Weather-proof type LED Lighting Fittings 【LYAA46/LYBA46 Series】
Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑥Optional Parts : Guard②Correlated Color Temperature : 5,000K③Power Consumption : 52.6W⑤Body Material : LYAA46～（Stainless steel）、LYBA46～（Steel plate）⑦Voltage ： AC100-242V±6％⑧Ambient Temperature : -20℃～+40℃（Able to use in seasonal high-temperture place up to 60℃）

⑨Luminaire Flex：7,700Lm⑩Energy Efficiency：146.3Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED52.6W (LYAA4601001)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LYAA4601001) x1pc

Power Consumption (W)LED (LYAA4601001)
x1pc
Fluorescent36W-2
x1pc

52.6
85
0

DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LYAA4601001)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

14.2Lx

2.5 times

36.1LxPowerConsumption

85W

38% Down

52.6W

Lamp
Life12,000h

5 Times60,000h

60,00012,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED52.6W (LYAA4601001)x6pcs
Subject

Fluorescent36W-2 x15pcs

LED (LYAA4601001) x6pcs

Power Consumption (W)LED (LYAA4601001)
x6pcs
Fluorescent36W-2x39pcs

316
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYAA4601001)
x6pcs

Quantity

15pcs

60% Down6pcs

Average
Illuminance213.1Lx

Equivalent

216.8Lx

PowerConsumption

1,275W

75% Down

315.6W

Lamp
Life

12,000h

5 Times

60,000h6Fluorescent36W-2
x39pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYAA46/LYBA46 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LYAA4601001/LYBA4601001
Model No.LYAA4601411/LYBA4601411
Model No.LYAA4601421/LYBA4601421
Model No.LYAA4601461/LYBA4601461
Model No.LYAA4601511H/LYBA4601511H
Model No.LYAA4601131/LYBA4601131

Trough type
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

2.4kg
3.6kg
4.1kg
3.8kg
3kg（Without pole）
2.8kg

Illuminance Level= 2.5 times brighter thanFluorescent 36W-2

Weather-proof type LED Lighting Fittings 【LYAA38/LYBA38 Series】
Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Degree of Protection : IP55④Lamp Life : 60,000h⑥Optional Parts : Guard②Correlated Color Temperature : 5,000K③Power Consumption : 43.6W⑤Body Material : LYAA38～（Stainless steel）、LYBA38～（Steel plate）⑦Voltage ： AC100-242V±6％⑧Ambient Temperature : -20℃～+40℃（Able to use in seasonal high-temperture place up to 60℃）

⑨Luminaire Flex：6,300Lm⑩Energy Efficiency：144.4Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED43.6W (LYAA3801001)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LYAA3801001) x1pc

Power Consumption (W)LED (LYAA3801001)
x1pc
Fluorescent36W-2
x1pc

43.6
85
0DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LYAA3801001)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

14.2Lx

2.1 times

29.6LxPowerConsumption

85W

49% Down

43.6W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED43.6W (LYAA3801001)x8pcs
Subject

Fluorescent36W-2 x15pcs

LED (LYAA3801001) x8pcs

Power Consumption (W)LED (LYAA3801001)
x8pcs
Fluorescent36W-2
x39pcs

349
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYAA3801001)
x8pcs

Quantity

15pcs

47% Down

8pcs

Average
Illuminance213.1Lx

Equivalent236.5Lx

PowerConsumption

1,275W

73% Down

348.8W

Lamp
Life12,000h

5 Times

60,000h8Fluorescent36W-2
x39pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYAA38/LYBA38 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LYAA3801001/LYBA3801001
Model No.LYAA3801411/LYBA3801411
Model No.LYAA3801421/LYBA3801421
Model No.LYAA3801461/LYBA3801461
Model No.LYAA3801511H/LYBA3801511H
Model No.LYAA3801131/LYBA3801131

Trough type
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

2.4kg
3.6kg
4.1kg
3.8kg
3kg（Without pole）
2.8kg

Illuminance Level= 2.1 times brighter thanFluorescent 36W-2

Weather-proof type LED Lighting Fittings 【LYAA25/LYBA25 Series】
Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑥Optional Parts : Guard②Correlated Color Temperature : 5,000K③Power Consumption : 29.8W⑤Body Material : LYAA25～（Stainless steel）、LYBA25～（Steel plate）⑦Voltage ： AC100-242V±6％⑧Ambient Temperature : -20℃～+40℃（Able to use in seasonal high-temperture place up to 60℃）

⑨Luminaire Flex：4,250Lm⑩Energy Efficiency：142.6Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED29.8W (LYAA2501001)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LYAA2501001) x1pc

Power Consumption (W)LED (LYAA2501001)
x1pc
Fluorescent36W-2x1pc

29.8850DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LYAA2501001)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

14.2Lx

41% Up20Lx

PowerConsumption

85W

65% Down

29.8W

Lamp
Life12,000h

5 Times

60,000h60,00012,0000

20,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED29.8W (LYAA2501001)x10pcs
Subject

Fluorescent36W-2 x15pcs

LED (LYAA2501001) x10pcs

Power Consumption (W)LED (LYAA2501001)
x10pcsFluorescent36W-2
x39pcs

298
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYAA2501001)
x10pcsQuantity

