Español

Please Read
DeutschIEC PELV/NEC® Class 2
30 mA
24 V

EnglishQS Wallstations
Installation Guide
Contents

Français

Overview  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  . 2Power Group Wiring Example  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  . 3Wiring/Installation .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  . 4Mounting  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  . 7Troubleshooting  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  .  . 8

中文Português
日本語®

Wallstation circuits are classified as IEC PELV/NEC® Class 2 circuits. As Class 2
circuits, they comply with the requirements of NFPA® 70, National Electrical Code®
(NEC®). As PELV circuits, they comply with the requirements of IEC 60364-4-41,
VDE 0100 Part 410, BS7671:1992, and other equivalent standards. When installing
and wiring to these wallstations, follow all applicable national and/or local wiring
regulations. External circuits connected to input, output, and other communication
terminals of wallstations must be supplied from a listed Class 2 source or comply
with the requirements for PELV circuits, as applicable in your country.

Italiano

For Programming, see the QS Wallstation Programming
Guide (P/N 0301639) at www.lutron.com/qs

Overview

QS Wallstation Models

Installation Instructions

Power Group Wiring Example• QS wallstations can be programmed to control
lights, shades, or lights and shades.
• Unprogrammed (out-of-box) QS wallstations,Sivoia® QS shades, GRAFIK Eye® QS control
units, and Energi Savr NodeTM units will all work
together until they are programmed otherwise.
• Contact closure inputs allow operation withoccupancy/vacancy sensors, partitioning, andmore.

seeTouch®
seeTouch®
International Keypads
Keypads
QSWE-2B
QSWS2-1B
QSWE-3B
QSWS2-2B
QSWE-4B
QSWS2-3B
QSWE-5BRL
QSWS2-5B
QSWE-5BRLIRQSWS2-7B
QSWE-6BRL
QSWS2-2BRL
QSWE-7BRL
QSWS2-3BRL
QSWE-8BRL
QSWS2-5BRL
QSWE-8BRLIRQSWS2-2BRLIRQSWE-10BRL
QSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BD
ArchitraveTM
Signature SeriesTM
Keypads
Keypads
QSWA-KP5-DN
QSWAS-1B
QSWA-KP5-DW
QSWAS-2B
QSWA-KP7-DN
QSWAS-3B
QSWA-KP7-DW
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD
Notes• Read all instructions carefully before starting
installation.
• Lutron recommends that wallstations be installed
by a qualified electrician.
• Use only a cloth with warm water and mild soap toclean faceplates (no chemical cleaners).

QS Link Limits• The QS wired communication link is limited to
100 devices and 100 zones. Each QS wallstation
counts as 1 device and 0 zones.
• QS wallstations use 1 power draw unit (PDU) on
the QS link. Refer to the QS Link Power Draw
Units specification submittal (Lutron P/N 369405)
and the diagram on the opposite page for more
information concerning Power Draw Units.

•
•
•
•
•
•
•
•

Compatible Components
The following devices are compatible with the QS
link. For more information on each, refer towww.lutron.com/qs
GRAFIK Eye® QS control units
QS wallstations
Sivoia® QS shades
QS Interfaces (contact closure, Ethernet/RS232)
Quantum® system
Energi Savr NodeTM units
QS Sensor Module
QS Keyswitch

On the QS link, there are devices that supply power and devices that consume power. Each device has a
specific number of Power Draw Units (PDUs) it either supplies or consumes. A Power Group consists of one
device that supplies power and one or more devices that consume power; each Power Group may have
only one power-supplying device. Refer to the QS Link Power Draw Units specification submittal(Lutron P/N 369405) for more information concerning PDUs.
Within Power Groups on the QS link, connect all 4 terminals (1, 2, 3, and 4), shown by the letter A in the
diagram. Between devices on the QS link that supply power, connect only terminals 1, 3, and 4 (NOT
terminal 2), shown by the letter B on the diagram.
Wiring can be T-tapped or daisy-chained.

A

Power Group 1

LUTRONGRAFIK Eye® QScontrol unit
Supplies PDUs

B

(Do not connect
Terminal 2: 24 V )Wallstations
Consume PDUs

B
LUTRON

LUTRON(Do not connect
Terminal 2: 24 V

Connect only 3
terminals between
power groups:
1: Common
3 and 4: Data

B

Energi Savr NodeTM
unit
Supplies PDUs)

Power Group 3

Do not connect
Terminal 2: 24 V

A

LUTRONQS Sensor Module with Occupancy Sensor
Consume PDUs

B
(Do not connect
Terminal 2: 24 V )Occupant Copy

LUTRON

Connect all 4
terminals within apower group:
1: Common
2: 24 V
3 and 4: Data

Power Group 2

A

QS Power Supply
Supplies PDUs

2

A

LUTRON

Control Interfaces
Consume PDUs

Occupant Copy

Quantum® Panel
Supplies PDUs
3

Installation Instructions

LUTRON

LUTRON(2) 12 AWG(4.0 mm2)

LUTRON

LUTRON

LUTRON

LUTRONPower (terminals
1 and 2)2
1 pair 1.0 mm (18 AWG)

153 to 610 m(500 to 2000 ft)

Power (terminals
1 and 2)2
1 pair 4.0 mm (12 AWG)
Data (terminals 3 and 4)
2
1 twisted, shielded pair 0.5 mm (22 AWG)

Installation Instructions

4

:

