Explosion-proof type / Dust Ignition-proof type LED Lighting Fittings 【LZWA1404-CA Series】

Replacement LED Lighting Fixture for Mercury 250W
【Specifications】①Type of Protection : ExdeⅡB+H2T6Gb / ExtD A20 IP65 T80℃
②Hazardous Area : Zone1,2/Zone21,22③Degree of Protection : IP66
④Correlated Color Temperature : 5,000K⑤Power Consumption : 59W⑥Lamp Life : 60,000h⑦Body Material : Aluminum die-cast⑧Optional Parts : Guard⑨Voltage ： AC220-240V±6％⑩Ambient Temperature : -20℃～+55℃⑪Luminaire Flex：6,150Lm⑫Energy Efficiency：104.2Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in China●With anti-glare cover【1 Unit Comparison】 : Mercury250Wx1pc / LED59W (LZWA140411-CA)x1pc
Subject

Mercury250W x1pc

LED (LZWA140411-CA) x1pc

Power Consumption (W)LED (LZWA140411CA) x1pc

59

Mercury250W x1pc

2700Distribution
Curve100200300

Lamp Life (H)LED (LZWA140411CA) x1pc

60,000Mercury250W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.2Lx

56% Up8.1Lx

PowerConsumption

270W

78% Down

59W

Lamp
Life12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury250Wx40pcs / LED59W (LZWA140411-CA)x25pcs
Subject

Mercury250W x40pcs

LED (LZWA140411-CA) x25pcs

Power Consumption (W)LED (LZWA140411CA) x25pcs
Mercury250W
x40pcs

1,475
10,8000Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LZWA140411CA) x25pcs

25Mercury250W x40pcs

Quantity40pcs

38% Down

25pcs

Average
Illuminance209.3Lx

Equivalent202Lx

PowerConsumption

10,800W

86% Down

1,475W

Lamp
Life

12,000h

5 Times

60,000h

40010203040

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWA1404-CA series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 250W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZWA140441-CA
Model No.LZWA140442-CA
Model No.LZWA140446-CA
Model No.LZWA140411-CA

Ceiling type
Pipe pendant type
Bracket typeSpecial direct type/Stanchion type

50

Illuminance Level = 56% brighter than Mercury 250W

Explosion-proof type / Dust Ignition-proof type LED Lighting Fittings 【LZWA1403-CA Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6Gb / ExtD A20 IP65 T80℃
②Hazardous Area : Zone1,2/Zone21,22③Degree of Protection : IP66
④Correlated Color Temperature : 5,000K⑤Power Consumption : 45W⑥Lamp Life : 60,000h⑦Body Material : Aluminum die-cast⑧Optional Parts : Guard⑨Voltage ： AC220-240V±6％⑩Ambient Temperature : -20℃～+55℃⑪Luminaire Flex：4,450Lm⑫Energy Efficiency：98.9Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in China●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED45W (LZWA140311-CA)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZWA140311-CA) x1pc

Power Consumption (W)LED (LZWA140311CA) x1pc
Fluorescent36W-2
x1pc

45850DistributionCurve2040 60

80 100Lamp Life (H)LED (LZWA140311CA) x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.6Lx

72% Up23.4LxPowerConsumption

85W

47% Down

45W

Lamp
Life12,000h

5 Times

60,000h60,00012,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED45W (LZWA140311-CA)x9pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZWA140311-CA) x9pcs

Power Consumption (W)LED (LZWA140311CA) x9pcs
Fluorescent36W-2
x15pcs405
1,2750Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZWA140311CA) x9pcs

Quantity

15pcs

40% Down

9pcs

Average
Illuminance

204Lx

Equivalent210.8Lx

PowerConsumption

1,275W

68% Down

405W

Lamp
Life

12,000h

5 Times

60,000h9Fluorescent36W-2
x15pcs1505101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWA1403-CA series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZWA140341-CA
Model No.LZWA140342-CA
Model No.LZWA140346-CA
Model No.LZWA140311-CA

Ceiling type
Pipe pendant type
Bracket typeSpecial direct type/Stanchion type

Illuminance Level = 72% brighter than Fluorescent 36W-2