Ever-evolving PLC.

FC6A

Latest evolution. The MicroSmart FC6A Plus
expands the limits of productivity, allowing forcontrolling not only large-size machines, but also
entire small-size production lines.

More Power.
More Performance.
		More Connectivity.

• Up to 2,060 I/O (incl. a maximum of 511 analog I/O)
• Extremely fast basic instruction execution of 21 ns• User program size: 800 KB (100,000 steps)• BACnet/IP protocol
The MicroSmart FC6A Plus can also handle large
programs such as positioning, PID, flow totalization andrecipes.
A maximum of 2,060 digital/analog I/O (All-in-One CPU
module: 528 I/O), 33 ports of serial communication, PID
control using PID module with up to 126-I/O expandability.
Can be used in larger system configurations thanconventional ones where micro PLCs are used.
* Maximum expansion of All-in-One CPU module:
System configuration of DIO+AIO (528 I/O), serial
communication (9 I/O), temperature control (up to 30
I/O) using temperature module is possible.
Multi-point system configuration can be set up flexibly
with the Ethernet cable and expansion interface module(unibody master/slave). Flexibly configure up to 10
expansion racks (15 modules max. per rack) to fit thecontrol panels or installation sites.
Only a small number of points, such as one or two, canbe added easily by using cartridges. Optional springclamp block connector is available to reduce wiring.

HMI Module

IDEC's ever-evolving MicroSmart FC6A Plus reduces
wiring and labor, and creates robust and stylish control
panels.
Cartridge Base Module

2

FC6A Plus
Expansion Interface Module (slave)
Expansion Modules

Up to 10expansion racks

Expansion rack 3

Expansion rack 2

Expansion rack 1

Expansion Interface Module(master)

Expansion Modules

MicroSmart FC6A Plus
3

Power, Performance, and Connectivity
The MicroSmart FC6A All-in-One.
High performance and easy programming.
• Up to 528 I/O (incl. a maximum of 511 analog I/O)
• Extremely fast basic instruction execution of 42 ns• User program size: 640 KB (80,000 steps)• Easy and quick programming
Parameters such as the status of peripheral input
devices connected to the PLC, results of logical operation
to peripheral output devices. These parameters need to
be checked and changed on-site. Simplify your work byusing the FC6A's HMI module. No PC required.
Perform run/stop of CPU module, parameter check/change, calendar display, and clock setting using the
LCD with 32 characters × 4 lines and six buttons.
Ethernet ports can be used for Email and Web Server
Functions.
With cartridges available in 10 types, a small numberof I/O and communication port can be added easily in alimited space. The FC6A-PC4 Bluetooth communication
cartridge enables wireless communication with barcode
readers and other peripheral devices. Eliminating theneed to adjust the cable length on-site shortens thetime for installation and maintenance.

4

HMI Module

FC6A All-in-One

CPU Module

Expansion Modules

5Adaptive Design

Plus

Plus

All-inOne

Plus

All-inOne

Dual Ethernet ports

RJ45 Ethernet PortSD Memory

One port can be configured for information system such as
FTP, Web Server, and Email functions, and the second port canbe configured for a control network including Modbus TCP, toprovide you with powerful maintenance and control capabilities.
BACnet/IP also supported. (System software ver 1.20 or later)

Supports the Modbus TCP protocol, and internet
connections such as Web Server and Email functions
for remote monitoring and control.
(All-in-One: HMI module is required.)

SD card for data logging, program storage/transfer,or user program updating.

Plus

All-inOne

Replaceable Battery
Battery can be replaced by the user, enabling predictive
maintenance.

Plus

Plus

All-inOne

Pull-up/down Removable
Power Supply Terminal

Plus

9 ports max.

Up to 33 Serial Ports

Simplifies wiring, installation, and module replacement—
just wire the terminal block plugged into a module.

Using a combination of communication cartridges andFC6A-SIF52 modules, up to 33 serial ports can be utilized.

Plus

Can be used to transfer user programs from WindLDR to CPU
module and for monitoring, without the need of power supply.

All-inOne

Removable Terminal Blocks

Plus

All-inOne

RJ45 RS232C/485 Serial Port
Supports Modbus RTU, user communication, maintenancecommunication, and data link communication.

All-inOne

Plus

Reduced Wiring

Digital/Analog/Communication Cartridges

I/O Modules

Spring clamp terminal available.

Digital cartridge: 3 types (4-point digital input/4-point transistor output)
Analog cartridge:4 types (2-point analog input/output)
Communication cartridge: 3 types (Serial/Bluetooth communication)

Digital input module:	  5 modules
Digital output module: 10 modules
Digital mixed I/O module:	  2 modules
Analog I/O module:
12 modules

6

All-inOne

USB Port

Pull-up/down terminal reduces wiring (patented).

All-inOne

Plus

All-inOne

Unmatched Performance

6×

Up to 2,060 I/O

Positioning Control

A maximum of 511 analog I/O.
(when using a 32-point FC6A Plus CPU module + an
expansion interface module + 32-point digital I/O
modules (63 modules) + digital cartridges (3 cartridges)+ a cartridge base module + an HMI module)

Equipped with features needed for simple positioning
control, such as zero return and 2-axis linear
interpolation.

