selection
Event Output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit withstandby alarm
Alarm output, Low limit alarm
Alarm output, Low limit withstandby alarm
Alarm output, High/Low limits
alarm
Alarm output, High/Low limits
with standby alarm
Alarm output, High/Low limit range
alarm
Alarm output, High/Low limit range
with standby alarm
Alarm output, Process high alarm
Alarm output, Process high withstandby alarm
Alarm output, Process low alarm
Alarm output, Process low withstandby alarm
Pattern end output
Loop break alarm output
Output during AT
Turns ON during AT.
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event
output. When 013 to 015 is selected, each output is common to multiple event
outputs.

EV2 alarm hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV2
allocation].

EV2 alarm delay time
0 to 10000 seconds

Available when 001 to 012 (Alarm output) is selected in [Event output EV2
allocation].

- 162 -

Data

Character,
Factory Default

Setting Item, Setting Range
EV2 alarm Energized/De-energized: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV2
allocation].

Loop break alarm time
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV2
allocation].

Loop break alarm band
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point
follows the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV2
allocation].

Event output EV3 allocation[Event Output Allocation Table]
Selection
Event output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit
with standby alarm
Alarm output, Low limit alarm
Alarm output, Low limit
with standby alarm
Alarm output, High/Low limits alarm
Alarm output, High/Low limits
with standby alarm
Alarm output, High/Low limit range
alarm
Alarm output, High/Low limit range
with standby alarm
Alarm output, Process high alarm
Alarm output, Process high withstandby alarm
Alarm output, Process low alarm
Alarm output, Process low
with standby alarm
Pattern end output
Loop break alarm output
Output during AT
Turns ON during AT.
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event
output.
When 013 to 015 is selected, each output is common to multiple event outputs.

EV3 alarm hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV3
allocation].

- 163 -

Data

Character,
Factory Default

Setting Item, Setting Range
EV3 alarm delay time
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV3
allocation]

EV3 alarm Energized/De-energized: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV3
allocation].

Loop break alarm time
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV3
allocation].

Loop break alarm band
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point
follows the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV3
allocation].

Event output EV4 allocation[Event Output Allocation Table]
Selection
Event output
Remarks
No event
Alarm output, High limit alarm
Alarm output, High limit withstandby alarm
Alarm output, Low limit alarm
Alarm output, Low limit withstandby alarm
Alarm output, High/Low limits
alarm
Alarm output, High/Low limits
with standby alarm
Alarm output, High/Low limit range
alarm
Alarm output, High/Low limit range
with standby alarm
Alarm output, Process high alarm
Alarm output, Process high withstandby alarm
Alarm output, Process low alarm
Alarm output, Process low withstandby alarm
Pattern end output
Loop break alarm output
Output during AT
Turns ON during AT.
When 001 to 012 (Alarm output) is selected, one alarm can be set to one event
output.
When 013 to 015 is selected, each output is common to multiple event outputs.

- 164 -

Data

Character,
Factory Default

Setting Item, Setting Range
EV4 alarm hysteresis
Thermocouple, RTD input: 0.1 to 1000.0 ( )DC voltage, current input: 1 to 10000 (The placement of the decimal point
follows the selection.)
Available when 001 to 012 (Alarm output) is selected in [Event output EV4
allocation].

EV4 alarm delay time
0 to 10000 seconds
Available when 001 to 012 (Alarm output) is selected in [Event output EV4
allocation].

EV4 alarm Energized/De-energized: Energized: De-energized
Available when 001 to 012 (Alarm output) is selected in [Event output EV4
allocation].

Loop break alarm time
0 to 200 minutes [Setting to 0 (zero) disables the Loop break alarm.]
Available when 014 (Loop break alarm output) is selected in [Event output EV4
allocation].

Loop break alarm band
Thermocouple, RTD input without decimal point: 0 to 150 ( )Thermocouple, RTD input with decimal point: 0.0 to 150.0 ( )DC voltage, current input: 1 to 1500 (The placement of the decimal point
follows the selection.)
Available when 014 (Loop break alarm output) is selected in [Event output EV4
allocation].

