Dust Ignition-proof type LED Lighting Fittings 【LKBB0705 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : SDP-13④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：120.0Lm/W②Hazardous Area : Zone20,21,22⑤Power Consumption : 40W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：4,800Lm●Warranty LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED40W (LKBB070541)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LKBB070541) x1pc

Power Consumption (W)LED (LKBB070541)
x1pc
Fluorescent36W-2
x1pc

4085
0Distribution
Curve

20406080 100

Lamp Life (H)LED (LKBB070541)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx2 Times

27.5LxPowerConsumption

85W

53% Down

40W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED40W (LKBB070541)x8pcs
Subject

Fluorescent36W-2 x15pcs

LED (LKBB070541) x8pcs

Power Consumption (W)LED (LKBB070541)
x8pcs
Fluorescent36W-2
x15pcs320
1,275
0Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LKBB070541)
x8pcs

Quantity

15pcs

47% Down

8pcs

Average
Illuminance

204Lx

Equivalent

220.1Lx

PowerConsumption

1,275W

75％ Down

320W

Lamp
Life12,000h5 Times

60,000h8Fluorescent36W-2
x15pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LKBB0705 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LKBB070541
Model No.LKBB070542
Model No.LKBB070546
Model No.LKBB070551H
Model No.LKBB070510Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

11kg
11.5kg11.5kg11kg(without pole)
11.5kgIlluminance Level = 2 times brighter than Fluorescent 36W-2

Dust Ignition-proof type LED Lighting Fittings 【LKBB0704 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : SDP-13④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：116.7Lm/W②Hazardous Area : Zone20,21,22⑤Power Consumption : 33W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：3,850Lm●Warranty LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED33W (LKBB070441)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LKBB070441) x1pc

Power Consumption (W)LED (LKBB070441)
x1pc
Fluorescent36W-2
x1pc

33
850

Distribution
Curve

20406080 100Lamp Life (H)LED (LKBB070441)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx

60％Up

21.8LxPowerConsumption85W

61% Down

33W

Lamp
Life

12,000h

5 Times

60,000h60,00012,0000

20,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED33W (LKBB070441)x10pcs
Subject

Fluorescent36W-2 x15pcs

LED (LKBB070441) x10pcs

Power Consumption (W)LED (LKBB070441)
x10pcsFluorescent36W-2x15pcs

330
1,275
0Distribution
Curve500

1,000 1,500

Construction Fee (%)
LED (LKBB070441)
x10pcsQuantity

15pcs

33% Down

10pcs

Average
Illuminance

204Lx

Equivalent217.8Lx

PowerConsumption

1,275W

74％ Down

330W

Lamp
Life

12,000h

5 Times

60,000h10Fluorescent36W-2
x15pcs

150

510

1520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LKBB0704 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LKBB070441
Model No.LKBB070442
Model No.LKBB070446
Model No.LKBB070451H
Model No.LKBB070410

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

11kg
11.5kg11.5kg11kg(without pole)
11.5kgIlluminance Level = 60％ brighter than Fluorescent 36W-2