Product Datasheet

HFUG-B2315AN

Pressurized Outside to In / Dead-end Filtration Ultrafiltration(UF) Membrane Module
The HFUG-B2315AN module is Toray's latest UF innovation that features hollow fibers
with a smaller diameter but with improved membrane durability and performance.
The result is an increased surface area per module for more production output.
Membrane Characteristics

Unit

Membrane Material

Value

PVDF (Polyvinylidene fluoride)

Nominal Pore Size

µm

0.01

Outer Membrane Surface Aream² (ft²)

75 (807)

Operating Parameters

Unit

ValueMaximum Feed water / Filtrate Flow

m³/h (gpm)

12.5 (55)

Maximum Backwash Flow

m³/h (gpm)

13.8 (61)Maximum Air Flow

Nm³/h (scfm)

6.7 (3.9)

Maximum Inlet PressurekPa (psi)

300 (43.5)

Maximum Backwash PressurekPa (psi)

300 (43.5)

Normal Operating Transmembrane PressurekPa (psi)

0–200 (0–29)

Operating Temperature Range°C (°F)

1–40 (34–104)

pH Range

During Filtration

1–10

During Cleaning

0–12*Please contact Toray for operating manual and preliminary design, as capacity per module ishighly dependent on feed water quality.

Product Certifications & Compliances(Please contact Toray for details on the certified modules)• NSF/ANSI/CAN 61 for drinking water applications• NSF/ANSI 419 to comply with the U.S. EPA's Long Term 2 Enhanced Surface Water
Treatment Rule (LT2ESWTR), which allows membrane manufacturers to prove
Cryptosporidium reduction• Association of Membrane Separation Technology of Japan

Applications
Drinking water, Industrial process water, Pretreatment for seawater RO desalination,
Tertiary wastewater
1 of 201-MB2-06-240827

Product Datasheet

HFUG-B2315AN

Pressurized Outside to In / Dead-end Filtration Ultrafiltration(UF) Membrane ModuleDimensions and Weight

Unit

Value

Diametermm (in)178 (7.01)

Length *1mm (ft)2,332 (7.651)

Full of Water

kg (lbs)

65 (143)

After Draining

kg (lbs)

35 (77)

Connections *2(2) Air Out(3) Feed Drain / Air In

Value

Housing type joint, 2 inches (U.S.)
Screw, 2.3 inches (original)
Housing type joint, 2 inches (U.S.)

Material Composition *3

CasinguPVC

Cap & Sockets

uPVC

Potting

Epoxy resin

O-ring

EPDM

2,332 (7.65’)(1) Filtrate / Backwash(B) AIR OUT

ø178 (7.0”)

Weight(A) FILTRATEBACK WASH

Please contact Toray for more detailed drawing and dimensions.
*1 This model has 3 connection option (TYPE A/B/C).
The length above is for TYPE A. In case of TYPE B, 2,372mm (7.782ft) In case of TYPE C, 2,336mm (7.677ft).
*2 The connections above is for TYPE A. TYPE B and C have different connection methods,
so the value is different from TYPE A.
*3 The Material Composition above is for TYPE A.
If you need TYPE B or C detail information, please contact Toray.

(C) FEEDDRAIN/AIR IN

Toray accepts no responsibility for results obtained by the application of this information or the safety or suitabilityof Toray's products, either alone or in combination with other products. Users are advised to make their own tests todetermine the safety and suitability of each product combination for their own purposes.
All data may change without prior notice, due to technical modifications or production changes. Please be sure toinquire about the latest product specifications.

Headquarters
Japan +81 3 3245 4542
Asia Pacific
China (TBMC) +86 10 8048 5216
Singapore (TAS) +65 6226 0525
Korea (TAK) +82 2 3279 7365
Americas (TMUS)
USA +1 (858) 218 2360

Europe & Sub-Saharan Africa(TMEU)
Switzerland +41 61 415 8710
Middle East (TMME)
Saudi Arabia +966 13 568 0091
U.A.E. +971 4 392 8811
©2024 Toray Industries, Inc.

LinkedInYouTubeFor more info, please visit

water.toray

2 of 201-MB2-06-240827