Touch

The generic term for the SmartAXIS FT1A-*12RA-*, FT1A-*14KA-* and FT1A-*14SA-*.

● Be certain to read this manual carefully before performing installation, wiring, or maintenance work,or operating the Touch.
● This product has been manufactured with careful regard to quality. However, if you intend to use thisproduct in applications where failure of this equipment may result in damage to property or injury,
ensure that it used in conjunction with appropriate fail-safe backup equipment.
● IIn this manual, safety precautions are categorized in order of importance to Warning and Caution:
Warning notices are used to emphasize that improper operation may cause severe personal injury or death.

● The Touch is not intended to be used for applications which require high reliability and safety, such as
medical equipment, nuclear equipment, railways, aircraft, and vehicles.
The Touch cannot be used for these applications.
● For other applications which require high reliability in function and precision, provide a failsafe design
and redundant design for the entire system including the Touch.
● Emergency and interlocking circuits must be configured outside of the Touch.
● If relays in the Touch output circuits should fail, outputs may remain at on or off state.
For output signals which may cause serious accidents, configure monitor circuits outside the Touch.
● The Touch self-diagnostic function may detect internal circuit or program errors, stop programs, andturn outputs off. Configure circuits so that the system containing the Touch are not jeopardized when
outputs turn off.
● Emergency and interlocking circuits must be configured outside of the Touch.
Do not use the Touch’s internal touch switches for an emergency circuit. If the Touch failed, theexternal equipment connected to the Touch will no longer be protected and serious injury to operatorsand equipment damage may be caused.
● Turn off the power to the Touch before installation, removal, wiring, maintenance, and inspection of
the Touch. Failure to turn power off may cause electrical shock or fire hazard.
● Special expertise is required to install, wire, configure, and operate the Touch. People without such
expertise must not use the Touch.
● The Touch uses an LCD (liquid crystal display) as a display device. The liquid inside the LCD isharmful to the skin. If the LCD is broken and the liquid attaches to your skin or clothes, wash theliquid off using soap, and consult a doctor immediately.
● <Hazardous locations warnings>
The following equipment is suitable for use in Class I, Division 2, Groups A, B, C and D hazardous
locations, or non hazardous locations only.
FT1A-M12RA type (version V121), FT1A-C12RA type (version V121, V200),
FT1A-M/C14KA/SA (version V110 or later) [TC: T4A]
The following equipment is suitable for use in Class I, Division 2, Groups C and D hazardous
locations, or non hazardous locations only.
FT1A-M12RA type (version V200 or later), FT1A-C12RA type (version V300 or later) [TC: T4A]
[TC: Temeprature code]- This equipment is an open-type device meant to be installed in an enclosure suitable for theenvironment that is only accessible with the use of a tool or key.
- Warning - Explosion Hazard - Do not disconnect equipment while the circuit is live or unless the area
is know to be free of ignitable concentrations.
- Avertissement: Risque d'explosion. Ne pas débrancher tant que le circuit est sous tension, à moins
qu'il ne s'agisse d'un emplacement non dangereux.

● Prevent the Touch from falling while moving or transporting, otherwise damage or malfunction of the
Touch will result.
● Use the product within the environmental limits given in the catalog and manual. Use of the product inhigh-temperature or high-humidity environments, or in locations where it is exposed to condensation,
corrosive gas or large shock loads can create the risk of electrocution and fire.
● The Touch is designed for use in pollution degree 2. Use the Touch in environments of pollution
degree 2. (based on the IEC60664-1 rating)● Install the Touch according to the instructions in the User’s Manual. Improper installation will result infalling, failure, electrical shock, fire hazard, or malfunction of the Touch.
● Prevent metal fragments or wire chips from dropping inside the Touch housing. Ingress of such fragments
and chips may cause fire hazard, damage, and malfunction.
● Use a power supply of the rated value. Using a wrong power supply may cause fire hazard.
● The Touch uses “PS2 of EN61131” as DC power supply. (based on the IEC/EN61131 rating)● Use wire of a proper size to meet the voltage and current requirements.
● When exporting the Touch to Europe, use an EN60127 (IEC60127) approved fuse on the power line
outside the Touch.
● When exporting the Touch to Europe, use an EU-approved circuit protector.
● Make sure of safety before starting and stopping the Touch. Incorrect operation of the Touch may
cause mechanical damage or accidents.
● Use the Touch in a local area network if you download, upload or monitor the project data via the
Ethernet port.
● The touch panel of the Touch is made of glass, and will break if exposed to excessive shock.
Take due care when handling it.
● When more than one button is pressed at the same time, due to the detection characteristics of ananalog type touch panel, only the gravity center of the pressed area is sensed and the unit assumes
that only one button is pressed. Thus, when more than one button is pressed simultaneously, theresulting operation is not guaranteed.
● The screen becomes blank when the backlight is burnt out; however, the touch panel remains enabled.
Incorrect touch panel operation will occur when operating the touch panel when the backlight appears
to be turned off but is actually burnt out. Note that this erroneous operation may result in damage.
● Do not push hard or scratch the touch panel and protection sheet with a hard object such as a tool,
because they are damaged easily.
● At temperatures over the rated operating temperature, the clock accuracy is affected. Adjust the clock
before use.

