ADAM-6015
ADAM-6017
ADAM-6018+

ADAM-6015

RoHS
COMPLIANT
2002/95/EC

Specifications

7-ch Isolated RTD Input Modbus TCP Module
8-ch Isolated Analog Input Modbus TCP Modulewith 2-ch DO
8-ch Isolated Thermocouple Input Module

ADAM-6017

COMPLIANT
2002/95/EC

Specifications

Analog Input

Analog Input

7 (differential)
 Channels> 10 MΩ Input Impedance
2 or 3 wire
 Input Connections
Pt, Balco and Ni RTD
 Input Type RTD Types and Temperature Ranges

 Channels
 Input Impedance

-50°C
~
150°C
0°C
~
100°C
0°C
~
200°C
0°C
~
400°C
-200°C~
200°C
Pt 1000
-40°C
~
160°C
Supports both IEC 60751 ITS90 (0.0385 W/W/°C) andJIS C 1604 (0.0392 W/W/°C)
Balco 500
-30°C
~
120°C
Ni 518
-80°C
~
100°C
0°C
~
100°C
± 0.1 % or better Accuracy
High speed mode
±0.5% or better± 25 ppm/°C Span Drift± 6 μV/°C
 Zero Drift
16-bit Resolution
 Sampling Rate
10 sample/ second (total)High speed mode:1K sample/second (total)
CMR @ 50/60 HZ 90dB
NMR @ 50/60 HZ 60dB
* high speed mode does not support CMR/NMR Wire Burnout Detection

 lnput Type lnput Range

Pt 100Ordering Information
 ADAM-6015

RoHS

7-ch Isolated RTD Input
Modbus TCP Module Accuracy
 Span Drift Zero Drift Resolution
 Sampling Rate Common-Mode
Voltage Power Dissipation
 Output Delay

RoHS
COMPLIANT
2002/95/EC

Specifications
Analog Input

8 (differential)> 10 MΩ (voltage)
120 Ω (current)
mV, V, mA±150mV , ±500mV , ±1 V ,±5V , ±10V, 0 ~ 150mV, 0 ~500mV , 0 ~ 1V , 0 ~ 5V , 0 ~10V, 0 ~ 20mA , 4 ~ 20mA ,±20mA±0.1% (voltage)±0.2% (current)±25 ppm/°C±6 μV/°C
16-bit10 or 100 sample/ second(total)CMR @ 50/60 HZ 90dB
NMR @ 50/60 HZ 67dB
350VDC

Digital Output
 Channels

ADAM-6018+

 Channels
8 (differential)
 lnput Type
Thermocouple
 Thermocouple Type and Range:JKTE

0 ~ 760°C
0 ~ 1,370°C-100 ~ 400°C
0 ~ 1,000°C

RS
B

500 ~ 1,750°C
500 ~ 1,750°C
500 ~ 1,800°C

 Accuracy@25°C

Type J,K,E,R,S: ±0.1% FSR
Max
Type B: ±0.15% FSR Max
Type T: ±0.2% FSR Max
 Span Drift±25 ppm/°C
 Zero Drift±6 μV/°C Resolution
16-bit Sampling Rate
10 sample/ second (total) Wire Burnout Detection

Ordering Information
 ADAM-6018+

2, open collector to 30 V, 100mA max. load
300 mW for each module
On: 100μs
Off: 150μs

8-ch Isolated Thermocouple
Input Module

Ordering Information
 ADAM-6017

8-ch Isolated AI with 2-ch DO
Modbus TCP Module

Common Specifications
General Certification

 LAN
 Power Consumption
 Connectors

 Watchdog
CE, FCC, UL*Class I, Division 2, Groups
A, B, C and D Hazardous
Locations for ADAM-6015 andADAM-6017
10/100Base-T(X)
2.5 W @ 24 VDC (ADAM-6015)
2.7 W @ 24 VDC (ADAM-6017)
1 W @ 24 VDC (ADMA-6018+)
1 x RJ-45 (LAN), Plug-in screw
terminal block (I/O and power)

System (1.6 second)and Communication(programmable)
10 ~ 30 VDC

 Power Input
 Supports Peer-to-Peer Supports GCL
 Supports Modbus/TCP, TCP/IP, UDP, RESTful
 Supports MQTT (D version), SNMP (D version)
Protocols (ADAM-6017 and ADAM-6018+)

Protection
 Isolation Protection 2,000 VDC
 Built-in TVS/ESD Protection
 Power Reversal Protection

Environment Operating-10 ~ 70°C (14 ~ 158°F)-40 ~ 70°C (-40~158°F)(D version)
 Storage Temperature -20 ~ 80°C (-4 ~ 176°F)-40 ~ 85°C ( -40~185°F)(D version) Operating Humidity 20 ~ 95% RH(non-condensing) Storage Humidity
0 ~ 95% RH(non-condensing)
Temperature

Ethernet I/O Modules: ADAM-6000
All product specifications are subject to change without notice.

Last updated: 26-Apr-2024

ADAM-6022
ADAM-6024

ADAM-6022

Ethernet-based Dual-loop PID Controller
12-ch Isolated Universal Input/Output
Modbus TCP Module

RoHS
COMPLIANT
2002/95/EC

Specifications

 Channels
 Output Type Output Range

2
V, mA
0 ~ 10 VDC, 4 ~ 20 mA, 0 ~ 20 mA

 Wet Contact

 Wet Contact2
Logic level 0: close to GND
Logic level 1: open
Logic level 0: 0 ~ 3 VDC
Logic level 1: 10 ~ 30 VDC

 Channels
 Power Dissipation

2, open collector to 30 V, 100 mA max. load
300 mW for each module

Ordering Information
 ADAM-6022

Ethernet-based Dual-loop PID Controller

Common Specifications
General Certification
 LAN
 Power Consumption
 Connectors

CE, FCC, UL
10/100Base-T(X)
4 W @ 24 VDC
1 x RJ-45 (LAN), Plug-in screw
terminal block (I/O and power) Watchdog
System (1.6 second)and Communication(programmable) Power Input
10 ~ 30 VDC
 Supports Modbus/TCP, TCP/IP, UDP, RESTful(D version), MQTT (D version), SNMP (D version)

