Explosion-proof type LED Lighting Fittings 【LZLA27 Series】

Replacement LED Lighting Fixture for Mercury 100W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast⑩Luminaire Flex：2,750Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 31.5W⑧Optional Parts : Guard⑪Energy Efficiency：87.3Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury100Wx1pc / LED31.5W (LZLA270141)x1pc
Subject

Mercury100W x1pc

LED (LZLA270141) x1pc

Power Consumption (W)LED (LZLA270141)
x1pc

31.5

Mercury100W x1pc

1200Distribution
Curve50100

150

Lamp Life (H)LED (LZLA270141)
x1pc

60,000Mercury100W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

7.3Lx

60% Up11.7LxPowerConsumption

120W

74% Down

31.5W

Lamp
Life12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10mLighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury100Wx28pcs / LED31.5W (LZLA270141)x18pcs
Subject

Mercury100W x28pcs

LED (LZLA270141) x18pcs

Power Consumption (W)LED (LZLA270141)
x18pcs
Mercury100W
x28pcs

567
3,360
0

Distribution
Curve

1,000 2,000 3,000 4,000

Construction Fee (%)
LED (LZLA270141)
x18pcs18

Mercury100W x28pcs

Quantity

28pcs

36% Down

18pcs

Average
Illuminance

205.3Lx

Equivalent209.9Lx

PowerConsumption

3,360W

83% Down567W

Lamp
Life

12,000h

5 Times

60,000h280510 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA27 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 100W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZLA270141
Model No.LZLA270142
Model No.LZLA270146
Model No.LZLA270151H
Model No.LZLA270110

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8㎏

Illuminance Level = 60% brighter than Mercury 100W

Explosion-proof type LED Lighting Fittings 【LZLA15 Series】

Replacement LED Lighting Fixture for Mercury 100W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast②Hazardous Area : Zone1/Zone2⑤Power Consumption : 20W⑧Optional Parts : Guard③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury 100Wx1pc / LED20W (LZLA150141)x1pc
Subject

Mercury 100Wx1pc

LED (LZLA150141) x1pc

Power Consumption (W)LED (LZLA150141)
x1pc

20

Mercury 100Wx1pc

120
0Distribution
Curve

50100150

Lamp Life (H)LED (LZLA150141)
x1pc

60,000Mercury 100Wx1pc

Quantity
Average
Illuminance

1pc

Equivalent

1pc

7.3Lx

Equivalent

7Lx

PowerConsumption

120W

83% Down

20W

Lamp
Life12,000h

5 Times

60,000h

12,000020,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

Line-upModel No.LZLA150141
Model No.LZLA150142
Model No.LZLA150146
Model No.LZLA150151H
Model No.LZLA150110

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8kg

Illuminance Level = Equivalent to Mercury 100W

Explosion-proof type LED Lighting Fittings 【LZLA15 Series】

Replacement LED Lighting Fixture for Incandescent 200W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast②Hazardous Area : Zone1/Zone2⑤Power Consumption : 20W⑧Optional Parts : Guard③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Incandescent 200Wx1pc / LED20W (LZLA150141)x1pc
Subject

Incandescent 200Wx1pc

LED (LZLA150141) x1pc

Power Consumption (W)LED (LZLA150141)
x1pc
Incandescent
200Wx1pc

202000Distribution
Curve100200300

Lamp Life (H)LED (LZLA150141)
x1pc
Incandescent
200Wx1pc

Quantity
Average
Illuminance

1pc

Equivalent

1pc

4.4Lx

1.6 Times

7Lx

PowerConsumption

200W

90% Down

20W

Lamp
Life

1,000h

7.1 Times

60,000h60,0001,000
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Incandescent 200Wx48pcs / LED20W (LZLA150141)x30pcs
Subject

Incandescent 200W x48pcs

LED (LZLA150141) x30pcs

Power Consumption (W)LED (LZLA150141)
x30pcsIncandescent 200W
x48pcs

600
9,600
0

Distribution
Curve

5,000 10,00015,000

Construction Fee (%)
LED (LZLA150141)
x30pcsQuantity
Average
Illuminance

48pcs

37% Down

30pcs

213Lx

Equivalent

208.7Lx

Power
Consumption

9,600W

94% Down

600W

Lamp
Life

1,000h60 Times

60,000h30

Incandescent 200W
x48pcs

480102030 4050 60

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA15 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Incandescent 200W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZLA150141
Model No.LZLA150142
Model No.LZLA150146
Model No.LZLA150151H
Model No.LZLA150110

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8kg

Illuminance Level = 1.6 times brighter than Incandescent 200W

Explosion-proof type LED Lighting Fittings 【LZLA15 Series】

Replacement LED Lighting Fixture for Fluorescent 18W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast⑩Luminaire Flex：1,650Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 20W⑧Optional Parts : Guard⑪Energy Efficiency：82.5Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent18W-2x1pc / LED20W (LZLA150141)x1pc
Subject

