● お客様へ

太陽光発電計測表示・遠隔監視システム

ASP サービス仕様※ ASP サービスの性質上、予告なくアップデートが行われる場合がございます。
予めご了承ください。

2016.08.25

Solar Link ARCH・ソーラー リンク アーク

目次
はじめに........................................................................................................................................................................................................ 1
動作環境（閲覧パソコン）. ......................................................................................................................................................1
Solar Link ARCH のご使用前に............................................................................................................................................................. 2
設定メニュー画面..................................................................................................................................................................................... 5
ID・パスワード変更画面.................................................................................................................................................................. 6
受変電設備の異常判定設定画面.................................................................................................................................................... 7
メール通知項目設定画面.................................................................................................................................................................. 8
メール送信先設定メニュー...........................................................................................................................................................10
更新停止検出設定画面....................................................................................................................................................................14
計算式設定画面..................................................................................................................................................................................15
一括監視画面：パワーコンディショナのみ.................................................................................................................................18
一括監視画面：パワーコンディショナと受変電設備..............................................................................................................20
一括監視画面：買電電力量／売電電力量の表示........................................................................................................................21
メニューアイコン...................................................................................................................................................................................21
現在のトレンドグラフ画面.................................................................................................................................................................23
データ表示画面........................................................................................................................................................................................24
データダウンロード画面.....................................................................................................................................................................26【資料】発電データ等の概略...............................................................................................................................................................27
記録一覧画面............................................................................................................................................................................................28
システム障害履歴画面..........................................................................................................................................................................30
PCS 状況画面.............................................................................................................................................................................................31
PCS 状況一覧画面...................................................................................................................................................................................32
PCS 故障履歴画面...................................................................................................................................................................................33
フレックスエリア...................................................................................................................................................................................35
お知らせ画面............................................................................................................................................................................................39【オプション】受変電設備履歴画面.................................................................................................................................................40
各履歴の CSV ダウンロード................................................................................................................................................................41【オプション】一括監視画面：ストリング状況表示.................................................................................................................42【オプション】PCS・ストリング状況画面....................................................................................................................................43【オプション】グループ監視...............................................................................................................................................................44【ご参考】よくあるお問い合わせ.....................................................................................................................................................45【ご参考】「異常」表示時の確認ポイント.....................................................................................................................................49
スマートフォン・タブレットでの表示..........................................................................................................................................50【ご参考】ソフトウェア仕様...............................................................................................................................................................52

遠隔監視システム ASP サービス 取扱説明書

はじめに
この度は、株式会社ラプラス・システムの、太陽光発電計測表示・遠隔監視システム
Solar Link ARCH（ソーラーリンクアーク）ASP サービスを導入いただき、ありがとうございます。
◆遠隔監視システム ASP サービスについて
ASP サービスとは Application Service Provider Service の略で、インターネットを経由してご要望のサービスを Web ブラウザから提供する仕組みです。
ラプラス・システムがご提供する遠隔監視システムでは、太陽光発電施設に設置した計測システム
が受け取ったパワーコンディショナ（本紙内では「PCS」とも表記）の発電状況、故障の情報、および施工時に指定していただいた機器の情報を、インターネット経由でラプラス・システムのデータサーバーに蓄積し、この情報をインターネットに接続された Windows パソコンの Web ブラウザにてご確認いただけます。その日の発電量のグラフ表示、過去の日毎・月毎等のグラフ表示、ならびに CSV 形式でのデータダウンロードも行うことができます。
太陽光発電施設
パワー
コンディ
ショナ

ラプラス
データ
サーバー

USB

LAN

RS485-1

Internet

OR

Viewer

RS485-2

TX2 RX2
DVI-D

RS232C

DC5V

ZERO

計測機器
お客様パソコン（閲覧パソコン）

動作環境（閲覧パソコン）
項

対応 OS
対応 Web ブラウザ
※ 64bit OS では
32bit のブラウザをご使用ください。
画面解像度

お客様パソコン（閲覧パソコン）※他環境下での閲覧につきまして、動作保証は行っておりません。

目

条

件

Windows 7 / 10 (32bit/64bit)
Internet Explorer 11（ver.9、10 も可）／ Google Chrome ／ Mozilla Firefox※ 上記以外のブラウザではグラフ画面が正しく表示されない場合があります。

Adobe Flash Player のインストールが必要。
http://get.adobe.com/jp/flashplayer/ から無償でダウンロード可能。

1280 x 1024 pixel以上を推奨（1024 x 768 pixelでも使用可）。

※スマートフォン・タブレットでの表示については Page 50 を参照してください。

―1―

SW

PW ST2 ST1TX1 RX1

Solar Link ARCH・ソーラー リンク アーク

Solar Link ARCH のご使用前にSolar Link ARCH をお使いになるには、ログインする必要があります。

ログイン前の確認「ログイン情報」のご提供時に、以下の情報をお知らせします。
□ マスター ID ／マスターパスワード□ 一括監視画面 URL ／設定メニュー画面 URL□ グループ監視画面 URL（グループ画面をオプションで使用される場合）※「ログイン情報」は、原則として、計測データのアップロードの確認完了後にご提供します。

ログイン「ログイン情報」に記載された各画面の URL を入力すると、ログイン画面が表示されます。
マスター ID とマスターパスワードを入力して、「ログイン」ボタンをクリックします。

◆「ログイン状態を保持する。」にチェックを入れてから「ログイン」ボタンをクリックした場合、ログアウトせずに Web ブラウザを終了しても、同じパソコンの Web ブラウザでは URL の入力のみで各画面が表示されます。この状態はログアウト（Page 3）するまで継続します。
※ 最後のログインから 90 日間アクセスしなかった場合には、自動的にログアウトします。
サーバーメンテナンス等が発生した場合にも、ログアウトすることがあります。

◆「ログイン状態を保持する。」にチェックを入れずに「ログイン」ボタンをクリックした場合、
Web ブラウザの終了により自動的にログアウトします。

―2―

遠隔監視システム ASP サービス 取扱説明書

ログインできない場合
ID またはパスワードに誤りがあった場合、「認証情報に誤りがあります。」と表示されます。

ID とパスワードをご確認の上、再度ログインを行ってください。

なお、Web ブラウザの表示メニューのエンコードが「Unicode（UTF-8）」以外では、ログインできない場合があります。以下の方法でご確認ください。
Internet Explorer

メニューバーの［表示］→［エンコード］

Google Chrome

ウィンドウ右上の Chrome メニュー→［設定］→［詳細設定を表示］→［ウェブコンテンツ］→［フォントをカスタマイズ］→［エンコード］

Mozilla Firefox

メニューバーの［表示］→［文字エンコーディング］

ログアウト
ログイン後、各画面の右上にある「ログアウト」ボタンをクリックするとログアウトします。

「ログインできないとき」ボタン
任意に設定した ID とパスワードが不明になった時
等、任意に設定した ID とパスワードを一度リセット
する場合に使用します。
リセットするには、「ログイン情報（Page 2）」に記載されたマスター ID とマスターパスワードの入力が必要です。
リセット後は、マスター ID・マスターパスワードで再度ログインを行ってください。

―3―

Solar Link ARCH・ソーラー リンク アーク

通知メール設定のお願い
Solar Link ARCH には、設備の故障等の被害を最小限に抑えるため、パワーコンディショナや受変電設
備から送信される異常信号を計測システムが検知した場合にメール通知する機能があります。
本システム導入時には、通知用メールアドレスが未登録ですので、お客様にてご登録をお願いします（Page10）。通知する故障項目を選択することも可能です（Page 8）。
【Step 1】設定メニュー画面にログインし、「メール送信先設定メニュー」ボタンをクリックします。

▼【Step 2】「メールアドレス設定」ボタンをクリックします。

▼【Step 3】メールアドレスを入力し、「テスト送信」ボタンをクリックしてテストメールの受信を確認した後、「編集を保存」ボタンをクリックします。以上で設定完了です。

Solar Link ARCH における「ノード」「サイト」「グループ」
ノード

データをアップロードする単位。計測機器（Solar Link Viewer、Solar Link ZERO、ストリング監視機器等）1 つが、1 ノードに相当する。

サイト

一括監視画面に表示する単位。1 ノード～数ノードをまとめて表示したもの。

グループ

数サイトをひとまとめにしたもの。

【概念図】

グループ

サイト

サイト

ノード

PCS 等

ノード

PCS 等

PCS 等

ノード

PCS 等

PCS 等

―4―

PCS 等

遠隔監視システム ASP サービス 取扱説明書

設定メニュー画面
Web ブラウザに設定メニュー画面 URL を入力すると表示される画面です。各種設定の確認・変更を行うことができます。

ID・パスワード変更

受変電設備の異常判定設定

メール通知項目設定

ログインに必要な ID とパスワードを変更することができます（Page 6）。
変更後は「ID・パスワードのリセット」画面（Page 3）以外は、変更した ID とパスワー
ドのみが有効となります。マスター ID とマスターパスワードはリセット操作（Page 3）の際に必要となりますので、大切に管理してください。
各接点入力項目の発生／復帰を、一括監視画面の「サイト状況」の表示（異常／正常）に反映するかどうかを、設定することができます（Page 7）。
接点計測を行っていない場合もメニューは表示されますが、設定はできません。

パワーコンディショナや受変電設備の故障や異常などの信号を受け取った場合に、どの項目をメール通知の送信対象とするのか、どの送信パターンで送るのかを設定することができます（Page 8）。

通知メールの送信先アドレスの登録や、登録したメールアドレスのグループ設定を行うことができます（Page 10）。
メール送信先設定メニュー

更新停止検出設定

更新停止（計測機器～サーバー間が無通信の状態）が発生してから、何分後に一括監視画面やシステム障害履歴画面へ反映させてメール通知を行うかを設定することができます（Page 14）。

PCS 毎に設定されている計測チャンネルや数値を用いて任意の計算式を作成し、一括監視画面に表示することができます（Page 15）。
計算式設定

―5―

Solar Link ARCH・ソーラー リンク アーク

ID・パスワード変更画面
設定メニュー画面で「ID・パスワード変更」ボタンをクリックすると表示される画面です。
マスター ID とマスターパスワードから、他の ID とパスワードに変更することができます。
新しい ID を１回、新しいパスワードを 2 回、それぞれ入力し、「設定を変更」ボタンをクリックしてください。

設定可能な文字と文字数
ID は、半角英数字で 5 文字以上 32 文字以内です（記号は使用できません）。
パスワードは、半角英数字または記号 で 8 文字以上 128 文字以内です。
※ ID はアルファベットで始まる必要があります。
   数字だけを設定した場合、「不正な文字が含まれています」等のメッセージが表示されます。
       ※エラーメッセージが表示された場合は、違う内容で ID を設定しなおしてください。