2
V, mA
0 ~ 10 VDC, 4 ~ 20 mA, 0 ~ 20 mA
2
Logic level 0: close to GND
Logic level 1: open
Logic level 0: 0 ~ 3 VDC
Logic level 1: 10 ~ 30 VDCDigital Output

Digital Output
 Channels
 Power Dissipation

6 (differential)±10 VDC, 0 ~ 20 mA, 4 ~ 20 mA

Digital Input
 Channels
 Dry Contact

Digital Input
 Channels
 Dry Contact

 Channels
 Input Range

Analog Output

6 (differential)±10 VDC, 0 ~ 20 mA, 4 ~ 20 mA

Analog Output
 Channels
 Output Type Output Range

COMPLIANT
2002/95/EC

Analog Input
2 (3 AI, 1 AO, 1 DI, 1 DO for each control loop)

Analog Input
 Channels
 Input Range

RoHSSpecifications

General Loop Number

ADAM-6024

Supports
 Peer-to-Peer (Receiver only) GCL (Receiver only)

Ordering Information
 ADAM-6024

Analog Input

 Input Impedance Accuracy
 Resolution
 Sampling Rate CMR @ 50/60 Hz
 NMR @ 50/60 Hz
 Span Drift Zero Drift

Analog Output

2, open collector to 30 V, 100 mA max. load
300 mW for each module Accuracy
 Resolution
 Drift
 Current Load Resistor
 Voltage Load Resistor

12-ch Isolated Universal I/O Modbus TCP Module

Protection

20 MΩ±0.1% of FSR
16-bit10 sample/second
90 dB
60 dB
±25 ppm/° C±6 μV/° C Isolation Protection
2,000 VDC
 Built-in TVS/ESD Protection
 DI Over Voltage Protection 35 VDC
 Power Reversal Protection±0.1% of FSR
12-bit±50 ppm/° C
Max. 500Ω
Min. 1K Ω Storage Temperature

Environment Operating Temperature Operating Humidity
 Storage Humidity-10 ~ 50° C (14 ~ 122° F)
D version: -40 ~ 70° C(-40~158°F)-20 ~ 80° C (-4 ~ 176° F)
D version: -40 ~ 80° C(-40~176° F)
20 ~ 95% RH(non-condensing)0 ~ 95% RH(non-condensing)

Online Download www.advantech.com/products

ADAM-6050
ADAM-6051
ADAM-6052

ADAM-6050

RoHS
COMPLIANT
2002/95/EC

Specifications

18-ch Isolated Digital I/O Modbus TCP
Module14-ch Isolated Digital I/O Modbus TCP
Module with 2-ch Counter
16-ch Source-type Isolated Digital I/O
Modbus TCP Module

ADAM-6051

RoHS
COMPLIANT
2002/95/EC

Specifications

ADAM-6052

Digital Input

Digital Input

Digital Input

12
Logic level 0: Closed to GND
Logic level 1: Open
Logic level 0: 0 ~ 3 VDC
 Wet Contact
Logic level 1: 10 ~ 30 VDCor floating
Support DO type:
Sink (NPN) Supports 3 kHz Counter Input(32-bit + 1-bit overflow) Keep/Discard Counter Value when Power-off
 Supports 3 kHz Frequency Input

 Channels
 Dry Contact

 Channels

Digital Output

 Channels
2 ModeCounter, Frequency
 Keep/Discard Counter Value when Power-off Maximum Count
4,294,967,295(32-bit + 1-bit overflow)
 Input Frequency
Frequency Mode:
0.2 ~ 4500 Hz
Counter Mode: 0 ~ 4.5 kHz

 Channels

6 (sink type), open collector
to 30 V, 100 mA maximumload Supports 5 kHz Pulse Output
 Supports High-to-Low and Low-to-High Delay
OutputDigital Output

Ordering Information
 ADAM-6050-D1

Counter Input

18-ch Isolated DI/O Modbus
TCP Module Channels

2 (sink type), open collector
to 30 V, 100 mA maximumload Supports 5 kHz Pulse Output
 Supports High-to-Low and Low-to-High Delay
Output8
Dry/Wet Contact decided byswitch or jumper
 Dry Contact
Logic level 0: Open
Logic level 1: Closed to GND
 Wet Contact
Logic level 0: 0 ~ 3 VDC or
floating
Logic level 1: 10 ~ 30 VDCSupport DO type:
Source (PNP) Supports 3 kHz Counter Input(32-bit + 1-bit overflow) Keep/Discard Counter Value when Power-off
 Supports 3 kHz Frequency Input

Digital Output
 Channels
8 (Source Type) Voltage Range
10 ~ 35 VDC
 Current
1 A (per channel)
 Supports 5 kHz Pulse Output
 Supports High-to-Low and Low-to-High Delay
Output Supports Over Current Protection

Ordering Information
 ADAM-6052-D

Ordering Information
 ADAM-6051-D

COMPLIANT
2002/95/EC

Specifications

 Channels
 Dry Contact

12
Logic level 0: Closed to GND
Logic level 1: Open
 Wet Contact
Logic level 0: 0 ~ 3 VDC
Logic level 1: 10 ~ 30 VDC or
floating
Support DO type:
Sink (NPN) Supports 3 kHz Counter Input(32-bit + 1-bit overflow) Keep/Discard Counter Value when Power-off
 Supports 3 kHz Frequency Input

RoHS

16-ch Source-type Isolated
DI/O Modbus TCP Module

16-ch Isolated DI/O withCounter Modbus TCP Module

Common Specifications
General Certification

FCC, CE, UL*Class I, Division 2, Groups A,
B, C and D Hazardous Locations
 LAN
1-port 10/100Base-T(X) Power Consumption 2 W @ 24 VDC
 Connectors
1 x RJ-45 (LAN), Plug-in screw
terminal block (I/O and power) Watchdog
System (1.6 second) andCommunication (programmable) Power Input
10 ~ 30 VDC
 Supports Peer-to-Peer, GCL
 Supports User Defined Modbus Address Supports Modbus/TCP, TCP/IP, UDP,
RESTful, MQTT ( D version), SNMP (Dversion) Protocol

