2Name & Function

3

Safety Precautions(1) Analog Potentiometer(2) Analog Input(3) Ethernet Port 1
ACT LEDLINK LEDTop

Special expertise is required to use the MICROSmart.

(11)

(13)

● Read this instruction sheet and the user's manual to make sure of correct operation before starting

(14)
(10)

installation, wiring, operation, maintenance, and inspection of the MICROSmart.
Keep this instruction sheet where it can be accessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorous quality control system, but users
must add backup or failsafe provisions to control systems use the MICROSmart in applications where
heavy damage or personal injury may be caused if the MICROSmart should fail.
● Install the MICROSmart according to the instructions described in this instruction sheet and the user's
manual. Improper installation will result in falling, failure, or malfunction of the MICROSmart.
● Make sure that the operating conditions are as described in the user’s manual. If you are uncertain
about the specifications, contact IDEC before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order of importance from Warning andCaution:

(9)

(1)
(2)
(3)
Left Side(4)

Right Side

(5)(6) (7) (8)
(20)

(21)

(22)

Warning notices are used to emphasize that improper operation may cause severe personal injury or death.

(15)
(16)

Caution notices are used where inattention might cause personal injury or damage to equipment.
(17)
Left Side● Turn off the power to the MICROSmart before starting installation, removal, wiring, maintenance, or+

I7 COM COM

Source input
wiring100.0±0.2

L

L
L

L
L

+ -

L
L
L
L

+ -

L

L
L

L
L

20.4 to28.8V DC

- +

Q1 Q0

24VDC Input
I4 I5
I6
+

Sink input
wiring

L

L

Q5 Q4 Q3 Q2

I3When an expansion module is not connected next, don’t peel off the protection sticker.

20.4 to28.8V DC-

Packing(Pcs/pack): FC6A Unit (1), Connector with analog input cable (1), Battery holder with battery (1)Instruction Sheet (this manual) (1).

20.4 to28.8V DC+FC6A-D16P1CEE
FC6A-D16P4CEEDIN Rail Hook

[ Direct Mounting on Panel Surface]
Pull out the DIN Rail hook on the back of the module andinsert the direct mounting hook (FC6A-PSP1PN05) into the slot.
Attach the module to the mounting plate using the screw holes.
Attach the module to the mounting plate using M4 tapping screws,
as shown below, or make 5 to 6mm mounting holes and secure
the module using M4 pan head screws.
Always give sufficient consideration to operability,
Screw Hole ease-of-maintenance, and environmental resistance when
deciding on the mounting position.

L

L

Q6

(4)

FC6A-D16P1CEE,-D16P4CEE

Transistor Protect Source output(3)

FC6A-D16K1CEE,-D16K4CEE

L

V0(-) COM0(+) COM0(+) Q7(1)

FC6A-D16R1CEE,-D16R4CEE(1) Pull out the DIN Rail Hook.
(2) Put the groove of the module on the
DIN Rail.
(3) Press the modules towards the DIN Rail.
(4) Push in the DIN Rail Hook.

Q035-mm-wide
DIN Rail

AWG20

I15
I16

6
4

I7
COM

5
3

I17
COM

2

NC

1

NC

sensor

NPN-

20.4 to 28.8V DC

+

PNP

+

20.4 to 28.8V DC

Source input
wiring-Sink input
wiring

19
17
15
13
11
9
7
5
3
1

Terminal No. OUTPUT Terminal No. OUTPUT

L
Q10
L
Q11
L
Q12
L
Q13
L
Q14
L
Q15
L
Q16
L
Q17
- +
COM(-)
20.4- 28.8VDC
+V

-

+

L
L
L
L
L
L
L
L

20.4 to 28.8V DC

20
18
16
14
12
10
8
6
4
2

Q0
Q1
Q2
Q3
Q4
Q5
Q6
Q7
COM(+)
-V

19
17
15
13
11
9
7
5
3
1

L
Q10
L
Q11
L
Q12
L
Q13
L
Q14
L
Q15
L
Q16
L
Q17
+ COM(+)
20.4
to 28.8V DC-V

Recommended ferrule
AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H0,25/10 HBL(9025740000), Ｈ0,25/12T GE (9021020000)
AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H0,34/10 TK(9025750000), H0,34/12 TK (9025770000)
AI 0,5-6 (3200687), AI 0,5-8 (3200014), AI-TWIN 2×0,5-8 (3200933),
H0,5/12D W(9019000000), H0,5/16D W (9019020000),
H0,5/14D ZH W (9037380000)
AI 0,75-6 (3200690), AI 0,75-8 (3200519), Al-TWIN 2×0,75-8 (3200807),
H0,75/12D GR (9019030000), H0,75/14D GR (9019040000),
H0,75/14D ZH GR (9037410000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)
AI 0,5-8 GB (1208966)
AI 1-8 (3200030), H1,0/14D R (9019080000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