15pcs

33% Down

10pcs

Average
Illuminance213.1Lx

Equivalent200.1Lx

PowerConsumption

1,275W

77% Down

298W

Lamp
Life

12,000h

5 Times

60,000h10Fluorescent36W-2
x39pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYAA25/LYBA25 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LYAA2501001/LYBA2501001
Model No.LYAA2501411/LYBA2501411
Model No.LYAA2501421/LYBA2501421
Model No.LYAA2501461/LYBA2501461
Model No.LYAA2501511H/LYBA2501511H
Model No.LYAA2501131/LYBA2501131

Trough type
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type1.9kg3.1kg
3.6kg
3.3kg
2.5kg（Without pole）
2.3kg

Illuminance Level= 41% brighter thanFluorescent 36W-2

Weather-proof type LED Lighting Fittings 【LYAA19/LYBA19 Series】
Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑥Optional Parts : Guard②Correlated Color Temperature : 5,000K③Power Consumption : 23.5W⑤Body Material : LYAA25～（Stainless steel）、LYBA25～（Steel plate）⑦Voltage ： AC100-242V±6％⑧Ambient Temperature : -20℃～+40℃（Able to use in seasonal high-temperture place up to 60℃）

⑨Luminaire Flex：3,300Lm⑩Energy Efficiency：140.4Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED23.5W (LYAA1901001)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LYAA1901001) x1pc

Power Consumption (W)LED (LYAA1901001)
x1pc
Fluorescent36W-2
x1pc

23.5
850

DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LYAA1901001)
x1pc
Fluorescent36W-2x1pc

Quantity

1pc

Equivalent

1pc

AverageIlluminance

14.2Lx

10% Up15.6LxPowerConsumption

85W

72% Down

23.5W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED23.5W (LYAA1901001)x14pcs
Subject

Fluorescent36W-2 x15pcs

LED (LYAA1901001) x14pcs

Power Consumption (W)LED (LYAA1901001)
x14pcsFluorescent36W-2x39pcs

329
1,2750Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYAA1901001)
x14pcsQuantity

15pcs

7% Down

14pcs

Average
Illuminance213.1Lx

Equivalent

218Lx

PowerConsumption

1,275W

74% Down

329W

Lamp
Life

12,000h

5 Times

60,000h14

Fluorescent36W-2
x39pcs

15
14

14

15

15

16

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYAA19/LYBA19 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LYAA1901001/LYBA1901001
Model No.LYAA1901411/LYBA1901411
Model No.LYAA1901421/LYBA1901421
Model No.LYAA1901461/LYBA1901461
Model No.LYAA1901511H/LYBA1901511H
Model No.LYAA1901131/LYBA1901131

Trough type
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

1.9kg
3.1kg
3.6kg
3.3kg
2.5kg（Without pole）
2.3kg

Illuminance Level= 10% brighter thanFluorescent36W-2

Weather-proof type LED Lighting Fittings 【LYAA14/LYBA14 Series】
Replacement LED Lighting Fixture for Fluorescent 18W-2【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑥Optional Parts : Guard②Correlated Color Temperature : 5,000K③Power Consumption : 16W⑤Body Material : LYAA25～（Stainless steel）、LYBA25～（Steel plate）⑦Voltage ： AC100-242V±6％⑧Ambient Temperature : -20℃～+40℃（Able to use in seasonal high-temperture place up to 60℃）

⑨Luminaire Flex：2,300Lm⑩Energy Efficiency：143.7Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent18W-2x1pc / LED16W (LYAA1401001)x1pc
Subject

Fluorescent18W-2 x1pc

LED (LYAA1401001) x1pc

Power Consumption (W)LED (LYAA1401001)
x1pc
Fluorescent18W-2
x1pc

16
490

Distribution
Curve

204060Lamp Life (H)LED (LYAA1401001)
x1pc
Fluorescent18W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.4Lx

2 times

10.9LxPowerConsumption

49W

67% Down

16W

Lamp
Life8,500h

7.1 Times

60,000h60,0008,500
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent18W-2x39pcs / LED16W (LYAA1401001)x20pcs
Subject

Fluorescent18W-2 x39pcs

LED (LYAA1401001) x20pcs

Power Consumption (W)LED (LYAA1401001)
x20pcsFluorescent18W-2
x39pcs

320
1,911
0

Distribution
Curve

1,000 2,000 3,000

Construction Fee (%)
LED (LYAA1401001)
x20pcsQuantity39pcs

49% Down20pcs

Average
Illuminance211.1Lx

Equivalent

217.4Lx

PowerConsumption

1,911W83% Down

320W

Lamp
Life

8,500h

7.1 Times

60,000h20

Fluorescent18W-2
x39pcs390102030

4050

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYAA14/LYBA14 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 18W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LYAA1401001/LYBA1401001
Model No.LYAA1401411/LYBA1401411
Model No.LYAA1401421/LYBA1401421
Model No.LYAA1401461/LYBA1401461
Model No.LYAA1401511H/LYBA1401511H
Model No.LYAA1401131/LYBA1401131

Trough type
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

1.5kg
2.7kg
3.2kg
2.9kg
2.5kg（Without pole）
1.9kg

Illuminance Level= 2 times brighter thanFluorescent 18W-2