Drain

Signature SeriesTM, ArchitraveTM

LUTRON

LUTRONIEC PELV/NEC® Class 2 control wiring(2) 18 AWG (1.0 mm2)
1: Common
2: 24 V

Lutron Cable P/N

Data (terminals 3 and 4)
2
1 twisted, shielded pair 0.5 mm (22 AWG)

A

Wire Gauge

Data
link

A

B

Wire Strip length

B

C

LUTRONC

seeTouch® International
IEC PELV/
NEC® Class 2
control wiring

IEC PELV/NEC® Class 2 control wiring(2) 18 AWG (1.0 mm2)
1: Common
2: 24 V

LUTRON

LUTRON

Wire Sizes (check compatibility in your area)

Less than 153 m (500 ft)

1(2) 12 AWG(4.0 mm2)

4 in (10 mm)
QS Link Wiring Length2

LUTRON

LUTRON1

IEC PELV/NEC®
Class 2 control
wiring3

LUTRON

2. Mount Wallbox. Ensure corerct size. See“Mounting” for details.
3. Prepare Wallstations. Remove the faceplate andset aside.
4. Prepare wires. Strip insulation from wires so that
4 in (10 mm) of bare wire is exposed.

2

4

T-Tap
LUTRON

3

LUTRON

LUTRON

LUTRON

4

AC N
AC N
099 942 971 099 942 971

LUTRON

LUTRON

Data link
Drain:

LUTRON

LUTRON

500 to 2000 ft/153 to 610 m

1

LUTRON

LUTRON

2

Daisy chain

LUTRON

LUTRON

seeTouch®

3

LUTRON<500 ft/153 m

4

LUTRON

Connect the appropriate size wires to terminals 1
and 2 for power, according to your link length (seetable opposite).

seeTouch®, seeTouch® International
Data link: (1) twisted, shielded pair
22 AWG (0.5 mm2)
3: MUX
4: MUX
Drain

Allowable Wiring Configurations

OFF OFF OFF

ON
ON

1. Turn Power OFF. Turnpower OFF at circuit
breaker/MCB (or removefuse).

ON

Warning! Shock hazard. May result
in serious injury or death. Always turnOFF the circuit breaker/MCB or remove
the main fuse from the power line before
doing any work.

Wiring the QS Link
Connect two 22 AWG (0.5 mm2) ­shielded, twisted
pair wires to terminals 3 and 4 of the wallstation’scontrol link connector. Shielding (drain) of thetwisted pair wires must be connected together asshown, but do not connect the shielding to earth/ground or the wallstation and do not allow it tocontact the grounded wallbox.

30 mA 30 mA• Control link wiring must not be run in the sameraceway as line voltage.
• Refer to the system installation guide and Lutron job • The drain/shield wire must be maintained throughout
drawings for power cable and data cable (control
the control link. Do not connect the shield to earth/link) wiring restrictions and limitations.
ground or allow contact with the grounded wallbox.
• Connect the wallstation to the control link inside the • Do not connect high-voltage power to lowwallstation’s wallbox or in a junction box (provided
voltage ter­mi­nals. Improper wiring can result inby others).
personal injury or damage to the control or to other• Use the wire connector required by local code.
equipment.

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

Wiring/Installation

1

GRX-CBL-346S (non-plenum)
GRX-PCBL-346S (plenum)(2) 12 AWG(4.0 mm2)(2) 12 AWG(4.0 mm2)1

3

3Data link: (1) twisted, shielded pair
22 AWG (0.5 mm2)
3: MUX
4: MUX

Occupant Copy

Occupant Copy

IEC PELV/NEC® Class 2
control wiring
Data link

2

2
4

4

GRX-CBL-46L (non-plenum)
GRX-PCBL-46L (plenum)

Signature SeriesTM, ArchitraveTM

Drain

Drain
Data link: (1) twisted, shielded pair
22 AWG (0.5 mm2)
3: MUX
4: MUX
5

IEC PELV/NEC® Class 2 control wiring(2) 18 AWG (1.0 mm2)
1: Common
2: 24 VInstallation Instructions

seeTouch®

:

Mounting
Carefully mount and align the wallstation asshown. Screw top and bottom screw into thecontrol and wallbox. Replace adapter (for insert
versions; screw to control), button assembly, andfaceplate in the order shown.

Signature SeriesTM
Adapterscrews Mounting
screwsseeTouch®
Mounting screws

AdapterscrewsWallboxControl

Buttons
Adapter

WallboxseeTouch® International

Control(3) 18 AWG(1.0 mm2)

A

1
2
3

B

CommonInput 2
Input 1

ArchitraveTM
Mounting screws

FaceplateC

CommonInput 2
Input 1

Faceplate

Buttons
Adapter4

AC N
099 942 971(3) 18 AWG(1.0 mm2)

Note: If a wallstation has devices connected
to it through contact closure inputs,
CCI1 “presses” the top button and CCI2
“presses” the bottom button. To change
this behavior, refer to Application Note 428(seeTouch® Advanced Programming Mode)at www.lutron.com.
Exception: On a 2-button wallstation
configured for partitioning, panic, orsequencing functionality, CCI1 closure
action follows the top button and opening
action follows the bottom button.

