Automatic Water
System Pump
42755 SERIES

FR

Pompe automatiquepour réseau d’eau

DE

Automatikpumpe
für Wasseranlagen

IT

Pompa automatica
dell’impianto idrico

NL

Automatischewatersysteempomp

SE

Automatisk vattensystempump

ES

Bomba para sistema
automático de agua

Automatic Water
System Pump
Purpose of this manual

The purpose of this manual is to provide necessary information for product installation,
operation and maintenance.
CAUTION: Read this manual carefully before installing, using or servicing
this product. Failure to follow the instructions within this manual could resultin explosion, property damage, severe personal injury and/or death.
NOTICE: Save this manual for future reference, and keep it readily available
at the location of the unit.

SafetyWARNING:•The operator must be aware of safety precautions to prevent physicalinjury.
•Operating, installing or maintaining the unit in any way that is notcovered in this manual could cause death, serious personal injury
or damage to the equipment. This includes any modification to
the equipment or use of parts not provided by Xylem. If there is aquestion regarding the intended use of equipment, please contact a
Xylem representative before proceeding.
•
Do not change the service application without the approval of an
authorized Xylem representative.
DANGER: Failure to follow this instruction manual may lead to significant
property damage or may result in serious injury or death.

Safety terminology and symbols
About safety messages
It is extremely important that you read, understand and follow the safety messages andregulations carefully before handling the product. They are published to help preventthese hazards:•
Personal accidents and health problems•
Damage to the product•Product malfunction
Hazard Level: Indication:
DANGERA hazardous situation which, if not avoided, will result in death or serious injury.
WARNINGA hazardous situation which, if not avoided, could result in death or serious injury.
CAUTION
Ahazardous situation which,if not avoided,could result in minor or moderate injury.
NOTICEA potential situation which, if not avoided, could result in undesirable conditions.
A practice not related to personal injury.
Hazard categories
Hazard categories can either fall under hazard levels or let specific symbols replace
the ordinary hazard levels symbols. Electrical hazards are indicated by the following
specific symbols:
ELECTRICAL HAZARD:
These are examples of other categories that can occur. They fall under theordinary hazard levels and may use complementing symbols:•
Crush hazard•
Cutting hazard•
Arc flash hazard

User safety

General safety rules
These are safety rules apply:••••

Always keep work area clean
Pay attention to the risks presented by gas and vapors in the work area.
Avoid all electrical dangers. Pay attention to the risks of electric shock or arc flash
hazards
Always bear in mind the risk of drowning, electrical accidents and burninjuries

Safety equipment
Use safety equipment according to the company regulations. Use this safety equipment
within the work area:•
Hard hat•
Gas mask•
Safety goggles, preferably with side shields•
Hearing protection•
Protective shoes•
First-aid kit•
Protective gloves•
Safety devices
NOTICE: Never operate a unit unless safety devices are installed.

Electrical connections
Electrical connections must be made by certified electricians in compliance withall international, national, state and local regulations. For more information about
requirements, see sections dealing specifically with electrical connections.
2Precautions before work
Observe these safety precautions before you work with the product or are in connection
with the product:•
Provide a suitable barrier around the work area, for example, a guard rail•
Make sure that all safety guards are in place and secure•
Make sure that you have a clear path of retreat•
Make sure that the product cannot roll or fall over and injure people ordamage property•
Make sure that the lifting equipment is in good condition•
Use a lifting harness, a safety line and a breathing device as required•
Allow all system and pump components to cool before you handle them•Make sure that the product has been thoroughly cleaned•
Disconnect and lock out power before you service the pump•
Check the explosion risk before you weld or use electric hand tools

Wash the skin and eyes
Follow these procedures for chemicals or hazardous fluids that have come into
contact with your eyes or skin:
Condition
Chemicals or
hazardous fluids
in eyes
Chemicals or
hazardous fluids
on skinAction1. Hold your eyelids apart forcibly with your fingers
2. Rinse the eyes with eyewash or running water for al least 15 minutes
3. Seek medical attention
1. Remove contaminated clothing
2. Wash the skin with soap and water for a least 1 minute
3. Seek medical attention, if necessary

Environmental safety
The work area
Always keep the station clean
Waste and emissions regulations
Observe these safety regulations regarding waste and emissions:••••

Appropriately dispose of all waste
Handle and dispose of the processed liquid in compliance with applicable
environmental regulations
Clean up all spills in accordance with safety and environmental procedures
Report all environmental emissions to the appropriate authorities
WARNING: Radiation Hazard. Do NOT send the product to Xylem if it has
been exposed to any nuclear radiation

Electrical installation
For electrical installation recycling requirements, consult your local electric utility
Recycling guidelines
Always follow local laws and regulations regarding recycling
WARNING: This pump is designed for use with fresh water and salt water ONLY.
Use with any other hazardous, caustic, or corrosive material could result indamage to the pump and the surrounding environment, possible exposure tohazardous substances and injury.

WARNING: Do not use a pump if it presents some damage suchas burned or broken pressure switch, exposed electric wire
and/or contacts.

C

STOP

3

Installation/Mounting
CAUTION: Not For Continuous Duty, Intermittent Duty Only
CAUTION: Installation Notes: To avoid the risk of fire. Be sure thatthe area where pump is installed is isolated from gas, fuel tanks,electrical wiring looms or flammable substances. Failure to do so
may cause injury or death.
CAUTION: Installation Notes: To avoid the risk of fire. Do not install
this product if visible damaged. If damage exposes electricalcontacts, electrical sparks could ignite fuel fumes. Failure to do so
may cause injury or death.

1: Select pump location. Pump must be installed in a dry, ventilatedarea.
Figure 2.
VerticalVerticalHorizontal
Horizontal

NOTE:DoDo Not Submerge
NOTE:
Submerge

2: Connect fittings suppliedwith the pump to the vessels
plumbing. Use ½” (13mm)
I.D. flexible hose (preferably
braided or reinforced) to
reduce vibration through theplumbing system (Figure 1).
Use hose clamps on the slip on
barb hose connectors.
Important: Install strainer pumpinlet to protect valves fromdebris.
3: Fasten pump to a flat surface. If
mounting vertically; install withpumphead down (Figure 2)
Do not over tighten screws toallow rubber mounts to absorb
vibration.
4: Install inlet (A) and discharge(B) fittings. Firmly push slide
clips (C) forward to lock fittingsin place. – Figure 3

Figure 1.

Figure 3.

Inlet Strainer (A)Discharge (B)Figure 4.

City Water
Inlet

Water
Heater

Water
Tank

Check
Valve
Pumpgard
Strainer
Do Not Plumb Autofill to
Pump Suction Line
4

Autofill Tank Valve,
Plumb to Tank

WARNING
FI R E HA ZA R D
Wiring must comply with applicable electrical standards and include
a properly sized fuse or circuit breaker. Improper wiring can cause afire resulting in injury or death.

CAUTION: Suggested wiring information is given as a reference. For proper
information, please reference ABYC E-11, AC and DC Electrical Systems on
Boats guidelines.

Wire Size Table

Total Wire Length - feet (meters)
Pump
Voltage

0 - 20 ft(0 - 6 m)

20 - 35 ft(6 - 9 m)

35 - 55 ft(9 - 12 m)

12 VDC		
24 VDC		#14 AWG(2.5 mm2)#16 AWG(1.5 mm2)#12 AWG(4 mm2)#14 AWG(2.5 mm2)#10 AWG(6 mm2)#12 AWG(4 mm)CAUTION: Motor case could get hot during extended operation. Prolonged contact with skin
may cause a burn.
WARNING: Electrical connections should be performed by a competent marine electrical technician.
CAUTION: Disconnect power from the system before working on the unit to avoid personal
injury, damage to the surrounding environment and/or damage to the unit.

Electrical Installation
DiagramFigure 5.

Start Up
Figure 6.

Initial
InitialStart
Start Up Up• Fill water tank
• Open all faucets• Turn pump switch “ON”
NOTE: Expect a 5 second delay
for power up.

Demand OffOff
Demand• When water is free of air, turnall faucets off beginning withthe faucet closest to the pump
(Figure 6)

Demand On On
DemandImportant: Do not operate the pump more than 15 minutes continuously.
5Winterizing
CAUTION: Allowing water to freeze in the system may result in damage to thepump and plumbing system. Non-Toxic antifreeze for potable water may be
used with Jabsco pumps. Follow manufacturer’s recommendations. Refer toboat or equipment manufacturer’s instructions for their specific winterizing anddrainage procedures. Do not use automotive antifreeze to winterize potablewater systems . These solutions are highly toxic and may cause serious injury
or death if ingested.
1. Drain the water tank. Open tank drain valve. You may use the pump to drain
the tank by opening all the faucets in the system. Allow the pump to operate
until the tank is empty. Do not operate the pump more than 15 minutes
continuously.
2. Open all faucets and purge the water from the plumbing system. Turn off
power to the pump. Be sure that all the water from the drain lines is drained.
3. Remove quick-connect inlet and outlet fittings from the pump and turn thepump on to pump out remaining water from the pump head. Be sure tohave a catch pan or a rag under the pump to prevent water from spilling
onto the boat. Turn the pump off once the plumbing is empty. Leave thefittings disconnected from the pump until the system is ready to be usedagain. Make a note on your tank filler that the plumbing is not connected.
4. Be sure that all faucets are left open to protect against damage to theplumbing.

Model Reference
Model

Nominal DC Volts

Open Flow
GPM (LPM)

Operating Pressure
PSI (Bar)

Cut-out
Pressure PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Dimensions:

Width – 6 1/8 inches (155.58mm), Height – 4 3/4 inches (120.65mm),
Length – 9 7/8 inches (250.83mm)

Operation
Attribute

12 Volt

24 Volt

Time to reach full speed after faucet opened

5 seconds
or less

5 seconds
or less

Time to shut off after faucet completely closed

5 seconds
or less

5 seconds
or less

Over Voltage Threshold Setting (Unit automatically shuts off / will not run)

16 Volts DC

31 Volts DC

Under Voltage Threshold Setting (Unit automatically shuts off / will not run)

9 Volts DC

18 Volts DC

Under Current Threshold Setting (Unit automatically shuts off / will not run)

2 AMPS

2 AMPS

KEY

Model No.

QTY

2Valve Kit

18911-7030

13Diaphragm Kit

18912-3040

1

4Lower Housing Kit

18915-9002

1

5

Pressure Switch

37121-0010

1

6Service Kit

18920-9043

1

Motor 12V DC

18753-5236

1

Motor 24V DC

18753-5237

1

8Side Clips

30648-1000

1

9

Pump Head Assembly

18914-0030

1

10

Pumpgard™ Strainer (not shown)

46400-9500

1

7

Description

Accessories – Snap-In Port Fittings

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Install to ABYC
H-22, H-23 and E-11
We hereby declare, under our sole responsibility, that our productto which this declaration relates has been designed to comply inaccordance with the following Directives:
Electromagnetic Compatibility Directive 2004/108/EC
Recreational Craft Directive 2003/44/EC
Restriction of Hazardous Substances Directive (RoHS) 2011/65/EU
With the relevant selections of the following Standards:
ISO 8846:1990 / Ignition Protection
6

Pompe automatiquepour réseau d’eau
Le but de ce manuel

Est de fournir les informations nécessaires pour l'installation du produit, son
exploitation et sa maintenance.
ATTENTION: Lisez attentivement ce manuel avant d’installer, utiliser ou
réparer ce produit. Le non-respect des instructions de ce manuel peut
provoquer une explosion, des dommages matériels, des blessures graves et/ou la mort.
AVIS: Conservez ce manuel pour vous y référer ultérieurement, et pour qu'ilsoit facilement disponible à l'emplacement de l'unité.

SÉCURITÉAVERTISSEMENT:•
L'opérateur doit connaître les précautions de sécurité pour éviter les blessures physiques.
•
L'exploitation, l'installation ou l'entretien de l'appareil d'une façon non conforme aux
instructions de ce manuel peut entraîner la mort, des blessures personnelles graves ou
endommager l'équipement. Cela comprend toute modification de l'équipement ou l'utilisationde pièces non fournies par Xylem. Si vous avez une question concernant l'utilisation prévue del’équipement, veuillez contacter un représentant Xylem avant de poursuivre.
•
Ne pas modifier l'application de service sans l'approbation d'un représentant autorisé de Xylem.
DANGER: Le non-respect de ces instructions pourrait provoquer une
explosion, des dommages matériels, des blessures graves et/ou la mort.

TERMINOLOGIE ET SYMBOLES DE SÉCURITÉ
A propos des messages de sécurité: Il est extrêmement important que vous lisiez, compreniez
et suiviez attentivement les messages et règlementations de sécurité avant de manipuler le produit. Ils sontpubliés pour aider à prévenir les risques suivants:•
Accidents personnels et problèmes de santé•Dommages du produit•
Dysfonctionnement du produit
Niveau de risque: Indications:
DANGER
Une situation dangereuse qui, si elle n’est pas évitée, entraînera la mort ou
des blessures
AVERTISSEMENT
Une situation dangereuse qui, si elle n’est pas évitée, pourrait entraîner lamort ou des blessures graves.
ATTENTION
Une situation dangereuse qui, si elle n’est pas évitée, pourrait entraîner desblessures mineures ou modérées.
AVIS
Une situation potentielle qui, si elle n’est pas évitée, peut entraîner desconditions indésirables.
Une pratique non liée à des blessures personnelles.
Catégories de danger
Les catégories de danger peuvent être classées parmi les niveaux de risque ou
des symboles spécifiques remplacent le risque ordinaire symboles de niveaux. Les
risques électriques sont indiqués par les symboles spécifiques suivants:
RISQUE ÉLECTRIQUE
Voici des exemples d'autres catégories qui peuvent se produire. Ils sontclassés parmi les niveaux de risque ordinaires et peuvent utiliser des symboles
complémentaires:
1.
Risque d'écrasement;
2.
Risque de coupe;
3.
Risque d'arc électrique

SÉCURITÉ DE L’UTILISATEUR
Règles générales de sécurité
Ces règles de sécurité s'appliquent:••••

Maintenez toujours la zone de travail propre.
Faites attention aux risques constitués par les gaz et les vapeurs dans la zone
de travail.
Évitez tous les risques électriques. Faites attention aux risques de chocélectrique ou d'arc électrique.
Toujours garder à l'esprit le risque de noyade, d'accidents électriques et debrûlures.