ID・パスワードの変更後は、新しい ID・パスワードで再度ログインを行い、正しく変更されていることを確認してください。

※

ボタンをクリックすると、設定メニュー画面が表示されます。
―6―

遠隔監視システム ASP サービス 取扱説明書

受変電設備の異常判定設定画面
設定メニュー画面で「受変電設備の異常判定設定」ボタンをクリックすると表示される画面です。
ノードを選択して「編集」ボタンをクリックすると、下図のような画面が表示されます。

①

②
③

④

⑤

⑥

① ノード

サイトの全てのノードが表示されます（接点計測を行っていない場合も表示されます）。接点入力項目を計測しているノードを選択してください。

② 編集

選択したノードの全ての接点入力項目が一覧表示されます。

③ 接点項目内容

接点項目名が表示されます（接点計測を行っていない場合は表示されません）。

サイト状況に④反映する

各接点入力項目の発生／復帰を、一括監視画面の「サイト状況」（Page 19）の表示（異常／正常）に反映する場合は、チェックを入れます（接点計測を行っていない場合は設定できません）。

⑤ Prev/Next

Prev、1、2…Next のボタンで表示ページを切り替えることができます。

⑥ 編集を保存

設定を保存します。

※

ボタンをクリックすると、設定メニュー画面が表示されます。
―7―

Solar Link ARCH・ソーラー リンク アーク

メール通知項目設定画面
設定メニュー画面で「メール通知項目設定」をクリックすると表示される画面です。

②

①
④

⑤

③

⑥

⑦

⑧
⑨
① ノード

サイトの全てのノードが表示されます（接点計測を行っていない場合も表示されます）。接点入力項目を計測しているノードを選択してください。

② 編集

選択したノードの通知項目が表示されます。

③ 送信パターン設定

メールの送信時間帯（送信パターン）を設定する画面を開きます。

④ 内容

通知項目名が表示されます。

⑤ 発生 /復帰

メール通知が必要な項目にチェックを入れます。初期設定では ｢発生」の全ての項
目にチェックが入っています。

⑥ 送信グループ

項目ごとにメールの送信先をグループ単位で選択します。送信グループの設定はメールグループ設定画面で行います（Page 13）。初期設定ではすべての項目が「全員」で設定されています。

⑦ 送信パターン

項目ごとにメールを送信する時間帯（送信パターン）を選択します。
送信パターンの設定は③のボタンをクリックして表示される画面で行います（Page 9）。
初期設定ではすべての項目が「[A] 常時送信」で設定されています。

⑧ Prev/Next

表示ページは 20 項目毎に分かれます。Prev、1、2…Next のボタンで表示ページを切り替えることができます。

⑨ 編集を保存

設定を保存します。

この画面での設定内容は、設定を行ったノードで計測している全ての PCS が一括で設定されます（PCS 毎の設定はできません）。

【概念図】 ノード 1 を選択して設定を行うと、PCS1 ～ 3（黒色部分）を 一括で設定します。
※ PCS 毎の設定はできません。

ノード 1 ～ 3（黄色部分）の設定をまとめて行うことはできませんので、ノード毎に設定してください。
※

サイト

ノード 1

PCS1

ノード 2

PCS

ノード 3

PCS

PCS2

PCS3

PCS

ボタンをクリックすると、設定メニュー画面が表示されます。
―8―遠隔監視システム ASP サービス 取扱説明書

送信パターン設定画面
メール通知項目設定画面でをクリックすると表示される画面です。

①

③

②

① 送信時間帯

メールの送信時間帯を設定します。
送信パターン A は常時送信で固定されています。
送信パターン B ～ E は任意の時間帯を時・分単位（00 時 00 分～ 23 時 59 分）
で設定することができます。

② 中止

設定を保存せずに画面を閉じます。

③ 保存

設定を保存して画面を閉じます。

●送信パターンが「07 時 00 分～ 19 時 00 分」の場合
0時

7時

19時

送信時間帯

23時

…

・06 時 59 分 59 秒の発生 … メール送信されません
・07 時 00 分 00 秒の発生 … メール送信されます
・19 時 00 分 59 秒の発生 … メール送信されます
・19 時 01 分 00 秒の発生 … メール送信されません
選択した送信パターンのメール送信時間帯前の発生は、メール送信の時間帯になってもメールは送信されませんが、送信時間帯中の発生であればメール送信時間帯後にメールが送信される場合があります（Page 48）。
送信パターンはノード毎に設定をする必要があります。

―9―

Solar Link ARCH・ソーラー リンク アーク

メール送信先設定メニュー
設定メニュー画面で「メール送信先設定メニュー」ボタンをクリックすると表示される画面です。

メール通知項目の送信先メールアドレスを設定することができます（Page 10）。
メールアドレス設定

登録したメールアドレスをグループ設定することができます（Page 13）。
メールグループ設定

メールアドレス設定画面
メール送信先設定メニュー画面で「メールアドレス設定」ボタンをクリックすると表示される画面です。

メールアドレスは半角英数字 128 文字以内で設定する必要があります（RFC 5321, RFC 5322 準拠）。
メールアドレスを入力後、「テスト送信」ボタンをクリックすると確認メッセージが表示され、「はい」
ボタンのクリックでメールのテスト送信が行われます。
必ず、テストメールが受信できているか、確認してください。
確認した後、画面下の「編集を保存」ボタンをクリックしてください。

※

ボタンをクリックすると、設定メニュー画面が表示されます。

※

ボタンをクリックすると、メール送信先設定画面が表示されます。
― 10 ―

遠隔監視システム ASP サービス 取扱説明書《重要》通知メールの受信に、各社携帯電話向けメールアドレスを指定される場合
ラプラス・システムから送信したメールが、携帯電話サービス事業者にて迷惑メール拒否設定等によりブロックされると、他のユーザー様のメールアドレスを含む全てのメール送信がブロックされ続ける場合があります。
※ 送信元サーバーとの調整が必要なため、この状態が解消されるまでには数日を要する場合があります。

このようなトラブルを未然に防ぐため、以下のドメインを含むメールアドレスの受信が拒否されないように設定をお願いします。
・全てのパソコンメールを拒否しない設定
・受信可能なメールアドレスに次のドメインを登録@lapsys.co.jp
通知メールは “no-reply-service@lapsys.co.jp” のアドレスにて送信しますが、別のアドレスにてサー
バーメンテナンス情報等も送信させていただく場合がありますので、上記ドメインでの登録をお願いします。また、携帯電話側の設定方法は、携帯電話サービス事業者にご確認ください。

◆ 使用可能なメールアドレスの例
RFC 5321, RFC 5322 準拠のメールアドレスに限り、登録と送信を行っていただけます。メールアド
レス設定画面の「テスト送信」ボタンをクリックした場合に「不正なメールアドレスです」と表示される場合は、下記をご参照ください。
主な携帯電話サービス事業者では、メールアドレスの「@」より左側に以下の条件が示されています。
・登録可能な文字数は、半角文字 3 ～ 30 文字です（一部は 4 ～ 20 文字）。
・登録可能な文字の種類は、半角英数字および「-」（ハイフン）、「.」（ドット）、「_  」（アンダーバー）です。
・スペースは使用できません。
・先頭は英文字のみ使用できます。
・「@」の直前となる最後に「.」（ドット）を使用することはできません。
・「.」（ドット）をメールアドレスの「@」より左側で連続使用することはできません。
※上記は、メールアドレスを新規作成される場合の条件です。ご使用のメールアドレスが上記の条件にしたがっていない場合は、メールアドレスを変更されるか、他のメールアドレスをご利用ください。
※パソコン用のメールアドレスにおいても同等の条件となります（一部、使用可能な記号が緩和されます）。
※ Solar Link ARCH では、総文字数 128 文字以下でメールアドレスを設定してください。

― 11 ―

Solar Link ARCH・ソーラー リンク アーク◆通知メールのサンプル
一括監視画面でサイト名称を変更（Page21）しても、通知メールのノード名は変更されません。

件 名： NOTICE  ノード名称
送信者： no-reply-service@lapsys.co.jp
メール本文：PCS の異常信号を受信すると、日付、時
刻、PCS 番号、メーカー故障コード、項
目名、状態が 1 行ずつ表示されます。

ノード名称

2016-01-27 10:36:55 PCS1 UF14 インバータ異常 発生
2016-01-27 10:37:55 PCS1 UF14 インバータ異常 復帰
2016-01-27 10:39: -- -- 交流不足電圧 発生※ このメールは自動送信専用です。
※ 返信はできませんのでご注意ください。

受変電設備では PCS 番号、メーカー、
故障コードが「-- --」と表示されます。

※発生・復帰チェックボックス（Page 8）にチェックが入っている項目については、5 分間で検知された項目がまとめて 1 通のメールで通知されます。同じ事象が 5 分以内に検知された場合は、検知された回数だけメールに記載されます。

― 12 ―

遠隔監視システム ASP サービス 取扱説明書

メールグループ設定画面
メール送信先設定メニュー画面で「メールグループ設定」ボタンをクリックすると表示される画面です。
①① グループ一覧②③

登録したグループ名が一覧で表示されます（初期設定では「全員」のみ）。

②

選択メール
アドレス一覧

グループ登録したメールアドレスが表示されます。このエリアへの登録は、「登録メールアドレス一覧」の中から「＜＜」「＞＞」ボタンを使用して行います。

③

登録メール
アドレス一覧

「メールアドレス設定」画面で事前に登録したメールアドレスが表示されます。

●グループの編集方法＜グループにメールアドレスを追加する場合＞②「登録メールアドレス一覧」から追加したいメールアドレスを選択します。

③「<<」ボタンをクリックすると「選
択メールアドレス一覧」に追加されます。

＜グループからメールアドレスを削除する場合＞① 編集したいグループ名を「グループ一覧」から選択します。

②「選択メールアドレス一覧」から削除したいメールアドレスを選択します。
― 13 ―③「>>」ボタンで「登録メールアド
レス一覧」にメールアドレスが移されます。

Solar Link ARCH・ソーラー リンク アーク●グループ追加①②①「新規作成」ボタンをクリックします。
②「グループ新規作成」画面が表示されるので、グループ名を入力します（最大文
字数 10 文字）。
「中止」ボ③「保存」ボタンで設定を保存し、タンで設定をキャンセルします。

