B-1816 (7)INSTRUCTION SHEETFC6A Series
CPU module
All-in One typeThis sheet provides brief operating instructions of the MICROSmart programmable controller.
For details, see the FC6A Series MICROSmart User’s Manual.

Safety Precautions
Special expertise is required to use the MICROSmart.
● Read this instruction sheet and the user's manual to make sure of correct operation before starting
installation, wiring, operation, maintenance, and inspection of the MICROSmart.
Keep this instruction sheet where it can be accessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorous quality control system, but users
must add backup or failsafe provisions to control systems use the MICROSmart in applications where
heavy damage or personal injury may be caused if the MICROSmart should fail.
● Install the MICROSmart according to the instructions described in this instruction sheet and the user's
manual. Improper installation will result in falling, failure, or malfunction of the MICROSmart.
● Make sure that the operating conditions are as described in the user’s manual. If you are uncertain
about the specifications, contact IDEC before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order of importance from Warning and Caution:2

Direct Mounting Hook
(FC6A-PSP1PN05)

Specification

Screw HoleOperating Temperature: -10 to +55°C (no freezing)
Expanded Operating Temperature: -25 to -10°C, +55 to 65°C (no freezing)* See the user's manual for details on use in Expanded Operating Temperatures.
Storage Temperature: -25 to +70°C (no freezing)
Relative/Storage Humidity: 10 to 95%RH (no condensation),
Altitude or Air Pressure: 1,013 to 795hPa (0 to 2,000 m) during operation
1,013 to 701hPa (0 to 3,000 m) during transport,
Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,
acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,
Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes, 6 directions, 3 times each
Installation Location : Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C / 65°C
Temperature Code: T4A

DIN Rail Hook

Screw Hole

[Direct Mounting on Panel Surface]
Pull out the DIN Rail Hook on the back of
the module and insert the direct mounting
Hook (FC6A-PSP1PN05) into the slot.
Attach the module to the mounting plateusing the screw holes.
Attach the module to the mounting plateusing M4 tapping screws, as shown
below, or make 5 to 6mm mounting holes
and secure the module using M4 panhead screws.
Always give sufficient consideration tooperability, ease-of-maintenance, andenvironmental resistance when deciding
on the mounting position.

3

Name & Function

Type FC6A-C*1* (Screw fastened type)(1) Analog Input(11) Input LEDs [IN](2) Function Switch
Output LEDs [OUT](3) Serial Port1
Power LED [PWR](4) SD Memory Card Slot
Run LED [RUN](5) USB Port
Error LED [ERR](6) Power Supply Terminals
SD Memory Card Status LED [SD](7) LINK LED
Battery Status LED [BAT](8) ACT LED
Status LED [STAT](9) Ethernet Port 1(10) Output Terminals
(16)

(1)
(17)

(15)

(14)

(13)

(19)

TOP

(12) Input Terminals(13) Cartridge Slot 2(14) Cartridge Slot 1(15) Analog Potentiometer(16) Sencer Power Terminals*1(17) Communication Connector(18) Expansion Connector(19) Battery Holder

Operating
Surrounding Air
Temperature
55 °C
maximum+24V 0V COM I0(10)

Left Side(5)(20) SD Memory Card Cover(21) USB Port Cover(22) Power Supply Terminals Cover*2(23) Ethernet Port 1 Cover(24) Serial Port 1 Cover

I5

I6+24V 0V COM I0

I1

I2

I3

I4

I5

I6

Input (24V DC)

Sensor Power

24VDC Power Input+24V 0V FE

100 to 240V AC
Power Input

N

L

COM0 Q0PE

40mm
minimum

40mm
minimum

DIN Rail

Relay Output
Q1 Q2 Q3 COM1 Q4-+Power Supply
10.2 to 18.0VDC

20mm minimum

L

L

L: Fuse+--Power Supply
20.4 to 28.8VDC

L: LoadPower Supply
85 to 264VAC

Transistor Sink Output
WiringTransistor Protect Source Output
WiringTransistor Sink Output
Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(-) V0(+)

Transistor Protect Source output
Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(+) V0(-)

L

L

L

L

L

L

L

-

L

+

L

L

L

L

L

L

L
+

Right Side-

Operating
Surrounding Air
Temperature
35°C
maximum*See the user's manual for more details on the wiring.

