®

with EcoSystem® Control Unit
Installation and Operation Guide

Please Read

The GRAFIK Eye® QS with EcoSystem®
control unit allows for control of both lights
and shades, without interfaces, using
a single control unit. Features include
pushbutton scene recall, info screenthat displays energy savings and status,
IR receiver, astronomic timeclock, contact
closure input, and engravable backlit
buttons that are easy to find and operate.
The built-in EcoSystem® bus link cancontrol up to 64 EcoSystem® devices.

LUTRON

Model Numbers: QSGRJ-6E, QSGRJ-8E, QSGRJ-16E
QSGR-6E, QSGR-8E, QSGR-16E
Unit Capacity (watts)
MLV
Zone Capacity (watts)
MLV

120 V~ 50/60 Hz

220 - 240 V~ 50/60 Hz

2000 W

3000 W

2000 VA / 1600 W

3000 VA / 2400 W

25 – 800 W

40 – 1200 W

25 – 800 VA / 25 – 600 W

40 – 1200 VA / 40 – 960 W

See page 7 for EcoSystem® bus ratings; see page 8 for IEC PELV/NEC® Class 2 ratings.
For California residents only:
The batteries in these devices contain
Perchlorate Material – special handling may apply.
For more information visit
www.dtsc.ca.gov/hazardouswaste/perchlorate
EnglishEspañol

Français

Contents
Features and Functions of the
GRAFIK Eye® QS with EcoSystem®
Control Unit . . . . . . . . . . . . . . . . . . . . . . . . . . . . 3
Wiring the GRAFIK Eye® QS with EcoSystem®
Control Unit
Overview of Line Voltage/Mainsand EcoSystem® Wiring . . . . . . . . . . . . . . . . . . . . . 4
Line Voltage Wiring Details. . . . . . . . . . . . . . . . . . . 5
EcoSystem® Bus Wiring Details . . . . . . . . . . . . . . . 7
Overview of IEC PELV/NEC® Class 2 Wiring . . . . . 8
QS Link Control Wiring Details. . . . . . . . . . . . . . . . 9Powering More Than 3 Wallstations Example. . . 10

Completing Installation of the
GRAFIK Eye® QS with EcoSystem®
Control Unit . . . . . . . . . . . . . . . . . . . . . . . . . . . 11
General Functionality . . . . . . . . . . . . . . . . . . . 12
Pre-Programmed Button Functionality . . . . . 13
Zone Button Operation
Zone LED Displays for % of Lighting Levels . . . . 14

Programming Mode
Entering and Exiting Programming Mode . . . . . . 15
Navigating Menus in Programming Mode . . . . . . 15
Wireless Mode. . . . . . . . . . . . . . . . . . . . . . . . . 16
FCC Information . . . . . . . . . . . . . . . . . . . . . . . . . . 16

Zone Setup
Assigning Load Types. . . . . . . . . . . . . . . . . . . . . . 17
Assigning Non-Dim Load Types. . . . . . . . . . . . . . 17
Setting Load Types . . . . . . . . . . . . . . . . . . . . . . . . 18
Setting High End or Low End Trim. . . . . . . . . . . . 19
Setting Minimum Level (optional). . . . . . . . . . . . . 19
Labeling a Zone (optional) . . . . . . . . . . . . . . . . . . 20

Scene Setup
Setting Zone Levels, Fade Rates,
and Shade Group Actions . . . . . . . . . . . . . . . . . . 21
Labeling a Scene (optional) . . . . . . . . . . . . . . . . . 22
Enabling/Disabling Daylighting in a Scene . . . . . 22

Setting Save Mode
Save Mode Settings . . . . . . . . . . . . . . . . . . . . . . . 23
Quick Scene Programming:
Save by OK Mode . . . . . . . . . . . . . . . . . . . . . . . . . 23

Contact Closure Input (CCI) Setup. . . . . . . . . 29
Occupancy Sensor Setup . . . . . . . . . . . . . . . . 31
Associating Wireless Occupancy Sensors . . . . . 32
Selecting the Mode . . . . . . . . . . . . . . . . . . . . . . . . 33
Scene Mode . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 34
Zone Mode . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 35
Labeling an Occupancy Sensor (optional). . . . . . 36
Configuring Occupancy Sensor Settings(optional) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 37

Daylight Sensor Setup . . . . . . . . . . . . . . . . . . 38
Associating Wireless Daylight Sensors . . . . . . . . 39
Assigning the Mode . . . . . . . . . . . . . . . . . . . . . . . 40
Zone Mode . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 41
Group Mode . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 42
Labeling a Daylight Sensor (optional) . . . . . . . . . 44

Pico® Wireless Control Setup . . . . . . . . . . . . . 45
Associating with a GRAFIK Eye® QS
Wireless Control Unit . . . . . . . . . . . . . . . . . . . . . . 46
Associating through a QS Sensor Module . . . . . 47

IR Setup . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 48
Enabling/Disabling the IR Receiver . . . . . . . . . . . 49
Associating the QS IR Eye with a
GRAFIK Eye® QS Control Unit . . . . . . . . . . . . . . . 50
Associating through a QS Sensor Module . . . . . 52

Associating Sivoia® QS Shades/Drapes
and GRAFIK Eye® QS Control Units . . . . . . . . 53
Adjusting Shade Settings
Setting Limits. . . . . . . . . . . . . . . . . . . . . . . . . . . . . 54
Preset Adjustment: Simple Method . . . . . . . . . . . 55
Preset Adjustment: Advanced Method . . . . . . . . 55
Naming a Group of Shades . . . . . . . . . . . . . . . . . 56
Enable/Disable “Stop If Moving”
Functionality . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 57

Timeclock Operation
Setting Time and Date . . . . . . . . . . . . . . . . . . . . . 61
Setting Location . . . . . . . . . . . . . . . . . . . . . . . . . . 62
Setting Daylight Saving Time . . . . . . . . . . . . . . . . 62
Adding an Event . . . . . . . . . . . . . . . . . . . . . . . . . . 63
Deleting an Event . . . . . . . . . . . . . . . . . . . . . . . . . 64
Viewing an Event . . . . . . . . . . . . . . . . . . . . . . . . . . 64
Setting a Holiday . . . . . . . . . . . . . . . . . . . . . . . . . . 65
Viewing a Holiday . . . . . . . . . . . . . . . . . . . . . . . . . 65
Deleting a Holiday . . . . . . . . . . . . . . . . . . . . . . . . . 65
Copying a Schedule . . . . . . . . . . . . . . . . . . . . . . . 66
Deleting a Schedule . . . . . . . . . . . . . . . . . . . . . . . 66

Afterhours . . . . . . . . . . . . . . . . . . . . . . . . . . . . 67
Afterhours Examples. . . . . . . . . . . . . . . . . . . . . . . 68
Setting Up Afterhours . . . . . . . . . . . . . . . . . . . . . . 69
Ending Afterhours . . . . . . . . . . . . . . . . . . . . . . . . . 69

Diagnostics and Special Settings
Enabling/Disabling the Timeclock . . . . . . . . . . . . 70
Enabling/Disabling the Backlighting . . . . . . . . . . 70
Diagnostics . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 70
Setting the Security Password . . . . . . . . . . . . . . . 71

Language Selection. . . . . . . . . . . . . . . . . . . . . 72
Faceplate Removal . . . . . . . . . . . . . . . . . . . . . 72
Troubleshooting . . . . . . . . . . . . . . . . . . . . . . . 73
Troubleshooting: Wireless Functions. . . . . . . 74
Troubleshooting: Shade Functions . . . . . . . . 75
Troubleshooting: EcoSystem® Functions. . . . 76
Warranty . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 77
Contact Information . . . . . . . . . . . . . . . . . . . . 77

Associating Sivoia® QS Triathlon® Shades
with GRAFIK Eye® QS Control Unit . . . . . . 58
Setting Upper and Lower Limits of a Sivoia®
QS Triathlon® Shade with GRAFIK Eye® QSControl Unit . . . . . . . . . . . . . . . . . . . . 59
Associating Multiple GRAFIK Eye® QSControl Units . . . . . . . . . . . . . . . . . . . . . . . . . . 60

EcoSystem® Setup
Building the System . . . . . . . . . . . . . . . . . . . . . . . 24
Assigning/Unassigning an EcoSystem® Device
to a Zone . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 25
Addressing EcoSystem® Devices. . . . . . . . . . . . . 26
Reset Missing Ballast Addresses. . . . . . . . . . . . . 27
Diagnostics . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 28®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 2

Features and Functions of the GRAFIK Eye® QS with EcoSystem® Control Unit
Hinged faceplate
Page button
Switches between displaying
zones 1 to 8 and 9 to 16 on
16-zone unit

Zone numbers

1 9

2 10

3 11

4 12

5 13

Zone raise/lower buttons
Zone LEDs display current
lighting zone levels

6 14

7 15

Master buttons
Temporarily raise and lower
lighting levels on unit

8 16

9-16
1-8

OK

Note: Zones 1, 2, and 3 areintegral line voltage dimmingzones that can control line
voltage loads. Remaining zones
are EcoSystem® zones only.
Zones 1, 2, and 3 can be either
EcoSystem® zones or line voltage
zones (no zone can be both)“OK” button
Used for programming
Timeclock button
Displays current
timeclock info
Infrared receiverFor handheld remote use
Scene buttons
With integral scene
indicator LEDs

Optional Shadebutton groups
Preset and raise/lower
buttons with integral LEDs
(maximum of 3 button
groups)Hinged faceplate

Info screen
Displays status orprogramming functions

USB type mini B
For programming via PC

Note: 6-zone control unit will show only zones 1 through 6.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 3

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
Overview of Line Voltage/Mains and EcoSystem® Wiring
Two E1 and two E2 connections areprovided for ease of wiring, and toprovide two connecting points; there is
only one EcoSystem® link on the unit.
Note: Ballasts and other EcoSystem®
devices must NOT obtain power from aline voltage output on the GRAFIK Eye®
QS with EcoSystem® control unit.
EcoSystem® Bus Wiring(See the bus wiring details section forcomplete specification)
Two 16 AWG (1.5 mm2)
each terminal
Line Voltage/Mains
Cables and Load Wiring
12 AWG (4.0 mm2)
each terminal
L
N

E2
E1

E2
E1

EcoSystem® devices:ballasts, drivers, or interfaces
LN

To additional
EcoSystem® devices

Distribution
Panel

Terminal labels:
L: Hot/Live
N: Neutral: Ground120 - 127 V~or
220 - 240 V~
Distribution
Panel
Incandescent load

1, 2, 3: Dimmed/Switchedline voltage outputs

Load controlled
by power module
or interface
Power module
or interface®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 4

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
Line Voltage Wiring Details• Use properly certified cable for all line
voltage/mains cables.
• Proper short-circuit and overload
protection must be provided at the
distribution panel. You can use up to a
20 A circuit breaker for your installation.
• Install in accordance with all local andnational electrical codes.
• IEC PELV/NEC® Class 2 terminals may
be temporarily unplugged for ease of IR,
occupancy sensor, and control wiring.
• Notice: Risk of damage to unit. Do notconnect line voltage/mains cable to IEC
PELV/NEC® Class 2 terminals.
Step 1: Install wallbox. Mount a 3½ in(89 mm) deep 4-gang U.S. wallbox on adry, flat indoor surface that is accessible
and allows for system programming andoperation. Allow at least 4½ in (110 mm)
clearance above and below the faceplate
to ensure proper heat dissipation. Allow
1 in (25 mm) for faceplate overhang on
all sides.
Note: 4-gang wallbox available from
Lutron; P/N 241400.

Step 2: Test load wiring.
• Turn power OFF at the circuit breaker orfuse box.
• Connect a standard light switch between
the live lead and load wire to test thecircuit.
• Turn power ON and check for short oropen circuits. If load does not operate,
the circuit is open. If the circuit breakertrips (fuse blows or opens), a load short
may exist. Correct short or open circuits
and test again.

Faceplate overhangs
wallbox on all sides;
allow 1 in (25 mm)
LUTRON4` in(110 mm)

Hot/Live

SwitchLoad

Neutral

Step 3: Check control unit wiring.
• Earth/ground terminal connection must
be made as shown in line voltage wiring
diagrams.
• Do not mix different load types on thesame zone.
• Follow all local and national electricalcodes when installing IEC PELV/
NEC® Class 2 wiring with line voltage/
mains wiring.
WARNING! Shock hazard. May
result in serious injury or death.
Always turn off circuit breaker or
remove main fuse from powerline before doing any work.
Before connecting the loads
to the GRAFIK Eye® QS with
EcoSystem® control unit, test theloads for short-circuits.

LUTRON(continued on next page)®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 5

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
Line Voltage Wiring Details (continued)
Step 4: Connect line voltage and loads
to control unit.
• Strip 9 in (8 mm) of insulation off the line
voltage/mains cables in the wallbox.

9 in(8 mm)• Connect the line voltage/mains, ground,and load wires to the appropriate
terminals on the back of the control unit.
L: Hot/Live
N: Neutral: GroundTerminals 1, 2, 3: Dimmed/Switchedline voltage outputs

The recommended installation torque is
5.0 in∙lb (0.6 N∙m) for line voltage/mains
connections and 5.0 in∙lb (0.6 N∙m) forthe earth/ground connection.
Note: See the zone setup section fora list of compatible load types andinstructions for programming the GRAFIK
Eye® QS with EcoSystem® control unit toproperly recognize them.

Notice: Risk of damage to unit. GRAFIK Eye® QS with EcoSystem® control units must
be installed by a qualified electrician in accordance with all applicable regulations andbuilding codes. Improper wiring can result in damage to control units or other equipment.

Note: To avoid overheating and possible damage to equipment, do not install control
units to dim receptacles, motor-operated appliances, or fluorescent lighting notequipped with LutronR Hi-lume®, Eco-10®, Tu-Wire®, EcoSystem® electronic dimmingballasts, or other EcoSystem® devices approved for your location. In dimmed magnetic
low-voltage circuits, you can prevent transformer overheating and failure by avoiding
excessively high current flow. Do not operate control units with any lamps removed
or burned out; replace any burned out lamps immediately; use only transformers thatincorporate thermal protection or fused primary windings. Control units are designed
for residential and commercial use, for indoor use only.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 6

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
EcoSystem® Bus Wiring Details
EcoSystem® bus wiring may beconsidered NEC® Class 1 or IEC PELV/
NEC® Class 2.
• NEC® Class 1: EcoSystem® bus wiring
may be run in the same conduit as mains
voltage wiring to fixtures.
• IEC PELV/NEC® Class 2: EcoSystem®
bus wiring must be separated from all
mains and NEC® Class 1 wiring.
• Consult applicable national and local
codes for compliance.
• Lutron recommends using two different
colors for E1 and E2 (EcoSystem® bus)
wires. This will prevent wiring mistakes
in junction boxes where several different
EcoSystem® bus wires combine. Use
the following instructions for wiring the
EcoSystem® bus.
• Each EcoSystem® link can have only
1 GRAFIK Eye® QS with EcoSystem®
control unit connected to it. No additional
EcoSystem® bus supplies can be on thelink.
• Up to 64 EcoSystem® devices can beconnected to the EcoSystem® link.
• No other devices may be connected to
the EcoSystem® link.
WARNING! Shock hazard. May
result in serious injury or death.
Do not wire live. Interrupt power
via circuit breaker before wiringand servicing the EcoSystem®
bus supply.

®

Step 1: Use the wire size chart at right todetermine which wire size to use basedon the length of the EcoSystem® bus.
Step 2: Wire the EcoSystem® busfrom terminal E1 and terminal E2 to all
EcoSystem® devices.

Wiring Size and Bus Length
EcoSystem® bus wires E1 and E2 are notpolarity sensitive. EcoSystem® bus length
is limited by the wire gauge used for E1
and E2 as follows:
Wire Gauge

Step 3: If wiring the EcoSystem® bus as
IEC PELV/NEC® Class 2, maintain proper
separation from mains and NEC® Class 1
wiring.

Maximum EcoSystem®
Bus Length

12 AWG(4.0 mm2)

2200 ft (671 m)

Step 4: Turn on circuit breaker toenergize.

14 AWG(2.5 mm2)

1400 ft (427 m)

16 AWG(1.5 mm2)

900 ft (275 m)

18 AWG(1.0 mm2)

570 ft (175 m)

EcoSystem® Bus
18 V-

250 mA

Note: Some EcoSystem® devices(ballasts, drivers, and interfaces)
accept connections to daylightsensors and occupancy sensors.
For instructions on installing andoperating these devices, refer totheir individual instruction sheets.
EcoSystem® bus wiring cables (16 AWG/
1.5 mm2) are available from Lutron, partnumbers C-CBL-216-GR-1 (non-plenum)and C-PCBL-216-CL-1 (plenum).

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 7

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
Overview of IEC PELV/NEC® Class 2 Wiring

1 2

IR Wiring
18 AWG (1.0 mm2)
each terminal
From external
IR connection(by others)

1: IR DATA
2: IR COM

Contact Closure Input Wiring
24 V- 50 mA
For settings, see CCI Mode Setup.
A B C

A: CCI SIG
B: 24 VC: CCI COM

QS Link Control Wiring
24 V- 100 mA

Example:Occupancy sensor(maximum 1)

18 AWG (1.0 mm2)
each terminal

A: CCI SIG
B: 24 VC: CCI COM

LUT-ELI-3PH
Example:Emergency lighting interface (maximum 1)

To control stations,shades, or other
GRAFIK Eye® QScontrol units

1 2 3 4A B C

Signal+V Input
Circuit Common

Common and power (terminals 1 and 2):
Two 18 AWG (1.0 mm2) each terminal (for link <500 ft/153 m)
Two 12 AWG (4.0 mm2) each terminal (for link 500-2000 ft/153-610 m)

Data (terminals 3 and 4):
Twisted, shielded pair 22 AWG (0.5 mm2)
each terminal

1: COM
2: 24 V-*
3: MUX
4: MUX*Do not connect terminal 2
between any GRAFIK Eye® QScontrol unit and any other power
supply, including another GRAFIK
Eye® QS control unit.
Refer to the QS Link Power Draw
Units specification submittal(LutronR P/N 369405) for more
information concerning PDUs.