③●グループ名編集①②③①●グループ名削除①②①①「グループ一覧」から編集したいグループ
名を選択し、「編集」ボタンをクリックします。
②「グループ名編集」
画面が表示され、グルー
プ名を入力します（最大文字数 10 文字）。
③「保存」ボタンで設定を保存し、「中止」ボタンで設定をキャンセルします。

①「グループ一覧」から削除したいグループ
名を選択し、「削除」ボタンをクリックします。
② 確認画面の「はい」ボタンで削除し、「いいえ」ボタンでキャンセルします。

更新停止検出設定画面
設定メニュー画面で「更新停止検出設定」ボタンをクリックすると表示される画面です。
※更新停止とは、計測機器とサーバーが通信できていない状態です（Page 45）。

①②

更新停止の発生から何分後に一括監視画面に「更新停止」と表示させるかを設定します。
① 監視画面表示 10 分後以降から、5 分刻みで設定できます（10 分後、15 分後、20 分後、・・・最長
60 分後）。初期設定では 10 分後に設定されています。

②

履歴・メール
通知

一括監視画面に「更新停止」が表示されてから何分後にシステム障害履歴（Page 30）に記録、更新停止メールを発報するかを設定します。0 分後以降から、5 分刻みで設定できます（0 分後、5 分後、10 分後、・・・最長 60 分後）。初期設定では 0 分後に設定されています。
― 14 ―

遠隔監視システム ASP サービス 取扱説明書

計算式設定画面
計測チャンネルリストの計測項目を用いて、任意の計算式を作成することができます。また、作成した計算式を組み合わせて、算出することもできます。関数も使用可能です（Page 17）。

①

②

① サイト

③

⑤

④

⑥

⑦

サイトを選択します。

② 計測チャンネルリスト ①で選択したサイトで計測されている項目を表示します。
③ 計算式リスト

計算式を設定します。設定した計算式は一括監視画面の「フレックスエリア」の数
値アイテム・状態アイテムの設定に使用できます（Page 37）。

④ 名称

フレックスエリアの数値アイテム・状態アイテム設定の中でこの名称が表示されます。最大文字数は 30 文字です。

⑤ 計算式

計算式を設定します（Page 16）。最大文字数は 1024 文字で、使用可能な文字は下記のみです。
• 半角数字 • 関数名に使われる半角英字 • 演算記号 + - * / ( ) [ ]⑥ 項目

設定した計算式の項目をリストから選択できます（設定必須ではありません）。
計算結果には影響しません。

⑦ 単位設定した計算式の単位をリストから選択できます（設定必須ではありません）。
計算結果には影響しません。

― 15 ―

Solar Link ARCH・ソーラー リンク アーク

計算式の入力方法●計算式の入力例
計算式の [ ] で囲まれた数字は、該当する計測チャンネルの No. の値となります。
例）下記の計算式設定画面の場合、[7] ＝「P1 交流電力」の計測値となります。

①②③※ A 区画の PCS は 2 台とします。
※発電所は A 区画と B 区画の合計 2 区画とします。

A 区画 PCS 合計発電電力①[7] ＋ [16]売電金額②
[11]*36③

発電所合計発電電力[f1] ＋ [f2]

計測チャンネルリストでは「No.7：P1 交流電力、No.16：P2 交流電力」となっているので、A 区画 PCS 合計発電電力の計算式は [7] ＋ [16]となります。
計測チャンネルリストでは「No.11：売電電力量」、売電単価は 36 円とすると、売電金額の計算式は [11]*36 となります。
※ [ ] の付いていない数字はそのまま数字として扱われます。

計算式リストでは「No.f1：A 区画 PCS 合計発電電力」、「No.f2：B
区画 PCS 合計発電電力」となっているので、A 区画と B 区画の合計
発電電力の計算式は、[f1] ＋ [f2] となります。

※ [f1] のように [ ] で囲まれた f 付きの数字は、該当する No. の計算式から算出された値を示します（[f1] ＝ [7] ＋ [16]）。

― 16 ―

遠隔監視システム ASP サービス 取扱説明書

計算式で使用可能な関数
計算式リストに以下の関数を入力して計算することもできます。
関数

計算内容

計算例

abs(x)

x の絶対値を返す

abs(8) = 8
abs(-4) = 4

min(x,y)x, y の内小さい方を返す

min(-2,5) = -2

max(x,y)x, y の内大きい方を返す

max(-10,-20) = -10

1 つの計算式の中に、複数の関数を入れ子にすることも可能です。
（例）売電がプラス、買電がマイナスの値で取得されるチャンネルで、それぞれをプラスの値に直して表示する。

abs と min を使用した計算式― 17 ―

Solar Link ARCH・ソーラー リンク アーク

一括監視画面：パワーコンディショナのみ
Web ブラウザに一括監視画面 URL を入力すると表示される画面です。
パワーコンディショナ等の計測状況を確認することができます。
受変電設備として日射計と気温計のみが含まれる場合もこの画面となります。

①
⑤

②
③
④
⑦
⑭

⑥

⑧
⑩

⑨
⑪

⑫

⑬

⑮

PCS6 台で、日射計・気温計の設置・計測が有るサイトの画面例※ PCS4 が異常、「サイト状況」の表示も「異常」へ変化。

① メニューアイコンから一括監視画面トップページの設定（以下）を行うことができます。

[ 編集モード ON] を選択すると編集モード（赤字）に切り替わり、一括監視画面内で編集可能な名称部分
がピンク枠で囲まれます（Page 21）。
[ フレックスエリア表示 ] は「編集モード ON」を選択して編集モード（赤字）に切り替えると表示されます。
フレックスエリアの表示・非表示の切り替えを行います（Page 23）。

② 現在の合計発電電力が表示されます。 ※数値は 1 分毎更新［最大 14 桁 + 小数１桁］。
③ 本日の合計発電電力量が表示されます。 ※数値は 10 分毎更新。毎日 0 時 0 分リセット［最大 16 桁］。
④ 計測開始時からの総積算発電電力量が表示されます。 ※数値は 10 分毎更新［最大 16 桁］。
⑤ 現在の日射強度、現在の外気温度が表示されます。 ※日射計と気温計を設置していない場合は非表示。

― 18 ―

遠隔監視システム ASP サービス 取扱説明書「異常」表示となります。
⑥ サイト状況が表示されます。以下の場合、・何れかの PCS から故障・異常信号を受けた場合。
・PCS ～計測機器間または計測機器～サーバー間の通信が途絶えた場合。
・設定メニューの「受変電設備の異常判定設定」画面（Page 7）で、「サイト状況に反映する」にチェックを入れた接点入力項目が発生した場合。

異常時

正常時

⑦

―

現在のトレンドグラフ画面が表示されます（Page 23）。

⑧―

データ表示画面が表示されます（Page 24）。

⑨―

データダウンロード画面が表示されます（Page 26）。

⑩―

記録一覧画面が表示されます（Page 28）。

⑪―

システム障害履歴画面が表示されます（Page 30）。

⑫―PCS 状況一覧画面が表示されます（Page 32）。

⑬―

PCS 故障履歴画面が表示されます（Page 33）。

⑭ PCS 情報が表示されます。

計測機器に接続されている各 PCS 毎の、現在の発電電力と状況を確認することができます。
各 PCS のボックスをクリックすると PCS 状況画面が表示されます（Page 31）。
PCS 毎の現在の発電電力が表示されます［最大 3 桁＋小数 1 桁］。
PCS 毎の状況が表示されます。状況に応じ、以下のように変化します。
正常（緑）： PCS が正常に稼動し、計測機器とサーバー間の通信も正常な状態です。
異常（赤）： 計測機器が PCS から故障・異常信号を受信している状態です。
PCS 無通信（黄）： 計測機器が PCS と通信できていない状態です。
更新停止（灰）：計測機器からサーバーへデータがアップロードされていない状態です。

→ 該当する PCS の運転状態を確認してください。
→ ルーター等ネットワーク機器を確認してください。

※ PCS の機種により、日没時の発電停止にて、「正常」が「PCS 無通信」となる場合があります。

⑮ ①のメニューアイコンから「フレックスエリア表示」にチェックを入れると、フレックスエリアが表示されます（Page 35）。初期設定では非表示になっています。

― 19 ―

Solar Link ARCH・ソーラー リンク アーク

一括監視画面：パワーコンディショナと受変電設備
パワーコンディショナに加えて、受変電設備等の監視を行う場合の一括監視画面です（オプション）。

⑯⑰⑱

PCS 台数 6 台で、受変電設備・日射計・気温計の設置・計測が有るサイトの画面例※一部の PCS が異常となり、「サイト状況」の表示も「異常」へ変化。

⑯―

受変電設備履歴画面が表示されます（Page 40）。

⑰ リモート I/O などで計測している各受変電設備の接点入力項目と状況が表示されます。
緑： 受変電設備の通常の稼動状態です。
赤＋「発生」： 該当の故障・異常・状態項目の発生状態です。 → 該当する機器の状態を確認してください。

⑱ リモート I/O などで計測している電圧、電流、電力、力率、温度等の計測値が表示されます。
― 20 ―

遠隔監視システム ASP サービス 取扱説明書

一括監視画面：買電電力量／売電電力量の表示
電力会社等が用意するメーターのパルス信号の電力量を計測する場合、「受変電設備」の枠の上部に「本日の買電電力量」「本日の売電電力量」が表示されます（オプション）。

⑲⑲ 本日の買電電力量 、本日の売電電力量を示します（それぞれ、計測している場合のみ）。
［最大 8 桁］
※値はメーター等からパルス信号を受け取り積算値を表示。毎日 0 時 0 分リセット。

メニューアイコン
一括監視画面右上の「メニューアイコン」をクリックすると、ドロップダウンで設定ウィンドウが表示されます。編集モードから閲覧モードに切り替える時に、変更内容を保存するかどうかの確認
画面が表示されます。「はい」をクリックすると保存され、一括監視画面に変更内容が反映されます。
また、元の名称や配置に戻すリセット機能はありませんのでご注意ください。

編集モード ON
設定ウィンドウの「編集モード ON」を選択し、閲覧モードから編集モードに切り替えると画面の編集が可能になります。編集モード中は「編集モード ON」が赤文字で表示されます。
メニュー
アイコン

閲覧モード（編集不可）

編集モード（編集可能）●名称変更
編集モード時は編集可能な名称枠がピンク色に変わります。名称枠をダブルクリックすると、入力可能になります（入力可能な最大文字数は、サイト名称は 32 文字、PCS 名称は 14 文字）。
サイト名称

