11E0001019C11Instruction Manual
Vapor Tight Type LED Lighting Fittings

To be conserved

LCMA

Thank you very much for purchasing our LED lighting fittings.
Please read this instruction manual to use the product properly.
After installing the product, be sure to hand this manual over to the user of the product.
Prior to use

1) Prior to installing the fitting, check if the product is as per your order.
2) Check for a loose or damaged part due to an accident in transit, etc.

Performance

Instructions for use

ModelLamp

Input Voltage(Frequency)

Input Current

LCMA2602
LCMA2601

26W×226W×1

100-242 V AC
(50/60 Hz)

0.60-0.25A
0.31-0.13A

PowerConsumption
59.5-58.5W
30.5W

IPratingIP55

The LED lamp is turned on by applying the rated voltage to the power wire of the fitting.

How to Install the Fitting
Pipe Pendant Type, Bracket Type
4-φ8Mou ti g Holes

Suspension Hook

Mounting Interrval 500

Positioning Box
O Ring2-8×12
Mounting Holes

Suspension Hardware

Bracket Pipe A

Fixing Nut

Bracket Pipe B

Positioning Box CoverFastening Ring
Power Supply side

Locking Screws

Rubber Plug

Suspension Pipe A

Suspension Pipe B

Fitting

Bracket Type

Pipe Pendant Type
Suspension HookRed Marks

Rubber Plug SideO Ring

Fix the positioning box and suspension
hardware on the mounting surface
firmly.
Screw the suspension pipes A and B
into the fitting.
Put the fastening ring around thesuspension pipe A and screw in theterminal box cover.
Confirm that the O ring is in thegroove of the terminal box cover.
Raise the fitting and fit it to thesuspension hardware. Hook thesuspension hook onto the terminalbox.
After connection of the power
cable(white and brown: power wires,
green: grounding wire) , unhook thesuspension hook and place it in thepositioning box cover.
Fit the positioning box cover onto thepositioning box and turn the fastening
ring 90 degrees until the protrusions(red marks) align with each other.

Positioning Box Cover
Cross-Section

Suspension Pipe A

Suspension Pipe B

Special Direct Mount TypeTighten the locking screw and confirm
that the suspension pipe A andfastening ring don't turn.
Tighten the fixing nuts on thesuspension hardware.

4-φ8×12 Oblong Holes

Fix the fitting on the mounting surface firmly.
Loosen the set bolt and open the lamp house gently until it is supported by theinclination plate. The lamp house can be opened down to 90 degrees byremoving the inclination plate from the retainer.
Connect the power cable inside the positioning box.
Raise the lamp house gently and tighten the set bolt.
NB: The colors of power wire are white and red. The color of earth wire is black.

500
Mounting Interval

Hinge Side
Lamp House

Inclination Plate
Set Bolt--

Disassembly and Disposal

Stanchion Type
Locking Screw

Clamp Fixing Screw

1) In the period when the product is in use, neverdisassemble it.
2) For disposal of the product, follow the regulations andrules of your local government.

Junction Box

Clamp
Clamp Holder

FittingStand Pole
Support(not supplied)
Short Nipple G3/4
(not supplied)Box(not supplied)

Pass the lead wire through the stand poleand insert the pole into the junction box
in the arrow direction.
Fix the clamp with the clamp fixing screw.
Tighten the locking screw on the junction
box. Confirm that the box does not turn.
Attach the box and short nipple to thebottom of the stand pole.
Fix the stand pole completely with the polefixing hardware and box mounting screw.

