SPEC SHEET

SGP

Potentiometer Transmitter (1-output)
Features:

SGP (1-input 1-output) converts the signal from a potentiometer (inproportion to valve opening) into isolated DC voltage/current.

Functions:Sensor correction (Input value correction)
Normal/Reverse modeFilter time constantManual mode
Input and output types can be changed.
Output high and low limits

Model: SGP - PM ② - ③ - ④
Model name
Input 1
Output 1
Power supply
OptionINPUT 1

③ Power supply
0

Potentiometer
Resistance 100Ω to 10kΩPM1

100 to 240V AC 50/60Hz
24V AC/DC 50/60Hz
For SGPL (with serial communication function),
only [0: 100 to 240V AC] is selectable.

DC Voltage

DC Current② OUTPUT 1
14 to 20mA (allowable load resistance 750Ω max.)

20 to 20mA (allowable load resistance 750Ω max.)※1

30 to 16mA (allowable load resistance 900Ω max.)※1

4

2 to 10mA (allowable load resistance 1500Ω max.)

50 to 10mA (allowable load resistance 1500Ω max.)※1

A0 to 10mV (allowable load resistance 10kΩ min.)※2

B0 to 100mV (allowable load resistance 100kΩ min.)※2

C0 to 1V (allowable load resistance 1000Ω min.)※2D

0 to 5V (allowable load resistance 5000Ω min.)※2E

1 to 5V (allowable load resistance 5000Ω min.)F

0 to 10V (allowable load resistance 10kΩ min.)※2G-5 to 5V (allowable load resistance 10kΩ min.)④ Option
0No option needed

1

Multi-rotation trimmer

2

Moisture-proof treatment

3

Multi-rotation trimmer + Moisture-proof treatment※1: 0mA or less: Out of base accuracy.
※2: 0V or less: Out of base accuracy.

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

SPEC SHEET
Performance
Base accuracy (at 25℃)
Display accuracy
Temperature coefficient
Response time
Insulation resistanceDielectric strength

General specifications

Input
Input zero adjustment range
Power supply
Power consumption
Operating temperature, humidity
Storage temperature
Material
Mounting method
External dimensions
Weight±0.1% of each input span
Base accuracy ±1 digit± 0.015%/℃ (0 to 10mV output: ±0.02%/℃)
0.5 sec. max. (0→90%)
100MΩ minimum, at 500V DC
2.0kV AC for 1 minuteTotal resistance: 100Ω to 10kΩ, Excitation: 0.5V DC, Minimum span: 50% of total resistance.
0 to 50% of total resistance
Input span adjustment range
50 to 100% of total resistance
100 to 240V AC 50/60Hz
85 to 264V AC
Allowable voltage range
24V AC/DC 50/60Hz
20 to 28V AC/DC
100 to 240 V AC: Approx. 9 VA max. (SGPL: Approx. 10 VA max.)
24 V AC: Approx. 6 VA max.
24 V DC: Approx. 3 W max.
-10 to 55℃ (Non-condensing, No icing), 35 to 85%RH (Non-condensing)-10 to 60℃
Case: Flame-resistant resin, Black color, Panel: Polycarbonate
DIN rail22.5(W) x 89(H) x 70(D)mm (without socket)
Approx. 77g (without socket)

Terminal arrangement

Measurement range
Input code

Measurement range

Resolution

PM-1999 to 9999※1※ Decimal point position change and scaling are possible.

Power supply voltage

PWR ⑬ - ⑭

100 to 240V AC, 24V AC/DC

OUT ⑨ - ⑫

OutputPotentiometer ①-④-⑤

Potentiometer input
Serial communication(For SGPL)

RS-485

Circuit configuration(8P Socket)

SHINKO TECHNOS CO., LTD. Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

20190507