PCS 名称

変更箇所
影響範囲

・データ表示画面
・データダウンロード画面

・データダウンロード画面からダウンロードした   CSV データの PCS 名称・PCS 状況一覧画面 ・PCS・ストリング状況画面
・PCS 故障履歴画面とダウンロードした CSV データの   PCS 名称
・通知メール― 21 ―

Solar Link ARCH・ソーラー リンク アーク●ウィンドウ配置
PCS 情報エリア内の各 PCS ウィンドウや、受変電設備エリア内の各状態表示、数値表示ウィンドウをドラッグアンドドロップで上下左右に配置できます（エリア外には配置不可）。
※編集モード時は監視画面の数値、状態は更新されません。

●エリア入れ替え
PCS 情報エリア、受変電設備エリア、フレックスエリアをエリアごとに上下に入れ替えて閲覧頻度の高いエリアを上部に表示できます。

※パワーコンディショナーの増設時やシステムのバージョンアップ時に、変更内容が元に戻る場合がございます。
あらかじめご了承ください。
― 22 ―

遠隔監視システム ASP サービス 取扱説明書

フレックスエリア表示
編集モード中、「フレックスエリア表示」を選択して赤文字に切り替えると、画面最下部にフレック
スエリアが表示されます。閲覧モード中は表示・非表示を切り替えることはできません。フレック
スエリア機能については、「フレックスエリア」（Page 35）をご参照ください。

フレックスエリア非表示

フレックスエリア表示

現在のトレンドグラフ画面
ボタンをクリックすると表示される画面です。
一日の発電電力の推移を確認できます。
グラフ上にマウスカーソルを移動させると、時刻に対応した発電電力値を確認できます。
発電電力値

時刻
※

ボタンをクリックすると、一括監視画面が表示されます。

※

ボタンをクリックすると、PCS 状況一覧画面が表示されます。

※

ボタンをクリックすると、   故障履歴画面が表示されます。

※

ボタンをクリックすると、データダウンロード画面が表示されます。
― 23 ―

Solar Link ARCH・ソーラー リンク アーク

データ表示画面
ボタンをクリックすると表示される画面です。
システム全体の発電電力量・日射・気温等のデータが、グラフおよび帳票にて表示できます。
データ範囲
データ単位

時間報

日報

月報

年報

期間指定
（指定可能なデータ期間）

１分

１時間分

１日間分

×

×

24 時間以内

１時間

×

１日間分

×

×

24 時間以内

１日

×

×

１ヶ月間分

×

31 日以内

１ヶ月

×

×

×

１年間分

12 ヶ月以内※ データ単位については「データ単位の詳細」（Page 27）をご参照ください。
※ PCS 毎の値は、データダウンロード画面から、CSV ファイルをダウンロードしてください。
※ データ単位「1 分」の表示可能な期間は、計測後 1 年間です。

― 24 ―

遠隔監視システム ASP サービス 取扱説明書

データ表示画面の操作「エリア」と「サイト」を選択します（複数の登録がない場合は選択不要です）。
データ単位を「１分」、「１時間」、「１日」、「１ヶ月」から選択します。
   ※本紙内ではデータ単位で「1 分」を選択して得られるデータを「1 分値」と表記することがあります。

データ範囲を「時間報」、「日報」、「月報」、「年報」、「期間指定」から選択します。
※データ単位により、選択できるデータ範囲が制限されます。

「PCS」（＝パワーコンディショナ）または「ストリング」を選択します。
パワーコンディショナの計測のみの場合は選択不要です（「PCS」選択済み）。
※ 監視対象がパワーコンディショナのみの場合には「ストリング」は表示されません。

選択したデータ単位とデータ範囲に応じた開始日時と終了日時を選択します。
「データ表示」ボタンをクリックして、グラフと帳票の表示を開始します。
  ※「期間指定」の場合、データ期間の左枠に「開始日時」、右枠に「終了日時」を入力します。

※

ボタンをクリックすると、一括監視画面が表示されます。
― 25 ―

Solar Link ARCH・ソーラー リンク アーク

データダウンロード画面
ボタンをクリックすると表示される画面です。
システム全体の発電電力量・日射・気温等のデータが、CSV 形式でダウンロードできます。
データ範囲
データ単位

時間報

日報

月報

年報

期間指定
（指定可能なデータ期間）

１分

１時間分

１日間分

×

×

24 時間以内

１時間

×

１日間分  

××

24 時間以内

１日

×

×

１ヶ月間分

×

31 日以内

１ヶ月

×

×

×

１年間分

12 ヶ月以内※ データ単位については「データ単位の詳細」（Page 27）をご参照ください。
※ データ単位「1 分」のデータダウンロード可能な期間は、計測後 1 年間です。

データダウンロード画面の操作「エリア」と「サイト」を選択します（複数の登録がない場合は選択不要です）。
データ単位を「１分」、「１時間」、「１日」、「１ヶ月」から選択します。
データ範囲を「時間報」、「日報」、「月報」、「年報」、「期間指定」から選択します。
※ データ単位により、選択できるデータ範囲が制限されます。

「PCS」（＝パワーコンディショナ）または「ストリング」を選択します。
パワーコンディショナの計測のみの場合は選択不要です（「PCS」選択済み）。
※ 監視対象がパワーコンディショナのみの場合には「ストリング」は表示されません。

選択したデータ単位とデータ範囲に応じた開始日時と終了日時を選択します。
      「データダウンロード」ボタンをクリックして、データのダウンロードを開始します。
※「期間指定」の場合、データ期間の左枠に「開始日時」、右枠に「終了日時」を入力します。

※

ボタンをクリックすると、一括監視画面が表示されます。
― 26 ―

遠隔監視システム ASP サービス 取扱説明書【資料】発電データ等の概略
主な各項目の単位と数値について（施設毎に対象項目や項目名が異なります）
項目名
日射量

単位（データ単位）

備

考

最大値 1.43（日射計が設置されている場合のみ）
kW/m² （1 分値）
平均値※ 1 分値は日射強度、1 時間値以上は日射量
kWh/m²（1 時間値以上）

気温

℃

買電電力量

kW （1 分値）
kWh（1 時間値以上）

積算値

電力会社から供給された電力量（買電設備のみ）※ 1 分値は電力、1 時間値以上は電力量

売電電力量

kW （1 分値）
kWh（1 時間値以上）

積算値

電力会社へ送出した電力量（売電設備のみ）※ 1 分値は電力、1 時間値以上は電力量

Px 直流電圧

平均値 気温計から送られてくる温度（気温計が設置されている場合のみ）V

平均値 太陽光発電パネルからパワーコンディショナに送られてきた電圧値

またはA

平均値 太陽光発電パネルからパワーコンディショナに送られてきた電流値

Px 直流電力または

Px 太陽電池電力

kW （1 分値）
kWh（1 時間値以上）

Px 交流電圧V

平均値 パワーコンディショナから送出した電圧値

Px 交流電流A

平均値 パワーコンディショナから送出した電流値

Px 交流電力kW （1 分値）
kWh（1 時間値以上）

Px 故障

分

積算値 故障信号を送出していた時間（１分以内の故障時は小数で表示）

Px 系統異常分

積算値 系統異常信号を送出していた時間（１分以内の異常時は小数で表示）

JBx-x 直流電流

A

平均値 ストリング監視装置が送出した電流値

JBx-x 直流電圧

V

平均値 ストリング監視装置が送出した電圧値

JBx-x 温度℃

平均値 ストリング監視装置が送出した温度

またはPx 太陽電池電圧
Px 直流電流Px 太陽電池電流

積算値

積算値

太陽光発電パネルからパワーコンディショナに送られてきた電力量※ 1 分値は直流電力、1 時間値以上は直流電力量

パワーコンディショナから送出した電力量※ 1 分値は交流電力、1 時間値以上は交流電力量※ Px はパワーコンディショナとその番号を示します。
※ JBx-x は接続箱（集電箱）とストリングの番号を示します。
データ単位の詳細
データ範囲

データ単位

固定
時間報

１時間分

日報

１日間分

１時間

日報

１日
１ヶ月

１分

詳

期間指定

細

24 時間以内

１分の対象データは、各分の 00 秒～ 59 秒までに計測されたデータの平均値もしくは積算値

１日間分

24 時間以内

１時間の対象データは、各時の 00 分～ 59 分まで

月報

１ヶ月間分

31 日以内１日の対象データは、0 時 00 分～ 23 時 59 分まで

年報

１年間分

12 ヶ月以内

１ヶ月の対象データは、各月１日～末日まで※１分データに限り、サーバー上の保存期間は計測後 1 年間です。保存期間を超えた１分データの表示とダウンロード
は出来なくなります。1 時間・１日・１ヶ月の各データは取り出しが可能です。
― 27 ―

Solar Link ARCH・ソーラー リンク アーク

記録一覧画面
ボタンをクリックすると表示される画面です。メンテナンスなどの実施記
録などにご活用ください。

⑩
①

②

③

④

⑤

⑥

⑨
⑦

⑧

② タイトル「詳細記録」画面（Page 29）で登録したタイトルが、最新の履歴行にのみ表示されます。

③ 状況「詳細記録」画面（Page 29）で選択した状況が表示されます。

④ 日時「詳細記録」画面（Page 29）で選択した年、月、日、時、分が表示されます。

⑤ 担当者「詳細記録」画面（Page 29）で登録した担当者名が表示されます。

⑥ 詳細

クリックすると「詳細記録」画面（Page 29）に遷移し、編集可能になります。

⑦ 追加

最新の履歴行にのみ表示されます。クリックすると「詳細記録」画面（Page 29）に遷移し、タイトルは引き継いだまま新たに状況を追加できます。

⑧ チェックボックス

削除したい履歴行にチェックを入れます（チェックは複数可）。チェックを入れると選択行がオレンジ色に変わります。左端の列が「＞」の状態でチェックを入れると、隠れているすべての履歴行にチェックが入ります。

⑨ 削除⑧で選択した行が削除されます。

⑩ 新規作成クリックすると新規の「詳細記録」画面（Page 29）が表示されます。

＞① 折りたたみ

最新の履歴行にのみ表示され、履歴の表示／非表示を切り替えます。
「＞」をクリックすると「    」に変わり、該当タイトルの全履歴が表示されます。
「     」をクリックすると「＞」に変わり、最新の履歴行以外は非表示になります。
＞●制限事項
1 タイトルの履歴登録数：10 件まで
1 ページに表示するタイトル数：最大 100 タイトルまで（100 件を越える場合は次ページに表示）※表示順序は「日時」の降順とします。
※登録済みのタイトルデータが 1,000 件を越える場合は、「最も古い履歴から削除されますがよろしいですか」という確認画面が表示されます。「はい」で最も古い履歴から削除されます。

