11E0000989A11Instruction Manual
Vapor Tight Type LED Lighting Fittings

To be conserved

LCAB

Thank you very much for purchasing our LED lighting fittings.
Please read this instruction manual to use the product properly.
After installing the product, be sure to hand this manual over to the user of the product.
Prior to use

1) Prior to installing the fitting, check if the product is as per your order.
2) Check for a loose or damaged part due to an accident in transit, etc.

Performance

IP rating
IP 65

Rated Input Voltage (Frequency)
100-242 V AC (50/60 Hz)

How to Install the Fitting■ Pipe Pendant Type, Bracket TypeFirmly mount the positioning box to the ceiling.
NB: For the bracket type, the suspension angle range is from 0 ° (just under) to45°.
Screw the suspension pipe into the lamp housing and tighten the rotation
preventive screw.

4-φ8 Hole

Positioning box

Screw the positioning box cover into the suspension pipe.
Lifting up the lamp housing, hook the suspension hook on the positioning box.
After the power cable is connected, remove the suspension hook. It can be
stored in the positioning box. Secure the positioning box cover using the screws.

Cover packing
Suspension hook
Positioning box coverRotation
reventive screw
4-Cover screw

Rotate the lamp housing to your desired position and then tighten the rotation
preventive screw of the positioning box cover.

Suspension pipe
2-Rotation preventive screw

Bracket Type

Pipe Pendant Type■ Stanchion Type
3-Rotation preventive screw

Terminal box

Lead the lamp leads through the pole. Then insert the terminal box into the pole in
the arrow direction.
NB: For the stanchion type, the illuminating angle range is from 0° (just under) to 15°.
Tighten the terminal box rotation preventive screws (one of the three screws
penetrates into the pole).
Connect a commercial explosion-proof box and short nipple on the bottom part ofthe pole.
Secure the pole using support fittings and the screw that is to mount the box.

■ Special direct Mount TypeFirmly mount the mount fitting to
the structure (e.g. ceiling).
Support fitting(out of our supply scope)pole
Short nipple G3/4
(out of our supply scope)Box (out of our supply scope)

2-φ9 Hole

Mount fitting

Connect a commercial box(included in our list of optionalitems).

■ Handrail Mount Type
Support fitting

Pipe
Mounting band

Hook the mounting band onto the support and insert the pipe.
While holding the support horizontal, fix it with the supplied
hexagonal bolts and nuts.
Lift the fitting and align the mounting bracket hole with thesupport hole. with the support hole.
Fix with the supplied hexagonal bolts and nuts.
Determine the mounting angle and tighten the bolts on both sidesof the bracket.

Mount Fitting

Prepare a commercial flameproof flexible conduit and junction box(optionally available from SEIWA) and connect the wires.

Instructions for use

Maintenance

The LED lamp is turned on by applying the rated voltage to thepower wire of the fitting.

1) In cleaning the fitting, gently wipe with water or mild detergent.
Don ’t use thinner, benzene or alkaline detergent. Such chemicals
might cause discoloration or deterioration in quality and strength,resulting in a damage.

Disassembly and Disposal

2) Prior to maintenance, be sure to turn off the power.
3) Carry out maintenance properly in accordance with the related lawand regulations.

1) I
2) Fy4) If a repair is needed, consult us.

CAUTIONS
1. The product should be installed at an angle within the range from 0° (oriented downward) to 90° (oriented horizontally).
If the product is installed at an angle out of the allowable range, an insulation failure or electric shock might result.
2. Prior to maintenance or inspection, be sure to turn off the power.
3. Confirm that the screws and bolts are fastened properly and tightly.
4. In the case of the stanchion type, be sure to provide a support at least 1500 mm above the bottom of the pole.
5. For outdoor use, waterproof the screwed portion of the conduit, the cable entry fittings and the joint with the stand pole to prevent
rainwater infiltration.
6. When installing the fitting, be sure to connect external wires inside a specified part of the fitting. Don't open any other part of thefitting unless necessary.
7. The supply voltage variation should be within ±6% of the rating.
8. Plug the entries of the terminal box which are not used.
9. The ambient temperature should be within the range of -20°C to +40 °C. The use of the product out of this range may shorten theservice life.
10. Confirm that the fitting is adequately grounded.
11. Prior to maintenance or inspection, be sure to turn off the power.
12. To prevent shortening of the service life, avoid turning on the fitting in direct sunlight.
13. To avoid noise or malfunctioning, don't use a radio, television or wireless infrared remote control near the fitting.
14. Don't open the front glass. The LED internal parts may be very hot. Don't touch the LED light sources. Otherwise a malfunction orlighting failure might occur.
15. In the case of white LEDs, luminescent color and brightness may vary with individual LEDs. Also note that they differ in terms ofattenuation over time.
16. The product must be mounted on a sturdy wall surface or structure which is vibration-free and less susceptible to damage. Otherwise,
it might fall or be damaged.
17. For use in an unfavorable location (a very hot, cold or humid place or a place in which there is strong wind or vibration, a salt damage
environment or a dusty or corrosive gas atmosphere), a special countermeasure should be taken.
18. The LED light sources and the power supply unit cannot be replaced.

