B-1044(2)(4)Meter(EU2B-YM)

1 Type Numbers
ȷPushbutton switch and Emergency stop switch EU2B-YB111FB
Operator (style / function)
Button color
B1 : Flush pushbutton
R : Red G : Green B : Black
Contact arrengement/ Momentary
Y : Yellow W : White S : Blue
10 : 1NO 01 : 1NC
B2 : Extended pushbutton
20 : 2NO 02 : 2NC
Button color ofTerminal shape/ Momentary
11 : 1NO1NC 30 : 3NO
emergency stop
C : Standard screw terminal
B3 : Mushroom pushbutton
03 : 3NC 21 : 2NO1NC
switch are limited "R".
F : IP20 screw terminal/ Momentary
12 : 1NO2NC
BV3: Mushroom
Contact arrengement of emergency stop switch are limited "01","02","11","03","12".
/ Emergency stop

Lens unit (style ) L1:Pilot light
Operating voltage
66 : AC/DC 6V (Full voltage type)
11 : AC/DC 6V (Full voltage type)
22 : AC/DC 24V (Full voltage type)
16 : AC 100/110V (Transformer type)
116 : AC 115V (Transformer type)
126 : AC 120V (Transformer type)
26 : AC 200/220V (Transformer type)
386 : AC 380V (Transformer type)EU2B-YL22FDR
Lamp color
R : Red
G : Green A : Amber
Y : Yellow W : White S : BluePW : Pure White
Terminal shape
C : Standard screw terminal
F : IP20 screw terminal
236 : AC 230V (Transformer type)
46 : AC 400/440V (Transformer type)

246 : AC 240V (Transformer type)
486 : AC 480V (Transformer type)ᲧNotes for OperationᲧ
ȷContact bouncing
When the control unit is operating, the contacts will bounce. When designing a control circuit,take the contact bounce time into consideration (reference value: 20 ms).
(3) Pilot Light (Type EU2B-YL)
500 V
AC/DC 6, 12, 24V (Full voltage type)AC 100/110, 115, 120, 200/220, 230, 240, 380,
400/440, 480V (Transformer type)
Impulse Withstand Voltage (Uimp) 4kV
100 M minimum (500V DC megger)
Insulation Resistance
LED lamp (Type LSTD by IDEC)Light source
Amber, Blue, Green, Pure White, Red, White, Yellow
Colors50/60 Hz
Frequency (AC)Rated Power Consumption (approx.) 0.3W (Full voltage type), 1.5VA (Transformer type)
life (reference value)
Applox 40,000 hours
Weight (approx.)
108g (Full voltage type), 150g (Transformer type)
Rated insulation voltage (Ui)Rated Operating Voltage (Ue)

ᲧNotes for OperationᲧ
ȷThe LED built-in lamp is super bright type. Note that the LED lamp may turn on even when the
power is turned off because of induction.
ȷIDEC does not guarantee exchange of an LED lamp, because it will affect explosion protection
characteristics. Call IDEC when you need to replace LED lamps.

35.0<EU2B-YSK>

1.0 to 4.5(Panel thickness)

20.3

4

67.7

62.1
60.1
(IP20 screw terminal) (Standard screw terminal)

33.5(2) Parts Description
Pilot LightᲦEU2B-YL

Pushbutton switch and Emergency stop switch, EU2B-YB/ YBVSelecter switch and Key selector switch, EU2B-YS/ YSKContact block,Type EU2B-N

Contact unit,
Contact unit consistsof a contact block
adapter and contact
blocks.
Operator
Pushbutton switch andEmergency stop switch,Type EU2B-UB/ UBVSelector switch and Key selector switch,Type EU2B-US/ USK(Spade terminal)

Contact block
adapterᲦ
Type EU2B-J

Lamp unit
Type EU2B-XL
is available in Fullvoltage type andTransformer type.
Pilot light Lens unit,
Type EU2B-UL

3.4
maximumĬLift

EU2B-YL
ĭ
Turn

ĭ
Turn

locking lever

5.5
minimum

5.5
minimum(Ferrule)
࣭Without
insulating sheath

8.0

maximum

࣭Insulating sheath

Insulating
sheathWire

8.0

maximum(*1) Dimension after clamping
Meter,
Type EU2B-YM(3) Panel thickness/ Mounting hole layoutĬ
Lift(Ring terminal)

Meter, EU2B-YM

1) Panel thickness: 1.0 to 4.5 mm
Mounting hole layout: See the right figures.
(*)The meter can be mounted on the top mounting holes of the standard 50mm mounting
centers. The meter can be mounted on any mounting hole with the 70mm or larger
mounting center.
2)Panel mounting
+0.2
4.8 0
70 minimum
To remove the contact unit (for pilot
lights, remove the lamp unit) from theoperator (or lens unit). To remove thelocking ring from the operator. To insert
the operator into the panel cut-out fromthe front, tighten the locking ring fromthe back, then install the contact unit tothe operator.
<Removing the contact unit and lamp unit>
To remove the contact unit or the lamp unit from the operator, pull the protruding part of thelocking lever outwards as shown in the diagram (using a screwdriver etc.) and turn it to the left.
The contact unit or lamp unit can be pulled out.
EU2B-YB/ YBV
EU2B-YS/ YSKWiring(1) Applicable wires
Stranded wire: 1.25 to 2.5 mm2, solid wire: φ1.2 to φ1.6 mm (AWG16 to 14)(Note) Do not connect more than 2 wires to the same terminal.
(2) Applicable crimping terminal(Note) Do not use ring terminals for EU2B control units with IP20 protection.
(Note) When connecting 2 ferrules to the EU2B control unit, use ferrules without insulating
sheath.
(*1)‫ڧ‬1.8 maximum

1.0 to 4.5(Panel thickness)(*1)‫ڧ‬1.8 maximum

13.3

um

27.3

<EU2B-YM>

ini
m

67.7

<Removing the Contact block>To remove the contact block, insert a flat screwdriver under the latch of the contact block
adapter and disengage the latch. (See the figure below)
Note: When reinstalling the contact block after maintenance or wiring,
make sure that the contact configuration is correct. Installing thecontact block in the incorrect position or incomplete installation may
cause malfunction of the switch.
<Installing the Contact block>
Before installing the contact block, remove the contact block adapter
from the operator, and install the contact block on the contact block
adapter definitely.
Note: Do not install the contact block with the control block adapter
attached to the operator. Otherwise, malfunction may result.

m

13.3

<EU2B-YL>.5+0 0

ȷPilot Light

50 m maximum (initial value)
6kV
100 M minimum (500V DC megger)
Pushbutton swtich Ჴ1,000,000 operations minimum
Selecter switch
Ჴ500,000 operations minimum
Key selecter switch Ჴ500,000 operations minimum
Emergency stop switch Ჴ50,000 operations minimum
Pushbutton swtich Ჴ250,000 operations minimum Operating Frequency : 1,800 operations/hour
Selecter switch
Ჴ250,000 operations minimum Operating Frequency : 900 operations/hour)
Key selecter switch Ჴ250,000 operations minimum Operating Frequency : 900 operations/hour
Emergency stop switch Ჴ50,000 operations minimum Operating Frequency : 900 operations/hour)
3 contacts maximum.
250V/10A fuse (Type aM IEC60269-1/IEC6026-9-2
1000A
Emergency stop switch: 60 N
Emergency stop switch: 7.0 mm
Emergency stop switch: 9.0 mm
EU2B-YB111C : 92g, EU2B-YS211C : 98g
EU2B-YSK211C : 120g, EU2B-YBV302C : 120g

24.5

<EU2B-YS>

32.5

500V
2.8A
1.4A
-

19.3

.5
30


ȷSelector switch and Key selector switch
EU2B-YS311N1F ‫ڧ‬Operator (style )‫ڧ‬: May be followed by key removal
S : Selector (Knob operator)
position code and/or different key
SK : Key selector (Key operator)
number code for key selector
switch. (Refer to the catalog)
Position / function
2 : 2-position / Maintained
Terminal shape
2R : 2-position / Maintained (Overlap)
C : Standard screw terminal
2J : 2-position / Maintained (Special function)
F : IP20 screw terminal
21 : 2-position / Spring return from right
Circuit code Blank:None
3 : 3-position / Maintained
N1:Separate designation
Contact arrengement
31 : 3-position / Spring return from rightetc. Refer to the catalog
10
:
1NO
11
:
1NO1NC
32 : 3-position / Spring return from left
01 : 1NC 30 : 3NO
33 : 3-position / Spring return two-way
20 : 2NO 03 : 3NC
02 : 2NC 21 : 2NO1NC 12 : 1NO2NC

Contact block
Short-circuit Protective Device
Conditional Short-circuit Current
Minimum Direct Opening Force
Minimum Direct Opening Travel
Maximum Travel
Weight (approx.)

