Explosion-proof type LED Road Lighting Fittings 【LZIP795D】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 77.5W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard, Glare cut panel⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED77.5W (LZIP795D)x1pc
Subject

Mercury400W x1pc

LED (LZIP795D) x1pc

Distribution
Curve

RoadRoad

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.8Lx

1.8 times

24.4LxPowerConsumption

425W

82% Down

77.5W

Lamp
Life

12,000h

5 Times

60,000hPower Consumption (W)LED (LZIP795D) x1pc

77.5

LED (LZIP795D) x1pc

Mercury400W x1pc

425
0100200

Calculation Condition

Lamp Life (H)

300

400

60,000Mercury400W x1pc

500Lighting Quantity : 1pc
Area : 40mx7m
Lighting Height : 7m

12,000010,000 20,00030,00040,00050,00060,000 70,000

Line-upModel No.LZIP795D

Pole type7.3kg(without pole)

Illuminance Level = 1.8 times brighter than Mercury 400W

Explosion-proof type LED Road Lighting Fittings 【LZIP605D】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 59W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard, Glare cut panel⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED59W (LZIP605D)x1pc
Subject

Mercury400W x1pc

LED (LZIP605D) x1pc

Distribution
CurveRoad

Road

Quantity

1pc

Equivalent

1pc

Average
Illuminance

13.8Lx

33% Up18.4LxPowerConsumption

425W

86% Down59W

LampLife12,000h

5 Times

60,000hPower Consumption (W)LED (LZIP605D) x1pc

59

LED (LZIP605D) x1pc

Mercury400W x1pc

425
0100200

Calculation Condition

Lamp Life (H)

300

400

60,000Mercury400W x1pc

500

Lighting Quantity : 1pc
Area : 40mx7m
Lighting Height : 7m

12,0000

10,000 20,00030,00040,00050,00060,000 70,000

Line-upModel No.LZIP605D

Pole type7.3kg(without pole)

Illuminance Level = 33% brighter than Mercury 400W

Explosion-proof type LED Road Lighting Fittings 【LZIP375D】

Replacement LED Lighting Fixture for Mercury 250W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 36.5W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard, Glare cut panel⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury250Wx1pc / LED36.5W (LZIP375D)x1pc
Subject

Mercury250W x1pc

LED (LZIP375D) x1pc

Distribution
CurveRoadRoadQuantity

1pc

Equivalent

1pc

Average
Illuminance

9Lx

21% Up10.9LxPowerConsumption

270W

86% Down

36.5W

Lamp
Life

12,000h

5 Times

60,000hPower Consumption (W)LED (LZIP375D) x1pc

36.5

LED (LZIP375D) x1pc

Mercury250W x1pc

270
050

100

150

Calculation Condition

Lamp Life (H)

200

250

60,000Mercury250W x1pc

300

Lighting Quantity : 1pc
Area : 40mx7m
Lighting Height : 7m

12,000010,000 20,00030,00040,00050,00060,000 70,000

Line-upModel No.LZIP375D

Pole type7.3kg(without pole)

Illuminance Level = 21% brighter than Mercury 250W