● Use a Class 2 power supply source when power supply voltage less than 30V DC is required to(25)

power the terminal.

Unavailable

(20)

(27)

Relay Output
WiringAC Power
Wiring

12VDC Power Input

L(25) Dummy Cartridges(26) Analog Port Cover(27) Communication Connector Protection Sticker(28) Expansion Connector Protection Sticker(26)● Use copper conductor only.

(28)● When the MICROSmart is used in a Surrounding Air Temperature of 65°C, reduce the I/O voltage

Available

and I/O utilization. See the user's manual for details.

10

For UL/cUL, Horizontal mounting only.

Applicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening Torque(21)

Left Side

Right Side

(22)

Dimensions

8

All dimensions in mm.

(23) (24)163.0

Assembling Modules
The
Side ofthe Battery Holder

73.0

2.7
[3.3]

The recommended ferrule is made by Phoenix Contact or Weidmüller. To crimp the ferrules shown
below, use a special crimping tool. (CRIMPFOX6 (1212034) or PZ 6 Rote L (1444050000))To the terminal block, use the recommended screwdriver made by Phoenix Contact or Weidmüller andtighten terminal screws tightening torque.
Type FC6A-C*1* (Screw fastened type)
Applied cable
AWG24

1. Grasp the battery holder and remove it from the module.* (a)2. Remove the old back up battery from the battery holder (c)by pulling the outside hook. (b)3. Install a new back up battery in the battery holder.
Push the battery in until the outsite hook (b) clicks.
4. Insert the battery holder into the module. (a)* The length of the battery holder is 36 mm.

4.0
90.0

4

[FC6A-C40R*AE, -C40R*CE, -C40K*CE, -C40P*CE, -C40R*DE, -C40K*DE, -C40P*DE]
2.9
[8.1]

*1 Not used with DC power supply types.
*2 FC6A-C40*4* (Push-in type) do not have a power supply terminal cover.

AWG22
UL1007b

Alternative Batteries Compatible with BR2032
CR2032X or CR2032W
Murata
CR2032A or CR2032B
Panasonic● Change the battery before the old battery expires.

110.0● La piles peut exploser en cas de mauvais usage. Ne pas recharger, démonter ou jeter la piles au feu.

73.0

90.0

90.0

by Function Switch is enabled in WindLDR and a program is downloaded with
Automatic start after download enabled.
To run the PLC, the function switch must be set to 1.

2.9 [8.1]
13.6 [12.6]

110.0
98.0±0.2

4.3

95.0
83.0±0.2

2-ø

4.3

(1)

(3)

(4)

90.0
83.0±0.2

90.0
83.0±0.2.5ø450.0±0.235-mm-wide
DIN Rail(1) Pull out the DIN Rail Hook.
(2) Put the groove of the module on the
DIN Rail.
(3) Press the modules towards the DIN Rail.
(4) Push in the DIN Rail Hook.

50.0±0.235-mm-wide
DIN Rail

AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

AWG20
AWG18

AI 0,5-8 GB (1208966)
AI 1-8 (3200030), H1,0/14D R (9019080000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

Recommended ferrule

AWG24

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

AWG22

AI 0,34-8 (3203066), H0,34/12 TK (9025770000)

AWG20

AI 0,5-8 (3200014), H0,5/14D W (9019010000)

AWG18

AI 0,75-12 (3200849), Al-TWIN 2×0,75-10 (3200975),
H0,75/18 W (9025910000), H0,75/16D ZH GR (9037420000)

AWG16

H1,5/18D SW (9019140000)

AWG20

AI 0,5-8 GB (1208966)

AWG18

AI 1-12 (3200674), H1,0/16 GE (9025950000)

AWG16

H1,5/18D SW (9019140000)
Tighten torque0.51 N-m( ) indicates the Type No. of PHOENIX CONTACT GmbH & Co. KG and Weidmüller Interface GmbH & Co. KG.

11 Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.

For details about mounting and removing modules, see the user’s manual.

(2)

AWG16

Screwdriver2-ø

[ Mounting on DIN Rail ]Use a 35-mm-wide DIN Rail and BNL6
mounting clips to secure the modules.