Note: Use appropriate wire connecting devices
as specified by local codes.

Note: The GRAFIK Eye® QS control unit must
be powered by a Normal/Emergency
distribution panel for proper ELI
operation. Refer to the LUT-ELI-3PH
Installation Guide for the complete
wiring diagram.
®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 8

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
QS Link Control Wiring Details
T-Tap Wiring Example• System communication uses IEC PELV/NEC®
Class 2 wiring.
• Follow all local and national electrical codes when
installing IEC PELV/NEC® Class 2 wiring with line
voltage/mains wiring.
• Each terminal accepts up to two 18 AWG (1.0 mm2)
wires.
• Total length of control link must not exceed
2000 ft (610 m).
• Make all connections in the control unit’s wallbox.
• Wiring can be T-tapped or daisy-chained.
• IEC PELV/NEC® Class 2 24 V- 150 mA.
System Limits
The QS wired communication link is limited to
100 devices or 100 zones.
The GRAFIK Eye® QS control unit supplies
3 Power Draw Units (PDUs) on the QS link. Referto the QS Link Power Draw Units specification
submittal (LutronR P/N 369405) for more information
concerning Power Draw Units.

To EcoSystem® link 1
GRAFIK Eye® QS
with EcoSystem®
control unit

seeTouch® QSwallstation
LUTRON

QS smart
power
panel

To EcoSystem®
link 2

LUTRON

LUTRON

Sivoia® QS
shade/drape
LUTRON

LUTRON

Daisy-Chain Wiring Example
To EcoSystem® link 2

To EcoSystem® link 1
GRAFIK Eye® QS
with EcoSystem®
control unit

GRAFIK Eye® QS
with EcoSystem®
control unit

Sivoia®
QS
shade/drape
LUTRON

LUTRON

seeTouch® QSwallstations

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

QS smart
power panel

Wire Sizes (check compatibility in your area)
QS Link Wiring Length

Wire Gauge

LutronR Cable Part Number

Less than 500 ft (153 m)

Power (terminals 1 and 2); 1 pair 18 AWG (1.0 mm2)

GRX-CBL-346S (non-plenum)
GRX-PCBL-346S (plenum)

Data (terminals 3 and 4); 1 twisted, shielded pair 22 AWG (0.5 mm2)
Power (terminals 1 and 2); 1 pair 12 AWG (4.0 mm2)

Up to 2000 ft (610 m)

Data (terminals 3 and 4); 1 twisted, shielded pair 22 AWG (0.5 mm2)

GRX-CBL-46L (non-plenum)
GRX-PCBL-46L (plenum)

Notes:• For more information regarding LutronR cable specifications, please see LutronR P/N 369596 and P/N 369597 at www.lutron.com• For wire runs over 2000 ft (610 m), please contact LutronR Technical Support®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 9

Wiring the GRAFIK Eye® QS with EcoSystem® Control Unit (continued)
Powering More Than 3 Wallstations Example
The GRAFIK Eye® QS with EcoSystem® control unit can power up to 3 seeTouch® wallstations. An external 24 V- power supply isrequired to power more than 3 wallstations.
• The communication signals on the QS• The +24 VDC wire from the power supply • The Common wire from the power
supply connects to QS link terminal 1
link (terminals 3 and 4) connect fromconnects to QS link terminal 2 on all ofon all of the wallstations it is powering
the wallstations to the GRAFIK Eye® QS
the wallstations it is powering. This wire
and terminal 1 on the GRAFIK Eye® QScontrol unit on twisted, shielded cable
does not connect to terminal 2 on thecontrol unit.
just as when an additional power supply
GRAFIK Eye® QS control unit.
is not being used. Control unit shown inrear view.

LutronR cable
GRX-CBL-346S-500 (non-plenum) or
GRX-PCBL-346S-500 (plenum)
1 twisted pair
22 AWG(0.5 mm2)

seeTouch® QS wallstations
4
3
2
1

4
3
2
1

4
3
2
1

4
3
2
1

1 2

A B C

1 2 3 4GRAFIK Eye® QS with EcoSystem®
control unit (rear view)(1) 18 AWG(1.0 mm2)
Common
QSPS-P1-1-50(powers up to 8 seeTouch® QSwallstations)

To power source®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 10

Completing Installation of the GRAFIK Eye® QS with EcoSystem® Control Unit
7.9 in(200 mm)

1. Mount the control unit in the wallbox asshown using the four screws provided.
Note: Follow all local and national
electrical codes when installing
IEC PELV/NEC® Class 2 wiringwith line voltage/mains wiring.
2. Verify installation:• Restore power.
• Press the top scene button. The LED
will light.
• Press the zone raise and lower buttons.
Make sure the control unit is dimming all
connected loads.
3. Apply the protective overlay to thecontrol unit.

3.5 in(87 mm)3.75 in(95 mm)Wall

Note: When tightening mounting
screws, make sure that thehinged cover and faceplate
will open fully, as shown.

Protective overlay(apply after installation)®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 11

General Functionality
The info screen turns off 30 seconds after the last button press orcompletion of the last scene change. See example screens below.

OK

9-16
1-8

16

The Master buttons activate the info screen. These buttons
temporarily raise or lower all dimmable lights (except those
programmed as unaffected in the current scene). Adjustments
are temporary and do not affect scene programming.
Note: Master buttons affect all zones.

Scene 1The “OK” button activates the info screen (when off), which thenshows the current scene and its fade time. In “Save Always”
mode, it allows fade time adjustment. In “Save by OK” mode,pressing a second time allows zone adjustment; pressing athird time allows fade adjustment.

Scene 1The Timeclock button activates the info screen and displays thecurrent time and the next event scheduled to occur. Pressing
a second time displays the time, date, and afterhours status.
Pressing a third time displays location and sunrise/sunset times.
Pressing a fourth time displays the language selection screen.
Pressing once more returns to the first screen.

11:23 AM Fri

Master raise
Master lower

Master buttons
9-16
1-8

Page
buttonOK“OK” button

Timeclock(back) button

Adjust fade3

seconds

Next: 5:00 PM
Scene 1The Page button is on 16-zone units only. Pressing the Page button will toggle the unit
between page 1 (zones 1 through 8) and page 2 (zones 9 through 16). Two LEDs above
each zone LED bar indicate the unit’s current page. Upon switching pages, the LED bars
for all 8 zones of that page will show their level for the current scene.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 12

Pre-Programmed Button Functionality
The GRAFIK Eye® QS with EcoSystem® control unit controls most lighting loads without
special programming. Each unit ships with pre-programmed default settings for thescene and shade buttons. For load types other than those shown below (dimmableor non-dim), assign the load type before proceeding. See the scene setup section for
instructions on changing scene settings.
Scene Button Pre-Programmingfor Dimmable Loads
Scene 1: All zones to 100%
Scene 2: All zones to 75%
Scene 3: All zones to 50%
Scene 4: All zones to 25%
All zones Off

Shade Button Pre-Programmingfor Sivoia® QS shades
All shades fully open
All shades to 50%
All shades fully closed
Lower/Raise all shades(Applies only to units with shade keypads)®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 13

Zone Button Operation
Each zone column (LEDs and buttons)
represents one zone of lights. On 16-zone
units, the page button toggles between
zones 1 through 8 and zones 9 through
16. Page LEDs above each column will
indicate which zone is currently active on
the control unit. Pressing any button ona column turns on the info screen anddisplays the zone’s current light level andcurrent energy savings.

Zone LEDs
LEDs indicate
light level(see below)

1 9

2 10

2 10

3 11

4 12

5 13

3 11

Zone Raise
Zone Lower

Pressing the raise and lower buttons on azone causes different actions depending
on zone type (see below).
Dimmable zones:• Press and hold to raise/lower all lights in azone; release to stop
• Press raise or lower to stop a zone that isfading• Raising lights from off to full on or loweringfrom full on to off takes 5 seconds• Press raise and lower simultaneously totoggle between full on and off• Press and hold lower for 6 seconds after
the zone has gone to 0% light level to
set the zone as unaffected in the current
scene. The zone will not change when thisscene is initiated, and the Master buttons
will not raise/lower the zone in this scene.
Non-dim zones:• Press raise to turn zone on• Press lower to turn zone off

Zone LED Displays for % of Lighting Levels
Light Level
(%)

Off

1–17

18-33

34-49

50-66

67-82

83-99

On/
100

UA

Dimmable
Load Types
Non-Dim
Load Types
Legend:UA = Unaffected (lights are not affected byscene button or Master buttons)
LED onLED off

Note: To set zone types, see the zone
setup section.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 14

Programming Mode
Entering and Exiting Programming Mode
Entering programming mode:
Main menu
Press and hold the top and bottom scene
Timeclockbuttons simultaneously for 3 seconds. The
Scene setup
LEDs in the scene buttons will scroll from
top to bottom, confirming that you are in
programming mode, and the info screen
will display the main menu.
Exiting programming mode:
Scene 1Press and hold the top and bottom scene
Fade time
buttons simultaneously for 3 seconds. The
3 seconds
info screen will go to Scene 1.

16

Master buttons
9-16
1-8

OK

“OK” button
Timeclock (back) button
Press and hold the top andbottom buttons for 3 seconds
to enter or exit programmingmode

Navigating Menus in Programming Mode
Master Buttons
The Master buttons allow you to move through the menu
choices. The current choice is highlighted on the info screen.
OK Button
The “OK” button chooses the current highlighted menu choice.
This will either take you to the next menu or accept a setting you
have selected. When the screen displays a Yes/No question, the“OK” button is “Yes”.
Timeclock Button
The Timeclock button functions as a “back” button during
programming mode. Pressing the Timeclock button takes
you back one step in the current menu. Pressing it repeatedly
will eventually return you to the main menu, but will not exit
programming mode. When the screen displays a Yes/Noquestion, the Timeclock button is “No”.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 15

Wireless Mode
Many models of the GRAFIK Eye® QS control unit support wireless communication withother Lutron® products. This feature allows for easy integration of wireless sensors,
keypads, remotes, and shades for single-room wireless applications
Units supporting wireless communication are labeled “GRAFIK Eye® QS Wireless” on
the front label of the unit.
The wireless feature of the GRAFIK Eye® QS Wireless control unit has three (3) modesof operation.
• Ignore Programming (default): The GRAFIK Eye® QS Wireless control unit will only
respond to normal operation commands from wireless devices associated while in
Enabled mode.
• Disabled: Use for wired-only systems.
• Enabled (30 minutes): The GRAFIK Eye® QS Wireless control unit will respond to any
programming commands from nearby LutronR QS wireless (and compatible) products.
The GRAFIK Eye® will automatically revert to “Ignore Programming” mode if there is noactivity for 30 minutes.
Changing the wireless mode of the GRAFIK Eye® QS Wireless control unit:
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Wireless Mode” and press
Shade labelsthe “OK” button to accept.
Wireless Mode
3. Use the Master buttons to highlight the desired wireless mode,and press the “OK” button to accept.
4. The info screen will display a confirming “Saved” message.
Wireless Mode
5. Exit programming mode.
Enabled (30 minutes)

Note: The wireless signal has a range of 30 ft (9 m) throughstandard construction or 60 ft (18 m) line of sight.

SavedSaved

®

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

FCC Information
Changes or modifications not expressly approvedby Lutron Electronics Co. could void the user’s
authority to operate this equipment.
Note: This equipment has been tested andfound to comply with the limits for a Class B
digital device, pursuant to Part 15 of the FCC
rules. Operation is subject to the following: (1)This device may not cause harmful interference,and (2) this device must accept any interference
received, including interference that may cause
undesired operation.
These limits are designed to provide
reasonable protection against harmful interference
in a residential and commercial installation. Thisequipment generates, uses, and can radiateradio frequency energy and, if not installed andused in accordance with the instructions, maycause harmful interference to radio or television
reception. However, there is no guaranteethat interference will not occur in a particularinstallation. If this equipment does cause harmfulinterference to radio or television reception, which
can be determined by turning the equipment off
and on, the user is encouraged to try to correct
the interference by one or more of the following
measures:• Reorient or relocate the receiving antenna.
• Increase the separation between the equipment
and receiver.
• Connect the equipment into an outlet on acircuit different from that to which the receiver isconnected.
• Consult the dealer or an experienced radio/TV
technician for help.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 16

Zone Setup
16

Assigning Load Types
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight
CCI Setup“Zone setup” and press theZone setup“OK” button to accept.
3. Use the Master buttons to highlight“Load type”. Press the “OK” button
to accept. See “Setting Load Types”
Zone Setup
table on the next page.
Load Type
4. Use the zone raise/lower buttons
Non-Dim Load Typeto choose the load type for thatzone. See the list on the next pagefor supported load types. Press the“OK” button to accept.
Load Type5.
The info screen will confirm thatSet zones
your load type has been saved.
6. Exit programming mode.

Saved

®

Masterbuttons

9-16
1-8

1 9

OK

2 10

3 11

“OK” button

4 12

5 13

6 1

Use thezone
raise/lower
buttons tochoose theload type forthat zone.

Assigning Non-Dim Load Types
Zones assigned to non-dim loads have five available configurations:• LOFO: Last On, First Off
Main menu• FOFO: First On, First Off
CCI Setup• FOLO: First On, Last Off
Zone setup• LOLO: Last On, Last Off• 60/40: On at 60%, off at 40%
Scenes made up of both dim and non-dim
Zone Setup
load types will toggle the non-dim loads
before the dim loads in a “First” on/off
Load Typeconfiguration, and after the dim loads in a
Non-Dim Load Type
“Last” on/off configuration.
1. Enter programming mode.
2. Use the Master buttons to highlight “Zone
Load Typesetup” and press the “OK” button to accept.
Set zones
3. Use the Master buttons to highlight “Non-Dim
Load type”. Press the “OK” button to accept.
See “Setting Load Types” table on the next
page.
4. Use the zone raise/lower buttons to choose
the non-dim load type for that zone. (Zones
not programmed as non-dim will be displayed
Saved
as Unaffected.) Press the “OK” button to accept.
5. The info screen will confirm that your loadtype has been saved.
6. Exit programming mode.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 17

Zone Setup (continued)
Setting Load Types
Direct control via
GRAFIK Eye® QScontrol unitTo
EcoSystem®
link

Control via
power module orinterfacePowermodule orinterface

LUTRON
LUTRONZones
4 – 16Zones
1–3

Fixture load type

Choose this load type from the menu
on the GRAFIK Eye® QS control unit:

Incandescent

IncandescentPower module

MLV (magnetic low-voltage)

MLV

Power module

ELV (electronic low-voltage)—

Power module

Hi-Lume®/Eco-10®

—

Fluorescent module

0-10 V—

Fluorescent module

Non-dim lighting loads

Non-dimNon-dim

Neon/Cold cathodeNeon, CC

Neon, CC

Tu-Wire®

Tu-WireTu-WireAdvance Mark X®

Tu-WireTu-WireEcoSystem®

Digital load

—

DMX

—

DMX

RGB/CMY DMX—RGB/CMY DMX

EcoSystem® switching(e.g., XPJ)

Non-dim digital—

Cree LR4/LR6 LED

Cree LR4/LR6 LED

Fluorescent module

LED

Incandescent*Power module

EcoSystem®

Digital load

—

DMX

—

DMX

RGB/CMY DMX—RGB/CMY DMX

EcoSystem® switching (e.g., XPJ)

Non-dim digital—

Load Type Notes• All electronic low-voltage(ELV) lighting used with aninterface must be rated for reverse
phase control dimming. Before
installing an ELV light source,
verify with the manufacturer that
their transformer can be dimmed.
When dimming, an ELV interface(such as the PHPM-PA-DV-WH)
must be used with the control
unit.
• For all DMX or RGB/CMY DMX
lighting, an external DMX interface(such as the QSE-CI-DMX) must
be used with the control unit.
• Maximum total lighting load for
Lutron® Tu-Wire® and AdvanceMark X® electronic dimmingballasts (120 to 127 V~ only)
must not exceed 6 A per zone or
16 A per unit.
For non-EcoSystem® loads:• Not all zones must be connected;
however, connected zones musthave a minimum load:
120 - 127 V~: 25 W
220 - 240 V~: 40 W
• Maximum zone loads:
120 - 127 V~: 800 W
220 - 240 V~: 1200 W• Maximum total lighting load formagnetic low-voltage (MLV) varies
by input voltage:
120 - 127 V~: 800 VA / 600 W
220 - 240 V~: 1200 VA / 960 W* Use incandescent load type unless otherwise specified in the LED product selection tool available at www.lutron.com/ledtool.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 18

Zone Setup (continued)
Setting High End or Low End Trim
• If you are unsure about appropriate high and low end settings,
please contact LutronR Technical Support for assistance.
• High and low end trim settings limit the maximum and minimum
output of a dimming zone. Trim levels are set automatically when
the load type is programmed.
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight
CCI Setup“Zone setup” and press the “OK” button
Zone setup
to accept.
3. Use the Master buttons to highlight“High end” or “Low end” (this example
shows low end). Press the “OK” button toZone setup
accept.
High end
4. Use the zone raise/lower buttons to
Low end
set the high end or low end trim forthat zone. The info screen will display
each zone number and percentage as
you adjust it. Press the “OK” button to
Low endaccept.
Set zones
5. The info screen will confirm that yoursetting has been saved.
6. Exit programming mode.
Zone 2
10%

Saved

16

Masterbuttons

9-16
1-8

1 9

OK

2 10

3 11

“OK”
button

4 12

5 13

6 1

Use thezone
raise/lower
buttons to
set the highend or low
end trim forthat zone.