CO O P E R S BURG , P A 18036 US A

30 mA

Wiring the Contact Closure Input (CCI)
The contact closure inputs must be dry contact
closure, solid state, open collector, or active-low(NPN)/active-high (PNP) output.
• Open collector NPN or active-low on-state voltage
must be less than 2 V and sink 3.0 mA.
• Open collector PNP or active-high on-state voltage
must be greater than 12 V and source 3.0 mA.
• The outputs must stay in the closed or open states
for at least 60 msec in order to be recognized by
the wallstation.
If there is any question as to whether the third-party
device generating these outputs is compatible withthese specifications, contact the manufacturer.

seeTouch® International
Mounting screws
Adapter screws
Wallbox
WallboxControl
Faceplate

Control
AdapterArchitraveTM

Signature SeriesTM(3) 18 AWG(1.0 mm2)A
B
C

Faceplate(3) 18 AWG(1.0 mm2)

Input 1
Input 2
CommonA
B
C

Input 1
Input 2
CommonWallstation Type

Wallbox Size(high x wide x deep)

Lutron P/N

seeTouch®

3.7 x 2.2 x 2.75 in
95 x 55 x 70 mm
3 x 3 x 1.4 in
75 x 75 x 35 mm
4.4 x 1.5 x 2.8 in
113 x 39.x 71 mm
4.4 x 1.25 x 2.75 in
112 x 32 x 70 mm

241519seeTouch®
International
Signature SeriesTM
ArchitraveTM
Installation Instructions

Buttons6

Occupant Copy

Occupant Copy

Power Up
Turn ON control breaker, or replace main fuse.
Installation is Complete
For Programming functions, see the
QS Wallstation Programming Guide atwww.lutron.com/qs.

241683
WBOX-SA1-Q1
2413997

Installation Instructions

Troubleshooting: LED Functionality

Troubleshooting: Shade Functions

LED Behavior

Symptom

Possible Causes

RemedyEDU (electronic drive unit of theshade) will not move

EDU is not powered

Check EDU power

Shade fabric is caught on something

Check and unbind shade fabric

EDU is not assigned to a keypad

Assign the EDU to a keypad

Presets have been set incorrectly

Try using raise/lower buttons on keypad

Limits have been set incorrectly

Set limits correctly

Shade fabric is caught on something

Check and unbind shade fabric

Shade moves in the opposite
direction when raise/lower buttons
are pushed

Open and close limits have been reversed

Set limits correctly

Keypad LEDs are off and keypad will
not control any shade

No power is going to keypad

Check and wire power to keypad

Keypad LEDs are on but keypad will
not control any shade

All presets are set to the same height

Try using raise/lower buttons on keypad

Meaning and Remedy

All Keypad Types“Reverse Waterfall”
LEDs light beginning at the bottom, continuing to light until all areon; then LEDs go off beginning at the bottom, continuing until allare off. Cycle then repeats.

Unable to communicate on QS link, or alone on QS link. Check link wiring.

No LED feedback at all, even when a button is pushed.

No power to wallstation. Check power wiring.
Another device on QS link is in programming or assignment mode. Take
that device out of programming mode, or put this keypad into programming
mode and then exit programming mode, which turns off programming modeon all devices.

All LEDs are flashing rapidly.

Wallstation is in advanced programming mode. Press and hold the top andbottom buttons for 3 seconds to exit advanced programming mode.

EDU (electronic drive unit of theshade) does not fully open or fully
close

Shade Keypads
Top and bottom LEDs are flashing together.

Keypad is in assignment mode. Press and hold the top and bottom buttons
for 3 seconds to exit assignment mode.

All LEDs flash 3 times, pause, then repeat.

Keypad is in assignment or limit set mode and cannot find or communicate
with any shades assigned to the QS link. Check the shade wiring.
Wait 60 seconds, and the keypad will automatically return to normal mode(without any user intervention). Or, press and hold the top and bottom
buttons for 3 seconds to immediately exit the mode.

Top and bottom LEDs light in an alternating pattern (top LED
lights, then goes off, then bottom LED lights, then goes off; cycle
repeats).

Keypad is in limit set mode, or another device on the link is in limit set
mode. Press and hold the top and raise buttons for 3 seconds to exit limit
set mode.

Top and bottom LEDs blink slowly, and one other LED blinks
rapidly.

Keypad is in preset adjust mode. Press and hold the top and bottom buttons
to exit preset adjust mode.

Keypad does not operate all the
shades it is assigned to

Other Keypads
A single LED is flashing.

“Forward Waterfall”
LEDs light and go off in sequence from top to bottom.

Installation Instructions

Keypad is configured for either zone toggle, partitioning, or shade toggle andis in programming mode. Press and hold the top and bottom buttons to exit
programming mode.

Shades in a room move on their own

Communications link is not wired to the EDU

Check and wire the EDU link

EDU has been unassigned from keypad

Reassign the EDU to the keypad

Open and close limits are the same

Set limits correctly

EDU has been unassigned from keypad

Reassign the EDU to the keypad

All presets are set to the same height

Try using raise/lower buttons on keypad

EDU is not wired correctly

Check and rewire EDU

Keypad is not wired correctly

Check and rewire keypad

EDUs are assigned to a keypad in another room

Reassign the EDU to the correct keypad

Keypad is configured for scene, panic, sequence, fine tune, or scene/zone
lockout, and is in programming mode. Press and hold the top and bottom
buttons to exit programming mode.

8

Occupant Copy

Occupant Copy

9

Installation Instructions

Troubleshooting
Symptom

Possible Causes

No communication with GRAFIK Eye® control unit or Energi Savr
NodeTM unit.