Fluorescent18W-2 x1pc

LED (LZLA150141) x1pc

Power Consumption (W)LED (LZLA150141)
x1pc
Fluorescent18W-2
x1pc

20490

Distribution
Curve

204060Lamp Life (H)LED (LZLA150141)
x1pc
Fluorescent18W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.3Lx

32% Up7Lx

PowerConsumption

49W

59% Down

20W

Lamp
Life8,500h

7.1 Times

60,000h60,0008,500
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5mReflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent18W-2x39pcs / LED20W (LZLA150141)x30pcs
Subject

Fluorescent18W-2 x39pcs

LED (LZLA150141) x30pcs

Power Consumption (W)LED (LZLA150141)
x30pcsFluorescent18W-2
x39pcs600
1,9110Distribution
Curve

1,000 2,000 3,000

Construction Fee (%)
LED (LZLA150141)
x30pcsQuantity

39pcs

23% Down

30pcs

Average
Illuminance

205.5Lx

Equivalent

208.7Lx

PowerConsumption

1,911W

69% Down

600W

Lamp
Life8,500h

7.1 Times60,000h30

Fluorescent18W-2
x39pcs390102030

Calculation Condition

Line-up
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8kg

50

Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA15 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 18W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZLA150141
Model No.LZLA150142
Model No.LZLA150146
Model No.LZLA150151H
Model No.LZLA150110

40Illuminance Level = 32% brighter than Fluorescent 18W-2

Explosion-proof type LED Lighting Fittings 【LZLA11 Series】

Replacement LED Lighting Fixture for Incandescent 200W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast⑩Luminaire Flex：1,250Lm②Hazardous Area : Zone1/Zone2⑤Power Consumption : 15.5W⑧Optional Parts : Guard⑪Energy Efficiency：80.6Lm/W③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Incandescent200Wx1pc / LED15.5W (LZLA110141)x1pc
Subject

Incandescent200W x1pc

LED (LZLA110141) x1pc

Power Consumption (W)LED (LZLA110141)
x1pc
Incandescent200W
x1pc

15.5200
0

DistributionCurve

50 100 150 200 250

Lamp Life (H)LED (LZLA110141)
x1pc
Incandescent200W
x1pc

Quantity

1pc

Equivalent1pc

Average
Illuminance

4.4Lx

18% Up5.2Lx

PowerConsumption200W

92% Down

15.5W

Lamp
Life

1,000h60 Times

60,000h60,0001,000
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Incandescent200Wx48pcs / LED15.5W (LZLA110141)x39pcs
Subject

Incandescent200W x48pcs

LED (LZLA110141) x39pcs

Power Consumption (W)LED (LZLA110141)
x39pcsIncandescent200W
x48pcs605
9,600
0Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LZLA110141)
x39pcsQuantity

48pcs

19% Down

39pcs

AverageIlluminance

213Lx

Equivalent

204.7Lx

PowerConsumption

9,600W

94% Down

604.5W

Lamp
Life

1,000h60 Times

60,000h39

Incandescent200W
x48pcs

48
0

10

2030

40

Calculation Condition

Line-up
Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8kg

60

Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA11 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Incandescent 200W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZLA110141
Model No.LZLA110142
Model No.LZLA110146
Model No.LZLA110151H
Model No.LZLA110110

50

Illuminance Level = 18% brighter than Incandescent 200W

Explosion-proof type LED Lighting Fittings 【LZLA11 Series】

Replacement LED Lighting Fixture for Incandescent 100W
【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum die-cast②Hazardous Area : Zone1/Zone2⑤Power Consumption : 15.5W⑧Optional Parts : Guard③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Voltage ： AC100-242V±6％
DC100-110V●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Incandescent100Wx1pc / LED15.5W (LZLA110141)x1pc
Subject

Incandescent100W x1pc

LED (LZLA110141) x1pc

Power Consumption (W)LED (LZLA110141)
x1pc
Incandescent100W
x1pc

15.5100
0Distribution
Curve50100150

Lamp Life (H)LED (LZLA110141)
x1pc
Incandescent100Wx1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

3Lx

1.7 Times

5.2Lx

PowerConsumption

100W

85% Down

15.5W

Lamp
Life

1,000h60 Times

60,000h60,0001,000
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Incandescent100Wx70pcs / LED15.5W (LZLA110141)x39pcs
Subject

Incandescent100W x70pcs

LED (LZLA110141) x39pcs

Power Consumption (W)LED (LZLA110141)
x39pcsIncandescent100W
x70pcs605
7,000
0 2,0004,0006,0008,000

Distribution
Curve

Construction Fee (%)
LED (LZLA110141)
x39pcsQuantity

70pcs

44% Down

39pcs

Average
Illuminance

211Lx

Equivalent

204.7Lx

Power
Consumption

7,000W

91% Down

604.5W

Lamp
Life

1,000h60 Times

60,000h39

Incandescent100W
x70pcs

70
020

40

60

80

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZLA11 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Incandescent 100W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LZLA110141
Model No.LZLA110142
Model No.LZLA110146
Model No.LZLA110151H
Model No.LZLA110110

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

6.5kg
7kg
7kg
6.5kg(without pole)
8kg

Illuminance Level = 1.7 Times brighter than Incandescent 100W

P24