Expanded Memory

Improved PID Algorithm

Program memory size is 800KB (100,000 steps)
maximum with 2,000 timers, 512 counters, and
260,000 data registers. Double the capacity of
conventional PLCs. This allows handling of large andcomplex programs such as PID, flow totalization andrecipes.

A new and improved PIDD algorithm enables cascade
control that needs complex programming.

Fast Processing Speed

Modbus TCP, RTU Protocols

Processing speed is 4 times faster than IDEC FC5A
MicroSmart Pentra.

These two leading industrial communication protocols
are supported in the CPU module and FC6A-SIF52
communication module. Communication monitor
shortens the debugging time, and communication toother devices is quick and seamless.

Fast I/O Refresh

Automatic Email Function

Expansion I/O refresh is 0.1 ms with four digital I/O
modules + one analog I/O module.

Remote access to system status using web browser.
Get periodic report and error notification alarm
anywhere with Email function.

High-Speed Outputs

Upgradable Software

Advanced instructions:
ARAMP: Advanced Ramp
JOG: Pulse with direction
ABS: Set the origin

System software and user programs are upgradable
through WindLDR, data file manager, or SD memory.

Time-Base Applications

iOS/Android Apps: WindEDIT

Real-time clock is built in. Obtain time from SNTP
server.

Perform status check, run/stop check and operation,
parameter check/change, user program download/
upload of FC6A with your smart phone or tablet
without PC or HMI module.
Files/folders in SD memory can be displayed as a list,
downloaded, uploaded, and deleted. Format operationis also possible.

7

Industrial Internet of Things

Wireless Communication
Wireless communication achieved with Bluetooth
cartridge. Use the iOS/Android App to monitor/change
parameters, upgrade user program, and monitor
logged data in the SD memory without opening
a control panel. System upgrade and predictive
maintenance cannot be more easier. Use your smart
phone or tablet to wirelessly communicate via theBluetooth cartridge of the FC6A, or over wifi or internet.
The FC6A microsite links to App Store and Google Playapplication download sites.

E-mail Function
App Store

Google PlayFTP Server/Client Functions
Store real time on-site information in the host FC6A or
PC to manage operation effectively. Because systems
in multiple FC6A can be upgraded at the same time,
downtime and management are minimized.

iOS & Android
WindEDITFTP Server/Client

Email Function
Connecting the Ethernet port on the CPU or on theoptional HMI module to the internet enables email
notification to quickly inform personnel of alarms andevents, allowing them to take remedial action quickly.
Can be used with third-party email servers such as
Gmail and Yahoo.

SCADA Monitoring and Control
Connecting the Ethernet or one of the serial
communication ports on the FC6A to a SCADA
system, all data required for display screen, trend,
and troubleshooting can be sent to the SCADA system.
Sending the data or commands from the SCADA system
to the CPU enables remote management.

SCADA
Monitoring & Control

Wireless Communication

Security/FTP/Web Server/App
Up to 16 user accounts can be set up by setting usernames and passwords. Ensure security by separately
setting the monitoring and operation authorities.

8

BEMS/HEMS

Multiple Communication Options

Email

Email Function

Modbus TCP/RTU Protocol

Values stored in the FC6A can be sentin Email format. Up to 255 templates
can be configured to multiple recipients.
Third-party email servers such as Gmail
or Yahoo supported.

Supports both protocols and can be
configured as a master or slave.

Web Server

CAN J1939 Protocol

CAN
used in diesel power
J1939 Commonly
applications, in vehicle networks fortrucks, buses, agriculture & forestry
machinery, and marine navigation
systems.

WindLDR
VFD
SCADA
Monitoring & Control

BACnet/IP Protocol
This leading building automation control
protocol is supported in the Plus CPU
module. Optimal decentralized control
is acheived by operating as a controller
with a B-ASC profile that communicateswith a host device. Efficient and energysaving building control can be realized by
gatewayless communication.

Operator
Interface
PLC

Remote I/O Module
ECU
PLC

Operator
InterfaceTemperature
Control

PLC

FC6A connects you to the world.
9

Manage yourproduction...
		from anywhere

Micro PLC with Web Server Function
Equipped on MicroSmart FC6A Plus as standard

WindLDR Programming Software

Wep Page Editor makes it simple to create professional and dynamic web
pages to monitor and control your system remotely from PC, smart phoneor tablet, via a web browser.

The dialog-driven programming tool combines logic andintuition with an incredibly easy-to-use interface. No
knowledge in ladder programming required. Just use
the configurator, shortcut key, simulation and monitor
functions to make programs quickly.

Web Page Editor: No HTML Programming
RequiredWind LDR 8.2 or later version has a new Web Page
Editor, which makes it simple to create professional anddynamic web pages to monitor and control the FC6A,
with no HTML or Java Script knowledge.

Symbol Factory: Over 7,000 Images
With over 7,000 pre-built practical images that can beimported, you can construct a professional web page inminutes.