Recommended ferrule
Al 0,25-10 (3241128)
Al 0,34-10 (3241129)
Al 0,5-10 (3201275), Al-TWIN2×0,5-10 (3203309),
H 0,5/16D W (9019020000), H 0,5/16D ZH W (9037390000)

AWG16

Al 0,75-10 (3201288), Al-TWIN 2×0,75-10 (3200975),
H 0,75/16D GR (9019050000), H 0,75/16D ZH GR(9037420000)
AI 1,5-10 (3200195), H 1,5/16D SW (9019130000)

AWG20

Al 0,5-10 GB (3203150), H 0,5/16 DS W (9202910000)

AWG18

AI 1-10 (3200182), H 1,0/16D R (9019100000)

AWG16

AI 1,5-10 (3200195), H 1,5/16D SW (9019130000)

AWG18

SZS 0,6×3,5 (1205053) , SDS 0,6×3,5×100 (9008330000)

Tighten torque0.51 N-m

Input Terminals and Output Terminals :Applied cable
AWG24
UL1007
AWG22/ UL2464
AWG20
UL1015[ FC6A-D16R1CEE, -D16R4CEE, -D16K1CEE, -D16K4CEE, -D16P1CEE, -D16P4CEE ]Input Terminals
Output Terminals

Q1

35-mm-wide
DIN Rail

-

Q2

(2)

: LoadQ5 Q4 Q3

[ Mounting on DIN Rail ]Use a 35-mm-wide DIN Rail and BNL6
mounting clips to secure the modules.

when power supply voltage less than 30V DC isrequired to power the terminal.
● For UL/cUL, use transistor outputs under resistive
load and Limited energy.
● Use copper conductor only.
● When the MICROSmart is used in a Surrounding
Air Temperature of 65°C, reduce the I/O voltage
and I/O utilization. See the user's manual for details.

Power Supply
20.4 to 28.8V DC-

FC6A-D32P3CEE
FC6A-D32P4CEE

L

9
7Screwdriver● Use an isolated type or SELV power supply source: FuseFE

2-wiresensorTransistor Protect Source+24V 0V+

FC6A-D32K3CEE
FC6A-D32K4CEE

Wiring* Enabled is the default setting for Run/Stop PLC by Function Switch in WindLDR.
* For details on the function switch, see the user's manual.

For details about mounting and removing modules, see the user’s manual.

AWG22
UL1007/ UL2464

UL101524VDC Power Input

Switch is enabled in WindLDR and a program is downloaded with Automatic
start after download enabled. To run the PLC, the function switch must be set to 1.

Mounting Modules

AWG20
AWG18

Power Supply Terminals● The PLC will not run if the function switch is 0 when Run/Stop PLC by Function

6

AWG20

AWG24

numbers FC6A-D*4*.

Q6● The default setting of the function switch is 0.

16-I/O TypeTransistor Sink-

on the dimensions.

* Dimensions in brackets [ ] are for type

9

I5
I6

Applied cable.5* See the user's manual for more details

Transistor Sink Output

Default Setting of the Function Switch

UL1015

ø4

Alternative Batteries Compatible with BR2032
CR2032X or CR2032W
Murata
CR2032A or CR2032B
Panasonic

10
8- 2-wire +sensor• FC6A-D*4*

2-● Change the battery before the old battery expires.
● Do not change the battery when the MICROSmart is power ON. Doing so may damage the product.
● Change the battery within 1 minute of turning off the power supply, or the device value will be reset toits initial values.
● Battery May Explode If Mistreated. Do Not Recharge,Disassemble Or Dispose Of In Fire.
● La piles peut exploser en cas de mauvais usage. Ne pas recharger, démonter ou jeter la piles au feu.

5

Q0
Q1
Q2
Q3
Q4
Q5
Q6
Q7
COM(-)+V

AWG16

V0(+) COM0(-) COM0(-) Q7

b

20
18
16
14
12
10
8
6
4
2

AWG16

73.0

Q0

c

8.2

70.0

Alternative Batteries Compatible On The List As Below. Use of Another
Battery May Present A Risk of Fire Or Explosion.
● Avertissement: Remplacez uniquement la batterie par BR2032 de PANASONIC,ou par une batterie compatible de la liste ci-dessous. L'utilisation d'une
autre piles peut présenter un risque de feu ou d'explosion.

I13
I14

Source input
wiring

AWG24

UL1007/ UL2464

70.0[ FC6A-D32K3CEE, -D32K4CEE, -D32P3CEE, -D32P4CEE ]TheSide ofthe Battery Holder

+

AWG18

● Warning: Replace Only The Battery With Panasonic BR2032, Or The

13
11

Applied cable

All dimensions in mm.

