Weather-proof type LED Lighting Fittings 【LCAB Series】

Replacement LED Lighting Fixture for Fluorescent 18W-2【Specifications】①Degree of Protection : IP65
④Lamp Life : 60,000h⑦Voltage ： AC100-242V±6％②Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast③Power Consumption : 34W⑥Optional Parts : Guard⑧Luminaire Flex：2,900Lm⑨Energy Efficiency：85.3Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent18W-2x1pc / LED34W (LCAB100341)x1pc
Subject

Fluorescent18W-2 x1pc

LED (LCAB100341) x1pc

Power Consumption (W)LED (LCAB100341)
x1pc
Fluorescent18W-2
x1pc

34
490Distribution
Curve

204060Lamp Life (H)LED (LCAB100341)
x1pc
Fluorescent18W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.4Lx

2.6 times

13.8LxPowerConsumption

49W

31% Down

34W

Lamp
Life8,500h

7.1 Times

60,000h60,0008,500
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent18W-2x39pcs / LED34W (LCAB100341)x15pcs
Subject

Fluorescent18W-2 x39pcs

LED (LCAB100341) x15pcs

Power Consumption (W)LED (LCAB100341)
x15pcsFluorescent18W-2
x39pcs510
1,911
0Distribution
Curve

1,000 2,000 3,000

Construction Fee (%)
LED (LCAB100341)
x15pcsQuantity

39pcs

62% Down

15pcs

Average
Illuminance211.1Lx

Equivalent

207.4Lx

PowerConsumption

1,911W

73% Down

510W

Lamp
Life

8,500h

7.1 Times

60,000h15

Fluorescent18W-2
x39pcs3901020304050Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCAB Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 18W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCAB100341
Model No.LCAB100342
Model No.LCAB100346
Model No.LCAB100351H
Model No.LCAB100311

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

7kg
7kg
7kg
6kg(without pole)
6kgIlluminance Level = 2.6 times brighter than Fluorescent 18W-2

Weather-proof type LED Lighting Fittings 【LCIA1104 Series】

Replacement LED Lighting Fixture for Mercury 250W
【Specifications】①Degree of Protection : IP65
④Lamp Life : 60,000h⑦Voltage ： AC100-242V±6％②Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑧Luminaire Flex：5,800Lm③Power Consumption : 56W⑥Optional Parts : Guard⑨Energy Efficiency：103.6Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury250Wx1pc / LED56W (LCIA110441)x1pc
Subject

Mercury250W x1pc

LED (LCIA110441) x1pc

Power Consumption (W)LED (LCIA110441)
x1pc

56

Mercury250W x1pc

270
0Distribution
Curve100200300

Lamp Life (H)LED (LCIA110441)
x1pc

60,000Mercury250W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.2Lx

33% Up6.9Lx

PowerConsumption

270W

79% Down

56W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury250Wx40pcs / LED56W (LCIA110441)x30pcs
Subject

Mercury250W x40pcs

LED (LCIA110441) x30pcs

Power Consumption (W)LED (LCIA110441)
x30pcs
Mercury250W
x40pcs

1,680
10,8000Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LCIA110441)
x30pcs30

Mercury250W x40pcs

Quantity

40pcs

25% Down

30pcs

Average
Illuminance209.3Lx

Equivalent

206.2Lx

PowerConsumption

10,800W

84% Down

1,680W

Lamp
Life12,000h

5 Times60,000h40010203040

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCIA1104 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 250W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCIA110441
Model No.LCIA110442
Model No.LCIA110446
Model No.LCIA110452H
Model No.LCIA110461HCeiling type
Pipe pendant type
Bracket type
Stanchion type
Pole type7.5kg8kg
8kg
6.5kg(without pole)
6.5kg(without pole)

50

Illuminance Level = 33% brighter than Mercury 250W

LED High-bay Lighting Fittings 【LFHC8001100-CA】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Degree of Protection : IP65
④Lamp Life : 50,000h⑦Beam Angle : 100°
⑩Energy Efficiency：133.0Lm/W②Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑧Ambient Temperature : -30℃～+55℃③Power Consumption : 80W⑥Voltage ： AC100-240V±6％⑨Luminaire Flex：10,641Lm●Warranty period of LED Lighting Fittings = 3 years●Made in China【1 Unit Comparison】 : Mercury400Wx1pc / LED80W (LFHC8001100-CA)x1pc
Subject

Mercury400W x1pc

LED (LFHC8001100-CA) x1pc

Power Consumption (W)LED (LFHC8001100CA) x1pc

80

Mercury400W x1pc

425
0 100 200 300 400 500

Distribution
Curve

Lamp Life (H)LED (LFHC8001100CA) x1pc

50,000Mercury400W x1pc

Quantity

1pc

Average
Illuminance

9Lx

PowerConsumption

425W

Lamp
Life

12,000h

Equivalent

1pc

71% Up15.4Lx

81% Down

80W

4.2 Times

50,000h

12,000020,000

40,00060,000Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury400Wx24pcs / LED80W (LFHC8001100-CA)x14pcs
Subject