Protection
 Power Reversal Protection
 Isolation Protection 2,000 VDC

Ethernet I/O Modules: ADAM-6000

Environment Operating
Temperature-20 ~ 70°C (-4 ~ 158°F)
D version-40 ~ 70°C (-40~158°F)
 Storage Temperature -30 ~ 80°C (-22 ~ 176°F)
D version-40 ~ 85°C ( -40~185°F)
 Operating Humidity 20 ~ 95% RH(non-condensing) Storage Humidity
0 ~ 95% RH(non-condensing)ADAM-6060
ADAM-60666-ch Digital Input and 6-ch Relay
Modbus TCP Module
6-ch Digital Input and 6-ch Power Relay
Modbus TCP Module
ADAM-6000 Series Dimensions
Unit: mm60.00

112.00

56.00

56.00

10.00

R35.00

ADAM-6060

ADAM-6066

Front View

Rear View

RoHS

COMPLIANT
2002/95/EC

28
6.5

Specifications
General

122
142

56.00
120

 Connectors
 Watchdog Timer Power Input
 Supports Peer-to-Peer Supports GCL
 Supports Modbus/TCP, TCP/IP, UDP, DHCP,SNMP, RESTful and MQTT Protocol

2-SCREW
M3

M3

.50

1-port 10/100Base-T(X)
2 W @ 24 VDC (ADAM-6060)
2.5 W @ 24 VDC (ADAM-6066)
1 x RJ-45 (LAN), Plug-in screw terminal block (I/O and power)
System (1.6 second) and Communication (programmable)
10 ~ 30 VDC

14.00

7.50

Digital Input

R2 Channels
 Dry Contact

6
Logic level 0: Closed to GND
Logic level 1: Open
Logic level 0: 3 VDC
 Wet Contact
Logic level 1: 10 ~ 30 VDC or floating
Support DO type: Sink (NPN) only Supports 3 kHz Counter Input (32-bit + 1-bit overflow)
Keep/Discard
CounterValuewhen Power-off Supports 3 kHz Frequency Input
 Supports Inverted DI Status

30.00

.0

Ø8

28

Side View

Wall Mounting View

Relay Output (Form A)

Protection
2,000 VDC
 Isolation Voltage
 Power Reversal Protection

Environment Operating Temperature Storage Temperature Operating Humidity
 Storage Humidity-40 ~ 70°C ( -40~158°F)-40 ~ 80°C (-40~176°F)
20 ~ 95% RH (non-condensing)0 ~ 95% RH (non-condensing)

46.00

44.00

70.00

6
 Channels
 Contact Rating (Resistive) ADAM-6060: 120 VAC @ 0.5 A
30 VDC @ 1 A
ADAM-6066: 250 VAC @ 5 A
30 VDC @ 3 A
500 VAC (50/60 Hz)
 Breakdown Voltage
7 ms
 Relay On Time
3 ms
 Relay Off Time
Total
Switching
Time
10 ms

1 GΩ min. at 500 VDC
 Insulation Resistance
20 operations/minute Maximum Switching
Rate (at rated load)
 Supports Pulse Output

DIN-Rail Mounting View

27.00

 LAN
 Power Consumption

27.00

Top View

ADAM-6000 Series Common Specifications
General Dimensions (W x H x D) 70 x 120 x 30 mm
 Enclosure
ABS+PC Mounting
DIN 35 rail, stack, wall

Ordering Information
 ADAM-6060-D1
 ADAM-6066-D

6-ch DI and 6-ch Relay Modbus TCP Module
6-ch DI and 6-ch Power Relay Modbus TCP Module

Online Download www.advantech.com/products

ADAM-6217
ADAM-6224

ADAM-6217

COMPLIANT
2002/95/EC

 Span Drift Zero Drift Resolution
 Accuracy Sampling Rate CMR @ 50/60 Hz
 NMR @ 50/60 Hz
 Common ModeRoHSCOMPLIANT
2002/95/EC

Analog Output
8 (differential)> 10 MW (voltage)
120 W (current)
mV, V, mA±150 mV, ±500 mV, ±1 V, ±5 V, ±10 V, 0 ~ 20 mA,
4 ~ 20 mA, ±20 mA± 30 ppm/°C± 6 μV/°C
16-bit± 0.1% of FSR (Voltage) at 25°C
± 0.2% of FSR (Current) at 25°C
10 sample/second (total)
92 dB
67 dB
200 VDC

Ordering Information
 ADAM-6217

ADAM-6224

Specifications

Analog Input lnput Type lnput Range

4-ch Isolated Analog Output Modbus TCP
ModuleRoHS

Specifications
 Channels
 Input Impedance

8-ch Isolated Analog Input Modbus TCP
Module8-ch Isolated Analog Input Modbus TCP Module Channels
 Output Impedance Output Settling Time Driving Load
 Programmable
Output Slope Output Type Output Range Accuracy
 Resolution
 Current Load Resistor
 Drift

4
2.1 Ω
20 μs
Voltage: 2kΩ
Current: 500 Ω
0.125 ~ 128 mA/sec
0.0625 ~ 64 V/sec
V, mA
0 ~ 5 V, 0 ~ 10 V, ± 5 V, ± 10 V, 0 ~ 20 mA, 4 ~ 20 mA± 0.3% of FSR (Voltage) at 25°C
± 0.5% of FSR (Current) at 25°C
12-bit0 ~ 500 Ω± 50 ppm/°C

Digital Input
 Channels
 Dry Contact

4 (Dry Contact only)
Logic 0: Open
Logic 1: Closed to DGND

 Support DI Filter
 Support Inverted DI Status
 Support Trigger to Startup or Safety Value

Ordering Information
 ADAM-6224

Common Specifications
General Ethernet
 Protocol
 Connector Power Input
 Watchdog Timer Dimensions
 Protection
 Power Consumption

