11E0200062A11

Instruction Manual
Vapor Tight Type LED Lighting Fittings

To be conserved

LCBB

Thank you very much for purchasing our LED lighting fittings.
Please read this instruction manual to use the product properly.
After installing the product, be sure to hand this manual over to the user of the product.
Prior to use

1) Prior to installing the fitting, check if the product is as per your order.
2) Check for a loose or damaged part due to an accident in transit, etc.

Performance

Input Voltage(Frequency)IPrating100-242V AC(50/60Hz)

IP65

Names of the Components and Installation Method■ Pipe Pendant Type, Bracket Type

Bracket Type

Pipe Pendant TypeFix the terminal box and the suspension bracket on the mounting surface securely.
NB: For the bracket type, fix it on a vertical mounting surface securely.
Screw suspension pipes A and B into the fitting.
After putting the fastening ring around suspension pipe A, screw the terminal box cap onto the suspension pipe. Confirm that the O ring is in
the groove of the terminal box.
Lift the fitting, fit suspension pipe B to the suspension bracket.
Completely fix the stand pole with the support (not supplied) and prescribed terminal box mounting screws.
Connect the power and grounding wires inside the terminal box and conduct insulation treatment on them. Then, remove the suspension
hook and place the hook in the terminal box cap. The black and white wires are power wires. You need not care about polarity. The green
wire is a grounding wire.
Fit the terminal box cap onto the terminal box and turn the fastening ring 90 degrees until the projection aligns with the red mark.
Tighten the locking screws.
Tighten the fixing nuts on the suspension hardware.
NB1: The pipe, locking screws and cross recessed hexagon blots should be tightened securely. Otherwise, the lamp house might fall.
NB2: Caulk the threaded connections.
NB3: For the bracket type, the lamp house may be installed within an angle range of 0° (down) to 45° (oblique). For the direct mount andPipe pendant type, The lamp house may be installed within an angle range of 0° (down).
For the direct mount and Pipe pendant type, The lamp house may be installed within an angle range of 0° (down).
End with a rubber plug

Suspension HookRed MarkO Ring

Terminal Box Cap Cross
Locking Screw
Locking Nut

Suspension Pipe A

Suspension Pipe B--■ Stanchion TypeճLocking Bolts

ղPan-HeadPole Connection Box

Clampձ

Clamp Holder

Stand Pole

Pass the lead from the fitting through the stand pole and insert the pole into thepole connection box in the arrow direction.
Fix the clamp with the pan-head screw.
Tighten the locking screw on the pole connection box.
Be sure to waterproof the commercial terminal box (not supplied) and shortnipple (not supplied) and the screw on the lower part of the pole with a sealing
agent.
Fix the stand pole with a pole support (not supplied) and the mounting hole of aterminal box (not supplied) securely.
Connect the power and grounding wires inside the terminal box (not supplied)and conduct insulation treatment on themյSupport, Not supplied

Screw G3/4
մ

Short Nipple G3/4.,Not supplied

ն

Terminal Box, Not supplied■ Special Direct Mount Type
Holes

Holes
Flexible Fitting(Increased Safety)ճմղInterval 500
ձPass the lead from the lighting fitting through the flexible fitting and attachthe flexible fitting to the fitting.
Attach the other end of the flexible fitting to the terminal box.
Fix the fitting and the terminal box on the mounting surfaces securely.
Connect the power and grounding wires inside the terminal box (notsupplied) and conduct insulation treatment on them.

Terminal Box

How to Use

The LED lamp is turned on by applying the rated voltage to the power cable of the product.

Maintenance■ Inspection 1) In cleaning the fitting, gently wipe with water or mild detergent. Don’t use thinner, benzene or alkaline detergent. Suchchemicals might cause discoloration or deterioration in quality and strength, resulting in a damage.
2) Prior to maintenance, be sure to turn off the power.
3) Carry out maintenance properly in accordance with the related law and regulations.
4) If a repair is needed, consult us.
Disassembly and Disposal
1) In the period when the product is in use, never disassemble it.
2) For disposal of the product, follow the regulations and rules of your local government.
Reordering

Nameplate

When reordering, please let us know:・Drawing or drawing No. for the delivered product・Manufacturing lot number on the nameplate
If the above information is unavailable, give us any material showing the appearance of the product or details of the product specification(dimensions, mounting interval, lamp type, etc.).

--

CAUTIONS
1. The product should be oriented within an angle range of 0° (down) to 90° (horizontal).If the product is installed at an angle out of theallowable range, an insulation failure or electric shock might result.
2. Prior to maintenance or inspection, be sure to turn off the power.
3. Confirm that the screws and bolts are fastened properly and tightly.
4. In the case of the stanchion type, be sure to provide a support at least 800 mm above the bottom of the pole.
5. For outdoor use, waterproof the screwed portion of the conduit, the cable entry fittings and the joint with the stand pole to prevent
rainwater infiltration.
6. When installing the fitting, be sure to connect external wires inside a specified part of the fitting. Don't open any other part of the fitting
unless necessary.
7. The supply voltage variation should be within ±6% of the rating.
8. Close unused entries of the terminal box with plugs.
9. The ambient temperature should be within the range of -20°Cto +40°C. The use of the product out of this range may shorten the servicelife.
10. In grounding work, be sure to follow the technical standards for electrical equipment and explosion-protected equipment of your country.
Inadequate grounding might cause an explosion, fire or electric shock.
11. Prior to maintenance or inspection, be sure to turn off the power.
12. To prevent shortening of the service life, avoid turning on the fitting in direct sunlight.
13. To avoid noise or malfunctioning, don't use a radio, television or wireless infrared remote control near the fitting.
14. Don't open the front glass. The LED internal parts may be very hot. Don't touch the LED light sources. Otherwise a malfunction or lighting
failure might occur.
15. For white LED lamps, the luminescent color and brightness may vary with individual LEDs because of their nature. Also note that the rateof attenuation with time varies with individual LED lamps.
16. The product must be mounted on a sturdy wall surface or structure which is vibration-free and less susceptible to damage. Otherwise, itmight fall or be damaged.
17. For use in an unfavorable location (a very hot, cold or humid place or a place in which there is strong wind or vibration, a salt damage
environment or a dusty or corrosive gas atmosphere), a special countermeasure should be taken.
18. The LED lamp and the power supply unit cannot be replaced.