Setting Minimum Level (optional)
Some local regulations specify a minimum lighting level for
dimming zones in occupied buildings. If this pertains to you,follow these steps to set up your minimum lighting level.
1. Enter programming mode and selectZone setup“Zone setup,” then “Min level”. Press
Low endthe “OK” button to accept.
2. Use the Master buttons to highlight “Off”
Min level
if you want your lights to go all the way
off at their minimum light level, or “10%”if you want that to be the minimum light
Min level
level. Press the “OK” button to accept.
Note: Non-dim loads will turn off
Offregardless of the minimum level setting.
3. The info screen will confirm that yourminimum level has been saved.
4. Exit programming mode.
Saved

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 19

Zone Setup (continued)
16

Labeling a Zone (optional)
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Zone setup” and press
CCI Setupthe “OK” button to accept.
Zone setup
3. Use the Master buttons to highlight “Label” and press the“OK” button to accept.
4. Use the Master buttons to change the zone number to yourZone setup
desired zone. Custom zone labels will appear if previously set.
Press the “OK” button to accept.
Min level
5. Use the Master buttons to highlight “Custom” and press theLabel“OK” button to accept. Or, highlight “Default” to return thezone label to the default (e.g., Zone 1).
6. Use the Master buttons to scroll through the characters
Label zone
(lowercase and uppercase letters, plus numbers 0 through 9).
The character you are currently changing will be underlined
Zone 2on the screen. Press OK to select the character you want,then repeat for all available characters. Choose a space (nocharacter) and press OK for any remaining characters. Press
the “OK” button to accept.
Label zone 2
Note: Custom zone labels will always begin with the zone
number and a colon (e.g., 1: Uplights).
Custom
7. The info screen will confirm that your name has been saved.
8. Exit programming mode.
Note: On 16-zone units, use the page button to access all zones.
Label zone 2

9-16
1-8

MasterbuttonsOK“OK”
buttonPage button

1 / 11

A

1: A

Saved

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 20

Scene Setup
Setting Zone Levels, Fade Rates, and Shade Group Actions
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Scene setup” and press
Timeclockthe “OK” button to accept.
Scene setup
3. Use the Master buttons to highlight “Levels” to adjust lighting
and/or shade levels. Press the “OK” button to accept. Use theMaster buttons to highlight the scene number of your desired
Scene setup
scene. Press the “OK” button to accept.
Levels
4. Set each zone to the desired light level for this scene using
the zone raise/lower buttons. The info screen will display theLabelszone and percentage as you adjust it.
To set a zone as unaffected, lower the light levels all the way
Scene setup
to off, then hold the zone lower button for 3 seconds. The
screen will display “---” and the three middle LEDs for thezone will be lit to indicate this zone is unaffected by the scene
Scene 1(the zone will not change when this scene is initiated).
When all zones are at the desired level, press the “OK” button
to accept.
Scene 1
5. Use the Master buttons to set the fade time for this scene.
Set zones
Press the “OK” button to accept.
6.
Note: This step is applicable only if you have shades on your
3 seconds
system. If you do not have or do not wish to set shade groups
for this scene, press the “OK” button to skip this step.
Scene 1Set each shade group to the desired level for this scene.
Adjust fade
3 seconds

Scene 1
Set shadeGroupsWhen all shade groups are at the desired level, press the“OK” button to accept.
For shade programming, see the section on adjusting shadesettings.
7. The info screen will confirm that your scene has been saved.
8. Exit programming mode.

16

Masterbuttons

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

1 9

2 10

3 11

4 12

5 13

Shade
button group

2 10

3 11

Zone raise

Zone lower

Saved

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 21

Scene Setup (continued)
Labeling a Scene (optional)
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight
Timeclock“Scene setup” and press the
Scene setup“OK” button to accept.
3. Use the Master buttons to highlight“Labels” and press the “OK” button
Scene setup
to accept.
4.
Use the Master buttons to highlight
Levelsyour desired scene. Press theLabelsLabels“OK” button to accept.
5. Use the Master buttons tohighlight “Custom” and press the
Select scene:“OK” button to accept.
Scene 1
6. Use the Master buttons to scroll
through the characters (lowercase
and uppercase letters, plus numbers
0 through 9). The character you areLabel scene 1
currently changing will be underlinedon the screen. Press OK to selectCustomthe character you want, then repeat
for all available characters. Choosea space (no character) and press OK
for any remaining characters. Press
Label scene 1
the “OK” button to accept.
1 / 107. The info screen will confirm thatA
1: A
your name has been saved.
8. Exit programming mode.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonEnabling/Disabling Daylighting in a Scene
1. Enter programming mode.
Scene setup
2. Use the Master buttons to highlight “Scene
Labelssetup” and press the “OK” button to accept.
LabelsDaylighting
3. Use the Master buttons to highlight “Daylighting”
and press the “OK” button to accept.
4. Use the Master buttons to highlight your desired
Daylighting
scene. Press the “OK” button to accept.
5. Use the Master buttons to select “Enable” or
Scene 1
“Disable”. When daylighting is disabled in ascene, the GRAFIK Eye® QS control unit will
not respond to daylight sensors information
Scene 1
when that scene is active.
Press OK to save.
Daylighting
6. Exit programming mode.
Enable

Saved

Saved

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 22

Setting Save Mode
The “Save Mode” of the GRAFIK Eye® QS control unit can be adjusted to turn quick
scene programming on and off, or to disable the use of zone and/or scene buttons
for specific applications.
Main menu
Scene setup
Save mode

Save mode
Save always

Saved

Save Mode Settings
Save by OK (default): Quick scene programming mode; zone
adjustments are temporary until the “OK” button is pressed toconfirm the selection.
Save always: Automatically save changes made to lighting
levels or fade time to Off (Master button changes aretemporary).
Save never: Do not save any temporary changes to lighting
levels or fade time.
Four scenes (typically used for rented spaces): Zone raise/
lower buttons are disabled. Master raise/lower buttons,
wallstations, and IR receiver are still enabled for adjustmentof light level, but these changes are not saved.
Button disable (typically used in a public space): Only theTimeclock button, IR receiver, and wallstations can be used
to make temporary changes.
Changing the Save Mode
1. Enter programming mode.
2. Use the Master buttons to highlight “Save mode” and press
the “OK” button to accept.
3. Use the Master buttons to highlight the desired save mode.
The save modes are listed and explained below.
4. Press the “OK” button to accept. The info screen will confirm
that your save mode has been saved.
5. Exit programming mode.

®

16

9-16
1-8

MasterbuttonsOK“OK”
buttonZone raise/lower buttons

Quick Scene Programming:“Save by OK” Mode
By default, the GRAFIK Eye® QS control
unit is in “Save by OK” mode, whichallows you to quickly set scenes without
entering program mode.
1. Press the button for the scene you want
to set; its LED will light and the lights will
go to the current settings.
2. Use the zone raise/lower buttons to set
all lights to the desired levels. Press the“OK” button to select.
3. Set the fade time to the desired length
using the Master buttons, and press the“OK” button to save.
4. The info screen will confirm that the newscene settings have been saved.
Notes• Using the Master buttons to raise or
lower lighting settings is still temporary.
• To set a zone to unaffected (---), press
and hold the zone lower button for
6 seconds after the zone has gone to 0%
light level.

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 23

EcoSystem® Setup
After EcoSystem® devices are wired and powered, they must be addressed before
the system can control them. The “Build System” command automates this process.

16

Note: All existing EcoSystem® programming will be deleted when the “Build System”
command is run, including EcoSystem® sensor programming on the GRAFIK
Eye® QS control unit.
Building the System
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “EcoSystem” and press theZone setup“OK” button to accept.
EcoSystem
3. Use the Master buttons to highlight “Build system” and press
the “OK” button to accept.
4. Press the “OK” button to erase all current programming, reset
EcoSystem
and address EcoSystem® devices, and find sensors on thesystem.
Build system
5. Exit programming mode.
Assign zones

Build system
Erase digital load
Programming?

Masterbuttons

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

1 9

2 10

3 11

4 12

5 13

6 1

Use Zone 4
raise/lower
buttons toverify all
EcoSystem®
deviceshave beenaddressed.

Note: After running “Build System”, Zone 4 will control all
EcoSystem® devices for diagnostics and verificationof wiring. (This feature is disabled once any of theaddressed devices are assigned to a zone on the
GRAFIK Eye® QS control unit.) Use the Zone 4 raise/
lower buttons to verify that all devices are correctly
addressed. If a device does not respond, repeat the“Build System” command and/or check the wiring.

Searching...
xFound

x Loads
Found®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 24

EcoSystem® Setup (continued)
Assigning/Unassigning an EcoSystem® Device to a Zone
EcoSystem® devices must be addressed on the system (see previous page) before
assigning or unassigning to a zone.
Main menu
Zone setup

Zone setup
EcoSystem

EcoSystem
Assign zones
Address All

Assign zones
Ballast 2 / 23
*Unassigned*

Assign zones

1. Enter programming mode.
2. Use the Master buttons to highlight “EcoSystem” and press
the “OK” button to accept.
3. Use the Master buttons to highlight “Assign zones” and press
the “OK” button to accept.
4. Use the Master buttons to scroll through the EcoSystem®
devices on the link. The selected device will flash, and theinfo screen will display the device number and the numberof devices on the link. If the device is currently assigned to azone, the zone number will display at the bottom of the screen
and the LEDs for the zone will go on; otherwise, the info
screen will display “*Unassigned*”.
• Press the zone raise button to assign the device tothat zone.
• Press the zone lower button to unassign the device tothat zone.
5. Press the Timeclock (back) button to return to the EcoSystem®
menu. EcoSystem® devices will return to normal levels.
6. Exit programming mode.

16

Masterbuttons

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

1 9

2 10

3 11

Zone LEDs

4 12

5 13

6 1

Use thezone raiseor lower
button to
assign or
unassign an
EcoSystem®
device tothat zone.

Ballast 2 / 23
Zone 3Notes• Devices that were previously assigned to a zone will be
removed from the old zone and assigned to the new zone
(each device can be assigned to only 1 zone at a time).
• Devices can be assigned only to zones set to EcoSystem®
load type.
• Refer to the Zone Setup section for instructions on changing
load type.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 25

EcoSystem® Setup (continued)
Addressing EcoSystem® Devices
The “Address All” command can be used to add/replace EcoSystem® devices on
the system without running the “Build System” command (this avoids erasing all theexisting programming information).
The “Address All” command will treat replacement EcoSystem® devices ascompletely new devices added to the system, increasing the total device count withevery new/replacement device.
Note: If the system already contains 64 EcoSystem® devices, go to “Reset Missing
Ballast Addresses” screen on next page.
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “EcoSystem” and press theZone setup“OK” button to accept.
EcoSystem
3. Use the Master buttons to highlight “Address all” and press
the “OK” button to accept. All EcoSystem® devices in thesystem will go to full On. As each EcoSystem® device is
EcoSystem
addressed, the GRAFIK Eye® QS control unit will display
information about it, and the device will go to its low end.
Assign zones
This will take several minutes. The system will then return
Address all
to the main menu.
4. To program new/replacement devices, follow the instructions
to assign EcoSystem® devices to a zone.
Address all
5. Exit programming mode.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonAddress all ?
Press OK

Searching...
xFound

x Loads
Found®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 26

EcoSystem® Setup (continued)
16

Reset Missing Ballast Addresses (software revision 9.003 or higher)*If the GRAFIK Eye® EcoSystem® contains 64 ballasts and there is a need to replacesome ballasts, this menu can be used to reset the addresses of the missing ballasts,
before the replacement ballasts can be added to the system.
Follow the steps below to reset the addresses for the missing ballasts:
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “EcoSystem” menu andZone setup
press OK button to accept.
EcoSystem
3. In the “EcoSystem” menu, use the master buttons to highlight“Reset missing ballast(s)” and press OK to accept.
4. The GRAFIK Eye® QS control unit screen will prompt the user to
EcoSystem
confirm the start of the reset process. Press OK to accept. The
user will be prompted to ensure that all ballasts are powered
Reset missing ball...
up. Press OK to accept.
Diagnostics
5. The GRAFIK Eye® QS control start searching for missing
ballasts. Once the process is completed, the unit will display
the number of ballasts that were found missing. If this count isaccurate, press OK to continue. If not, press the back button to
Resetstart over after making sure that all ballasts are powered up.
missing
6. If the user pressed OK to continue, the GRAFIK Eye® QS control
ballast(s)?
unit will reset the addresses for the missing ballasts.
7. Once the process of resetting addresses is complete, thescreen will confirm the number of ballasts that have been reset.
Press OK to go back to the “EcoSystem” menu.
Ensure all

9-16
1-8

MasterbuttonsOK“OK”
buttonballasts are
powered up

Searchingmissingballast(s)X missing.
Reset missing
ballast(s)?

Yballast(s)
Reset

Done
Re-setting
X ballast(s)*This screen menu is only available in units with software revision 9.003 or higher. If you want to reset ballasts on a unit with an older version of software, pleasecontact Lutron Customer Support.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 27

EcoSystem® Setup (continued)
16

Diagnostics (software revision 9.003 or higher)
The diagnostics menu in the EcoSystem® Setup can beused to verify the EcoSystem® communication.
Follow the steps below for verification of EcoSystem®
communication:
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight
Zone Setup
the “EcoSystem” menu and press
EcoSystem
the “OK” button to accept.
3. In the “EcoSystem” menu, use
the Master buttons to highlight
EcoSystem“Diagnostics” and press “OK” toaccept.
Reset missing ball...
4. In the “Diagnostics” menu, use
LabelsDiagnostics
the Master buttons to highlight“Override” and press “OK” toaccept.
Diagnostics
5. Use the Master buttons to selectthe options for “Full ON,” “Min
Override
Level,” or “OFF” and press OK to
send the ballasts on the link to the
Link Silence
selected levels for verifying the linkcommunication.
Override
6. Once the process of verifying
communication is complete, press
Full ONthe back button to go back to the“EcoSystem” menu.

9-16
1-8

MasterbuttonsOK“OK”
buttonLink Silence (software revision 9.003 or higher)
Link silence is a feature for Lutron Field Service only. It allows theuser to disable the communication over the ballast link for smoothfirmware upgrades on ballasts. Follow the steps below to set the linkstatus to “silence”:(Link mode is set to normal, by default, when the Grafik Eye® QScontrol unit powers up.)
1. In the “EcoSystem” menu, use the Master
Diagnostics
buttons to highlight “Link Silence” and press
Override
OK to select it.
Labels2.
Use the Master buttons to select between
Link Silence“Normal” and “Silence” options, press OK to
confirm.
Link Silence
3. The info screen will confirm that the selected linkstatus is saved.
Silence

Ballast Link
Silence®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 28

Contact Closure Input (CCI) Setup(wired directly to the GRAFIK Eye® QS control unit)

16

The integral contact closure input (CCI) on the back of the GRAFIK Eye® QS control
unit can be configured as:

9-16
1-8

Masterbuttons
OK

Occupancy (default): Allows a wired occupancy sensor to be included in the list ofavailable sensors when setting up occupancy actions.
Emergency: This setting allows the GRAFIK Eye® QS control unit to work with a
LUT-ELI-3PH emergency lighting interface. When an emergency situation is detected,
all lights will go to full on, and will not change until the emergency signal is cleared.
Afterhours: Allows the CCI to start and end Afterhours.
Timeclock: Allows the CCI to enable and disable the timeclock.
Lockout: Prevents the user from making any changes to the control unit. The current scene will stay on until the CCI
enables normal operation.
Never Save: Prevents any changes from being saved while the CCI is being used.
Disable CCI: The CCI will have no effect on the system and will not appear on the list of available occupancy sensors
within the sensor setup menu.

“OK”
buttonTimeclock(back) button

Changing the operation of the contact closure input:
Main menu
Save Mode
CCI Setup

CCI menu

1. Enter programming mode.
2. Use the Master buttons to highlight “CCI Setup” and press the “OK” button to accept.
3. Use the Master buttons to highlight “CCI Mode” and press the “OK” button to accept.
4. Use the Master buttons to highlight the mode you wish the CCI to control. Press the“OK” button to accept.
5. The info screen will confirm that your setting has been saved.
6. Exit programming mode.

CCI Mode
CCI Type

CCI Mode
SavedSaved

Occupancy(continued on the next page)®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 29

Contact Closure Input (CCI) Setup (continued)(wired directly to the GRAFIK Eye® QS control unit)

16

The integral contact closure input (CCI) on the back of the GRAFIK Eye® QS control unit
is compatible with either type of contact closure device:
Maintained (default): The GRAFIK Eye® QS control unit will act on both a contact
closure and a contact open/release event.
Example: “CCI Mode” set to “Afterhours.” Contact closure starts “Afterhours.”
Contact open/release ends “Afterhours.”
Momentary: The GRAFIK Eye® QS control unit will act on only contact closure events.
Example: “CCI Mode” set to “Afterhours.” Contact closure starts “Afterhours.”
Contact open/release has no effect. Second contact closure ends “Afterhours.”

