Explosion-proof type LED Lighting Fittings 【LZAB2602-V2 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Luminaire Flex：7,200Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 58W⑧Optional Parts : Guard⑪Energy Efficiency：124.1Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED58W (LZAB260241V2)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZAB260241V2) x1pc

Power Consumption (W)LED (LZAB260241V2)
x1pc
Fluorescent36W-2
x1pc

58
850

DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LZAB260241V2)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx

2.4 Times

32.1LxPowerConsumption

85W

32% Down

58W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED58W (LZAB260241V2)x8pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZAB260241V2) x8pcs

Power Consumption (W)LED (LZAB260241V2)
x8pcs
Fluorescent36W-2
x15pcs464
1,2750Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZAB260241V2)
x8pcs

Quantity

15pcs

47% Down

8pcs

Average
Illuminance

204Lx

Equivalent

256.5Lx

PowerConsumption1,275W

64% Down

464W

Lamp
Life

12,000h

5 Times

60,000h8Fluorescent36W-2
x15pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZAB2602-V2 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZAB260241V2 Ceiling type
Model No.LZAB260242V2 Pipe pendant typeModel No.LZAB260246V2 Bracket type
Model No.LZAB260251HV2 Stanchion type
Model No.LZAB260210V2 Direct type16kg
16.5kg16kg
14.5kg(without pole)
15.5kgIlluminance Level = 2.4 times brighter than Fluorescent 36W-2

Explosion-proof type LED Lighting Fittings 【LZAB2601-V2 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-1【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Luminaire Flex：3,600Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 30W⑧Optional Parts : Guard⑪Energy Efficiency：120.0Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-1x1pc / LED30W (LZAB260141V2)x1pc
Subject

Fluorescent36W-1 x1pc

LED (LZAB260141V2) x1pc

Power Consumption (W)LED (LZAB260141V2)
x1pc
Fluorescent36W-1
x1pc

30
470

DistributionCurve

10 20 30 40 50

Lamp Life (H)LED (LZAB260141V2)
x1pc
Fluorescent36W-1x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

6.9Lx

2.3 Times

15.8LxPowerConsumption

47W

36% Down

30W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-1x30pcs / LED30W (LZAB260141V2)x14pcs
Subject

Fluorescent36W-1 x30pcs

LED (LZAB260141V2) x14pcs

Power Consumption (W)LED (LZAB260141V2)
x14pcsFluorescent36W-1
x30pcs

420
1,410
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZAB260141V2)
x14pcsQuantity

30pcs

53% Down

14pcs

Average
Illuminance

207Lx

Equivalent

220.9Lx

PowerConsumption

1,410W

70% Down

420W

Lamp
Life

12,000h

5 Times

60,000h14

Fluorescent36W-1
x30pcs

30010

203040Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZAB2601-V2 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-１
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZAB260141V2 Ceiling type
Model No.LZAB260142V2 Pipe pendant type
Model No.LZAB260146V2 Bracket type
Model No.LZAB260151HV2 Stanchion type
Model No.LZAB260110V2 Direct type

13kg
13.5kg13kg
11.5kg(without pole)
12.5kgIlluminance Level = 2.3 times brighter than Fluorescent 36W-1