2-port 10/100 Base-TX (for Daisy Chain)
Modbus TCP, TCP/IP, UDP, HTTP, DHCP,RESTful,
SNMP (B version), MQTT (B version)
Plug-in 5P/15P screw terminal blocks
10 - 30 VDC (24 VDC standard)
System (1.6 seconds)
Communication (Programmable)
70 x 122 x 27 mm
Built-in TVS/ESD protection
Power Reversal protection
Isolation protection: 2500 VDC
ADAM-6217: 3.5W @ 24 VDC
ADAM-6224: 6W @ 24 VDC

Features Daisy chain connection with auto-bypass protection
 Remote monitoring and control with smart phone/pad Group configuration capability for multiple module setup Flexible user-defined Modbus address Intelligent control ability by Peer-to-Peer and GCL function
 Multiple protocol support: Modbus TCP, TCP/IP, UDP, HTTP, DHCP, RESTful
SNMP (B version), MQTT (B version) Web language support: XML, HTML 5, Java Script System configuration backup
 User Access Control

Environment Operating Temperature Storage Temperature Operating Humidity
 Storage Humidity

Ethernet I/O Modules: ADAM-6000

4-ch Isolated Analog Output Modbus TCP Module-10 ~ 70°C (14 ~ 158°F)-40 ~ 70°C (-40~158°F) (B version)-20 ~ 80°C (-4 ~ 176°F)-40 ~ 85°C ( -40~185°F) (B version)
20 ~ 95% RH (non-condensing)0 ~ 95% RH (non-condensing)ADAM-6250
ADAM-6251
ADAM-6256

ADAM-6250

RoHS
COMPLIANT
2002/95/EC

15-ch Isolated Digital I/O Modbus TCP
Module16-ch Isolated Digital Input Modbus TCP
Module16-ch Isolated Digital Output Modbus TCP
ModuleADAM-6251

RoHS
COMPLIANT
2002/95/EC

ADAM-6256

RoHS
COMPLIANT
2002/95/EC

Specifications
Digital Input

Digital Output

 Channels

 Channels

ADAM-6250: 8
ADAM-6251: 16
 Dry Contact
Logic 0: Open
Logic 1: Closed to DGND
 Wet Contact
Logic 0: 0 ~ 3 VDC or 0 ~ -3 VDC
Logic 1: 10 ~ 30 VDC or -10 ~ -30 VDC(Dry/Wet Contact decided by Switch) Input Impedance
5.2 kW (Wet Contact)
 Transition Time
0.2 ms Frequency Input Range
0.1 ~ 3kHz
 Counter Input
3kHz (32 bit + 1 bit overflow) Keep/Discard Counter Value when power off
 Supports Inverted DI Status Output Voltage Range
 Normal Output Current
 Pulse Output
 Delay Output

ADAM-6250: 7 (Sink Type)
ADAM-6256: 16 (Sink Type)
10 ~ 30 VDC
100 mA (per channel)
Up to 5kHz
High-to-Low and Low-to-High

Ordering Information
 ADAM-6250
 ADAM-6251
 ADAM-6256

15-ch Isolated Digital I/O Modbus TCP Module
16-ch Isolated Digital Input Modbus TCP Module
16-ch Isolated Digital Output Modbus TCP Module

Common Specifications
Features

General Cerification
 Ethernet
 LED Indication
 Protocol
 Connector Power Input
 Watchdog Timer Dimensions
 Protection

 Power Consumption

CE,FCC,UL
2-port 10/100 Base-TX (for Daisy Chain)
ADAM-6250: 8 DI + 7 DO
ADAM-6251: 16 DI
ADAM-6256: 16 DO
Modbus/TCP, TCP/IP, UDP, HTTP, DHCP,
MQTT, SNMP
Plug-in 5P/15P screw terminal blocks
10 - 30 VDC (24 VDC standard)
System (1.6 seconds)
Communication (Programmable)
70 x 122 x 27 mm
Built-in TVS/ESD protection
Power Reversal protection
Over Voltage protection: +/- 35VDC
Isolation protection: 2500 VDC
ADAM-6250: 3 W @ 24 VDC
ADAM-6251: 2.7 W @ 24 VDC
ADAM-6256: 3.2 W @ 24 VDC

 Daisy chain connection with auto-bypass protection
 Remote monitoring and control with smart phone/pad Group configuration capability for multiple module setup DI/O LED Indication
 Flexible user-defined Modbus address.
 Intelligent control ability by Peer-to-Peer and GCL function
 Multiple protocol support: Modbus/TCP, TCP/IP, UDP, HTTP, DHCP, MQTT, SNMP
 Web language support: XML, HTML 5, Java Script System configuration backup
 User Access Control

Environment Operating Temperature -10 ~ 70°C (14 ~ 158°F)-40 ~ 70°C (-40~158°F) (B version)
 Storage Temperature -20 ~ 80°C (-4 ~ 176°F)-40 ~ 80°C ( -40~176°F) (B version) Operating Humidity
20 ~ 95% RH (non-condensing) Storage Humidity
0 ~ 95% RH (non-condensing)

Online Download www.advantech.com/products

ADAM-6260
ADAM-6266

ADAM-6260

6-ch Relay Output Modbus TCP Module
4-ch Relay Output Modbus TCP Modulewith 4-ch DI

RoHS
COMPLIANT
2002/95/EC

ADAM-6266

RoHS
COMPLIANT
2002/95/EC

Specifications
Relay Output

Digital Input

 Channels
 Contact Rating (Resistive)
 Max. Switching Voltage
 Breakdown Voltage
 Max. Breakdown Capacity
 Frequency of Operation
 Set/Reset Time Mechanical Endurance Isolation between Contact
 Insulation Resistance

ADAM-6260: 5 Form C and 1 Form A
ADAM-6266: 4 Form C
250 VAC @ 5A
30 VDC @ 5A
400 VAC
300 VDC
500 VAC (50/60Hz)
1250 VA
360 operations/hour with load
72,000 operations/hour without load
8 ms/8 ms> 15 x 106 operations
1000 Vrms> 10 GΩ @ 500 VDC