- 165 -

Data

12.15 SV Limit Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
SV high limit
SV low limit to Scaling high limit
SV low limit
Scaling low limit to SV high limit- 166 -

Data

12.16 Transmission Output Parameter Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Transmission output type
: PV transmission: SV transmission: MV transmission
Transmission output high limit
When PV or SV transmission is selected:
Transmission output low limit to Input range high limit
When MV transmission is selected in [Transmission output type]:
Transmission output low limit to 105.0%
Transmission output low limit
When PV or SV transmission is selected:
Input range low limit to Transmission output high limit
When MV transmission is selected in [Transmission output type]:-5.0% to Transmission output high limit- 167 -

Data

12.17 Communication Parameter Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Communication protocol: Shinko protocol: MODBUS ASCII: MODBUS RTU: SV digital transmission
Instrument number
0 to 95
Communication speed: 9600 bps: 19200 bps: 38400 bps
Data bit/Parity: 8 bits/No parity: 7 bits/No parity: 8 bits/Even: 7 bits/Even: 8 bits/Odd: 7 bits/Odd
Stop bit: 1 bit: 2 bits
Response delay time
0 to 1000 ms- 168 -

Data

12.18 Other Parameters Setting Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Set value lock
: Unlock: Lock (None of the set values – except Set value lock –can be changed.)
Program start Auto/Manual: Manual start
If thekey is pressed when power is turned on, andin Program control Stop (in Standby), the selected
pattern number program will be performed from Step 0.
: Automatic start
When power is turned on, the selected pattern number
program will be automatically performed from Step 0.
Step SV when program control starts
SV low limit to SV high limit
Program control start type
: PV start
Only when program control starts, the step SV isadvanced to the PV, then program control starts.
: PVR start
When program control starts and in pattern repeating, thestep SV is advanced to the PV, then program control
starts.
: SV start
Program control starts from the step SV which has been
set in [Step SV when program control starts].
Power restore action: Stops after power is restored.
Stops current program control, and returns to Standby.
: Continues after power is restored.
Continues (Resumes) previous program control after
power is restored.
: Suspends after power is restored.
Suspends (on hold) current program control, andperforms control using the step SV from the point ofsuspension.
Pressing the
key cancels suspension, and program
control resumes.

- 169 -

Data

Character,
Factory Default

Setting Item, Setting Range
Step time unit
: Hours:Minutes: Minutes:Seconds
Step time indication: Remaining time
Indicates remaining step time.
: Step time
Indicates step time which has been set.
Step SV indication: SV corresponding to the step time progress
Updates step SV corresponding to the step time progress.
: Step SV
Indicates the step SV which has been set during program
pattern setting.
Pattern end output time
0 to 10000 seconds
Step SV Hold function when program ends
: Not Holding (of Step SV Hold function): Holding (of Step SV Hold function)
Time signal output TS1 / Status (RUN) output: Time signal output TS1: Status (RUN) output
Available when Time signal output (TS option) is ordered.

Time signal output TS2 / Status (HOLD) output: Time signal output TS2: Status (HOLD) output
Available when Time signal output (TS option) is ordered.

Time signal output TS3 / Status (WAIT) output: Time signal output TS3: Status (WAIT) output
Available when Time signal output (TS option) is ordered.

Time signal output TS4 / Status (FAST) output: Time signal output TS4: Status (FAST) output
Available when Time signal output (TS option) is ordered.

Time signal output TS5 / Status (STOP) output: Time signal output TS5: Status (STOP) output
Available when Time signal output (TS option) is ordered.

Overshoot suppression Enabled/Disabled: Disabled: Enabled
Overshoot suppression factor
0.1 to 10.0
Available when ‘Enabled’ is selected in [Overshoot suppression
Enabled/Disabled].

- 170 -

Data

Character,
Factory Default

Setting Item, Setting Range

Data

Output status when input errors occur: Output OFF: Output ON
Available only for controllers using direct current and voltage inputs, and direct
current output.

Backlight selection: All are backlit.
: PV Display is backlit.
PV color: Green: Red: Orange: When any alarm (EV1 to EV4) is ON: GreenRed
When alarm is OFF: Green
When any alarm (EV1 to EV4) is ON: The PV color turns
from green to red continuously according to the alarm.
: When any alarm (EV1 to EV4) is ON: Orange
Red
When alarm is OFF: Orange
When any alarm (EV1 to EV4) is ON: The PV color turns
from orange to red continuously according to the alarm.
: PV color changes continuously.
PV color changes continuously according to the PV color
range.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV + PV color range]: Red: PV color changes continuously + Any alarm (EV1 to EV4)
is ON: Red
PV color changes continuously according to the PV color
range. In addition, when any alarm (EV1 to EV4) is ON:
PV color turns red.
PV is lower than [SV – PV color range]: Orange
PV is within [SV PV color range]: GreenPV is higher than [SV + PV color range]: Red
Any alarm (EV1 to EV4) is ON: Red
PV color range
Thermocouple, RTD input: 0.1 to 200.0 ( )DC voltage, current input: 1 to 2000 (The placement of the decimal point
follows the selection.)
Available when

(PV color changes continuously) or[PVcolor changes continuously + Any alarm (EV1 to EV4) is ON: Red] is selected in[PV color].