※

ボタンをクリックすると、一括監視画面が表示されます。
― 28 ―

遠隔監視システム ASP サービス 取扱説明書

詳細記録画面
記録一覧画面の「新規作成」または「詳細」「追加」ボタンをクリックすると表示される画面です。

①
②
③
④
⑤

⑥
① タイトル「新規作成」ボタンをクリックした場合は、案件のタイトルを入力します（最大 50 文字まで）。
「詳細」または「追加」ボタンをクリックした場合は、既存のタイトルが表示されます。

② 日時「新規作成」ボタンをクリックした場合は、プルダウン形式で年、月、日、時、分を選択します（初期設定は画面を開いた日時）。
※選択可能な過去の「年」は、最も古い計測・集計データと同じ年となります。
「詳細」ボタンをクリックした場合は、当該履歴の設定日時が表示され、「追加」ボタンをクリックした場合は、画面を開いた日時が表示されます。

③ 状況

プルダウン形式で、新規／対応中／解決／保留／中止／その他／- を選択します（新規作成時の初期設定は「新規」）。

④ 担当者

担当者を入力します（最大 10 文字まで）。

⑤ 内容「新規作成」ボタンをクリックした場合は、対応内容を入力します（最大 256 文字まで）。
「詳細」または「追加」ボタンをクリックした場合は、最新の履歴が表示されます。

⑥ 編集を保存

編集内容を保存します。

※

ボタンをクリックすると、記録一覧画面が表示されます。
― 29 ―

Solar Link ARCH・ソーラー リンク アーク

システム障害履歴画面
ボタンをクリックすると表示される画面です。
ネットワーク無通信等、10 分以上のデータアップロード停止時に更新停止検出の発生となります（Page45）。現在までのデータが再びアップロードされると復帰となります。
これらの発生または復帰の履歴が、表示起点日から最大 10,000 件まで表示されます。
※ 表示起点日は当日が表示されています（表示起点日は変更可能です）。
ボタンをクリックすると、履歴を CSV 形式でダウンロードできます。

発生 または 復帰
内容表示
サイト番号
西暦年 - 月 - 日 時 : 分 : 秒

システム障害履歴の CSV データ仕様（各履歴の CSV ダウンロード→ Page 41）※ダウンロードファイル名は「終了西暦年 月日 _ 開始西暦年月日 _system_status.csv」のように表示されます。
（2015 年 1 月 1 日～ 2015 年 1 月 18 日の場合：2015 0118_20150101 _system_status.csv）
なお、上記ファイル名の 斜体部分 は、CSV ダウンロード時に指定しない場合は表示されません。
定

義

日時
内容
状態
状態コード
サイト番号

内

容

西暦年 - 月 - 日 時 : 分 : 秒○

内容表示（「更新停止検出」のみ）
発生 または 復帰
1 または 0
サイト内の通知を出した計測機器の通し番号○○

CSV ダウンロードサンプルデータ（※表示されている項目と数値はサンプルです。）
日時 , 内容 , 状態 , 状態コード , サイト番号
2013/09/05 23:09:00, 更新停止検出 , 復帰 ,0,1
2013/09/05 19:21:00, 更新停止検出 , 発生 ,1,1
2013/09/05 18:48:00, 更新停止検出 , 復帰 ,0,1※

画面内の表示

ボタンをクリックすると、一括監視画面が表示されます。
― 30 ―○

遠隔監視システム ASP サービス 取扱説明書

PCS 状況画面
一括監視画面の各 PCS のボックスをクリックすると表示される画面です。
各 PCS の電圧・電流・電力の現在値、発電電力の 1 日積算値、および運転状況が表示されます。
※ PCS の機種によっては、表示されない項目もあります。

各 PCS のボックスをクリック※※

ボタンをクリックすると、一括監視画面が表示されます。
ボタンをクリックすると、PCS 故障履歴画面が表示されます。
― 31 ―

Solar Link ARCH・ソーラー リンク アーク

PCS 状況一覧画面
ボタンをクリックすると表示される画面です。
各 PCS の電圧・電流・電力の現在値、発電電力の 1 日積算値、および運転状況が表示されます。
※ PCS の機種によっては、表示されない項目もあります。

※※

ボタンをクリックすると、一括監視画面が表示されます。
ボタンをクリックすると、PCS 故障履歴画面が表示されます。
― 32 ―

遠隔監視システム ASP サービス 取扱説明書

PCS 故障履歴画面
ボタンをクリックすると表示される画面です。
PCS の詳細故障の発生または復帰の履歴が、表示起点日から最大 10,000 件まで表示されます。
※ 表示起点日は当日が表示されています（表示起点日は変更可能です）。
ボタンをクリックすると、履歴を CSV 形式でダウンロードできます。

発生 または 復帰
異常詳細コードの内容表示
サイト番号                                                 パワーコンディショナ設定 ID または名称
                       西暦年 - 月 - 日 時 : 分 : 秒
  異常詳細コード（内容は “ 内容 ” 欄に表示されます）。

《注意》「状態」欄の表示についてご利用のパワーコンディショナの通信仕様によっては、故障状態の「発生」しか取得できない場合があります。この場合、「状態」欄においても「発生」しか表示されません。
なお、「無通信」状態の履歴は計測機器からの通知ですので、「発生」と「復帰」が表示されます。

※※

ボタンをクリックすると、一括監視画面が表示されます。
ボタンをクリックすると、PCS 状況一覧画面が表示されます。
― 33 ―

Solar Link ARCH・ソーラー リンク アーク

PCS 故障履歴の CSV データ仕様（各履歴の CSV ダウンロード→ Page 41）※ダウンロードファイル名は「起点西暦年 月日 _ 終了西暦年月日 _pcs_status.csv」のように表示されます。
（2015 年 1 月 1 日～ 2015 年 1 月 18 日の場合：2015 0101_20150118 _pcs_status.csv）
なお、上記ファイル名の 斜体部分 は、CSV ダウンロード時に指定しない場合は表示されません。
定

義
日時

内

容

西暦年 - 月 - 日 時 : 分 : 秒

画面内の表示○PCS メーカーコード
PCS MAKER CODE

パワーコンディショナ製造メーカーコード（ラプラスオリジナル）
弊社で独自に割り振っているコードです。
接続されているパワーコンディショナが同一メーカーの場合は、常に同じコードが表示されます。

PCS 型式コード
PCS MODEL CODE

パワーコンディショナ型式コード（ラプラスオリジナル）
弊社で独自に割り振っているコードです。
接続されているパワーコンディショナが同一型式の場合は、常に同じコードが表示されます。

PCS

パワーコンディショナの番号 または 名称
番号の場合は接続されているパワーコンディショナの ID 順に
１番から順番に割り振られます。

○

異常詳細コード（ラプラスオリジナル）
弊社で独自に割り振っているコードです。内容は内容欄に表示されます。
異常詳細コードは、計測しているパワーコンディショナや設備機器から送られてくる信号の各項目に独自に割り振っているコード番号で、接続されているパワーコンディショナや設備機器から送られてくる信号の識別に使用しています。コードの割り振りはパワーコンディショナの示す情報が一様で無いため、それぞれの仕様により個々に行っています。

○

異常詳細コード
LAPLACE CODE

異常詳細コード ( メーカー取説コード )MAKER CODE

パワーコンディショナから送られるコードです。
機種により空欄の場合があります。

異常グループ名称
ERROR

故障 または 系統異常 または その他

内容
ERROR NAME

異常詳細コードの内容表示
パワーコンディショナ等から送られてくる異常詳細コードの内容です。

○

発生 または 復帰（メーカーにより発生のみの場合があります）○

状態
STATUS
状態コード
STATUS CODE
サイト番号

1 または 0
サイト内の通知を出した計測機器の通し番号○

CSV ダウンロードサンプルデータ
日時 ,PCS メーカーコード,PCS 型式コード,PCS,異常詳細コード,異常詳細コード( メーカー取説コード ),異常グループ名称 ,内容 ,状態 ,状態コード,サイト番号
2013/09/06 15:20:00,018,001,PCS1,5000,,その他 ,無通信 PCS,復帰 ,0,1
2013/09/06 15:20:00,018,001,PCS2,5000,,その他 ,無通信 PCS,復帰 ,0,1
2013/09/06 14:59:36,018,001,PCS2,5000,,その他 ,無通信 PCS,発生 ,1,1
2013/09/06 14:59:36,018,001,PCS1,5000,,その他 ,無通信 PCS,発生 ,1,1
2013/09/06 14:46:58,018,001,PCS1,0007,UA211,その他 ,SPD 異常 ( サージプロテクタ）,復帰 ,0,1
2013/09/06 14:46:26,018,001,PCS1,0007,UA211,その他 ,SPD 異常 ( サージプロテクタ）,発生 ,1,1
2013/09/06 14:46:26,018,001,PCS1,0006,UA808,その他 ,系統電圧上昇抑制 ,復帰 ,0,1
2013/09/06 14:46:15,018,001,PCS1,0006,UA808,その他 ,系統電圧上昇抑制 ,発生 ,1,1

― 34 ―

遠隔監視システム ASP サービス 取扱説明書

フレックスエリア
一括監視画面のトップページ上で、表示させたい計測値などを任意で追加・削除したり、それらをレイアウトできる機能を持つエリアです。

フレックスエリアの表示／非表示
一括監視画面右上のメニューアイコンから編集モード ON にし、「フレックスエリア表示」をクリッ
クして赤文字になると、画面最下部にフレックスエリアが表示されます（Page 23）。初期設定では非表示です。

③①②① 名称変更②「▼」マーク

編集可能な名称枠がピンク色に変わります。名称枠をダブルクリックするとテキストボックス状態となり、入力可能になります。
※初期設定では「フレックスエリア」の文字は入っていません。
エリア最下部の▼をドラッグして、フレックスエリアの縦幅を広げることができます。
※アイテムの最大追加可能数は 100 です。エリアの最大サイズは、最大数のア
イテムすべてを縦・横隙間なく表示できる広さとします。

「●数値アイテム追加」 各ボタンをクリックすると、フレックスエリア内にそれぞれの新規アイ③「○状態アイテム追加」 テムを作成できます。閲覧モード中はボタンは非表示になります。アイボタン
テム設定については Page 36 をご参照ください。