Before installing the Touch, make sure that the specifications of the product conform to yourrequirements, and that no parts are missing or damaged due to accidents during transportation.
● Touch Unit 1● Power plug
(Attached to the Touch) 1

Interface Specification

RS232C, RS422/485

Connector

Detachable Terminal Block 9pin

Applicable cable

RS232C: AWG16 to AWG28
RS422/485: AWG16 to AWG28 Shielded twisted-pair
Stripped wire length 7mm (Solid wire)

Recommended ferrule

Tightening Torque
No.
1
2
3
4
5
6
7
8
9

● Environmental Specifications

H0,34/12 TK (For AWG22), H0,5/14D W, H0,5/14 OR (For AWG20)
H0,5/14D ZH W, H0,5/14 ZH OR (For AWG20, For 2 wires)(Weidmüller)
AI 0,34-8 TQ (For AWG22), AI 0,5-8 WH (For AWG20)
AI-TWIN2×0,5-8WH (For AWG20, For 2 wires)(Phoenix Contact)

0 to 55˚C: FT1A-M (Monochrome LCD models)-20 to 55˚C: FT1A-C (Color LCD models) (No freezing)

Relative

10 to 95% RH (No condensation)

Storage Temperature-20 to +60˚C:(No freezing)

Storage Humidity

10 to 95% RH (No condensation)

Altitude0.25N-mOperation: 0 to 2,000m
Transport: 0 to 3,000m

Pollution Degree2

Corrosion Immunity

Free from corrosive gases

Function
Send Data
Receive Data
Request to Send
Clear to Send
Signal Ground
Send Data (+)
Send Data (-)
Receive Data (+)
Receive Data (-)

No.1

Communication type

● Electrical Specifications

No.9● Communication I/F plug
(Attached to the Touch) 1● Mounting clips 2● I/O Terminals

Applicable
cable

FT1A-*12RA
AWG16 to AWG22
Stripped wire length 6.5 mm,coating diameter ø3.4 mm or lower (Solid wire)

Recommended
ferruleH0,34/12 TK (For AWG22, For 1 wire)
H0,5/14D W, H0,5/14 OR(For AWG20, For 1 wire)
H0,75/14D GR, H0,75/14W、H1,0/16D R,
H1,0/16GE (For AWG18, For 1 wire)
H0,75/16D ZH GR, H0,75/16 ZH W
(For AWG18, For 2 wire)
H1,5/16D SW, H1,5/16R(For AWG16, For 1 wire) (Weidmüller)
AI 0,34-8 TQ (For AWG22, For 1 wire)
AI 0,5-8 WH (For AWG20, For 1 wire)
AI 0,75-8 GY, AI 1-10 RD (For AWG18, For 1 wire)
AI-TWIN 2×0,75-10 GY (For AWG18, For 2 wire)
AI 1,5-10 BK (For AWG16, For 1 wire)(Phoenix Contact)Type● USB Clamp Band 2● FT1A-*12RA

FT1A-*12RA

Type

Note:
The Touch is not equipped with terminating resistance. When using the RS422/485 interface, insert
terminating resistance with the appropriate value (around 100 to 120 Ω) between terminal No. 8 (RDA)
and terminal No. 9 (RDB) as required.