 Channels
 Dry Contact

ADAM-6266: 4
Logic 0: Open
Logic 1: Closed to DI COM
 Wet Contact
Logic 0: 0 ~ 3 VDC or 0 ~ -3 VDC
Logic 1: 10 ~ 30 VDC or -10 ~ -30 VDC(Dry/Wet Contact decided by Switch) Input Impedance
5.2 kW (Wet Contact)
 Transition Time
0.2 ms Frequency Input Range 0.1 ~ 3kHz
 Counter Input
3kHz (32 bit + 1 bit overflow) Keep/Discard Counter Value when power off
 Supports Inverted DI Status

Ordering Information
 ADAM-6260
 ADAM-6266		Common Specifications
General Ethernet
 LED Indication
 Protocol
 Connector Power Input
 Watchdog Timer Dimensions
 Protection

 Power Consumption

2-port 10/100 Base-TX (for Daisy Chain)
ADAM-6260: 6 RL
ADAM-6266: 4 RL + 4 DI
Modbus/TCP, TCP/IP, UDP, HTTP, DHCP, SNMP,
MQTT
Plug-in 5P/15P screw terminal blocks
10 - 30 VDC (24 VDC standard)
System (1.6 seconds)
Communication (Programmable)
70 x 122 x 27 mm
Built-in TVS/ESD protection
Power Reversal protection
Over Voltage protection: +/- 35VDC
Isolation protection: 2500 VDC
ADAM-6260: 4.5 W @ 24 VDC
ADAM-6266: 4.2 W @ 24 VDC

Ethernet I/O Modules: ADAM-6000

6-ch Relay Output Modbus TCP Module
4-ch Relay Output Modbus TCP Module with 4-ch DI

Features Daisy chain connection with auto-bypass protection
 Remote monitoring and control with smart phone/pad Group configuration capability for multiple module setup DI/O LED Indication
 Flexible user-defined Modbus address.
 Intelligent control ability by Peer-to-Peer and GCL function
 Multiple protocol support: Modbus/TCP, TCP/IP, UDP, HTTP, DHCP, SNMP,
MQTT
 Web language support: XML, HTML 5, Java Script System configuration backup
 User Access Control

Environment Operating Temperature -10 ~ 70°C (14 ~ 158°F)-40 ~ 70°C (-40~158°F) (B version)
 Storage Temperature -20 ~ 80°C (-4 ~ 176°F)-40 ~ 80°C ( -40~176°F) (B version) Operating Humidity
20 ~ 95% RH (non-condensing) Storage Humidity
0 ~ 95% RH (non-condensing)ADAM-6315
ADAM-6317

ADAM-6315

IoT OPC UA Ethernet I/O - RTD Module
IoT OPC UA Ethernet I/O - AI Module

RoHS
COMPLIANT
2002/95/EC

ADAM-6317

RoHS
COMPLIANT
2002/95/EC

Specifications

Specifications

Analog Input

Analog Input

 Channels
8 (differential)
 Input Impedance> 10 MΩ Input Connections
2 or 3 wire
 Input TypePt, Balco and Ni RTD
 RTD Types and Temperature Ranges
Pt 100-50°C - 150°C
0°C - 100°C
0°C - 200°C
0°C - 400°C-100°C - 100°C-200°C - 200°C*Supports both IEC 60751 ITS90 (0.00385Ω/Ω/°C) and JIS C 1604 (0.00392Ω/Ω/°C)
Pt 1000-40°C - 160°C
Balco 500
-30°C - 120°C
Ni 5080°C - 100°C
Ni 518-80°C - 100°C
 Accuracy± 0.1 % or better
High speed mode ±0.5% or better Span Drift± 25 ppm/°C
 Zero Drift± 6 μV/°C
 Resolution
16-bit Sampling Rate
Normal speed mode:10 sample/ second (total)High speed mode:1024 sample/second (total)
CMR: 90 dB @ 50/60 HZ
NMR: 60 dB @ 50/60 HZ* High speed mode does not support CMR/NMR Wire Burnout Detection

Digital Input

 Channels
6 Dry contact
logic 0: Open; logic 1: Closed to ground Wet contact
logic 0: 0 ~ 3 VDC or floating; logic 1: 10 ~ 30 VDCSupport DO type: Sink (NPN) and Source (PNP) DI0~DI5 support 3 kHz counter input
 DI0~DI5 support 3 kHz frequency input

 Channels
 Sampling Rate Resolution
 Input Range

8 (differential)
10 or 100 samples/ second (total)
16 bits
0 ~ 150mV, 0 ~ 500mV,
0 ~ 1V, 0 ~ 5V, 0 ~ 10V,
±150 mV, ±500 mV, ±1V,
±5 V, ±10 V, ±20 mA,
0 ~ 20 mA, 4 ~ 20mA

Digital Input
 Channels
 Dry contact




11
logic 0: Open
logic 1: Closed to groundWet contact
logic 0: 0 ~ 3 VDC or floating
logic 1: 10 ~ 30 VDCSupport DO type:
Sink (NPN) and Source (PNP)
DI5~DI10 support 3 kHz counter input
DI5~DI10 support 3 kHz frequency input

Digital Output
 Channels
 Output type

10Sink type, 30 VDC,
0.1A max. per channel
DO4~DO9 support 3 kHz pulse output

Ordering Information
 ADAM-6317-A1

OPC UA and Security Remote I/O - AI Module

Digital Output

 Channels
8 Output type
Sink type, 30 VDC, 0.1A max. per channel
 DO2~DO7 support 3 kHz pulse output

Ordering Information

 ADAM-6315-A1

OPC UA and Security Remote I/O - RTD Module		Common Specifications
General Power input Power Consumption
 LAN port
 Connectors
 Watchdog
 Protocol

10 ~ 30 VDC
2.9 W @ 24 VDC (ADAM-6317)
2.8 W @ 24 VDC (ADAM-6350)
2-port 10/100 Base-T(X) (for Daisy Chain)
2 x RJ-45 (LAN), Plug-in screw terminal block (I/O and power)
System and Communication
OPC UA, Modbus

Protection

 Isolation
 Power Reversal Protection

2,500 VDCOPC UA Max Monitored Items
600 (A maximum of 32 ScaledValueHistory items can be included inall sessions) Max Sessions
4 (including security or non-security session) Max Subscriptions per
1
Session Support security/certificate management