1.0 to 4.5(Panel thickness)

32.2

6

Electrical Life<EU2B-YB2> <EU2B-YB3> <EU2B-YBV3>

ȭ3.

Contact resistance
Impulse Withstand Voltage (Uimp)
Insulation ResistanceMechanical Life

Arrangement and Mounting<Installing the contact unit and lamp unit>
To install the contact unit, place theTOP marking on the operator and the TOP marking on thecontact block adapter in the same direction,and then attach the contact unit to EU2B-YB
EU2B-YL
the operator. Then turn the locking EU2B-YS
lever to the right. Follow the same
TOP marking
TOP marking
procedure when installing the lamp
unit.
Ĭ
Ĭ
Note: When installing the lamp unit,
check that the inner lens is not loose.
ĭĭ
Note: The contact block adapters forTOPemergency stop switches cannot be
inneer lens
used for pushbutton, selector andkey selector switches.

6.9 maximum(2) Pushbutton swtich, Selecter switch, Key selecter switch and Emergency stop switch(Type EU2B-YB/ EU2B-YS/ EU2B-YSK/ EU2B-YBVȷContact Rating
Rated Insulation Voltage (Ui)600V
Thermal Current (Ith)
10A
24V
120V
240V
Rated Operating VoltageᲢUeᲣResistive load AC12 10A(*) 10A(*)
6A
Rated Operating CurrentᲢIeᲣ AC
6A
3A
50/60Hz Inductive load (AC15 10A(*)
Resistive load (DC12)
8A
2.2A
1.1A
DC
Inductive load (DC13
4A
1.1A
0.55A
(*)10A (< 2 contact blocks by one control unit), 9A (= 3 contact blocks by one control unit)
Minimum switching capacity : 5 mA at 3V AC/DC(applicable range may vary with operating conditions and load types)
ȷSpecifications

3(1) Dimension<EU2B-YB1>

ȭ 28


Explosion protectionųGroup and category
II2GD
Type of Explosion protection Ex de IIC, Ex tD A21 IP65ų
Ex de IIC Gb, Ex tb IIIC Db IP65(Meter)
Test certificated
PTB 08 ATEX 1053 U / PTB 08 ATEX 1003 U / PTB**ATEX****U
Degree of protection (IEC/EN 60529)
ųFrom panel front
IP65
Terminal
IP20 (EU2B-Y***F), None (EU2B-Y***C)Standard operating environmentųAmbient temperature-20 to +50é (no freezing)ųRelative humidity
45 to 85%RH (no condensation)ųAltitude2,000m maximumųPollution degree3
Shock resistance
100 m/s2, Emergency stop switch: 150 m/s2
Operating extremes(Without Meter)
1,000 m/s2
Damage limits
5 to 55 Hz, amplitude 0.5 mm
Operating extremes
Vibration resistance
Emergency stop switch:
5 to 500 Hz, amplitude 0.35 mm, acceleration 50 m/s2
(Without Meter)
30 Hz, amplitude 1.5 mm
Damage limits
Emergency stop switch:
5 to 500 Hz, amplitude 0.35 mm, acceleration 50 m/s2

Note: When the contact unit is removed from theemergency stop switch operator, the NO contact closes
and the NC contact opens. Do not turn the locking
lever when the contact unit is removed from thelocking lever
operator (the red indicator is protruding out. See theindicator (red)figure on the right). Otherwise, the switch may bedamaged.
<Panel mounting for the operator, lens unit and meter>
To remove the locking ring from the operator and check that the rubber gasket is in place. To
insert the operator from panel front into the panel hole. To place the projection on the operator
with TOP marking and the recess on the mounting panel in the same direction. ( The meter has
no projection.)
TOP marking Projection
And tighten the locking ring using ring wrench
Nameplate or
Padlocking cover
XN9Z-T1 to a torque of 2.5 N᳽m. When using a
Recess on the panel
nameplate or padlocking cover, install it between
the operator and panel. Make sure that the grooveof the namplate or padlocking cover, and the
Rubberprojection on the TOP marking of the operator is gasket
Locking ringin the same direction.
Recess on the
Note: The locking ring for emergency stop
Nameplate
switches and meter is metallic. The meter can’tNameplatemount the nameplate or podlocking cover.
gasket

6.9 maximum
3.6 minimum(General requirements)Ū The EU2B control units are exclusively designed for the EC2B flameproof and increased
safety control box. When using the EU2B control units for other purposes, make sure that the operating conditions are appropriate.
Ū When using the emergency stop switch for safety-related equipment in a control system, tomake sure of correct operation, refer to the safety standards and regulations in each country
and region depending on the application purpose of the actual machines and installations.
Before using the emergency stop switch, perform risk assessment to make sure of safety.
(Opening the shipping carton)Ū Check that the product is what you have ordered. Using an incorrect model might result in
malfunction or accident.
(Installation)
Ū Read this instruction manual to make sure of correct installation of the EU2B control units.
Install the EU2B control units without getting in the substances such as dust, concrete powder,or metal powder, otherwise contact failure or insulation failure may result.
（Operation)
Ū Stop operation immediately if abnormal operation occurs. Otherwise, a secondary accident
may occur.
（Maintenance and inspection)Ū The surface temperature of the EU2B control units may become extremely high during
operation. Before maintenance or inspection of the EU2B control units, be sure to wear
gloves to prevent burn on your hand.

IEC/EN 60079-0, IEC/EN 60079-1, IEC/EN 60079-7
IEC/EN 61241-0, IEC/EN 61241-1, IEC/EN 60079-31
IEC/EN 60947-1, IEC/EN 60947-5-1
IEC/EN 60947-5-5 (Emergency stop switch)
IEC/EN 60051-1, IEC/EN 60051-2, IEC/EN 60051-9(Meter）

ȭ40

Applicable Standards(General requirements)‫ە‬
Use the EU2B control units that are applicable for use in hazardous areas, otherwise
explosion or fire hazard may result. (Hazardous area: potentially explosive atmosphere
where explosive gas or vapor may exist) Because the EU2B control unit is a Ex component, itcannot be be used as an explosion-proof equipment on its own. To use the EU2B control
units in Japan, it should be certifified by TIIS (Technology Institution of Industrial Safety) as a
 finished product.
‫ ە‬EU2B control units can be installed only in zones 1 and 2. Do not use in zone 0.
‫ ە‬Turn power off to the EU2B control units before installation, removal, wiring, maintenance, orinspection, otherwise explosion, fire hazard, or electric shock may result.
‫ ە‬Special expertise is required to install, wire, operate, maintain, and inspect the EU2B control
 units. People without such expertise must not use the EU2B control units, otherwise damage
 or accident may result.
‫ ە‬Do not disassemble, repair, or modify the EU2B control units, otherwise damage or accident
may result.
‫ ە‬Do not use a damaged the EU2B control units, otherwise damage or accident may result.
(Wiring and operation)‫ ە‬When connecting with external devices, make sure that each cable is connected to thecorrect terminal, otherwise electric shock, fire hazard, or explosion may result.
‫ ە‬Use wires of a proper size to meet voltage and current requirements. Tighten the M3.5
terminal screws to a tightening torque of 1.0 to 1.3 N᳽m. Incorrect wiring may cause
 abnormal temperature rise and lead to fire hazard and explosion.
‫ ە‬Operate the EU2B control units under the rated current and voltage specified in this
instruction manual, otherwise short-circuiting, fire hazard, or explosion may result.
(Maintenance and inspection)‫ ە‬When measuring the insulation resistance of the control units, make sure that potentiallyexplosive atmosphere of explosive gas or vapor does not exist in the vicinity, otherwise
explosion or fire hazard may result. Do not touch the terminal carelessly. Otherwise, electric
shock may result.

50 minimum(*)

Product Specifications

33 +0.5
02(1) General Specifications

ȭ40

Caution notices are used where inattention might cause personal injury or damage to equipment.

ȷDC ammeter or voltmeter
EU2B-YM010VDF-PER-R
Function M : Meter
Set pointerInput voltage or current
blank : non -R : with set pointer010 : 0-10V
Type of meter
Specification of scale
001 : 0-1mA
VD : DC voltmeter-PER : 0~100%
Terminal shape
420 : 4-20mA
MD : DC ammeter-60HZ : 0~60Hz
C : Standerd screw terminal
etc.
-80HZ : 0~80Hz etc.
F : IP20 screw terminal

8

Warning notices are used to emphasize that improper operation may cause severe personal
injury or death.