AI 0,75-6 (3200690), AI 0,75-8 (3200519), Al-TWIN 2×0,75-8 (3200807),
H0,75/12D GR (9019030000), H0,75/14D GR (9019040000),
H0,75/14D ZH GR (9037410000)

SZS 0,6×3,5 (1205053), SDS 0,6×3,5×100 (9008330000)* Enabled is the default setting for Run/Stop PLC by Function Switch in WindLDR.
* For details on the function switch, see the user's manual.

Mounting Modules

2.7
[3.3]

UL1007/UL2464

UL1015● The PLC will not run if the function switch is 0 when Run/Stop PLC

CPU module All-in-One type

AWG18

AWG16

4.0

● The default setting of the function switch is 0.

6

95.0

Default Setting of the Function Switch

TYPE

AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H0,34/10 TK(9025750000), H0,34/12 TK (9025770000)
AI 0,5-6 (3200687), AI 0,5-8 (3200014), AI-TWIN 2×0,5-8 (3200933),
H0,5/12D W(9019000000), H0,5/14D W (9019010000),
H0,5/14D ZH W (9037380000)

Type FC6A-C*4* (Push-in type)[FC6A-C16R*AE, -C16R*CE,-C16K*CE,-C16P*CE, -C16R*DE, -C16K*DE,-C16P*DE][FC6A-C24R*AE, -C24R*CE,-C24K*CE, -C24P*CE ]● Battery May Explode If Mistreated. Do Not Recharge, Disassemble Or Dispose Of In Fire.

5

2.9 [8.1]
13.6 [12.6]

2-ø

● Do not change the battery when the MICROSmart is power ON. Doing so may damage the product.

its initial values.

UL1015

Recommended ferrule
AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H0,25/10 HBL(9025740000), Ｈ0,25/12T GE (9021020000)

Applied cable
4.5● Change the battery within 1 minute of turning off the power supply, or the device value will be reset to

When an expansion module is not connected next,
don’t peel off the protection sticker.

2.9
[8.1]

proper tightening torque of 0.51 N-m.
● Use an IEC60127-approved fuse on the power line and output circuit to meet voltage and current

4.3

2.9 [8.1]
13.6 [12.6]

of such fragments and chips may cause fire hazard, damage, or malfunction.
● Use wires of a proper size to meet voltage and current requirements. Tighten terminal screws to the

163.0
151.0±0.2

2-ø

2.9
[8.1]

● Prevent metal fragments and pieces of wire from dropping inside the MICROSmart housing. Ingress

The Alternative Batteries Compatible On The List As Below.
Use of Another Battery May Present A Risk of Fire Or Explosion.
● Avertissement: Remplacez uniquement la batterie par BR2032
de PANASONIC, ou par une batterie compatible de la liste
ci-dessous. L'utilisation d'une autre piles peut présenter unrisque de feu ou d'explosion.

100.0±0.2● Warning: Replace Only The Battery With Panasonic BR2032, Or

Battery Holder
The
Side ofthe Battery Holder
c

AWG20

/ UL246490.0
83.0±0.2

in places where it is subjected to high-temperature, high-humidity, condensation, corrosive gases,
excessive vibrations, or excessive shocks itwill result in electrical shocks, fire hazard, or malfunction.
● The environment rating for using the MICROSmart is “Pollution degree 2.”

Type No.
40-I/O Type
24-I/O Type
16-I/O Type
Relay
FC6A-C40R*AE FC6A-C24R*AE FC6A-C16R*AE
100-240VAC
Relay
FC6A-C40R*CE FC6A-C24R*CE FC6A-C16R*CE
Transistor Sink
24VDC
FC6A-C40K*CE FC6A-C24K*CE FC6A-C16K*CE
Transistor Protect Source FC6A-C40P*CE FC6A-C24P*CE FC6A-C16P*CE
Relay
FC6A-C40R*DE
FC6A-C16R*DE
12VDC
Transistor Sink
FC6A-C40K*DE
FC6A-C16K*DE
Transistor Protect Source FC6A-C40P*DE
FC6A-C16P*DE* 1: Screw fastened type, 4: Push-in type
Packing(Pcs/pack): FC6A Unit (1), Connector with analog input cable (1), Battery holder with battery (1)Instruction Sheet (this manual) (1).