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

Changing the type of contact closure input:
Main menu
Save Mode
CCI Setup

CCI menu
CCI Mode
CCI Type

CCI Type

1. Enter programming mode.
2. Use the Master buttons to highlight “CCI Setup” and press the“OK” button to accept.
3. Use the Master buttons to highlight “CCI Type” and press the“OK” button to accept.
4. Use the Master buttons to highlight the type you wish the CCI
to control. Press the “OK” button to accept.
5. The info screen will confirm that your setting has been saved.
6. Exit programming mode.
Note: The “Emergency CCI Mode” is different from the other
CCI modes in that “Emergency Mode” will activate on
a contact open/release and will deactivate on a contact
closure. The CCI must be set to “Maintained” (default) for
proper “Emergency Mode” operation.

Maintained

SavedSaved®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 30

Occupancy Sensor Setup
Lutron® occupancy and vacancy sensors work with the GRAFIK Eye® QS Wireless control unit to automatically adjust light levels
when occupancy or vacancy is detected.
Wired occupancy and vacancy sensors may be connected to the contact closure input on the GRAFIK Eye® QS control unit, a QS
Sensor Module (QSM), a Contact Closure Interface in the GRAFIK Eye® QS system, or an EcoSystem® device addressed to the
GRAFIK Eye® QS control unit.
CCI Connection

QS Link

WiredOccupancy
Sensor

LUTRONGRAFIK Eye® QScontrol unit

QS
Sensor Module(QSM)

LUTRONGRAFIK Eye® QScontrol unit

QS Link

EcoSystem® Bus

Wired
Occupancy
Sensor

LUTRONGRAFIK Eye® QScontrol unit

Wired
Occupancy Sensor

EcoSystem®
device

LUTRONGRAFIK Eye® QS with
EcoSystem® control
unit

QSE-IO

Wired
Occupancy Sensor

Wireless Radio Powr SavrTM occupancy and vacancy sensors can be associated with a GRAFIK Eye® QS Wireless or QSM. Wirelesssensors must first be associated to one of these devices before they will be recognized by a GRAFIK Eye® QS Wireless system.
QS Link

LUTRONGRAFIK Eye® QScontrol unit

LUTRON

Wireless
Occupancy Sensor

Wireless
Occupancy Sensor

GRAFIK Eye® QScontrol unit

QS
Sensor Module (QSM)

Wireless
Wireless
Occupancy Sensor Occupancy Sensor

The following steps are required to program occupancy sensors with a GRAFIK Eye® QS control unit.
1. Connect wired sensors, or associate wireless sensors.
2. Choose the mode of operation (scene control or zone control).
3. Select sensors.
4. Assign sensor actions.
5. Configure sensor settings (optional).

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 31

Occupancy Sensor Setup (continued)
Associating wireless occupancy sensors and GRAFIK Eye® QS Wireless control units(for wireless enabled units only):
1. Make sure the wireless mode of the GRAFIK Eye® QS control
Main menu
unit is “Enabled”.
Zone Setup
2. Enter programming mode.
Sensor Setup
3. Use the Master buttons to highlight “Sensor Setup” and press
the “OK” button to accept.
4. Use the Master buttons to highlight “Add wireless sensors” andSensor Setup
press the “OK” button to accept.
5.
Press and hold the “Lights Off” button ( on some sensors) on
Add wireless sensors
the occupancy sensor for 6 seconds. The lens will start flashing
Daylight
and the info screen on the GRAFIK Eye® QS Wireless control unit
will display the sensor’s serial number.
6. Press the “OK” button on the GRAFIK Eye® QS control unit.
Add wireless sensors
A screen will confirm that the sensor has been assigned.
(To disassociate a wireless occupancy sensor from the GRAFIK
Initiate association
Eye® QS control unit, Refer to the Radio Powr SavrTM occupancy
of sensors
sensor install guide to return the sensor to its “out-of-box”
functionality. Doing so will remove its programming from the
GRAFIK Eye® QS control unit.)
Occupancy
7. Repeat the above steps for all desired sensors.
8. Exit programming mode.
xxxx-xxxx
Press OK to Save

*Assigned*
Saved

Associating wireless occupancy sensors throughQS Sensor Modules (QSM):
1. Press and hold the “Program” button on the QSM for 3 seconds
to enter programming mode. There will be 1 audible beep
and the Status LED will begin flashing. The info screen on the
GRAFIK Eye® QS control unit will display that the QSM is inprogramming mode.
2. Press and hold the “Lights Off” button ( on some sensors) on
the occupancy sensor for 6 seconds. There will be 3 audible
beeps from the QSM to verify association.
3. Press and hold the “Program” button on the QSM for 3 seconds
to exit programming mode.
Note: The wireless signal has a range of 30 ft (9 m) throughstandard construction or 60 ft (18 m) line of sight.

®

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

Press and hold“Lights Off” orbutton to associate/
disassociateRadio Powr SavrTM
Occupancy Sensors“Program” button

QS Sensor Module (QSM)

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 32

Occupancy Sensor Setup (continued)
When the GRAFIK Eye® QS system is first powered up, occupancy sensors connectedto the contact closure input (and the first three associated wireless Radio Powr SavrTM
occupancy sensors) will automatically operate in “Scene Mode.” Their defaults willbe “No Action” for the occupied state and “Scene Off” for the unoccupied state.
For additional sensors and/or alternate functionality, please complete all required
programming actions.
Selecting the Mode
Scene Mode (default) is useful when the GRAFIK Eye® QS control unit is controlling
lights in a single room or area. Up to 16* sensors can be assigned to the GRAFIK
Eye® QS control unit to activate a scene when the space is occupied, and anotherscene when unoccupied.
Zone Mode is useful when the GRAFIK Eye® QS control unit is controlling lights in
multiple areas within a room. Up to four sensors can be assigned to each zone (asensor can be assigned to more than one zone) to send the zones to configurable
occupied and unoccupied levels.
Main menu
1. Enter programming mode.
EcoSystem
2. Use the Master buttons to highlight “Sensor Setup” and press
the “OK” button to accept.
Sensor Setup
3. Use the Master buttons to highlight “Occupancy” and press
the “OK” button to accept.
Sensor Setup
4. Use the Master buttons to highlight “Mode” and press the“OK” button to accept.
Daylight
5. Use the Master buttons to highlight “Zone Mode” to assign
Occupancy
sensors to zones, or “Scene Mode” (default). Press the“OK” button to accept. A screen will confirm your selectedmode has been saved and you will return to the Daylight Sensor
Occ Sensor
screen.
Note: Changing modes will remove all previous occupancyModeassignments.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

ActionsOcc Sensor
Scene ModeOcc Sensor
OR

Zone Mode

SavedSaved* Applicable only to units that ship with firmware version 9.003 and higher. Previous versions support up to 4 sensors.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 33

Occupancy Sensor Setup (continued)
Scene Mode
This step allows you to assign up to 16* occupancy sensors to the GRAFIK Eye® QScontrol unit.
Selecting Sensors
Occ Sensor
1. If not already done, associate occupancy sensors and set to
Setup“Scene Mode”.
2. Use the Master buttons to highlight “Setup” and press
Labelsthe “OK” button to accept. The info screen will display“Searching” while the unit detects available occupancy
sensors.
3. Use the Master buttons to scroll through the list of available
Searching
Saved
occupancy sensors. When the desired sensor is displayed,press the “OK” button to select it. Then choose “Assign” or“Unassign” from the following menu and press OK. Once asensor has been assigned, it will appear with an asterisk (*)
in the sensor list. Repeat for additional sensors.
Sensorx/yNote: If wireless sensors are not found, verify that they are
xxxxxxxx
associated correctly.
yyyy-yyyy
RF

Assignment
AssignUnassign*Assigned*
Saved

Sensorxxxxxxxx
yyyy-yyyy
RF

*x/y

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

Setting the Sensor Action
1. Press the Timeclock (back) button to return to the Occ Sensor
screen. Use the Master buttons to highlight “Actions” andpress the “OK” button. By default, the occupied scene is set
to “No Action” and the unoccupied scene is set to “Scene
Off”.
2. Use the Master buttons to highlight the scene you wish touse for occupied status and press the “OK” button to accept.
Repeat for the scene you wish to use for unoccupied status.
Press the “OK” button to accept.
3. Exit programming mode.

Occ Sensor
Actions

3 seconds
Setup

Occupied Scene

Unoccupied Scene

Scene 1

Scene Off

SavedSaved* Applicable only to units that ship with firmware version 9.003 and higher. Previous versions support up to 4 sensors.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 34

Occupancy Sensor Setup (continued)
Zone Mode
This step allows you to assign up to four occupancy sensors per zone to the GRAFIK
Eye® QS control unit. Sensors can be added to more than one zone.
Selecting Sensors
Occ Sensor
1. If not already done, associate sensors and set to “Zone Mode”.
Setup
2. Use the Master buttons to highlight “Setup” and press the“OK” button to accept.
Labels
3. You can assign up to four sensors per zone, and a sensor canbe assigned to more than one zone. Use the Master buttons toscroll through the sensors until the one you wish to assign or
unassign is highlighted, and press the “OK” button to select it.
4.
Use the zone raise and lower buttons for each desired zone
Searching
Saved
to assign or unassign the sensor to that zone. The zone raise
button assigns the displayed sensor, and the zone lower button
unassigns it. Press the Timeclock (back) button to return to thelist of available sensors. Once a sensor has been assigned,
Sensorx/y
it will appear with an asterisk (*) in the sensor list. Repeat forxxxxxxxx
additional sensors.
yyyy-yyyy
Note: If wireless sensors are not found, verify that they areRFassociated correctly.
SensorSet Zones

Sensorxxxxxxxx
yyyy-yyyy
RF

*x/y

16

Actions

3 seconds
Setup®

Occupied
Select Occupied
Level

OK

“OK”
buttonTimeclock(back) button

1 9

Setting the Sensor Action
1. Press the Timeclock (back) button to return to the Occ Sensor
screen. Use the Master buttons to highlight “Actions” and press
the “OK” button to accept.
2. Use the zone raise and lower buttons to adjust each zone to thedesired occupied level and press the “OK” button to save.
To set a zone as unaffected, lower the light levels all the way tooff, then hold the zone lower button for 3 seconds. The screen
will display “---” and the three middle LEDs for the zone will be
lit to indicate this zone is unaffected by the scene (the zone will
not change when this scene is initiated).
3. Use the zone raise and lower buttons to adjust each zone to thedesired unoccupied level, and press the “OK” button to save.
4. Exit programming mode.
Occ Sensor

Masterbuttons

9-16
1-8

2 10

2 10

3 11

4 12

5 13

3 11

Zone raise: Press toassign the displayedsensorZone lower: Press tounassign the displayedsensorUnoccupied
Select Unoccupied
Level

SavedSaved

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 35Occupancy Sensor Setup (continued)
Labeling an Occupancy Sensor (optional)
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Sensor Setup” and press
Zone Setup
the “OK” button to accept.
Sensor Setup
3. Use the Master buttons to highlight “Occupancy” and press
the “OK” button to accept.
4. Use the Master buttons to highlight “Labels” and press the
Sensor Setup“OK” button to accept.
5.
Use the Master buttons to display an occupancy sensor to
Daylight
label and press OK to select.
Occupancy
6. Use the Master buttons to scroll through the characters(lowercase and uppercase letters, plus numbers 0 through 9).
The character you are currently changing will be underlined
Occ Sensor
on the screen. Press OK to select the character you want,then repeat for all available characters. Choose a space (noLabelscharacter) and press OK for any remaining characters. The
Settings
info screen will confirm that your name has been saved.
Repeat for all desired sensors.
7. Exit programming mode.
Sensor
x/y

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

xxxxxxxx
yyyy-yyyy
RF

Label sensor x/y
1 / 11

1: A

A

SavedSaved®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 36

Occupancy Sensor Setup (continued)
Configuring Occupancy Sensor Settings (optional)
Occupancy Sensor Settings
Main menu
Note: These settings affect all sensors assigned to the
EcoSystemGRAFIK Eye® QS control unit.
Sensor Setup
Grace Period: If the GRAFIK Eye® QS control unit istransitioning to an unoccupied state, motion detected within
the grace period will return the lights to the previously
Sensor Setup
occupied level.
Range: 0 – 30* seconds (default 15 seconds).
Daylight
Vacancy Delay: An additional time delay after vacancy is
Occupancy
detected and before unoccupied action occurs. Use whenoccupancy sensor does not provide sufficient delay.
Range: 0 – 30 minutes (default 0 minutes).
Occ Sensor
Auto Turnoff: If lights assigned to an occupancy sensor are
turned on manually without the sensor reporting occupancy,
Settings
the GRAFIK Eye® QS control unit can be set to automaticallyDiagnostics
turn off the lights after a set time delay. Disable this feature bysetting the time delay to 0 (disabled).
Range: Disabled or 1 – 30 minutes (default Disabled).
Settings
Zone Fade: When in Zone Mode, lights can be set to fade to
the unoccupied levels over this period of time.
Auto Turnoff
Range: 0 – 59 seconds; 1 – 10 minutes (default 10 seconds).
Zone Fade
Configuring the Sensor Settings:
1. Enter programming mode.
2. Use the Master buttons to highlight “Sensor Setup” and press
Auto Turnoff
the “OK” button to accept.
3. Use the Master buttons to highlight “Occupancy” and press
5 minutes
the “OK” button to accept.
4. Use the Master buttons to highlight “Settings” and press the“OK” button to accept.
5. Use the Master buttons to highlight the setting you wish toconfigure. Press the “OK” button to accept.
SavedSaved
6. Use the Master buttons to adjust the value of the selected
setting. Press the “OK” button to accept.
7. The info screen will confirm that your setting has been saved.
8. Exit programming mode.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button* Applicable only to units that ship with firmware version 8.027 and higher. Previous versions support settings between 15–30 seconds.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 37

Daylight Sensor Setup
LutronR daylight sensors work with the GRAFIK Eye® QS Wireless control unit to automatically adjust electric light levels when naturallight in the room changes.
Wired daylight sensors may be connected to a QS Sensor Module (QSM) in the QS system, or to an EcoSystem® device addressed to
the GRAFIK Eye® QS control unit.
QS Link

EcoSystem® Bus

LUTRON
LUTRONQS
Sensor Module(QSM)

LUTRONGRAFIK Eye® QScontrol unit

Wired
Daylight
Sensor

EcoSystem® device

LUTRON

Wired
Daylight
SensorGRAFIK Eye® QS
with EcoSystem®
control unit

Wireless Radio Powr SavrTM daylight sensors can be associated with a GRAFIK Eye® QS control unit or QSM. Wireless sensors mustfirst be associated with one of these devices to be recognized by a GRAFIK Eye® QS wireless system.
QS Link

LUTRON

Wireless
Daylight Sensor

GRAFIK Eye® QScontrol unit

LUTRONGRAFIK Eye® QScontrol unit

QS
Sensor Module(QSM)

Wireless
Daylight Sensor

The following steps are required to program daylight sensors with a GRAFIK Eye® QS control
unit. Instructions for each step are on the pages that follow.
1. Connect wired sensors, or associate wireless sensors.
2. Assign the mode of operation: zone control or group control.
(If you assign group mode, set up the groups.)
3. Assign sensors to zones or groups.
4. Calibrate the system to achieve the desired response to natural light.
Note: The Daylighting feature is not supported for the DMX load type.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 38

Daylight Sensor Setup (continued)
Associating wireless daylight sensors and GRAFIK Eye® QS Wireless control units(for wireless enabled units only):
1. Make sure the wireless mode of the GRAFIK Eye® QS control
Main menu
unit is “Enabled”.
Zone Setup
2. Enter programming mode.
Sensor Setup
3. Use the Master buttons to highlight “Sensor Setup” and press
the “OK” button to accept.
4. Use the Master buttons to highlight “Add wireless sensors” andSensor Setup
press the “OK” button to accept.
5.
Press and hold the “Link” button on the daylight sensor until the
Add wireless sensors
sensor starts flashing. The info screen on the GRAFIK Eye® QS
Daylight
control unit will display the sensor’s serial number.
6. Press the “OK” button on the GRAFIK Eye® QS control unit. A
screen will confirm that the sensor has been assigned.
Add wireless sensors(To disassociate a wireless daylight sensor from the GRAFIK
Eye® QS control unit, Refer to the Radio Powr SavrTM daylight
Initiate association
sensor install guide to return the sensor to its “out-of-box”
of sensors
functionality. Doing so will remove its programming from the
GRAFIK Eye® QS control unit.)
7. Repeat the above steps for all desired sensors.
Daylight
8. Exit programming mode.
xxxx-xxxx
Press OK to Save

*Assigned*
Saved

Associating wireless daylight sensors throughQS Sensor Modules (QSM):
1. Press and hold the “Program” button on the QSM for 3 seconds
to enter programming mode. There will be 1 audible beep
and the Status LED will begin flashing. The info screen on the
GRAFIK Eye® QS control unit will display that the QSM is inprogramming mode.
2. Press and hold the “Link” button on the daylight sensor for 6
seconds. There will be 3 audible beeps from the QSM to verify
association.
3. Press and hold the “Program” button on the QSM for 3 seconds
to exit programming mode.
Note: The wireless signal has a range of 30 ft (9 m) throughstandard construction or 60 ft (18 m) line of sight.