● USB Cable Lock Pin 2

IEC/EN 61131-2:2007*1: When using the Touch as the EMC Standard Approved Products, attach a ferrite core
(ZCAT3035-1330 manufactured by TDK Corporation) to the power cables and the communication cables.
If there a risk of an error occurring due to noise, install the product separated from sources of noisesuch as power lines, high voltage lines, and load lines. Also attach a ferrite core to the I/O cable(ZCAT3035-1330 manufactured by TDK Corporation).

Operating Temperature

I/O
OUT
IN
OUT
IN
OUT
OUT
IN
IN

Name
SD
RD
RS
CS
SG
SDA
SDB
RDA
RDB

UL508, CSA C22.2 No.142 (c-UL)

EMC Standard*1

FT1A-*14KA/14SA

Rated Voltage

24V DCPower Consumption

9.2W max.
When USB2 is unused: 5.8W max.

Power Voltage Range

20.4 to 28.8V DC

Allowable Momentary PowerInterruption

10 msec max.

11.0W max.
When USB2 is unused: 8.1W max.

50A max.

● FT1A-*12RA

All dimensions in mm.

FT1A-*14KA/14SA
AWG20 to AWG22
Stripped wire length 5 mm,coating diameter ø2.6 mm or lower (Solid wire)
H0,34/12 TK (For AWG22, For 1 wire)
H0,5/14D W, H0,5/14 OR(For AWG20, For 1 wire)
H0,5/14D ZH W、
H0,5/14 ZH OR(For AWG20, For 2 wire)(Weidmüller)
AI 0,34-8 TQ (For AWG22, For 1 wire)
AI 0,5-8 WH (For AWG20, For 1 wire)
AI-TWIN2×0,5-8WH(For AWG20, For 2 wire)(Phoenix Contact)

Tightening Torque

0.5 to 0.6N-m

0.2N-mScrewdrive

SZS 0.6×3.5 (Phoenix Contact)

SZS 0.4×2.5 (Phoenix Contact)<Cable Attached Dimensions>

Terminal Arrangement (Terminal Arrangement and I/O Wiring Diagrams)● FT1A-*12RA
Power supply terminal● FT1A-*14KA/14SA
1 SD
5 SG

● FT1A-*14KA/14SA

Port

9 RDB

Ry OUTDC IN

Q0 COM0

Q1 COM1Q2 COM2Q3 COM3

L

L

L

L

I0

I1

I2

I3

I4

I5

I6

2-wireSensor

I7

Analog voltage
output device
77.0

Caution notices are used where inattention might cause personal injury or damage to equipment.

● Serial Interface (Port)

Safety Standard: Fuse● FT1A-*14KA

65.5

Confirm that the delivered product is what you have ordered. Read this instruction sheet to make sureof correct operation. Make sure that the instruction sheet is kept by the end user.
This manual is the instruction sheet of the SmartAXIS Series FT1A Touch.
Unless otherwise specified, SmartAXIS refers to the SmartAXIS Series FT1A Touch.

Make sure to turn off the power to the Touch before wiring each interface.
Always use ferrules when wiring stranded wire and multiple wires to the terminal block. Otherwise there
is a risk of wires becoming disconnected.

L : Load
116.0

4.0

54.9
(58.9)

Power supply terminal

104.5

1 SD
5 SG

Port

9 RDB

No.

Name

Description
FT1A-*12RA

FT1A-*14RA/14SA

Tr. OUT

DC IN

Analog OUT

Q0

Q1

Q2

V
Q3 COM(-) (+)

L

L

L

L

AQ0
(+)

AQ0
(-)

AQ1
(+)

AI0 AI0 AI1 AI1(+) (-) (+) (-)
AQ1
(-)

I0

I1

I2

Analog voltage/ Analog voltage/current input
current input
devicedevice(1)

Display(2)

Touch Panel(3)

Power Supply Terminal(4)

Serial Interface (Port)

RS232C, RS422/485 Connector: Terminal Block 9 pin(5)Ethernet Interface(Ethernet)