Backlight time
0 to 99 minutes- 171 -

12.19 Auto/Manual Control Switch Group
Upper left: PTN Display, PV Display
The PTN Display is unlit, and the PV Display indicates setting item characters.
Lower left: STEP Display, SV/MV/TIME Display
The STEP Display is unlit, and the SV/MV/TIME Display indicates factory default value.
Right side: Indicates the setting item and setting range.
Character,
Factory Default

Setting Item, Setting Range
Auto/Manual control switch: Auto (Automatic control): Manual (Manual control)- 172 -

Data

13. Making Program Pattern Table and Data Table
Before setting program, make a program pattern table and data table.
13.1 Making Program Pattern Table
Please make a copy of the program pattern table (p.177), and follow the procedure below.
(1) Write a block number (Step SV, Step time, PID, Time signal 1 to 8, Wait, Alarm, Output) for
each step from Step 0 in numerical order.
(Even if the same block number is used, write for every step.)(2) Draw a line graph of step SV.
Explanation of Program Pattern Table
Program pattern table consists of Y axis which represents the step SV ( ,represents the step time (Hours:Minutes, Minutes:Seconds).
Step SV is considered to be the SV at the end of the step.
Step time is considered to be the step process time.

), and X axis which• The relation between the step SV and Step time can be explained as follows.
Step 0: The control is performed so that the temperature reaches from 0 to 500 for 30 minutes.
Depending on the selection in [Program control start type], control is performed as follows.
• When SV start is selected: Performs control from the step SV set in [Step SV when
program control starts] so that the temperature reaches 500 .
• When PV start or PVR start is selected: Step SV and time are advanced to PV, andcontrol starts so that the temperature reaches 500 .
Step 1: The control is performed so that SV is maintained at 500 for 1 hour.
Step 2: The control is performed so that SV rises from 500 to 1000 for 40 minutes.
Step 3: The control is performed so that SV is maintained at 1000 for 1 hour.
Step 4: The control is performed so that SV drops from 1000 to 0 for 2 hours.
• PID block includes: OUT1 proportional band, Integral time, Derivative time, ARW, OUT2 proportionalband
10 types of PID block (0 – 9) can be set.
• Time signal 1 to 8 (TS1 – TS8) includes: Time signal output OFF time and Time signal output ONtime.
16 types of Time signal block (0 – 15) can be set for Time signal 1 to 8 (TS1 – TS8) respectively.
For Time signal 1 to 5 (TS1 – TS5), the Time signal output can be used only when Time signal output
is selected in [Time signal output/Status output].
• Wait block includes Wait values.
10 types of Wait block (0 – 9) can be set.
• Alarm block includes: EV1 alarm value, EV2 alarm value, EV3 alarm value, EV4 alarm value
10 types of Alarm block (0 – 9) can be set.
• Output block includes: OUT1 high limit, OUT1 low limit, OUT2 high limit, OUT2 low limit, OUT1
rate-of-change.
10 types of Output block (0 – 9) can be set.

- 173 -

Program Pattern Table Example
Pattern 1
Step number

0

1

2

3

4

Step SV
500
Step time
0:30
PID block number
1
Time signal 1 block number
0ONOFFTime signal 2 block number
2
ON
OFF

500
1:00
1
1

1000
0:40
2
0

1000
1:00
2
1

0
2:00
1
0

2

2

2

2

Time signal 3 block number
ON
OFF

1

2

1

2

0

Time signal 4 block number
ON
OFFTime signal 5 block number
ON
OFF

1

1

1

1

0

0

0

0

0

1

Time signal 6 block number
ON
OFF

1

0

1

0

1

Time signal 7 block number
ON
OFFTime signal 8 block number
ON
OFF

2

0

2

0

2

0

0

0

0

2

Wait block number
Alarm block number
Output block number

1
1
0

0
2
1

1
1
0

0
2
1

0
1
0

1000

500

0

(Fig. 13.1-1)- 174 -

13.2 Making Data Table
Please make a copy of Data Table (p.178), and follow the procedure below.
(1) Write data for blocks in each group, by referring to the Block numbers in the Program pattern table.
(2) For other setting items, write the data in the table if required.
About settings in each block setting group
If program pattern is not set for a step, its block number becomes 0 (zero). We highly recommend thatyou leave the factory default values of Block 0 in each block setting group as they are, and set thevalues from Block 1.
Data Table Example• PID block setting group (*1)
OUT1
Block number
P-band
0
10
1
10
2
10

Integraltime
200 sec
200 sec
200 sec

Derivativetime
50 sec50 sec50 sec• Time signal block setting group (TS option)
Time signal output OFF time
Block number

OUT2
P-band
1.0 times
1.0 times
1.0 times

ARW
50%
50%
50%

Time signal output ON time

(Hours:Minutes)(Hours:Minutes)