90.0

Battery Holdera1. Grasp the battery holder and remove it from the module.* (a)2. Remove the old back up battery from the battery holder (c)by pulling the outside hook. (b)3. Install a new back up battery in the battery holder.
Push the battery in until the outsite hook (b) clicks.
4. Insert the battery holder into the module. (a)* The length of the battery holder is 36 mm.

I3
I4

20.4 to 28.8V DC

AWG22

-

Type No.

73.0

12.6
[12.7]

Assembling Modules

14
12

NPN

-

+ 2-wire -Power supply Terminals :• FC6A-D*1*[ FC6A-D16R1CEE, -D16R4CEE, -D16K1CEE, -D16K4CEE, -D16P1CEE, -D16P4CEE ]+32-I/O Type

FC6A-D16R1CEE
FC6A-D16R4CEE
FC6A-D16K1CEE
FC6A-D16K4CEE

Relay
24VDC

4

I11
I12

The recommended ferrule is made by Phoenix Contact or Weidmüller. To crimp the ferrules shown
below, use a special crimping tool. (CRIMPFOX6 (1212034) or PZ 6 Rote L (1444050000))To the terminal block, use the recommended screwdriver made by Phoenix Contact or Weidmüller andtighten terminal screws tightening torque.

Dimensions
70.0

I10

17
15

Applicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening Torque10

DIN Rail

For UL/cUL, Horizontal mounting only.

8

INPUT

19

I1
I2

Applicable connector: FC4A-PMC20P (20-Pin MIL Connector)*See the user’s manual for more details on the wiring.

a: 40mm minimum
b: 20mm minimum

2-wiresensorOutput Typea-

* [ ] indicates the display of LED on FC6A
* FC6A-D*4* dose not have Power Supply Terminals Cover.

Direct Mounting Hook
(FC6A-PSP1PN05)

Power Supply Type

+

L
L
L
L
L
L
L
L

20.4 to 28.8V DC

I2

TYPE

20mm minimum

Unavailable
Available

Terminal No.

I0

18
16

Applicable connector: FC4A-PMC20P (20-Pin MIL Connector)
Output Terminals
FC6A-D32K3CEE, -D32K4CEE
FC6A-D32P3CEE, -D32P4CEE

b

I1

1

Plus CPU module20.4 to 28.8V DC

a

b

INPUT

20

Terminal No. OUTPUT Terminal No. OUTPUT

I0This symbol mark means that batteries and accumulators, at their end-of life,
should be disposed of separately from your household waste.
If a chemical symbol is printed beneath the symbol shown above,this chemical
symbol means that the battery or accumulator contains a heavy metal at a certain
concentration. This will be indicated as follows:
Hg : Mercury (0.0005%) Cd : Cadmium (0.002%) Pb : Lead (0.004%)
In the European Union there are separate collection systems for used batteries andaccumulators.
Please dispose of batteries and accumulators correctly in accordance with each country or local regulation.

PNP

Horizontal mounting

Operating
Surrounding Air
Temperature
35°C
maximum

Terminal No.

sensorSink input
wiringQ2 Q1

in places where it is subjected to high-temperature, high-humidity, condensation, corrosive gases,
excessive vibrations, or excessive shocks itwill result in electrical shocks, fire hazard, or malfunction.
● The environment rating for using the MICROSmart is “Pollution degree 2.”● Prevent metal fragments and pieces of wire from dropping inside the MICROSmart housing. Ingressof such fragments and chips may cause fire hazard, damage, or malfunction.
● Use wires of a proper size to meet voltage and current requirements. Tighten terminal screws to theproper tightening torque.
(Power supply Terminals: 0.51 N-m, Input Terminals and Output Terminals: 0.28 N-m)
● Use an IEC60127-approved fuse on the power line and output circuit to meet voltage and current
requirements.(Recommended fuse: Littelfuse 5×20mm slow-blow type 218000 series/Type T)
This is required when exporting equipment containing MICROSmart to Europe.
● Use an EU-approved circuit breaker. This is required when exporting equipment containing
MICROSmart to Europe.
● If relays or transistors in the MICROSmart output modules should fail, outputs may remain on or off.
For output signals which may cause heavy accidents, provide a monitor circuit outside of the MICROSmart.
● Do not disassemble, repair, or modify MICROSmart modules.

DIN Rail

Available

Relay Output

equipment.