IEEE802.3u
10BASE-T/100BASE-TX Connector: RJ-45(6)

USB Interface (USB1)

USB2.0 (Device) Connector: Mini-B

1 SD

(7)

USB Interface (USB12)

USB1.1 (External device) Connector: TypeA

5 SG

(8)

Output (Q0 to Q3)
Terminal (Q0 to Q3, AQ0 to AQ1)

Relay output (10A)(9)

Input Terminal (I0 to I7)

Digital input, Analog input(10)

Slot 1(11)

Slot 2

I3

I4

I5

I6

Optional device (Sold separately)
Digital, Analog I/O cartridge

1530

Analog voltage/current input device

2-wireSensor: FuseTransistor output, Analog output<Cable Attached Dimensions>

I7

L : Load● FT1A-*14SA

20
50

FT1A Series● Applicable Standards

RS485/422

INSTRUCTION SHEETFor applications which require clock accuracy, adjust the clock periodically.
● Do not install the Touch in areas subjected to strong ultraviolet rays, since ultraviolet rays may impair
the quality of the LCD.
● Do not attempt to disassemble, repair or modify the Touch. This can create the risk of fire or electrocution.
● When disposing of the Touch, do so as an industrial waste.
● Do not switch off the power or pull out the USB Flash Drive while it is being accessed, as this may
result in destruction of the stored data. If the data on the USB Flash Drive is corrupted, format the
USB Flash Drive.
● Handling of Batteries and Devices with Built-in Batteries in EU Member StatesNote) The right symbol mark is for EU countries only and is according to the directive
2006/66/EC Article 20 information for end-users and Annex II.
This symbol mark means that batteries and accumulators, at their end-of life,
should be disposed of separately from your household waste.
If a chemical symbol is printed beneath the symbol shown above, this chemical
symbol means that the battery or accumulator contains a heavy metal at a certain concentration.
This will be indicated as follows :Hg : mercury (0.0005%), Cd : cadmium (0.002%), Pd : lead (0.004%)
In the European Union there are separate collection systems for used batteries and accumulators.
Please dispose of batteries and accumulators correctly in accordance with each country or local
regulation.
● Regarding the Marine Standard Approved
This product (FT1A-*14KA/SA and FT1A-*12RA (FT1A Version V120 or later)) complies with thefollowing the Marine Standard.
- ABS (American Bureau of Shipping), DNV GL (DNV GL AS), LR (Lloyd’s Register of Shipping), NK(Nippon Kaiji Kyokai) (Regarding the usable area, environment, please contact us.)- When using this product as the Marine Standard Approved Products, attach a ferrite core
(ZCAT3035-1330 manufactured by TDK Corporation) to the power cables (2 turns), the cable foreach communication port (2 turns). And attach a ferrite core (ZCAT3035-1330 manufactured by TDK
Corporation) to the cable for communication cartridge (2turns).
● Recommended continuous turn on time is 15 hours when first use or did not turn on for a long time.
When battery charging and discharging is repeated without that, battery life becomes shorter than thespecification value.

RS232C

B-2073 (3)Power supply terminal

Port

9 RDB

Tr. OUT

Q0

Q1

Q2

V
Q3 COM(+) (-)

L

L

L

L

DC IN

Analog OUT
AQ0
(+)

AQ0
(-)

AQ1
(+)

AI0 AI0 AI1 AI1(+) (-) (+) (-)AQ1(-)

Analog voltage/ Analog voltage/current input
current input
devicedevice

I0

I1

I2

I3

I4

2-wireSensor

I5

I6

I7

Analog voltage/current input device: FuseL : Load

Depending on the type of connection cable used the dimensions shown above will change.
The dimensions given here are intended for reference only.

● Operating Environment
For designed performance and safety of the Touch, do not install the Touch in the following environments:● Where dust, briny air, or iron particles exist.
● Where oil or chemical splashes for a long time.
● Where oil mist is filled.
● In direct sunlight.
● Where strong ultraviolet rays exist.
● Where corrosive or combustible gasses exist.
● Where the Touch is subjected to shocks or vibrations.
● Where condensation occurs due to rapid temperature change.
● Where high-voltage or arc-generating equipment (electromagnetic contactors or circuit protectors)
exists in the vicinity.