--11E0000742E11

Safety Precautions-

To be conserved

Prior to use, please read the safety precautions and instruction manual thoroughly to use the product properly.
After installing the product, be sure to hand the safety precautions and instruction manual over to the user of the product.
Please keep the manual in a handy place for later reference.
● The various marks have the following meanings:

WARNING: Improper handling may lead to a human death or serious bodily injury.
CAUTION:

Improper handling may lead to a bodily injury or property damage.

Be sure tofollow theinstructions.

Be sure to turnoff the power.

Disassembly &conversion
prohibited.

Don’t use neara water source.

Be sure toground.

Prohibited.

Don’t touch.

CautionBe careful ofignition.

WARNING
Don’t use the product in a hazardous location where a flammable or explosive atmosphere such as a gaseous, steamy or
dusty atmosphere may exist. Use in such a location might cause an explosion or fire.
The ambient temperature should be within the operating temperature range specified in the instruction manual. If theproduct should be used at a temperature higher than specified, an early lighting failure or malfunction might occur or a firemight result.
If a product must be oriented in a specific manner for use, install it properly according to the marking on its body or theinstruction manual. Otherwise, a fire or electric shock might result.
For electrical connections, use crimp-type terminals, etc. to secure the connections and conduct insulation treatment. An
inadequate connection or inadequate insulation might cause an imperfect contact, leading to a fire or electric shock.
In grounding work, be sure to follow the technical standards for electrical equipmentof your country. Inadequate grounding
might cause a fire or electric shock.
Do ’t o ert the produ t.
Conversion might cause the product to fall or result in a fire or electric shock.
Do ’t o er the produ t ith a i flaa leSuch a material or thing might cause a fire.

aterial su h as loth or paper or put a ythi g i the produ t.

Do ’t e d, t ist or pull the po er a le y for e.
Inadequate handling of the cable might damage it and result in a fire or electric shock.
The parts once removed for cleaning should be replaced properly according to the instruction manual.
An improperly placed part might cause the product to fall, resultng in an injury or property damage.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Do ’t ope LED la p prote ti e o ers su h as the fro t glass a d glass glo e.
Do ’t tou h a LED la p, other ise a alfu tio or lighti g failure ight o ur.
Before cleaning, be sure to turn off the power.
Otherwise, a fire or electric shock might result.
L照般6- 1 /2 -WARNING
If you continue to use the product in an abnormal condition (smoke, odor, etc.), a fire or electric shock might result. If you
detect an abnormality, immediately turn off the power switch. Confirm that the abnormal condition has been eliminated andmake a repair call.
Do ’t use the produ t i a stro g orrosi e gas at osphere hi h o tai s hydro hlori a id or hlori e gases or the like.
Use in a corrosive gas atmosphere might cause the product to corrode and fall, resulting in an injury.
The product should be mounted on a surface robust enough to support its weight, properly according to the instruction
manual. Improper installation might cause the product to fall or result in an electric shock or injury.

CAUTIONAny product not marked as a product for outdoor use should not be used outdoors or in a humid place or near a water
source. Its use in such a place might cause a fire or electric shock.
Do ’t use the produ t at a oltage other tha the rated oltage i di ated o the a eplate.
Otherwise, breakage, fire or electric shock might result.
For a product marked with a frequency, don’t use the product at a frequency other than 50 or 60 Hz (local power supplyfrequency). Use at a wrong frequency might cause a fire.
Installation of the product should be carried out by a qualified person.
Installation by an unqualified person is legally prohibited.
Never touch LED light sources and their surroundings.
The light sources and their surroundings are very hot, so an accidental touch might cause a burn.
To ensure brightness and safety, carry out periodical cleaning and inspection.
If used in an extended period without maintenance or inspection, a smoke, fire or electric shock might result.
A lighting fitting has a service life. A product which has been used for eight to ten years may have degraded internal partseven if it looks normal. For safety and energy saving, we recommend you check and replace it. The LED module design life is60,000 hours (different from the lighting fitting life) when used at an ambient temperature of 30°C, 10 hours per day, 3,000hours per year. If used at a higher temperature or more hours per year, the life would be shortened. Have a specialist inspect
the product every three years. If used for an extended period without inspection, a smoke, fire, or electric shock might result.

Resycling
Ni-Cd
Ni-MH

JBRC

Please bring used Secondary batteries to the recycling station for effective use of precious
resources and global environment conservation.

Japan Portable Rechargeable Battery Recycling Center

Phone +81 3 6403 5763

CONTACT DETAILSFor further information on the product, contact any of our offices listed below (if you like to make an inquiry, let us know the model nameindicated on the product nameplate).

SEIWA ELECTRIC MFG.CO., LTD.
Head Office

36 Shinike, Terada, Joyo, Kyoto Pref. 610-0192 JapanTokyo Branch

2-19-6 Yanagibashi, Taito-ku, Tokyo 111-0052 Japan

Phone
Fax
Phone
Fax

+81 774 55 8181
+81 774 58 2034
+81 3 5833 8946
+81 3 5833 8971

Please note that the above addresses and phone numbers may be changed.
L照般6- 2 /2 -