I4+12V 0V FE

equipment.

Output TypeI3

100-240V AC power supply type: Support of sensor power which is in the circle area of above figure isable to be used instead of 24V DC external power.
24V DC power supply type: No support of sensor power. Therefore 24V DC external power is required.
12V DC power supply type: No support of sensor power. Therefore 12VDC external power is required.

+● Install the MICROSmart in environments as described in the user's manual. If the MICROSmart is used

Power Supply Type

I2

L

Horizontal mounting(3)● The MICROSmart is designed for installation in equipment. Do not install the MICROSmart outside of

1

I1

+

Input (24V DC)

Sensor Power

(18)

(2)

a

This symbol mark means that batteries and accumulators, at their end-of life,
should be disposed of separately from your household waste.
If a chemical symbol is printed beneath the symbol shown above,this chemical
symbol means that the battery or accumulator contains a heavy metal at a certain
concentration. This will be indicated as follows:
Hg : Mercury (0.0005%) Cd : Cadmium (0.002%) Pb : Lead (0.004%)
In the European Union there are separate collection systems for used batteries andaccumulators.
Please dispose of batteries and accumulators correctly in accordance with each country or local regulation.

Sensor(2 wires)-

20mm minimum(12)(6) (7) (8) (9)requirements.(Recommended fuse: Littelfuse 5×20mm slow-blow type 218000 series/Type T)
This is required when exporting equipment containing MICROSmart to Europe.
● Use an EU-approved circuit breaker. This is required when exporting equipment containing
MICROSmart to Europe.
● If relays or transistors in the MICROSmart output modules should fail, outputs may remain on or off.
For output signals which may cause heavy accidents, provide a monitor circuit outside of the MICROSmart.
● Do not disassemble, repair, or modify MICROSmart modules.

-

Sensor(2 wires)

DC Power
WiringMount the FC6A MICROSmart as follows. To provide ample ventilation, ensure that there is sufficientspace between the FC6A MICROSmart and other devices, heat sources, and panel surfaces.

Available

Warning notices are used to emphasize that improper operation may cause severe personal injury or death.

inspection on the MICROSmart. Failure to turn off the power may cause damage, electrical shocks orfire hazard.
● Emergency stop and interlocking circuits must be configured outside the MICROSmart. If such a circuit isconfigured inside the MICROSmart, failure of the MICROSmart may cause disorder of the control
system, damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND D HAZARDOUS
LOCATIONS, OR NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereuses de classe 1, groupes
A,B,C et D; ou dans des zones non dangereuses.
● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT EQUIPMENT WHILE THE CIRCUITIS LIVE OR UNLESS THE AREA IS KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.
● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant que le circuit est sous tension,ou à moins ďêtre certain que lieu ďutilisation soit exempt de concentrations inflammables.
● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE INSTALLED IN AN ENCLOSURESUITABLE FOR THE ENVIRONMENT THAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOLOR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté à ľenvironnement ďutilisation etuniquement accessible avec un outil ďouverture ou une clé.
● WARNING - EXPLOSION HAZARD - THE USB PORT IS NOT FOR USE IN HAZARDOUS LOCATIONS.
● Avertissement: risque d'explosion. Le port USB ne doivent pas être utilisés dans des emplacements
dangereux.

DC Source Input Wiring+

Installation in Control Panel & Mounting Direction

7(4)● Turn off the power to the MICROSmart before starting installation, removal, wiring, maintenance, or

DC Sink Input Wiring* See the user's manual for more details on the product specifications.

(11)

Caution notices are used where inattention might cause personal injury or damage to equipment.

Wiring9.5

ø4* Dimensions in brackets [ ] are for type numbers FC6A-C*4* (Push-in type).
* See the user's manual for more details on the dimensions.