● Installation● Make a panel cut-out on the panel with the dimensions shown below.

All dimensions in mm.

B
A
A

66.0

B
+1.0
0

Panel Cut-out
+1.0
0

105.0

1.0 to 5.0● The Touch has the mounting clip positions not only on the top and bottom side (0.3 to 0.35 N-m).
TOP● Ambient Temperature● Allow sufficient space for ventilation, and install the equipment away from heat sources.
● Allow at least 100mm between the Touch and walls or other equipment.
● Do not install the Touch where the ambient temperature exceeds the rated operating ambient
temperature range. When mounting the Touch in such locations, provide a forced air-cooling fan or
air-conditioner to keep the ambient temperature within the rated temperature range.
● The Touch is designed to install on a vertical plane so that natural air-cooling is provided. If you install
it using any other orientation, use forced-air cooling, or lower the ambient operating temperature.

Mounting Clip
Panel

● Derating● FT1A-*12RA
When using the Touch at an ambient temperature of 45°C or higher, reduce the output current of each
output terminal as shown in the figure below.

● Cautions when connecting external devices
The Touch power supply is non-isolating. Interference or external noise from external devices due towiring may cause adverse effects on the internal circuits of the Touch or external devices.
To prevent such damage, choose a proper solution depending on your system setup.
● Use a separate earth ground from the external noise source device.
● The wire for grounding should be thick and short in order to direct the noise from the noise source
device to the earth ground.
● Use a separate power supply from the external noise source device.
● Insert an isolator on the communication line of the Touch and the non-isolated communication device(i.e. PLC) to prevent damage.

● System Mode
Press the System Mode at the top of the Maintenance Screen. The Top page Screen appears.

● Cautions for using the Touch connected to a personal computer
When connecting the Touch to a computer via the Serial Interface (Port) or USB Interface, the Touch or
the computer may break down depending on the conditions of the computer. Make sure of the following
cautions, in order to prevent an accident.
● If the computer has a 3-pin power plug or power plug with a ground lead type.
Make sure to use a plug socket including a ground input electrode or ground the earth lead, respectively.
● If the computer has a 2-pin power plug without ground lead, follow the procedure below whenconnect the Touch to the computer.
(1) Pull out the power plug of the computer from the AC outlet.
(2) Connect the Touch to the computer.
(3) Insert the power plug of the computer into the AC outlet.

Initial Setting, Self Diagnosis and Initialization of the data, etc can be executed in the System mode.

When using the USB interface (USB1, USB2), attach the USB cable lock pin to prevent disconnecting
the USB cable from the Touch.

[Installed upright in landscape orientation](1) Insert the USB cable into the USB port.

Output Current

BOTTOM
Mounting Clip Position

10A(2) Strain the “Edge part” of the USB cable lock pin, and insert the “Edge part” to the 2 holes upper theUSB port.

1A
0

45°C

50°C

Ambient Temperature

55°C

Note:
If operating the Touch in a high-temperature environment, reducing the brightness of the backlight canhelp to limit the temperature rise of internal components.
The relationship between ambient temperature, the output current of each output terminal, andbrightness is approximately as shown in the figure below.

● Do not tighten excessively, otherwise the Touch may warp and cause wrinkle on the display, or impair
the waterproof characteristics.
● If the mounting clips are tightened obliquely to the panel, the Touch may fall off the panel.
● When installing the Touch into a panel cut-out, make sure that the gasket is not twisted. Especiallywhen re-installing, take special care because any twists in the gasket will impair the waterproof
characteristics.
● Even in the panel thickness range, there is a risk that the waterproof characteristics cannot be
maintained due to the panel materials and size.
● Orientation
The Touch is designed to install on a vertical landscape. If you install it with any other orientation,
confirm the limitations about operating temperature.