Reordering
When reordering, please let us know:
・Drawing or drawing No. for the delivered product・Manufacturing lot number on the nameplate
If the above information is unavailable, give us any material
showing the appearance of the product or details of theproduct specification (dimensions, mounting interval, lamp
type, etc.).
Nameplate
器具銘板

MaintenancePrecaution in lamp replacement● Any lamp other than the applicable lamp specified below may not be used with this product. The specified lamp is not sold for any
purpose other than maintenance of the product.
*If lamp replacement is required, please contact us.
NB: For lamp replacement, the required distance between the fitting end face and the wall surface is as follows:
Distance between fitting and wall
Model
1.2m
LCMA
Applicable lamp

Inspection

Model

Wattage

Lamp
Color Temperature
LLPA1WG13K5003
5,000K
LCMA
26W
LLPA1WG13K3003
3,000K
Note: The use of a lamp other than the above lamp might result in a fire, electric shock, or explosion.

1) I lea i g the fitti g, ge tly ipe ith ater or ild deterge t. Do ’t use thi er, e ze e or alkali e deterge t. Su hchemicals might cause discoloration or deterioration in quality and strength, resulting in a damage.
2) Prior to maintenance, be sure to turn off the power.
3) Carry out maintenance properly in accordance with the related law and regulations.
4) If a repair is needed, consult us.
CAUTIONS

1. The product should be installed at an angle within the range from 0° (oriented downward) to 90° (oriented horizontally).
Do ’t i stall the produ t ith its lo gitudi al side orie ted erti ally. Doi g so ight ause a i sulatio failure or ele tri sho k.
2. Prior to maintenance or inspection, be sure to turn off the power.
3. Confirm that the screws and bolts are fastened properly and tightly.
4. In the case of the stanchion type, be sure to provide a support at least 1500 mm above the bottom of the pole.
5. For outdoor use, waterproof the screwed portion of the conduit, the cable entry fittings and the joint with the stand pole to prevent
rainwater infiltration.
6. When installing the fitting, be sure to connect external wires inside a specified part of the fitting. Don't open any other part of the fitting
unless necessary.
7. The supply voltage variation should be within ±6% of the rating.
8. The ambient temperature should be within the range of -20°Cto +40°C. The use of the product out of this range may shorten the servicelife.
9. Confirm that the fitting is adequately grounded.
10. Prior to maintenance or inspection, be sure to turn off the power.
11. To prevent shortening of the service life, avoid turning on the fitting in direct sunlight.
12. To avoid noise or malfunctioning, don't use a radio, television or wireless infrared remote control near the fitting.
13. The product must be mounted on a sturdy wall surface or structure which is vibration-free and less susceptible to damage. Otherwise, it
might fall or be damaged.
14. The specified lamp is not sold for any purpose other than maintenance of the product. If lamp replacement is required, please contact us.
The use of a lamp other than the specified lamp might result in a fire, electric shock, or explosion. Don’t open the lamp house for fiveminutes after turning off the power. If you don’t allow five minutes before opening it, an explosion might occur.
15. For use in an unfavorable location (a very hot, cold or humid place or a place in which there is strong wind or vibration, a salt damage
environment or a dusty or corrosive gas atmosphere), a special countermeasure should be taken.

--

11E0001020C11

Safety Precautions-

To be conserved

Prior to use, please read the safety precautions and instruction manual thoroughly to use the product properly.
After installing the product, be sure to hand the safety precautions and instruction manual over to the user of the product.
Please keep the manual in a handy place for later reference.
● The various marks have the following meanings:

WARNING: Improper handling may lead to a human death or serious bodily injury.
CAUTION:

Improper handling may lead to a bodily injury or property damage.

Be sure tofollow theinstructions.

Be sure to turnoff the power.

Disassembly &conversion
prohibited.

Don’t use neara water source.

Be sure toground.

Prohibited.

Don’t touch.

CautionBe careful ofignition.

