B-1797(5)FC6A Series
Communication Cartridge
This sheet provides brief operating instructions of the MICROSmart
programmable controller. For details, see the FC6A Series MICROSmart
User’s Manual.

Safety Precautions
Special expertise is required to use the MICROSmart.
● Read this instruction sheet and the user's manual to make sure ofcorrect operation before starting installation, wiring, operation,maintenance, and inspection of the MICROSmart.
Keep this instruction sheet where it can be accessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorousquality control system, but users must add backup or failsafe provisions
to control systems use the MICROSmart in applications where heavy
damage or personal injury may be caused if the MICROSmart shouldfail.
● Install the MICROSmart according to the instructions described in this
instruction sheet and the user's manual.
Improper installation will result in falling, failure, or malfunction of theMICROSmart.
● Make sure that the operating conditions are as described in the user’smanual. If you are uncertain about the specifications, contact IDEC
before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order ofimportance from Warning and Caution:

Warning notices are used to emphasize that improper operation may
cause severe personal injury or death.

1TYPE

RS485

AA

B SGA

B SG

B SG

Terminal
resistor

5

Dimensions

Specification

12.5
17.8

34.8

All dimensions in mm.

6Parts Description

Caution notices are used where inattention might cause personal injury ordamage to equipment.

FETerminal
A *2
B *3
SG *4

I/O
INPUT and OUTPUTINPUT and OUTPUT-Shield

RS485
InterfacedeviceDescriptionData A
Data B
Signal Ground*2 Two A terminals are interconnected.
*3 Two B terminals are interconnected.
*4 Two SG terminals are interconnected.

(2)

For details about wiring of the cartridge, see the user’s manual.
Use a proper cable for wiring the terminals.
Crimp the ferrules to the wire cable.
Before wiring, read the user’s manual for the remote device connected tothe cartridge.
Use the shielded cable and connect the shields of the cable to ground tosuppress the influence of noises.
If the communication quality is unstable, insert appropriate termination
resistors matched to the characteristic impedance of the cable.
Over 1/2W resistors are recommended for the terminal resistor.

● Use minimum 60°C wire copper conductor only.

7

WiringApplicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening TorqueThe recommended ferrule is made by IDEC, Weidmüller or Phoenix Contact.
To crimp the ferrules shown below, use a special crimping tool.
(S3TL-CR04T (S3TL-CR04T), PZ 6 Roto L (1444050000) or CRIMPFOX6(1212034))
To the terminal block, use the recommended screwdriver made by IDEC,
Weidmüller or Phoenix Contact and tighten terminal screws tightening torque.

FC6A-PC1
FC6A-PC1
RS232

Applied cable● Turn off the power to the MICROSmart before starting installation,

B SG

Terminalresistor

Operating Temperature: -10 to +55°C (no freezing)
Storage Temperature: -25 to +70°C (no freezing)
Relative/Storage Humidity: 10 to 95%RH (no condensation),
Altitude or Air Pressure: 0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport,
Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,
acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,
Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes,
6 directions, 3 times each
Installation Location: Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C
Temperature Code: T4A*See the user’s manual for more details on the product specifications.

(1)A

Cartridge

Cartridge slot 1

attached or removed when tilted, it may be damaged or cause operatingproblems. When not using Cartridge, attach the Cartridge cover.
● For UL/cUL, Horizontal mounting only.

Applicable model
FC6A Series MICROSmart CPU module

3

FC6A-PC3
RS485● Attach or remove the cartridge straight to the unit. If the cartridge is

RS232C : FC6A-PC1
RS485 : FC6A-PC3

2

FC6A-PC3

FC6A-PC3

44.6

INSTRUCTION SHEET● The MICROSmart is designed for installation in equipment. Do notinstall the MICROSmart outside of equipment.
● Install the MICROSmart in environments as described in the user'smanual. If the MICROSmart is used in places where it is subjected tohigh-temperature, high-humidity, condensation, corrosive gases,excessive vibrations, or excessive shocks itwill result in electricalshocks, fire hazard, or malfunction.
● The environment rating for using the MICROSmart is “Pollution degree 2.”● Prevent metal fragments and pieces of wire from dropping inside theMICROSmart housing. Ingress of such fragments and chips may cause
fire hazard, damage, or malfunction.
● Use wires of a proper size to meet voltage and current requirements.
Tighten terminal screws to the proper tightening torque of 0.2 N･m.
● Do not disassemble, repair, or modify MICROSmart modules.