30 : 30A 50 : 50A
150 : 150A etc.

ȭ 64

In this operation instruction manual, safety precautions are categorized in order of importance toWarning and Caution:

20 : 20A
100 : 100A

ȭ24

S afety P recau ti o n s

39

EU2B Flameproof and Increased Safety Control Units
Confirm that the delivered product is what you have ordered. Read this instruction manual to make sure ofcorrect operation. Make sure that the instruction manual is kept by the end user.

-R : with set pointerTerminal shape
C : Standard screw terminal
F : IP20 screw terminal

33

Specification of overload scale
3 : 3 times 2 : 2 times 5 : 5 times N : Non
Type of meter A : AC ammeter
Measuring range: 1 : 1A5 : 5A
Direct measuring
For current transformers : 10 : 10A 15 : 15A
60 : 60A 75 : 75A

Accuracy Class
2.5
100MΩ minimum(500V DC megger)
Insulation Resistance
Rated Insulation Voltage(Ui)300V
Principle of action
Moving-iron instrument
4kV
AC ammeter Impulse Withstand Voltage(Uimp)
Power Consumption
1VA
5A, 10A, 30A, 50A etc.
Specification of Measuring Range
1A, 5ASpecification of Input Current
3 times etc.
Specification of Overload Scale
Rated Insulation Voltage(Ui)150V
Principle of action
Permanent-magnet moving -coil instrument
Impulse Withstand Voltage(Uimp)
2.5kV
DC ammeter
0 to 1mA DC, 4 to 20mA DC etc.
Specification DC ammeter
DC voltmeterof Input DC voltmeter
0 to 10V DC etc.
Power Consumption
0.15W max.
270g
Weight(approx.)
㸫Notes for Operation㸫
ȷFor AC ammeter of measuring range of 10A or avobe, use a current transformer
screwdrivercommercially available. Installthe current transformer in the non-hazardous area.
ȷTerminal polarity of meter.
Note that the upper terminal is positive (No.1) and the lower terminal is negative(No.2) when installed on the control box.
ȷZero-setting the pointer and setting the set pointer
Using a flat screwdriver with the tip of 0.8t×5w or smaller, adjust the pointershaft for zeroand the set pointer by turning the shafts as shown at the right. Do not apply
setting the pointerexcessive force on the shaft, otherwise the shaft will be damaged.
shaft forsetting
the set pointerȷDC voltmeter and DC ammeter do not require zero adjustment.

48

INSTRUCTION MANUAL

Set pointerblank : non

1 : 1A 5 :5A

32
ȭ38

Input current

62

Function M : Meterȭ40

EU2B-YM53A10F-R

ȭ40

ȷAC ammeterĮ
Pulllocking lever࣭Recommended crimping terminal (WAGO)
Ferrule with insulating sheath: 216-204,
Ferrule without insulating sheath: 216-104, Crimping plier: 206-204(3) Recommended tightening torqueEU2B control units (M3.5) : 1.0 to 1.3Nm

Incorrect wiring may cause fire hazard. Observe the following conditions.
࣭Be sure to install an insulating tube on the crimping
Insulating tube (covered)terminal or the crimping terminal with insulation.
࣭When connecting solid wires or stranded wires directly,
strip the insulation as mentioned below and insert the wire
Wire
all the way in.
5.5 to 6.0
EU2B Control units: 8.6 mm maximum
࣭When using stranded wires, make sure that there are no wire whiskers.
࣭Make sure that the spade and ferrules are inserted all the way in.

5

Commissioning

Before commissioning, ensure that:ȷwires are correctly connected,
ȷthe EU2B control unit is installed been fitted in accordance with this instruction manual,ȷthe EU2B control unit is not damaged.

TOP

Į
Pull

Draw. No. B-1044C
Feb. 3, 2012

6

Maintenance and Inspection(1) Notes for inspecting the EU2B control units
1) Observe the laws and regulations set by each country.
2) Never disassemble the control units.
3) Do not use tools that cause impact sparks during maintenance and inspection.
4) When using measuring devices, use explosion-protected types.
5) Do not carry out under the explosion-hazardous environment.
(2) Maintenance and inspection
Perform daily or periodical maintenance and inspection for items listed in the below table.
Table. Maintenance and Inspection Example
Actions
Inspection Inspection Inspections
methodItems
ȷExchangeȷNo damages
VisualUnit
ȷCleaningȷNo rustingȷNo loosening of the locking ring ȷTighteningȷReplacement
ȷNo cracks
Packings VisualȷNo apparent deformation
ȷTighteningȷNo loosening of screws
Terminal Visual
TactileȷNo dirt on the insulation materials ȷCleaning

7

Accessories and spare parts

1) Color buttons for Pushbutton switchᲴųųųFlush/ HW1A-B1š, Extended/ HW1A-B2š, Mushroom/ HW1A-B4š
Note: Specify a color code in place of š.
( R: red, G: green, B: black, Y: yellow, W: white, S: blue )2) Color lens for Pilot light: EU9Z-Lš (Install tool TW-KC1)
Note: Specify a color code in place of š.
( R: red, G: green, A: amber, Y: yellow, W: white, S: blue )Note: Use a white (W) color lens for pure white illumination.
3) Nameplate: EU9Z-NMš
Code( š
LegendMarking plate for0(blank)nameplate: EU9Z-NPš
1
ON
2
OFF
3
START
4
STOP
31
OFF-ON35
HAND-AUTO
53
HAND-OFF-AUTO

ȭ38

ȭ40

ȷInstalling the marking plate to a nameplate
Marking plate(See fig. 1)
for nameplate
ȷRemoving the marking plate from a nameplate ղNameplate(See fig. 2)
Flat screwdriver
To remove the marking plate, insert a flatscrewdriver between the marking plate andMarking plate
nameplate.
ձ
for nameplateȷWhen using a nameplate, the mounting panel
thickness is decreased by 1.5 mm. 1.0 to 3.0
Nameplatemm4) Nameplate sticker for Emergency stop switch:
EU9Z-NVS27(Fig. 1)
(Fig. 2)
Legend "EMERGENCY STOP"
13.3
23.2
5) Padlocking cover:for Emergency stop switch/ EU9Z-PCE
for Pushbutton switch (Flush, Extended) andKey selector switch/ EU9Z-PC
ȷWhen using a padlocking cover, the mounting
1.0 to 10.5 (Panel thickness)
panel thickness is decresed by 1.5 mm. (1.0 to
3.0 mm)6) Mounting hole plug: EU9Z-BP (See the right figures)(Note) Only use accessories and spare parts specified by IDEC. Use of any other accessories
and spare parts will void the warranty.

8

DisposalObserve the laws and regulations set by each country concerning refuse disposal.
Specifications and other descriptions in this manual are subject to change without notice.

Draw. No. B-1044C
Feb. 3, 2012

6-64 Nishimiyahara 2-chome, Yodogawa-ku, Osaka, 532-0004, Japan
http://www.idec.com
B-1044-1(2)(3) Voyant lumineux (Type EU2B-YL)
Tension nominale d’isolement (Ui) 500 V
C.A./C.C. 6, 12, 24V (Type pleine tension)
Tension nominale deC.A. 100/110, 115, 120, 200/220, 230, 240, 380,
fonctionnement (Ue)400/440, 480V (Type transformateur)Tension de tenue aux chocs (Uimp) 4kV
100 M minimum (mégohmmètre500V C.C.)
Résistance d’isolement
Lampe à DEL (Type LSTD par IDEC)
Source de lumière
Ambre, bleu, vert, blanc pur, rouge, blanc, jaune
Couleurs
50/60 Hz
Fréquence (C.A.)
0.3W (Type pleine tension), 1.5VA (Type transformateur)
Consommation nominale (approx.)Durée de service (valeur de référence) Environ 40,000 heures
108g (Type pleine tension), 150g (Type transformateur)
Poids (approx.)ᲧRemarques sur le fonctionnementᲧȷLa lampe à DEL intégrée est de type très lumineuse. Noter que la lampe à DEL peut s’allumermême lorsque l’alimentation est coupée, en raison de l’induction.
ȷIDEC ne garantit pas le remplacement des lampes à DEL, car cela affecterait les caractéristiquesde protection contre l’explosion. Pour faire remplacer les lampes à DEL, contacter IDEC.