― 35 ―

Solar Link ARCH・ソーラー リンク アーク

アイテム設定数値アイテムまたは状態アイテムを追加したら、アイテムごとに設定を行います。アイテム内の①②③のアイコンは、閲覧モード中は非表示になります。

③

②

①

① ツールアイコン アイテムの設定画面が表示されます（Page 37・Page 38）。

②「U」アイコン

アイテムを簡単に揃えて配置できる吸着機能の ON・OFF を切り替えることができます（初期設定では ON）。
[ON の場合 ]マークがピンク色になり、アイテムを他のアイテムの一定距離に近づけると、近づけたアイテムがもう一方のアイテムに吸着します。
[OFF の場合 ]アイテムが吸着することなく、自由に配置することができます。

③「×」アイコン

アイテムが削除されます。削除時に「このアイテムを削除しますか？」という警告画
面が表示されます。

― 36 ―

遠隔監視システム ASP サービス 取扱説明書

数値アイテム設定画面
をクリックすると表示される画面です。

①
②
③
④
⑤
⑥
⑦
⑧
① 名称

アイテム名称を入力します（最大文字数 14 文字）。

② 項目

1 段階目では計測値・計算式を、2 段階目では計測項目・計算項目をプルダウンから選択します。

③ 時間単位表示される数値の演算期間（1 分、1 時間、1 日、1 ヶ月、1 年、総積算）をプルダウ
ンから選択します。

④ 小数桁数

プルダウンから選択します。
小数点以下の表示桁数（0 ～ 3）を示し、初期設定は「1」です。

⑤ データ範囲[ 最小値（含む）]
表示される項目の最小閾値で、この値より小さい値は「--」と表示されます。
[ 最大値（含まない）]
表示される項目の最大閾値で、この値以上の値は「--」と表示されます。

⑥ 背景色

カラーパレットから選択します。アイテムの数値表示部分の背景色を選択できます。

⑦ 文字色

カラーパレットから選択します。アイテムの数値表示部分の文字色を選択できます。

⑧ OK ／中止「OK」ボタンで設定保存でき、「中止」ボタンで設定をキャンセルできます。
※「OK」ボタンで一括監視画面には反映されません。下記をご確認ください。

編集モードから閲覧モードに切り替える
時、左図の確認画面が表示されます。
「はい」をクリックすると一括監視画面に変更内容が反映されます。

― 37 ―

Solar Link ARCH・ソーラー リンク アーク

状態アイテム設定画面
をクリックすると表示される画面です。

①
②
③
④
⑤
⑥
⑦
① 名称

アイテム名称を入力します（最大文字数 14 文字）。

② 項目

プルダウンから選択します。1 段階目で計測・計算から選択し、2 段階目で計測項目・計算項目を任意に選択することができます。

③ データ範囲[ 最小値（含む）]
表示される項目の最小閾値で、この値より小さい値は「--」と表示されます。
[ 最大値（含まない）]
表示される項目の最大閾値で、この値以上の値は「--」と表示されます。

④ 表示テキスト

直接入力します。範囲外、範囲内それぞれの状態に対して、任意で文言を設定できます（最大文字数 14 文字）
。

⑤ 背景色

カラーパレットから選択します。アイテムの状態表示部分の背景色を選択できます。

⑥ 文字色

カラーパレットから選択します。アイテムの状態表示部分の文字色を選択できます。

⑦ OK ／中止「OK」ボタンで設定保存でき、「中止」ボタンで設定をキャンセルできます。
※「OK」ボタンで一括監視画面には反映されません。下記をご確認ください。

編集モードから閲覧モードに切り替える
時、左図の確認画面が表示されます。
「はい」をクリックすると一括監視画面に変更内容が反映されます。

― 38 ―

遠隔監視システム ASP サービス 取扱説明書

お知らせ画面
各画面の右上にある「お知らせ」ボタンをクリックすると表示される画面です。
ラプラス・システムからのサービスに関するお知らせが表示されます。
未読の新着情報がある場合は、ボタン上に「新着」と表示されます。
※大切なお知らせの場合があるので、「新着」が表示されている場合は、必ず確認してください。

※ログイン画面・設定メニュー画面・お知らせ画面に、「お知らせ」ボタンは表示されません。

「お知らせ」ボタンをクリック

④
⑤

①

②

③
※上記の表示内容はサンプルです。

① タイトル

お知らせのタイトルが表示されます。

② 本文

お知らせの本文が表示されます。

③ 通知日時お知らせの通知日時が表示されます。

④ 新着マーク

未読のお知らせの場合に表示されます。

「既読にする」 未読のお知らせの場合に表示されます。このボタンを押すと既読になり、⑤「④新着マーク」と「⑤「既読にする」ボタン」が非表示となります。
ボタン※

ボタンをクリックすると、「お知らせ」ボタンを押す前の画面に戻ります。
― 39 ―

Solar Link ARCH・ソーラー リンク アーク【オプション】受変電設備履歴画面
ボタンをクリックすると表示される画面です。
受変電設備の異常の発生または復帰の履歴は、表示起点日から最大 10,000 件まで表示されます。
※ 表示起点日は当日が表示されています（表示起点日は変更可能です）。
ボタンをクリックすると、履歴を CSV 形式でダウンロードできます。

発生 または 復帰
異常詳細コードの内容表示
サイト番号
西暦年 - 月 - 日 時 : 分 : 秒
異常詳細コード（内容は “ 内容 ” 欄に表示されます）。

※

ボタンをクリックすると、一括監視画面が表示されます。
― 40 ―

遠隔監視システム ASP サービス 取扱説明書

受変電設備履歴の CSV データ仕様※ダウンロードファイル名は「起点西暦年 月日 _ 終了西暦年月日 _status.csv」のように表示されます。
（2015 年 1 月 1 日～ 2015 年 1 月 18 日の場合：2015 0101_20150118 _status.csv）
なお、上記ファイル名の 斜体部分 は、CSV ダウンロード時に指定しない場合は表示されません。
定

義

内

容

画面内の表示日時

西暦年 - 月 - 日 時 : 分 : 秒( メーカーコード )受変電設備では常に 099（型式コード）受変電設備では機器に合わせ 001 から始まる番号（機器番号）

受変電設備では常に 0

異常詳細コード
LAPLACE CODE

異常詳細コード（ラプラスオリジナル）
弊社で独自に割り振っているコードで、内容は内容欄に表示されます。
コードの割り振りはそれぞれの仕様により個々に行っています。

異常詳細コード ( メーカー取説コード )MAKER CODE○○

受変電設備では空白

異常グループ名称
ERROR

受変電設備では常にその他

内容
ERROR NAME

異常詳細コードの内容表示（計測項目名）○

発生 または 復帰○

状態
STATUS
状態コード
STATUS CODE
サイト番号

1 または 0
サイト内の通知を出した計測機器の通し番号○

CSV ダウンロードサンプルデータ
日時 ,,,, 異常詳細コード , 異常詳細コード ( メーカー取説コード ), 異常グループ名称 , 内容 , 状態 , 状態コード , サイト番号
2013/09/06 15:09:37,099,001,0,6050,, その他 ,PAS 地絡 (67), 復帰 ,0,1
2013/09/06 15:09:14,099,001,0,6050,, その他 ,PAS 地絡 (67), 発生 ,1,1
2013/09/06 15:03:13,099,001,0,6005,, その他 , 受電 過電流 (51R), 復帰 ,0,1
2013/09/06 14:48:47,099,001,0,6049,, その他 ,PAS 閉 , 復帰 ,0,1
2013/09/06 14:48:08,099,001,0,6049,, その他 ,PAS 閉 , 発生 ,1,1

各履歴の CSV ダウンロード
システム障害履歴、PCS 故障履歴、受変電設備履歴の各画面にあるボタンをクリックして表示される画面にて、取り出すデータの開始年月日と終了年月日を指定し、各履歴の CSV データを最大 10,000 件までダウンロードすることができます。10,000 件を超えた場合
は、超えたデータが含まれるように開始年月日と終了年月日を再指定してダウンロードして下さい。
この故障や障害の履歴データは、過去の開始年月日と、それより現在に近い年月日をそれぞれ「年」、「月」、「日」の順番で指定し、「実行」ボタンをクリックします。
※ 設定した日付がファイル名に反映されます。

― 41 ―

Solar Link ARCH・ソーラー リンク アーク【オプション】一括監視画面：ストリング状況表示
パワーコンディショナ以外に、パワーコンディショナ毎・接続箱毎のストリングの故障（電流故障、
電圧故障、温度故障）の最新 1 分値を参照して、状況が一括監視画面に表示されます。
※対応可能な機器の場合のみ

PCS 情報【PCS・ストリング状況】
各 PCS の現在の発電電力と状況、およびストリングの状況が表示されます。
各 PCS のボックスをクリックすると、PCS・ストリング状況画面（Page 43）が表示されます。
ストリング毎の状況が表示されます。状況により、表示が変化します。
正常（緑）：全てのチャンネルに、一つも故障が無い状態です。

異常（赤）： 何れかのチャンネルに、一つ以上の故障が有る状態です。
無通信（黄）：

全てのチャンネル値が取得できない状態です。

（灰）： ストリング計測を行っていない状態です。
「ーー」― 42 ―

遠隔監視システム ASP サービス 取扱説明書【オプション】PCS・ストリング状況画面
一括監視画面の各 PCS のボックスをクリックすると表示される画面です。
※ストリング計測を行っていても、一括監視画面の PCS 情報内にストリング状況が表示されない場合があります。

【画面表示例１】

各 PCS のボックスをクリック【画面表示例２】

左側は、PCS の電圧・電流・電力の現在値、発電電力の 1 日積算値、および運転状況が表示されます。
右側は、接続されているストリング監視機器からの各種情報（温度・電圧・電流・直流電力値等）が表示されます。接続するストリング監視機器により、表示される項目が異なります。
※※

ボタンをクリックすると、一括監視画面が表示されます。
ボタンをクリックすると、PCS 故障履歴画面が表示されます。
― 43 ―

Solar Link ARCH・ソーラー リンク アーク【オプション】グループ監視
いくつかのサイトまたはグループを上位監視画面として、まとめて監視できます。以下 2 タイプの画面があります。
【表タイプ】

④

①
②
③

⑤

【窓タイプ】⑤① 現在のグループ全体の合計発電電力が表示されます。 （数値は 10 分毎更新）［最大 14 桁 + 小数１桁］［最大 16 桁］② 本日のグループ全体の合計発電電力量が表示されます。（数値は 10 分毎更新。毎日 0 時 0 分リセット）③ 計測開始からのグループ全体の総積算発電電力量が表示されます。 （数値は 10 分毎更新）［最大 16 桁］④ グループ全体のサイト状況が表示されます。以下の場合、「異常」表示となります。
・ グループ内の何れかの PCS から故障信号を受けた場合
・ グループ内の何れかのPCS～計測機器間または計測機器～サーバー間の通信が途絶えた場合
・ 設定メニューの「受変電設備の異常判定設定」で、「サイト状況に反映する」にチェックを入れた
接点入力項目が、グループ内の何れかのサイトで発生した場合
グループ内の全てのサイトが正常な時