2. Pay careful attention to the direction of the cartridge and attach it
directly onto the unit.

Recommended ferrule

AWG24 S3TL-H025-10WJ (S3TL-H025-10WJ), AI 0,25-6 (3203040)(1)

removal, wiring, maintenance, or inspection on the MICROSmart.
Failure to turn off the power may cause damage, electrical shocks or fire
hazard.
(1)Terminal● Emergency stop and interlocking circuits must be configured outside theRS232C or RS485 communication port
MICROSmart. If such a circuit is configured inside the MICROSmart,(2)Connector
failure of the MICROSmart may cause disorder of the control system,Connects to the cartridge slot 1 or 2 connector on the CPU module.
damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND D
Connecting Cartridge
HAZARDOUS LOCATIONS, OR NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereuses
1. Insert flat head screwdrivers into the screwdriver insertion slots in bothde classe 1, groupes A,B,C et D; ou dans des zones non dangereuses.
locations of the unit, and while pushing the tabs of the cartridge cover,● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT
pull the cartridge cover directly upward to remove it.
EQUIPMENT WHILE THE CIRCUIT IS LIVE OR UNLESS THE AREA IS
KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.
CPU module● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant quele circuit est sous tension, ou à moins ďêtre certain que lieu ďutilisationsoit exempt de concentrations inflammables.
● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE
INSTALLED IN AN ENCLOSURE SUITABLE FOR THE ENVIRONMENTTHAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOL OR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté àľenvironnement ďutilisation et uniquement accessible avec un outilďouverture ou une clé.

RS ER SD

UL1007/ UL2464 AWG22 S3TL-H034-10WT (S3TL-H034-10WT), AI 0,34-6 (3203053)
AWG20 S3TL-H05-12WA (S3TL-H05-12WA), AI 0,5-6 (3200687)

RD DR SGRS232C
Interfacedevice

4ShieldI/OOUTPUTOUTPUTOUTPUT
INPUT
INPUT-*1 constant voltage terminal

Screwdiver insertion slot

Tighten torque
0.2 N･m( ) indicates the Type No. of IDEC CORPORATION, Weidmüller Interface GmbH& Co. KG and PHOENIX CONTACT GmbH & Co. KG.
*See the user's manual for recommended tools and ferrules other than those listedabove.

8FE

Terminal
RS (RTS) *1
ER (DTR)SD (TxD)
RD (RxD)
DR (DSR)
SG (SG)

Screwdriver
S3TL-D04-25-75 (S3TL-D04-25-75), SZS 0.4×2.5 (1205037)

Description
Request to Send
Data Terminal ReadyTransmit Data
Receive Data
Data Set ReadySignal Ground

Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.
EU Authorized Representative : APEM SAS55, Avenue Edouard Herriot BP1, 82303 Caussade Cedex, France
UK Authorized Representative : APEM COMPONENTS LIMITED
Drakes Drive, Long Crendon, Buckinghamshire, HP18 9BA, UK
Manufacturer :IDEC CORPORATION
2-6-64,Nishimiyahara,Yodogawa-ku, Osaka,JapanMICROSmart User’s manual can be downloaded fromhttps://www.idec.com/FC6Amanuals

Cartridge coverhttps://www.idec.com
2021.09

B-1797(5)

1形番構成

外形寸法

5

詳しい配線方法については、ユーザーズマニュアルをご参照ください。
接続ケーブル条件に合致するケーブルをユーザー様にて加工し、ご使用ください。
本製品の通信相手となる機器のマニュアルを熟読した上で配線してください。
ノイズによる誤動作の恐れがある場合は、配線ケーブルのシールド線を接地してください。
通信状態が不安定な場合、特性インピーダンスに合わせた終端抵抗をケーブルの両端に挿入ください。定格1/2W以上の抵抗をご使用ください。

RS232C通信カートリッジ：FC6A-PC1
RS485通信カートリッジ：FC6A-PC3
適合機種
FC6A形マイクロスマート CPUモジュール

2

ＦＣ６Ａ形通信カートリッジ
この度は、弊社製品をお買い上げいただき、誠にありがとうございます。
ご注文の製品に間違いがないかを確認のうえ、この取扱説明書の内容をよくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管されるよう手配ください。

44.6

取扱説明書

仕様

使用周囲温度：-10～+55℃（氷結なきこと）
保存周囲温度：-25～+70℃（氷結なきこと）
使用/保存周囲湿度：10～95%RH（結露なきこと）
標高：動作時：0～2000ｍ（1013～795hPa）
輸送時：0～3000m（1013～701hPa）
耐振動：5 ～ 8.4Hz片振幅3.5mm
8.4 ～ 150Hz加速度9.8m/s2（1G）XYZ各方向
耐衝撃：147m/s2（15G）11ms XYZ 3軸6方向各3回

72時間※電気的仕様に関する詳細はユーザーズマニュアルをご覧ください。

312.5
17.8

34.8

入出力配線

6FC6A-PC1

各部の名称

適合電線

FC6A-PC1
RS232

安全上のご注意
本製品の取り扱いには専門の知識が必要です。
②
・本製品の取り付け、配線作業、運転および保守・点検を行う前に、この取扱説明書およびユーザーズマニュアルをよくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管されるよう手配ください。
・本製品は弊社の厳しい品質管理体制のもとで製造されておりますが、①①
万一本製品の故障により重大な故障や損害の発生するおそれがある用途へご使用の際は、バックアップやフェールセーフ機能をシステムに追加してください。
・取扱説明書、ユーザーズマニュアルに記載の指示に従って取り付けて① 端子部ください。取り付けに不備があると落下、故障、誤動作の原因となります。
シリアルインターフェイス（RS232CまたはRS485）を装備した・使用条件が、取扱説明書やユーザーズマニュアルの内容と相違ないこ機器を接続する端子部です。とを必ずご確認ください。
接続する機器は、通信カートリッジの種類によって異なります。
内容に不明な点がある場合は、使用する前に弊社までご相談ください。
端子名の詳細は「6. 入出力配線」の項を参照ください。
・本取扱説明書では、誤った取り扱いをした場合に生じることが想定さ② 接続コネクタ
れる危険の度合いを「警告」「注意」として区別しています。
CPU モジュールのカートリッジスロット1 または2と接続します。
それぞれの意味するところは以下のとおりです。