Remarque: Lorsque l’unité de contact est retirée del’opérateur d’interrupteur d’arrêt d’urgence, le contact
NO se ferme et le contact NC s’ouvre. Ne pas tourner
le Témoin de levier de verrouillage (rouge) levier deverrouillage pendant que l’unité de contact est retirée
Témoin de levier
de l’opérateur (le témoin rouge dépasse). Voir la figure
de verrouillage
ci-contre à droite). Sinon, l’interrupteur risque d’être(rouge)endommagé.
<Montage du panneau pour l’opérateur, la lentille et l’appareil de mesure>
Retirer la bague de verrouillage de l’opérateur et vérifier si le joint en caoutchouc est en place.
Insérer l’opérateur dans le trou du panneau par l’avant du panneau. Aligner dans le même sensla partie saillante de l’opérateur indiquée par la marque TOP et la cavité du panneau demontage. (L’appareil de mesure n’a pas de partie saillante.)
Serrer ensuite la bague de verrouillage au moyen d’une clé polygonale XN9Z-T1, avec un couple
de serrage de 2,5 N･m. Lors de l’utilisation
Partied’uneplaquesignalétiqueoud’un Marque TOP
Plaque signalétique ou
saillante
Couvercle-cadenas
couvercle-cadenas, l’installer entre l’opérateuret le panneau. S’assurer que la rainure de laCavité du panneau
plaque signalétique ou du couvercle-cadenas
est dans le même sens que la partie saillante Joint en
Bague
sur la marque TOP de l’opérateur.
caoutchoucde verrouillage
Remarque: La bague de verrouillage desCavité
delainterrupteurs d’arrêt d’urgence et de l’appareil
plaquede mesure est métallique. Il n’est pas possible signalétiquede monter la plaque signalétique ou leJoint de plaquecouvercle-cadenas sur l’appareil de mesure.
signalétique<Installation de l’unité de contact et de la lampe>
Pour installer l’unité de contact, aligner dans le même sens la marque TOP de l’opérateur et lamarque TOP de l’adaptateur de bloc à contacts, puis fixer l’unité de contact à l’opérateur.
Tourner ensuite le levier de verrouillage vers la droite. Suivre la même procédure pour installer lalampe.
EU2B-YL
EU2B-YB

ȭ40
35.0<EU2B-YSK><Retrait du bloc à contacts>
Pour retirer le bloc à contacts, insérer un tournevis plat sous le cliquet de l’adaptateur de bloc à
contacts, et désengager le cliquet. (Voir la figure ci-dessous.)
Remarque: Lors de la réinstallation du bloc à contacts après la maintenance ou le câblage,s’assurer que la configuration du contact est adéquate. L’interrupteur
risque de mal fonctionner si le bloc à contacts n’est pas installé dansla bonne position ou si l’installation est incomplète.
< Installation du bloc à contacts >Avant d’installer le bloc à contacts, retirer de l’opérateur l’adaptateurde bloc à contacts, et bien installer le bloc à contacts sur l’adaptateurde bloc à contacts.
Remarque: Ne pas installer le bloc à contacts alors que l’adaptateurde bloc à contacts est fixé à l’opérateur. Sinon, il y a risque dedysfonctionnement.

1.0 to 4.5(Épaisseur du panneau)

20.3

67.7

33.5

62.1
(Borne à vis IP20)

60.1(Borne à vis standard)(2) Description des pièces
Voyant lumineuxᲦEU2B-YL

Interrupteur à bouton-poussoir et interrupteur d’arrêt d’urgence,
EU2B-YB/ YBV Sélecteur et sélecteur à clé, EU2B-YS/ YSKBloc à contacts,
Type EU2B-N(Cosse ouverte)

Lentille de voyant lumineux,
Type EU2B-UL

OpérateurInterrupteur à bouton-poussoir etinterrupteur d’arrêt d’urgence,
Type EU2B-UB/ UBVSélecteur et sélecteur à clé,Type EU2B-US/ USKAppareil de mesure, EU2B-YM

Appareil de mesure,Type EU2B-YM

3.4
maximum(3) Épaisseur du panneau / Disposition des trous de montage
1) Épaisseur du panneau: 1,0 à 4,5 mm
Disposition des trous de montage: Voir les illustrations ci-contre à droite.
(*)L’appareil de mesure peut être monté par-dessus les trous de montage des centres demontage 50 mm standards. L’appareil peut être monté sur tout trou de montage dont le centre
de montage est de 70 mm ou plus.
2)Montage du panneau
+0.2
4.8 0
Retirer l’unité de contact (pour les
70 minimum
voyants lumineux, retirer la lampe) del’opérateur (ou de la lentille). Retirer labague de verrouillage de l’opérateur.
Insérer l’opérateur dans le panneau
découpé par l’avant, serrer la bague deverrouillage par l’arrière, puis installer
l’unité de contact sur l’opérateur.
<Retrait de l’unité de contact et de la lampe>
Pour retirer de l’opérateur l’unité de contact ou la lampe, tirer la partie saillante du levier deverrouillage vers l’extérieur, tel qu’illustré sur le schéma (au moyen d’un tournevis, etc.), et letourner vers la gauche.
L’unité de contact ou la lampe peut être retirée en tirant.
EU2B-YB/ YBV
EU2B-YS/ YSKĬEU2B-YLĬSouleverĭ
Tourner

Levier de verrouillage③(Tirer)Levier de verrouillage

TOP

Į
Tirer

(Cosse circulaire)

5.5
minimum

5.5
minimum(Virole)࣭Sansgaine isolante

8.0

maximum

࣭Gaine isolante

Gaineisolante
Fil

8.0maximum(*1) Dimensions après serrage࣭Borne de sertissage recommandée (WAGO)
Virole avec gaine isolante: 216-204,
Virole sans gaine isolante: 216-104, pince à sertir: 206-204(3) Couple de serrage recommandé
Blocs de commande EU2B (M3,5): 1,0 à 1,3 Nm

Un câblage inadéquat peut causer un incendie. Respecter les conditions suivantes.
࣭S’assurer d’installer un tube isolant sur la borne de sertissage, ou d’installer une borne desertissage isolée.
࣭Lors de la connexion directe de fils solides ou de fils multibrins, enlever l’isolation tel que
mentionné ci-dessous et insérer le fil à fond.
Insulating tube (covered)
Blocs de commande EU2B: 8,6 mm maximum
࣭Lors de l’utilisation de fils multibrins, s’assurer qu’il n’y apas de « filaments » (whiskers).
Wire
5.5 to 6.0
࣭S’assurer que la cosse et les viroles sont insérées à fond.

5

Souleverĭ
TournerCâblage

6.9 maximum
3.6 minimum

Unité de contact
L’unité de contact est
composée d’unadaptateur de blocs àcontacts et de blocs à contacts.

Adaptateur debloc à contacts, La lampe de typeEU2B-XL est disponible
Type EU2B-J
en type pleine tension
et en type transformateur.

4(1) Câbles utilisables
Fil multibrins: 1,25 à 2,5 mm2 ; fil plein: φ1,2 à φ1,6 mm (AWG 16 à 14)(Remarque) Ne pas connecter plus de 2 fils à la même borne.
(2) Borne de sertissage utilisable(Remarque) Ne pas utiliser de cosses circulaires pour blocs de commande EU2B avec protection IP20.
(Remarque) Lors de la connexion de 2 viroles sur le bloc de commande EU2B, utiliser des viroles sansgaine isolante.
(*1)‫ڧ‬1.8 maximum

1.0 to 4.5(Épaisseur du panneau)32.5(*1)‫ڧ‬1.8 maximum

13.3<EU2B-YM>

um

27.3

TOP

m

67.7

ĭ

lentille
intérieure

ini

13.3

<EU2B-YL>

Marque TOP
Ĭ

ĭ

m

24.5

<EU2B-YS>

6

19.3

Marque TOP
Ĭ

ȭ
3.

32.2

Remarque: Lors de l’installation de lalampe, s’assurer que la lentilleintérieure n’est pas mal fixée.
Remarque: Les adaptateurs de bloc
à contacts pour interrupteurs d’arrêt
d’urgence ne peuvent être utiliséspour les interrupteurs à bouton-poussoir,
les sélecteurs et les sélecteurs à clé.

6.9 maximum

1.0 to 4.5(Épaisseur du panneau)

ȭ40

EU2B-YS.5+0 0

ᲧRemarques sur le fonctionnementᲧȷRebondissement des contacts
Les contacts rebondissent pendant le fonctionnement du bloc de commande. Lors de laconception d’un circuit de commande, tenir compte du temps de rebondissement des contacts(valeur de référence: 20 ms).