®

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

Radio Powr SavrTM
Daylight Sensor“Link”
button“Program” button

QS Sensor Module (QSM)

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 39

Daylight Sensor Setup (continued)
Assigning the Mode
Zone Mode (default) is useful when the GRAFIK Eye® QS control unit is controlling
lights in multiple rooms or areas. Zone mode allows each zone to adjust its light levelbased on measured daylight levels. Each zone can be assigned to only one sensor (asensor can be assigned to more than one zone). Each zone can have a unique target
light level.
Group Mode is useful when groups or rows of lights for daylighting go across multiple
zones. A group can consist of any combination of EcoSystem® loads in the system.
For convenience, zones set to line-voltage load types (applies only to zones 1-3)
are included in the list of available groups. Each group can be assigned to only one
sensor (a sensor can be assigned to more than one group). Each group can have aunique target light level.
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Sensor Setup” and press
Zone Setup
the “OK” button to accept.
Sensor Setup
3. Use the Master buttons to highlight “Daylight” and press the“OK” button to accept.
4. Use the Master buttons to highlight “Mode” and press the
Sensor Setup“OK” button to accept.
5.
Use the Master buttons to highlight “Zone Mode” to assign
Daylight
sensors to zones, or “Group Mode” to assign sensors to a
Occupancygroup of EcoSystem® loads (or line-voltage zones). Press the“OK” button to accept. A screen will confirm your selectedmode has been saved and you will return to the Daylight Sensor
Daylight Sensor
screen.
Note: Changing modes will remove all previous daylightMode
assignments.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button

Setup

Daylight Sensor

Daylight Sensor
OR

Zone

Group

®

SavedSaved

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 40

Daylight Sensor Setup (continued)
Zone Mode
This step allows you to assign sensors to zones on the GRAFIK Eye® QS control unit.
Each zone can be assigned to only one sensor, but sensors can be assigned to morethan one zone.
Daylight Sensor
Setup
Calibrate

Searching
Saved

Sensorx/yxxxx-xxxx:
RF

SensorSet Zones

Assigning Sensors
1. If not already done, associate daylight sensors and set to“Zone Mode”.
2. Use the Master buttons to highlight “Setup” and press the“OK” button to accept. Available sensors will be displayed.
3. Use the Master buttons to scroll through the sensors until the
one you wish to assign or unassign is highlighted, and press
the “OK” button to select it.
4. Use the zone raise and lower buttons for the desired zones toassign or unassign the sensor to those zones. The zone raise
button assigns the displayed sensor, and the zone lower button
unassigns it. Press the Timeclock (back) button to return to thelist of available sensors. Repeat for additional sensors.
Calibrating the Sensors
1. Put any wireless Radio Powr SavrTM daylight sensors associatedwith the desired zones into “Calibrate Mode”: Press and holdthe “Cal” button for 6 seconds until the sensor flashes.
Note: After 5 minutes, “Calibrate Mode” will timeout, and thesensor will return to normal mode.
2. Press the Timeclock (back) button to return to the Daylight
Sensor screen. Use the Master buttons to highlight “Calibrate”
and press the “OK” button to accept.
3. Use the Master buttons to select the desired zone and press
the “OK” button to accept.
4. Use the Master buttons to select the desired light level for thezone, and press the “OK” button to accept. Repeat for all zone
levels you wish to calibrate.
5. Exit programming mode.
Note: If wireless sensors are not found, verify that they areassociated correctly.
Sensor Name

Daylight Sensor

Adjust Light
More light

Setup
3 seconds
Calibrate

Zone 1

®

Saved
Saved

16

Masterbuttons

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

1 9

2 10

2 10

3 11

4 12

5 13

3 11

Zone raise: Press toassign the displayedsensorZone lower: Press tounassign the desired
sensorRadio Powr SavrTM
Daylight Sensor“Cal”
buttonLess light

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 41

Daylight Sensor Setup (continued)
Group Mode
This step allows you to assign daylight sensors to a group of EcoSystem® loads
connected to the GRAFIK Eye® QS with EcoSystem® control unit. You may also
assign daylight sensors to line-voltage zones in this mode. Each group can be
assigned to only one sensor, but sensors can be assigned to more than one group.
Daylight Sensor
Daylight Groups
Setup

Configure Groups
Group 1

Group 1
Ballast 2/23
*Unassigned*

ORGroup 1
Ballast 2/23

Setting Up Groups
1. If not already done, associate daylight sensors and set to“Group Mode”.
2. Use the Master buttons to highlight “Daylight Groups” andpress the “OK” button to accept.
3. Use the Master buttons to scroll through the list of available
daylight groups. Up to 16 groups of EcoSystem® loads can be
defined. Press the “OK” button to accept.
4. Use the Master buttons to scroll through the EcoSystem®
devices on the link. Press the “OK” button to add or remove
the selected device. The currently selected device will display
its current assignment status:
Unassigned if it is not assigned to any group
Assigned if it is assigned to the selected (displayed) group
Group if it is currently assigned to another group
5. Press the Timeclock (back) button to return to the list of
configurable groups, and repeat these steps to assign devices
to other groups.
Note: Each EcoSystem® device can be assigned to only one
group. Assigning a device already associated withanother group will replace its existing programming.

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button*Assigned*(continued on next page)OR
Group 1
Ballast 2/23
*Group 2*®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 42

Daylight Sensor Setup (continued)
Group Mode (continued)
Daylight Sensor
Setup
Calibrate

Searching
Saved

Sensorxxxx-xxxx
RF

Sensor x
Group 1
*Unassigned*

Sensor x
Group 1
*Assigned*

x/y

16

Selecting Sensors
1. Press the Timeclock (back) button to return to the Daylight
Sensor menu.
2. Use the Master buttons to highlight “Setup” and press the“OK” button to accept.
3. Use the Master buttons to scroll through the list of available
daylight sensors. When the desired sensor is displayed, press
the “OK” button to select it.
4. Use the Master buttons to scroll through the list of available
groups. When the desired group is displayed, press “OK”
to assign or unassign the sensor to that group. Press theTimeclock (back) button to return to the list of available
sensors. Repeat for additional sensors.

9-16
1-8

Calibrate

Setup

3 seconds
Calibrate®

“OK”
buttonRadio Powr SavrTM
Daylight Sensor“Cal”
buttonAdjust Light
More light

Group 1

OK

Timeclock(back) button

Calibrating the Sensors
1. Put any wireless Radio Powr SavrTM daylight sensors
associated with the desired zones into “Calibrate Mode”:
Press and hold the “Cal” button for 6 seconds until the
sensor flashes.
Note: After 5 minutes, “Calibrate Mode” will timeout, and thesensor will return to normal mode.
2. Press the Timeclock (back) button to return to the Daylight
Sensor screen. Use the Master buttons to highlight “Calibrate”
and press the “OK” button to accept.
3. Use the Master buttons to select the desired group and press
the “OK” button to accept.
4. Use the Master buttons to select the desired light level for thegroup, and press the “OK” button to accept. Repeat for allgroup levels you wish to calibrate.
5. Exit programming mode.
Note: If wireless sensors are not found, verify that they areassociated correctly.
Daylight Sensor

Masterbuttons

Saved
Saved

Less light

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 43

Daylight Sensor Setup (continued)
Labeling a Daylight Sensor (optional)
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Sensor Setup” and press
Zone Setup
the “OK” button to accept.
Sensor Setup
3. Use the Master buttons to highlight “Daylight” and press the“OK” button to accept.
4. Use the Master buttons to highlight “Labels” and press the
Sensor Setup“OK” button to accept.
Daylight
5. Use the Master buttons to display a daylight sensor to label
and press OK to select.
Occupancy
6. Use the Master buttons to scroll through the characters(lowercase and uppercase letters, plus numbers 0 through 9).
The character you are currently changing will be underlined
Daylight Sensor
on the screen. Press OK to select the character you want,then repeat for all available characters. Choose a space (noLabelscharacter) and press OK for any remaining characters. The
Diagnostics
info screen will confirm that your name has been saved.
Repeat for all desired sensors.
7.
Exit
programming mode.
Sensor
x/y

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) buttonxxxx-xxxx
RF

Label sensor x/y
1 / 11

1: A

A

SavedSaved®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 44

Pico® Wireless Control Setup
LutronR Pico® wireless controls can be associated with a GRAFIK Eye® QS system to control the light level of a specific zone or to act
as a scene controller. Pico® wireless controls can be associated directly to GRAFIK Eye® QS Wireless control units, or to a wired or
wireless GRAFIK Eye® QS control unit via a QS Sensor Module (QSM) wired on the QS link.
QS Link

LUTRONGRAFIK Eye® QScontrol unit
QS Sensor Module(QSM)

LUTRONGRAFIK Eye® QScontrol unit

Pico® WirelessControlPico® WirelessControl

Available Pico®
Wireless Control
Models2-button(2B)

2-buttonwithraise/lower(2BRL)

3-button(3B)

3-buttonwithraise/lower(3BRL)

4-buttonscene control(4B-Gxx-L31)

4-buttonzone control(4B-Gxx-L01)

Default Functionality of the Pico® wireless control
Zone Function1

Scene Function2

Top (On) Button

All assigned zones 100%

Scene 1

Center (Preset) Button(3B and 3BRL) or
second button from top(4B-Gxx-L31)

All assigned zones at programmed preset
level(Press and hold to save current levels on
assigned zone as preset)

Scene 2Raise/Lower Buttons(if available)

Vary intensity of all assigned zones

Vary intensity of all zones affected bycurrent scene

Bottom (Off) Button

All assigned zones Off

Scene Off

1 In zone function, user can program preset levels for assigned zones on any Pico® wireless control button. Instructions for reprogramming zone levels are provided on the next page.
2 In scene function, the starting scene of the Pico® wireless control is selectable and zone levels in each scene can be adjusted by following the instructions in Scene Setup.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 45

Pico® Wireless Control Setup (continued)
Associating the Pico® wireless control with a GRAFIK Eye® QS Wireless control unit:(for wireless enabled GRAFIK Eye® QS control units only)
1. Make sure the wireless mode of the GRAFIK Eye® QS control unit is
Pico“Enabled”.
Change type?
2. On the Pico® wireless control, press and hold the top (on) and bottom(off) buttons for 3 seconds. The info screen on the GRAFIK Eye® QSPress OK
control unit will display the Pico® wireless control options. Press the“OK” button on the GRAFIK Eye® QS control unit to select the desired
operation type for the Pico® wireless control.
Change type?
3. To assign the Pico® wireless control as a zone controller, use the Master
Zone
buttons to select “Zone” and press the “OK” button to accept.
3a. Use the zone raise/lower buttons for a zone to select a desired preset
level, and then press the zone raise and lower buttons simultaneouslyORfor 1 second (until the zone LEDs flash at the programmed preset level).
Repeat for all zones you wish to control with the Pico® wireless control.
Change type?
3b. To program other Pico® wireless control buttons (not including
Scene
Raise/Lower), press the desired button and repeat step 3a.
OR

MasterbuttonsOK“OK”
buttonPress andhold thetop scene
button for
3 seconds
to assign
Pico® asa scenecontroller.

Zone LEDs
1 9

2 10

Zone Raise

4.
Button Setup
First Scene

1

Scenes 1–2, off

5.
SavedSaved

To assign the Pico® wireless control as a scene controller, use the Masterbuttons to select “Scene” and press the “OK” button to accept. Use theMaster buttons to select the desired starting scene for the PICO andpress the “OK” button to accept. Press and hold the top scene buttonon the GRAFIK Eye® QS control unit for 3 seconds (until the scene LEDs
flash).
On the Pico® wireless control, press and hold the top and bottom buttons
for 3 seconds until the LEDs on the GRAFIK Eye® QS control unit stop
flashing.

Zone Lower

Top/OnbuttonNote: The wireless signal has a range of 30 ft (9 m) through standard
construction or 60 ft (18 m) line of sight.

Bottom/Off
buttonPico®
Wireless
Control®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 46

Pico® Wireless Control Setup (continued)
Associating the Pico® wireless control through a QS Sensor Module (QSM):(for wired or wireless enabled GRAFIK Eye® QS control units)
1. Press and hold the “Program” button on the QSM for 3
QSM
seconds to enter programming mode. There will be 1 audible
Programming
beep and the Status LED will begin flashing. The info screen on
the GRAFIK Eye® QS control unit will display that the QSM is inprogramming mode.
2. Press and hold the bottom button on the Pico® wireless control
QSM
for 6 seconds. There will be 3 audible beeps from the QSM to
verify association.
Change type?
3. Press and hold the “Program” button on the QSM for 3
Press OK
seconds to exit programming mode.
4. On the Pico® wireless control, press and hold the top (on)and bottom (off) buttons for 3 seconds, until the LEDs on the
Change type?
GRAFIK Eye® QS control unit begin to flash and the QSM
beeps
1 time. Press the “OK” button on the GRAFIK Eye® QS
Zone
control unit to select the desired operation mode for the Pico®
wireless control.
5.
To assign the Pico® wireless control as a zone controller, useORthe Master buttons to select “Zone” and press the “OK” button
Change type?
to accept.
5a. Use the zone raise/lower buttons for a zone to select a desired
Scene
preset level, and then press the zone raise and lower buttons
simultaneously for 1 second (until the zone LEDs flash at the
programmed preset level). Repeat for all zones you wish tocontrol with the Pico® wireless control.
Button Setup
5b. To program other Pico® wireless control buttons (not includingFirst Scene
1
Raise/Lower), press the desired button and repeat step 5a.

“Program” button

QS Sensor Module(QSM)

Top/OnbuttonBottom/Off
buttonPico®
Wireless
ControlOR

Scenes 1–2, off

6.

SavedSaved

7.

To assign the Pico® wireless control as a scene controller,
use the Master buttons to select “Scene” and press the “OK”
button to accept. Use the Master buttons to select the desired
starting scene for the PICO and press the “OK” button toaccept. Press and hold the top scene button on the GRAFIK
Eye® QS control unit for 3 seconds (until the scene LEDs flash).
On the Pico® wireless control, press and hold the top andbottom buttons for 3 seconds until the LEDs on the GRAFIK
Eye® control unit stop flashing and the QSM beeps 1 time.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 47

IR Setup
An infrared (IR) remote can directly control the GRAFIK Eye® QS control unit throughthe infrared receiver on the front of the GRAFIK Eye® QS control unit.

IR
Remote
LUTRONGRAFIK Eye® QScontrol unit

An externally powered IR repeater can also be connected to the IR terminals on
the GRAFIK Eye® QS control unit to obtain IR remote control. This is useful for
integrating third party devices with the GRAFIK Eye® QS control unit (e.g. home theaterapplications.) For a complete list of the GRAFIK Eye® QS control unit’s IR programming
commands, please see www.lutron.com/qs.
IR Terminal
Third
Party
DeviceIR
Remote

LUTRONGRAFIK Eye® QScontrol unit

An IR remote can also indirectly control the GRAFIK Eye® QS control unit through the
QS IR Eye or a Lutron® IR receiver wired to a QS Sensor Module (QSM) to control
the light level of a specific zone or to act as a scene controller. The QS IR Eye and IR
receivers wired to the QSM must first be associated with the GRAFIK Eye® QS control
unit before they will be recognized by a GRAFIK Eye® QS system.

QS Link

QS Link
IR
RemoteQS
IR Eye

LUTRONGRAFIK Eye® QScontrol unit®

IR
Remote
LUTRONGRAFIK Eye® QScontrol unit

QS Sensor Module(QSM)

Wired IR
ReceiverGRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 48

IR Setup (continued)
Enabling/disabling the IR receiver on the GRAFIK Eye® QS control unit:
Note: These steps will also enable or disable the IR terminals on theMain menu
GRAFIK Eye® QS control unit.
Wireless Mode
1. Enter programming mode.
IR Setup
2. Use the Master buttons to highlight “IR Setup” and press the “OK” button
to accept
3. Use the Master buttons to highlight “Integral IR” and press the “OK” button
IR menu
to accept.
4.
Use the Master buttons to highlight either “Enabled” or “Disabled” andIntegralIR
Timeclockpress the “OK” button to accept. The info screen will confirm that yourProgramming
settings have been saved.
5. Exit programming mode.

MasterbuttonsOK“OK”
buttonIntegral IR
EnabledSavedSaved®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 49

IR Setup (continued)
The QS IR Eye offers advanced programmable scene control depending on the IR remote being used.
Use the chart below to select the appropriate control mode on the GRAFIK Eye® QS control unit:
IR Remote
GRX-IT
GRX-8ITMIR-ITFS
C-FLRC
Third Party IR Remote

Control Mode
4 Buttons & Off or 5 Buttons
8 Buttons & Off
Favorite or Zone control
Favorite or Zone control
Default

Associating the QS IR Eye with a GRAFIK Eye® QS control unit:
Note: For use with LutronR remote models GRX-IT and GRX-8IT, or with
IR Eyethird-party IR remotes.
Change type?
1. Point the IR remote at the QS IR Eye. To enter programming mode, press andhold the top and bottom buttons on the remote for 3 seconds until the LED on
Press OK
the QS IR Eye begins to flash slowly.
2. Press and hold the top scene button on the GRAFIK Eye® QS control unit for
3 seconds. The scene LEDs will flash to confirm that the QS IR Eye has been
Change type?
associated. Press the “OK” button to continue.
3.
Use the Master buttons to select “Scene” and press the “OK” button to accept.
Scene
4. Use the Master buttons to select one of the scene control types (listed below)
to correspond to the IR remote that will be used with the QS IR Eye. Press the“OK” button to accept.
If “Default” was not selected, the info screen will prompt you to select which
Change type?
scene will correspond to the top button of the IR remote. Use the Masterbuttons to select the desired scene, and press the “OK” button to accept. The
Default Scene
info screen will confirm that your settings have been saved.
Note: The “Default” scene control type will activate whichever scene commandis transmitted to the GRAFIK Eye® QS control unit.
5. Point the IR remote at the QS IR Eye. To exit programming mode, press andhold the top and bottom buttons on the remote for 3 seconds.
Button Setup
First
Scene

MasterbuttonsOK“OK”
buttonPress andhold thetop scene
button for
3 seconds
to associate
QS IR Eye

GRX-IT

GRX-8IT

1
LED

QS IR Eye

SavedSaved®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 50

IR Setup (continued)
Associating the QS IR Eye with a GRAFIK Eye® QS control unit (continued):
Note: For use with Lutron® remote models MIR-ITFS and C-FLRC.
IR Eye1. Point the IR remote at the QS IR Eye. To enter programming mode, press
Change type?
and hold the “On” (top) button on the remote for 5 seconds, then, within
1 second, press and hold the “Off” (bottom) button on the remote for
Press OK
5 seconds. The LED on the QS IR Eye will begin to flash slowly. Press the“OK” button on the GRAFIK Eye® QS control unit to continue.
2a. To assign the QS IR Eye as a zone controller, use the Master buttons toChange type?
select “Zone” and press the “OK” button to accept. Use the zone raise/
lower buttons on the GRAFIK Eye® QS control unit to select a desiredZone
preset level, then press the zone raise and lower buttons simultaneouslyfor 1 second (until the zone LEDs flash at the programmed preset level).
Repeat for all zones you wish to assign to the QS IR Eye. The info screen
will confirm that your settings have been saved.