Équipement de sécurité. Utilisez un équipement de sécurité selon les règlements
de l'entreprise. Utilisez cet équipement de sécurité dans la zone de travail:••••CasqueLunettes de sécurité, de préférence avec des protections latérales
Chaussures de protection
Gants de protection

•
•
•
•

Masque à gaz
Protection de l'ouïe
Trousse de premiers soins
Dispositifs de sécurité

AVIS : Ne jamais faire fonctionner la pompe sans que les dispositifs desécurité ne soient installés.
Raccordements électriques
Les connexions électriques doivent être effectuées par des électriciens certifiés enconformité avec toutes les réglementations internationales, nationales, provinciales
et locales. Pour plus d'informations sur les exigences, voir les sections traitant
spécifiquement des branchements électriques.
7Précautions à prendre avant travaux

Respectez ces consignes de sécurité avant de travailler avec le produit ou d'être en
relation avec le produit:
•
•
•
•
•
•
•
•
•
•

Assurez une barrière autour de la zone de travail, par exemple, un rail de garde
Assurez-vous que tous les dispositifs de sécurité sont en place et sécurisés
Assurez-vous que vous avez une issue de secours
Assurez-vous que le produit ne peut pas rouler ou basculer et blesser des personnes ou
endommager des biens
Assurez-vous que l'équipement de levage est en bon étatUtilisez un harnais de levage, une ligne de sécurité et un dispositif de respiration nécessaire
Permettez à tous les composants du système et de la pompe de refroidir avant de les manipuler
Assurez-vous que le produit a été soigneusement nettoyé
Débranchez et verrouillez l’alimentation avant d’intervenir sur la pompe
Vérifiez le risque d’explosion avant de souder ou d’utiliser des outils électriques manuels

Lavez-vous la peau et les yeux Suivez ces procédures pour les produits chimiques
ou des liquides dangereux qui ont été en contact avec les yeux ou la peau:
Condition

Produits chimiques ou
liquides dangereux
dans les yeux
Produits chimiques ou
liquides dangereux surla peau

Action à mener

1. Maintenez les paupières écartées avec les doigts
2. Rincez les yeux avec de l’eau de lavage oculaire ou courante pendant au moins 15 minutes
3. Consulter un médecin
1. Retirez les vêtements contaminés
2. Lavez la peau avec de l’eau et du savon pendant au moins 1 minute
3. Consulter un médecin si nécessaire

SÉCURITÉ DE L’ENVIRONNEMENT
La zone de travail Gardez la station propre
Règlements concernant les déchets et les émissions
Respectez les consignes de sécurité suivantes concernant les déchets et émissions:••••Éliminez tous les déchets de manière appropriée
Manipulez et éliminez le liquide traité conformément aux réglementations
environnementales en vigueur
Nettoyez tous les déversements conformément aux procédures
environnementales et de sécurité
Signalez toute émission environnementale aux autorités compétentes
AVERTISSEMENT: Risque d'irradiation. Ne PAS envoyer le produit à Xylems'il a été exposé à un rayonnement nucléaire.

Installation électrique Pour les besoins de recyclage de l'installation électrique,consultez votre compagnie d'électricité locale.
Directives pour le recyclage
Conformez-vous toujours aux lois et réglementations locales concernant le recyclage.
AVERTISSEMENT : Cette pompe est conçue UNIQUEMENT pour l’eau claire et l’eau salée. L’utilisation
avec toutes autres substances dangereuses, caustiques ou corrosives pourraient endommager la pompe
et le milieu environnant, provoquant potentiellement une exposition aux substances dangereuses, avec
blessures.

AVERTISSEMENT: Ne pas utiliser une pompe en présence decertains dommages, comme un pressostat brûlé ou cassé, un filélectrique et/ou de contact exposés.

C

ARRÊT
STOP

8

Installation/Fixation
MISE EN GARDE: Ne se prête pas à une utilisation continue.Seulement prévu
pour une utilisation intermittente.
CAUTION: Notes d’installation : Pour éviter tout risque d’incendie. Ne pas installer
ce produit s’il présente visiblement des dommages. Si des contacts électriques sont
exposés à cause des dommages, des étincelles électriques peuvent enflammer lesvapeurs de carburant. Le non-respect de ces instructions peut provoquer des blessuresvoire un décès.
1: Sélectionner l’emplacement de la pompe. La pompe doit êtreinstallée dans un endroit sec, bien ventilé.
Figure 2.
VerticaleVerticalHorizontal
Horizontale

N.B. : Do
Ne pasNOTE:
Notsubmerger
Submerge

2 : Connecter les raccords fournis
avec la pompe à la plomberie dubateau. Utiliser un tuyau souple
de diamètre interne 13 mm (depréférence tressé ou renforcé)
afin de réduire les vibrations au
niveau de la plomberie (Figure 1).
Utiliser des colliers de serrage surles connecteurs encliquetables àembout cannelé.
Important : Installer une crépine
d’aspiration pour protéger lesvannes contre les débris.
3 : Fixer la pompe sur une surface
plane. En cas d’installation
verticale, procéder à l’installation
avec la tête de pompe orientéevers le bas (Figure 2). Ne pas
trop serrer les vis pour permettreaux montants en caoutchoucd’absorber les vibrations.
4 : Installer les embouts d’arrivée(A) et de sortie (B). Pousser
fermement les clips coulissants(C) vers l’avant pour bloquer lesembouts. – Figure 3

Figure 1.

Figure 3.

Crépined’aspiration (A)Évacuation (B)Figure 4.

Réservoird’eau

Arrivée
d’eau de ville

Chauffe-eau

Clapetanti-retour
Ne pas raccorder
l’arrivée duremplissage
automatique au tuyau
d’aspiration

CrépinePumpgard
Vanne du réservoir de remplissage
automatique, raccorder au réservoir

9

AVERTISSEMENTDANGER D’INCENDIE
Le câblage doit respecter les normes électriques en vigueur et com­prendre
un fusible ou un disjoncteur de taille adéquate. Tout câblage fautif pourrait
occasionner un incendie entraînant blessure ou mort.
MISE EN GARDE: Les informations de câblage recommandé sontfournies à titre de référence. Pour des informations exactes, consulter
les directives « ABYC E-11, AC et DC Electrical Systems on Boats ».

Tableau de données électriques
Longueur totale de fil – pieds (mètres)
Tensionde pompe0 - 20 pieds(0 - 6 m)

12 VDC		
24 VDC		#14 AWG(2,5 mm2)#16 AWG(1,5 mm2)

20 - 35 pieds 35 - 55 pieds(6 - 9 m)(9 - 12 m)#12 AWG(4 mm2)#14 AWG(2,5 mm2)#10 AWG(6 mm2)#12 AWG(4 mm)MISE EN GARDE: Le boîtier du moteur peut chauffer s’il fonctionne
pendant de longues périodes. Un contact prolongé avec le boîtier
peut donc entraîner des brûlures.
AVERTISSEMENT: Les branchements électriques doivent êtreréalisés par un électricien de marine compétent.
ATTENTION: Coupez l’alimentation du système avant tout travail
sur l’unité pour éviter les blessures, les dommages du milieu
environnant et/ou de l’unité.

Figure 5.

porte-fusible
fil de terre vert

OU

Gris
fusibleRouge (+)

disjoncteur
Noir (-)

batterie de 12 V

Démarrez vers le haut
Figure 6.

Initial Start
Up
Démarrage
initial• Remplir le réservoird’eau• Ouvrir tous lesrobinets• Mettrel’interrupteur de lapompe sur « ON »DemandOff
DemandeFermé

N.B. : S’attendre à un
délai de 5 secondes
avant le démarrage.

DemandOn
DemandeOuvert• Lorsque aucune
bulle d’air nes’échappe plus
des canalisations,
fermer tous
les robinets encommençant parcelui situé le plus
près de la pompe(Figure 6)

Important : Ne pas laisser la pompe tourner plus de 15 minutes de suite.
10

Hivérisation
MISE EN GARDE: Si de l’eau restant dans le système gèle, la pompe et la plomberie
pourraient être endommagées. Il est possible d’utiliser un antigel pour eau
potable non toxique dans les pompes Jabsco. Suivre les recommandations dufabricant. Se reporter aux instructions du fabricant du bateau ou de l’équipement
pour connaître les procédures d’hivérisation et d’évacuation de l’eau spécifiques.
Ne pas utiliser d’antigel automobile pour procéder à l’hivérisation de systèmesd’alimentation en eau potable car ces solutions sont extrêmement toxiques etpourraient entraîner blessures ou mort en cas d’ingestion.
1. Assécher le réservoir d’eau. Ouvrir la vanne de vidange. Il est possible
d’utiliser la pompe pour vider le réservoir en ouvrant tous les robinets dusystème. Laisser la pompe fonctionner jusqu’à ce que le réservoir soit vide. Ne
pas laisser la pompe tourner plus de 15 minutes de suite.
2. Ouvrir tous les robinets et laisser l’eau s’égoutter des canalisations. Mettrela pompe hors tension. Veiller à ce que toute l’eau soit bien évacuée descanalisations.
3. Déconnecter les raccords à assemblage rapide d’arrivée et de sortie de lapompe et mettre la pompe en marche pour évacuer l’eau restant dans latête de pompe. Veiller à placer un récipient ou un chiffon sous la pompe afind’éviter tout déversement d’eau dans le bateau. Une fois les canalisations
vidées, éteindre la pompe. Laisser tous les raccords déconnectés de lapompe jusqu’à ce que le système soit de nouveau prêt à être utilisé. Indiquer
sur le réservoir que les canalisations ne sont pas connectées.
4. Veiller à ce que tous les robinets soient laissés ouverts afin de ne pas
endommager la plomberie.

Le code du modèle du fabricant
ModèleVolts nominauxde C.C

Ouvrezl’écoulement
GPM (LPM)

Pression defonctionnement
PSI (Bar)

Pression decoupe-circuit
PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Dimensions: Largeur – 6 1/8 pouces (155.58mm), Hauteur – 4 3/4 pouces (120.65mm),
Llongueur – 9 7/8 pouces (250.83mm)
Fonctionnement
Attribut
Heure d’atteindre à toute vitesse après le robinet ouvert
Heure de couper après le robinet complètement fermé
Au-dessus de la configuration de seuil de tension (l’unité a automatiquement coupé/ne fonctionnera pas)
Sous la configuration de seuil de tension (l’unité a automatiquement
coupé/ne fonctionnera pas)
Sous la configuration actuelle de seuil (l’unité a automatiquement coupé/
ne fonctionnera pas)

Clé

12 Volt

24 Volt

5 secondes
ou moins
5 secondes
ou moins

5 secondes
ou moins
5 secondes
ou moins

16 Volts DC

31 Volts DC

9 Volts DC

18 Volts DC

2 AMPS

2 AMPS

Model No.

Qté

2

Kit de valve

18911-7030

1

3

Kit de membrane

18912-3040

14Abaissez le kit de logement

18915-9002

1

5

Mano-contact

37121-0010

1

6

Entretenez le kit

18920-9043

1Moteur - 12V DC

18753-5236

1Moteur - 24V DC

18753-5237

1

8

Clips latéraux

30648-1000

19Assemblée principale de pompe

18914-0030

1

10

Tamis de Pumpgard™ (non affiché)

46400-9500

1

7

Description

Accessoires

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Installez sur ABYC

H-22, H-23 et E-11

Nous déclarons par la présente que, sous notre entière responsabilité,
le produit auquel cette déclaration se rapporte a été conçu pour êtreconforme aux dispositions des Directives suivantes :Directive 2004/108/CE relative à la compatibilité électromagnétique
Directive 2003/44/CE relative aux bateaux de plaisanceDirective 2011/65/UE relative à la limitation de l’utilisation de certaines
substances dangereuses dans les équipements électriques et électroniqueAvec les parties appropriées des normes suivantes :ISO 8846:1990 / Protection contre l’inflammation
11

Automatikpumpe
für Wasseranlagen
Diese Anleitung soll die

Notwendigen Informationen für Montage, Bedienung und Wartung der Pumpe
bereitstellen.
GEFAHR: Lesen Sie sich diese Anleitung sorgfältig durch, bevor Sie die Pumpe installieren,
benutzen, warten oder reparieren. Das Nichtbeachten der Anweisungen in dieser Anleitung kann zu
Explosionen, Sachschäden, schweren Verletzungen und/oder Todesfällen führen.
HINWEIS: Bewahren Sie diese Anleitung zum Nachschlagen auf und halten Sie sie stets
griffbereit am Standort der Anlage verfügbar.

SICHERHEITWARNUNG:•
Der Betreiber muss die Sicherheitsvorschriften kennen, um Verletzungen zu vermeiden. Wird das
Gerät anders als in dieser Anleitung beschrieben bedient, installiert oder gewartet, kann dies zu
Todesfällen, schweren Personenschäden oder Schäden an der Pumpe führen.
•
Dies schließt jedwede Veränderung an der Pumpe sowie die Verwendung von nicht von Xylemgelieferten Ersatzteilen ein. Sollten Sie Fragen bezüglich der angestrebten Verwendung der
Pumpe haben, wenden Sie sich vorher bitte an einen Vertreter von Xylem.
•
Setzen Sie ohne Genehmigung durch einen autorisierten Xylem-Vertreter die Pumpe nicht anders
als in der Dokumentation beschrieben ein.
GEFAHR: Das Nichtbeachten der Anweisungen kann zu Explosionen, Sachschäden, schweren
Verletzungen und/oder Todesfällen führen.

SICHERHEIT - BEGRIFFE UND SYMBOLE
Zu den Sicherheitsmeldungen
Es ist überaus wichtig, dass Sie die Sicherheitsmeldungen und -vorschriften lesen, verstehen und beachten, bevor Sie
die Pumpe handhaben. Ihre Veröffentlichung soll folgenden Gefahren vorbeugen:•Unfällen und Gesundheitsproblemen•
Beschädigungen der Pumpe•
Fehlfunktionen der Pumpe
Gefahrenstufe:
GEFAHRWARNUNGVORSICHTHINWEIS

Erklärung:
Eine Gefährdung, die schwere oder tödliche Verletzungen zur Folge hat, wenn sie nicht
vermieden wird.
Eine Gefährdung, die schwere oder tödliche Verletzungen zur Folge haben könnte,
wenn sie nicht vermieden wird.
Eine Gefährdung, die leichte oder mittelschwere Verletzungen zur Folge haben könnte,
wenn sie nicht vermieden wird.
Eine mögliche Gefährdung, die ungewollte Zustände zur Folge haben könnte, wenn sie
nicht vermieden wird
Ein Gebrauch, der keine Verletzungsgefahr beinhaltet

Gefahrenkategorien. Gefahrenkategorien können Gefahrenstufen zugeordnet sein oder durchbesondere Symbole die üblichen Symbole der Gefahrenstufen ersetzen. Gefahren durch elektrischen Stromwerden durch folgende Symbole angezeigt:GEFÄHRLICHE ELEKTRISCHE SPANNUNG
Sie sind Beispiele für weitere mögliche Gefahrenkategorien. Sie fallen unter die üblichen
Gefahrenstufen und können durch ergänzende Symbole angezeigt werden:•
Quetschgefahr•
Schnittgefahr•
Lichtbogengefahr

BEDIENERSICHERHEIT
Allgemeine SicherheitsanweisungenDiese Sicherheitsregeln beinhalten:••••

Sauberhalten des Arbeitsbereiches
Beachtung der Gefahren durch Gas und Dämpfe im Arbeitsbereich.
Vermeidung aller elektrischen Gefahren. Beachten Sie die Gefahr von Stromschlägen und
Lichtbögen
Denken Sie stets an die Gefahr des Ertrinkens, eines Stromunfalls oder einer Verbrennung

Sicherheitsausrüstung. Verwenden Sie die in Ihrem Betrieb vorgeschriebene Sicherheitsausrüstung.
Verwenden Sie im Arbeitsbereich die folgende Sicherheitsausrüstung:••••

Schutzhelm
Schutzbrille, vorzugsweise mit Seitenschutz
Sicherheitsschuhe
Schutzhandschuhe

•
•
•
•

Gasmaske
Gehörschutz
Erste-Hilfe-Kasten
Schutzvorrichtungen

HINWEIS: Bedienen Sie niemals eine Pumpe ohne installierte Schutzvorrichtungen!
Elektroanschlüsse
Die Elektroanschlüsse müssen von geprüften Elektroinstallateuren gemäßinternationalen, nationalen, bundesstaatlichen und lokalen Vorschriften gelegt
werden. Weitere Informationen über die Anforderungen finden Sie in den
Abschnitten über die elektrischen Anschlüsse.
12

Sicherheitsvorkehrungen vor Arbeitsbeginn
Befolgen Sie die folgenden Sicherheitsvorkehrungen, bevor Sie mit der Arbeit an der Pumpe beginnen oderwenn Sie sich im Bereich der Pumpe befinden:
•
•
•
•
•
•
•
•
•
•

Grenzen Sie den Arbeitsbereich auf geeignete Weise ein, zum Beispiel mit einem Geländer.
Sorgen Sie dafür, dass alle Schutzvorrichtungen an ihrem Platz und sicher sind.
Sorgen Sie für einen freien Fluchtweg.
Sorgen Sie dafür, dass die Pumpe nicht rollen oder kippen und so Menschen verletzen oder Eigentum
beschädigen kann.
Sorgen sie dafür, dass die Hebezeuge in gutem Zustand sind.
Verwenden Sie bei Bedarf ein Hebegeschirr, eine Sicherheitsleine und/oder ein Atemschutzgerät.
Lassen Sie alle System- und Pumpenbauteile abkühlen, bevor Sie Sie anfassen.
Vergewissern Sie sich, dass die Pumpe gründlich gereinigt wurde.
Trennen Sie vor einer Wartung die Pumpe vom Strom und verriegeln Sie sie.
Überprüfen Sie die Explosionsgefahr, bevor Sie schweißen oder elektrische Handwerkzeuge benutzen.