11E0000742E11

Safety Precautions-To be conserved

Prior to use, please read the safety precautions and instruction manual thoroughly to use the product properly.
After installing the product, be sure to hand the safety precautions and instruction manual over to the user of the product.
Please keep the manual in a handy place for later reference.
● The various marks have the following meanings:

WARNING: Improper handling may lead to a human death or serious bodily injury.
CAUTION:Improper handling may lead to a bodily injury or property damage.

Be sure tofollow theinstructions.

Be sure to turnoff the power.

Disassembly &conversion
prohibited.

Don’t use neara water source.

Be sure toground.

Prohibited.

Don’t touch.

CautionBe careful ofignition.

WARNING
Don’t use the product in a hazardous location where a flammable or explosive atmosphere such as a gaseous, steamy or
dusty atmosphere may exist. Use in such a location might cause an explosion or fire.
The ambient temperature should be within the operating temperature range specified in the instruction manual. If theproduct should be used at a temperature higher than specified, an early lighting failure or malfunction might occur or a firemight result.
If a product must be oriented in a specific manner for use, install it properly according to the marking on its body or theinstruction manual. Otherwise, a fire or electric shock might result.
For electrical connections, use crimp-type terminals, etc. to secure the connections and conduct insulation treatment. An
inadequate connection or inadequate insulation might cause an imperfect contact, leading to a fire or electric shock.
In grounding work, be sure to follow the technical standards for electrical equipmentof your country. Inadequate grounding
might cause a fire or electric shock.
Do ’t o ert the produ t.
Conversion might cause the product to fall or result in a fire or electric shock.
Do ’t o er the produ t ith a i fla
a leSuch a material or thing might cause a fire.

aterial su h as loth or paper or put a ythi g i the produ t.

Do ’t e d, t ist or pull the po er a le y for e.
Inadequate handling of the cable might damage it and result in a fire or electric shock.
The parts once removed for cleaning should be replaced properly according to the instruction manual.
An improperly placed part might cause the product to fall, resultng in an injury or property damage.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Do ’t ope LED la p prote ti e o ers su h as the fro t glass a d glass glo e.
Do ’t tou h a LED la p, other ise a alfu tio or lighti g failure ight o ur.
Before cleaning, be sure to turn off the power.
Otherwise, a fire or electric shock might result.
L照般6- 1 /2 -WARNING
If you continue to use the product in an abnormal condition (smoke, odor, etc.), a fire or electric shock might result. If you
detect an abnormality, immediately turn off the power switch. Confirm that the abnormal condition has been eliminatedand make a repair call.
Do ’t use the produ t i a stro g orrosi e gas at osphere hi h o tai s hydro hlori a id or hlori e gases or the like.
Use in a corrosive gas atmosphere might cause the product to corrode and fall, resulting in an injury.
The product should be mounted on a surface robust enough to support its weight, properly according to the instruction
manual. Improper installation might cause the product to fall or result in an electric shock or injury.

CAUTIONAny product not marked as a product for outdoor use should not be used outdoors or in a humid place or near a watersource. Its use in such a place might cause a fire or electric shock.
Do ’t use the produ t at a oltage other tha the rated oltage i di ated o the a eplate.
Otherwise, breakage, fire or electric shock might result.
For a product marked with a frequency, don’t use the product at a frequency other than 50 or 60 Hz (local power supplyfrequency). Use at a wrong frequency might cause a fire.
Installation of the product should be carried out by a qualified person.
Installation by an unqualified person is legally prohibited.
Never touch LED light sources and their surroundings.
The light sources and their surroundings are very hot, so an accidental touch might cause a burn.
To ensure brightness and safety, carry out periodical cleaning and inspection.
If used in an extended period without maintenance or inspection, a smoke, fire or electric shock might result.
A lighting fitting has a service life. A product which has been used for eight to ten years may have degraded internal partseven if it looks normal. For safety and energy saving, we recommend you check and replace it. The LED module design life is60,000 hours (different from the lighting fitting life) when used at an ambient temperature of 30°C, 10 hours per day, 3,000hours per year. If used at a higher temperature or more hours per year, the life would be shortened. Have a specialist
inspect the product every three years. If used for an extended period without inspection, a smoke, fire, or electric shockmight result.

Resycling
Ni-Cd
Ni-MH

JBRC

Please bring used Secondary batteries to the recycling station for effective use of precious
resources and global environment conservation.

Japan Portable Rechargeable Battery Recycling Center

Phone +81 3 6403 5763

CONTACT DETAILSFor further information on the product, contact any of our offices listed below (if you like to make an inquiry, let us know the model nameindicated on the product nameplate).

SEIWA ELECTRIC MFG.CO., LTD.
Head Office

36 Shinike, Terada, Joyo, Kyoto Pref. 610-0192 JapanTokyo Branch

2-19-6 Yanagibashi, Taito-ku, Tokyo 111-0052 Japan

Phone
Fax
Phone
Fax

+81 774 55 8181
+81 774 58 2034
+81 3 5833 8946
+81 3 5833 8971

Please note that the above addresses and phone numbers may be changed.
L照般6- 2 /2 -