WARNING
Don’t use the product in a hazardous location where a flammable or explosive atmosphere such as a gaseous, steamy or
dusty atmosphere may exist. Use in such a location might cause an explosion or fire.
The ambient temperature should be within the operating temperature range specified in the instruction manual. If theproduct should be used at a temperature higher than specified, an early lighting failure or malfunction might occur or a firemight result.
If a product must be oriented in a specific manner for use, install it properly according to the marking on its body or theinstruction manual. Otherwise, a fire or electric shock might result.
For electrical connections, use crimp-type terminals, etc. to secure the connections and conduct insulation treatment. An
inadequate connection or inadequate insulation might cause an imperfect contact, leading to a fire or electric shock.
In grounding work, be sure to follow the technical standards for electrical equipmentof your country.
Inadequate grounding might cause a fire or electric shock.
Do ’t o ert the produ t.
Conversion might cause the product to fall or result in a fire or electric shock.
Do ’t o er the produ t ith a i fla
a leSuch a material or thing might cause a fire.

aterial su h as loth or paper or put a ythi g i the produ t.

Do ’t e d, t ist or pull the po er a le y for e.
Inadequate handling of the cable might damage it and result in a fire or electric shock.
When replacing the lamp, make sure that the lamp is of the type specified in the instruction manual or the instruction on
the body. An unsuitable lamp might cause a fire or electric shock.
The parts once removed for lamp replacement or cleaning should be replaced in their original places properly according tothe instruction manual. An improperly placed part might fall, leading to an injury or property damage.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Do ’t ope LED la p prote ti e o ers su h as the fro t glass a d glass glo e.
Do ’t tou h a LED la p, other ise a alfu tio or lighti g failure ight o ur.
直L G13 照般6- 1/2 -WARNING
Before cleaning, be sure to turn off the power.
Otherwise, a fire or electric shock might result.
If you continue to use the product in an abnormal condition (smoke, odor, etc.), a fire or electric shock might result. If youdetect an abnormality, immediately turn off the power switch. Confirm that the abnormal condition has been eliminatedand make a repair call.
Do ’t use the produ t i a stro g orrosi e gas at osphere hi h o tai s hydro hlori a id or hlori e gases or the like.
Use in a corrosive gas atmosphere might cause the product to corrode and fall, resulting in an injury.
The product should be mounted on a surface robust enough to support its weight, properly according to the instruction
manual. Improper installation might cause the product to fall or result in an electric shock or injury.

CAUTIONAny product not marked as a product for outdoor use should not be used outdoors or in a humid place or near a water
source. Its use in such a place might cause a fire or electric shock.
Do ’t use the produ t at a oltage other tha the rated oltage i di ated o the a eplate.
Otherwise, breakage, fire or electric shock might result.
For a product marked with a frequency, don’t use the product at a frequency other than 50 or 60 Hz (local power supplyfrequency). Use at a wrong frequency might cause a fire.
Installation of the product should be carried out by a qualified person.
Installation by an unqualified person is legally prohibited.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Never touch the lamp and its surroundings while the power is on or just after the power is turned off. The lamp and its
surroundings are very hot, so an accidental touch might cause a burn.
To ensure brightness and safety, carry out periodical cleaning and inspection.
If you find a problem, discontinue the use of the product and have it repaired by a specialist.
A lighting fitting has a service life. A product which has been used for eight to ten years may have degraded internal partseven if it looks normal. For safety and energy saving, we recommend you check and replace it. The LED module design life is60,000 hours (different from the lighting fitting life) when used at an ambient temperature of 30°C, 10 hours per day, 3,000
hours per year. If used at a higher temperature or more hours per year, the life would be shortened. Have a specialist
inspect the product every three years. If used for an extended period without inspection, a smoke, fire, or electric shockmight result.

CONTACT DETAILSFor further information on the product, contact any of our offices listed below (if you like to make an inquiry, let us know the model nameindicated on the product nameplate).

SEIWA ELECTRIC MFG.CO., LTD.
Head Office

36 Shinike, Terada, Joyo, Kyoto Pref. 610-0192 JapanTokyo Branch

2-19-6 Yanagibashi, Taito-ku, Tokyo 111-0052 Japan

Phone
Fax
Phone
Fax

+81 774 55 8181
+81 774 58 2034
+81 3 5833 8946
+81 3 5833 8971

Please note that the above addresses and phone numbers may be changed.
直L G13 照般6- 2/2 -