Explosion-proof type LED Floodlight 【LZIB13087V2】

Replacement LED Floodlight for Mercury 400W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast⑩Luminaire Flex：12,250Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 110.5W⑧Optional Parts : Guard⑪Energy Efficiency：110.8Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED110.5W (LZIB13087V2)x1pc
Subject

Mercury400W x1pc

LED (LZIB13087V2) x1pc

Power Consumption (W)LED (LZIB13087V2)
x1pc

110.5

Mercury400W x1pc

425
0 100 200 300 400 500

Lamp Life (H)LED (LZIB13087V2)
x1pc

60,000Mercury400W x1pc

12,0000Distribution
Curve

20,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°

Quantity

1pc

Equivalent

1pc

Average
Illuminance

3.4Lx

2.2 Times

7.6Lx

PowerConsumption

425W

74% Down

110.5W

LampLife12,000h

5 Times

60,000hLine-upModel No.LZIB13087V2Floodlight type17kg

Illuminance Level = 2.2 times brighter than Mercury 400W

Explosion-proof type LED Floodlight 【LZIB13077V2】

Replacement LED Floodlight for Mercury 400W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast②Hazardous Area : Zone1/Zone2⑤Power Consumption : 97W⑧Optional Parts : Guard⑩Luminaire Flex：10,600Lm⑪Energy Efficiency：109.2Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED97W (LZIB13077V2)x1pc
Subject

Mercury400W x1pc

LED (LZIB13077V2) x1pc

Power Consumption (W)LED (LZIB13077V2)
x1pc

97

Mercury400W x1pc

425
0 100 200 300 400 500

Lamp Life (H)LED (LZIB13077V2)
x1pc

60,000Mercury400W x1pc

12,0000Distribution
Curve

20,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°Quantity

1pc

Equivalent

1pc

Average
Illuminance

3.4Lx

1.9 Times

6.6Lx

PowerConsumption

425W

77% Down

97W

Lamp
Life

12,000h

5 Times

60,000hLine-upModel No.LZIB13087V2Floodlight type

17kg

Illuminance Level = 1.9 times brighter than Mercury 400W

Explosion-proof type LED Floodlight 【LZIB13047V2】

Replacement LED Floodlight for Mercury 250W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast②Hazardous Area : Zone1/Zone2⑤Power Consumption : 56W⑧Optional Parts : Guard⑩Luminaire Flex：6,100Lm⑪Energy Efficiency：108.9Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan
Comparison Data 【1 Unit Comparison】 : Mercury250Wx1pc / LED56W (LZIB13047V2)x1pc
Subject

Mercury250W x1pc

LED (LZIB13047V2) x1pc

Power Consumption (W)LED (LZIB13047V2)
x1pc

56

Mercury250W x1pc

2700100200300

Lamp Life (H)LED (LZIB13047V2)
x1pc

60,000Mercury250W x1pc

12,0000DistributionCurve

20,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°

Quantity

1pc

Equivalent

1pc

Average
Illuminance

1.6Lx

2.4Times

3.8Lx

PowerConsumption

270W

79% Down

56W

Lamp
Life

12,000h

5 Times

60,000hLine-upModel No.LZIB13047V2

Floodlight type

16kg

Illuminance Level = 2.4 times brighter than Mercury 250W