Explosion-proof type LED Lighting Fittings 【LZBP5290 Series】
Ra98 type
Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 50.2W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED50.2W (LZBP5290)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZBP5290) x1pc

Power Consumption (W)LED (LZBP5290) x1pc

50.2

Fluorescent36W-2
x1pc

85
0

DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LZBP5290) x1pc

60,000

Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx

58% Up21.5LxPowerConsumption

85W

41% Down

50.2W

Lamp
Life12,000h

5 Times

60,000h

12,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED50.2W (LZBP5290)x10pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZBP5290) x10pcs

Power Consumption (W)LED (LZBP5290)
x10pcsFluorescent36W-2
x15pcs

502
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZBP5290)
x10pcsQuantity
Average
Illuminance

15pcs

33% Down

10

Fluorescent36W-2
x15pcs10pcs

150204Lx

More than 200Lx

215.1Lx

PowerConsumption

1,275W

61% Down502W

Lamp
Life

12,000h

5 Times

60,000h5101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZBP5290 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZBP5290
Model No.LZBP5290
Model No.LZBP5290
Model No.LZBP5290
Model No.LZBP5290
Model No.LZBP5290

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

8.3kg
8.8kg
8.6kg
8.1kg(without pole)
8.3kg
6.7kg

Illuminance Level = 58% brighter than Fluorescent 36W-2

Explosion-proof type LED Lighting Fittings 【LZBP4850 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 47.3W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED47.3W (LZBP4850)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZBP4850) x1pc

Power Consumption (W)LED (LZBP4850) x1pc

47.3

Fluorescent36W-2x1pc

85
0DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LZBP4850) x1pc

60,000

Fluorescent36W-2x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx2.6 Times

35.6LxPowerConsumption

85W

44% Down

47.3W

Lamp
Life

12,000h

5 Times

60,000h

12,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED47.3W (LZBP4850)x6pcs
SubjectFluorescent36W-2 x15pcs

LED (LZBP4850) x6pcs

Power Consumption (W)LED (LZBP4850)
x6pcs
Fluorescent36W-2
x15pcs284
1,2750Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZBP4850) x6pcs

Quantity
Average
Illuminance

15pcs

60% Down

6

Fluorescent36W-2
x15pcs6pcs

150204Lx

More than 200Lx

213.6Lx

PowerConsumption

1,275W

78% Down

283.8

Lamp
Life

12,000h

5 Times

60,000h5101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZBP4850 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZBP4850
Model No.LZBP4850
Model No.LZBP4850
Model No.LZBP4850
Model No.LZBP4850
Model No.LZBP4850

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

8.3kg
8.8kg
8.6kg
8.1kg(without pole)
8.3kg
6.7kg

Illuminance Level = 2.6 times brighter than Fluorescent 36W-2

Explosion-proof type LED Lighting Fittings 【LZBP2550 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 25W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED25W (LZBP2550)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZBP2550) x1pc

Power Consumption (W)LED (LZBP2550) x1pc

25

Fluorescent36W-2
x1pc

85
0

DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LZBP2550) x1pc

60,000

Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx30% Up17.7LxPowerConsumption

85W

70% Down

25W

Lamp
Life12,000h

5 Times60,000h

12,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED25W (LZBP2550)x12pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZBP2550) x12pcs

Power Consumption (W)LED (LZBP2550)
x12pcsFluorescent36W-2
x15pcs

300
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZBP2550)
x12pcsQuantityAverage
Illuminance

15pcs

20% Down12Fluorescent36W-2
x15pcs12pcs

150204Lx

More than 200Lx

212.1Lx

PowerConsumption

1,275W

76% Down

300W

Lamp
Life

12,000h

5 Times

60,000h5101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZBP2550 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZBP2550
Model No.LZBP2550
Model No.LZBP2550
Model No.LZBP2550
Model No.LZBP2550
Model No.LZBP2550

Ceiling type
Pipe pendant type
Bracket type
Stanchion typeSpecial direct type
Easy replacement type

8.3kg
8.8kg
8.6kg
8.1kg(without pole)
8.3kg
6.7kg

Illuminance Level = 30% brighter than Fluorescent 36W-2