MicroSmart User’s manual can be downloaded from http://www.idec.com/FC6Amanuals

http://www.idec.com
2020.112

7仕様

使用周囲温度：-10～+55℃（氷結なきこと）
拡張使用周囲温度：-25～-10℃、+55～65℃（氷結なきこと）* 拡張使用周囲温度で使用するための詳細は、ユーザーズマニュアルを参照ください。
保存周囲温度：-25～+70℃（氷結なきこと）
使用/保存周囲湿度：10～95%RH（結露なきこと）
標高または大気圧：動作時：1013～795hPa（0～2000ｍ）
輸送時：1013～701hPa（0～3000m）
耐振動：5 ～ 8.4Hz 片振幅3.5mm 8.4 ～ 150Hz加速度9.8m/s2（1G）XYZ各方向
2
耐衝撃：147m/s （15G）11ms XYZ 3軸6方向各3回

取扱説明書

3

本製品の取り扱いには専門の知識が必要です。
・本製品の取り付け、配線作業、運転および保守・点検を行う前に、この取扱説明書およびユーザーズ
マニュアルをよくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管されるよう手配ください。
・本製品は弊社の厳しい品質管理体制のもとで製造されておりますが、万一本製品の故障により重大な故障や損害の発生するおそれがある用途へご使用の際は、バックアップやフェールセーフ機能をシステムに追加してください。
・取扱説明書、ユーザーズマニュアルに記載の指示に従って取り付けてください。取り付けに不備があると落下、故障、誤作動の原因となります。
・使用条件が、取扱説明書やユーザーズマニュアルの内容と相違ないことを必ずご確認ください。
内容に不明な点がある場合は、使用する前に弊社までご相談ください。
・本取扱説明書では、誤った取り扱いをした場合に生じることが想定される危険の度合いを「警告」「注意」として区別しています。それぞれの意味するところは以下のとおりです。

！

2時間

40mm
以上

(17)

(16)

(15)

(14)

(13)

(19)

天面

(12) 入力端子部(13) カートリッジスロット 2(14) カートリッジスロット 1(15) アナログボリューム(16) センサ用電源端子部 *1(17) 拡張コネクタ(18) 増設コネクタ(19) 電池ホルダ

DIN レール

動作周囲温度(6) (7) (8) (9)

(10)

(26)

(25)

(20)

8

（単位：mm）［FC６A-C40R*AE, -C40R*CE, -C40K*CE, -C40P*CE, -C40R*DE, -C40K*DE, -C40P*DE の場合］

(28)

73.0

2.7
[3.3]

90.0

警告
(21)
(24)
(23)

DC24V電源タイプ

DC12V電源タイプ* 端子仕様リレー出力

FC6A-C40R*CE

FC6A-C24R*CE

FC6A-C16R*CE

トランジスタシンク出力

FC6A-C40K*CE

FC6A-C24K*CE

FC6A-C16K*CE

トランジスタプロテクトソース出力

FC6A-C40P*CE

FC6A-C24P*CE

FC6A-C16P*CE

FC6A-C40R*DE

トランジスタプロテクトソース出力

FC6A-C40P*DE-

FC6A-C16R*DE

L

L: ヒューズ+--L : 負荷外部電源
AC85～264V

トランジスタプロテクトソース出力
配線例
トランジスタプロテクトソース出力

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(+) V0(-)

L

L

L

L

L

L

L

-

L

+

L

L

L

L

L

L

L

※出力配線時の電源仕様に関する詳細は、ユーザーズマニュアルを参照ください。

10

適合電線／推奨フェルール端子／推奨ドライバ／締付トルク

推奨のフェルール端子はフェニックス・コンタクト社またはワイドミュラー社製品です。
下記推奨フェルール端子を圧着する際には、専用の圧着工具（CRIMPFOX 6（1212034）またはPZ 6 Rote L（1444050000））をご使用ください。
端子台に配線する際には、下記推奨ドライバをご使用ください。またねじ締め付けが必要な場合は、下記の推奨締付トルクで締め付けてください。

2.9 [8.1]
13.6 [12.6]

UL1007/UL2464

AWG16

UL101535mm幅
DINレール① DINレールフック
を下げる
直付け用取付けフック（FC6A-PSP1PN05）③ DINレールに沿わせる
ねじ止め用穴FC6A-C16K*DE
FC6A-C16P*DE