<EU2B-YB2> <EU2B-YB3> <EU2B-YBV3>

ȭ 28(2) Interrupteur à bouton-poussoir, sélecteur, sélecteur à clé et interrupteur d’arrêt d’urgence(Type EU2B-YB/ EU2B-YS/ EU2B-YSK/ EU2B-YBVȷValeurs nominales de contact
Tension nominale d’isolement (Ui) 600V
10A
Courant thermique (Ith)
240V
120V
24V
500V
Tension nominale de fonctionnement Ue
Charge résistive C.A.12 10A(*) 10A(*)
6A
2.8A
C.A.
Courant nominal de
3A
6A
1.4A
50/60Hz Charge inductive (C.A.15 10A(*)
fonctionnement Ie
Charge résistive (C.C.12)
1.1A
2.2A
8A
C.C.
Charge inductive (C.C.13
0.55A
1.1A
4A
(*)10A (< 2 blocs à contacts par bloc de commande), 9A (= 3 blocs à contacts par bloc de commande)
Capacité minimale de permutation : 5 mA à 3V C.A./ C.C.
(la plage applicable peut varier suivant les conditions d’utilisation et les types de charge)
ȷSpécifications
Résistance de contact
50 m maximum (valeur initiale)
Tension de tenue aux chocs (Uimp) 6kV
Résistance d’isolement
100 M minimum (mégohmmètre 500V C.C.)
Durée mécaniqueInterrupteur à bouton-poussoir : 1,000,000 opérations minimum
Sélecteur: 500,000 opérations minimum
Sélecteur à clé: 500,000 opérations minimumInterrupteur d’arrêt d’urgence :50,000 opérations minimum
Durée électriqueInterrupteur à bouton-poussoir : 250,000 opérations minimum(Fréquence de fonctionnement: 1,800 opérations/heure)
Sélecteur: 250,000 opérations minimum(Fréquence de fonctionnement: 900 opérations/heure)
Sélecteur à clé: 250,000 operations minimum(Fréquence de fonctionnement: 900 opérations/heure)Interrupteur d’arrêt d’urgence :50,000 operations minimum(Fréquence de fonctionnement: 900 opérations/heure)
Bloc à contacts
3 contacts maximum.
Dispositif de protection de court-circuit Fusible 250V/10A fuse (Type aM IEC60269-1/IEC6026-9-2
Courant de court-circuit conditionnel 1000A
Force minimale d’ouverture directe Interrupteur d’arrêt d’urgence: 60 N
Course minimale d’ouverture directe Interrupteur d’arrêt d’urgence: 7.0 mm
Interrupteur d’arrêt d’urgence: 9.0 mm
Course maximale
EU2B-YB111C : 92g, EU2B-YS211C : 98g
Poids (approx.)
EU2B-YSK211C : 120g, EU2B-YBV302C : 120g

3 Arrangement et montage(1) Dimension<EU2B-YB1>

8

II2GD
ųGroupe et catégorieType de protection contre
Ex de IIC, Ex tD A21 IP65
l’explosionų
Ex de IIC Gb, Ex tb IIIC Db IP65(Appareil de mesure)
Certifié par essai
PTB 08 ATEX 1053 U / PTB 08 ATEX 1003 U / PTB**ATEX****U
Degré de protection (CEI/EN 60529)
ųDe l’avant du panneau
IP65
Borne
IP20 (EU2B-Y***F), Aucun (EU2B-Y***C)
Environnement d’exploitation standardųTempérature ambiante-20 à +50é (sans congélation)ųHumidité relative
HR 45 à 85%RH (sans condensation)ųAltitude2,000m maximumųDegré de pollution
3
Résistance au choc
100 m/s2, Interrupteur d’arrêt d’urgence:
Conditions extrêmes
d’exploitation
150 m/s2 (Sans appareil de mesure)
Limites de dommages 1,000 m/s2
5 à 55 Hz, amplitude 0.5 mm
Conditions extrêmes
Résistance à la vibration
Interrupteur d’arrêt d’urgence:d’exploitation
5 à 500 Hz, amplitude 0.35 mm, accélération 50 m/s2
(Sans appareil de mesure)
Limites de dommages 30 Hz, amplitude 1.5 mm
Interrupteur d’arrêt d’urgence:5 à 500 Hz, amplitude 0.35 mm, accélération 50 m/s2

.530

46 : C.A. 400/440 V (type transformateur) 486: C.A. 480 V (type transformateur)Protection contre l’explosion㸫Remarques sur le fonctionnement㸫ȷPour un ampèremètre C.A. dont la plage de mesure est de 10 A ou plus, utiliser un transformateur de courant
Tournevis
disponible dans le commerce. Installer le transformateur de courant dans une zone non dangereuse.
ȷPolarité des bornes de l’appareil de mesure.
Noter que la borne supérieure est positive (No 1) et que la borne inférieure est négative.(No 2) lorsqu’ellessont installées sur le boîtier de commande.
ȷMise à zéro de l’index et réglage de l’index de consigne
Au moyen d’un tournevis plat à pointe 0,8t × 5w ou plus petite, ajuster l’index
Arbre de mise à
et l’index de consigne en tournant les arbres tel qu’illustré ci-contre à droite. Ne pas appliquer une
zéro de l’index
force excessive sur l’arbre, sinon il risque d’être endommagé.
Arbre de réglage del’index de consigneȷLa mise à zéro n’est pas nécessaire pour le voltmètre C.C. et l’ampèremètre C.C.

ȷSélecteur et sélecteur à clé
EU2B-YS311N1F ‫ڧ‬‫ڧ‬: Peut être suivi d’un code deOpérateur (style)position de retrait de la clé
S: Sélecteur (Opérateur à bouton)
et/ou d’un code numérique de
SK: Sélecteur à clé (Opérateur à clé)clé différent pour sélecteur à clé.
Position / fonction(Voir le catalogue.)
2 : Position 2 / Maintenue
Forme
de
borne
2R: Position 2 / Maintenue (Chevauchement)
C: Borne à vis standard
2J : Position 2 / Maintenue (Fonction spéciale)
F: Borne à vis IP20
21 : Position 2 / Rappel par ressort de la droite
Code de circuit vide: Aucun
3 : Position 3 / Maintenue
N1: Désignation distincte
Arrangement
descontacts
31 : Position 3 / Rappel par ressort de la droite
etc. (Voir le catalogue.)
10: 1NO 11: 1NO1NC
32 : Position 3 / Rappel par ressort de la gauche
01:
1NC
30:
3NO
33 : Position 3 / Rappel par ressort bidirectionnel
20: 2NO 03: 3NC
02: 2NC 21: 2NO1NC 12: 1NO2NC
ȷVoyant lumineux
EU2B-YL22FDR
Couleur de lampe
Lentille (style ) L1:Voyant lumineux
R : Rouge G: Vert A: Ambre
Tension de fonctionnement
Y : Jaune W: Blanc S: Bleu
66 : C.A./C.C. 6 V (type pleine tension)
11 : C.A./C.C. 6 V (type pleine tension)
PW: Blanc pur
22 : C.A./C.C. 24 V (type pleine tension)
16 : C.A.100/110V (type transformateur)
Forme de borne
116: C.A. 115 V (type transformateur)
126: C.A.120 V (type transformateur)
C: Borne à vis standard
26 : C.A. 200/220 V (type transformateur) 236 : C.A. 230 V (type transformateur)
F: Borne à vis IP20
246: C.A. 240 V (type transformateur)386: C.A. 380 V (type transformateur)

CEI/EN 60079-0, CEI/EN 60079-1, CEI/EN 60079-7
CEI/EN 61241-0, CEI/EN 61241-1, CEI/EN 60079-31
CEI/EN 60947-1, CEI/EN 60947-5-1
CEI/EN 60947-5-5 (Interrupteur d’arrêt d’urgence)
CEI/EN 60051-1, CEI/EN 60051-2, CEI/EN 60051-9(Appareil de mesure）

50 minimum(*)

1 Numéros de type
ȷInterrupteur à bouton-poussoir et interrupteur d’arrêt d’urgence EU2B-YB111FB
Couleur de bouton
Opérateur (style / fonction)
R: Rouge G: Vert B: Noir
B1: Bouton-poussoir de vidange
Arrangement des contacts
Y: Jaune W: Blanc S: Bleu
/ Momentané
10: 1NO 01: 1NC
B2: Bouton-poussoir étendu
La couleur du bouton
Forme de borne
20: 2NO 02: 2NC/ Momentané
C: Borne à vis standard de l’interrupteur d’arrêt
11: 1NO1NC 30: 3NO
B3: Bouton-poussoir coup de poing 03: 3NC 21: 2NO1NC
d’urgence est limitée à « R ».
F: Borne à vis IP20
/ Momentané
12: 1NO2NC
BV3: Coup de poing
L’arrangement des contacts de l’interrupteur d’arrêt d’urgence est limité à/ Arrêt d’urgence« 01 », « 02 », « 11 », « 03 » et « 12 ».