Haut und Augen waschen: Befolgen Sie nach Haut- oder Augenkontakt folgende Verfahren für
Chemikalien und gefährliche Flüssigkeiten:
Situation
Chemikalien odergefährliche
Flüssigkeiten im Auge
Chemikalienoder gefährliche
Flüssigkeiten auf
der Haut

Maßnahmen
1. Augenlieder mit den Fingern offen halten
2. Augen mit einer Augenreinigungsflüssigkeit oder fließendem Wasser
mindestens 15 Minuten lang spülen
3. Arzt aufsuchen
1. Kontaminierte Kleidung entfernen
2. Haut mit Wasser und Seife mindestens 1 Minute lang waschen
3. Gegebenenfalls einen Arzt konsultieren

UMWELTSICHERHEIT
Der Arbeitsbereich Halten Sie die Station stets sauber
Vorschriften für Abfälle und Emissionen
Beachten Sie die folgenden Sicherheitsvorschriften für Abfälle und Emissionen:•
Entsorgen Sie alle Abfälle vorschriftsmäßig•
Behandeln und entsorgen Sie Flüssigkeiten gemäß den geltenden Umweltschutzbestimmungen•Beseitigen Sie ausgelaufene Flüssigkeiten gemäß den Sicherheits- und Umweltverfahren•
Melden Sie alle Umweltemissionen den zuständigen BehördenWARNUNG: Strahlungsgefahr. Senden Sie das Produkt NICHT an Xylem
zurück, wenn es radioaktiver Strahlung ausgesetzt war.
Elektroinstallation: Konsultieren Sie bezüglich der Recyclinganforderungen fürdie Elektroinstallation Ihren örtlichen Stromversorger.
Recycling-Richtlinien: Befolgen Sie stets die örtlichen Gesetze und Vorschriftenzum Recycling.
WARNUNG: Diese Pumpe ist AUSSCHLIESSLICH für den Einsatz in Gewässern
mit Süß- oder Salzwasser ausgelegt. Die Verwendung zusammen mit
Gefahrstoffen, ätzenden oder korrosiven Substanzen kann zur Beschädigung
der Pumpe wie auch anderer Gegenstände am Einsatzort führen. Dabei kann es
neben der Freisetzung gefährlicher Substanzen auch zu Verletzungen kommen.

WARNUNG: Pumpen dürfen nicht in Betrieb genommen
werden, wenn sie Beschädigungen wie z. B. einen durchgebrannten oder anderweitig defekten Druckschalter aufweisenoder ein Leitungsdraht und/oder -kontakt freiliegt.

C

STOPP
STOP

13

Einbau/Montage
VORSICHT: Nicht für den Dauerbetrieb vorgesehen, nur im
Aussetzbetrieb verwenden.
VORSICHT: Einbauhinweise: Zur Brandvermeidung: Sicherstellen, dass

der Bereich, in dem die Pumpe eingebaut wird, von Gas, Kraftstofftanks,
elektrischen Kabelbäumen oder entzündlichen Substanzen isoliert ist.
Andernfalls kann es zu Verletzungen, eventuell sogar mit Todesfolge,
kommen.

WARNUNG: Hinweise zum Einbau: Um das Entstehen von
Bränden zu vermeiden, bauen Sie dieses Produkt auf keinen Fallein, wenn es offensichtlich beschädigt wurde. Wenn bei einer
Beschädigung elektrische Kontakte freigelegt werden, kann sichbeim Überspringen elektrisch erzeugter Funken Kraftstoffnebel
entzünden. Bei Nichtbeachtung drohen Verletzungen, unter
Umständen mit Todesfolge.
Abbildung 2.
Horizontal
Horizontal

Senkrecht
VerticalHINWEIS:
NichtSubmerge
eintauchen
NOTE:
Do Not1: Einbauort für die Pumpe auswählen. Die Pumpe muss in einem trockenen,
belüfteten Bereich eingebaut werden.
2: Die mit der Pumpe gelieferten
Anschlussstutzen an die
Rohrleitungsanlage desWasserfahrzeugs anschließen.
Flexiblen Schlauch (nach Möglichkeit
Litzenschlauch oder verstärkten
Abbildung 1.
Schlauch) mit 13 mm (½”) Innen-øverwenden, um Vibrationen in derRohrleitungsanlage zu reduzieren(Abbildung 1). Die aufsteckbaren
Schlauchanschlussstutzen mit
Schlauchklemmen befestigen.
Wichtig: Einen Pumpeneinlass mit
Sieb einbauen, um ein Eindringen
von Schmutzrückständen in die
Ventile zu vermeiden.
3: Pumpe auf einer ebenen Fläche befestigen.Die
Vertikalmontage erfolgt mit dem Pumpenkopf nach
unten (Abbildung 2). Die Schrauben nicht zu fest
anziehen, damit die Gummimontageteile Vibrationen
absorbieren können.
4: Einlass- (A) und Auslass- (B) Anschlussstutzen
anbringen. Die Seitenklemmen (C) mit festem
Druck nach vorn schieben, bis die Anschlussstutzen
einrasten. – Abbildung 3
Abbildung 3.

Einlasssieb (A)Auslass (B)Abbildung 4.

Einlass für
städtische
Wasserversorgung

Wassererhitzer

Wassertank

Rückschlagventil
PumpgardSieb
Autofill nicht an
Pumpenansaugleitunganschließen.
14

Autofill-Tankventil,
an Tank anschließen

WARNHINWEISBR A N DGE FA HR !
Die Verdrahtung muss alle geltenden Vorschriften für Elektroanlagen
erfüllen und eine angemessen dimensionierte Sicherung bzw. einen
geeigneten Leistungstrennschalter aufweisen. Eine unsachgemäße
Verdrahtung kann einen Brand verursachen, der zu Verletzungen odersogar zum Tod führen kann.
VORSICHT: Die angegebenen Verdrahtungsempfehlungen sindals Richtschnur zu verstehen. Die genauen Informationen sind den
Vorschriften gemäß ABYC E-11 sowie für bordmontierte AC- und
DC-Elektroanlagen zu entnehmen.

Kabelquerschnitttabelle

Gesamtkabellänge – in Fuß (Meter)
Pumpenspannung

0 - 20 ft(0 - 6 m)

20 - 35 ft(6 - 9 m)

35 - 55 ft(9 - 12 m)

12 VDC		
24 VDC		

Nr.14 AWG
(2,5 mm2)
Nr.16 AWG
(1,5 mm2)

Nr.12 AWG
(4 mm2)
Nr.14 AWG
(2,5 mm2)

Nr.10 AWG
(6 mm2)
Nr.12 AWG
(4 mm)VORSICHT: Das Motorgehäuse kann sich bei Langzeitbetrieb erhitzen. Längerer
Hautkontakt kann zu Verbrennungen führen.
WARNUNG: Arbeiten an Strom führenden Leitungen darf ausschließlich ein ausgebildeter
Elektrotechniker vornehmen.
VORSICHT: Trennen Sie das System von der Stromversorgung, bevor Sie am Gerät zu arbeiten
beginnen. So verhindern Sie, dass es am Einsatzort zu Verletzungen oder Beschädigungen kommt
und/oder dass das Gerät beschädigt wird.

Abbildung 5.

Sicherungshaltersfgrünen
Erdleiter

oder
grau
Sicherungrote Kabel (+)

Leistungsschalters
schwarze Kabel (-)

Batterie DC 12 V

Beginnen Sie oben
Abbildung 6.

Inbetriebnahme
InitialStart Up

Demand Off aus
Bedarfssteuerung

Bedarfssteuerung
Demand On ein• Wassertank füllen
• Alle Hähne
aufdrehen• Pumpenschalter
einschalten (ON)HINWEIS: Der
Einschaltvorgang
erfolgt mit einer
Verzögerung von 5
Sekunden.
• Wenn das Wasser
entlüftet ist, alle
Hähne zudrehen.
Dabei mit dem
Hahn beginnen,
der der Pumpe
am nächsten ist(Abbildung 6)

Wichtig: Die Pumpe nicht länger als 15 Minuten im Dauerbetrieb laufen
lassen.
15

Einwinterung
VORSICHT: In der Anlage gefrierendes Wasser kann zur Beschädigung der Pumpe und desRohrleitungssystems führen. Ungiftiges trinkwassergeeignetes Frostschutzmittel ist für Jabsco-Pumpen
zulässig. Herstelleranweisungen befolgen. Die spezifischen Einwinterungs- und Drainageverfahren
sind den Anweisungen des Boots- oder Geräteherstellers zu entnehmen. Für die Einwinterung vonTrinkwasseranlagen kein Frostschutzmittel für Kraftfahrzeuge verwenden. Diese Lösungen sindhochgiftig und können bei Verzehr schwere oder sogar lebensgefährliche Verletzungen hervorrufen.
1. Den Wassertank entleeren. Das Ablassventil des Tanks öffnen. Durch Aufdrehen aller Hähne inder Anlage kann der Tank mit der Pumpe entleert werden. Die Pumpe laufen lassen, bis der Tankleer ist. Die Pumpe nicht länger als 15 Minuten im Dauerbetrieb laufen lassen.
2. Alle Hähne aufdrehen und das Wasser aus dem Rohrleitungssystem ablassen. Die Pumpe
ausschalten. Sicherstellen, dass das ganze Wasser aus den Ablassleitungen abgeführt worden
ist.
3. Die Schnellkupplungs-Einlass- und –Auslassstutzen von der Pumpe abnehmen. Die Pumpe
einschalten, um ggf. noch im Pumpenkopf befindliches Wasser abzupumpen. Mit einer
Auffangschale oder einem Lappen unter der Pumpe sicherstellen, dass kein Wasser in das
Boot ausläuft. Die Pumpe ausschalten, sobald das Rohrleitungssystem entleert ist. Die
Anschlussstutzen erst dann erneut an der Pumpe anbringen, wenn das System wieder
einsatzbereit ist. Am Einfüllstutzen des Tanks mit einer Notiz darauf hinweisen, dass das
Rohrleitungssystem nicht angeschlossen ist.
4. Sicherstellen, dass alle Hähne aufgedreht bleiben, um Beschädigungen des Rohrleitungssystems
zu vermeiden.

Referenzmodell
ModellNominale
Gleichstrom-VoltÖffnen Sie Fluss
GPM (LPM)

Betriebsdruck
PSI (Bar)

Ausschnitt-Druck
PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Größe:

Breite – 6 1/8 Zoll (155.58mm), Höhe – 4 3/4 Zoll (120.65mm),
Llongueur – 9 7/8 Zoll (250.83mm)

Betrieb
AttributZeit, volle Geschwindigkeit nach dem Hahn zu erreichen geöffnet
Zeit, nach dem Hahn abzustellen vollständig geschlossen

12 Volt

24 Volt

5 seconds
or less
5 seconds
or less

5 seconds
or less
5 seconds
or lessÜber Spannungs-Schwellwert-Einstellung (Maßeinheit automatisch stellte
16 Volts DC
ab,/wird nicht laufen)
Unter Spannungs-Schwellwert-Einstellung (Maßeinheit automatisch stellte
9 Volts DC
ab,/wird nicht laufen)
Unter aktueller Schwellwert-Einstellung (Maßeinheit automatisch stellte
2 AMPSab,/wird nicht laufen)
KEY

18 Volts DC
2 AMPS

Modell Nr.

Quantität

2

Ventil-Installationssatz

18911-7030

13Membran-Kit

18912-3040

1

4

Senken Sie Gehäuse-Installationssatz

18915-9002

1

5

Druckschalter

37121-0010

1

6

Halten Sie Installationssatz instand

18920-9043

1

Motor 12V DC

18753-5236

1

Motor 24V DC

18753-5237

18

Seitliche Klipps

30648-1000

1

9Hauptpumpe

18914-0030

1

10

Pumpgard™ Sieb (nicht gezeigt)

46400-9500

1

7Beschreibung

31 Volts DC

Zubehör

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Führen Sie den Einbau in ABYC
H-22, H-23 und E-11 durch
Wir erklären als Hersteller in alleiniger Verantwortung, dass wir
das Produkt, das Gegenstand dieser Erklärung ist, mit dem Ziel
der Konformität mit den Anforderungen folgender Richtlinien
entwickelt haben:
EMV-Richtlinie 2004/108/EG
Richtlinie über Sportboote 2003/44/EC
RoHS 2011/65/EU
Dasselbe gilt für die relevanten Teile der folgenden Normen:
ISO 8846:1990 / Zündschutz
16Pompa automatica
dell’impianto idrico
Questo manuale ha lo scopo di fornire le informazioni necessarie per l’installazione,
il funzionamento e la manutenzione del prodotto.

PERICOLO: Leggere attentamente questo manuale prima di installare, utilizzare o ripararequesto prodotto. La mancata osservanza delle istruzioni contenute in questo manuale può causare
esplosione, danni materiali, lesioni personali gravi e/o morte.
AVVISO: Conservare questo manuale per riferimento futuro e tenerlo facilmente accessibile inprossimità dell'unità.

SICUREZZAAVVISO:••••

L’operatore deve essere a conoscenza delle misure di sicurezza per evitare lesioni fisiche.
Tutti i dispositivi a pressione possono esplodere, rompersi o rilasciare il loro contenuto se sottoposti apressione eccessiva. Prendere tutte le misure necessarie per evitare una pressione eccessiva.
L’utilizzo, l’installazione o la manutenzione dell’unità secondo modalità non indicate in questo
manuale possono causare morte, gravi lesioni personali o danni alle attrezzature. Ciò include ogni
modifica alle attrezzature o l’utilizzo di parti non fornite da Xylem. In caso di dubbi relativi alla
destinazione d’uso delle attrezzature, contattare un rappresentante Xylem prima di procedere.
Non modificare l’applicazione di servizio senza l’approvazione di un rappresentante autorizzato Xylem.

PERICOLO: La mancata osservanza di tali istruzioni può causare esplosione,
danni materiali, lesioni personali gravi e/o morte.