１：ねじ締めタイプ、４：プッシュインタイプ

梱包内容（入り数）：本体ユニット（1）、アナログ入力用ケーブル付コネクタ（1）、電池ホルダ（電池付き 1）、取扱説明書（本書 1）。
DINレールフック

ねじ止め用穴AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H 0,34/10 TK(9025750000), H 0,34/12 TK (9025770000)
AI 0,5-6 (3200687), AI 0,5-8 (3200014),
AI-TWIN 2×0,5-8 (3200933), H 0,5/12D W(9019000000),
H 0,5/14D W (9019010000), H 0,5/14D ZH W (9037380000)
AI 0,75-6 (3200690), AI 0,75-8 (3200519),
Al-TWIN 2×0,75-8 (3200807), H 0,75/12D GR (9019030000),
H 0,75/14D GR (9019040000),
H 0,75/14D ZH GR (9037410000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H 1,5/14D SW (9019120000)
AI 0,5-8 GB (1208966)
AI 1-8 (3200030), H 1,0/14D R (9019080000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H 1,5/14D SW (9019120000)

2.9
[8.1]

95.0

2.7
[3.3]

適合電線

UL1007/UL2464

73.0

4.0
90.0

90.0

UL1015推奨フェルール端子

AWG24

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

AWG22

AI 0,34-8 (3203066), H0,34/12 TK (9025770000)

AWG20

AI 0,5-8 (3200014), H0,5/14D W (9019010000)

AWG18

AI 0,75-12 (3200849), Al-TWIN 2×0,75-10 (3200975),
H0,75/18 W (9025910000), H0,75/16D ZH GR (9037420000)

AWG16

H1,5/18D SW (9019140000)

AWG20

AI 0,5-8 GB (1208966)

AWG18

AI 1-12 (3200674), H1,0/16 GE (9025950000)

AWG16

H1,5/18D SW (9019140000)
推奨ドライバ

推奨締付トルク

4.3

110.0
98.0±0.2

2-ø

4.3

95.0
83.0±0.2

2.9 [8.1]
13.6 [12.6]2-ø

2.9 [8.1]
13.6 [12.6]

SZS 0,6×3,5 (1205053) , SDS 0,6×3,5×100 (9008330000)（

110.51 N・m）内はフェニックス・コンタクト社またはワイドミュラー社製品の発注形番

廃棄上のご注意・本製品を廃棄するときは、産業廃棄物として扱ってください。

ユーザーサポート情報④ DINレールフックを
上げる

.5

ø4
［直付け取付けの場合］
本体裏面のDINレールフックを引き出し（Ｉ/Ｏタイプは、直付け用取付けフック（保守部品：FC6A-PSP1PN05）を本体に取り付け、ねじ止め用穴を使用して取付板に取り付けます。
取付ねじは、M4ナベ小ねじ（6mmまたは8mm）をご使用下さい。

推奨フェルール端子
AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H 0,25/10 HBL(9025740000), Ｈ 0,25/12T GE (9021020000)

・FC6A-C*4*形（プッシュインタイプ）の場合[FC6A-C16R*AE, -C16R*CE, -C16K*CE,[FC6A-C24R*AE, -C24R*CE,-C16P*CE, -C16R*DE, -C16K*DE,-C24K*CE, -C24P*CEの場合]-C16P*DE, の場合]
110.0

AWG20
AWG18
AWG16

4.5

2-ø

取付け

35mm幅
DINレール

AWG20

AWG18

50.0±0.2

I/O16点FC6A-C16R*AE

FC6A-C40K*DE

4.3

90.0
83.0±0.2

I/O24点

トランジスタシンク出力

163.0
151.0±0.2

2-ø・工場出荷時、機能スイッチは０の状態です。
・ WindLDR で［機能スイッチで PLC を RUN/STOP する］を有効にしている場合、［ダウンロード後、自動的に PLC を RUN スタートする］を有効にしてプログラムを
ダウンロードしても、機能スイッチが 0 では PLC は RUN しません。
RUN させるには、機能スイッチを 1 にする必要があります。

② DINレールにひっかける

FC6A-C24R*AE

リレー出力

注意

詳しい取付け、取外し方法は、ユーザーズマニュアルをご参照ください。
［DINレール取付けの場合］取り付けには必ずDINレールを使用し、止め金具（BNL6）で固定してください。