MasterbuttonsOK“OK”
buttonPress andhold thetop scene
button for
3 seconds
to associate
QS IR EyeOR
SavedSaved

2b. To assign the QS IR Eye as a scene controller, use the Master buttons
to select “Scene” and press the “OK” button to accept. Use the Masterbuttons to select “Favorite”, and press the “OK” button to accept. Use
the Master buttons to select your desired favorite scene, and press the“OK” button to accept. Press and hold the top scene button on the
GRAFIK Eye® QS control unit for 3 seconds (until the scene LEDs flash).
The info screen will confirm that your settings have been saved.
3. Point the IR remote at the QS IR Eye. To exit programming mode, press
and hold the “On” (top) button on the remote for 5 seconds, then, within
1 second, press and hold the “Off” (bottom) button on the remote for
5 seconds.

OR
Change type?
Scene

Zone LEDs
1 9

2 10

Zone Raise
Zone Lower

LED

Change type?
QS IR Eye

Favorite

Button Setup
Favorite
Scene

1

SavedSaved

MIR-ITFS
C-FLRC®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 51

IR Setup (continued)
Associating IR receivers through a QS Sensor Module (QSM):
1. Upon power up, the QSM will automatically detect andMain menu
configure wired IR receivers after a valid signal is received.
Wireless ModeUse an IR remote to send a signal to all connected receivers
in the system.
IR Setup
2. Enter programming mode on the GRAFIK Eye® QS control unit.
3. Use the Master buttons to highlight “IR Setup” and press the“OK” button to accept
IR menu
4. Use the Master buttons to highlight “Programming” andIntegral IR
press the “OK” button to accept. The info screen will display“Searching” while the unit detects available infrared receivers.
Programming
5. Use the Master buttons to scroll through the list of available
infrared receivers (the displayed IR receiver will flash). When thedesired IR receiver is displayed, press the “OK” button to selectit. Press the “OK” button again to continue.
6a.
To assign the IR receiver as a zone controller, use the MasterSearching...
Saved
buttons to select “Zone” and press the “OK” button to accept.
Use the zone raise/lower buttons for a zone to select a desiredpreset level, then press the zone raise and lower buttons
simultaneously for 1 second (until the zone LEDs flash at the
IR Setup
x/y
programmed preset level). Repeat for all zones you wish tocontrol with the IR receiver.
xxxx-xxxx
QS

1

QSM
Change Type?
Press OK

MasterbuttonsOK“OK”
buttonPress andhold thetop scene
button for
3 seconds
to assign
IR receiver
as a scene
controller.

Zone LEDs
1 9

2 10

Zone Raise
Zone Lower

OR
6b. To assign the IR receiver as a scene controller, use the Masterbuttons to select “Scene” and press the “OK” button to accept.
Press and hold the top scene button on the GRAFIK Eye® QScontrol unit for 3 seconds (until the scene LEDs flash).
7. Press the Timeclock (back) button twice to return to the list ofavailable IR receivers and repeat as needed.
8. Exit programming mode on the GRAFIK Eye® QS control unit.

Change type?

Wired IR
Receiver

Change type?

Zone

Scene

®

QS Sensor
Module (QSM)

SavedSaved

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 52

Associating Sivoia® QS Shades/Drapes and GRAFIK Eye® QS Control Units
When a GRAFIK Eye® QS system consists of Sivoia® QS shades (or drapes) and a GRAFIK Eye® QS with
one or more shade button groups, you can associate the shade button groups on the control unit with theshades so the shade buttons can directly control the shades.
For Sivoia® QS Shades wired directly to
the GRAFIK Eye® QS control unit:
To associate or disassociate shades
with a shade button group:
1. On the GRAFIK Eye® QS control unit
shade button group you wish to assign
shades to, enter shade programming
mode: Press and hold the top (open) andbottom (close) buttons simultaneously
for 3 seconds. The top and bottom LEDs
will flash. Shades that are unassigned
will move to up (open), and shades thatare assigned will move to close (down).
2. Tap the top (open) button to startassigning.
3. Tap the top (open) button repeatedly tocycle forward through the addresses;
tap the bottom (close) button to cycle
backward.
4. Press the shade group lower button toassociate the shade.
Press the shade group raise button todisassociate the shade.
Lower button: Press to
associate
Raise button: Press todisassociate

5. Exit shade programming mode: Press
and hold the top (open) and bottom(close) buttons simultaneously for 3
seconds. The top and bottom LEDs
will stop flashing.

®

For Wireless Sivoia® QS Shades:
To associate shades with a shade button group:
1. Make sure the wireless mode of the GRAFIK Eye® QS control
unit is “Enabled”.
2. On the GRAFIK Eye® QS control unit shade button group you
wish to assign shades to, enter shade programming mode:
Press and hold the top (open) and bottom (close) buttons
simultaneously for 3 seconds. The top and bottom LEDs
will flash.
3. The LEDs on the electronic drive unit (EDU) and the wirelessantenna of unassociated shades/drapes will blink slowly. On
the shade/drape that you wish to associate with the shade
button group, tap any button; the LED on the EDU will blink
rapidly to indicate the shade is now associated with theshade button group on the GRAFIK Eye® QS control unit.
4. Repeat step 2 to associate additional shades/drapes to thatshade button group.
5. Exit shade programming mode: Press and hold the top (open)
and bottom (close) buttons simultaneously for 3 seconds. The
top and bottom LEDs will stop flashing.
6. Repeat steps 1 through 5 for additional shade button groups,
as applicable.
To disassociate shades with a shade button group:
Repeat, in the same order, the steps above for associatingshades/drapes. When in shade programming mode, tap
any button on the electronic drive unit (EDU) of the shades/
drapes that you wish to disassociate from the shade button
group; the green LEDs on the EDU and antenna will blink
slowly to indicate the shade is disassociated from the shade
button group on the GRAFIK Eye® QS control unit.

Open
PresetClose

Press and hold the top(open) and bottom (close)
buttons on the GRAFIK
Eye® QS control unit shade
button group to enter orexit shade programming
mode.

LED

Sivoia® QS Wirelessshade/drape EDU

Note: The wireless signal has a range of 30 ft (9 m) throughstandard construction or 60 ft (18 m) line of sight.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 53

Adjusting Shade Settings (for Wired and Wireless Sivoia® QS Shades/Drapes)
Setting Limits(for wired shades/drapes only)
Note: Entering “Limit Setup” mode
may cause shades to moveapproximately 8 in (200 mm) up or
down. Be sure that each shadeis positioned so that the fabriccan safely move 8 in (200 mm) up
or down before entering “Limit
Setup” mode.
1.On any shade button group, press andhold simultaneously the top and raise
buttons. The LEDs next to the top andbottom buttons will cycle.

At any time while in “Limit Setup” mode,
you can move all shades together to theircurrent open limit by double-tapping the
top button, or to their current close limit
by double-tapping the bottom button.
Note: Shade/drape electronic drive units(EDUs) must first be associated toa shade button group before its
limits can be adjusted.

®

2. Select the EDU you want to adjust using
the top button on the shade button
group. Each time you press and release
the top button, a different EDU that is
assigned to that shade button group will
open and close in an 8 in (200 mm) range
to indicate it is selected.
Tap the top button until the EDU for the
shade you wish to adjust moves. (Youcan also use the bottom button, whichmoves through the assigned EDUs in the
opposite order.)3. Adjust the currently selected EDU to
the desired level for the open limit (themaximum the shade is allowed to open)
using the raise and lower buttons.

7. Repeat steps 2 through 6 to set the open
and close limits for each shade assigned
to the shade button group.
8. Press and hold simultaneously the top
and raise buttons on the shade button
group to exit “Limit Setup” mode.
Note: Remote limits cannot be set for
Sivoia® QS wireless shades throughthe GRAFIK Eye® QS control unit.
Limits must be set manually at
the wireless shade EDU. (Seethe Sivoia® QS wireless shade
instructions.)

4. Press and hold the top button on theshade button group for 5 seconds tostore the current position as the open
limit. The LED next to the top button will
flash quickly for 2 seconds.
5. Adjust the currently selected EDU to
the desired level for the close limit (themaximum the shade is allowed to close)
using the raise and lower buttons.
6. Press and hold the bottom button on
the shade button group for 5 seconds
to store the current position as the close
limit. The LED next to the bottom button
will flash quickly for 2 seconds.

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 54

Adjusting Shade Settings (for Wired and Wireless Sivoia® QS Shades/Drapes) (continued)
Preset Adjustment: Simple Method
1. Use the raise and lower buttons on theshade button group to set all electronic
drive units (EDUs) of the shades to thedesired preset levels.

2. Press and hold the middle button on theshade button group for 5 seconds tosave the EDU preset positions. The LED
next to the button will flash and then light
continuously, indicating the preset has
been stored.

Preset Adjustment: Advanced Method• The advanced method for adjustingpresets is needed only if you wish tohave the shades assigned to the shade
button group set at different positions in
the preset. If, however, you wish all the
shades in the group to be lined up with
one another in the preset, you should use
the Simple Method at left.
• Entering “Assignment” mode will cause
the shades to move between their open
and close limits. Verify that the open andclose limits have been set correctly.

1. On the shade button group whose
Note: Once EDU presets have beenpreset you wish to adjust, press andassigned to buttons on a shadehold simultaneously the top and bottom
button group, those presets are
buttons. The LEDs next to the buttons
accessible for an EDU only using
will flash. EDUs for the assigned shades
the shade button group it iswill move to their closed limits, and EDUs
assigned to, and a shade button
for unassigned shades will move to theirgroup can access preset levels only
open limits.
for those EDUs assigned to it.
2. Press and release the middle button onthat shade button group. The adjacent
LED will blink rapidly. EDUs for assigned
shades will automatically move to theircurrent preset settings.

®

3. Use the raise and lower buttons to move
all EDUs for assigned shades together tothe desired preset setting.

4. To move an EDU individually to its
desired preset setting, select the EDU
using the top button on the shade button
group. Each time you press and release
the top button, a different EDU that is
assigned to that shade button groupwill open and close in an 8 in (200 mm)
range. Press repeatedly until the EDU
for the shade you wish to adjust moves.
Adjust that EDU to the desired heightusing the raise and lower buttons.
Repeat this step for all assigned EDUs.
5. Once you are satisfied that all theassigned EDUs are set to the positions
you want to assign as the preset, press
and hold the middle button on the shade
button group for 5 seconds. The preset
will be saved.
6. Press and hold simultaneously the top
and bottom buttons on the shade button
group for 5 seconds to exit to normal
mode. The LEDs next to the buttons willstop flashing.

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 55

Adjusting Shade Settings (for Wired Window Treatments) (continued)
Naming a Group of Shades
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Shade Setup” and press
Sensor Setup
the “OK” button to accept.*
Shade Setup
3. Use the Master buttons to highlight “Shade Labels” and press
the “OK” button to accept.
4. Use the Master buttons to highlight your desired shade group.
Shade Setup
Press the “OK” button to accept.
5. Use the Master buttons to highlight “Custom” and press the
Shade
LabelsTimeclock“OK” button to accept.
Stop If Moving
6. Use the Master buttons to scroll through the characters(lowercase and uppercase letters, plus numbers 0 through 9).
The character you are currently changing will be underlined
Select groupon the screen. Press OK to select the character you want,then repeat for all available characters. Choose a space (noShade Grp 1
character) and press OK for any remaining characters. Press
the “OK” button to accept.
7. The info screen will confirm that your name has been saved.
8. Exit programming mode.
Label shade grp

16

9-16
1-8

MasterbuttonsOK“OK”
buttonCustomLabel shade grp 1
1 / 11

A

1: A

Saved

* Applicable only to units that ship with firmware version 9.003 and higher. For previous versions, skip step 2 and proceed to step 3.

®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 56

Adjusting Shade Settings (for Wired Window Treatments) (continued)
Enable/Disable “Stop If Moving” Functionality (software revision 9.003 or higher)
If the GRAFIK Eye® QS control unit can be configured to enable/disable the “Stop If
Moving” functionality: pressing shade column button stops the shade if it is alreadymoving, otherwise the shade is sent to the programmed level.
Follow the steps below to disable the “Stop If Moving” functionality (it is enabled bydefault):
1. Enter programming mode.
Main Menu
2. Use the Master buttons to highlight “Shade Setup” and press
Shade
Setup
the “OK” button to accept.
Timeclock3.
In the Shade Setup menu, use the master buttons to highlight
Wireless Mode
“Stop If Moving” and press OK to accept.
4. For the desired shade column (on bottom left of QSG unit),press the “Open” button to enable “Stop If Moving” for that
Shade Setup
column or press the “Close” button to disable the “Stop If
Moving” feature. The display screen will change momentarily
Shade Labels
to indicate if “Stop If Moving” is enabled or disabled for the
Stop If Moving
selected shade column.
5. LEDs on the “Open” and “Close” buttons will indicate thecurrent selection for the shade column.
Stop If Moving
6. Once the process is complete, hit the back button to go backto the main menu.
For each shade16

Masterbuttons

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

1 9

2 10

3 11

4 12

5 13

Open button‘Open’ Enables

Shadebutton group

Shade Group N...

Close button

Stop If Moving
Disabled®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 57

Associating Sivoia® QS Triathlon® Shades with GRAFIK Eye® QS Control Unit
Confirm Wireless Mode Enabled
1. Enter Programming mode: Press andhold the top and bottom Scene buttons
simultaneously for 3 seconds. The LEDs
in the Scene buttons will scroll from top
to bottom, confirming the control unit isin Programming mode, and the Info
screen will display the Main menu.

1

2

3

4

5

MasterbuttonsInfoscreenShade button groups

6

OK

1
2
3
4
Off

GRAFIK Eye® QS Control Unit

2. Use the Master
Main menu
buttons to highlight
Shade labels“Wireless Mode” inthe Main menu, andWireless modepress the OK button
to accept.
3. Use the MasterWireless mode
buttons to highlight“Enabled” and press
Enabledthe OK button toaccept.
4. The Info screen will
display a confirming“Saved” message.
Saved
5. Exit Programming
mode: Press andhold the top andbottom Scene buttons
simultaneously for 3 seconds. The Info
screen will go to Scene 1.

Associate Shades
1. Tap the Shade button on the shade toassign. The Shade button LED will turn onsolid green, and the shade will wait in thismode for 30 seconds.

Roller Shade Button

Scenebuttons
Honeycomb Shade Button

2. Choose a Shade button group on the
GRAFIK Eye® QS control unit. Press andhold the Close button in that group for
6 seconds. All LEDs in the Shade button
group and the Shade button LED will
flash then turn off.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 58

Setting Upper and Lower Limits of a Sivoia® QS Triathlon® Shadewith GRAFIK Eye® QS Control Unit
1. Verify that the shade is associated with
the intended Shade button group of the
GRAFIK Eye® QS control unit.
2. Tap the Shade button on the Sivoia® QS
Triathlon® shade. The Shade button LED
will turn on solid green, and the shade
will wait in this mode for 30 seconds.

4. Use the Raise/Lower buttons to position
the shade at the desired level for theupper limit (the maximum the shade isallowed to open).

7. Use the Raise/Lower buttons to position
the shade at the desired level for the
lower limit (the maximum the shade isallowed to close).

5. Press and hold the Open button for 5
seconds to store the current position as
the upper limit. The Open button LED will
flash quickly for 2 seconds

8. Press and hold the Close button for
5 seconds to store the current position
as the lower limit. The Close button LED
will flash quickly for 2 seconds.

6. Set the lower limit: Repeat steps 2 and 3
to enter Limit Set mode.

9. Repeat steps 1 through 8 to set theupper and lower limits for each Sivoia®
QS Triathlon® shade.

OR

Tap shade button

3. In the GRAFIK Eye® QS Shade button
group associated with the shade,simultaneously press and hold the Openand Raise buttons for 5 seconds.

®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 59

Associating Multiple GRAFIK Eye® QS Control Units
When there is more than one GRAFIK
Eye® QS control unit in a system, it isoften convenient to associate them sothat certain functions carry over to otherassociated GRAFIK Eye® QS control
units.