TERMINOLOGIA E SIMBOLI DI SICUREZZA
Informazioni sui messaggi di sicurezzaÈ estremamente importante leggere, comprendere e seguire i messaggi e le normedi sicurezza prima di maneggiare il prodotto. Questi sono forniti per aiutare aprevenire i seguenti rischi:•
Infortuni personali e problemi di salute•
Danni al prodotto•
Malfunzionamento del prodotto
Livelli di pericolo Indicazione
PERICOLO
Indica una situazione pericolosa che, se non evitata, provoca il decesso o lesioni gravi.
AVVERTENZA
Indica una situazione pericolosa che, se non evitata, può provocare il decesso o lesioni
gravi.
ATTENZIONE
Indica una situazione pericolosa che, se non evitata, può provocare lesioni lievi omoderate.
AVVISO
Indica una situazione pericolosa che, se non evitata, può provocare condizioni
indesiderate.
Una pratica non correlata a lesioni personali.
Categorie di pericolo
Le categorie di pericolo possono sia rientrare sotto i livelli di pericolo o sostituire
con simboli specifici i simboli di livello di pericolo ordinario. I rischi di natura
elettrica sono indicati con i seguenti simboli specifici:
RISCHIO DI NATURA ELETTRICA:
Questi sono esempi di altre categorie che possono verificarsi. Essi rientrano sotto
i livelli di pericolo ordinario e possono essere accompagnati da altri simboli:•
Pericolo di schiacciamento•
Pericolo di taglio•
Pericolo di archi elettrici

SICUREZZA DELL’UTENTE
Norme generali di sicurezza
Si applicano le seguenti norme di sicurezza:••••

Tenere sempre l’area di lavoro pulita
Prestare attenzione ai rischi presentati da gas e vapori nell’area di lavoro
Evitare tutti i pericoli elettrici Prestare attenzione ai rischi di scosse elettricheo di archi elettrici
Tenere sempre presente il rischio di annegamento, incidenti elettrici e
ustioni

Dispositivi di protezione individuale Utilizzare dispositivi di protezione individualesecondo le normative aziendali. Utilizzare i seguenti dispositivi di protezione individuale
all'interno dell'area di lavoro:••••

Elmetto protettivo
Occhiali di sicurezza, preferibilmente con protezioni laterali
Scarpe di protezione
Guanti di protezione

•
•
•
•

Maschera antigas
Protezione dell'udito
Kit per pronto intervento
Dispositivi di sicurezza

AVVISO: Non utilizzare mai un'unità priva dei dispositivi di sicurezza installati.
Collegamenti elettrici
I collegamenti elettrici devono essere effettuati da elettricisti certificati in conformità
a tutte le normative internazionali, nazionali, statali e locali. Per ulteriori informazioni
sui requisiti, vedere le sezioni relative ai collegamenti elettrici.
17Precauzioni prima dell'utilizzo. Osservare le seguenti precauzioni di sicurezza
prima di lavorare con il prodotto o di effettuare collegamenti con il prodotto:
•
•
•
•
•
•
•
•
•
•

Prevedere una barriera adeguata attorno all'area di lavoro, ad esempio un
guard rail
Assicurarsi che tutte le protezioni di sicurezza siano installate e fissate
Assicurarsi di avere una via di fuga
Assicurarsi che il prodotto non possa rotolare o cadere ferendo persone ocausando danni materiali
Assicurarsi che le attrezzature di sollevamento siano in buone condizioni
Utilizzare una cinghia di sollevamento, una linea di sicurezza e un dispositivo
di respirazione secondo necessità
Lasciar raffreddare tutti i componenti del sistema e della pompa prima dimaneggiarli
Assicurarsi che il prodotto sia stato accuratamente pulito
Scollegare e bloccare l’alimentazione prima di intervenire sulla pompa
Verificare il rischio di esplosione prima di effettuare saldature o utilizzare
attrezzi elettrici manuali

Lavare la pelle e gli occhi. In caso di contatto di sostanze chimiche o fluidi
pericolosi con gli occhi o con la pelle, attenersi alle seguenti procedure:
Condizione
Sostanze chimiche ofluidi pericolosi negli
occhi
Sostanze chimiche ofluidi pericolosi sulla
pelle

Azione1. Tenere le palpebre aperte a forza con le dita
2. Sciacquare gli occhi con un lavaggio oculare o acqua corrente per almeno 15 minuti
3. Richiedere l’intervento di un medico
1. Rimuovere gli indumenti contaminati
2. Lavare la pelle con acqua e sapone per almeno 1 minuto
3. Richiedere l’intervento di un medico, se necessario

SICUREZZA AMBIENTALE
Area di lavoro. Tenere sempre l'area di lavoro pulita.
Norme su rifiuti e sulle emissioni
Osservare queste norme di sicurezza in materia di rifiuti ed emissioni:•
Smaltire opportunamente tutti i rifiuti•
Maneggiare e smaltire il liquido di processo nel rispetto delle norme
ambientali applicabili•
Pulire tutte le perdite in conformità con le procedure di sicurezza e ambientali•
Segnalare tutte le emissioni ambientali alle autorità competenti
AVVISO: Pericolo di radiazioni. NON inviare il prodotto a Xylem se è statoesposto a radiazioni nucleari.
Impianto elettrico
Per i requisiti di riciclaggio dell'impianto elettrico, rivolgersi al gestore della reteelettrica locale.
Linee guida per il riciclaggio
Attenersi sempre alle leggi e alle normative locali in materia di riciclaggio.
AVVERTENZA: Questa pompa è stata concepita per l’uso ESCLUSIVO con
acqua potabile e acqua salata. L’utilizzo del prodotto con qualsiasi altro
materiale pericoloso, caustico o corrosivo può causare danni alla pompa
e all’ambiente circostante, la possibile esposizione a sostanze pericolose elesioni.

AVVERTENZA: Non utilizzare una pompa che presenti danni
quali interruttori di pressione bruciati o rotti, cavi elettrici e/ocontatti esposti.

C

ALTO
STOP

18

Installazione/Montaggio
ATTENZIONE: Non per funzionamento in continuo; solo per
funzionamento intermittente
ATTENZIONE: Note per l’installazione: per evitare il rischio d’incendio.
Accertarsi che l’area dove la pompa viene installata sia isolata da gas,
serbatoi del carburante, gruppi di cavi elettrici o sostanze infiammabili.
L’inosservanza di questa precauzione può causare lesioni o la morte.
ATTENZIONE: Indicazioni per l’installazione: per evitare il rischio di
incendio. Non installare questo prodotto se visibilmente danneggiato.
Se il danno espone i contatti elettrici, le scintille potrebbero incendiarei fumi di carburante. Il mancato rispetto di queste indicazioni può
causare gravi lesioni o perfino la morte.
Figura 2.
Horizontal
Orizzontale

VerticaleVertical

NOTA:Do
nonNotsommergere
NOTE:
Submerge

1: Scegliere la sede per la pompa. La pompa deve essere installata inun’area asciutta e ventilata.
2: Collegare i raccordi forniti conla pompa al sistema idraulicodell’imbarcazione. Usare un tubo
flessibile con diametro internodi 13 mm (preferibilmente
intrecciato o rinforzato) per ridurre
Figura 1.
le vibrazioni nel sistema idraulico(Figura 1). Usare morsetti per tubo
flessibile sui contatti sui connettoridel giunto a gomito.
Importante: installare il filtro
in entrata della pompa perproteggere le valvole dai detriti.
3: Fissare la pompa su una superficie
piatta. Se l’installazione è verticale:installare con la testa della pompa
rivolta in basso (Figura 2). Non
stringere eccessivamente leviti per evitare che i supportidi gomma non assorbano levibrazioni.
4: Installare i raccordi di entrata (A) e di scarico (B). Spingere
decisamente in avanti i clip laterali (C) per bloccare i raccordi inposizione. – Figura 3.
Figura 3.

Filtro in entrata (A)Scarico (B)Figura 4.

Entrata dell’acquadi città

Boilerdell’acqua

Tanica dell’acqua

Valvola dicontrollo
FiltroPumpgard
Non collegare il tubo diriempimento automatico
alla linea di aspirazionedella pompa

Valvola di riempimento
automatico della tanica, collegare
il tubo alla tanica.
19

AVVERTENZAPERICOLO D’INCENDIO
Il cablaggio deve soddisfare tutti gli standard elettrici del caso, ecomprendere un fusibile di dimensione appropriata o un interruttore
disgiuntore. Il cablaggio scorretto può causare un incendio con rischio
di infortuni o di morte.
ATTENZIONE: Le informazioni sul cablaggio consigliato sono fornite
come riferimento. Per le informazioni corrette, consultare le linee
guida Sistemi elettrici CA, CC e ABYC E-11 sulle barche.

Tabella del cablaggio
Lunghezza totale del filo piedi (metri)
Tensionedella pompa

0 - 20 piedi(0 - 6 m)

20 - 35 piedi(6 - 9 m)

35 - 55 piedi(9 - 12 m)

CC 12V		
CC 24V		#14 AWG(2,5 mm2)#16 AWG(1,5 mm2)#12 AWG(4 mm2)#14 AWG(2,5 mm2)#10 AWG(6 mm2)#12 AWG(4 mm)ATTENZIONE: In occasione di prolungato funzionamento, la cassadel motore potrebbe diventare molto calda. Il contatto prolungato
con la pelle può causare ustione.
AVVERTENZA: I collegamenti elettrici devono essere effettuati da
un tecnico elettrico marino competente.
ATTENZIONE: Scollegare l’alimentazione dall’impianto prima dilavorare sull’unità, per evitare lesioni personali, danni all’ambiente
circostante e/o danni all’unità stessa.

Figura 5.

fusibile in linea
cavo diterra verdeO
grigiofusibilerosso (+)

interruttore
nero (-)

Batteria 12V DC

Avvii in su
Figura 6.

Initial
AvvioStart
inizialeUp

DemandOff
Richiesta spenta

Richiesta accesa
DemandOn• Riempire la tanica
dell’acqua• Aprire tutti irubinetti• Spostare su “ON”
l’interruttore della
pompa
NOTA: Attendere
5 secondi perl’alimentazione dellapompa.
• Quando nell’acqua
non c’è più aria,
chiudere tutti irubinetti, partendo
dal rubinetto più
vicino alla pompa(Figura 6)

Importante: Non far funzionare la pompa più di 15 minuti di seguito.
20

Preparazione per l’inverno
ATTENZIONE: Se l’acqua nel sistema si congela, la pompa e il sistema idraulico possono
danneggiarsi. Con le pompe Jabsco, si possono usare prodotti antigelo non tossici per acqua potabile.
Seguire le raccomandazioni del produttore. Per le procedure specifiche di drenaggio e preparazione
per l’inverno, vedere le istruzioni del produttore dell’imbarcazione o delle attrezzature. Per preparare
per l’inverno i sistemi dell’acqua potabile, non usare antigelo per autoveicoli. Queste soluzioni sono
altamente tossiche e, se ingerite, possono causare serie lesioni o la morte.
1. Svuotare la tanica dell’acqua. Aprire la valvola di svuotamento della tanica. Per svuotare la tanica,
si può usare la pompa aprendo tutti i rubinetti del sistema. Lasciare in funzione la pompa fino aquando la tanica è vuota. Non far funzionare la pompa più di 15 minuti di seguito.
2. Aprire tutti i rubinetti ed espellere l’acqua dal sistema idraulico. Spegnere la pompa. Verificare
che tutta l’acqua sia svuotata dalle linee di scarico.
3. Rimuovere i raccordi a connessione rapida di entrata e di uscita dalla pompa, e accendere la
pompa per svuotare l’acqua rimanente dalla testa della pompa. Accertarsi di tenere una bacinella
di raccolta o uno straccio sotto la pompa per evitare che l’acqua si versi sulla barca. Dopo che ilsistema idraulico è vuoto, spegnere la pompa. Lasciare sconnessi i raccordi dalla pompa fino aquando il sistema è pronto per essere usato di nuovo. Annotare sul riempitore della tanica che ilsistema idraulico non è collegato.
4. Accertarsi di lasciare aperti tutti i rubinetti per proteggere da danni il sistema idraulico.

Modello di riferimento
Modello

Volt nominali
di CC

Apra il flusso
GPM (LPM)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Dimensioni:

Pressione di funzionamento Pressione del ritaglio
PSI (Bar)
PSI (BAR)

Larghezza – 6 1/8 pollici (155.58mm), Altezza – 4 3/4 pollici (120.65mm),
Lunghezza – 9 7/8 pollici (250.83mm)

Funzionamento
Attributo
Tempo di raggiungere velocità completa dopo il rubinetto aperto
Tempo di spegnere dopo il rubinetto completamente chiuso

12 Volt

24 Volt

5 secondi odi meno5 secondi odi meno5 secondi odi meno5 secondi odi menoSopra la regolazione della soglia di tensione (unità automaticamente ha
16 Volts DC
spento/non funzionerà)
Nell’ambito della regolazione della soglia di tensione (unità automatica9 Volts DC
mente ha spento/non funzionerà)
Nell’ambito della regolazione corrente della soglia (unità automaticamente
2 AMPSha spento/non funzionerà)
Cod.

18 Volts DC
2 AMPS

Modello no.

Qua.

2

Kit della valvola

18911-7030

1

3

Kit membrana

18912-3040

1

4

Abbassi il kit dell’alloggiamento

18915-9002

1

5

Pressostato37121-0010

1

6

Assista il kit

18920-9043

1

Motore 12V DC

18753-5236

1

Motore 24V DC

18753-5237

1

8

Clip laterali

30648-1000

19Assemblea capa della pompa

18914-0030

1

10

Setaccio di Pumpgard™ (non indicato)46400-9500

1

7

Descrizione

31 Volts DC

Accessori - Raccordi Port

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Installare su ABYC
H-22, H-23 ed E-11
Con il presente documento, di cui abbiamo la
responsabilità esclusiva, dichiariamo che il prodotto alquale la presente dichiarazione fa riferimento è stato
concepito per essere conforme con le seguenti Direttive:
Direttiva sulla compatibilità elettromagnetica 2004/108/CE
Direttiva sulle unità da diporto 2003/44/CE
RoHS 2011/65/UE
Con le parti specifiche dei seguenti standard:
ISO 8846:1990 / Protezione antincendio
21Automatischewatersysteempomp
Het doel van deze handleiding is om de nodige informatie te verstrekken
over de installatie, bediening en onderhoud van het product.

GEVAAR: Lees deze handleiding zorgvuldig door voordat u dit product installeert, gebruikt ofonderhoudt. Wanneer u de instructies in deze handleiding niet volgt, kan dat leiden tot explosie,
materiële schade, ernstig lichamelijk en/of dodelijk letsel.
LET OP: Bewaar deze handleiding voor toekomstig gebruik en in de directeomgeving van het apparaat.

VEILIGHEID
WAARSCHUWING:

•
•
•

•

De gebruiker moet zich bewust zijn van veiligheidsmaatregelen om lichamelijk letsel te voorkomen.
Een apparaat dat onder druk staat kan exploderen, scheuren of zijn inhoud verliezen als de druk tehoog is. Neem alle noodzakelijke maatregelen om overdruk te voorkomen.
Het bedienen, installeren of onderhouden van het apparaat op een manier die niet wordt behandeld
in deze handleiding kan ernstig lichamelijk of dodelijk letsel of schade aan de apparatuur
veroorzaken. Dit geldt ook voor aanpassingen aan de apparatuur of gebruik van onderdelen die niet
geleverd zijn door Xylem. Als u een vraag heeft over het beoogde gebruik van de apparatuur, neemdan contact op met een vertegenwoordiger van Xylem voordat u verder gaat.
Verander de servicetoepassing niet zonder de goedkeuring van een bevoegde vertegenwoordiger
van Xylem.

GEVAAR: Als u deze instructies niet opvolgt, kan dit leiden tot explosie,
materiële schade, ernstig lichamelijk en/of dodelijk letsel.

VEILIGHEIDSTERMINOLOGIE EN SYMBOLEN
Betreffende veiligheidswaarschuwingen. Het is uiterst belangrijk dat u deveiligheidswaarschuwingen en -reglementen zorgvuldig leest, begrijpt en volgt
voordat u het product gebruikt. Deze worden gepubliceerd om de volgende
gevaren te voorkomen:
1.
2.
3.