Output Current10A
Output Current5A

Brightness
100%

Output Current1A

Output terminal not used

OperatingTemperature

50%

FT1A-M
Monochrome LCD
models0 to 55°C

0 to 50°C

0 to 55°C

0 to 55°C

0 to 50°C

FT1A-C-20 to 55°C -20 to 50°C
Color LCD models (No freezing) (No freezing)-20 to 55°C
(No freezing)-20 to 55°C
(No freezing)-20 to 50°C
(No freezing)

Portrait
Portrait
Landscape(Clockwise) (Counter Clockwise) (Rotated 180°)

Horizontal

Landscape
0

35°C

45°C

50°C

55°C

Ambient Temperature

Edge Part● Adjusting the Brightness and Contrast
The brightness and contrast of the Touch display can be adjusted on the Adjust Brightness/Contrast
Screen. Adjust the brightness and contrast to the best condition as required.
(1) Press the Brightness (color LCD models) or Brightness/Contrast (monochrome LCD models) on the
Maintenance Screen. The Adjust Brightness/Contrast Screen appears.
Color LCD models

Monochrome LCD models(2) Press << and >> at the bottom the Adjust Brightness/Contrast Screen to adjust the contrast to the
optimal setting.
Color LCD models

Monochrome LCD models

Clamp part
(3) Press × to close the Adjust Brightness/Contrast Screen.
To adjust the brightness and Contrast in the System Mode, use << and >> located at the bottom of
the Top Page.
Top Page (Color LCD models)Note:Fasten the USB clamp band without the space between the clamp part and it, and the inclination.
OK

Note:
Since contrast adjustment is not possible on color LCD models, the contrast adjust function is not
displayed.

NG● Adjusting the Touch Panel(1) A gap may be caused in the operation accuracy of the touch panel by the secular distortion, etc.
Adjust the touch panel according to the following procedure when there is a gap in the operation of
the touch panel.
Press Main Menu on Top Page in System Mode. The Main Menu appears.

Orientation● FT1A-*14KA/14SA
When used at ambient temperatures of 40°C or higher, limit the usage of analog current output and theanalog cartridge as shown in the figure below.
Power Voltage
Range

Touch Analog Output

Cartridge

OperatingTemperature

20.4 to 24V DC

Voltage/current output
cannot be used

Voltage output (FC6A-PK2AV)/
current output (FC6A-PK2AW) cannot be used

55°C

20.4 to 28.8V DC

Current output
cannot be used

Voltage output (FC6A-PK2AV)/
current output (FC6A-PK2AW) cannot be used

50°C

20.4 to 28.8V DC

No restrictions

Voltage output (FC6A-PK2AV)/
current output (FC6A-PK2AW) cannot be used

45°C

20.4 to 28.8V DC

Current output
cannot be used

Current output (FC6A-PK2AW) cannot be used

45°C

No restrictions

No restrictions

40°C

Power Supply Voltage: 20.4 to 28.8 V
Unit Analog: No restrictions,
Cartridge: No restrictions

Brightness
100%

Top Page (Color LCD models)

10%
30°C

40°C

50°C

55°C

Maintain and inspect the Touch periodically to ensure the best performance.
Do not disassemble, repair, or modify the Touch during inspection.
● Turn off the power supply before wiring.
● Make the wiring as short as possible and run all wires as far away as possible from high-voltage andlarge-current cables. Follow all the procedures and precautions when wiring the Touch.
● Separate the Touch power supply wiring from the power lines of I/O devices and motor equipment.
● Ground the functional earth terminal to make sure of correct operation.
● Always use ferrules when wiring stranded wire and multiple wires to the terminal block. Otherwise
there is a risk of wires becoming disconnected.
● Power Supply Terminal● Pin assignment is shown in the following table.
+-

Power supply 24V DC (+24V)
Power supply 0V (0V)
Functional Earth (FE)Ambient Temperature

Note:
If operating the FT1A-*14KA/14SA in a high-temperature environment, reducing the brightness of thebacklight can help to limit the temperature rise of internal components.
The relationship between ambient temperature and brightness is approximately as shown in the figure
below.
The values shown above may vary with individual products. Please use this information as a referenceat the time of design.

Top Page (Monochrome LCD models)

When installing the Touch in a diagonal, the limitations are same as a horizontal.
Confirm the visibility of the display in a final installation.

