Weather-proof type LED Lighting Fittings 【LCIP7950 Series】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Degree of Protection : IP65
③Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑦Voltage : AC100-242V±6％⑨Surge protection : 15kV

②Lamp Life : 60,000h④Power Consumption : 77.5W⑥Optional Parts : Guard, Glare cut panel⑧Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED77.5W (LCIP7950)x1pc
Subject

Mercury400W x1pc

LED (LCIP7950) x1pc

Power Consumption (W)LED (LCIP7950) x1pc

77.5

Mercury400W x1pc

425
0 100 200 300 400 500

DistributionCurve

Lamp Life (H)LED (LCIP7950) x1pc

60,000Mercury400W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

9Lx

2.2 Times

19.5LxPowerConsumption

425W

82% Down

77.5W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury400Wx24pcs / LED77.5W (LCIP7950)x10pcs
Subject

Mercury400W x24pcs

LED (LCIP7950) x10pcs

Power Consumption (W)LED (LCIP7950)
x10pcs
Mercury400W
x24pcs775
10,2000Distribution
Curve

5,000

10,000 15,000

Construction Fee (%)
LED (LCIP7950)
x10pcs10

Mercury400W x24pcs

Quantity
Average
Illuminance

24pcs

58% Down

2410pcs
0215.9Lx

More than 200Lx

205.7Lx

PowerConsumption

10,200W

92% Down

775W

Lamp
Life12,000h

5 Times60,000h

510 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCIP7950 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 400W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCIP7950
Model No.LCIP7950
Model No.LCIP7950
Model No.LCIP7950
Model No.LCIP7950
Model No.LCIP7950
Model No.LCIP7950

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

Pole type

7.0kg
7.3kg
7.2kg
7.2kg(without pole)
9.9kg
6.0kg
7.2kg(without pole)

Illuminance Level = 2.2 times brighter than Mercury 400W

Weather-proof type LED Lighting Fittings 【LCIP6050 Series】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Degree of Protection : IP65
③Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑦Voltage : AC100-242V±6％⑨Surge protection : 15kV

②Lamp Life : 60,000h④Power Consumption : 59W⑥Optional Parts : Guard, Glare cut panel⑧Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED59W (LCIP6050)x1pc
Subject

Mercury400W x1pc

LED (LCIP6050) x1pc

Power Consumption (W)LED (LCIP6050) x1pc

59

Mercury400W x1pc

425
0 100 200 300 400 500

Distribution
Curve

Lamp Life (H)LED (LCIP6050) x1pc

60,000Mercury400W x1pc

Quantity

1pc

Equivalent1pc

Average
Illuminance

9Lx

1.6 Times

14.4LxPowerConsumption425W

86% Down

59W

Lamp
Life12,000h

5 Times

60,000h

12,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury400Wx24pcs / LED59W (LCIP6050)x14pcs
Subject

Mercury400W x24pcs

LED (LCIP6050) x14pcs

Power Consumption (W)LED (LCIP6050)
x14pcs
Mercury400W
x24pcs826
10,2000Distribution
Curve

5,000

10,000 15,000

Construction Fee (%)
LED (LCIP6050)
x14pcs

14Mercury400W x24pcs

Quantity
Average
Illuminance

24pcs

42% Down

2414pcs
0215.9Lx

More than 200Lx

205.6Lx

PowerConsumption

10,200W

92% Down

826W

Lamp
Life

12,000h

5 Times

60,000h5

10 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCIP6050 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 400W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCIP6050
Model No.LCIP6050
Model No.LCIP6050
Model No.LCIP6050
Model No.LCIP6050
Model No.LCIP6050
Model No.LCIP6050

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

Pole type

7.0kg
7.3kg
7.2kg
7.2kg(without pole)
9.9kg
6.0kg
7.2kg(without pole)

Illuminance Level = 1.6 times brighter than Mercury 400W

Weather-proof type LED Lighting Fittings 【LCIP3750 Series】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Degree of Protection : IP65
③Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑦Voltage : AC100-242V±6％⑨Surge protection : 15kV

②Lamp Life : 60,000h④Power Consumption : 36.5W⑥Optional Parts : Guard, Glare cut panel⑧Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED36.5W (LCIP3750)x1pc
Subject

Mercury400W x1pc

LED (LCIP3750) x1pc

Power Consumption (W)LED (LCIP3750) x1pc

36.5

Mercury400W x1pc

425
0 100 200 300 400 500

DistributionCurve

Lamp Life (H)LED (LCIP3750) x1pc

60,000Mercury400W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

9Lx

Equivalent

8.6Lx

PowerConsumption

425W

91% Down

36.5W

Lamp
Life

12,000h

5 Times

60,000h

12,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury400Wx24pcs / LED36.5W (LCIP3750)x24pcs
Subject

Mercury400W x24pcs

LED (LCIP3750) x24pcs

Power Consumption (W)LED (LCIP3750)
x24pcs
Mercury400W
x24pcs876
10,2000

Distribution
Curve

5,000

10,000 15,000

Construction Fee (%)

Quantity
Average
Illuminance

24pcs

Equivalent

LED (LCIP3750)
x24pcs24

Mercury400W x24pcs

24

24pcs
0215.9Lx

More than 200Lx

204.3Lx

PowerConsumption

10,200W

91% Down

876W

Lamp
Life

12,000h

5 Times

60,000h510 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

LZIP3750 series is equivalent to Mercury 400W Lighting.
We recommend replacing the same number of existing 400W mercury lamps as installed.

Line-upModel No.LCIP3750
Model No.LCIP3750
Model No.LCIP3750
Model No.LCIP3750
Model No.LCIP3750
Model No.LCIP3750
Model No.LCIP3750

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

Pole type

7.0kg
7.3kg
7.2kg
7.2kg(without pole)
9.9kg
6.0kg
7.2kg(without pole)

Illuminance Level = Equivalent to Mercury 400W