Persoonlijke ongevallen en gezondheidsproblemen
Schade aan het product
Storingen
Gevarenniveau
GEVAARWAARSCHUWINGLET OPOPMERKING

Indicatie
Een gevaarlijke situatie die, indien niet vermeden, leidt tot ernstig ofdodelijk letsel
Een gevaarlijke situatie die, indien niet vermeden, kan leiden tot ernstig ofdodelijk letsel
Een gevaarlijke situatie die, indien niet vermeden, kan leiden tot licht ofmatig letsel
Een potentiële situatie die, indien niet vermeden, kan leiden tot ongewenste
omstandigheden
Een handeling die niet tot lichamelijk letsel zal leiden

Gevarencategorieën. Gevarencategorieën kunnen ofwel vallen onder degevarenniveaus of specifieke symbolen zijn die de gewone gevarenniveaus
symbolen vervangen.
Elektrische gevaren worden aangegeven met de volgende specifieke symbolen:
ELEKTRISCH GEVAAR
Dit zijn voorbeelden van andere categorieën die kunnen optreden. Ze vallen onderde gewone gevarenniveaus en kunnen aanvullende symbolen gebruiken:•••

Pletgevaar
Snijgevaar
Vlamoverslag

GEBRUIKSVEILIGHEID
Algemene veiligheidsvoorschriften
De volgende veiligheidsvoorschriften dienen in acht genomen te worden:••••

Houd de werkplek schoon.
Let op de risico's van gassen en dampen in het werkgebied.
Vermijd alle elektrische gevaren. Besteed aandacht aan de risico's van eenelektrische schok of vlamoverslag.
Houd altijd rekening met het risico van verdrinking, elektrische ongelukken enbrandwonden.

Veiligheidsuitrusting. Gebruik veiligheidsapparatuur volgens de regelgeving van
het bedrijf. Gebruik de volgende veiligheidsuitrusting in de werkruimte:
•
•
•
•

Helm
Veiligheidsbril, bij voorkeur met zijkappen
Beschermende schoenen
Beschermende handschoenen

•
•
•
•

Gasmasker
Gehoorbescherming
EHBO-kit
Veiligheidsvoorzieningen

OPMERKING: Gebruik nooit een apparaat voordat de veiligheidsvoorzieningen zijn geïnstalleerd
Elektrische aansluitingen. Elektrische aansluitingen dienen gemaakt te worden
door gecertificeerde elektriciens in overeenstemming met alle internationale,
nationale, provinciale en lokale regelgeving. Raadpleeg de paragrafen die specifiek
bezighoudt met elektrische aansluitingen voor meer informatie over de vereisten.
22

Voorzorgsmaatregelen voorafgaand aan werkzaamheden. Neem de volgendevoorzorgsmaatregelen in acht voordat u het product gebruikt of in aanraking komt
met het product:
•
•
•
•
•
•
•
•
•
•

Zorg voor een doelmatige afscherming rondom de werkruimte,
bijvoorbeeld een vangrail
Zorg ervoor dat alle veiligheidsmiddelen en veilig aanwezig zijn
Zorg ervoor dat u een duidelijke vluchtweg heeft
Zorg ervoor dat het product niet kan wegrollen of omvallen, om persoonlijk
letsel of schade te voorkomen
Zorg ervoor dat het hijsmateriaal in goede staat verkeert
Gebruik een hijsharnas, een veiligheidslijn en een beademingsapparaat
wanneer vereist
Laat alle systeem- en pomponderdelen afkoelen voordat u ermee inaanraking komt
Zorg dat het product grondig is gereinigd
Ontkoppel en schakel de pomp uit voordat u deze onderhoudt
Controleer het risico van explosies voordat u gaat lassen of elektrischhandgereedschap gebruikt

Was huid en ogen. Volg deze procedures voor chemicaliën of gevaarlijke
vloeistoffen die in contact zijn gekomen met uw ogen of huid:
ToestandChemicaliën ofgevaarlijke vloeistoffen
in de ogen
Chemicaliën ofgevaarlijke vloeistoffen
op de huid

Behandeling

1. Houd uw oogleden met uw vingers uit elkaar
2. Spoel de ogen met oogwater of stromend water gedurende ten minste 15 minuten
3. Raadpleeg een arts
1. Verwijder besmette kleding
2. Was de huid met water en zeep gedurende ten minste 1 minuut
3. Roep medische hulp in indien nodig

MILIEUVEILIGHEID
De werkruimte. Houd de ruimte schoon
Regelgeving voor afval en emissies
Neem deze veiligheidsvoorschriften met betrekking tot afval en emissies in acht:••••

Adequate afvoer van afval
Verwerk en voer verwerkte vloeistof af in overeenstemming met degeldende milieuvoorschriften
Ruim gemorste stoffen op conform geldende veiligheids en
milieuprocedures
Meld alle milieuemissies aan de bevoegde autoriteiten
WAARSCHUWING: Stralingsgevaar. Stuur het product NIET naar Xylem als
het is blootgesteld aan radioactieve straling.

Elektrische installatie. Raadpleeg uw plaatselijke elektriciteitsmaatschappij voor
recycling voorschriften van de elektrische installatie.
Richtlijnen voor recycling. Volg altijd de plaatselijke wet- en regelgeving met
betrekking tot recycling.
WAARSCHUWING: Deze pomp is UITSLUITEND ontwikkeld voor gebruik inzoet en zout water. Gebruik in combinatie met andere gevaarlijke, caustischeof corrosieve materialen kan resulteren in schade aan de pomp en deomgeving, mogelijke blootstelling aan gevaarlijke stoffen en letsels.

WAARSCHUWING: Gebruik de pomp niet indien beschadigd
door een doorgebrande of gebroken drukschakelaar, blootliggende elektrische bedrading en of blootliggende contacten.

C

STOP

23

Installatie/montage
VOORZICHTIG: Niet voor continu gebruik, alleen voor periodiek
gebruik
VOORZICHTIG: Opmerkingen betreffende installatie: Zorg ter
voorkoming van brandgevaar dat de ruimte waarin de pompzich bevindt is afgeschermd van gas, brandstoftanks, elektrischekabelbundels of brandbare stoffen. Dit niet doen, kan letsel
veroorzaken of dodelijke gevolgen hebben.
OPGELET: Installatierichtlijnen: Om brandgevaar te voorkomen.
Installeer dit product niet als het zichtbaar beschadigd is. Als door
schade elektrische contacten vrij bereikbaar worden, kunnen
elektrische vonken brandstofdampen doen ontsteken. Als u dezerichtlijnen niet volgt kan dit ernstige schade en zelfs de dood tot
gevolg hebben.
Figuur 2.
Verticaal
VerticalHorizontal
Horizontaal

OPMERKING:NOTE: Do niet
Not onderdompelen
Submerge

1: Kies de locatie voor de pomp. Dit moet een droge,
geventileerde ruimte zijn.
2: Sluit de met de pomp meegeleverde
koppelingen aan op de leidingen van
het vat. Gebruik een flexibele slang (bijvoorkeur omvlochten of versterkt) met
een binnendiameter van ½” (13 mm)om trillingen door het leidingsysteem
te verminderen (figuur 1). Bevestig
de slangklemmen op de inschuifbareslangtules.

Figuur 1.

Belangrijk: monteer een pompinlaat met een zeef
om de kleppen tegen vuil te beschermen.
3: Bevestig de pomp op een plat oppervlak. Bij verticale
montage monteert u de pomp met de pompkop omlaag(Figuur 2). Draai de schroeven niet te strak aan zodat derubberen bevestigingen trillingen kunnen opvangen.
4: Monteer de fittings voor de aanvoer (A) en de afvoer (B).
Duw de schuifklemmen (C) naar voren om de koppelingen te
blokkeren. – Figuur 3
Figuur 3.

Inlaatzeef (A)Afvoer (B)Figuur 4.

WatertankInlaatopenbarewaterleiding

Waterverwarmer

Terugslagklep
Pumpgard zeef
Las de automatischevulvoorziening niet aan
de aanzuigleiding vande pomp.
24

Tankklep automatischevulvoorziening, aan tank lassen

WAARSCHUWINGB R A N DGE VA A R
De bedrading moet aan de geldende elektrische normen
voldoen en over een zekering van de juiste stroomsterkte of een
stroomonderbreker beschikken. Verkeerde bedrading kan in brand en
bijgevolg letsel of dodelijke gevolgen resulteren.
VOORZICHTIG: De voorgestelde bedrading is uitsluitend bedoeld
ter referentie. Raadpleeg voor de juiste informatie de richtlijnen
ABYC E-11, AC en DC – Elektrische systemen op boten.

Bedradingstabel
Totale draadlengte - feet (meter)
Pompspanning

0 - 20 ft(0 - 6 m)

20 - 35 ft(6 - 9 m)

35 - 55 ft(9 - 12 m)

12 VDC		
24 VDC		#14 AWG(2,5 mm2)#16 AWG(1,5 mm2)#12 AWG(4 mm2)#14 AWG(2,5 mm2)#10 AWG(6 mm2)#12 AWG(4 mm)VOORZICHTIG: Bij langdurig gebruik kan de motorbehuizing
warm worden. Langdurig contact met de huid kan brandwonden
veroorzaken.
WAARSCHUWING: Elektrische aansluitingen moeten worden uitgevoerd door een bevoegde
scheepselektrotechnicus.
OPGELET: Koppel de stroom af van het systeem alvorens aan de eenheid te werken om
persoonlijke letsels, schade aan de omgeving en/of schade aan de eenheid te voorkomen.

Figuur 5.

inline zekering
Groene
grond

OF
Grijs
Zekering

Rood (+)

Schakelaar
Zwart (+)

12v Accu

Opstarten
Figuur 6.

InitialStart Up
Eersteinbedrijfstelling

DemandOff
Aanvoer UIT• Vul de watertank• Open alle kranen• Zet depompschakelaar inde stand “ON”
OPMERKING: Het kan
tot 5 seconden duren
voordat de pomp
aanspringt.
• Als het water geen
luchtbellen meer
bevat, draait u allekranen dicht, te
beginnen met dekraan het dichtst bij
de pomp (figuur 6).

DemandOn
Aanvoer AAN

Belangrijk: laat de pomp niet langer dan 15 minuten continu draaien.
25

Winterklaar maken
VOORZICHTIG: Laat geen water in het systeem bevriezen. Dit kan depomp en het leidingsysteem beschadigen. Niet-giftig antivriesmiddel voor
drinkwater is toegestaan voor Jabsco-pompen. Volg de aanwijzingen van defabrikant op. Raadpleeg de instructies van de boot- of apparatuurfabrikant
voor specifieke werkwijzen betreffende winterklaar maken en aftappen.
Gebruik geen antivriesmiddel voor auto’s om drinkwatersystemen winterklaar
te maken. Deze oplossingen zijn zeer giftig en kunnen bij inslikken ernstig ofdodelijk letsel veroorzaken.
1. Tap de watertank af. Open de aftapkraan van de tank. U mag de tank met
behulp van de pomp aftappen door alle kranen in het systeem te openen.
Laat de pomp draaien totdat de tank leeg is. Laat de pomp wel niet langer
dan 15 minuten continu draaien.
2. Open alle kranen en laat het water uit het leidingsysteem stromen. Schakel
de stroomtoevoer naar de pomp uit. Zorg dat er geen water achterblijft inde aftapleidingen.
3. Haal de inlaat- en uitlaatsnelkoppelingen van de pomp en schakel depomp in om het resterende water uit de pompkop te pompen. Plaats een
opvangbak of een doek onder de pomp om te voorkomen dat er water
op de boot wordt gemorst. Schakel de pomp uit zodra de leidingen leegzijn. Monteer de koppelingen pas weer op de pomp als u het systeem
terug gebruikt. Plak op uw tankvuldop een etiket met de waarschuwing
dat de leidingen zijn losgekoppeld.
4. Zorg dat alle kranen open zijn om schade aan de leidingen te voorkomen.

Model referentie
Model

De nominale Volts
van gelijkstroom

Open Stroom
GPM (LPM)

Werkende Druk
PSI (Bar)De Druk van het
knipsel PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Afmeting:

breedte – 6 1/8 inch (155.58mm), hoogte – 4 3/4 inch (120.65mm),
lengte – 9 7/8 inch (250.83mm)

Bediening
Attributen
Tijd om volledige snelheid na geopende tapkraan te bereiken
Tijd om na volledig gesloten tapkraan af te sluiten
Over het Plaatsen van de Drempel van het Voltage (de Eenheid sluit zal
automatisch af/niet lopen)
Onder het Plaatsen van de Drempel van het Voltage (de Eenheid sluit zal
automatisch af/niet lopen)
Onder het Huidige Plaatsen van de Drempel (de Eenheid sluit zal automatisch af/niet lopen)
sleutelbeschrijving

12 Volt

24 Volt

5 secondenof minder
5 secondenof minder

5 secondenof minder
5 secondenof minder

16 Volts DC

31 Volts DC

9 Volts DC

18 Volts DC

2 AMPS

2 AMPS

Modelleer Nr. hoeveelheid

2

De Uitrusting van de klep

18911-7030

1

3

Middenrif set

18912-3040

1

44 De lagere Uitrusting van de Huisvesting

18915-9002

1

5

De Schakelaar van de druk

37121-0010

1

6

De Uitrusting van de dienst

18920-9043

1

Motor 12V DC

18753-5236

1

Motor 24V DC

18753-5237

1

8

Zij Klemmen

30648-1000

1

9De HoofdAssemblage van de pomp

18914-0030

1

10

Van Pumpgard™ de getoonde (niet Zeef)

46400-9500

1

7

Accessoires – port fittingen

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Installeren tot ABYC
H-22, H-23 en E-11
We verklaren hierbij, onder onze eigen
verantwoordelijkheid, dat ons product waarop dezeverklaring betrekking heeft, is ontworpen om te voldoen
aan de volgende richtlijnen:richtlijn elektromagnetische compatibiliteit 2004/108/EG;
richtlijn pleziervaartuigen 2003/44/EG;
RoHS 2011/65/EU.
Met de relevante selecties van de volgende normen:
ISO 8846:1990 / Bescherming tegen ontsteking
26

Automatisk
vattensystempump
Syftet med den här manualen är att ge nödvändig information för produktinstallation, drift och underhåll.

FARA: Läs den här manualen noga innan installation, användning eller
service and den här produkten. Underlåtelse att följa instruktionerna i
manualen kan resultera i explosion, egendomsskada, allvarlig personskada
och/eller dödsfall.
OBSERVERA: Spara den här manualen som framtida referens, och ha den
alltid i närheten av platsen för enheten.

SÄKERHETVARNING:•
Operatören måste vara medveten om säkerhetsföreskrifterna för att
förhindra fysisk skada.
•Alla tryckinnehållande enheter kan explodera, spricka, eller släppa sittinnehåll om de utsätts för övertryck. Vidta alla nödvändiga åtgärder för
att undvika övertryck.
•
Att använda, installera eller underhålla enheten på et sätt som inte
beskrivs i den här manualen kan orsaka dödsfall, allvarlig personskada
eller skada på utrustningen. Detta inkluderar alla förändringar på
utrustningen eller användning av delar som inte har tillhandahållits av
Xylem. Om det uppstår frågor angående den avsedda användningen av
utrustningen, vänligen kontakta Xylems representant innan du fortsätter.
•
Förändra inte tjänsteapplikation utan godkännande från en auktoriserad
Xylem-representant.
FARA: Underlåtelse att följa de här instruktionerna kan resultera i explosion,
egendomsskada, allvarlig personskada och/eller dödsfall.