Modbus/TCP Modbus/TCP connection

4

Environment Operating Temperature Storage Temperature Operating Humidity
 Storage Humidity-25° C ~ 70° C-25° C ~ 85° C
20 ~ 95% RH (non-condensing)0 ~ 95% RH (non-condensing)

Online Download www.advantech.com/products

ADAM-6350
ADAM-6360D
ADAM-6366

ADAM-6350

RoHS
COMPLIANT
2002/95/EC

Specifications

IoT OPC UA Ethernet I/O - DI/O Module
IoT OPC UA Ethernet I/O - SSR Relay Output Module
IoT OPC UA Ethernet I/O - SSR Relay Output Module

ADAM-6360D

RoHS
COMPLIANT
2002/95/EC

Specifications

Digital Input

Relay Output (PhotoMOS SPST) Channels
 Dry contact

 Channels
 Contact rating

18
logic 0: Open
logic 1: Closed to ground Wet contact
logic 0: 0 ~ 3 VDC or floating
logic 1: 10 ~ 30 VDCSupport DO type:
Sink (NPN) and Source (PNP) DI12~DI17 support 3 kHz counter input
 DI12~DI17 support 3 kHz frequency input

Digital Output(Resistive andInductive load) Relay-on time Relay-off time Isolation (Relay
output to power)
 Peak Load Current
 Total Power
Dissipation
 On-state resistance Channels
 Output type

Digital Input

18
Sink type, 30 VDC,
0.1A max. per channel
 DO12~DO17 support 3 kHz pulse output

8 (Form A)
1 A @25°C @30 VDC
0.7A @70°C @30 VDC
1.3 ms
0.8 ms
1500Vrms
4A (100ms (1 pulse))
400mW / channel
0.5Ω Channels
 Dry contact

14
logic 0: Open
logic 1: Closed to ground Wet contact
logic 0: 0 ~ 3 VDC or floating
logic 1: 10 ~ 30 VDCSupport DO type:
Sink (NPN) and Source (PNP) DI8~DI13 support 3 kHz counter input
 DI8~DI13 support 3 kHz frequency input

Digital Output
 Channels
 Output type6
Sink type, 30 VDC,
0.1A max. per channel
 DO0~DO5 support 3 kHz pulse output

Common Specifications
General Power input Power Consumption

 LAN port
 Connectors
 Watchdog
 Protocol

Protection
 Isolation
2,500 VDC
 Power Reversal Protection

RoHS
COMPLIANT
2002/95/EC

Specifications
Relay Output
 Channels
 Contact rating

6 (Form A)
0.25A@250VAC
2A@30VDC
3 ms
 Relay-on time
5 ms Relay-off time Electrical endurance Resistive, 0.25A@250VAC:
at contact application 1x105 operations/min.
Resistive, 2A@30VDC:
1x105 operations/min.
 Insulation Resistance 1 GΩDigital Input
 Channels
 Dry contact

18
logic 0: Open
logic 1: Closed to groundlogic 0: 0 ~ 3 VDC or floating Wet contact
logic 1: 10 ~ 30 VDCSupport DO type:
Sink (NPN) and Source (PNP) DI12~DI17 support 3 kHz counter input
 DI12~DI17 support 3 kHz frequency input

Digital Output
 Channels
 Output type6
Sink type, 30 VDC,
0.1A max. per channel
 DO0~DO5 support 3 kHz pulse output

Ordering Information
 ADAM-6350-A1

OPC UA
10 ~ 30 VDC
2.8 W @ 24 VDC(ADAM-6350)
2.8 W @ 24 VDC(ADAM-6360D)
4.5 W @ 24 VDC(ADAM-6366)2-port 10/100 Base-T(X)(for Daisy Chain)
2 x RJ-45 (LAN), Plug-in
screw terminal block(I/O and power)
System and Communication
OPC UA, Modbus

ADAM-6366

 Max Monitored Items 600(including all sessions)
4 (including security or
non-security session) Max Subscriptions per 1
Session Support security/certificate management

 Max Sessions

Modbus/TCP Modbus/TCP connection 4

Environment Operating Temperature -25° C ~ 70° C
 Storage Temperature -25° C ~ 85° C
 Operating Humidity
20 ~ 95% RH
 Storage Humidity

Ethernet I/O Modules: ADAM-6000(non-condensing)0 ~ 95% RH(non-condensing) ADAM-6360D-A1
 ADAM-6366-A1

OPC UA and Security
Remote I/O - DI/O
ModuleOPC UA and Security
Remote I/O - SSR
Relay Output Module
OPC UA and Security
Remote I/O - SSR
Relay Output Module

Ethernet I/O Modules:
ADAM-6000/6200/6300
Introduction
Advantech's ADAM-6000/6200/6300 Ethernet I/O modules are easily integrated so they can remotely monitor and control devices more flexibly.

Feature Highlights
Secured Cloud I/ORich IoT Protocols

Innovative ADAM-6000/6200 Secured Cloud I/O offers device management, OTA
updates, security and device monitoring functions in IoT era and help user easily manage
widespread assets across diverse applications

The ADAM-6000/6200 series supports multiple protocols for IoT applications: MQTT,
SNMP, Restful APIs, and Modbus, which are very flexible and can be easily integrated
with Microsoft Azure, Database, Network and SCADA systems.

Cloud Supports Azure IoT Hub

MQTT Actively publish MQTT messages with user
defined intervals.
 Shortens downtime with alarm event
notification.
 Privacy assured with the TLS (Transport
Layer Security).
 User defined topic to integrate existing
systems.

SNMP
 Device Management: UUID, networking setting, I/O channel configuration
 OTA Updates: firmware, certificate and configuration mass deployment
 Security: TLS, X.509 certificate, cipher suites, IP whitelisting, protocol disabled
 I/O Control: digital I/O on/off, analog I/O read/write, I/O value periodically
updated, alarm notificatio

Simple and Intuitive Logic Control

 Simple way to monitor I/O data on NMS(Network Management System).
 SNMP trap to notify alarm events.
 Reduces implementation cost with ADAMMIB (Management Information Base) file.

