Series
8800
Pump
Model: 88XX-2X03-0322
Flow Range: Open Flow = 1.40-1.95 LPM
At 80 PSI = .80-1.00 LPM

COMPLETING THE PART NUMBER:
88XX-2X03-0322
Aluminum Mounting Plate (Other Types Available)
See Performance Data for Recommended By-pass
Pressure and Code
By-Pass Pressure Relief Control Valve

3.38

Select Pumphead Model From Performance Data Chart
3 = Open Ports for 3/8” Compression Fitting
4 = Push to Connect Ports for 1/4” Tubing
5 = Push-to-Connect Ports for 3/8” Tubing

3.55
2.07

SPECIFICATIONS:n MOTOR:TYPE:LEADS:
TEMP. LIMITS:.23

DUTY CYCLE:

24 VAC, Permanent Magnet,
Totally Enclosed, Non-Ventilated
20 AWG, 6” LONG
This Motor is Not Equipped with Thermal
Protection. For User Safety, Optimal
Performance, and Maximum Motor Life, The
Motor Surface Temperature Should Not Exceed
150°F (66°C), as Shown on the Heat Rise Graph.
See Heat Rise Graph

.45

2.86

2.86

8.18

3.15

n PUMP DESIGN:

3 Chamber Diaphragm Pump, Self Priming,
Capable of Being Run Dry

n TYPICAL APPLICATION:

Pre-Filter Water Treatment (R.O. Boost)n MATERIALS:
HOUSINGS:VALVES:
DIAPHRAGM:FASTENERS:

Nylon
EPDM
Santoprene
Stainless Steeln LIQUID TEMPERATURE:

170°F (77°C) Max.

n PUMP CERTIFICATIONS:NSF Standard 58

3.21

n PRIMING CAPABILITIES:PRIME(FEET)

3.18
4.00

n FITTINGS:

88X0

88X1

88X2

4.5

5.5

6.5

TYPE
3/8" COMPRESSION
3/8" COMPRESSION
3/8" STEMSHAPEKIT NO.

CONNECTS TO…

STRAIGHT

25-145

3/8" TUBING

ELBOW

25-146

3/8" TUBINGSTRAIGHT

25-144

3/8" JOHN GUEST PUSH-ON FITTINGWEIGHT: 7 lbs.

Aquatec International, Inc.
17422 Pullman Street, Irvine, CA 92614
Sales: 949-225-2200 Fax: 949-225-2222
www.aquatec.com

Series 8800 Pump
Model: 88XX-2X03-0322
PERFORMANCE DATADISCHARGE
PRESSURE(PSI)
8070605040302010OPEN

88X0
FLOW
CURRENT(LPM)(AMPS)

PUMPHEAD MODEL
88X1
FLOW
CURRENT(LPM)(AMPS)

RECOMMENDED
BY-PASS PRESSURE
88X2
FLOW CURRENT
PSI
CODE
(LPM)
(AMPS)

0.80

1.10

0.90

1.25

1.00

1.45

0.87
0.93

1.03
0.97

0.98
1.00

1.17
1.10

1.10
1.25

1.35
1.24

0.98
1.00

0.89
0.81

1.10
1.20

1.02
0.93

1.40
1.45

1.10
1.200.72
0.63

1.30
1.40

0.84
0.72

1.30
1.40

0.52
0.48

1.50
1.60

0.60
0.56

110100JI

1.15
1.04908070HGF

1.55
1.65

0.92
0.80

6050ED1.85
1.95

0.66
0.634030BA

PERFORMANCE MEASURED WITH FLOODED INLET (0 PSI), 70°F (21°C) AMBIENT AND WATER TEMPERATURE, AND VOLTAGE CONTROLLED AT 24 VAC. POSITIVE INLET PRESSURE WILL INCREASE THE DISCHARGE PRESSURE BY A SIMILARAMOUNT, FOR A GIVEN FLOW. MAXIMUM INLET PRESSURE IS 60 PSI.
SHADED AREA DENOTES CONTINUOUS OPERATION CAPABILITY AT DESIGNATED PRESSURE AND CURRENT.

HEAT RISE
200RECOMMENDED
SHUT-OFFTEMPERATURE

180160140

1.45 AMPS
12010080600102030405060708090100

110120TIME (MINUTES)

All of the pump models in the Performance Data and Heat Rise charts are in the shaded area, meaning they are capable ofsustaining continual running, at any of the above listed pressures, without shutting down to allow the motor to cool. To
conserve wearing parts, however, the pump should only operate as needed.
Care should be exercised in selecting the proper transformer for this 24 VAC motor. The largest “wall mount” transformer
from Aquatec is only rated to .80 amps. Aquatec’s “table top” transformer is rated to 2.00 amps. By-Pass pressures mustalso be considered when selecting a suitable transformer, in the event the pump is allowed to reach the preset by-pass pressure for sustained periods.
ALL PERFORMANCE AND HEAT RISE FIGURES ARE APPROXIMATE. ACTUAL VALUES WILL VARY WITH AMBIENT CONDITIONS.