Dust Ignition-proof type LED Lighting Fittings 【LKAB0703 Series】

Replacement LED Lighting Fixture for Fluorescent 18W-2【Specifications】①Type of Protection : SDP-13④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：105.9Lm/W②Hazardous Area : Zone20,21,22⑤Power Consumption : 25.5W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65
⑥Lamp Life : 60,000h⑨Luminaire Flex：2,700Lm●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent18W-2x1pc / LED25.5W (LKAB070341)x1pc
Subject

Fluorescent18W-2 x1pc

LED (LKAB070341) x1pc

Power Consumption (W)LED (LKAB070341)
x1pc
Fluorescent18W-2
x1pc

25.5
490

Distribution
Curve

204060Lamp Life (H)LED (LKAB070341)
x1pc
Fluorescent18W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.3Lx

2.9 Times

15.4LxPowerConsumption

49W

48% Down

25.5W

Lamp
Life8,500h

7.1 Times

60,000h60,0008,500
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10mLighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent18W-2x39pcs / LED25.5W (LKAB070341)x14pcs
Subject

Fluorescent18W-2 x39pcs

LED (LKAB070341) x14pcs

Power Consumption (W)LED (LKAB070341)
x14pcsFluorescent18W-2
x39pcs357
1,9110Distribution
Curve

1,000 2,000 3,000

Construction Fee (%)
LED (LKAB070341)
x14pcsQuantity

39pcs

64% Down

14pcs

Average
Illuminance

205.5Lx

Equivalent

215.9Lx

PowerConsumption

1,911W

81% Down

357WLamp
Life8,500h

7.1 Times

60,000h14

Fluorescent18W-2
x39pcs390102030

4050

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LKAB0703 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 18W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LKAB070341
Model No.LKAB070342
Model No.LKAB070346
Model No.LKAB070351H
Model No.LKAB070311

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

7kg
7kg
7kg
7kg(without pole)
7kg

Illuminance Level = 2.9 times brighter than Fluorescent 18W-2

Dust Ignition-proof type LED Lighting Fittings 【LKAB0702 Series】

Replacement LED Lighting Fixture for Fluorescent 18W-2【Specifications】①Type of Protection : SDP-13④Correlated Color Temperature : 5,000K⑦Body Material : Aluminum alloy⑩Energy Efficiency：100.0Lm/W②Hazardous Area : Zone20,21,22⑤Power Consumption : 18W⑧Voltage ： AC100-242V±6％③Degree of Protection : IP65⑥Lamp Life : 60,000h⑨Luminaire Flex：1,800Lm●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent18W-2x1pc / LED18W (LKAB070241)x1pc
Subject

Fluorescent18W-2 x1pc

LED (LKAB070241) x1pc

Power Consumption (W)LED (LKAB070241)
x1pc
Fluorescent18W-2
x1pc

18
490

Distribution
Curve

204060Lamp Life (H)LED (LKAB070241)
x1pc
Fluorescent18W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

5.3Lx

1.9 Times

10.3LxPowerConsumption

49W

63% Down

18W

Lamp
Life

8,500h

7.1 Times

60,000h60,0008,500
020,000 40,000 60,000 80,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent18W-2x39pcs / LED18W (LKAB070241)x20pcs
Subject

Fluorescent18W-2 x39pcs

LED (LKAB070241) x20pcs

Power Consumption (W)LED (LKAB070241)
x20pcsFluorescent18W-2x39pcs

360
1,9110Distribution
Curve

1,000 2,000 3,000

Construction Fee (%)
LED (LKAB070241)
x20pcsQuantity

39pcs

49% Down

20pcs

Average
Illuminance

205.5Lx

Equivalent

205.6Lx

PowerConsumption

1,911W

81% Down

360W

Lamp
Life8,500h

7.1 Times

60,000h20

Fluorescent18W-2
x39pcs

39010

2030

4050

Calculation Condition
Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LKAB0702 Series has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 18W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Line-upModel No.LKAB070241
Model No.LKAB070242
Model No.LKAB070246
Model No.LKAB070251H
Model No.LKAB070211

Ceiling type
Pipe pendant type
Bracket type
Stanchion type
Direct type

7kg
7kg
7kg
7kg(without pole)
7kg

Illuminance Level = 1.9 times brighter than Fluorescent 18W-2