グループ内の何れかのサイトが異常な時⑤ サイト毎の状況が表示されます。
各サイト名の行や枠をクリックすると、それぞれの一括監視画面が表示されます。
異常時には、サイト状況の列に「異常」と表示されます。
「異常」の内容に関しては、それぞれの一括監視画面で確認を行います。
※ グループと各サイトの構成により、リンク先の一括監視画面毎に ID とパスワードが必要な場合があります。
― 44 ―

遠隔監視システム ASP サービス 取扱説明書【ご参考】よくあるお問い合わせ
PCS 無通信と更新停止
計測データが送られてこない状況として、「パワーコンディショナ（PCS）～ 計測機器間が無通信」と「計測機器～サーバー間が無通信」（＝ネットワークトラブル）の 2 つが考えられます。
◆「PCS 無通信」の状態：PCS ～ 計測機器間が無通信送信されてきた直近のデータに、PCS の故障や機器接続の問題と思われる空データや不正な状態があった。

パワーコンディショナ

計測機器

サーバ

この状況をサーバーが判断した場合、一括監視画面の PCS 状況にはと表示されます。

計測機器が PCS との通信に失敗した場合には、その計測機器からサーバーに無通信状態であるとの通知が入り、PCS 故障の無通信発生履歴を残し、メール送信の処理を行います。
→

PCS が正常に稼動しているかを確認してください。

◆「更新停止」の状態：計測機器 ～ サーバー間が無通信（＝ネットワークトラブル）（更新停止検出や履歴・計測機器の故障やネットワークの問題で、10 分を超えてデータがアップロードされていない
メール通知のタイミングについては Page 14 参照）。

パワーコンディショナ

計測機器

サーバ

この状況をサーバーが判断した場合、更新停止検出設定画面（Page 14）で設定した内容で、一括監視画面のPCS 状況にと表示され、更新停止検出発生の履歴を残します。さらに、メール通知

項目設定画面（Page 8）で発生通知を設定している場合はメール送信の処理を行います。

◆「計測機器 ― サーバー間の無通信」による、表示と履歴・メール送信処理までの流れ※発生・復帰時にメール通知の設定をし（Page 8）、監視画面表示をデータ更新停止から 10 分後、履歴・メール通知
を監視画面表示から 20 分後に設定している場合（Page 14）。

時刻

状

態

データ更新が停止

12：15

停止が 10 分間継続

12：35

メール送信

12: △△

データ更新が復旧

計測機器からのデータアップロードが確認できなくなった。

…

12：05

サーバーの処理

一括監視画面の PCS 状況に「更新停止」を表示。
更新停止検出「発生」の履歴・メール送信の準備。

…

（履歴とメールに記載の発生時刻は 12:05）。

…

5 分間で発生したすべての通知項目を 1 通にまとめて送信する。
一括監視画面の PCS 状況に「正常」を表示。
更新停止検出「復帰」の履歴・メール送信の準備。
― 45 ―

Solar Link ARCH・ソーラー リンク アーク

画面表示◆現在のトレンドグラフ画面・データ表示画面でグラフが表示されない。

ご使用の Web ブラウザに Adobe Flash Player をインストールする必要があります（無料で入手可能です）。

現在のトレンドグラフ画面にグラフが表示されない場合
トレンドグラフが表示される枠内の「Get ADOBE FLASH PLAYER」のボタンをクリックすると、プログラム入手の Web サイト（http://www.adobe.com/go/getflash）につながります。

◆ 一括監視画面が表示されない。

正しい URL、ユーザー名、およびパスワードを入力しても一括監視画面が表示されない場合（Web ブラウ
ザのエラーが表示）は、データサーバーとネットワーク接続が行えていないか、データサーバーが何らかの理由で停止している事も考えられます。
ただし、一括監視画面を表示するためのサーバーが停止しても、計測装置内のバックアップデータ等により、PCS から送られてきたデータが、できるだけ欠測とならないような構成となっております。

― 46 ―

遠隔監視システム ASP サービス 取扱説明書◆ 故障発生から一括監視画面に表示されるまでの時間を知りたい。

故障が発生した場合、一括監視画面には約２～３分後の表示となります。
パワーコンディショナの故障信号は６秒毎、受変電設備の接点入力信号は１秒毎に、それぞれ監視を行っていますが、計測機器がサーバーにデータを送る周期、サーバー内処理の周期、一括監視画面の更新周期により、タイムラグが発生するため、２～３分後の表示が目安となります。
故障からの復帰の場合も、一括監視画面には同様のタイミングで表示されます。
また、通信にネットワークを使用しているため、通信の混雑により遅延する場合もあります。
故障発生の検知

６
秒

６
秒

秒

６
秒

６
秒

６
秒

６
秒

６
秒

秒

６
秒

６
秒

６
秒

６
秒

６
秒

６
秒

６
秒

秒

６
秒

６
秒

60

６
秒

６
秒

６
秒

６
秒

６
秒

６
秒

６
秒

秒

６
秒

６
秒

６
秒

60

６
秒

６
秒

６
秒

６
秒

６
秒

データ送信

秒

６

データ送信

60

６

データ送信

データ送信

計測機器

サーバ

６

秒

計測 10 回分のデータをサーバに送信（60 秒毎）｛

60 秒毎のサーバ内処理

データ蓄積
Web 表示画面
メール送信

秒

最新画面の表示

60秒

画面更新の要求

最新画面の表示

画面更新の要求

最新画面の表示

画面更新の要求

最新画面の表示

画面更新の要求6060秒

故障発生の表示

監視画面の更新◆ 一括監視画面のデザインや項目が取扱説明書（本紙）と異なる。

各種の機能アップやインターフェースの向上の為に、予告無くデザインの一部等を変更する事があります。

― 47 ―

Solar Link ARCH・ソーラー リンク アーク

通知メール◆ 登録した通知メールが送られてこない。

携帯電話へのメールの場合、セキュリティの関係からメールサーバーで止まっている事が考えられます。
パソコンメールを拒否しない設定や、ご使用のメール送信サーバーからのメールが受信できるか確認してください（Page 11）。
携帯電話からのメールの詳細は、お使いの携帯電話会社や通信事業者にお問い合わせください。

◆ 通知メールが毎日送られてくる。

通知メールは、監視項目一覧の中から、「設定メニュー」の「メール通知項目設定」（Page 8）にて、メー
ル送信の対象として選択していただいた項目の発生・復帰を検知すると、登録されているメールアドレス
へ自動的に送信されます（初期設定では、全ての「発生」が選択されています）。
パワーコンディショナによっては、発電量の変化を軽微な故障として通知する機種もあります。
日出や日没時に毎日通知メールが送られてくる場合は、その監視項目を選択していることも考えられます（詳しくはパワーコンディショナの取扱説明書をご参照ください）。
メール通知項目設定画面（Page 8）や送信パターン設定画面（Page 9）、メールアドレス設定画面（Page10）、メールグループ設定（Page 13）をご参照いただき、必要に応じて変更を行ってください。

◆ 故障発生から通知メールが送信されるまでの時間を知りたい。

故障が発生した場合、通知メール送信は約２～７分後となります。
一括監視画面への表示と同様に、サーバー内処理の周期により最大２分のタイムラグが発生し、さらにメー
ル送信の処理を５分毎に行っているため、２～７分後の送信が目安となります。
※ メール送信の処理を５分間隔で行う理由は、メールを連続して大量送信すると、悪質なメールを大量に送るサーバーと誤解され、送信や受信に制限が掛かる恐れがあるためです。

◆ 送信時間帯後なのに、通知メールが送られてきた。

上記のとおり、故障発生から通知メールが送信されるまでに約 2 ～ 7 分かかります。送信パターン設定（Page9）で設定いただいた送信時間帯中での発生については、送信のタイミングが送信時間帯後であっても通知メールを送信します。
例）【送信時間帯】07：00 ～ 23：59 【発生時間】23：58→ 【通知メール送信時間】00：00 ～ 00：05◆ 通知メールを受信したが、一括監視画面では正常と表示されている。

一括監視画面へ反映される一括故障項目には、通知メールの通知対象となる詳細故障項目が含まれない場
合があります。詳細は、パワーコンディショナメーカーにご確認ください。

◆ サイト名称を変更したが、通知メールのタイトルが変更されていない。

通知メールのタイトルはノード名称であり、サイト名称とは連動しません。また、名称変更が可能なのは
サイト名称と PCS 名称、フレックスエリア名称のみで、ノード名称は変更できません（Page 12）。

― 48 ―

遠隔監視システム ASP サービス 取扱説明書【ご参考】「異常」表示時の確認ポイント①サイト状況
全ての PCS および受変電設備が正常に稼動し、計測機器とサーバー間の通信も正常な状態です。
・何れかの PCS から、故障・異常信号を受けた場合・PCS ～計測機器間または計測機器～サーバー間の通信が途絶えた場合・設定メニューの「受変電設備の異常判定設定」で、「サイト状況に反映する」  にチェックを入れた接点項目が発生した場合→「② PCS 情報」にて詳細を確認してください。

①

②

③

② PCS 情報

計測機器に接続されている各 PCS 毎の、
現在の発電電力と状況を確認することができます。
PCS 毎の現在の発電電力が表示されます［最大 3 桁＋小数 1 桁］。
PCS 毎の状況が表示されます。状況に応じ、以下のように変化します。

正常（緑）：PCS が正常に稼動し、計測機器とサーバー間の通信も正常な状態です。
異常（赤）：計測機器が PCS から故障・異常信号を受信している状態です。
PCS 無通信（黄）：計測機器が PCS と通信できていない状態です。

→ 該当番号の PCS の運転状態を確認してください。

→ ルーター等ネットワーク
更新停止（灰）：計測機器からサーバーへデータがアップロードされていない状態です。
機器を確認してください。
※ PCS の機種により、日没時の発電停止にて、「正常」が「PCS 無通信」となる場合があります。

③受変電設備緑：

計測している各受変電設備の接点項目と状況が表示されます。
受変電設備の通常の稼動状態です。

赤＋「発生」： 該当の故障・異常・状態項目の発生状態です。→ 該当する機器の状態を確認してください。
― 49 ―

Solar Link ARCH・ソーラー リンク アーク

スマートフォン・タブレットでの表示
一括監視画面と一部のグループ画面には、スマートフォンやタブレット向け表示機能が用意されています。
※全てのスマートフォン・タブレット、Web ブラウザでの動作や表示を保証するものではありません。