SICHERHEIT - BEGRIFFE UND SYMBOLE
Om säkerhetsmeddelanden. Det är extremt viktigt att du läser, förstår och följer
säkerhetsmeddelanden och bestämmelser noga innan du hanterar produkten. De är
publicerade för att hjälpa till att förebygga dessa skador:•••

Person olyckor och hälsoproblem
Skador på produkten
Produktfel
RisknivåFARA
VARNINGAKTSAMHETOBSERVERA

Indikering
En farlig situation som, om den inte undviks, kommer at resultera i dödsfall eller.
En farlig situation som, om den inte undviks, kan resultera i dödsfall eller allvarlig.
En farlig situation som, om den inte undviks, kan resultera i mindre eller smärre skada.
En potentiell situation som, om den inte undviks, kan resultera i oönskade följder
En hantering som inte är relaterad till person skada

Riskkategorier
Riskkategorierna kan antingen falla in under risknivåerna eller låta specifika
symboler ersätta de vanliga risknivå- symbolerna. Elektriska faror indikeras med
följande specifika symboler:
EL-FARA:Detta är exempel på kategorier som kan förekomma. De faller in under de vanliga
risknivåerna och kan ha komplementerande symboler:•
Krossfara•
Kap risk•
BlixtfarorANVÄNDARSÄKERHET
Allmänna säkerhetsregler. De här säkerhetreglerna är tillämpliga:••••Håll alltid arbetsytan ren
Var uppmärksam på riskerna som medföljer att ha gas och ångor iarbetsområdet.
Undvik alla elektriska faror. Var uppmärksam på riskerna för el-chock eller
ljusblixtar
Tänk alltid på riskerna för drunkning, elektriska olyckor och brännskador

Säkerhetsutrustning
Använd säkerhetsutrustning i enlighet med företagets bestämmelser. Använd den
här säkerhetsutrustningen inom arbetsområdet:••••Arbetshjälm
Säkerhetsglasögon, helst med sidoskydd
Skyddande skor
Handskar och

•
•
•
•

Gasmask
Hörselskydd
Första-hjälpen-kit
Säkerhetsenheter

OBSERVERA: Använd inte om inte säkerhetenheterna är installerade
Elektriska anslutningar
Elektriska anslutningar måste utföras av elektriker i enlighet med alla internationella,nationella, statliga och lokala bestämmelser. För mer information om krav, seavsnitten som handlar specifikt om elektriska anslutningar.
27

Förebygganden innan arbete
Efterlev dessa säkerhetsföreskrifter innan du arbetar med produkten eller är ianslutning till produkten:
•
•
•
•
•
•
•
•
•
•

Skapa en passande barriär runt arbetsområdet, till exempel ett skyddsstaket
Säkerställ att säkerhetsskydden är på plats och är säkrade
Se till att du har fri reträttväg
Säkerställ att produkten inte kan rulla eller tippa och skada folk eller skada
egendom
Kontrollera att lyftanordningen är i bra skicka
Använd en lyftsele, en säkerhetslina och en andningsapparat, såsom
Krävs Låt alla system och pumpkomponenter kylas av innan du hanterar
Dem Säkerställ att produkten har rengjorts ordentligt
Koppla ifrån och stäng av strömmen till din enhet innan du servar pumpen
Kontrollera explosionsrisken innan du svetsar eller använder elektriska
handverktyg

Tvätta huden och ögonen. Följ dessa förfarande för kemikalier eller farliga vätskor
som har kommit i kontakt med dina ögon eller med huden:
Tillstånd
Kemikalier eller
farliga vätskor iögonenKemikalier eller
farliga vätskor
på hudÅtgärd
1. Håll isär ögonlocken med fingrarna
2. Skölj ögonen med ögontvätt eller rinnande vatten i minst 15 minuter
3. Sök upp läkarvård
1. Ta bort kontaminerad klädsel
2. Tvätta huden med tvål och vatten i minst 1 minut
3. Sök läkarvård om det behövs

MILJÖSÄKERHET
Arbetsområdet. Håll alltid arbetsstationen ren
Avfalls- och utsläppsbestämmelser
Ta hänsyn till dessa säkerhetsbestämmelser angående avfall och utsläpp:••••

Avyttra allt avfall på ett lagenligt sätt
Hantera och avyttra de behandlade vätskorna i enlighet med de gällande
miljöbestämmelserna
Rengör alla föroreningar i enlighet med säkerhets- och miljöförfaranden
Rapportera alla miljöutsläpp till de tillämpliga myndigheterna
VARNING: Strålningsrisk. Skicka INTE produkten till Xylem om den har
utsatts för radioaktiv strålning.

Elektroniska delar
Vänd dig till din lokala återvinningsstation och fråga om återvinningen för
elektriska delar.
Riktlinjer för återvinning
Följ alltid lokala lagar och regler angående återvinning.
VARNING: Denna pump är konstruerad ENDAST för bruk med söt- och
saltvatten. Användning med andra farliga, frätande eller brännande material kan
resultera i skada på pump och den omgivande miljön, möjlig exponering för
farliga ämnen och personskada.

VARNING: Använd inte pumpen om den är skadad, t.ex. om tryckomkopplaren är bränd eller trasig, elektriska ledningar och/eller kontakter är exponerade.

C

STOPP
STOP

28

Installation/montering
VAR FÖRSIKTIG: Inte avsedd för kontinuerlig användning. Endast
intermittent bruk.
VAR FÖRSIKTIG: Installationsanvisningar: För att undvika
brandrisk. Se till att området där pumpen installeras är isolerat
rån gas, bränsletankar, elledningshylsor och brandfarliga material.
Underlåtelse att göra det kan leda till personskada eller död.
FÖRSIKTIGHET: Installationsvarning: För att undvika brandrisk,
installera inte denna produkt om den påvisar märkbara skador. Om
skadan exponerar elkontakter, kan gnistor antända bränsleångor.
Försummelse att inte följa denna försiktighetsvarning kan leda till
personskada eller dödsfall.
Figur 2.
LodrätVerticalHorizontalVågrät

OBS! Do
SänkNot
inteSubmerge
ned i vatten
NOTE:

1: Välj pumpplats. Pumpen måste
installeras i ett torrt, ventileratområde.
2: Anslut beslagen som levererades
med pumpen båtens rörledningar.
Använd en böjlig slang med 13
mm innerdiameter (helst omflätad
eller förstärkt) för att reducera
vibration i rörledningssystemet(fig. 1). Använd slangklämmor påden hullingförsedda, påskjutbaraslangkopplingen.
Viktigt: Installera ett silpumpintag för
att skydda ventilerna mot skräp.
3: Sätt fast pumpen på en flat yta. Om
den monteras vertikalt; installera
med pumphuvudet nedåtvänt (fig.
2). Dra inte åt skruvarna för hårtför att låga gummimonteringarnaabsorbera vibration.

Figur 1.

4: Installera intags- och uttagsbeslagen(A och B). Skjut ordentligt
glidklämmorna (C) framåt för att låsabeslagen. – Figur 3
Figur 3.

Intagssil (A)Utlopp (B)Figur 4.

Intag för
landvatten

Varmvattenberedare

Vattentank

Backventil
Pumpgard-sil
Anslut inte Autofill tillpumpens sugledning

Autofill-tankventil,
Anslut till tanken
29

VARNING!
BR A N DFA R A
Elledningarna måste uppfylla gällande elstandarder och inkluderarkorrekt anpassad säkring eller överspänningsskydd. Olämpliga
elledningar orsaka brand med personskada eller död som resultat.
VAR FÖRSIKTIG: Informationen om rekommenderad ledningsdragning
ges som referens. För information, se referens ABYC E-11, AC andDC Electrical Systems on Boats guidelines (riktlinjer för växel- ochlikströmselsystem på båtar).

Ledningstabell
Total trådlängd – fot (meter)
Pumpspänning

0 - 20 fot(0 - 6 m)

20 - 35 fot(6 - 9 m)

35 - 55 fot(9 - 12 m)

12 VDC		
24 VDC		#14 AWG(2,5 mm2)#16 AWG(1,5 mm2)#12 AWG(4 mm2)#14 AWG(2,5 mm2)#10 AWG(6 mm2)#12 AWG(4 mm)VAR FÖRSIKTIG: Motorhuset kan bli hett under långvarig drift.
Långvarig hudkontakt kan orsaka brännsår.
VARNING: Elektriska anslutningar ska göras av en behörig
marineltekniker.
VAR FÖRSIKTIG: Koppla från strömtillförseln från systemet innan
du börjar arbeta på enheten för att undvika personskada, skada på
omgivningen och/eller produktskada.

Figur 5.

inline säkring
grön
jordledare

eller
Gray
säkring

Röd (+)

brytarspets
Svart (-)

12V batteri

Börja
Figur 6.

InitialFörstaStart
start Up

Behov avOff
Demand• Fyll vattentanken• Öppna alla kranar• Slå på PÅ pumpen(“ON”)OBS! Det tar 5
sekunder att slå på
enheten.
• När det inte längre
finns luft i vattnet,
ska alla kranar
stängs så att dubörjar med kranen
närmast pumpen(fig. 6)

Behov påOnDemandViktigt: Låt inte pumpen vara igång oavbrutet längre är 15 minuter.
30

Vinterförberedelser
VAR FÖRSIKTIG: Om du låter vattnet frysa i systemet kan detta resultera
i skada på pump och rörledningssystem. Icke-toxiskt frostskyddsmedel
för drickbart vatten får användas med Jabsco-pumpar. Följ tillverkarens
rekommendationer. Du hänvisas till utrustningstillverkarens instruktioner
för deras särskilda rutiner för vinterförberedelse och dränering. Använd inte
frostskyddsmedel för fordon för att förbereda dricksvattensystem för vintern.
Dessa lösningar är mycket toxiska och kan orsaka allvarlig personskada eller
död efter förtäring.
1. Dränera vattentanken. Öppna tanktömningsventilen. Du kan använda
pumpen för att dränera tanken genom att öppna alla kranar i systemet.
Låt pumpen vara igång tills tanken är tom. Låt inte pumpen vara igång
oavbrutet längre är 15 minuter.
2. Öppna alla kranar och dränera vattnet från rörledningssystemet. Slå av
strömmen till pumpen. Se till att allt vatten från dräneringsledningarna har
dränerats.
3. Avlägsna snabbkopplingsin- och uttagen från pumpen och slå på
pumpen för att pumpa ut det återstående vattnet från pumphuvudet. Se
till att du har ett kärl eller en trasa under pumpen så att vattnet inte spillspå båten. Slå av pumpen är rörledningarna är tomma. Lämna beslagenfrånkopplade från pumpen tills systemet kan användas igen. Gör ennotering på påfyllningshalsen att rörledningen inte är ansluten.
4. Se till att alla kranar lämnas öppna för att skydda rörledningarna mot
skada.

Modell Referens
ModellNominell DC VoltÖppna Flow
GPM (LPM)

Arbetstryck PSI(Bar)

Skära ut Tryck
PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Dimensioner:

Bredd – 6 1/8 inches (155.58mm), Höjd – 4 3/4 inches (120.65mm),
Längd– 9 7/8 inches (250.83mm)

Drift
Attribut

12 Volt

24 Volt

5 sekunder 5 sekundereller mindre eller mindre
5 sekunder 5 sekundereller mindre eller mindre

Tid att nå full fart efter kran öppnas
Tid att stänga efter kran helt stängdÖverspänningströskelinställning ( Enheten stängs av automatiskt / kommer
16 Volts DC
inte att köra )Under spänningströskeln inställning ( Enheten stängs av automatiskt /9 Volts DC
kommer inte att köra )Enligt gällande tröskelinställning ( Enheten stängs av automatiskt /2 AMPSkommer inte att köra )Nyckel18 Volts DC
2 AMPS

Modell nr.

Mängd

2

Ventilsats

18911-7030

13Membransats

18912-3040

1

4Fäll ned att inhysa satsen

18915-9002

1

5

Tryckströmbrytare

37121-0010

1

6

Tjänste- sats

18920-9043

1

Motor 12V DC

18753-5236

1

Motor 24V DC

18753-5237

1

8

Sidogem

30648-1000

1

9

Head enhet för pump

18914-0030

1

10

Pumpgard™ filter, (Inte-visat)

46400-9500

1

7

Beskrivning

31 Volts DC

Tillbehör - Portbeslag

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Installeras till ABYC
H-22 och E-11
Vi försäkrar härmed under eget ansvar att produkten som denna
försäkran gäller har utformats i enlighet med följande direktiv:
Direktivet för elektromagnetisk kompatibilitet 2004/108/EC
Fritidsbåtsdirektivet 2003/44/EC
RoHS 2011/65/EU
Med ett relevant urval av följande standarder:
ISO 8846:1990 / Skydd mot antändning av omgivande gaser
31

Bomba para sistema
automático de agua
El propósito de este manual es proporcionar la información necesaria para lainstalación, operación y mantenimiento del producto.
PELIGRO: Lea este manual cuidadosamente antes de instalar, usar oreparar este producto. El incumplimiento de las instrucciones contenidas
en este manual puede ocasionar explosión, daños a la propiedad, lesiones
personales graves o la muerte.
AVISO: Guarde este manual para referencia futura y manténgalo disponible
donde esté ubicada la unidad.

SEGURIDAD
ADVERTENCIA:

•
•
•

•

El operador debe ser consciente de las precauciones de seguridad paraevitar lesiones físicas.
Cualquier dispositivo que contiene presión puede explotar, reventar
o descargar su contenido si existe un exceso de presión. Tome todas lasmedidas necesarias para evitar la un exceso de presión.
Operar, instalar o reparar la unidad en cualquier modo que no esté tratado
en este manual podría ocasionar muerte, lesiones personales o daños alequipo. Esto incluye cualquier modificación realizada al equipo o el uso depiezas no suministradas por Xylem. Si tuviese alguna pregunta con relación
al uso previsto del equipo, póngase en contacto con un representante deXylem antes de proceder.
No cambie la aplicación de servicio sin el consentimiento de unrepresentante autorizado de Xylem.

PELIGRO: El incumplimiento de estas instrucciones puede ocasionar explosión,daños a la propiedad, lesiones personales graves o la muerte.

SÍMBOLOS Y TERMINOLOGÍA DE SEGURIDAD
Acerca de los mensajes de seguridad.
Es muy importante que lea, entienda y siga cuidadosamente los mensajes deseguridad y las regulaciones antes de manipular el producto. Se publican para ayudara prevenir estos peligros:
1.
2.
3.

Accidentes personales y problemas de salud
Daños ocasionados al producto
Funcionamiento defectuoso del producto
Nivel de riesgo
PELIGROADVERTENCIA
PRECAUCIÓNAVISO

Indicación
Una situación peligrosa que, si no se evita, resultará en muerte o lesiones graves.
Una situación peligrosa que, si no se evita, podría resultar en lesiones graves o la muerte.
Una situación peligrosa que, si no se evita, podría resultar en lesiones menores o moderadas.
Una situación potencial que, si no se evita, podría resultar en condiciones no deseables
Una práctica no relacionada con lesiones personales

Categorías de peligro. Las categorías de peligro pueden caer bajo algún nivel
de riesgo o permitir que algún símbolo específico reemplace el símbolo depeligro común. Los peligros eléctricos se indican mediante los siguientes símbolos
específicos:
RIESGO ELÉCTRICO
Estos son ejemplos de otras categorías que pueden ocurrir. Caen bajo los niveles depeligro común y pueden utilizar símbolos complementarios:
1.
2.
3.