To associate two GRAFIK Eye® QScontrol units:
1. Begin with the GRAFIK Eye® QS control
unit that will “talk” (button presses will
be replicated on the other control unit; inthe drawing below this is GRAFIK Eye®
QS control unit A). Press and hold the top• Wired units: When first wired on the QS
and bottom scene buttons until the LEDs
link, all unprogrammed GRAFIK Eye® QS
flash (about 3 seconds).
wired control units will replicate scene
2.
Continue with the GRAFIK Eye® QS
activations and Master button presses bycontrol unit that will “listen” (replicate
other control units on the link. Associating
button presses on the other control unit;
or disassociating control units determinesin the drawing below this is GRAFIK Eye®
which units on the QS link will “talk”
QS control unit B). Press and hold the top
or “listen” to each other. Control units
scene button until the LEDs flash (about 3
associated on a wired QS link will also
seconds).
replicate timeclock and contact closure
3.
Return to the GRAFIK Eye® QS control
settings.
unitthat will “talk” (A). Press and hold the• Wireless units: GRAFIK Eye® QS
topandbottom scene buttons until the
Wireless control units will not
LEDs
stop
flashing (about 3 seconds).
automatically replicate scene activations
4.
Repeatingtheprocess in reverse allows
or Master button presses, and must
GRAFIKEye® QS control unit A to also
be programmed to do so. (Associating“listen” to GRAFIK Eye® QS control unit
two wireless control units will not passB, so that both units will follow eachtimeclock and contact closure settingsother.
to each other.) When associating multiple
To disassociate two GRAFIK Eye® QS
wireless control units, make sure thecontrol units:
wireless mode of both units is set to“Enabled.”
Simply repeat the association steps,in the same order; press and holdNote: The wireless signal has a range
the bottom scene button on B toof 30 ft (9 m) through standard
disassociate.
construction or 60 ft (18 m) lineof sight.

®

9-16
1-8

9-16
1-8

OK

On the unit that will “talk”, press
and hold the top and bottom
scene buttons for 3 seconds
to begin or end association ordisassociation with the unit thatwill “listen”.

OK

Associate
OR
Disassociate
On the unit that will “listen”, press and hold the
top scene button for 3 seconds to associate,or press and hold the bottom scene button for
3 seconds to disassociate with the unit that will“talk”.

OK

GRAFIK Eye® QScontrol unit A“Talks” to GRAFIK
Eye® QS control unit
B; scene activationand Master buttonpresses activatedon control unit A are
replicated on control
unit B.

OK

GRAFIK Eye® QScontrol unit B“Listens” to GRAFIK
Eye® QS control
unit A; control
unit B replicatesscene activations
and Master buttonpresses on control
unit A.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 60

Timeclock Operation
Setting Time and Date
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Timeclock” and press theTimeclockTimeclock“OK” button to accept.
Scene setup
3. Use the Master buttons to highlight “Time & date” and press
the “OK” button to accept.
4. Use the Master buttons to highlight either “12 Hr” or “24 Hr”
Timeclockformat for time display and press the “OK” button to accept.
5.
Use the Master buttons to highlight the current hour and press
End afterhours
the “OK” button to accept. Repeat for the current minutes.
Time & date
6. Use the Master buttons to highlight the current year and press
the “OK” button to accept. Repeat for the current month and date.
7.
The info screen will confirm that your time and date have
Set format
been saved.
8. Exit programming mode.

16

9-16
1-8

MasterbuttonsOK“OK”
button

12 Hr

Set time
08 : 00 AM

Set time
08 : 30

Set dateAM

Set date: 00 2009

March

®

Set date
17

Saved

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 61

Timeclock Operation (continued)
Setting Location
Main menu
TimeclockTimeclock
Scene setup

TimeclockTime & date
Location

Location byCountry, City
Lat/Longitude

Country16

1. Enter programming mode.
2. Use the Master buttons to highlight“Timeclock” and press the “OK” button
to accept.
3. Use the Master buttons to highlight“Location” and press the “OK” button
to accept.
4. Use the Master buttons to set yourlocation by either country and cityor latitude and longitude. Press the“OK” button to accept.
5. Use the Master buttons to highlightthe country and press the “OK” button
to accept. Repeat for the state andclosest city.
6. The info screen will confirm that yourtime and date have been saved.
7. Exit programming mode.

08 : 00
USA

State
Pennsylvania

City
Saved

Philadelphia

®

9-16
1-8

MasterbuttonsOK“OK”
buttonSetting Daylight Saving Time
1. Enter programming mode andTimeclockselect “Timeclock”. Use the Master
Locationbuttons to highlight “Set DST” andpress the “OK” button to accept.
Set DST
2. Use the Master buttons to highlight“Yes” if your location observes
daylight saving time, or “No” if it
DST
does not. Press the “OK” button toaccept.
: 00 Yes
3. If yes, use the Master buttons tochoose either “USA 2007” (thesecond Sunday in March to the first
Sunday in November), or “Other.”For “Other,” follow the screens to
set start and end dates and amountof time.
4. Press the “OK” button to accept.
The info screen will confirm thatyour time and date have beensaved.
5. Exit programming mode.

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 62

Timeclock Operation (continued)
Adding an Event
Main menu
TimeclockTimeclock
Scene setup

TimeclockView events
Add events

Add events
MondayAdd events
Local

Add events
Time of day

Set time
08 : 00 AM

16

Master
1. Enter programming mode.
buttons
2. Use the Master buttons to highlight “Timeclock” and press
OK“OK”
the “OK” button to accept.
button
3. Use the Master buttons to highlight “Add events” and press
the “OK” button to accept.
4. Use the Master buttons to highlight the recurrence for this event: day of the week, holiday, weekdays or
weekends. Press the “OK” button to accept.
5. Use the Master buttons to highlight the location of the timeclock event (local or remote). Press the“OK” button to accept.
• Local events affect scenes controlled by the GRAFIK Eye® QS Control Unit
• Remote events affect scenes controlled by another device on the QS link (e.g. Energi Savr NodeTM QS)
Note: Remote timeclock events provide a virtual timeclock to devices on the QS link without a built-in
timeclock. This allows the GRAFIK Eye® QS control unit to activate scenes on other devices without
affecting the space it controls.
6. Use the Master buttons to highlight the type of the event (fixed time of day or a relative time to sunrise orsunset). Press the “OK” button to accept.
7. For a fixed-time event, use the Master buttons to highlight the hour for your event to begin; press the“OK” button to accept. Repeat for the minutes.
For a relative time event, use the Master buttons and the “OK” button to set the hour, then the minutes
relative to sunrise or sunset (maximum of 1 hour, 59 minutes before or after sunrise or sunset).
8. Use the Master buttons to highlight the desired action for the timeclock event:• Scenes 1-16, Off• Shade Groups 1-3 open, preset, or close• Start/End Afterhours• Enable/Disable Occupancy• Enable/Disable Occupied Events• Enable/Disable Daylighting
9. The info screen will confirm that your event has been saved.
10. Repeat steps 4 through 9 for additional events.
11. Exit programming mode.
Add events
9-16
1-8

Scene
Scene 1®

Saved

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 63

Timeclock Operation (continued)
Deleting an Event
Main menu
TimeclockTimeclock
Scene setup

Timeclock
Copy schedule
Delete events

DeleteMondayDelete01/03

8:00 AM
Scene 516

1. Enter programming mode.
2. Use the Master buttons to highlight“Timeclock” and press the “OK” button
to accept.
3. Use the Master buttons to highlight“Delete events” and press the“OK” button to accept.
4. Use the Master buttons to highlight the
day of the week (or holiday) when theevent occurs; press the “OK” button toaccept.
5. Use the Master buttons to highlight theevent to delete; press the “OK” button toaccept.
6. A screen will appear, verifying you wish todelete the event. Press the “OK” button
to accept and delete; otherwise, press
the Timeclock button to go back.
7. The info screen will confirm that yourevent has been deleted.
8. Exit programming mode.

9-16
1-8

OK

“OK”
buttonTimeclock(back) button

Viewing an Event
TimeclockView
eventsDeleteeventsAdd events

Delete?

View events
MondayMondayDeletedView
8:00 AM
Scene 5®

Masterbuttons

1. Enter programming mode, select“Timeclock,” and select “View events”.
2. Use the Master buttons to highlight the
day of the week (or holiday) when theevent occurs; press the “OK” button toaccept.
3. Use the Master buttons to highlight theevent to view; press the “OK” button toaccept.
4. Press the “OK” button to return to theTimeclock menu.
5. Exit programming mode.

1/3
L

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 64

Timeclock Operation (continued)
Setting a Holiday
Timeclock
Delete schedule
Holiday

Holiday
Add
Setevent
holiday
View holiday

Set holiday
1/25

Feb

1

16

1. Enter programming mode.
2. Use the Master buttons to highlight“Timeclock” and press the “OK” button
to accept.
3. Use the Master buttons to highlight“Holiday” and press the “OK” button
to accept.
4. Use the Master buttons to highlight“Set holiday” and press the“OK” button to accept.
5. Use the Master buttons to highlightthe month of the holiday and press
the “OK” button to accept. Repeat forthe date.
6. The info screen will confirm that yourholiday has been set.
7. Exit programming mode.

Masterbuttons

9-16
1-8

OK

“OK”
buttonViewing a Holiday
1. Enter programming mode, selectView Holiday
1/25“Timeclock,” select “Holiday,” and select“View holiday”.
Feb 14
2. Use the Master buttons to scroll throughthe dates of the programmed holidays.
OR
3. If no holidays are programmed, the info
screen will display a screen informing you.
4. Exit programming mode.
MondayNo Holidays

Set holiday
1/25

Monday14
Feb

Note: The GRAFIK Eye® QS with
EcoSystem® control unit
supports up to 25 uniqueholidays. Follow the steps
in “Adding an Event” to add
Holiday timeclock events.

Saved

Deleting a Holiday
1. Enter programming mode, selectHoliday“Timeclock,” select “Holiday,” and selectView holiday“Delete holiday”.
Delete holiday
2. Use the Master buttons to highlight theholiday you wish to delete (or delete allholidays) and press the “OK” button toaccept.
Delete holiday
3.
Press the “OK” button to delete the
1/2
Mondayselected holiday. The info screen will
Feb 14
confirm that your holiday has been
deleted.
4. Exit programming mode.
Delete holiday
1/2

Delete?

®

DeletedGRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 65

Timeclock Operation (continued)
Copying a Schedule
1. Enter programming mode.
Timeclock2. Use the Master buttons to highlight
Copy schedule
Deleteschedule“Timeclock” and press the “OK” button
to accept.
Delete events
3. Use the Master buttons to highlight“Copy Schedule” and press the“OK” button to accept.
Copy from
4. Use the Master buttons to highlight the
Mondayday you want to copy the schedule fromand press the “OK” button to accept.
5. Use the Master buttons to highlight the
day you want to copy the schedule to
Copy toand press the “OK” button to accept.
6.
The info screen will ask you to confirm
MondayTuesday
overwriting all events occurring on theselected day to copy to; press the“OK” button to accept.
7. Exit programming mode.
TimeclockMondayOverwrite
all events?

Saved

16

9-16
1-8

MasterbuttonsOK“OK”
buttonDeleting a Schedule
1. Enter programming mode, selectTimeclock“Timeclock,” and select “Delete
Delete events
schedule”.
Delete schedule
2. Use the Master buttons to highlight the
day of the schedule you wish to delete
and press the “OK” button to accept.
Delete schedule
3. The info screen will confirm that yourevent has been deleted.
MondaySunday4. The info screen will ask you to confirm
deleting the schedule on the selected
day; press the “OK” button to accept.
5. Exit programming mode.
DeleteSundayschedule?

Deleted®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 66

Afterhours
The Afterhours feature of the GRAFIK Eye® QS control unit can be used to automatically set lights to an energy-saving level (typically“Scene Off”). This feature allows occupants to manually turn on lights, but will automatically turn them off after a specified amount oftime.
When Afterhours starts, the lights will flash to alert occupants that the lights will soon fade to the Afterhours Scene. Occupants thencan press a keypad button to extend the time until the Afterhours feature flashes the lights again.
The Afterhours feature of the GRAFIK Eye® QS control unit has three (3) modes of operation:• Enabled: The GRAFIK Eye® QS control unit will allow the Afterhours feature to be activated.
• Follow: The GRAFIK Eye® QS control unit will execute the Afterhours settings of another associated device on the QS link.
• Disabled (default): The GRAFIK Eye® QS control unit will not start the Afterhours feature (even if it receives commands from a
Timeclock event, contact closure input, or another device on the QS link).
Note: The Afterhours feature must be programmed to start or end through Timeclock events, the integral contact closure input, or
another associated device on the QS link. The GRAFIK Eye® QS control unit will activate this feature only if the “Afterhours”
mode has been set to “Enabled” or “Follow”.
Afterhours Settings
Flash count: The amount of times the lights will flash to alert the room that the Afterhours Scene will soon be activated.
Range: 0 to 15 flashes (default 3 flashes)
Delay to off: The amount of time after the end of the “Flash count” before the Afterhours Scene is activated.
Range: 1 to 180 minutes (default 5 minutes)
Delay to flash: The amount of time the system will wait after the Afterhours Scene is interrupted before flashing the lights again andrestarting the Delay to off countdown.
Range: 1 to 180 minutes (default 45 minutes)
Afterhours scene: The scene that the GRAFIK Eye® QS control unit will activate when the Delay to off expires.
Range: Scenes 1 to 16, Off (default Scene off)
(See example on the next page.)®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 67

Afterhours (continued)
Afterhours Examples

Afterhours ends

Afterhours starts;
Lights flash
Example 1: Typical Office

Delay to off

Afterhours Scene

Example 2: Late Night at Office

Delay to off

Delay to flash

Delay to off(lights
flash)

Afterhours Scene

Button press:
Office worker
Example 3: Late Night/Security Check

Delay to off

Delay to flash

Delay to off(lights
flash)

Button press:
Office worker®

Afterhours Scene

Delay to flash Delay to off(lights
flash)

Afterhours Scene

Button press:
Security guard

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 68

Afterhours (continued)
Setting Up Afterhours
1. Enter programming mode.
Main menu
2. Use the Master buttons to highlight “Timeclock”, and press
TimeclockTimeclockthe “OK” button to accept.
Scene setup
3. Use the Master buttons to highlight “Afterhours setup”, andpress the “OK” button to accept.
4. Use the Master buttons to select the desired “Afterhours”
Timeclockmode, and press the “OK” button to accept.
5. (If the “Afterhours” mode was set to “Enabled”)
Holiday
Use the Master buttons to highlight the desired values for
Afterhours setup
Flash count, Delay to off, Delay to flash, and Afterhours scene.
Press the “OK” button to accept each setting. The info screen
will confirm that your Afterhours settings have been saved.
Afterhours
6. Exit programming mode.
EnabledDelay to flash
45

minutes

Flash count3

Delay to off
5

Afterhours

minutes

Scene off

®

Saved

16

9-16
1-8

OK

Masterbuttons“OK”
buttonEnding Afterhours
Once activated, the Afterhours feature canbe overridden at any time and ended throughthe programming menu.
1. Enter programmingmode.
End afterhours
2. Use the Masterbuttons to highlight“Timeclock”, andpress the “OK” button
to accept.
3. Use the Masterbuttons to highlight“End Afterhours”, andpress the “OK” button
to accept. The info
screen will confirm
that “Afterhours”
mode is ended.
4. Exit programming
mode.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 69

Diagnostics and Special Settings
Enabling/Disabling the Timeclock
The timeclock can be enabled or disabled as desired.
1. Enter programming mode. Use the Master
Timeclockbuttons to select “Timeclock.” Press the“OK” button to accept.
MondayEnabled
2. Use the Master buttons to highlighteither “Enabled” or “Disabled”. Press the“OK” button to accept. The info screen will
confirm that your setting has been saved.
3. Exit programming mode.

16

9-16
1-8

OK

Masterbuttons“OK”
buttonSaved

Enabling/Disabling the Backlighting
The backlighting on the info screen can be enabled or disabled as
desired.
1. Enter programming mode and selectBacklighting“Backlighting”. Press the “OK” button toaccept.
MondayEnabled
2. Use the Master buttons to highlighteither “Enabled” or “Disabled”. Press the“OK” button to accept. The info screen will
confirm that your setting has been saved.
3. Exit programming mode.
Saved

®

Diagnostics
If you are having trouble with your control unit and call
LutronR Technical Support, you may be asked for
diagnostic information about your unit.
1. Enter programming mode andDiagnostics
select “Diagnostics”. Press theDevice SN“OK” button to accept.
2. Use the Master buttons to highlight
Link Info
the option that will display therequired information. The info
screen can display the device serial
number, link information, code
version, or USB status. There is
Link info
also an option to reset the USB
connection (do this only if asked toby LutronR Technical Support).
3. Exit programming mode.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 70

Diagnostics and Special Settings (continued)
Setting the Security Password
A four-digit password can be set as a security feature to protect the
programming settings on the GRAFIK Eye® QS control unit.
1. Enter programming mode
Diagnostics
2. Select “Diagnostics” and press the “OK” button
Reset USB
to accept.
Password
3. Select “Password” and press the “OK” button
to accept.
4. Select “Set Password” and press the “OK” button
Passwordto accept.
5.
You will be prompted to input a four-digit password.
Set Password
Use the Master buttons to scroll through the
Disablecharacters (uppercase letters and numbers 0 through9 only). The character you are currently changing
in the password will appear underlined on the info
screen. Press OK to select the desired character,
Password
4/4
and repeat for the remaining characters.
The info screen will confirm that your setting has
D
1: ABCD
been saved.
6. Exit programming mode.