ログイン
スマートフォン・タブレットの Web ブラウザを起動し、「ログイン情報」に記載の一括監視画面 URL を入力すると右図のログイン画面が表示されます。
◆ 右図のログイン画面が表示されればスマートフォン・タブレット表示に対応していますが、従来のパソコン用のログイン画面が表示された場合は非対応です（Page 2）。

マスター ID とマスターパスワードを入力して、「ログイン」ボタンをクリックします。
◆ 変更後の ID とパスワードも使用できます（Page 6）。
◆ 「ログイン状態を保持する」にチェックを入れてから「ログイン」ボタンをクリックした場合、次回のアクセス時は、URL の入力のみで一括監視画面を表示することができます。
この状態は一括監視画面でログアウトするまで継続します。
※ 最後のログインから 90 日間アクセスしなかった場合には、自動的にログアウトします。サーバーメンテナンス等が発生した場合にも、ログアウトすることがあります。

ログイン画面

画面説明①メニューアイコン
タップすると左のメニューが表示されます。

固定表示エリア②サイト状況（正常 または 異常）③現在の発電電力（kW）④本日の発電電力量（kWh）⑤日射強度 (kW/m2）・気温（℃）（※ 1）

画面切替エリア

⑥

⑦
スワイプで
画面切替
⑥グラフ画面（1時間毎の直流電力量・交流電力量・日射量・気温（※ 1））⑦ PCS毎の発電状況画面（正常 / 異常 / 更新停止 /PCS無通信）（※ 1）日射（日射強度・日射量）と 気温は、計測している場合のみ表示されます。
― 50 ―

遠隔監視システム ASP サービス 取扱説明書

メニューアイコンからの画面遷移

タブレットでの PC サイトでは、各種データのダウンロードボタンは表示されません。

サイト状況が異常の場合① PCS の稼働状況を確認するには
画面切替エリアをスワイプして、PCS 状況画面にて PCS の稼働状況を確認することができます。

スワイプ

PCS2 が異常発生中！

② PC サイトで詳細を確認するには
メニューアイコンから PC サイトに遷移して、PCS の状態や受変電設備の接点入力項目の状態を確認することができます。

タップ

PCS2 が異常である他、接点入力項目が 2 項目発生中！

― 51 ―

Solar Link ARCH・ソーラー リンク アーク【ご参考】ソフトウェア仕様
基本
名称

Solar Link ARCH（ソーラーリンクアーク）

動作環境（閲覧用パソコン）
対応 OS
対応 Web ブラウザ
※ 64bit OS では、32bit のブラウザをご使用ください。
画面解像度

Windows 7 / 10 (32bit/64bit)
Internet Explorer 11（ver.9、10 も可）／ Google Chrome ／ Mozilla Firefox※ 上記以外のブラウザではグラフ画面が正しく表示されない場合あります。
Adobe Flash Player のインストールが必要。
http://get.adobe.com/jp/flashplayer/ から無償でダウンロード可能。
1280 x 1024 pixel 以上を推奨 (1024 x 768 pixel でも使用可 )◆スマートフォンやタブレットの Web ブラウザでは、専用画面が表示されます（Windows タブレットはパソコン画面のみ）
基本機能
一括監視
PCS 状況一覧

PCS の発電状況や運転状況等様々な情報をネットワーク経由でクラウドサーバーに蓄積し、これをネットワークを通じて、一括監視画面として閲覧することが可能。
PCS 毎の発電電力を、より詳細に確認することが可能。

現在のトレンドグラフ 1 分毎の交流発電電力の推移をグラフで確認することが可能。
システム障害履歴
データ表示
データダウンロード
入力操作
メール通知機能計測機器～サーバー間の障害の発生・復帰の履歴を確認すること、CSV 形式でダウンロードすること、および更新停止時のメール通知することが、それぞれ可能。
発電電力量、日射、および気温の変化を、「グラフ」「帳票」で確認することが可能。
計測したデータを、CSV 形式でダウンロードすることが可能。
サイトや PCS、アイテムの名称変更や、詳細記録画面などでの入力が可能。
※ただし、いかなる場合も半角カタカナや機種依存文字は使用不可。
一つのサイトに登録できるメールアドレスは最大 20 件。それらをグループ化して、通知項目毎に送信対象者や送信時間帯の選択が可能である他、通知項目が発生／復帰した際のメール通
知要否の指定も可能。

オプション機能
受変電設備

一括監視画面にて受変電設備における計測項目の表示や接点入力項目発生時のサイト状況への反映、および接点入力項目が発生／復帰した際のメール通知要否の指定が可能。

ストリング監視

一括監視画面にて、ストリング毎の発電状況・故障状況の項目を表示すること、それぞれの詳細情報を確認すること、ダウンロードすることが、それぞれ可能。

グループ監視複数の地点で計測している場合、それらをグループとしてまとめて監視することが可能。
（通常の一括監視画面の上位に、複数サイトをまとめたグループ監視画面を追加）

PR 画面

PR 用に、発電電力の分かりやすい表示画面やグラフ画面等を提供することが可能。
※ API で遠隔監視システムから値を受け取って表示。コンテンツもまとめて提供が可能。
※発電電力表示画面は、個々の要望にお応えできる画面カスタマイズも可能。

Web カメラ

侵入者防止等の観点から、Web カメラを設置・操作して、サイト周辺の状況を確認することが
可能。

故障診断

過去の計測データを回帰分析して、日射量に応じた推定発電電力量を算出。
推定発電電力量に対する、実際の発電電力量の割合を「発電指標」として出力。
発電指標に対して任意のしきい値を設定し、メールでの通知を行うことが可能。

API

発電電力のデータを簡単に取得 ( ※ ) 可能なので、独自のアプリケーションを作成する際、取得したデータを利用することが可能。
※所定の URL を入力する形で弊社サーバーにリクエストを送り、必要なデータが XML 形式のレスポンスとして返される。

― 52 ―

遠隔監視システム ASP サービス 取扱説明書

改訂履歴
バージョン・内容

発行日

初版

ARCH ver. 1.6.0 起草。

2013.07.29

改定

ARCH ver. 1.7.0 画面変更と追加機能追記（システム障害履歴）。

2013.09.10

追加

一括監視画面に「本日の合計発電電力量」を追加表示（標準機能の追加）。
「よくあるお問い合わせ」追記（故障発生とメール送信のそれぞれの時間について）。

2013.11.06

改定。
ARCH ver. 1.7.1 画面変更と変更機能追記（認証情報リセット手順、履歴データ参照件数増加等）

2014.03.28

修正

更新停止の、継続停止の検出タイミング記載修正。

2014.05.28

追加

ARCH ver. 1.8.0「故障診断（オプション）」機能の追加。本社所在地の記載変更（裏表紙）。

2014.08.06

追加「故障診断（オプション）」機能の蓄積データのロックとリセット、注意、初期値について補足追加。

2014.08.26

修正

RFC 準拠の番号追記。画面内ボタンのスクリーンショット修正。

2014.10.08

追加

ARCH ver. 1.9.0「受変電設備の異常判定設定画面」ならびに「お知らせ画面」機能追加。
「故障通知メール設定のお願い」ページ追加。
「Solar Link ARCH における「ノード」「サイト」「グループ」」ページ追加。
「【ご参考】「異常」表示時の確認ポイント」ページ追加。
「【ご参考】ソフトウェア仕様」ページ追加。

2015.01.26

修正

グループ監視画面のスクリーンショット修正（お知らせボタン削除）。

2015.02.03

修正

PCS・ストリング状況画面のストリング ch 数変更（8 → 10）。各値の表示桁数（初期設定）修正。

2015.02.25

修正

Web カメラ画面（操作パネル装備タイプ）の動作環境を追記。

2015.06.01

変更

ARCH ver. 1.11「各履歴の CSV ダウンロード」のインターフェース変更。
最後のログインから自動的にログアウトするまでの日数を変更（30 日間→ 90 日間）。

2015.09.02

追加「メール通知項目設定画面」に「送信パターン設定」ボタンと「メール送信時間帯設定」機能を追加。

修正「メール通知項目設定画面」の「編集」ボタンの機能説明を修正。

2015.12.07

追加

ARCH ver 1.12 に対応。
「メール送信先設定メニュー」（メールアドレス設定画面・メールグループ設定画面）を追加。
「更新停止検出設定画面」を追加。
「メニューアイコン」機能（編集モード ON・フレックスエリア表示）を追加。
「記録一覧画面」を追加。
「フレックスエリア」機能を追加。

2016.02.24

追加「お知らせ画面」「【オプション】グループ監視」を追加。

2016.03.07

修正

1 分データのサーバー上の保存期間の誤記を１年間に修正（Page 24、26、27）。

2016.03.28

追加

スマートフォン・タブレットでの表示を追加 (Page 50、51)。

2016.04.05

追加

動作環境に Windows 10 を追加

2016.06.17

変更

データ表示での「PCS」、「ストリング」の分割表示の機能加筆。

2016.07.08

修正

詳細記録画面の記載内容を見直し（Page 29）。
PCS 故障履歴画面の《重要》の内容を修正（Page 33）。
「PCS 無通信と更新停止」に関する説明文の誤字修正（Page 45）

2016.08.25― 53 ―

著作権について本ソフトウェア、本説明書の著作権は株式会社ラプラス・システムに帰属します。
株式会社 ラプラス・システムの許可なく、内容の全部または一部を複製、改変、公衆送信する
ことは、著作権法上、禁止されております。

お問い合わせ先株式会社 ラプラス・システム
お電話でのお問い合わせ

弊社 HP からのお問い合わせ

TEL: 075-634-8073

http://www.lapsys.co.jp/

お問い合わせはコールセンターまで「お問い合わせ」フォームをご利用ください

・Microsoft, Windows, Internet Explorer は米国 Microsoft Corporation の米国およびその他の国における登録商標です。
・その他、本説明書で登場するシステム名、製品名、ブラウザ名、サービス名は、各開発メーカーの登録商標あるいは商標です。
・本説明書中では TM、R マークは明記していません。
・本説明書の内容を無断で転載することを禁じます。
・本説明書の内容は改良のため予告なく変更される場合があります。

株式会社 ラプラス・システム

2016.08.25〒 612-8083
京都市伏見区 京町 1-245
TEL:075-634-8073 ／ FAX:075-644-4832