Industrial Grade with Isolation & Wide-operating
ADAM-6000/6200/6300 series has a rugged
Temperaturedesign.
 Supports isolation protection to avoid
system damage from high-energy noise.
 Supports operating temperatures ofbetween -40 ~70°C and can perform inmost harsh environments.

ADAM-6000/6200 Peer-to-Peer (P2P) and Graphic Condition Logic (GCL) modules canperform as standalone products for measurement, control, and automation.

Peer-to-Peer(P2P) connection
 Easy channel mapping from different I/Omodules without extra programming effort
or additional controllers.
 Utilizes Peer-to-Peer modules, justconfigure settings through ADAM.NET utility.

Application Structure
Azure

SCADA / NMSAWSGraphic condition logic (GCL)

Easy Deployment and Robust Communication
Flexible deployment with daisy
chain networking and auto-bypass
protection
ADAM-6200/6300 series supports daisy chain
connectivity that offers flexible cabling and spacesaving capabilities. With Ethernet auto-bypass
function supported to prevent accidental power
failures if one of the modules unexpectedly
shuts down.

Ethernet

Analog Input

Humidity

Temperature

Vibration

Level

Humidity

Temperature

Vibration

Level

Analog Output

Digital Input

Digital Output

Pressure Valve

ON/OFF

Light Switch

ON/OFF

Light Switch

Pressure Valve GCL function is built-in ADAM-6000 and
ADAM-6200 modules for users to easily set
up logic rules in any application.
 User defined logic rules through graphicalconfiguration environment in ADAM.NET
utility.
 No additional controllers or programmingis needed.

Database

ADAM-6000/6200/6300 SeriesComparison
Series Name
Daisy-chain
Connectivity
MQTT
SNMP
ModbusProtocol RESTful
OPC UA
Cloud
I/O

ADAM-6000 Series

ADAM-6200 Series

ADAM-6300 Series

–









–





–

–
–

–






(By request)Ethernet I/O Modules:
ADAM-6000

Model

ADAM-6015

Analog Input
AnalogOutputDigital I/O

ADAM-6018+


16-bitResolution
Channels
Sampling Rate

7
10 Hz

Voltage Input–

Current Input–

8
10/100 Hz±150 mV, ±500 mV,±1 V, ±5 V, ±10 V,
0~150 mV, 0~500
mV, 0~1 V, 0~5 V,
0~10 V
0~20 mA, 4~20 mA,±20 mA

8
10 Hz

ADAM-6022

ADAM-6024

±10 V

±10 V

–

0~20 mA, 4~20 mA

0~20 mA, 4~20 mA

Pt, Balco, and Ni RTD–

Max. Min. Avg.
–

 (4 ~ 20mA only)
Max. Min. Avg.
–

Current Output

–

–

–

Voltage Output
Input Channels
Output Channels
High/Low Alarm
Settings
Isolation Protection

–
–
-

–
–
2 (sink)––
8 (sink)

2,000 VDC–––
Receiver Only2–
Receiver Only2
16-bit for analog inputs
16-bit for analog inputs
12-bit for analog outputs 12-bit for analog outputs
6
6
10 Hz
10 Hz

–

J, K, T, E, R, S, B
thermocoupleMax. Min. Avg.
–

DirectSensor Input
Burn-out Detection
Math. Functions
Channels

Remark

–

–

–

–
–
2
0~20,
4~20 mA @ 15 VDC
0~10 VDC @ 30 mA
2
2 (sink)

–
–
2
0~20,
4~20 mA @ 15 VDC
0~10 VDC @ 30 mA
2
2 (sink)––

2,000 VDC
Built-in dual loop PID
control algorithm

2,000 VDC–

Certification

CID2, UL, CE, FCC

CID2, UL, CE, FCC

UL, CE, FCC

CE, FCC

D version: Modbus TCP,
RESTful, MQTT, SNMP,ASCIIUL, CE, FCC

Model

ADAM-6050

ADAM-6051

ADAM-6052

ADAM-6060

ADAM-6066

D version: Modbus TCP, RESTful, MQTT, SNMP, ASCII

ProtocolDigital I/O

ADAM-6017

1x RJ-45 LAN port, 10/100 Mbps Ethernet

InterfacePeer-to-Peer1
GCL1

InterfacePeer-to-Peer1
GCL1
Input Channels
Output Channels
Extra Counter
Channels
Counter Input
Frequency Input
Pulse Output
High/Low Alarm
Settings
Isolation Protection
Protocol
Certification
12
6 (sink)

Modbus TCP

1x RJ-45 LAN port, 10/100 Mbps Ethernet






12
8
6
2 (sink)
8 (source)
6-ch relay
6
6-ch power relay

–

2

–

–

–

3 kHz
3 kHz


4.5 kHz4.5 kHz


3 kHz
3 kHz


3 kHz
3 kHz


3 kHz
3 kHz


–

–

–

–

–

CID2, UL, CE, FCC

: supported, – : not supported,  : optional

2,000 VDC
D version: Modbus TCP, RESTful, MQTT, SNMP, ASCIIUL, CE, FCC
CID2, UL, CE, FCC
UL, CE, FCC

UL, CE, FCC

Ethernet I/O Modules:
ADAM-6200

Model

ADAM-6217

ADAM-6224

Analog Input
Analog Output

ADAM-6251

ADAM-6256

ADAM-6260

ADAM-6266

Peer-to-Peer1



Receiver Only2











GCL















Channels

8

–

–

–

–

–

–

Input Impedance>10MΩ (voltage)120Ω (current)

–

–

–

–

–

–

Voltage Input±150 mV, ±500
mV, ±1 V,±5 V, ±10 V

–

–

–

–

–

–

Current Input

0~20 mA,
4~20 mA±20 mA

–

–

–

–

–

–

Sampling Rate

10 Hz

–

–

–

–

–

–

Burn-out
Detection

 (4~20 mA)