Miswire or loose connection at the control link data lines 3 and 4.

Wallstation buttons do not work; LEDs do not track; wallstation buttons
do not function as intended.

Wallstation is miswired.

Wallstation has not been programmed or has been programmed
incorrectly.

Wallstation is not powered.
Wallstation is not programmed to the correct device.
Wallstation has not been programmed or has been programmed
incorrectly.

LEDs do not light.

Miswire or loose connection at wallstation(s) or processor on the control
link common and power connections 1 and 2.
Wallstation has been programmed incorrectly.

Contact closure inputs or sensor input do not produce the desired resultin the system.

Miswire or loose connection at wallstation sensor/CCI connector.
Wallstation has not been programmed or has been programmed
incorrectly.

Internet: www.lutron.com
E-mail: product@lutron.com
World Headquarters
USA
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TEL +1.610.282.3800
FAX +1.610.282.1243
Toll-Free 1.888.LUTRON1
Technical Support 1.800.523.9466
North and South America
Technical Hotlines
USA, Canada, Caribbean: 1.800.523.9466
Mexico: +1.888.235.2910
Central/South America: +1.610.282.6701

European Headquarters
United Kingdom
Lutron EA Ltd.
6 Sovereign Close
LondonE1W 3JF United Kingdom
TEL +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
FREEPHONE (UK) 0800.282.107
Technical support +44.(0)20.7680.4481

Warranty: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code, NEC, and NFPA are registered trademarks of the National Fire Protection Association, Inc.,
Quincy, Massachusetts.
Lutron, , Sivoia, seeTouch, Quantum, and GRAFIK Eye are registered trademarks, and Energi Savr Node,
Signature Series and Architrave are trademarks of Lutron Electron­ics Co., Inc.
© 2012 Lutron Electronics Co., Inc.

ASIAN Headquarters
Singapore
Lutron GL Ltd.
15 Hoe Chiang Road
#07-03 Euro Asia Centre
Singapore 089316
TEL +65.6220.4666
FAX +65.6220.4333
Asia Technical Hotlines
Northern China: 10.800.712.1536
Southern China: 10.800.120.1536
Hong Kong: 800.901.849
Indonesia: 001.803.011.3994
Japan: +81.3.5575.8411
Macau: 0800.401
Singapore: 800.120.4491
Taiwan: 00.801.137.737
Thailand: 001.800.120.665853
Other countries: +65.6220.4666®

®

Lutron Electronics Co., Inc.
P/N 0301604 Rev. B 10/2012

Teclado

Lea con atención

IEC PELV/NEC® Class 2
24 V
30 mA

Contenido

Descripción general.......................................................................... 2
Ejemplo de cableado del grupo de alimentación................................ 3
Cableado/Instalación......................................................................... 4
Montaje............................................................................................ 7
Resolución de problemas.................................................................. 8

Para la programación, consulte la Guía de programaciónde botonera de pared QS (P/N 0301639)
en www.lutron.com/qs®

Los circuitos de las botoneras de pared se clasifican como IEC PELV/NEC®
Class 2. Como circuitos de Class 2, cumplen con los requisitos de NFPA® 70,
National Electrical Code® (NEC®). Como circuitos PELV, cumplen con los requisitos
de IEC 60364-4-41, VDE 0100 Parte 410, BS7671:1992 y otras normas
equivalentes. Al instalar y conectar el cableado a estas botoneras de pared,siga todas las normas de cableado nacionales y/o locales aplicables. Los circuitos
externos conectados a los terminales de entrada, salida y otros terminales
de comunicación de las botoneras de pared deben provenir de una fuente listado
como Class 2 o cumplir los requisitos de los circuitos PELV, según corresponda
en su país.

Español

Botoneras de pared QS
Guía de instalación•
Botoneras de pared
seeTouch® Internacional
QSWE-2B•
QSWE-3B

Las botoneras de pared QS se pueden programarpara controlar luces, cortinas, o luces
y cortinas.
Las botoneras de pared QS, cortinas Sivoia® QS,
unidades de control GRAFIK Eye® y unidades
Energi Savr NodeTM no programadas (como vienende fábrica) funcionarán en conjunto, a menos que
se los programe de otra manera.
• Las entradas de contacto seco permitirán
el funcionamiento con sensores de presencia/
vacancia, partición y mucho más.

QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

Límites del enlace QS• El enlace de comunicación cableado QS
puede tener hasta 100 dispositivos y 100 zonas.
Cada botonera de pared QS cuentacomo 1 dispositivo y 0 zonas.
• Las botoneras de pared QS utilizan 1 unidad
de consumo de energía (PDU) en el enlace QS.
Para obtener más información sobre las unidadesde consumo de energía, consulte el documentode especificaciones “Unidades de consumo deenergía del enlace QS” (Lutron P/N 369405) y eldiagrama de la página opuesta.