● Install the MICROSmart in environments as described in the user's manual. If the MICROSmart is used

(19)

40mm
minimum

Q5 Q4 NC COM0 Q3● The MICROSmart is designed for installation in equipment. Do not install the MICROSmart outside of(18)*(15) Analog Port Cover(16) Ethernet Port 1 Cover(17) Ethernet Port 2 Cover(18) Power Supply Terminals
Cover(19) USB Port Cover(20) SD Memory Card Cover(21) Communication Connector
Protection Sticker(22) Expansion Connector
Protection Sticker

40mm
minimum- 2-wire +sensor-COM1 Q7 Q6

inspection on the MICROSmart. Failure to turn off the power may cause damage, electrical shocks orfire hazard.
● Emergency stop and interlocking circuits must be configured outside the MICROSmart. If such a circuit
is configured inside the MICROSmart, failure of the MICROSmart may cause disorder of the control
system, damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND D HAZARDOUS
LOCATIONS, OR NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereuses de classe 1,
groupes A,B,C et D; ou dans des zones non dangereuses.
● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT EQUIPMENT WHILE THE CIRCUITIS LIVE OR UNLESS THE AREA IS KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.
● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant que le circuit est sous tension,ou à moins ďêtre certain que lieu ďutilisation soit exempt de concentrations inflammables.
● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE INSTALLED IN AN ENCLOSURESUITABLE FOR THE ENVIRONMENT THAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOLOR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté à ľenvironnement ďutilisation etuniquement accessible avec un outil ďouverture ou une clé.
● WARNING - EXPLOSION HAZARD - THE USB PORT IS NOT FOR USE IN HAZARDOUS
LOCATIONS.
● Avertissement: risque d'explosion. Le port USB ne doivent pas être utilisés dans des emplacements
dangereux.

Right Side(4) Ethernet Port 2
ACT LEDLINK LED(5) Power Supply Terminals(6) USB Port
(7) Input Terminals(8) Output Terminals(9) LEDs
Input LEDs [IN]Output LEDs [OUT]
Power LED [PWR]
Run LED [RUN]
Error LED [ERR]
SD Memory Card Status
LED [SD]
Battery Status LED [BAT]
Status LED [STAT](10) Function Switch(11) SD Memory Card Slot(12) Battery Holder(13) Communication Connector(14) Expansion Connector+ 2-wire -

+

90.0

This sheet provides brief operating instructions of the MICROSmart programmable controller.
For details, see the FC6A Series MICROSmart User’s Manual.

[ FC6A-D16*1CEE ] (12)Input Terminals

20mm minimum

Operating
Surrounding Air
Temperature
55°C
maximum

13.3[12.4]

FC6A Series
Plus CPU module[ FC6A-D32K3CEE, -D32K4CEE, -D32P3CEE, -D32P4CEE ]Mount the FC6A MICROSmart as follows. To provide ample ventilation, ensure that there is sufficientspace between the FC6A MICROSmart and other devices, heat sources, and panel surfaces.

90.0

INSTRUCTION SHEET

Installation in Control Panel & Mounting Direction

7

Specification

Operating Temperature: -10 to +55°C(no freezing)
Expanded Operating Temperature: -25 to -10°C, +55 to 65°C (no freezing)* See the user's manual for details on use in Expanded Operating Temperatures.
Storage Temperature: -25 to +70°C (no freezing)
Relative/Storage Humidity: 10 to 95%RH (no condensation)
Altitude to Air Pressure: 1,013 to 795hPa (0 to 2,000 m) during operation,
1,013 to 701hPa (0 to 3,000 m) during transport,
Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,
acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,
Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes, 6 directions, 3 times each
Installation Location : Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C / 65°C
Temperature Code: T4* See the user's manual for more details on the product specifications.

13.3[12.4]

B-1994 (4)AWG20

Recommended ferrule
AI 0,25-8 (3203037), Al 0,25-10 (3241128), H 0,25/12T GE (9021020000)
AI 0,34-8 (3203066), Al 0,34-10 (3241129), H 0,34/12 TK (9025770000)
AI 0,5-8 (3200014), AI 0,5-10 (3201275), Al-TWIN2×0,5-10 (3203309),
H 0,5/16D W (9019020000), H 0,5/16D ZH W (9037390000)
AI 0,5-8 GB (1208966), Al 0,5-10 GB (3203150)
H 0,5/14D W (9019010000), H 0,5/16 DS W (9202910000)
Screwdriver

SZS 0,4×2,5 (1205037) , SDS 0,4×2,5×75 (9009030000)

Tighten torque0.28 N-m( ) indicates the Type No. of PHOENIX CONTACT GmbH & Co. KG and Weidmüller Interface GmbH & Co. KG.

L

11Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.

L
L
L

MICROSmart User’s manual can be downloaded from http://www.idec.com/FC6Amanuals

L

20.4 to28.8V DC+ -http://www.idec.com

2020.02