–

–

–

–

–

–

Resolution

16-bit

–

–

–

–

–

–

Accuracy±0.1% of FSR(voltage) @ 25°C
±0.2% of FSR(current) @ 25°C

–

–

–

–

–

–

1

Channels

–

4

–

–

–

–

–

Voltage Output–

0~5 V, 0~10 V,±5 V, ±10 V

–

–

–

–

–

Current Output–

0~20 mA,
4~20 mA

–

–

–

–

–

Resolution–

12-bit

–

–

–

–

–

Input Channels–

4(dry contact only)

8

16

–

–

4

Output Channels––

7 (sink)–

16 (sink)–––

1 x Form A,
5 x Form C

Relay Output
Digital I/O

ADAM-6250

2x RJ-45 LAN port (Daisy-chain), 10/100 Mbps Ethernet

Interface

–

–

–

–

Contact Rating

–

–

–

–

–

4 x Form C

250 VAC @ 5A
30 VDC @ 5A

Counter Input

–

–

3 kHz

3 kHz

–

–

3 kHz

Frequency Input

–

–

3 kHz

3 kHz

–

–

3 kHz

Pulse Output

–

–

5 kHz

–

5 kHz

5 kHz

5 kHz

–

–

8 digital outputs,
7 digital inputs

3.5 W

6W

3W

LED Indicators
Power Consumption

16 digital inputs

16 digital outputs

6 relay

4 digital inputs,
4 relay

2.7 W

3.2 W

4.5 W

4.2 W

UL, CE, FCC

UL, CE, FCC

Isolation Voltage

2,500 VDC

Watchdog Timer

System (1.6 s), Communication (programmable)

Communication Protocol

Modbus TCP, RESTful, MQTT, SNMP, ASCIIPower Requirements

10~30 VDC (24 VDC standard)

Operating Temperature-40~70 °C (-40~158 °F)

Storage Temperature-40~85 °C (-40~185 °F)

Operating Humidity

20~95% RH (non-condensing)
0~95% RH (non-condensing)

Storage Humidity
Certification

UL, CE, FCC

UL, CE, FCC

UL, CE, FCC

UL, CE, FCC

UL, CE, FCC

Note 1: Peer-to-peer and GCL cannot be run simultaneously; only one feature can be enabled at a time.
Note 2: The ADAM-6224 can only act as a receiver and generate analog output when peer-to-peer or GCL mode is used.
: supported, – : not supported,  : optional

OPC UA Ethernet I/O Modules:
ADAM-6300

Model

ADAM-6315

ADAM-6317

ADAM-6318

ADAM-6324

ADAM-6350

ADAM-6360D

ADAM-6366

Description

IoT OPC UA
Ethernet I/O- RTD Input
ModuleIoT OPC UA
Ethernet I/O Analog Input
ModuleIoT OPC UA
Ethernet I/O- T/C Input
ModuleIoT OPC UA
Ethernet I/O Analog Output
ModuleIoT OPC UA
Ethernet I/O Digital I/O Module

IoT OPC UA
Ethernet I/O - SSR
Relay Output
ModuleIoT OPC UA
Ethernet I/O Relay Output
ModulePower Input

10~30 VDCLAN Port

2 x RJ-45 10/100 Mbps

Connectors

2 x RJ-45 (LAN), Plug-in screw terminal block (I/O and power)

Watchdog

System and Communication

ProtocolOPC UA, Modbus TCP

Isolation

2500 VDC

Power Reversal
Protection

Yes

Max Monitored
Items

600 (including all sessions)

Max Sessions

4 (including security or non-security session)Max
Subscriptions
per Session

1

SupportSecurity/
Certificate
Management

Yes

Modbus TCP Connections

4

GeneralProtection

OPC UA

Environment

OperatingTemperature-25° C~70° C (-13~158 °F)
Status, Error, Link, Active

LED Indicator
8

8

7

–

–

–

–

Voltage Input

RTD: Pt 100,
Pt 1000, Balco
500, Ni 518

0~150mV,
0~500mV,
0~1V, 0~5V,
0~10V,±150 mV,±500 mV, ±1V,
±5 V, ±10 V

Thermocouple:
J, K, T, E, R,
S, B

–

–

–

–

Current Input–

0 ~ 20 mA,
4 ~ 20 mA,± 20 mA

–

–

–

–

–

Sampling Rate

10 Hz (total)

10/100 Hz (total)

10 Hz (total)

–

–

–

–

Burn-out
Detection

Yes

Yes (4~20 mA)

Yes

–

–

–

–

Channels

Analog Input

Digital Input

Resolution

16-bit16-bit16-bit––––Digital Input
Channels

10

11

10

11

18

14

18

Counter Input

3 kHz (DI4~DI9)

3 kHz (DI5~DI10)

3 kHz (DI4~DI9)

3 kHz (DI5~DI10) 3 kHz (DI12~DI17)

3 kHz (DI8~DI13)

3 kHz (DI12~DI17)

Frequency Input

3 kHz (DI4~DI9)

3 kHz (DI5~DI10)

3 kHz (DI4~DI9)

3 kHz (DI5~DI10) 3 kHz (DI12~DI17)

3 kHz (DI8~DI13)

3 kHz (DI12~DI17)

Digital Output
Channels

10

10

13

12

18

6

6

Relay Output
Channels

–

–

–

–

–

8 x Form A (SSR)

6 x Form A
250 VAC @0.25 A,
30 VDC @ 2 A

Contact Rating

–

–

–

–

–

1 A @25°C @30 VDC
0.7A @70°C @30
VDC

Pulse Output

3 kHz(DO4~DO9)

3 kHz (DO4~DO9)

3 kHz(DO7~DO12)

3 kHz(DO6~DO11)

3 kHz(DO12~DO17)

3 kHz (DO0~DO5)

3 kHz (DO0~DO5)

Channels

–

–

–

4

–

–

–

–

–

–

CE, FCCCE, FCCCE, FCC

Digital Output

AnalogOutputType

Certification

–

–

–

0~5 V,
0~10 V, ± 5 V,
± 10 V,
0~20 mA,
4~20 mA

CE, FCCCE, FCCCE, FCCCE, FCC: supported, – : not supported,  : optional