Botoneras de pared
ArchitraveTM
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•
•
•
•
•

Notas
• Lea detenidamente todas las instrucciones antes
de comenzar con la instalación.
• Lutron recomienda que las botoneras de paredsean instaladas por un electricista competente.
• Utilice únicamente un paño con agua tibia
y jabón suave para limpiar las placas frontales(no utilice limpiadores químicos).
Instrucciones de instalación

Ejemplo de cableado del grupo de alimentación

Descripción general

Modelos de botoneras de pared QS
Botoneras de pared
seeTouch®
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BD
Botoneras de pared
Signature SeriesTM
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

Componentes compatibles
Los siguientes dispositivos son compatibles
con el enlace QS. Para obtener más información
sobre cada dispositivo, visite www.lutron.com/qs
Unidades de control GRAFIK Eye® QS
Botoneras de pared QS
Cortinas Sivoia® QS
Interfases QS (contacto seco, Ethernet/RS232)
Sistema Quantum®
Unidades Energi Savr NodeTM
Módulo de sensor QS
Interruptor QS

En el enlace QS, hay dispositivos que proporcionan alimentación y otros que la consumen. Cada dispositivo
tiene un número específico de las unidades de consumo de energía (PDU) que suministra o consume.
Un grupo de alimentación consta de un dispositivo que alimenta y uno o más dispositivos que consumen
energía; cada grupo de alimentación solo puede tener un dispositivo de alimentación. Consulte el documentode especificaciones “Unidades de consumo de energía en el enlace QS” (Lutron P/N 369405) para obtener
más información sobre las unidades de consumo de energía (PDU).
En los grupos de alimentación del enlace QS, conecte los cuatro terminales (1, 2, 3 y 4) según se muestra
en la letra A del diagrama. Entre los dispositivos del enlace QS que suministran alimentación, conecte solo
los terminales 1, 3 y 4 (NO conecte el terminal 2) según se indica en la letra B del diagrama.
El cableado puede conectarse en cadena o en derivación en T.

A
LUTRON

Unidad de control
GRAFIK Eye® QS
Suministra PDU

Copia para el ocupante

A

LUTRON

B

Interfases de control
Consume PDU(No conecte
el terminal 2: 24 V )Botoneras de pared
Consume PDU

LUTRON

LUTRON

LUTRON

B

B

UnidadEnergi Savr NodeTM
Suministra PDU(No conecte
el terminal 2: 24 V)

Grupo de alimentación 3A

Fuente dealimentación QS
Suministra PDU

Copia para el ocupante

Conecte los
4 terminales dentro
de un grupo
de alimentación:
1: Común
2: 24 V3 y 4: Datos

Grupo de alimentación 2A

Conecte solo
3 terminales
entre los gruposde alimentación:
1: Común
3 y 4: Datos
No conecte
el terminal
2: 24 V

LUTRON

Módulo de sensor QS con sensor de presencia
Consume PDU

B(No conecte
el terminal 2: 24 V )2Grupo de alimentación 1

Panel Quantum®
Suministra PDU
3

Instrucciones de instalación

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

Descarga
434(2) 4,0 mm2

LUTRON

LUTRON

LUTRON

1

Cableado de control
IEC PELV/
NEC® Class 2

2(12 AWG)

LUTRON

2

3
1

AC N
AC N
099 942 971 099 942 971

Derivación
en T

C
B

LUTRON

LUTRON

LUTRON

LUTRONLongitud del cableadodel enlace QS

Calibre del cable

Menos de 153 m(500 pies)

Alimentación (terminales
1 y 2)
2
1 par de 1,0 mm (18 AWG)

Descarga
Signature SeriesTM, ArchitraveTM

Cable Lutron P/N
1

Datos (terminales 3 y 4)2
1 par trenzado, blindado de 0,5 mm (22 AWG)
Alimentación (terminales
1 y 2)
2
1 par de 4,0 mm (12 AWG)
Datos (terminales 3 y 4)2
1 par trenzado, blindado de 0,5 mm (22 AWG)

4

Enlace de datos

A

LUTRON

LUTRONA

B

Cableado de control IEC PELV/
NEC® Class 2(2) 1,0 mm2 (18 AWG)
1: Común
2: 24 V

LUTRON

LUTRONLongitud de la sección pelada del cable

seeTouch® Internacional
Cableado de control
IEC PELV/NEC®
Class 2(2) 4,0 mm2(12 AWG)

1

LUTRON

LUTRON

Tamaños de cable (verifique la compatibilidad en su área)Instrucciones de instalación

Enlace dedatos

Enlace de datos: (1) par trenzado y blindado
0,5 mm2 (22 AWG)
3: MUX
Descarga
4: MUX

LUTRON

10 mm (4 pulg)

153 a 610 m(500 a 2 000 pies)

seeTouch®

seeTouch®, seeTouch® Internacional:

En serie

LUTRON

LUTRON:

LUTRON

LUTRON< 153 m/500 pies

153 a 610 m/500 a 2 000 pies

30 mA 30 mA

LUTRON

LUTRONOFF OFF OFF

ON
ON
ON

Configuraciones de cableado permitidas

C¡Advertencia! Riesgo de descarga
eléctrica. Puede ocasionar lesiones
graves o la muerte. APAGUE siempre
el cortacircuitos/microcortacircuitos o retire
el fusible principal de la línea de alimentación antes
de realizar cualquier trabajo.
1. Desconecte
la alimentación.
Desconecte la alimentación
en el cortacircuitos/
microcortacircuitos(o retire el fusible).
2. Monte la caja de empotrar. Asegurar el tamaño
correcto. Vea “Montaje” para más detalles.
3. Prepare las botoneras de pared. Retire la placa
frontal y apártela.
4. Prepare los cables. Pele el aislamiento de loscables de modo que queden expuestos 10 mm(4 pulg) del cable.