Power Supply Voltage: 20.4 to 24 V
Unit Analog Output: Cannot be used,
Cartridge: Voltage/current output cartridge cannot be used40%

Top Page (Monochrome LCD models)Upper HolesThe values shown above may vary with individual products. Please use this information as a referenceat the time of design.

0

Top Page (Monochrome LCD models)(3) Fasten the USB clamp band around the USB cable and the clamp part, secure them tightly.

5A

20.4 to 28.8V DC

Top Page (Color LCD models)● Use applicable cables for wiring and recommended ferrules (made by Weidmüller or Phoenix
Contact) as follows.
Applicable cable

Recommended
ferruleTightening Torque

AWG16 to AWG22, Stripped wire length 7 mm (Solid wire)
H0,34/12 TK (For AWG22), H0,5/14D W、H0,5/14 OR (For AWG20)
H0,75/14D GR, H0,75/14 W, H1,0/14D R, H1,0/14 GE (For AWG18)
H1,5/14D SW, H1,5/14 R (For AWG16)
H0,5/14D ZH W, H0,5/14 ZH OR (For AWG20, TWIN Pressure Terminal)
H0,75/14D ZH GR, H0,75/14 ZH W (For AWG18, TWIN Pressure Terminal)（Weidmüller）
AI 0,34-8 TQ (For AWG22), AI 0,5-8 WH (For AWG20)
AI 0,75-8 GY (For AWG18), AI 1-8 RD (For AWG18), AI 1,5-8 BK (For AWG16)
AI-TWIN 2×0,5-8 WH (For AWG20, TWIN Pressure Terminal)
AI-TWIN 2×0,75-8 GY (For AWG18, TWIN Pressure Terminal)（Phoenix Contact）
0.5 to 0.6N-m

Display

Wipe any stain of the display using a soft cloth slightly dampened with neutral
detergent or alcoholic solvent.
Do not use solvents such as thinner, ammonia, strong acid, and strong alkaline.

Terminals,
Connectors

Check the terminals and connectors to make sure of no loose screws,
incomplete insertion, or disconnected lines.

Mounting Clips

Make sure that all mounting clips and screws are tightened sufficiently.
If the mounting clips are loose, tighten the screw to the recommended tightening torque.

Backlight

The Touch backlight cannot be replaced by the customer.
When the backlight needs to be replaced, contact IDEC.

Touch Panel

A gap may be caused in the operation accuracy of the touch panelby the secular distortion, etc. Adjust the touch panel according to the following
procedure when there is a gap in the operation of the touch panel.

● Maintenance Screen
Turn on the power to the Touch, then press and holdthe upper-left corner of the screen for three seconds or longer.
Press and hold 3
The Maintenance Screen appears on the screen.
or more seconds

Maintenance Screen (Color LCD models)(2) Press Init Set, Initialize, and then Touch PnlAdj. The confirmation screen appears andasks “Touch Panel setting?” is displayed. Press Yes.
The Touch Panel Adjust Screen is displayed.

(3) Press the center of the ×, then the position of the symbol changes one after another. Press fivesymbols sequentially.

Press the center o f
the symbol.

Touch

Note:
When pressing the ×, make sure to press the center of the symbol. This will ensure the accuracy of thetouch panel operation.
(4) When normally recognized, the confirmation screen of (2) is restored.
At step (3), when pressing a point away from the center of the ×, a recognition error will result. Thenthe × returns to the initial position, then repeat the step of (3) again.

Maintenance Screen (Monochrome LCD models)SmartAXIS User’s manual can be downloaded from https://us.idec.com/c/SmartAXIS_FT1A

http://www.idec.com● Permission to show the Maintenance Screen can be set using the configuration software.
Refer to the User’s Manual for details.
● The Maintenance Screen is not displayed in the System Mode.

Manufacturer: IDEC CORPORATION, 2-6-64 Nishimiyahara, Yodogawa-Ku, Osaka 532-0004, Japan
EU Authorized Representative: APEM SAS
55, Avenue Edouard Herriot BP1, 82303 Caussade Cedex, France
UK Authorized Representative: APEM COMPONENTS LIMITED
Drakes Drive, Long Crendon, Buckinghamshire, HP18 9BA, UK
2023.09