Normes applicables

33 +0.5
0(Exigences générales)Ū Les blocs de commande EU2B sont conçus exclusivement pour le boîtier de commande
EC2B antidéflagrant et à sécurité augmentée. Pour toute autre utilisation des blocs de commande EU2B, s’assurer que les conditions d’utilisation sont appropriées.
Ū Lors de l’utilisation d’un interrupteur d’arrêt d’urgence pour le dispositif de sécurité d’unsystème de commande, s’assurer du bon fonctionnement en se reportant aux normes desécurité et réglementations du pays ou de la région, selon le but dans lequel les machines etinstallations sont exploitées.
Avant d’utiliser l’interrupteur d’arrêt d’urgence, procéder à une évaluation des risques pour
assurer la sécurité.
(Ouverture du carton d’emballage)Ū S’assurer que le produit est bien celui qui a été commandé. L’utilisation d’un modèle
inadéquat peut entraîner un dysfonctionnement ou un accident.
(Installation)
Ū Lire ce manuel d’instructions pour s’assurer d’installer correctement les blocs de commande
EU2B.
Installer les blocs de commande EU2B sans laisser pénétrer de substances telles quepoussières, poussières de ciment ou poussières métalliques, sinon il y a risque de mauvais
contact ou de mauvaise isolation.
（Utilisation)Ū Cesser immédiatement l’utilisation en cas de fonctionnement anormal. Sinon, il y a risqued’accident secondaire.
（Maintenance et inspection)
Ū La température de surface des blocs de commande EU2B peut être extrêmement élevéependant l’utilisation. Penser à mettre des gants avant d’effectuer la maintenance oul’inspection des blocs de commande EU2B, pour éviter les brûlures aux mains.

Spécifications du produitȭ 64(Exigences générales)
Utiliser des blocs de commande EU2B conçus pour l’utilisation dans les zones dangereuses,‫ە‬
sinon il y a risque d’explosion ou d’incendie. (Zone dangereuse: atmosphère potentiellement
explosive où il peut y avoir des gaz explosifs ou des vapeurs explosives) Le bloc decommande EU2B étant un composant Ex, il ne peut être utilisé seul en tant que dispositif
antidéflagrant. Pour l’utilisation au Japon, les blocs de commande EU2B doivent être certifiés par la TIIS (Technology Institution of Industrial Safety) en tant que produit fini.
‫ ە‬Les blocs de commande EU2B peuvent être installés dans les zones 1 et 2. Ne pas lesutiliser dans la zone 0.
‫ ە‬Couper l’alimentation des blocs de commande EU2B avant l’installation, le retrait, le câblage,
la maintenance ou l’inspection, sinon il y a risque d’explosion, d’incendie ou de déchargesélectriques.
‫ ە‬Une expertise particulière est requise pour installer, câbler, utiliser, entretenir et inspecter les blocs de commande EU2B. Les personnes sans cette expertise ne doivent pas utiliser les blocs de commande EU2B, sinon il y a risque de dommages ou d’accident.
‫ ە‬Ne pas démonter, réparer ou modifier les blocs de commande EU2B, sinon il y a risque dedommages ou d’accident.
‫ ە‬Ne pas utiliser des blocs de commande EU2B endommagés, sinon il y a risque dedommages ou d’accident.
(Câblage et utilisation)‫ ە‬Lors de la connexion à des dispositifs externes, s’assurer que chaque câble est connecté àla bonne borne, sinon il y a risque de décharges électriques, d’incendie ou d’explosion.
‫ ە‬Utiliser des câbles de la bonne taille et conformes aux exigences en matière de tension et decourant. Appliquer aux vis de borne M3,5 un couple de serrage de 1,0 à 1,3 N･m. Un câblage inadéquat peut causer une hausse anormale de température et entraîner un risqued’incendie et une explosion.
‫ ە‬Utiliser les blocs de commande EU2B avec le courant nominal et la tension spécifiés dans ce
manuel d’instructions, sinon il y a risque de court-circuit, d’incendie ou d’explosion.
(Maintenance et inspection)‫ ە‬Lors de la mesure de la résistance d’isolement des blocs de commande, s’assurer qu’il n’y apas d’atmosphère potentiellement explosive (gaz explosif ou vapeur explosive) à proximité,sinon il y a risque d’explosion ou d’incendie. Ne pas toucher la borne sans précaution. Sinon,
il y a risque de décharges électriques.

2(1) Spécifications générales

ȭ24

Le terme Attention est utilisé lorsqu’une inattention peut entraîner une blessure ou des dommages
matériels.

39

Le terme Avertissement est utilisé pour souligner qu’une utilisation inadéquate peut entraîner
une blessure grave ou le décès.

ȷAmpèremètre ou voltmètre C.C.
EU2B-YM010VDF-PER-R Index de consigne
M de fonction: Mètre
vide: non -R: avec index
Tension ou courant d’entréede consigne
010: 0 à 10 V
Type d’appareil de mesure
Spécification d’échelle
001: 0 à 1 mA VD: Voltmètre C.C.
-PER: 0 à 100%
420: 4 à 20 mA MD: Ampèremètre C.C. Forme de borne-60HZ: 0 à 60 Hz
C: Borne à vis standard
etc.
-80HZ: 0 à 80 Hz, etc.
F: Borne à vis IP20

33

C o n si g ne s d e s é c u rit é

48

Blocs de commande EU2B antidéflagrants et à sécurité augmentée
Vérifier que le produit livré correspond à celui qui a été commandé. Lire ce manuel d’instructions pour s’assurerd’utiliser correctement le produit. S’assurer que l’utilisateur final conserve le manuel d’instructions.

2.5
100MΩ minimum (mégohmmètre 500V C.C.)
300V
Appareil ferromagnétique
4kV
1VA
5A, 10A, 30A, 50A etc.
1A, 5A
3 fois etc.
150V
Instrument à aimant permanent et bobine mobile
2.5kV
0 to 1mA C.C., 4 to 20mA C.C. etc.
0 to 10V C.C. etc.
0.15W max.
270g

32
ȭ38

Spécification d’échelle de surcharge
Forme de bome
3: 3 fois 2: 2 fois 5: 5 fois N: Non
Type d’appareil de mesure A: Ampèremètre C.A.
C : Borne à vis standard
Plage de mesure
F : Borne à vis IP20
Mesure directe : 1: 1A 5: 5A
Pour transformateurs de courant: 10: 10A 15: 15A 20: 20A 30: 30A 50: 50A
60: 60A 75: 75A 100: 100A 150: 150A, etc.

MANUEL D’INSTRUCTIONSClasse de précision
Résistance d’isolement
Tension nominale d’isolement (Ui)Principe d’action
Ampèremètre Tension de tenue aux chocs (Uimp)
Consommation d’énergie
C.A.
Spécification d’échelle de mesure
Spécification de courant d’entrée
Spécification d’échelle de surcharge
Tension nominale d’isolement (Ui)Principe d’action
Ampèremètre
Tension de tenue aux chocs (Uimp)
C.C.
Ampèremètre C.C.
Spécification
Voltmètre C.C.
d’entréeVolmètre C.C.
Consommation d’énergie
Poids (approx.)

62

Index de consigne
vide: non -R: avec index de consigne

Courant d’entrée 1: 1A 5: 5A

Dans ce manuel d’instructions d’utilisation, les consignes de sécurité sont classées par ordred’importance sous les termes Avertissement et Attention:(4) Appareil de mesure(EU2B-YM)

EU2B-YM53A10F-R

M de fonction: Mètre

ȭ40

ȷAmpèremètre C.A.