Parameter Setting
Want to create a bar graph, gauge, pie chart, trend chart,pilot light, slider, pushbutton or other object on yourweb page? Just pick the object, drop it on the screen.
Data register values of the FC6A can be displayed, andparameters can also be changed on the web page.
Note: For Web Server Function and Email Function of the
FC6A All-in-One Model, use FC6A-PH1 HMI module.

10Compare FC6A Models

FC6A Plus CPU Module
Number of I/O

FC6A All-in-One CPU Module

16 I/O

32 I/O

16 I/O

24 I/O

40 I/OCAN J1939: 40 I/O

Rated Power Voltage 24V DC

24V DC

24V DC
100 to 240V AC

24V DC
100 to 240V AC

12V DC
24V DC
100 to 240V AC

12V DC
24V DC
100 to 240V AC

Shape

Program Capacity

800KB(100,000 steps)

800KB(100,000 steps)

384KB(48,000 steps)

384KB(48,000 steps)

384KB(48,000 steps)

640KB(80,000 steps)

Expansion Interface
Modules (Max.)

63 modules

63 modules

12 modules

15 modules

15 modules(12V DC Type: None)

15 modules(12V DC Type: None)

Maximum Digital I/O 2,044

2,060

404

508

528
(12V DC Type: 48)

528(12V DC Type: 48)

Maximum Analog I/O 511

511

101

125

127
(12V DC Type: 7)

126(12V DC Type: 7)

Communication
ProtocolModbus TCP
Modbus RTU
User Communication(Serial, TCP/UDP)FTP Client/Server
BACnet/IP
Bluetooth (SPP, iAP)
(optional cartridge)

Modbus TCP
Modbus RTU
User Communication(Serial, TCP/UDP)FTP Client/Server
BACnet/IP
Bluetooth (SPP, iAP)
(optional cartridge)

Modbus TCP
Modbus RTU
User Communication(Serial, TCP)
Bluetooth (SPP, iAP)
(optional cartridge)

Modbus TCP
Modbus RTU
User Communication(Serial, TCP)
Bluetooth (SPP, iAP)
(optional cartridge)

Modbus TCP
Modbus RTU
User Communication(Serial, TCP)
Bluetooth (SPP, iAP)
(optional cartridge)

CAN J1939
Modbus TCP
Modbus RTU
User Communication(Serial, TCP)
Bluetooth (SPP, iAP)
(optional cartridge)

IoT Functions

iOS, Android Apps
Web Server Functions
Email Function

iOS, Android Apps
Web Server Functions
Email Function

iOS, Android Apps
iOS, Android Apps
iOS, Android Apps
Web Server Functions (*1) Web Server Functions (*1) Web Server Functions (*1)
Email Function (*1)
Email Function (*1)
Email Function (*1)

iOS, Android Apps
Web Server Functions (*1)
Email Function (*1)

33

7

7

8

8

3 (*2)

3 (*2)

3 (*2)

3 (*2)

3 (*2)

Serial Port Extensibility 33
Cartridge

3 (*2)*1) Using FC6A-PH1 module*2) Using HMI module. For All-in-One, Analog and digital cartridges can be added to the HMI module.
For Plus, Analog, digital, communication cartridges can be added.
All-in-One CPU module System software Ver. 1.60 or later 
Plus CPU module System software Ver. 1.00 or later
HMI module System software Ver. 1.52 or later






11

www.idec.com

Head Office
6-64, Nishi-Miyahara-2-Chome, Yodogawa-ku, Osaka 532-0004, JapanUSA
IDEC Corporation
Germany APEM GmbH
Singapore IDEC Izumi Asia Pte. Ltd.
Thailand IDEC Asia (Thailand) Co., Ltd

Tel: +1-408-747-0550
Tel: +49-40-25 30 54 - 0
Tel: +65-6746-1155
Tel: +66-2-392-9765

opencontact@idec.com
service@eu.idec.com
info@sg.idec.com
sales@th.idec.com• MicroSmart logo is a trademark of IDEC Corporation.
• Ethernet is the registered trademark of Xerox Corporation, USA.
• All trademarks and registered trademarks are the property of their respective owners.
• Specifications and other descriptions in this brochure are subject to change without notice.
2018 IDEC Corporation, All Rights Reserved.
EP1623-1-A AUGUST 2018

Australia IDEC Australia Pty. Ltd.
Tel: +61-3-8523-5900 sales@au.idec.com
TaiwanIDEC Taiwan Corporation Tel: +886-2-2698-3929 service@tw.idec.com
info@hk.idec.com
Hong Kong IDEC Izumi (H.K.) Co., Ltd. Tel: +852-2803-8989

China/Shanghai IDEC (Shanghai) Corporation Tel: +86-21-6135-1515 idec@cn.idec.com
China/Shenzhen IDEC (Shenzhen) Corporation Tel: +86-755-8356-2977 idec@cn.idec.com
China/Beijing IDEC (Beijing) Corporation Tel: +86-10-6581-6131 idec@cn.idec.com
Japan
IDEC Corporation
Tel: +81-6-6398-2527 marketing@idec.co.jp