Weather-proof type LED Lighting Fittings 【LCIA1107 Series】

Replacement LED Lighting Fixture for Mercury 400W
【Specifications】①Degree of Protection : IP65
④Lamp Life : 60,000h⑦Voltage ： AC100-242V±6％②Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑧Luminaire Flex：9,600Lm③Power Consumption : 87W⑥Optional Parts : Guard⑨Energy Efficiency：110.3Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury400Wx1pc / LED87W (LCIA110741)x1pc
Subject

Mercury400W x1pcLED (LCIA110741) x1pc

Power Consumption (W)LED (LCIA110741)
x1pc

87

Mercury400W x1pc

425
0 100 200 300 400 500

DistributionCurve

Lamp Life (H)LED (LCIA110741)
x1pc

60,000Mercury400W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

9Lx

28% Up11.5LxPowerConsumption

425W

80% Down

87W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury400Wx24pcs / LED87W (LCIA110741)x18pcs
Subject

Mercury400W x24pcs

LED (LCIA110741) x18pcs

Power Consumption (W)LED (LCIA110741)
x18pcs
Mercury400W
x24pcs

1,566
10,2000

Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LCIA110741)
x18pcs18Mercury400W x24pcs

Quantity

24pcs

25% Down

18pcs

Average
Illuminance215.9Lx

Equivalent

206.2Lx

PowerConsumption

10,200W

85% Down

1,566W

Lamp
Life

12,000h

5 Times

60,000h2405

10 15 20 25 30

Calculation Condition
Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCIA1107 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 400W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCIA110741
Model No.LCIA110742
Model No.LCIA110746
Model No.LCIA110752H
Model No.LCIA110761H

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Pole type

8kg
8.5kg
8.5kg
7kg(without pole)
7kg(without pole)

Illuminance Level = 28% brighter than Mercury 400W

Weather-proof type LED Lighting Fittings 【LCIA1104 Series】

Replacement LED Lighting Fixture for Mercury 250W
【Specifications】①Degree of Protection : IP65
④Lamp Life : 60,000h⑦Voltage ： AC100-242V±6％②Correlated Color Temperature : 5,000K⑤Body Material : Aluminum die-cast⑧Luminaire Flex：5,800Lm③Power Consumption : 56W⑥Optional Parts : Guard⑨Energy Efficiency：103.6Lm/W●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Mercury250Wx1pc / LED56W (LCIA110441)x1pc
Subject

Mercury250W x1pc

LED (LCIA110441) x1pc

Power Consumption (W)LED (LCIA110441)
x1pc

56

Mercury250W x1pc

2700Distribution
Curve100200300

Lamp Life (H)LED (LCIA110441)
x1pc

60,000Mercury250W x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.2Lx

33% Up6.9Lx

PowerConsumption

270W

79% Down

56W

Lamp
Life

12,000h

5 Times

60,000h

12,000020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Mercury250Wx40pcs / LED56W (LCIA110441)x30pcs
Subject

Mercury250W x40pcs

LED (LCIA110441) x30pcs

Power Consumption (W)LED (LCIA110441)
x30pcs
Mercury250W
x40pcs

1,680
10,8000Distribution
Curve

5,000 10,000 15,000

Construction Fee (%)
LED (LCIA110441)
x30pcs30

Mercury250W x40pcs

Quantity

40pcs

25% Down

30pcs

Average
Illuminance209.3Lx

Equivalent

206.2Lx

PowerConsumption

10,800W

84% Down

1,680W

Lamp
Life12,000h

5 Times

60,000h

40010203040Design Illuminance : 200Lx
Area : 20mx20m
Lighting Height : 10m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LCIA1104 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Mercury 250W
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LCIA110441
Model No.LCIA110442
Model No.LCIA110446
Model No.LCIA110452H
Model No.LCIA110461H

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Pole type

7.5kg
8kg
8kg
6.5kg(without pole)
6.5kg(without pole)50

Calculation Condition

Illuminance Level = 33% brighter than Mercury 250W