11E0000909A11Installation manualConstituent Parts
LCTX0005V2 to 0007V2

Product Outline

Angle adjusting grip

Wire connection box coverFront cover

LED Floodlight

Item
Luminaire modelname

LCTX0005V2

LCTX0006V2

LCTX0007V2

Light distribution

LCTX0002V2

LCTX0003V2

LCTX0004V2

Narrow angle

Medium angle

Wide angle

LCTX0005V2 to 0007V2：16kg

WeightLCTX0002V2 to 0004V2：28kg

Wire connection
box

5000[K]

Color temperature
Finish color

Gray metallic

Suitable wire

3‐wire cable with a final outside diameter of 10 to 14 mm
equivalent to or more than 600V 2PNCT (type 2 EP rubber‐insulated chloroprene cabtyre cable)

Application

HandleOutdoor general application

Rated input voltage

100‐242V

Rain proof type

Voltage fluctuation range

Rated voltage ±6%‐5～35℃

Frequency

50 / 60Hz

Watertightness
Ambient temperature

LCTX0002V2 to 0004V2

Angle adjusting grip

● Precautions in use‐ Before installing the floodlight, confirm the range of motion of the floodlight as shown in Fig. 1(a) or 1(b). Paying attention to thepositional relation between the structure and the arm, take care that the floodlight does not contact the structure. An accidental
contact might cause a fire.

Wire connection box cover

Front cover

Wire connection box

HandleFig. 2‐

The angle adjusting grip (Fig. 2) is intended to be used for illuminating angle adjustment after installation and should not be used tocarry the fitting. If it is used to carry the fitting, the fitting might fall and cause an injury.

Installation of the Floodlight‐

Don’t look straight at the LED. Your eyes might be impaired.
The color and brightness of LEDs fluctuate more largely than ordinary light sources such as candescent lamps and fluorescent lamps.
The color of light may vary with individual LEDs. Note that when the illumination distance is short, there may be uneven brightness orcolor unevenness depending on the illuminated surface.

Carry out installation work in consideration of interference between the floodlight and structure.
Insertthe two M16 mounting bolts into the hole of the seat placed on the mounting surface of the building with the specified interval between
1.
them (55 mm) as shown in Fig. 3 and firmly tighten each mounting bolt together with a plain washer, spring washer and M16 hexagonal nut ata recommended torque (94‐108 N･m). Inadequate tightening might cause the floodlight to fall and result in an injury.

‐‐If the floodlight is used at a higher ambient temperature than 35°C or the LED is lit in a place exposed to direct sunlight, the internal
thermal fuse may be activated to turn off the LED. Though this is not a failure but a function to protect the electronic components, don’t use the floodlight in such an environment. A temperature rise might cause a fire or electrical failure or shorten the LED life.

‐

Be careful not to scratch the front cover of the floodlight. Scratching might cause damage, deterioration in watertightness or decline inilluminance. If a crack is found in the front cover, let us know since it must be replaced immediately.

‐

Don’t use the floodlight in a place where it may be water‐covered. The use in such a place might cause an electric leak, electric shock or
malfunction.

Hole (18)M16 hexagonal nut , Spring washer , Plain washer
M16 mounting bolt

Terminal block screwTerminal block

Groundingterminal screw

Mount

Cable retainer
Cable retainer
screw

Floodlight installation dimensions
Fastening nut

NB: The LCTX00022V2 to LCTX0004V2 have
* When the floodlight is installed on the ground and its
upward angle range is from 30 to 60 degrees, it cannot be
fixed due to the presence of the mounting bolts (M16). If themounting bolts interfere with rotation of the floodlight forangle adjustment, adjust the illuminating angle before fixing
the floodlight.

3‐wire cable
Outside diameter

different seat shapes from the above but
their installation dimensions are the same as
those of the LCTX0005V2 to LCTX0007V2.

Fig. 3Fig.4

2. Loosen the two screws on the wire connection box cover and remove the cover.
3. Pass a 3‐wire cable with a final outside diameter of 10 to 14 mm (equivalent to or more than 600V 2PNCT (type 2 EP rubber‐insulatedchloroprene cabtyre cable) through the fastening nut, connect it to the terminal block as shown in Fig. 4 and tighten the terminal block screw
firmly at a recommended torque (1.3‐1.5 N･m). Fix the 3‐wire cable with the cable retainer securely and tighten the cable retainer screw at arecommended torque (1.3‐1.5N･m) securely.
4. Tighten the two screws on the wire connection box cover evenly at a recommended torque (1.3‐1.5N ･ m) securely to prevent rainwater
infiltration. Also tighten the fastening nut securely to prevent rainwater infiltration.

(a)LCTX0005V2～0007V2(b)LCTX0002V2～0004V2

5. Carry out Class D grounding 100Ω or below for the floodlight using the grounding terminal in the wire connection box.
(recommended grounding terminal screw tightening torque: 1.3‐1.5N･m).

Fig. 1 Interference between the floodlight and the structure‐‐The product is a stationary floodlight. If it is not fixed for use, a fire, electric shock, burn or fall might result.
If a floodlight pedestal is used, note that this floodlight is heavier than conventional (HID) floodlights and a conventional pedestal may
not be rigid enough and cause an accident such as a fall. If you are going to use a pedestal, consult us.