ȭ40

B-1529(3)Mise en service

Avant la mise en service, s’assurer que:ȷles fils sont bien connectés ;ȷle bloc de commande EU2B est installé conformément au présent manuel d’instructions ;ȷle bloc de commande EU2B n’est pas endommagé.
Draw. No. B-1529D
Sep. 4, 2014

Maintenance et inspection

Encoches

BouchonĬ

Position d’insertion

ȷInterrupteur à bouton-poussoir

ȷRemplacement
ȷNettoyage
ȷSerrageȷRemplacement
ȷSerrageȷNettoyage

Opérateur (style / fonction)
B1: Bouton-poussoir devidange/ Momentané
B2: Bouton-poussoir étendu/ Momentané
B3: Bouton-poussoir
coup de poing/ Momentané

Accessoires et pièces de rechange

ȭ38

ȭ40

Encoches pour
tournevis

1 Numéros de type

Actions

1) Boutons de couleur pour interrupteur à bouton-poussoir:ųųųVidange/ HW1A-B1š, Étendu/ HW1A-B2š, Coup de poing/ HW1A-B4š
Remarque: Spécifier un code de couleur au lieu de š.
(R: rouge, G: vert, B: noir, Y: jaune, W: blanc, S: bleu)2) Lentille de couleur pour voyant lumineux: EU9Z-Lš (Outil d’installation TW-KC1)
Remarque: Spécifier un code de couleur au lieu de š.
(R: rouge, G: vert, A: ambre, Y: jaune, W: blanc, S: bleu)
Remarque: Utiliser une lentille de couleur blanche (W) pour un éclairage d’un blanc pur.
3) Plaque signalétique: EU9Z-NMš
Code(š)LégendePlaque d’identification pour plaque(vide)
0signalétique: EU9Z-NPš
1
ACTIVÉ
2
DÉSACTIVÉ
3
DÉMARRAGE
4
ARRÊT
31
ACTIVÉ/DÉSACTIVÉ
35
MANUEL-AUTO
53
MANUEL-DÉSACTIVÉ-AUTO
ȷInstallation de la plaque d’identification
Plaque d’identification
sur une plaque signalétique (Voir Fig. 1.)
pour plaque signalétique
ȷRetrait de la plaque d’identification d’une
PlaqueTournevis plat
plaque signalétique (Voir Fig. 2.)
signalétiqueղ
Pour retirer la plaque d’identification,
insérer un tournevis plat entre la plaque
Plaqued’identification et la plaque signalétique.
d’identification
ȷLors de l’utilisation d’une plaque signalétique, ձpour plaquesignalétiquel’épaisseur du panneau de montage diminuede 1,5 mm (1,0 à 3,0 mm).
Plaque4) Étiquette de plaque signalétique poursignalétiqueinterrupteur d’arrêt d’urgence: EU9Z-NVS27(Fig. 1)
(Fig. 2)
Légende « ARRÊT D’URGENCE »5) Couvercle-cadenas:
13.3
23.2
pour interrupteur d’arrêt d’urgence/ EU9Z-PCE
pour interrupteur à bouton-poussoir (Vidange,
Étendu) et sélecteur à clé/ EU9Z-PC
ȷLors de l’utilisation d’un couvercle-cadenas,l’épaisseur du panneau de montage diminue de
1.0 to 10.5
1,5 mm (1,0 à 3,0 mm).
(Épaisseur du panneau)
6) Fiche du trou de montage: EU9Z-BP (Voir les figures de droite.)(Remarque) Utiliser uniquement les accessoires et pièces de rechange spécifiés par IDEC.
L’utilisation de tout autre accessoire ou pièce de rechange annulera la garantie.

8

Soufflet en
caoutchouc

Élimination

Respecter les lois et réglementations en vigueur dans chaque pays en matière de traitementdes ordures.
Les spécifications et autres descriptions de ce manuel sont sujettes à modification sans préavis.

2

EU2B-YB111FB-D
Arrangement
des contacts
10 : 1NO
01 : 1NC
20 : 2NO
02 : 2NC
11 : 1NO1NC
30 : 3NO
03 : 3NC
21 : 2NO1NC
12 : 1NO2NC

Degré de protection
Aucune : IP65
D
: Type 4X*Pour un bouton-poussoir
de vidange ou étendu,
installer un soufflet en
caoutchouc (accessoire).
Couleur de bouton
R : Rouge
G : Vert
B : NoirY : Jaune
W : Blanc
S : Bleu
Forme de borne
C : Borne à vis standard
F : Borne à vis IP20

Spécifications du produit(1) Spécifications générales

Protection contre l’explosion
Type de protection contre
ULl’explosion(Remarque 1)
c-UL attendre

Classe I, Zone 1, AEx de IIC T6 Gb
Classe +, Div2, Groups A,B,C and D
Classe +, Zone 1, Ex de IIC T6 Gb
Voyantlumineux Classe I, Div2, Groups A,B,C and D
Classe I, Zone 1, Ex de IIB T6 Gb
Voyantlumineux Classe +, Div2, Groups C and D
E347230

Certifié par essai
Degré de protection
De l’avant du panneau(Remarque 2)

Type 4X(l’interrupteur de type vidange ou étendu
est fixé au soufflet en caoutchouc)
IP65

Remarque 1: Inscrit pour l’utilisation en Zone 1, 2 et Division 2.
Remarque 2: Les boutons-poussoirs de types vidange et étendu ne sont pas
certifiés PTB avec le soufflet en caoutchouc monté.
Remarque 3: Monter le bloc de commande EU2B sur une enveloppe métalliquemise à la terre.
(Comprend les produits inscrits aux répertoires UL et c-UL, et certifiés ATEX)
Remarque 4: Applications à degré de pollution 2 ou applications à degré depollution 3 lors de l’installation dans une enveloppe de Type 4X ou
IP65 ou meilleure, ou mention équivalente.
(2) Interrupteur à bouton-poussoir, sélecteur, sélecteur à clé et interrupteur d’arrêt d’urgence(Type EU2B-YB/ EU2B-YS/ EU2B-YSK/ EU2B-YBV)
ȷValeurs nominales de contact
Courant maximum, ampères
Voltampères
Désignation Ampères
maximum
du code de courantde valeurs d’épreuve
nominales thermique
120 volts
240 volts
480 volts
600 volts
de contact continue Fermer Ouvrir Fermer Ouvrir Fermer Ouvrir Fermer Ouvrir Fermer Ouvrir
10
720
A600
7200
60 6.00 30 3.00 15 1.50 12 1.20

3

Arrangement et montage(1) Dimensions (Interrupteur à bouton-poussoir avec soufflet en caoutchouc)

C onsignes de sécurité
Dans ce manuel d’instructions d’utilisation, les consignes de sécurité sont classées par
ordre d’importance sous les termes Avertissement et Attention:
Le terme Avertissement est utilisé pour souligner qu’une utilisation inadéquate
peut entraîner une blessure grave ou le décès.

Le terme Attention est utilisé lorsqu’une inattention peut entraîner une blessure ou
des dommages matériels.




 

Vérifier que le produit livré correspond à celui qui a été commandé. Lire ce manueld’instructions pour s’assurer d’utiliser correctement le produit. S’assurer que l’utilisateur
final conserve le manuel d’instructions.







1.0 to 4.5
ÉRCKUUGWTFWRCPPGCW

Ce manuel d’instructions décrit les produits inscrits aux répertoires UL et c-UL.
Pour les pièces autres que celles décrites dans ce manuel, voir le manueld’instructions de bloc de commande EU2B « B-1044 ».

3<EU2B-YB1>

Make Break
720
7200

<EU2B-YB2>

INSTRUCTION MANUAL
EU2B Control UnitsUL and c-UL Listed(Flameproof and Incneased Safety Construction)
This instruction manual describes UL and c-UL Listed products. For items other thandescribed in this manual, see EU2B control unit instruction manual "B-1044".
Confirm that the delivered product is what you have ordered. Read this instruction
manual to make sure of correct operation. Make sure that the instruction manual is kept
by the end user.

S afety P recau ti o n s

1.0 to 4.5
2CPGNVJKEMPGUU1) Soufflet en caoutchouc sur bouton-poussoir (matériau: caoutchouc de silicone)
Bouton-poussoir de vidange ………… EU9Z-DB1………… EU9Z-DB1N (Une plaque signalétiquepeut être appliquée)
Bouton-poussoir étendu ……………… EU9Z-DB2……………… EU9Z-DB2N (Une plaque signalétiquepeut être appliquée)







(2) Rubber boot on flush and extended pushbuttons<Installing the rubber boot on flush and extended pushbuttons>
Place the rubber boot on the cap, and push in the rubber boot holder straight.
The notches around the rubber boot must show evenly.
Push in the rubber boot holder further, around on the two notches on the holder,so that the holder fits the button completely.
Make sure that the rubber boot and rubber boot holder are installed straight.
Nameplate type: the EU2B and the rubber boot holder must be aligned so that when
installed, the anti-rotation projection on the EU2B comes to the center of grooveon the holder.
(Note)Make sure that the rubber boot is installed completely, otherwise Type 4X
degree of protection cannot be obtained.
(Note)Water drops might enter the rubber boot, but no water will enter the control box.

In this operation instruction manual, safety precautions are categorized in order ofimportance to Warning and Caution:

Notches〈Nameplate type〉

Rubber bootholderWarning notices are used to emphasize that improper operation may cause severe
personal injury or death.

Rubber bootCaution notices are used where inattention might cause personal injury or damage toequipment.