•

Conecte los cables del tamaño apropiado a lasterminales 1 y 2 para la alimentación, de acuerdo
con la longitud del enlace (consulte la tabla en lapágina opuesta).

2

•

•

Cableado del enlace QS
Conecte dos cables de par trenzado y blindado de0,5 mm2 (22 AWG) a los terminales 3 y 4 del conector
de enlace del control de la botonera de pared. Los
blindajes (la descarga) de los cables de par trenzado
se deben conectar juntos como se muestra en lailustración, pero no conecte el blindaje a tierra/masa ni
a la botonera de pared, ni permita que haga contacto
con la caja de empotrar conectada a tierra.

3•

Consulte la guía de instalación del sistema y los diagramas
de trabajo de Lutron para conocer las restricciones
y limitaciones del cable de alimentación y el cableadode datos (enlace del control).
Conecte la botonera de pared al enlace del control
dentro de la caja de empotrar de la botonera de paredo en una caja de conexiones (de otro proveedor).
Utilice el conector de cable exigido por los códigos locales.

El cableado del enlace del control no debe correr
en el mismo conducto que la tensión de línea.
El cable de descarga/blindaje debe ser continuo a lo largodel enlace de control. No conecte el blindaje a tierra/masa
ni permita que entre en contacto con la caja de empotrar
conectada a tierra.
No conecte la alimentación de alto voltaje a terminales
de bajo voltaje. Un cableado incorrecto puede causar
lesiones personales o daños al control o a otros equipos.

4

•

•

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

Cableado/Instalación

Cableado de control IEC PELV/
NEC® Class 2(2) 1,0 mm2 (18 AWG)
1: Común
2: 24 V

Signature SeriesTM, ArchitraveTM(2) 4,0 mm2(12 AWG)(2) 4,0 mm2(12 AWG)

Enlace de datos

2

1

GRX-CBL-346S (sin plenum)
GRX-PCBL-346S (con plenum)

3

3

GRX-CBL-46L (sin plenum)
GRX-PCBL-46L (con plenum)

Enlace de datos: (1) par trenzado
y blindado 0,5 mm2 (22 AWG)
3: MUX
4: MUX
Copia para el ocupante24

4

Copia para el ocupante

Cableado de control IEC PELV/
NEC® Class 2

Descarga

5

Enlace de datos: (1) par trenzado
y blindado 0,5 mm2 (22 AWG)
3: MUX
4: MUX

Descarga

Cableado de control IEC PELV/
NEC® Class 2 (2) 1,0 mm2 (18 AWG)
1: Común
2: 24 V
Instrucciones de instalación

seeTouch®

MontajeMonte y alinee cuidadosamente la botonera depared como se muestra. Ajuste los tornillos superior
e inferior en el control y la caja de empotrar. Vuelva
a colocar el adaptador (para versiones de inserción;
atornille al control) el montaje de botones y la placa
frontal en el orden que se muestra.

Control

Botones
Adaptador:

Caja deempotrar

Placa frontal
Control

Botones1

C

Tornillos de montaje

4

A

3

B

2

seeTouch® Internacional

Tornillos deladaptador(3) 1,0 mm2(18 AWG)
A
B
C

Entrada 1
Entrada 2
Común

Botones
Placa frontal

Tamaño de la Caja de
Empotrar(altura x ancho x profundidad)

seeTouch®

95 x 55 x 70 mm
3,7 x 2,2 x 2,75 pulg
75 x 75 x 35 mm
3 x 3 x 1,4 pulg
113 x 39.x 71 mm
4,4 x 1,5 x 2,8 pulg
112 x 32 x 70 mm
4,4 x 1,25 x 2,75 pulg

Signature SeriesTM
ArchitraveTM
Copia para el ocupanteControl
Placa frontal

Adaptador

Tipo debotonera depared

seeTouch®
Internacional

6

Caja deempotrar

ControlArchitraveTM(3) 1,0 mm2(18 AWG)
Entrada 1
Entrada 2
Común

Tornillos de montaje

Placa frontal

Común
Entrada 2
Entrada 1

Signature SeriesTM

ArchitraveTM
Adaptador

1,0 mm2(18 AWG)

Caja deempotrar

Instrucciones de instalación

Tornillos del Tornillos
adaptador demontajeTornillos deladaptador

Tornillos de montaje

seeTouch® Internacional

Común
Entrada 2
Entrada 1

A
BC

Signature SeriesTM

seeTouch®

Caja deempotrar

AC N
099 942 971(3) 1,0 mm2(18 AWG)

Nota: Si una botonera de pared tiene dispositivos
conectados a ella a través de entradasde contacto seco, CCI1 “presiona” el botón
superior y CCI2 “presiona” el botón inferior.
Para cambiar este comportamiento,
consulte la Nota de aplicación 428 (Modode programación avanzada de seeTouch® )en www.lutron.com.
Excepción: En una botonera de pared dedos botones configurada para las funciones
de partición, pánico o secuenciación,la acción de cierre CCI1 sigue al botón
superior y la acción de abertura sigue
al botón inferior.

CO O P E R S BURG , P A 18036 US A

30 mA

Cableado de la entrada de contacto seco (CCI)
Las entradas deben ser de cierre por contacto
seco, de estado sólido, de colector abierto,o salida de activo bajo (NPN)/activo alto (PNP).
• El voltaje del colector abierto NPN o bajo en activo
en estado encendido debe ser inferior a 2 V
y con una capacidad de corriente de sumidero
de 3,0 mA.
• El voltaje del colector abierto PNP activo en alto
en estado encendido debe ser mayor a 12 V
y fuente de 3,0 mA.
• Las salidas tienen que permanecer al menos
60 milisegundos en estado cerrado o abiertopara ser reconocidas por la botonera de pared.
Si hay alguna pregunta sobre si el dispositivo
de un tercero que genera estas salidas
es compatible con estas especificaciones,
comuníquese con el fabricante.

