Explosion-proof type LED Lighting Fittings 【LZWG4002624V2W】

Replacement LED Lighting Fixture for Fluorescent 36W-6【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：114.4Lm/W②Hazardous Area : Zone1/Zone2⑤Power Consumption : 92W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：10,530Lm●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-6x1pc / LED92W (LZWG4002624V2W)x1pc
Subject

Fluorescent36W-6 x1pc

LED (LZWG4002624V2W) x1pc

Power Consumption (W)
LED(LZWG4002624V2W)…

92

Fluorescent36W-6
x1pc

255
0

Distribution
Curve

200

400

Lamp Life (H)
LED(LZWG4002624V2W)…

60,000

Fluorescent36W-6
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

37.3Lx

49% Up55.6LxPowerConsumption

255W

64% Down

92W

Lamp
Life

12,000h

5 Times

60,000h

12,000050,000

100,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-6x6pcs / LED92W (LZWG4002624V2W)x4pcs
Subject

Fluorescent36W-6 x6pcs

LED (LZWG4002624V2W) x4pcs

Power Consumption (W)
LED(LZWG4002624V2W)…

368

Fluorescent36W-6x30pcs

1,530
0

Distribution
Curve

1,000

2,000

Construction Fee (%)
LED(LZWG4002624V2W)…

Quantity

6pcs

33% Down

4pcs

Average
Illuminance

223.8Lx

Equivalent

222.4Lx

PowerConsumption

1,530Ｗ

76% Down

368WLamp
Life12,000h

5 Times

60,000h

Fluorescent36W-6
x15pcs6053kg10Calculation Condition

Line-upRecessed type

5Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWG4002624V2W has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­62.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZWG4002624V2W

4Illuminance Level = 49％ brighter than Fluorescent 36W-6

Explosion-proof type LED Lighting Fittings 【LZWG2402624V2W】

Replacement LED Lighting Fixture for Fluorescent 36W-4【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：108.6Lm/W②Hazardous Area : Zone1/Zone2⑤Power Consumption : 58W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：6,300Lm●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-4x1pc / LED58W (LZWG2402624V2W)x1pc
Subject

Fluorescent36W-4 x1pc

LED (LZWG2402624V2W) x1pc

Power Consumption (W)
LED(LZWG2402624V2W)…

58

Fluorescent36W-4
x1pc

1700

Distribution
Curve100200Lamp Life (H)
LED(LZWG2402624V2W)…
Fluorescent36W-4
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

27.7Lx

20% Up33.3LxPowerConsumption

170W

66% Down

58W

Lamp
Life

12,000h

5 Times

60,000h60,00012,000050,000

100,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5mReflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-4x8pcs / LED58W (LZWG2402624V2W)x6pcs
Subject

Fluorescent36W-4 x8pcs

LED (LZWG2402624V2W) x6pcs

Power Consumption (W)
LED(LZWG2402624V2W)…

348

Fluorescent36W-4x30pcs

1,360
0

Distribution
Curve

1,000

2,000

Construction Fee (%)
LED(LZWG2402624V2W)…

Quantity

8pcs

25% Down

6pcs

Average
Illuminance

221.8Lx

Equivalent200Lx

PowerConsumption

1,360W

74% Down

348W

Lamp
Life12,000h5 Times

60,000h

Fluorescent36W-4
x15pcs8050kg10Calculation Condition

Line-upRecessed type

5Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWG2402624V2W has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­4
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZWG2402624V2W

6Illuminance Level = 20% brighter than Fluorescent 36W-4

Explosion-proof type LED Lighting Fittings 【LZWG4001624V2W】

Replacement LED Lighting Fixture for Fluorescent 36W-3【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：114.4Lm/W②Hazardous Area : Zone1/Zone2⑤Power Consumption : 46W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：5,265Lm●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-3x1pc / LED46W (LZWG4001624V2W)x1pc
Subject

Fluorescent36W-3 x1pc

LED (LZWG4001624V2W) x1pc

Power Consumption (W)
LED(LZWG4001624V2W…

46

Fluorescent36W-3x1pc

1320Distribution
Curve

50100150

Lamp Life (H)
LED(LZWG4001624V2…

60,000

Fluorescent36W-3
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

19.7Lx

41％Up

27.8LxPowerConsumption

132W

65% Down

46W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5mReflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-3x12pcs / LED46W (LZWG4001624V2W)x8pcs
Subject

Fluorescent36W-3 x12pcs

LED (LZWG4001624V2W) x8pcs

Power Consumption (W)
LED(LZWG4001624V2W)…

368

Fluorescent36W-3
x30pcs1,5840Distribution
Curve

1,000

2,000

Construction Fee (%)
LED(LZWG4001624V2W)…

Quantity

12pcs

33% Down

8pcs

Average
Illuminance236.6Lx

Equivalent

222.4Lx

PowerConsumption

1,584Ｗ

77% Down

368W

LampLife12,000h

5 Times

60,000h

Fluorescent36W-3
x15pcs12042kg

20Calculation Condition

Line-upRecessed type

10Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWG4001624V2W has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­3
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZWG4001624V2W

8Illuminance Level = 41% brighter than Fluorescent 36W-3

Explosion-proof type LED Lighting Fittings 【LZWG2401624V2】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Type of Protection : ExdeⅡB+H2T6X④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy②Hazardous Area : Zone1/Zone2⑤Power Consumption : 29W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：3,150Lm⑩Energy Efficiency：108.6Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●LED Lamp can be exchanged【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED29W (LZWG2401624V2)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LZWG2401624V2) x1pc

Power Consumption (W)LED (LZWG2401624V2)
x1pc

29

Fluorescent36W-2
x1pc

850DistributionCurve

20 40 60 80 100

Lamp Life (H)
LED(LZWG2401624V2)…

60,000

Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

14Lx

19% Up16.6LxPowerConsumption

85W

66% Down

29W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED29W (LZWG2401624V2)x12pcs
Subject

Fluorescent36W-2 x15pcs

LED (LZWG2401624V2) x12pcs

Power Consumption (W)LED (LZWG2401624V2)
x12pcs348

Fluorescent36W-2
x30pcs1,275
0Distribution
Curve

1,000

2,000

Construction Fee (%)
LED (LZWG2401624V2)
x12pcsQuantity

15pcs

20% Down

12pcs

Average
Illuminance

209.8Lx

Equivalent200Lx

PowerConsumption

1,275Ｗ

73% Down

348WLampLife

12,000h

5 Times

60,000h12Fluorescent36W-2
x15pcs150

Calculation Condition

Line-upRecessed type32.5kg20Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LZWG2401624V2 has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W­22.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LZWG2401624V2

10Illuminance Level = 19% brighter than Fluorescent 36W-2