Align
Notches forscrewdriverCap(General requirements)‫ە‬
Use the EU2B control units that are applicable for use in hazardous areas,otherwise
explosion or fire hazard may result. (Hazardous area: potentiallyexplosive atmosphere where explosive gas or vapor may exist) To use the EU2B
control unit as explosion-protection electric equipment, the EU2B has to be
Listed as an explosion-protection equipment.
‫ ە‬EU2B control units can be installed only in zones 1, 2 and division 2. Do not use
in zone 0 and division 1.

1 Type Numbers
EU2B-YB111FB-D

Operator (style / function)
B1 : Flush pushbutton
Contact arrengement/ Momentary
10 : 1NOB2 : Extended pushbutton 01 : 1NC/ Momentary
20 : 2NOB3 : Mushroom pushbutton 02 : 2NC/ Momentary
11 : 1NO1NC
30 : 3NO
03 : 3NC
21 : 2NO1NC
12 : 1NO2NC

2

Maximum
Volt-amperes

Arrangement and Mounting

Accessoires

Dgree of protection
None : IP65
D : Type 4X*For Flush/Extended pushbutton,
install a Rubber boot(accessory).
Button color
R : Red G : GreenB : Black Y : Yellow
W : White S : Blue
Terminal shape
C : Standard screw terminal
F : IP20 screw terminal

(2) Soufflet en caoutchouc sur boutons-poussoirs de types vidange et étendu<Installation du soufflet en caoutchouc sur les boutons-poussoirs de types vidange et étendu>
Mettre le soufflet en caoutchouc sur le bouchon, et enfoncer bien droit le support desoufflet en caoutchouc.
Les encoches autour du soufflet en caoutchouc doivent être uniformément visibles.
Enfoncer davantage le support de soufflet en caoutchouc, à l’emplacement des deux
encoches du support, de sorte que le support s’adapte parfaitement au bouchon.
S’assurer d’installer bien droit le soufflet en caoutchouc et son support.
Type plaque signalétique: l’EU2B et le support de soufflet en caoutchouc doivent êtrealignés de sorte que, une fois installés, la partie saillante anti-rotation de l’EU2B arrive au
centre de la rainure sur le support.
(Remarque) S’ assurer que le soufflet en caoutchouc est parfaitement installé, sinon ledegré de protection Type 4X ne pourra être obtenu.
(Remarque) Il se peut que des gouttes d’ eau pénètrent dans le soufflet en caoutchouc,mais l’ eau ne pénétrera pas dans le boîtier de commande.

Maximum current, amperes
ThermalContact
Continuous
RatingTest
Codedesignation Current
480 Volt
240 Volt
600 Volt
120 Volt
Amperes Make Break Make Break Make Break Make Break
10
30 3.00 15 1.50 12 1.20
A600
60 6.00(1) Câbles utilisables
Fil multibrins: 1,5 à 2,5 mm2, fil plein: φ1,2 àφ1,6 mm (AWG 16 à 14)(Remarque) Ne pas connecter plus de 2 fils à la même borne.

<EU2B-YB2>

Blocs de commande EU2B
Inscrits aux répertoires UL et c-UL
(Antidéflagrants et à sécurité augmentée)

Note 1: Listed for use in Zone 1, 2 and Division 2.
Note 2: Flush and extended pushbuttons are not PTB certified with the rubber bootmounted.
Note 3: Mount the EU2B control unit to a grounded metal enclosure.
(Includes UL and c-UL Listed, ATEX approved products)
Note 4: Pollution Degree 2 applications or Pollution Degree 3 applications when
installed in a Type 4X or IP65 or better enclosure or equivalent statement.
(2) Pushbutton swtich, Selecter switch, Key selecter switch and Emergency stop
switch(Type EU2B-YB/ EU2B-YS/ EU2B-YSK/ EU2B-YBV)ȷContact Rating(1) Dimension (Pushbutton switch with Rubber boot)CâblageȷPushbutton switch<EU2B-YB1>

MANUEL D’INSTRUCTIONS

4

5
UL 60079-0, UL 60079-1, UL 60079-7
CAN/CSA C22.2 No. 60079-0
CAN/CSA C22.2 No. 60079-1
CAN/CSA C22.2 No. 60079-7

Normes applicables<Retrait du soufflet en caoutchouc des boutons-poussoirs de typevidange et étendu>
Insérer doucement le tournevis plat (0,5t x 4w ou inférieur) dans une
encoche du support de soufflet en caoutchouc, et incliner dans le sensde la flèche ①.
Le soufflet en caoutchouc peut être retiré.
(Remarque): Pour éviter tout dommage, ne pas appliquer une force
excessive sur l’EU2B en retirant le soufflet en caoutchouc.
Le degré de protection désiré ne peut être assuré si l’EU2B
est endommagé.

Type 4X(Flush and Extended type switch is attachedto the rubber boot)
IP65



7

dangereuses, sinon il y a risque d’explosion ou d’incendie. (Zone dangereuse:
atmosphère potentiellement explosive où il peut y avoir des gaz explosifs ou
des vapeurs explosives) Pour utiliser le bloc de commande EU2B commeéquipement électrique de protection contre l’explosion, l’EU2B doit être inscrit en tant qu’équipement de protection contre l’explosion.
‫ ە‬Les blocs de commande EUB2 peuvent être installés dans les zones 1 et 2 etdans la division 2. Ne pas les utiliser dans la zone 0 et dans la division 1.

Aligner

Tableau: Exemple de maintenance et d’inspection
MéthodeInspections
Pièces à
inspecter d’inspection
ȷPas de dommages
Visuelle
Unité
ȷPas de rouilleȷBague de verrouillage bien serrée
ȷPas de fissures
Garnitures VisuelleȷPas de déformation visible
Borne
Visuelle
ȷPas de vis desserréesTactileȷPas de saletés sur les matériaux isolants(Exigences générales)‫ە‬
Utiliser des blocs de commande EU2B conçus pour l’utilisation dans les zones

E347230



(2) Maintenance et inspection
Effectuer régulièrement la maintenance et l’inspection des pièces énumérées dans le tableau
ci-dessous.

Support desoufflet en
caoutchouc

Test certificatedDegree of protection
From panel front(Note2)

(1) Remarques sur l’inspection des blocs de commande EU2B
1) Respecter les lois et réglementations en vigueur dans chaque pays.
2) Ne jamais démonter les blocs de commande.
3) Pendant la maintenance et l’inspection, ne pas utiliser d’outils pouvant causer des étincelles
lors des chocs.
4) Lors de l’utilisation de dispositifs de mesure, ceux-ci doivent être protégés contre l’explosion.
5) Ne pas emporter dans un environnement à risque d’explosion.

〈Type plaque signalétique〉

 

6

Product Specifications(1) General Specifications
Applicable Standards

UL 60079-0, UL 60079-1, UL 60079-7
CAN/CSA C22.2 No. 60079-0
CAN/CSA C22.2 No. 60079-1
CAN/CSA C22.2 No. 60079-7ẅ

Explosion protection
Type of Explosion protection UL(Note1)

Class I, Zone 1, AEx de IIC T6 Gb
Class +, Div2, Groups A,B,C and D
Class I, Zone 1, Ex de IIC T6 Gb
Pilot light Class I, Div2, Groups A,B,C and D

Exceptc-UL ẅẅẅ

Pilot light Class I, Zone 1, Ex de IIB T6 Gb

Class I, Div2, Groups C and D

ĬPush-in position<Removing the rubber boot from the flush and extended pushbuttons>
Gently insert the slotted screwdriver (0.5t x 4w or below)
inside a notch on the rubber boot holder, and tilt to thedirection shown with arrow ①.
The rubber boot can be removed.
(Note)：To prevent from damage, do not apply excessive force to the
EU2B when removing the rubber boot. The desired degree ofprotection cannot be ensured with the damaged EU2B.

4

Wiring(1) Applicable wires
Stranded wire: 1.5 to 2.5 mm2, solid wire: ȭ1.2 to ȭ1.6 mm (AWG16 to 14)(Note) Do not connect more than 2 wires to the same terminal.

5

Accessories

1) Rubber boot on pushbutton (Material : Silicone rubber)
Flush push button ………… EU9Z-DB1………… EU9Z-DB1N (Nameplate can be applied)
Extended push button …… EU9Z-DB2…… EU9Z-DB2N (Nameplate can be applied)

Draw. No. B-1529D
Oct. 29, 2014

6-64 Nishimiyahara 2-chome, Yodogawa-ku, Osaka, 532-0004, Japan
http://www.idec.com
B-1529-1(3)