Copia para el ocupante

Lutron P/N241519241683
WBOX-SA1-Q1
2413997

Encendido
Conecte el cortacircuitos o vuelva a colocar
el fusible principal.
La instalación está terminada
Para programar las funciones, consulte la Guíade programación de botonera de pared QS en
www.lutron.com/qs.
Instrucciones de instalación

Resolución de problemas: Funciones de los indicadores LED

Resolución de problemas: Funciones de las cortinas

Comportamiento de los indicadores LED

Síntomas

Posibles causas

Solución

La EDU (unidad de drive electrónico
de la cortina) no se mueve

La EDU no está conectada a la alimentación

Verifique la alimentación de la EDU

La tela de la cortina está atrapada en algo

Verifique y destrabe la tela de la cortina

La EDU no está asignada a una botonera

Asigne la EDU a una botonera

Los niveles predefinidos han sido configuradosde forma incorrecta

Intente usar los botones de aumentar/disminuiren la botonera

Los límites están configurados de forma incorrecta

Configure los límites correctamente

La tela de la cortina está atrapada en algo

Verifique y destrabe la tela de la cortina

La cortina se mueve en la dirección
opuesta cuando se presionan
los botones aumentar/disminuir

Los límites de abierta y cerrada están invertidos

Configure los límites correctamente

Los indicadores LED de la botonera
están apagados y la botonera
no controla ninguna cortina

No llega la alimentación a la botonera

Verifique la alimentación del cable a la botonera

Los indicadores LED de la botonera
están encendidos pero la botonera
no controla ninguna cortina

Todos los niveles predefinidos están configuradosa la misma altura

Intente usar los botones de aumentar/disminuiren la botonera

El enlace de comunicaciones no está cableado
a la EDU

Verifique y cablee el enlace de la EDU

La EDU ha sido desasignada desde la botonera

Reasigne la EDU a la botonera

Los límites de abierta y cerrada son los mismos

Configure los límites correctamente

La EDU ha sido desasignada desde la botonera

Reasigne la EDU a la botonera

Todos los niveles predefinidos están configuradosa la misma altura

Intente usar los botones de aumentar/disminuiren la botonera

La EDU no está cableada correctamente

Verifique y vuelva a cablear la EDU

La botonera no está cableada correctamente

Verifique y vuelva a cablear la botoneraLas EDU están asignadas a una botonerade otra habitación

Reasigne la EDU a la botonera correcta

Significado y solución

Todos los tipos de botoneras“Cascada invertida”
Los indicadores LED comienzan a encenderse desde abajo
hasta que todos quedan encendidos; luego se apagan desdeabajo hasta que todos quedan apagados. Luego se repite
el ciclo.

No hay comunicación en el enlace QS o solo en el enlace QS.
Verifique el cableado del enlace.

No hay respuesta de los indicadores LED,ni siquiera al presionar un botón.

No llega energía a la botonera de pared. Verifique el cableado de la alimentación.

Todos los indicadores LED parpadean rápidamente.

Otro dispositivo en el enlace QS está en el modo de programación o asignación.
Quite ese dispositivo del modo de programación o coloque esta botonera
en el modo de programación y luego salga del modo de programación;
esto apagará el modo de programación en todos los dispositivos.
La botonera de pared está en modo de programación avanzada.
Mantenga presionados los botones superior e inferior durante 3 segundospara salir del modo de programación avanzado.

La EDU (unidad de drive electrónico
de la cortina) no se abre ni se cierra
totalmente

Botoneras de cortinas
Los indicadores LED superior e inferior parpadean juntos.

La botonera está en el modo de asignación. Mantenga presionados los botones
superior e inferior durante 3 segundos para salir del modo de asignación.

Todos los indicadores LED parpadean 3 veces,hacen una pausa y luego repiten.

La botonera está en modo de asignación o ajuste de límites y no puede
encontrar ni comunicarse con cortinas asignadas al enlace QS.
Verifique el cableado de las cortinas.
Espere 60 segundos y la botonera volverá al modo normal automáticamente(sin la intervención del usuario). O bien, mantenga presionados los botones
superior e inferior durante 3 segundos para salir del modo de inmediato.

Los indicadores LED superior e inferior se encienden
de manera alternada (el indicador LED superior se enciende,luego se apaga, luego se enciende el indicador LED inferior,luego se apaga; el ciclo se repite).

La botonera está en el modo de ajuste de límites; o bien, otro dispositivo
en elenlace está en el modo de ajuste de límites. Mantenga presionados
los botones superior y aumentar durante 3 segundos para salir del modode ajuste de límites.

Los indicadores LED superior e inferior parpadean lentamente,
y otro indicador LED parpadea rápidamente.

La botonera está en el modo de ajuste de niveles predefinidos.
Mantenga presionados los botones superior e inferior parasalir del modo de ajuste de niveles predefinidos.