Adjustment of the illuminating angle
1. To adjust the illuminating angle, loosen the two handles with the floodlight supported by the angle adjusting grip securely (Fig. 2) and gently
adjust the illuminating angle. If the floodlight is not supported securely, it might suddenly turn, resulting in a damage or injury.
2. After adjustment of the illuminating angle, tighten the handles firmly (recommended tightening torque: 22‐25 N･m).
Inadequate tightening might cause the floodlight to fall, resulting in an accident.

LLPM00312‐2

11E0000741D11

Safety Precautions-To be conserved

Prior to use, please read the safety precautions and instruction manual thoroughly to use the product properly.
After installing the product, be sure to hand the safety precautions and instruction manual over to the user of the product.
Please keep the manual in a handy place for later reference.
● The various marks have the following meanings:

WARNING: Improper handling may lead to a human death or serious bodily injury.
CAUTION:

Improper handling may lead to a bodily injury or property damage.

Be sure tofollow theinstructions.

Be sure to turnoff the power.

Disassembly &conversion
prohibited.

Don’t use neara water source.

Be sure toground.

Prohibited.

Don’t touch.

CautionBe careful ofignition.

WARNING
Don’t use the product in a hazardous location where a flammable or explosive atmosphere such as a gaseous, steamy or
dusty atmosphere may exist. Use in such a location might cause an explosion or fire.
The ambient temperature should be within the operating temperature range specified in the instruction manual. If theproduct should be used at a temperature higher than specified, an early lighting failure or malfunction might occur or a firemight result.
If a product must be oriented in a specific manner for use, install it properly according to the marking on its body or theinstruction manual. Otherwise, a fire or electric shock might result.
For electrical connections, use crimp-type terminals, etc. to secure the connections and conduct insulation treatment. An
inadequate connection or inadequate insulation might cause an imperfect contact, leading to a fire or electric shock.
In grounding work, be sure to follow the technical standards for electrical equipmentof your country. Inadequate grounding
might cause a fire or electric shock.
Do ’t o ert the produ t.
Conversion might cause the product to fall or result in a fire or electric shock.
Do ’t o er the produ t ith a i fla
a leSuch a material or thing might cause a fire.

aterial su h as loth or paper or put a ythi g i the produ t.

Do ’t e d, t ist or pull the po er a le y for e.
Inadequate handling of the cable might damage it and result in a fire or electric shock.
The parts once removed for cleaning should be replaced properly according to the instruction manual.
An improperly placed part might cause the product to fall, resultng in an injury or property damage.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Do ’t ope LED la p prote ti e o ers su h as the fro t glass a d glass glo e.
Do ’t tou h a LED la p, other ise a alfu tio or lighti g failure ight o ur.
Before cleaning, be sure to turn off the power.
Otherwise, a fire or electric shock might result.
L照般4- 1/2 -WARNING
If you continue to use the product in an abnormal condition (smoke, odor, etc.), a fire or electric shock might result. If you
detect an abnormality, immediately turn off the power switch. Confirm that the abnormal condition has been eliminatedand make a repair call.
Don’t use the product in a strong corrosive gas atmosphere which contains hydrochloric acid or chlorine gases or the like.
Use in a corrosive gas atmosphere might cause the product to corrode and fall, resulting in an injury.
The product should be mounted on a surface robust enough to support its weight, properly according to the instruction
manual. Improper installation might cause the product to fall or result in an electric shock or injury.

CAUTIONAny product not marked as a product for outdoor use should not be used outdoors or in a humid place or near a water
source. Its use in such a place might cause a fire or electric shock.
Do ’t use the produ t at a oltage other tha the rated oltage i di ated o the a eplate.
Otherwise, breakage, fire or electric shock might result.
For a product marked with a frequency, don’t use the product at a frequency other than 50 or 60 Hz (local power supplyfrequency). Use at a wrong frequency might cause a fire.
Installation of the product should be carried out by a qualified person.
Installation by an unqualified person is legally prohibited.
Never touch LED light sources and their surroundings.
The light sources and their surroundings are very hot, so an accidental touch might cause a burn.
To ensure brightness and safety, carry out periodical cleaning and inspection.
If used in an extended period without maintenance or inspection, a smoke, fire or electric shock might result.
A lighting fitting has a service life. A product which has been used for eight to ten years may have degraded internal partseven if it looks normal. For safety and energy saving, we recommend you check and replace it.
*Operating conditions: ambient temperature of 30 ° C, 10 hours per day, 3,000 hours per year. If used at a higher
temperature or more hours per year, the life would be shortened. Have a specialist inspect the product every three years.If
used for an extended period without inspection, a smoke, fire or electric shock might result.

CONTACT DETAILSFor further information on the product, contact any of our offices listed below (if you like to make an inquiry, let us know the model nameindicated on the product nameplate).

SEIWA ELECTRIC MFG.CO., LTD.
Head Office

36 Shinike, Terada, Joyo, Kyoto Pref. 610-0192 JapanTokyo Branch

2-19-6 Yanagibashi, Taito-ku, Tokyo 111-0052 Japan

Phone
Fax
Phone
Fax

+81 774 55 8181
+81 774 58 2034
+81 3 5833 8946
+81 3 5833 8971

Please note that the above addresses and phone numbers may be changed.
L照般4- 2/2 -