！

警告4

接続方法

取り扱いを誤った場合、人が死亡または重傷を負う可能性があります。

1. FC6A形マイクロスマート CPUモジュール （カートリッジスロット1）のドライバ差込口（2 箇所）にそれぞれマイナスドライバを差し込み、！ 注 意
ダミーカートリッジのツメ部を押し込んだ状態で、ダミーカートリッジ取り扱いを誤った場合、人が障害を負うか物的障害が発生する可能性があをまっすぐ取り外します。
ります。
FC6A形マイクロスマート
CPUモジュール

！

UL1007／UL2464
RS ER SD

RS232CAWG22

S3TL-H034-10WT (S3TL-H034-10WT),
AI 0,34-6 (3203053)

AWG20

S3TL-H05-12WA (S3TL-H05-12WA),
AI 0,5-6 (3200687)

推奨締付トルク
0.2 N･m（ ）内は 弊社、ワイドミュラー社または フェニックス・コンタクト社製品の発注形番

インターフェイス

※上記以外の推奨工具・フェルール端子の詳細はユーザーズマニュアルをご覧ください。

機器

FE

端子名
RS（RTS）*1
ER（DTR）
SD（T×D）
RD（R×D）
DR（DSR）
SG（SG）＊１8シールド

入出力方向
出力出力出力入力
入力－

信号名称など
送信要求
データターミナルレディ
送信データ
受信データ
データセットレディ
信号グランド廃棄上のご注意・本製品を廃棄するときは、産業廃棄物として扱ってください。

RS端子は、一定出力端子です。

FC6A-PC3
RS485

ユーザーサポート情報

FC6A-PC3
RS485

A

B SG

A

B SG

最新のユーザーズマニュアルを、下記URLよりダウンロードして下さい。
A

・本製品は装置内への組み込み設置専用です。装置外には設置しないでください。
・カタログ、ユーザーズマニュアルに記載の環境下で、ご使用ください。
・高温、多湿、結露、腐食性ガス、過度の振動・衝撃のある所で使用すると、感電、火災、誤動作の原因となります。
・本製品の使用環境汚損度は「汚損度2」です。
・設置、配線作業時に配線くずやドリル加工による金属の切り粉などが、本製品内部に入らないように注意してください。配線くずなどが本製品内部に入ると、火災、故障、誤動作の原因となります。
・配線は印加電圧、通電電流に適した電線サイズを使用し、端子ねじは推奨締付トルク0.2 N･m で締め付けてください。
・分解、修理、改造等は行わないでください。

S3TL-H025-10WJ (S3TL-H025-10WJ),
AI 0,25-6 (3203040)

推奨ドライバS3TL-D04-25-75 (S3TL-D04-25-75),
SZS 0.4×2.5（1205037）

警告

注意

RD DR SG

推奨フェルール端子
AWG24

FC6A-PC3・取り付け、取り外し、配線作業および保守・点検は必ず電源を切って行ってください。破損のおそれ、感電および火災の危険があります。
・非常停止回路やインタロック回路などはマイクロスマート以外の外部回路で構成してください。これらの回路をFC6A形のシステムで構成するとFC6A形が故障した場合、機械の暴走、破損や事故のおそれがあります。

！

適合電線／推奨フェルール端子／推奨ドライバ／締付トルク

推奨のフェルール端子は弊社、ワイドミュラー社 またはフェニックス・コン
タクト社製品です。下記推奨フェルール端子を圧着する際には、専用の圧着工具 PZ 6 Roto L（1444050000）または CRIMPFOX 6（1212034）（単位：mm） をご使用ください。端子台に配線する際には、下記推奨ドライバをご使用ください。またねじ締め付けが必要な場合は、下記の推奨締付トルクで締め付けてください。

ドライバ差込口

B SGA

B SG

https://jp.idec.com/downloads/fc6a
ダミーカートリッジ
終端抵抗

2. 通信カートリッジの上下に注意して、通信カートリッジの接続コネクタをFC6A形マイクロスマート CPUモジュールのカートリッジスロット1にまっすぐ確実に押し込みます。

終端抵抗

FE

端子名
A *2
B *3
SG *4

カートリッジスロット 1

通信カートリッジ

入出力方向
入出力
入出力－シールド

RS485
インターフェイス
機器

信号名称など
データＡ
データＢ
信号グランド*2 端子Ａはカートリッジ内部で短絡されています。
*3 端子Ｂはカートリッジ内部で短絡されています。
*4 端子ＳＧはカートリッジ内部で短絡されています。

取扱説明書にご不明な点がございましたら、製品問合せ窓口にお問い合わせください。

製品問合せ窓口2021.09