Peligro de aplastamiento
Peligro de corte
Peligro de descarga de arco voltaico

SEGURIDAD DEL USUARIO
Normas generales de seguridad.
Estas reglas de seguridad son pertinentes:••••

Mantenga siempre el área de trabajo limpia.
Preste atención a los riesgos presentados por gases y vapores en el área de trabajo.
Evite todos los peligros eléctricos. Preste atención a los riesgos de choque eléctrico
o de descargas de arco voltaico.
Tenga siempre en cuenta el riesgo de ahogamiento, accidentes eléctricos y lesiones
por quemaduras.

Equipo de seguridad. Utilice equipo de seguridad conforme a las normas de lacompañía. Use este equipo de seguridad dentro de la zona de trabajo:•
Casco protector•
Máscara de gas•
Gafas protectoras, preferiblemente con•
Protección auditiva
protectores laterales•
Botiquín de primeros auxilios•
Calzado de seguridad•
Dispositivos de seguridad•
Guantes protectores
AVISO: Nunca opere una unidad a menos que los dispositivos de seguridad estén instalados.
Conexiones eléctricas
Las conexiones eléctricas las ha de hacer un electricista certificado siguiendo todos
los reglamentos internacionales, nacionales, estatales y locales. Para obtener más
información acerca de los requisitos, consulte las secciones que tratan específicamentede las conexiones eléctricas.
32

Precauciones antes del trabajo. Observe estas precauciones de seguridad antes
de trabajar con el producto o entrar en contacto con este:
•
•
•
•
•
•
•
•
•
•

Proporcione una barrera adecuada alrededor del área de trabajo, por
ejemplo, una barandilla
Asegúrese de que todas las protecciones de seguridad estén en su lugar ybien fijadas
Asegúrese de tener un camino de retirada despejado
Asegúrese de que el producto no puede rodar o caer y herir a personas ocausar daños a la propiedad
Asegúrese de que el equipo de elevación esté en buenas condiciones
Use un arnés de elevación, un cordón de seguridad y un dispositivo derespiración según sea necesario
Permita que todos los componentes de la bomba y el sistema se enfríen antes
de manipularlos
Asegúrese de que el producto se haya limpiado cuidadosamente
Desconecte y bloquee la alimentación antes de iniciar el mantenimiento dela bomba
Compruebe el riesgo de explosión antes de soldar o usar herramientas
eléctricas de mano

Lávese la piel y los ojos. Siga estos procedimientos para productos químicos ofluidos peligrosos que hayan entrado en contacto con los ojos o la piel:Condición

Productos químicos ofluidos peligrosos en
los ojos
Productos químicos ofluidos peligrosos enla pielAcción1. Sostenga los párpados separados a la fuerza con los dedos
2. Enjuague los ojos con colirio o agua corriente durante al menos 15 minutos
3. Procure atención médica
1. Quítese la ropa contaminada
2. Lave la piel con jabón y agua durante al menos 1 minuto
3. Procure atención médica, si fuese necesario

SEGURIDAD AMBIENTAL
El área de trabajo.
Mantenga siempre el puesto de trabajo limpio
Normativas sobre residuos y emisiones
Observe estas normas de seguridad en cuanto a emisiones y residuos:••••

Deshágase adecuadamente de todos los residuos
Manipule y deseche el líquido procesado siguiendo las normativas ambientales
pertinentes
Limpie todos los derrames con arreglo a los procedimientos de seguridad yambientales
Informe de todas las emisiones ambientales a las autoridades competentes
ADVERTENCIA: Peligro de radiación. NO envíe el producto a Xylem si haestado expuesto a radiaciones nucleares.

Instalación eléctrica. Para conocer los requisitos de reciclaje de las instalaciones
eléctricas, consulte a su compañía eléctrica local.
Pautas de reciclaje. Siga siempre las leyes y normativas locales sobre reciclaje.
ADVERTENCIA: La bomba está diseñada para funcionar con agua dulce yagua salada ÚNICAMENTE. Su uso con cualquier otro material peligroso,
cáustico o corrosivo podría provocar daños a la bomba y al entorno
circundante, la posibilidad de exposición a sustancias peligrosas y lesiones.

ADVERTENCIA: No use una bomba si presenta daños, como
conmutador de presión quemado o roto, o cables y/o contactos
eléctricos expuestos.

C

ALTO
STOP

33

Instalación/Montaje
PRECAUCIÓN: No apta para servicio continuo, sólo para usointermitente.
PRECAUCIÓN: Notas acerca de la instalación: Para evitar el riesgo
de incendio. Asegúrese de que el área donde se instala la bomba
esté aislada del gas, tanques de combustible, conductos de cableado
eléctrico o sustancias inflamables. Si no se respeta esta precaución,
pueden causarse lesiones o la muerte.
PRECAUCIÓN: Notas de instalación: Para evitar el riesgo deincendio. No instale este producto si está visiblemente dañado.
Si contactos eléctricos quedan expuestos por el daño, las chispas
eléctricas podrían encender gases combustibles. No hacerlo
podría causar lesiones o la muerte.
1: Seleccione la ubicación de la bomba. La bomba debe insta­­larse en unárea seca y ventilada.
Figura 2.
Horizontal
Horizontal

VerticalVertical

NOTE:
Notsumergir
Submerge
NOTA:DoNo

2: Conecte las conexiones provistas
con la bomba a las tuberíasde la embarcación. Utilice una
manguera flexible de ½” (13 mm)
de D.I. (preferentemente trenzada
Figura 1.
o reforzada) para reducir las
vibraciones a través del sistemade tuberías (Figura 1). Utiliceabrazaderas en los conectoresacanalados para manguera.
Importante: Instale un filtro en laentrada de la bomba para protegerlas válvulas contra los desechos.
3: Fije la bomba a una superficie
plana. Si el montaje es vertical;
instálela con el cabezal de labomba hacia abajo (Figura 2). No
apriete los tornillos en exceso para
permitir que los montajes de gomaabsorban las vibraciones.
4: Instale las conexiones de entrada (A) y de descarga (B). Empuje
firmemente las grapas laterales (C) hacia adelante para bloquear lasconexiones en su lugar. - Figura 3
Figura 3.

Filtro de entrada (A)Descarga (B)Figura 4.

Tanquede agua

Entrada de aguadel suministro
públicoCalentador
de agua

Válvulade retención

No conecte el
autollenado a latubería de succión dela bomba
34

FiltroPumpgard
Válvula de autollenado deltanque, conectar al tanqueADVERTENCIAPELIGRO DE INCENDIO
El cableado debe cumplir las normas eléctricas aplicables e incluir
un fusible o disyuntor de tamaño apropiado. El cableado incorrecto
puede originar incendios que pueden causar lesiones o muerte.
PRECAUCIÓN: Se provee información del cableado sugerido como referencia.
Para más información, consulte las directrices de la norma E-11 del ABYC, “SistemasEléctricos de CA y CC Instalados en Embarcaciones”.

Tabla de tamaños de cables

Longitud total del cable – pies (metros)
Voltaje dela bomba

0 - 20 pies
(0 - 6 m)

20 - 35 pies
(6 - 9 m)

35 - 55 pies
(9 - 12 m)

12 VCC		
24 VCC		Nº14 AWG(2.5 mm2)
Nº16 AWG(1.5 mm2)

Nº12 AWG(4 mm2)Nº14 AWG(2.5 mm2)

Nº10 AWG(6 mm2)Nº12 AWG(4 mm)

PRECAUCIÓN: La carcasa del motor puede calentarse durante el funcionamiento
por períodos largos. El contacto prolongado con la piel puede causar quemaduras.
ADVERTENCIA: Las conexiones eléctricas deberían ser realizadas
por un técnico eléctrico naval competente.
PRECAUCIÓN: Desconecte la energía del sistema antes de comenzar a trabajar en la
unidad para evitar lesiones personales, daños al entorno circundante y/o daños a la unidad.

Figura 5.

Fusible en línea
VerdeTierraeller
Gris
FusibleRojo (+)

Interruptor
Negro (-)

Batería 12V DC

Empiece para arriba
Figura 6.

Initial
Puestaen Start
marchaUp
inicialDemandadesactivada
DemandOff• Llene el tanquede agua• Abra todos losgrifos• Encienda la bomba
NOTA: Espere
un retardo de 5
segundos para elencendido.
• Cuando el agua
esté libre de aire,
cierre todos losgrifos empezando
por el más cercano
a la bomba (Figura
6)

DemandOn
Demandaactivada

Importante: No opere la bomba más de 15 minutos seguidos.
35

Acondicionamiento para invierno
PRECAUCIÓN: Si se deja congelar el agua en el sistema, puede ocasionarse daños
a la bomba y al sistema de tuberías. En las bombas Jabsco puede usarse anticongelanteno tóxico para agua potable. Siga las recomendaciones del fabricante. Consulte en las
instrucciones del fabricante de la embarcación o el equipo los procedimientos específicosde acondicionamiento para invierno. No utilice anticongelante para automóviles paraacondicionar para invierno los sistemas de agua potable. Estas soluciones son altamentetóxicas y pueden causar graves heridas o la muerte si se ingieren.
1. Drene el tanque de agua. Abra la válvula de drenaje del tanque. Puede utilizar la bomba
para drenar el tanque abriendo todas los grifos del sistema. Permita que la bomba
funcione hasta que el tanque esté vacío. No opere la bomba más de 15 minutos seguidos.
2. Abra todos los grifos y purgue el agua del sistema de tuberías. Apague la bomba.
Asegúrese de que se haya desagotado toda el agua de las tuberías de drenaje.
3. Retire las conexiones rápidas de salida y entrada de la bomba y enciéndala para bombear
hacia afuera el agua remanente en el cabezal de la misma. Asegúrese de tener unrecipiente para recolectar el agua o un paño debajo de la bomba para evitar que el agua
se derrame sobre la embarcación. Apague la bomba una vez que las tuberías estén vacías.
Deje las conexiones desconectadas hasta que el sistema esté listo para ser utilizado
nuevamente. Haga una nota en su llenador de tanque para recordar que las tuberías no
están conectadas.
4. Asegúrese de que todos los grifos estén abiertos para evitar daños a las tuberías.
Modelo de Referencia
ModeloVoltios nominales
de la C.C.

Abra el flujo
GPM (LPM)

Presión de funcionamiento PSI (Bar)

Presión del recorte
PSI (BAR)

42755-0092

12V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0094

24V dc5.0 (19)40 (2.75)

60 (4.1)

42755-0392

12V dc5.0 (19)25 (1.72)

35 (2.4)

42755-0394

24V dc5.0 (19)25 (1.72)

35 (2.4)

Dimensiones:

Ancho – 6 1/8 inches (155.58mm), Altura – 4 3/4 inches (120.65mm),
Largo – 9 7/8 inches (250.83mm)

Operación
Atributo
Hora de alcanzar velocidad completa después del grifo abierto
Hora de apagar después del grifo cerrado totalmente
Sobre la configuración del umbral del voltaje (la unidad apagó/no se
ejecutará automáticamente)
Bajo configuración del umbral del voltaje (la unidad apagó/no se ejecutará
automáticamente)
Bajo configuración actual del umbral (la unidad apagó/no se ejecutará
automáticamente)Clave

24 Volt
5 segundos
o menos
5 segundos
o menos

16 Volts DC

31 Volts DC

9 Volts DC

18 Volts DC

2 AMPS

2 AMPS

Modelo No.

Cant.

2

Kit de la válvula

18911-7030

1

3

Kit de diafragma

18912-3040

1

4Baje el kit de la cubierta

18915-9002

15Interruptor de presión

37121-0010

1

6Mantenga el kit

18920-9043

1

Motor 12V DC

18753-5236

1

Motor 24V DC

18753-5237

1

8

Clips laterales

30648-1000

1

9Asamblea principal de la bomba

18914-0030

1

10

Tamiz de Pumpgard™ (no mostrado)

46400-9500

1

7

Descripción

12 Volt
5 segundos
o menos
5 segundos
o menos

Accessorios – Adaptadores de cierre rápido

30649-1000
QUAD PORT x 1/2"
MALE QEST. STRAIGHT

30654-1000
QUAD PORT x 1/2"
HOSE BARB STRAIGHT

30655-1000
QUAD PORT x
1/2" MALE QEST.
90º ELBOW

30653-1000
QUAD PORT x 3/4"
HOSE BARB STRAIGHT

30651-1000
QUAD PORT x
1/2" HOSE BARB
90º ELBOW

30650-1000
QUAD PORT x
GARDEN HOSE STRAIGHT

30642-1000
QUAD PORT x
3/4" HOSE BARB
90º ELBOW

Instale de acuerdo con
ABYC H-22 y E-11
Declaramos, bajo nuestra absoluta responsabilidad, que nuestro
producto al que corresponde esta declaración ha sido diseñado
para cumplir con las siguientes Directivas:
Directiva de Compatibilidad Electromagnética 2004/108/CE
Directiva de Embarcaciones Recreativas 2003/44/CE
RoHS 2011/65/UE (Restricción de Sustancias Peligrosas)
Con las secciones correspondientes de las siguientes Normas:
ISO 8846:1990 / Protección contra Ignición
36