Mercury400W x24pcs

LED (LFHC8001100-CA) x14pcs

Power Consumption (W)LED (LFHC8001100CA) x14pcs
Mercury400W
x24pcs

1,120
10,2000

Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LFHC8001100CA) x14pcs

14Mercury400W x24pcs

Quantity24pcs

42% Down

14pcs

Average
Illuminance215.9Lx

Equivalent215.2LxPowerConsumption

10,200W

89% Down

1,120W

Lamp
Life

12,000h

4.2 Times

50,000h240Line-up
Beam Angle 80°
Beam Angle 100°
Beam Angle 120°

10 15 20 25 30

Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LFHC8001100-CA has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 400W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LFHC800180-CA
Model No.LFHC8001100-CA
Model No.LFHC8001120-CA5Calculation Condition

Illuminance Level = 71% brighter than Mercury 400W

Explosion-proof type LED Lighting Fittings 【LZBA40-V2 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Luminaire Flex：5,850Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 46W⑧Optional Parts : Guard⑪Energy Efficiency：127.1Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED46W (LZBA400141V2)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZBA400141V2) x1pc

Power Consumption (W)LED (LZBA400141V2)
x1pc
Fluorescent36W-2
x1pc

4685
0DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LZBA400141V2)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Average
Illuminance

13.6LxPowerConsumption

85W

Lamp
Life12,000h

Equivalent

1pc

2.2 Times30Lx

46% Down46W

5 Times

60,000h60,00012,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED46W (LZBA400141V2)x8pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZBA400141V2) x8pcs

Power Consumption (W)LED (LZBA400141V2)
x8pcs
Fluorescent36W-2
x15pcs368
1,2750Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LZBA400141V2)
x8pcs

Quantity

15pcs

47% Down

8pcs

Average
Illuminance

204Lx

Equivalent203.2Lx

PowerConsumption

1,275W

71％ Down

368W

Lamp
Life

12,000h

5 Times

60,000h8Fluorescent36W-2
x15pcs150

5101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : FL+5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZBA40-V2 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZBA400141V2 Ceiling type
Model No.LZBA400142V2 Pipe pendant type
Model No.LZBA400146V2 Bracket type
Model No.LZBA400151V2H Stanchion type
Model No.LZBA400110V2 Direct type

11kg
11.5kg11.5kg10kg(without pole)
12kg

Illuminance Level = 2.2 times brighter than Fluorescent 36W-2

Explosion-proof type LED Lighting Fittings 【LZBA24-V2 Series】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Luminaire Flex：3,500Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 29W⑧Optional Parts : Guard⑪Energy Efficiency：120.6Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED29W (LZBA240141V2)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZBA240141V2) x1pc
LED (LZBA240141V2)x1pc
Fluorescent36W -2x1pc

29850DistributionCurve

20 40 60 80 100

LED (LZBA240141V2)
x1pc
Fluorescent36W -2
x1pc

Quantity

1pc

1pc

Average
Illuminance

13.6Lx

18Lx

PowerConsumption

85W

29W

Lamp
Life

12,000h60,000h60,00012,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED29W (LZBA240141V2)x12pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZBA240141V2) x12pcs
LED (LZBA240141V2)
x12pcsFluorescent36W -2
x30pcs348
1,275
0Distribution
Curve

500 1,000 1,500

LED (LZBA240141V2)
x12pcsQuantity

15pcs

12pcs

Average
Illuminance

204Lx

215.7Lx

PowerConsumption

1,275Ｗ

348W

Lamp
Life

12,000h60,000h12

Fluorescent36W -2
x15pcs150

5101520

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZBA24-V2 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZBA240141V2 Ceiling type
Model No.LZBA240142V2 Pipe pendant type
Model No.LZBA240146V2 Bracket type
Model No.LZBA240151V2H Stanchion type
Model No.LZBA240110V2 Direct type

9.5kg
10kg
10kg
8.5kg(without pole)
10.5kgIlluminance Level = 32% brighter than Fluorescent 36W-2

Explosion-proof type LED Lighting Fittings 【LZLA27 Series】

Replacement LED Lighting Fixture for Mercury 100W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast⑩Luminaire Flex：2,750Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 31.5W⑧Optional Parts : Guard⑪Energy Efficiency：87.3Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury100Wx1pc / LED31.5W (LZLA270141)x1pc
Subject

Mercury100W x1pc

LED (LZLA270141) x1pc

Power Consumption (W)LED (LZLA270141)
x1pc

31.5

Mercury100W x1pc

1200Distribution
Curve50100150

Lamp Life (H)LED (LZLA270141)
x1pc

60,000Mercury100W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

7.3Lx

60% Up11.7LxPowerConsumption

120W

74% Down

31.5W

Lamp
Life12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury100Wx28pcs / LED31.5W (LZLA270141)x18pcs
Subject

Mercury100W x28pcs

LED (LZLA270141) x18pcs

Power Consumption (W)LED (LZLA270141)
x18pcs
Mercury100W
x28pcs567
3,3600Distribution
Curve

1,000 2,000 3,000 4,000

Construction Fee (%)
LED (LZLA270141)
x18pcs18

Mercury100W x28pcs

Quantity

28pcs

36% Down

18pcs

Average
Illuminance

205.3Lx

Equivalent

209.9Lx

PowerConsumption

3,360W

83% Down

567W

Lamp
Life

12,000h

5 Times

60,000h280510 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10mLighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA27 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 100W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZLA270141
Model No.LZLA270142
Model No.LZLA270146
Model No.LZLA270151H
Model No.LZLA270110

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8㎏

Illuminance Level = 60% brighter than Mercury 100W