I/O 40点

L

・FC6A-C*1*形（ねじ締めタイプ）の場合※WindLDR の初期設定では［機能スイッチで PLC を RUN/STOP する］は有効です。
※機能スイッチに関する詳細はユーザーズマニュアルを参照ください。

FC6A-C40R*AE

リレー出力

Q1 Q2 Q3 COM1 Q4

COM0 Q0PE

トランジスタシンク出力

AWG24

50.0±0.2

AC100-240Ｖ電源タイプ リレー出力

N

適合電線

機能スイッチの出荷時の状態

形番

出力仕様

！

BR2032 互換バックアップ電池
CR2032X or CR2032W
Murata
CR2032A or CR2032B
Panasonic

・電池残量がなくなる前に、バックアップ用電池を交換してください。
・バックアップ用電池の交換作業は電源遮断後、１分以内に行ってください。交換作業が長くなると、デバイス値が初期値に戻ります。
・通電状態では作業しないでください。製品が破損する恐れがあります。

6

リレー出力配線例

外部電源
DC20.4～28.8V

AWG22

1. 電池ホルダの両端をつまみ、引き抜きます。*（a）2. 電池ホルダから使用済みのバックアップ用電池を取り外します。
側
外側のツメ（b）を引きながら、下からバックアップ用電池を押します（c）。
3. 新しいバックアップ用電池を電池ホルダに取り付けます。
外側のツメ（b）にカチッと音がするまで押し込みます。
4. 電池ホルダを元の位置に差し込み（a）、奥までしっかり
押し込みます。

* 電池ホルダの引き出し寸法は 36mm です。
バックアップ用電池には、Panasonic 製 BR2032、もしくは下記のリストに記載されている互換電池のみ使用し、それ以外の電池は使用しないでください。

b

5

I6

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(-) V0(+)

100.0±0.2

a

形番構成
電源仕様

+

DC 電源タイプにはありません。
FC6A-C*4* 形（プッシュインタイプ）には、端子カバーはありません。

2.9[8.1]

電池ホルダの◆EU加盟国でのバッテリおよびバッテリ組込み機器の取扱いについての注意事項
注）以下のシンボルマークは欧州連合域内の国においてのみ有効です。

1

*1
*2

90.0
83.0±0.2

注意

このシンボルマークは電池及び蓄電池を廃棄する際、一般ゴミとは分別して処理する必要があるということを意味します。左記のシンボルマークの下に元素記号が表示されている場合、電池又は蓄電池に基準以上の重金属が含有されていることを意味します。濃度の基準は次のとおりです。
Hg : 水銀 (0.0005%)
Cd : カドミウム (0.002%)
Pb : 鉛 (0.004%)
電池および蓄電池は各国や地域の条例に従って、正しく廃棄してください。

-

バックアップ用電池の交換手順

側
c

I5

AC100-240V
AC電源入力右側面(22)

電池ホルダの

I4

外形寸法

4.0

電池ホルダ

I3

-

注意

・本製品は装置内への組み込み設置専用です。装置外には設置しないでください。
・カタログ、ユーザーズマニュアルに記載の環境下で、ご使用ください。
・高温、多湿、結露、腐食性ガス、過度の振動・衝撃のある所で使用すると、感電、火災、誤動作の原因となります。
・本製品の使用環境汚損度は「汚損度2」です。
・設置、配線作業時に配線くずやドリル加工による金属の切り粉などが、本製品内部に入らないように注意してください。配線くずなどが本製品内部に入ると、火災、故障、誤動作の原因となります。
・配線は印加電圧、通電電流に適した電線サイズを使用し、端子ねじは推奨締付トルク（0.51N・m）で締め付けてください。
・本製品の電源ライン、出力モジュールの出力ラインには印加電圧、通電電流に適したIEC60127
承認ヒューズをご使用ください。
（推奨:リテル社5×20mmスローブロー型218000シリーズ/タイプT）（マイクロスマートを組み込んだ機器を欧州に出荷する場合に適用）
・サーキットブレーカをご使用の場合は、EU承認品をご使用ください。
（マイクロスマートを組み込んだ機器を欧州に出荷する場合に適用）
・出力モジュールのリレー、トランジスタなどの故障により出力がONまたはOFFの状態になったままになることがあります。重大事故の可能性のある出力信号については外部に状態を監視する回路を設けてください。
・センサ電源は、マイクロスマートに接続するセンサの電源供給以外の用途では使用しないで下さい。
・分解、修理、改造等は行わないでください。