XYLEM LIMITED WARRANTY WARRANTS THIS PRODUCT TO BE FREE OF DEFECTS AND WORKMANSHIP FOR A PERIOD
OF 3 YEARS. THE WARRANTY IS EXCLUSIVE AND IN LIEU OF ANY AND ALL OTHER EXPRESS OR IMPLIED WARRANTIES,GUARANTEES, CONDITIONS OR TERMS OF WHATEVER NATURE RELATING TO THE GOODS PROVIDED HEREUNDER,INCLUDING WITHOUT LIMITATION ANY IMPLIED WARRANTIES OF MERCHANTABILITY AND FITNESS FOR A PARTICULARPURPOSE, WHICH ARE HEREBY EXPRESSLY DISCLAIMED AND EXCLUDED. EXCEPT AS OTHERWISE PROVIDED BY LAW,BUYER’S EXCLUSIVE REMEDY AND SELLER’S AGGREGATE LIABILITY FOR BREACH OF ANY OF THE FOREGOING WARRANTIES ARE LIMITED TO REPAIRING OR REPLACING THE PRODUCT AND SHALL IN ALL CASES BE LIMITED TO THE AMOUNTPAID BY THE BUYER HEREUNDER. IN NO EVENT IS SELLER LIABLE FOR ANY OTHER FORM OF DAMAGES, WHETHERDIRECT, INDIRECT, LIQUIDATED, INCIDENTAL, CONSEQUENTIAL, PUNITIVE, EXEMPLARY OR SPECIAL DAMAGES, INCLUDING BUT NOT LIMITED TO LOSS OF PROFIT, LOSS OF ANTICIPATED SAVINGS OR REVENUE, LOSS OF INCOME, LOSS OF
BUSINESS, LOSS OF PRODUCTION, LOSS OF OPPORTUNITY OR LOSS OF REPUTATION. THIS WARRANTY IS ONLY A
REPRESENTATION OF THE COMPLETE LIMITED WARRANTY. FOR A DETAILED EXPLANATION, PLEASE VISIT US AT www.
xylemflowcontrol.com/support/, CALL OUR OFFICE NUMBER LISTED, OR WRITE A LETTER TO YOUR REGIONAL OFFICE.
GARANTIE DE XYLEM LIMITED GARANTIT QUE CE PRODUIT EST EXEMPT DE DÉFAUT MATÉRIEL ET DE
FR LA
MAIN-D’OEUVRE POUR UNE DURÉE DE 3 ANNÉES. CETTE GARANTIE EST EXCLUSIVE ET EN LIEU DE TOUTES AUTRESGARANTIES EXPRESSES OU IMPLICITES, GARANTIES, CONDITIONS OU DISPOSITIONS DE TOUTE NATURE EN REGARD
DES BIENS FOURNIS CI-APRÈS, INCLUANT SANS LIMITE TOUTE GARANTIE IMPLICITE DE QUALITÉ MARCHANDE ET
D’ADAPTATION À UN USAGE PARTICULIER, QUI SONT CI-APRÈS FORMELLEMENT RÉFUTÉS ET EXCLUS. SAUF LORSQUE
LA LOI LE PRESCRIT, LE SEUL RECOURS DE L’ACHETEUR ET LA RESPONSABILITÉ REGROUPÉE DU VENDEUR POURVIOLATION DES GARANTIES CI-DESSUS EST LIMITÉ À LA RÉPARATION OU AU REMPLACEMENT DU PRODUIT ET SERADANS TOUS LES CAS LIMITÉ AU MONTANT DÉBOURSÉ PAR L’ACHETEUR POUR LE PRODUIT DÉFECTUEUX. EN AUCUN
CAS LE VENDEUR NE PEUT ÊTRE TENU RESPONSABLE D’AUCUNE FORME DE DOMMAGE, QU’IL SOIT DIRECT, INDIRECT,DÉTERMINÉ, CONSÉCUTIF, PUNITIF, EXEMPLAIRE OU DOMMAGES SPÉCIAUX, INCLUANT MAIS SANS S’Y LIMITER À LA
PERTE DE PROFIT, PERTE D’ÉCONOMIE OU DE REVENU ANTICIPÉ, PERTE DE BÉNÉFICE, PERTE D’AFFAIRES, PERTE DE
PRODUCTION, PERTE D’OPPORTUNITÉ OU PERTE DE RÉPUTATION. CETTE GARANTIE EST LA SEULE REPRÉSENTATION DE
LA GARANTIE LIMITÉE COMPLÈTE. POUR OBTENIR UNE EXPLICATION DÉTAILLÉE VEUILLEZ VISITER NOTRE SITE www.
xylemflowcontrol.com/support/, COMPOSER LE NUMÉRO DE TÉLÉPHONE DE NOTRE BUREAU INDIQUÉ OU ÉCRIRE UNE
LETTRE À NOTRE BUREAU RÉGIONAL.
BESCHRÄNKTE GARANTIE VON XYLEM GARANTIERT FÜR EINEN ZEITRAUM VON 3 JAHREN, DASS DIESESDE DIEPRODUKT FREI VON MATERIAL- UND VERARBEITUNGSMÄNGELN IST. DIESE GARANTIE IST DIE EINZIGE GÜLTIGEGARANTIE UND ERSETZT ALLE ANDEREN AUSDRÜCKLICHEN ODER KONKLUDENTEN GARANTIEN, BEDINGUNGENODER BESTIMMUNGEN, EGAL WELCHER ART, IN BEZUG AUF DIE HIERUNTER BEREITGESTELLTEN PRODUKTE,
EINSCHLIESSLICH (OHNE BESCHRÄNKUNG) ALLE KONKLUDENTEN GARANTIEN DER MARKTGÄNGIGKEIT UND
EIGNUNG FÜR EINEN BESTIMMTEN ZWECK, DIE HIERMIT AUSDRÜCKLICH ABGELEHNT UND AUSGESCHLOSSEN
WERDEN. VORBEHALTLICH ANDERER GESETZLICHER BESTIMMUNGEN IST DER AUSSCHLIESSLICHE ANSPRUCH UND
DER GESAMTE HAFTUNGSUMFANG DES VERKÄUFERS BEI VERLETZUNG DER OBIGEN GARANTIEN AUF DIE REPARATURODER DEN AUSTAUSCH DES PRODUKTS UND IN JEDEM FALL AUF DEN VOM KÄUFER HIERUNTER BEZAHLTEN BETRAGBESCHRÄNKT. AUF KEINEN FALL IST DER VERKÄUFER FÜR ANDERE SCHÄDEN HAFTBAR, EINSCHLIESSLICH DIREKTEUND INDIREKTE SCHÄDEN, SCHADENSERSATZ, NEBENSCHÄDEN, FOLGESCHÄDEN, STRAFSCHADENSERSATZ,
EXEMPLARISCHER SCHADENSERSATZ ODER BESONDERE SCHÄDEN UND EINSCHLIESSLICH (OHNE BESCHRÄNKUNG)
ENTGANGENEN GEWINN, VERLUST ERWARTETER EINSPARUNGEN ODER EINKOMMEN, ERTRAGSAUSFALL, GESCHÄFTSAUSFALL, PRODUKTIONSAUSFALL, ENTGANGENEN CHANCEN ODER RUFSCHÄDIGUNG. DIESE GARANTIE IST NUR EINEERKLÄRUNG DER VOLLSTÄNDIGEN BESCHRÄNKTEN GARANTIE. EINE AUSFÜHRLICHE ERLÄUTERUNG FINDEN SIE UNTER
www.xylemflowcontrol.com/support/, SIE KÖNNEN UNS AUCH UNTER DER ANGEGEBENEN BÜRONUMMER ANRUFENODER EIN SCHREIBEN AN DAS FÜR SIE ZUSTÄNDIGE REGIONALBÜRO SENDEN.
GARANZIA LIMITATA XYLEM GARANTISCE CHE I PRODOTTI SIANO ESENTI DA DIFETTI DI MATERIE PRIME E
IT LA
MANODOPERA PER UN PERIODO DI 3 ANNI. LA PRESENTE GARANZIA ANNULLA E SOSTITUISCE QUALSIASI ALTRAGARANZIA, CONDIZIONE O TERMINE ESPRESSO O IMPLICITO, DI QUALSIVOGLIA NATURA, RELATIVO ALLA MERCEFORNITA, COMPRESA MA SENZA LIMITAZIONE ALCUNA QUALSIASI GARANZIA IMPLICITA DI COMMERCIABILITA’ E
ADEGUATEZZA AD UN PARTICOLARE SCOPO, CHE SIA ESPRESSAMENTE NEGATO ED ESCLUSO. A MENO CHE DIVERSAMENTE PREVISTO DALLA LEGISLAZIONE IN VIGORE, IL RIMEDIO ESCLUSIVO DELL’ACQUIRENTE E LA RESPONSABILITA’
GENERALE DEL FORNITORE NEL CASO DI VIOLAZIONE ALLA PRESENTE GARANZIA SONO LIMITATE ALLA RIPARAZIONE OSOSTITUZIONE DEL PRODDO ED AD OGNI MODO ALL’IMPORTO CORRISPOSTO DALL’ACQUIRENTE. NEL CASO IN CUI IL
VENDITORE SIA RESPONSABILE DI QUALSIASI ALTRO POSSIBILE DANNO, DIRETTO, INDIRETTO, LIQUIDATO, INCIDENTE,CONSEQUENTE, PUNITIVO, ESEMPLARE O SPECIALE, COMPRESA MA NON SOLO LA PERDITA DI UTILE, RISPARMIO O
FATTURATO, REDDITO, PRODUZIONE, OPPORTUNITA’ O REPUTAZIONE. LA PRESENTE GARANZIA RAPPRESENTA LA SOLAED UNICA GARANZIA LIMITATA COMPLETA. PER UNA SPIEGAZIONE MAGGIORMENTE DETTAGLIATA, FARE RIFERIMENTO
A www.xylemflowcontrol.com/support/, CONTATTARE IL NUMERO PRECISATO IN SEGUITO OPPURE SCRIVERE AL
PROPRIO UFFICIO REGIONALE.
LIMITED GARANTIE GARANDEERT DAT DIT PRODUCT VRIJ IS VAN GEBREKEN EN FABRICAGEFOUTENNL XYLEMGEDURENDE EEN PERIODE VAN 3 JAAR. DE GARANTIE IS EXCLUSIEF EN IN PLAATS VAN ALLE ANDERE EXPLICIETE
OF IMPLICIETE GARANTIES OF VOORWAARDEN, VAN WELKE AARD DAN OOK MET BETREKKING TOT DE HIERONDERGENOEMDE PRODUCTEN, INCLUSIEF ZONDER BEPERKING ALLE GEÏMPLICEERDE GARANTIES VAN VERKOOPBAARHEID EN GESCHIKTHEID VOOR EEN BEPAALD DOEL, DIE HIERBIJ UITDRUKKELIJK WORDEN AFGEWEZEN EN
BUITENGESLOTEN. TENZIJ ANDERS BEPAALD DOOR DE WET, IS KOPER’S EXCLUSIEVE VERHAAL EN VERKOPER’S TOTALEAANSPRAKELIJKHEID VOOR HET SCHENDEN VAN EEN VAN DE BOVENSTAANDE GARANTIES BEPERKT TOT HET REPAREREN OF VERVANGEN VAN HET PRODUCT EN WORDT IN ALLE GEVALLEN BEPERKT TOT HET DOOR DE KOPER HIERONDERBETAALDE BEDRAG. IN GEEN GEVAL IS DE VERKOPER AANSPRAKELIJK VOOR ENIGE ANDERE VORM VAN SCHADE,
DIRECT, INDIRECT, VOORAF VASTGELEGDE, INCIDENTELE, BESTRAFFENDE, MORELE OF SPECIALE SCHADE, INCLUSIEF
MAAR NIET BEPERKT TOT VERLIES VAN WINST, VERLIES VAN VERWACHTE BESPARINGEN OF OPBRENGSTEN, VERLIESVAN INKOMSTEN , VERLIES VAN BEDRIJVIGHEID, VERLIES VAN PRODUCTIE, VERLIES VAN KANS OF VERLIES VAN REPUTATIE. DEZE GARANTIE BETREFT ALLEEN EEN WEERGAVE VAN DE VOLLEDIGE BEPERKTE GARANTIE. RAADPLEEG VOOREEN UITGEBREIDE TOELICHTING www.xylemflowcontrol.com/support/ OF BEL HET WEERGEGEVEN TELEFOONNUMMER
VAN HET BEDRIJF OF SCHRIJF EEN BRIEF NAAR UW REGIOKANTOOR.
BEGRÄNSADE GARANTI GARANTERAR ATT PRODUKTEN ÄR FRI FRÅN MATERIAL- OCH TILLVERKNINGSFELSE XYLEMS
UNDER EN PERIOD AV 3 ÅR. GARANTIN ÄR EXKLUSIV OCH GÄLLER I STÄLLET FÖR ALLA ANDRA UTTRYCKLIGAELLER UNDERFÖRSTÅDDA GARANTIER, OLIKA VILLKOR SOM RELATERAR TILL VARORNA HÄRUNDER, INKLUSIVE OCHUTAN UNDANTAG UNDERSFÖRSTÅDDA GARANTIER FÖR SÄLJBARHET OCH LÄMPLIGHET FÖR ETT SPECIFIKT ÄNDAMÅL,SOM HÄRMED UTTRYCKLIGEN BESTRIDS OCH UNDANTAS. MED UNDANTAG FÖR VAD SOM ANGES I LAGSTIFTNINGEN, ÄR KÖPARENS ENDA ÅTGÄRD OCH SÄLJARENS TOTALA ANSVAR FÖR BROTT MOT NÅGON AV DE FÖREGÅENDEGARANTIERNA BEGRÄNSAT TILL REPARATION ELLER BYTE AV PRODUKTEN, OCH SKA UNDER ALLA FÖRHÅLLANDEN BEGRÄNSAS TILL BELOPPET SOM KÖPAREN BETALAT HÄRUNDER. UNDER INGA FÖRHÅLLANDE ÄR SÄLJAREN ANSVARIGFÖR NÅGON ANNAN FORM AV SKADOR, VARE SIG DET ÄR DIREKTA, INDIREKTA, LEVERANSSKADOR, OFÖRUTSEDDASKADOR, FÖLJDSKADOR, SKADESTÅND SOM UTDÖMS I AVSKRÄCKANDE ELLER BESTRAFFANDE SYFTE, INKLUSIVE
MEN INTE BEGRÄNSAT TILL UTEBLIVEN VINST, FÖRLUST AV FÖRVÄNTAD BESPARING, FÖRLORAD INKOMST, FÖRLUST
AV AFFÄRER, FÖRLUST AV PRODUKTION, FÖRLUST AV MÖJLIGHET ELLER FÖRLORAT ANSEENDE. DENNA GARANTI ÄR
ENDBART EN REPRESENTATION AV DEN FULLSTÄNDIGA BEGRÄNSADE GARANTIN. FÖR EN DETALJERAD FÖRKLARING,BESÖK OSS PÅ www.xylemflowcontrol.com/support/, RING VÅRT KONTORSNUMMER I LISTAN ELLER SKRIV ETT BREV
TILL DITT REGIONALA KONTOR.
GARANTÍA LIMITADA DE XYLEM GARANTIZA QUE ESTE PRODUCTO CARECE DE DEFECTOS EN MATERIALES Y
ES LAMANO DE OBRA DURANTE UN PERÍODO DE 3 AÑOS. LA GARANTÍA ES EXCLUSIVA Y SUSTITUYE A CUALQUIEROTRA GARANTÍA EXPRESA O IMPLÍCITA, GARANTÍAS, CONDICIONES O TÉRMINOS DE CUALQUIER NATURALEZARELACIONADOS CON LOS ARTÍCULOS PROPRCIONADOS A CONTINUACIÓN, INCLUIDAS SIN LIMITARSE A CUALQUIERGARANTÍA IMPLÍCITA DE COMERCIABILIDAD E IDONEIDAD PARA UN FIN PARTICULAR, EXPRESAMENTE EXCLUIDA Y
DENEGADA POR LA PRESENTE. EXCEPTO CUANDO LA LEY DICTE ALGO DISTINTO, EL ÚNICO RECURSO DEL COMPRADORY LA RESPONSABILIDAD TOTAL DEL VENDEDOR EN CASO DE QUE SE INFRINJAN CUALESQUIERA DE LAS GARANTÍASANTERIORES SE LIMITAN A LA REPARACIÓN O LA SUSTITUCIÓN DEL PRODUCTO Y EN TODOS LOS CASOS SE LIMITARÁ AL
IMPORTE PAGADO POR EL COMPRADOR SEGÚN LO ESTIPULADO EN ESTE DOCUMENTO. EN NINGÚN CASO, EL VENDEDOR ES RESPONSABLE DE NINGÚN OTRO TIPO DE DAÑO, SEA ESTE DIRECTO, INDIRECTO, LIQUIDADO, INCIDENTAL,CONSECUENTE, PUNITIVO, EJEMPLAR O ESPECIAL, INCLUIDO PERO NO LIMITADO A LA PÉRDIDA DE BENEFICIO, PÉRDIDA DE AHORROS O INGRESOS PREVISTOS, PÉRIDA DE INGRESOS, PÉRDIDA DE NEGOCIO, PÉRDIDA DE PRODUCCIÓN,PÉRDIDA DE OPORTUNIDAD O PÉRDIDA DE REPUTACIÓN. ESTA GARANTÍA SOLO ES UNA REPRESENTACIÓN DE LAGARANTÍA LIMITADA COMPLETA. PARA OBTENER UNA EXPLICACIÓN DETALLADA, VISÍTENOS EN www.xylemflowcontrol.com/support/, LLAME AL NÚMERO DE NUESTRA OFICINA QUE APARECE LISTADO O ESCRIBA UNA CARTA A SUOFICINA REGIONAL.

UNITED STATES
17942 Cowan Irvine, CA 92614
Tel: +1 949 608 3900 Fax: +1 949 608 3887
UNITED KINGDOM
Bingley Road, Hoddesdon, Hertfordshire, EN11 0BU
Tel: +44 (0) 1992 450 145 Fax: +44 (0) 1992 467 132

www.xylemflowcontrol.com© 2016 Xylem Inc. All right reserved.
Jabsco is a trademark of Xylem Inc. or one of its subsidiaries.
43000-0118 Rev. E 7/2016