16

9-16
1-8

4/4

1: * * * *Password
Set Password
Disable®

Masterbuttons“OK”
buttonEnter Password

Saved

OK

D

When you re-enter programming mode
after setting your password, you will beprompted to enter your password. Use
the method in Step 5 above to select andenter each character.
Note: The characters will appear on theinfo screen as asterisks.

To disable your password, follow Steps
1 through 4 of “Setting the Security
Password”, and select “Disable” on the
Password menu.

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 71

Faceplate Removal

Language Selection
The GRAFIK Eye® QS control unit iscapable of operating in the following
languages:• English• French• Spanish• German• Italian• Portuguese
To change the language to one of thesechoices, press the Timeclock button
four times, until the “Language” screen
is displayed. (Note: Do not put the unit
in programming mode.) Use the Masterbuttons to highlight your preferredlanguage, and press the “OK” button to
select and save.

The faceplates may need to be removed to change the color
or to write in zone labels. To remove either faceplate, open it
fully (flush to the wall), and pull up (for the top faceplate) or
down (for the bottom faceplate) to pull the hinges out of theirslots.
Replace by sliding the hinges back into their slots.

Pull up to remove
top faceplate

1

2

3

4

5

6

OK

16

9-16
1-8

MasterbuttonsOK“OK”
buttonTimeclock(back) button®

Pull down toremove bottom
faceplate

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 72

Troubleshooting
Symptom

Possible Causes

Solution

Unit does not power up

Circuit Breaker is off

Switch circuit breaker on

Unit does not control loads

MiswireVerify wiring to unit and loads

Circuit breaker is tripping

System short circuited

Find and correct shorts

System overload

Verify zone/unit loading is within ratings (see Zone Setup section)

Zone control does not work

MiswireMake sure loads are connected to the right zones

Zone control yields incorrect
results

Loose or disconnected wire

Connect zone wires to loads

Burned out lamps

Replace bad lamps

Incorrect load type selected

Assign the zone to the appropriate load type (see Zone Setup section)

Dimming limits set incorrectly

Adjust High End/Low End values (see Zone Setup section)

One or more zones arealways “full on” and zone
intensity is not adjustable
Zone control affects morethan one zone

MiswireMake sure loads are connected to the right zones

Shorted line output

Check wiring; if wiring is correct, call LutronR Technical Support

Faceplate is warm

Normal operation

Solid-state controls dissipate about 2% of the connected load as heat. No action is required

Unit does not allow scenechange or zone adjustments

Unit is in wrong save mode

Change to correct save mode

QS device in system has locked the unit

Check programming and state of QS devices

Cannot program fade timefrom “Scene Off”

Fade time from “Scene Off” is notprogrammable; can only program fade time to“Scene Off”

Fade time from “Scene Off” is always 3 seconds

Integral (direct-wired) contact
closure input does not work

MiswireCheck wiring on contact closure input

QS devices on link are notworking

Timeclock events do not
occur
Sunrise or sunset events do
not occur at the correct time

Input CCI signal is not received

Verify the input device is operating properly

Unit is in wrong CCI mode and/or type

Change to correct CCI mode and/or type for your application

Miswire or loose connection on QS link

Verify QS link wiring to all devices

QS device is not associatedPlace the QS device into programming mode, and hold the “Scene 1” button on the
GRAFIK Eye® QS control unit to associate the two devices

QS device programming is incorrect

Verify the functionality and programming on the QS devices

Timeclock is disabled

Enable the timeclock

Time/date is not set correctly

Set the time/date

Location is not set correctly

Set the latitude and longitude of the unit’s location

Holiday schedule is in effectNormal schedule will resume when the holiday ends®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 73

Troubleshooting (continued)
Symptom

Possible Causes

Solution

Device does not respond to
infrared controls

IR Receiver is disabled

Enable the IR receiver

Miswire or loose connection on rear IR terminal

Verify rear IR terminal wiring

Security lockout fromprogramming mode

Security password set incorrectly

Call LutronR Technical Support to reset password

Troubleshooting: Wireless Functions (for wireless enabled units only)
Symptom

Possible Causes

Solution

Cannot associate awireless device to a unit

Unit does not support wireless functionality

Verify the unit says “GRAFIK Eye® QS Wireless” on the front label.

Associated wirelessdevices do not control unit

Wireless devices operate
incorrectly
Wireless devices selectively
operateInfo screen often prompts
for wireless device
association

Unit in incorrect wireless mode

Change wireless mode to “Enabled”

Maximum number of devices have been
associated with unit

Remove devices or associate with a different unit

Wireless device is out of range

Verify wireless device is in range: 30 ft (9 m) through standard construction, 60 ft (18 m) line ofsightWireless device has been unassigned from unit

Reassign wireless device to unit

Devices are not receiving power

Check wireless device’s battery/power wiring

Unit in incorrect wireless mode

Change to correct wireless mode (“Ignore Programming” or “Enabled”)

Multiple devices are associated to the unit with
contrasting settings

Verify the settings of wireless devices are consistent

Wireless device is out of range

Verify wireless device is in range: 30 ft (9 m) through standard construction, 60 ft (18 m) line ofsightRadio Powr SavrTM daylight sensors not incalibration mode

Follow instructions to calibrate daylight sensors

System is not configured correctly

Make sure wireless device settings are programmed as desired

Intended settings were not saved

Reprogram wireless device settings

Wireless devices not located correctly

Follow instructions for each device to verify it is located for ideal performance

Unit wireless mode set to “Enabled” and nearby
wireless systems are being programmed

Change wireless mode to “Ignore Programming”®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 74

Troubleshooting: Shade Functions
Symptom

Possible Causes

Solution

Shade EDU (electronic driveunit) will not move

EDU is not powered

Connect power to EDU

Shade fabric is caught on something

Check and unbind shade fabric

EDU is not assigned to a shade button group

Assign the EDU to a shade button group

All limits are set to the same height

Verify limit settings

Communications link is not wired to the EDU

Check and wire the EDU link

EDU has been unassigned from shade button
group

Reassign the EDU to the shade button group

Shade EDU does not fully
open or fully close

Limits have been set incorrectly

Set limits correctly

Shade fabric is caught on something

Check and unbind shade fabric

Shade moves in the
opposite direction whenraise/lower buttons arepushedOpen and close limits have been reversed

Set limits correctly

Shade button group does
not operate all the shades it
is assigned to

EDU has been unassigned from shade button
group

Reassign the EDU to the shade button group

All limits are set to the same height

Verify limit settings

EDU is not wired correctly

Check and rewire EDU

Shade button group is not wired correctly

Check and rewire shade button group

Shades in a room move on
their own

EDUs are assigned to a shade button group in
another room

Reassign the EDU to the correct shade button group

Unable to set limits on
Sivoia® QS wireless shades
through the GRAFIK Eye®
QS control unit.

Normal operation

Limits must be set manually on the Sivoia® QS wireless EDU (see Sivoia® QS wireless shadeinstallation guide)®

GRAFIK Eye® QS with EcoSystem® Installation and Operation Guide 75

Shade button group will not
control any shadeTroubleshooting: EcoSystem® Functions
Symptom

Possible Causes

Solution“Build System”
command does not find
EcoSystem® loads

E1 and/or E2 are miswired or not connected

Check wiring; if wiring is correct, call LutronR Technical Support

Cannot add an
EcoSystem® device toa zone after a “Build
System” or “Address all”
command has been run

Zone is not set to DigitalSet the zone to Digital

EcoSystem® device atfull brightness cannot be
controlled

E1 and E2 are not connected

Check E1 and E2 connections on the back of the GRAFIK Eye® QS with EcoSystem® control unit

EcoSystem® link is overloaded

Reduce number of EcoSystem® devices on link to 64 or fewer. Check voltage: Minimum voltageof 12 V-

EcoSystem® devices do
not flash when running
the “Build System”
command

EcoSystem® devices are not addressed
EcoSystem® devices are miswired

Address EcoSystem® devices
Check E1 and E2 wiring, and power wiring to EcoSystem® devices

EcoSystem® device is notaffected by a zone levelchangeEcoSystem® device is not addressed

Run the “Address all” command and assign the EcoSystem® device to a zone

EcoSystem® device is not assigned to a zone

Assign EcoSystem® device to a zone

Sensor is miswired

Check sensor wiring (refer to the sensor manufacturer’s instructions)Sensor was added after ”Build System”
command was run or EcoSystem® device may
not have detected sensor

Create motion (occupancy) or induce light (daylight) within the sensor’s range and run theappropriate “Sensor Setup” command

EcoSystem® device is being affected by the
daylight sensors

Recalibrate the associated daylight sensors

System does notrecognize sensors
connected to a
EcoSystem® device
Sensor wired directly to
an EcoSystem® device is
not found during sensor
setup
EcoSystem® device lightlevels can be lowered,but not raised to full On®

GRAFIK Eye® QS with EcoSystem® Control Unit Installation and Operation Guide 76

Contact Information

Warranty
Lutron Electronics Co., Inc.
One Year Limited Warranty
For a period of one year from the date of purchase, and subject
to the exclusions and restrictions described below, Lutron warrants
each new unit to be free from manufacturing defects. Lutron will,at its option, either repair the defective unit or issue a credit equal
to the purchase price of the defective unit to the Customer against
the purchase price of comparable replacement part purchasedfrom Lutron. Replacements for the unit provided by Lutron or, at its
sole discretion, an approved vendor may be new, used, repaired,reconditioned, and/or made by a different manufacturer.
If the unit is commissioned by Lutron or a Lutron approved third
party as part of a Lutron commissioned lighting control system, theterm of this warranty will be extended, and any credits against thecost of replacement parts will be prorated, in accordance with thewarranty issued with the commissioned system, except that theterm of the unit’s warranty term will be measured from the date ofits commissioning.
EXCLUSIONS AND RESTRICTIONSThis Warranty does not cover, and Lutron and its suppliers are notresponsible for:
1. Damage, malfunction or inoperability diagnosed by Lutron ora Lutron approved third party as caused by normal wear andtear, abuse, misuse, incorrect installation, neglect, accident,
interference or environmental factors, such as (a) use ofincorrect line voltages, fuses or circuit breakers; (b) failure to
install, maintain and operate the unit pursuant to the operating
instructions provided by Lutron and the applicable provisionsof the National Electrical Code and of the Safety Standardsof Underwriter’s Laboratories; (c) use of incompatible devices
or accessories; (d) improper or insufficient ventilation; (e)unauthorized repairs or adjustments; (f) vandalism; or (g) an act
of God, such as fire, lightning, flooding, tornado, earthquake,hurricane or other problems beyond Lutron’s control.
2. On-site labor costs to diagnose issues with, and to remove,repair, replace, adjust, reinstall and/or reprogram the unit or anyof its components.
3. Equipment and parts external to the unit, including those soldor supplied by Lutron (which may be covered by a separate
warranty).
4. The cost of repairing or replacing other property that is damaged
when the unit does not work properly, even if the damage wascaused by the unit.
EXCEPT AS EXPRESSLY PROVIDED IN THIS WARRANTY,
THERE ARE NO EXPRESS OR IMPLIED WARRANTIES OF ANY
TYPE, INCLUDING ANY IMPLIED WARRANTIES OF FITNESS FOR
A PARTICULAR PURPOSE OR MERCHANTABILITY. LUTRON
DOES NOT WARRANT THAT THE UNIT WILL OPERATE WITHOUTINTERRUPTION OR BE ERROR FREE.
NO LUTRON AGENT, EMPLOYEE OR REPRESENTATIVE HAS
ANY AUTHORITY TO BIND LUTRON TO ANY AFFIRMATION,
REPRESENTATION OR WARRANTY CONCERNING THE UNIT.
UNLESS AN AFFIRMATION, REPRESENTATION OR WARRANTYMADE BY AN AGENT, EMPLOYEE OR REPRESENTATIVE IS
SPECIFICALLY INCLUDED HEREIN, OR IN STANDARD PRINTEDMATERIALS PROVIDED BY LUTRON, IT DOES NOT FORM A
PART OF THE BASIS OF ANY BARGAIN BETWEEN LUTRON AND
CUSTOMER AND WILL NOT IN ANY WAY BE ENFORCEABLE BY
CUSTOMER.
IN NO EVENT WILL LUTRON OR ANY OTHER PARTY BE LIABLE
FOR EXEMPLARY, CONSEQUENTIAL, INCIDENTAL OR SPECIAL
DAMAGES (INCLUDING, BUT NOT LIMITED TO, DAMAGES FOR®

LOSS OF PROFITS, CONFIDENTIAL OR OTHER INFORMATION, OR
PRIVACY; BUSINESS INTERRUPTION; PERSONAL INJURY; FAILURE
TO MEET ANY DUTY, INCLUDING OF GOOD FAITH OR OF
REASONABLE CARE; NEGLIGENCE, OR ANY OTHER PECUNIARYOR OTHER LOSS WHATSOEVER), NOR FOR ANY REPAIR WORKUNDERTAKEN WITHOUT LUTRON’S WRITTEN CONSENT ARISINGOUT OF OR IN ANY WAY RELATED TO THE INSTALLATION,
DEINSTALLATION, USE OF OR INABILITY TO USE THE UNIT OR
OTHERWISE UNDER OR IN CONNECTION WITH ANY PROVISION
OF THIS WARRANTY, OR ANY AGREEMENT INCORPORATING
THIS WARRANTY, EVEN IN THE EVENT OF THE FAULT, TORT(INCLUDING NEGLIGENCE), STRICT LIABILITY, BREACH OF
CONTRACT OR BREACH OF WARRANTY OF LUTRON OR ANY
SUPPLIER, AND EVEN IF LUTRON OR ANY OTHER PARTY WASADVISED OF THE POSSIBILITY OF SUCH DAMAGES.
NOTWITHSTANDING ANY DAMAGES THAT CUSTOMERMIGHT INCUR FOR ANY REASON WHATSOEVER (INCLUDING,WITHOUT LIMITATION, ALL DIRECT DAMAGES AND ALL
DAMAGES LISTED ABOVE), THE ENTIRE LIABILITY OF LUTRONAND OF ALL OTHER PARTIES UNDER THIS WARRANTY ON ANY
CLAIM FOR DAMAGES ARISING OUT OF OR IN CONNECTION
WITH THE MANUFACTURE, SALE, INSTALLATION, DELIVERY,
USE, REPAIR, OR REPLACEMENT OF THE UNIT, OR ANY
AGREEMENT INCORPORATING THIS WARRANTY, AND
CUSTOMER’S SOLE REMEDY FOR THE FOREGOING, WILL BE
LIMITED TO THE AMOUNT PAID TO LUTRON BY CUSTOMERFOR THE UNIT. THE FOREGOING LIMITATIONS, EXCLUSIONSAND DISCLAIMERS WILL APPLY TO THE MAXIMUM EXTENTALLOWED BY APPLICABLE LAW, EVEN IF ANY REMEDY FAILSITS ESSENTIAL PURPOSE.
TO MAKE A WARRANTY CLAIM
To make a warranty claim, promptly notify Lutron within thewarranty period described above by calling the Lutron TechnicalSupport Center at (800) 523-9466. Lutron, in its sole discretion, will
determine what action, if any, is required under this warranty. To
better enable Lutron to address a warranty claim, have the unit’s serial
and model numbers available when making the call. If Lutron, in its
sole discretion, determines that an on-site visit or other remedial action
is necessary, Lutron may send a Lutron Services Co. representative
or coordinate the dispatch of a representative from a Lutron approved
vendor to Customer’s site, and/or coordinate a warranty service callbetween Customer and a Lutron approved vendor.
This warranty gives you specific legal rights, and you may also
have other rights which vary from state to state. Some states do
not allow limitations on how long an implied warranty lasts, so theabove limitation may not apply to you. Some states do not allow
the exclusion or limitation of incidental or consequential damages,
so the above limitation or exclusion may not apply to you.
NEC is a registered trademark of the National Fire Protection
Association, Quincy, Massachusetts.
Advance Mark X is a registered trademark of the AdvanceTransformer Company.
Lutron, , Sivoia, Hi-lume, Eco-10, Tu-Wire, Pico, seeTouch,
EcoSystem, Triathlon, and GRAFIK Eye are registered trademarks andRadio Powr Savr is a trademark of Lutron Electronics Co., Inc.
© 2015 Lutron Electronics Co., Inc.

Internet: www.lutron.com
E-mail: product@lutron.com
WORLD HEADQUARTERS
USA
Lutron Electronics Co., Inc.
7200 Suter Road, Coopersburg, PA 18036-1299
TEL +1.610.282.3800
FAX +1.610.282.1243
Toll-Free 1.888.LUTRON1
Technical Support 1.800.523.9466
North and South America Technical Hotlines
USA, Canada, Caribbean: 1.800.523.9466
Mexico: +1.888.235.2910
Central/South America: +1.610.282.6701
EUROPEAN HEADQUARTERS
United Kingdom
Lutron EA Ltd.
6 Sovereign Close, London, E1W 3JF United Kingdom
TEL +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
FREEPHONE (UK) 0800.282.107
Technical support +44.(0)20.7680.4481
ASIAN HEADQUARTERS
Singapore
Lutron GL Ltd.
15 Hoe Chiang Road, Tower 15, Euro Asia Centre,
Singapore 089316
TEL +65.6220.4666
FAX +65.6220.4333
Asia Technical Hotlines
Northern China: 10.800.712.1536
Southern China: 10.800.120.1536
Hong Kong: 800.901.849
Indonesia: 001.803.011.3994
Japan: +81.3.5575.8411
Macau: 0800.401
Singapore: 800.120.4491
Taiwan: 00.801.137.737
Thailand: 001.800.120.665853
Other countries: +65.6220.4666

Lutron Electronics Co., Inc.
P/N 032222 Rev. E 02/2015