0:00
0:20
0:00

0:00
0:30
0:30

0
1
2
• Wait block setting group
Block number
Wait value00 (*2)
1
10
2
5• Alarm block setting group (*3)
EV1 alarm value EV2 alarm value
Block number(Pattern end output) (Process high alarm)012• Output block setting group
OUT1
Block number
high limit
0100% (*5)
1
80%
2
100%
(*1)
(*2)
(*3)
(*4)
(*5)

EV3 alarm value

EV4 alarm value(High limit alarm)(Low limit alarm)

0 (*4)
600
1100

OUT1
low limit
0% (*5)
0%
10%

0

(*4)

5
10

OUT2
high limit
100%
80%
100%

OUT2
low limit
0%
0%
10%

0

(*4)

5
10

OUT1
rate-of change
0 %/sec
10 %/sec
0 %/sec

As PID constants are obtained by performing AT, values in the PID block setting group are factory default value.
As ‘Block 0 Wait value’ is used as Wait Disabled, the Wait value is factory default value.
As EV1 is used as Pattern end output, ‘EV1 alarm value’ setting item does not appear.
As Block 0 EV2, EV3, EV4 alarm values are used as No alarm action, their values are factory default value.
As Block 0 OUT1 high limit and low limit are used as MV setting range for manual control, their values are factory
default value.

- 175 -

• Other setting data
Setting ItemOUT1 proportional cycle
OUT2 proportional cycle
Number of repetitions
Pattern link
Communication protocol
Instrument number
Communication speed
Data bit/Parity
Stop bit
Response delay timeOvershoot suppression factor

Data
15 sec15 sec1Disabled
Shinko protocol
1
38400 bps
7 bits/Even
1 bit
10 ms
1.0

- 176 -

Program Pattern Table
Please make a copy of this table for use.
Pattern number
Step number
0

1

2

3

4

5

6

1000

500

0
Step SV
Step time
PID block numberTime signal 1 block number
ON
OFFTime signal 2 block number
ON
OFFTime signal 3 block number
ON
OFFTime signal 4 block number
ON
OFFTime signal 5 block number
ON
OFFTime signal 6 block number
ON
OFFTime signal 7 block number
ON
OFFTime signal 8 block number
ON
OFF
Wait block number
Alarm block number
Output block number- 177 -

7

8

9

10

11

12

13

14

15

Data Table
Please make a copy of this table for use.
• PID block setting group
OUT1
Integral
Block number
P-band
time
0
sec
1
sec

• Alarm block setting group
EV1 alarm value
Block number
Derivative
time
sec

ARW

sec

%
%

2

sec

sec

%

3

sec

sec

%

4

sec

sec

%

5

sec

sec

%

6

sec

sec

%

7

sec

sec

%

8

sec

sec

%

9

sec

sec

%

• Time signal block setting group (TS option)
Time signal output OFF time
Block number
(

0
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15

:

:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:

)

(

OUT2
P-band:EV3 alarm value

EV4 alarm value

(

(

(

)

)

)

0
1
2
3
4
5
6
7
8
9
• Output block setting group
OUT1
Block number
high limit
0
%
1
%
2
%
3
%
4
%
5
%
6
%
7
%
8
%
9
%

Time signal output ON time()

EV2 alarm value

)

:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:

• Other setting data
Setting item
OUT1 proportional cycle
OUT2 proportional cycle
Number of repetitions
Pattern link
Communication protocol
Instrument number
Communication speed
Data bit/Parity
Stop bit
Response delay timeOvershoot suppression factor• Wait block setting group
Block number
Wait value
0
1
2
3
4
5
6
7
8
9
- 178 -OUT1
low limit
%
%
%
%
%
%
%
%
%
%

OUT2
high limit
%
%
%
%
%
%
%
%
%
%

Data
sec
sec
times

bps

ms

OUT2
OUT1
low limit
rate-of change
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec
%
%/sec

- 179 -*****

Inquiries*****

For any inquiries about this unit, please contact our agency or thevendor where you purchased the unit after checking the following.
[Example]• Model ------------------------------ PCA1R00-410• Option ----------------------------- C, TS, TA• Serial number ------------------- No. 165F05000
In addition to the above, please let us know the details of themalfunction, or discrepancy, and the operating conditions.

SHINKO TECHNOS CO., LTD.
OVERSEAS DIVISION

Head Office : 2-5-1, Senbahigashi, Minoo, Osaka, Japan
http://www.shinko-technos.co.jp/e/
URL:
Tel : +81-72-727-6100
E-mail:overseas@shinko-technos.co.jp
Fax: +81-72-727-7006
No. PCA12E5

2020.01