I2+(24) シリアルポート 1 カバー(11) (25) ダミーカートリッジ(26) アナログポートカバー(27) 拡張コネクタ保護シール(28) 増設コネクタ保護シール

90.0
83.0±0.2！

DC24Ｖ入力

右側面(20) SD メモリカードカバー(21) USB ポートカバー(22) 電源端子カバー *2(23) Ethernet ポート 1 カバー

4

I1

電源出力

センサ用電源

L

L

163.0

・取り付け、取り外し、配線作業および保守・点検は必ず電源を切って行ってください。
破損のおそれ、感電および火災の危険があります。
・非常停止回路やインタロック回路などはマイクロスマート以外の外部回路で構成してください。
これらの回路をマイクロスマートのシステムで構成するとマイクロスマートが故障した場合、機械の暴走、破損や事故のおそれがあります。

+24V 0V COM I0

トランジスタシンク出力
配線例
取り付け可能

(5)

左側面

I6

DC24V電源入力

外部電源
DC10.2～18.0V

取扱いを誤った場合、人が障害を負うか物的障害が発生する可能性があります。

！

I5+24V 0V FE

+

(4)

(27)

I4

DC12V電源入力

取り付け不可警告

I3

DC24Ｖ入力+12V 0V FE

(18)

左側面

+

電源配線例
DC24V
DC12V

20mm 以上

35℃以下

(3)

I2

2線式
センサ

-

L

(12)

(2)

I1

-

2線式
センサ

AC100～240V電源タイプの場合：外部DC24V電源を使用せず、上図丸部のセンサ用電源を使用することも出来ます。
DC24V電源タイプの場合：上図丸部のセンサ用電源はありません。外部DC24V電源が必要です。
DC12V電源タイプの場合：上図丸部のセンサ用電源はありません。外部DC12V電源が必要です。

40mm
以上

取り付け可能(11) 入力表示 LED［IN］
出力表示 LED［OUT］
電源表示 LED［PWR］
運転表示 LED［RUN］
エラー表示 LED
［ERR］
SD メモリカードステータス LED［SD］
電池ステータス LED［BAT］
ステータス LED［STAT］

DCソース入力配線例+

センサ用電源55℃以下

取扱いを誤った場合、人が死亡または重傷を負う可能性があります。

！

電源出力

名称と機能
(1) アナログ入力(2) 機能スイッチ(3) シリアルポート 1(4) SD メモリカードスロット(5) USB ポート(6) 電源端子部(7) LINK LED(8) ACT LED(9) Ethernet ポート 1(10) 出力端子部(1)

安全上のご注意+24V 0V COM I020mm 以上例）FC6A-C*1*形（ねじ締めタイプ）の場合

この度は、弊社製品をお買い上げいただき、誠にありがとうございます。本製品を安全に正しくお使いいただくために、この取扱説明書およびFC6A形マイクロスマートユーザーズマニュアルをよくお読みください。この取扱説明書は最終ユーザー様で保管されるよう手配ください。

入出力配線
DCシンク入力配線例

動作周囲温度* 電気的仕様に関する詳細はユーザーズマニュアルを参照ください。

ＦＣ６Ａ形
ＣＰＵモジュール
オールインワンタイプ

9

取付け方向

FC6A形マイクロスマートは次のように取り付けてください。また、通気性が良くなるように、周囲の取り付け物、発熱体および盤面から十分なスペースを確保して取り付けてください。

2.9
[8.1]

B-1816(7)

最新のユーザーズマニュアルを、下記URLよりダウンロードして下さい。
https://jp.idec.com/c/MicroSmart_FC6A.5

ø4*［ ］内は、FC6A-C*4*形（プッシュインタイプ）の寸法。
※カバーを開いたときの各寸法は、マニュアルを参照ください。

2020.11