El teclado no opera todas las cortinas
a las que está asignado

Otras botoneras
Un solo indicador LED parpadea.
“Cascada frontal”
Los indicadores LED se encienden y se apagan
en una secuencia de arriba hacia abajo.
Instrucciones de instalación

La botonera está configurada para conmutación de zona, partición o conmutaciónde cortinas y está en el modo de programación. Mantenga presionados
los botones superior e inferior para salir del modo de programación.
La botonera está configurada para escena, pánico, secuencia, ajuste finoo bloqueo de escena/zona, y está en modo de programación. Mantengapresionados los botones superior e inferior para salir del modo de programación.
8

Copia para el ocupante

Las cortinas de una habitación
se mueven solas

Copia para el ocupante9

Instrucciones de instalación

Resolución de problemas
Síntomas

Posibles causas

No hay comunicación con la unidad de control GRAFIK Eye®
ni la unidad Energi Savr NodeTM.

Error de cableado o mala conexión en las líneas de datos 3 y 4 del enlace
de control.
No se ha programado la botonera de pared o se programó de manera
incorrecta.

Los botones de la botonera de pared no funcionan, los indicadores
LED no realizan ningún seguimiento; los botones de la botonerade pared no funcionan de la manera prevista.

La botonera de pared está cableada erróneamente.
La botonera de pared no está conectada a la alimentación.
La botonera de pared no está programada con el dispositivo correcto.
No se ha programado la botonera de pared o se programó de manera
incorrecta.

Los indicadores LED no se encienden.

Error de cableado o mala conexión en la(s) botonera(s) o en el procesador
en las conexiones 1 y 2 de la alimentación y el común del enlace de control.
La botonera de pared se programó de forma incorrecta.

Las entradas de contacto seco o del sensor no producen
los resultados deseados en el sistema.

Error de cableado o mala conexión en el conector de CCI/sensor
de la botonera de pared.
No se ha programado la botonera de pared o se programó de manera
incorrecta.

Internet: www.lutron.com
Correo electrónico: product@lutron.com
SEDE CENTRAL MUNDIAL
E.U.A
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TEL +1.610.282.3800
FAX +1.610.282.1243
Número gratuito 1.888.LUTRON1
Soporte Técnico 1.800.523.9466
América del Norte y América del Sur
Líneas de Asistencia Técnica
E.U.A, Canadá y el Caribe: 1.800.523.9466
México: +1.888.235.2910
América Central/América del Sur: +1.610.282.6701

SEDE CENTRAL EROPEA
Reino Unido
Lutron EA Ltd.
6 Sovereign Close
Londres
E1W 3JF Reino Unido
TEL +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
LLAMADA GRATUITA (Reino Unido): 0800.282.107
Soporte Técnico: +44.(0)20.7680.4481

Garantía: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code, NEC y NFPA son marcas comerciales registradas de la National Fire Protection Association,Inc., Quincy, Massachusetts.
Lutron, , Sivoia, seeTouch, Quantum, y GRAFIK Eye son marcas registradas y Energi Savr Node, Architrave, ySignature Series son marcas de Lutron Electronics Co., Inc.
© 2012 Lutron Electronics Co., Inc.

SEDE CENTRAL ASIÁTICA
Singapur
Lutron GL Ltd.
15 Hoe Chiang Road
07-03 Euro Asia Centre
Singapur 089316
TEL +65.6220.4666
FAX +65.6220.4333
Líneas de Asistencia Técnica en Asia
Norte de China: 10.800.712.1536
Sur de China: 10.800.120.1536
Hong Kong: 800.901.849
Indonesia: 001.803.011.3994
Japón: +81.3.5575.8411
Macao: 0800.401
Singapur: 800.120.4491
Taiwán: 00.801.137.737
Tailandia: 001.800.120.665853
Otros países: +65.6220.4666®

®

Lutron Electronics Co., Inc.
P/N 0301604 Rev. B 10/2012

QS Bedienstellen
Installationsanleitung

Bitte lesen

InhaltÜbersicht.......................................................................................... 2
Beispiel zur Gruppierung der Stromversorgungen............................. 3
Anschluss/Installation....................................................................... 4
Montage........................................................................................... 7
Fehlersuche...................................................................................... 8

Zur Programmierung siehe die Programmieranleitung
für QS Bedienstellen (Bestell-Nr. 0301639)
auf www.lutron.com/qs®

Die Kreise, in denen sich Bedienstellen befinden, werden als IEC PELV/NEC® Class
2 eingestuft. Als Kreise der Kategorie 2 genügen sie den Anforderungen NFPA® 70,
National Electrical Code® (NEC®). Als Schutzkleinspannungskreise mit Schutzerdung(PELV) genügen sie den Anforderungen IEC 60364-4-41, VDE 0100 Teil 410,
BS7671:1992 und anderen gleichwertigen Normen und Standards. Während
der Installation und Verdrahtung der Zusatzgeräte befolgen Sie alle im jeweiligen
Land geltenden und/oder örtlichen Verdrahtungsvorschriften. Externe Kreise,
die an Eingang, Ausgang oder andere Schnittstellen der Zusatzgeräte angeschlossen
werden, müssen der Kategorie 2 entsprechen oder allen in Ihrem Land geltenden
Anforderungen an Schutzkleinspannungskreise mit Schutzerdung entsprechen.

DeutschIEC PELV/NEC® Class 2
30 mA
24 V

Übersicht

QS Bedienstellen-Modelle
seeTouch®
Bedienstellen
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BDSignature SeriesTM
Bedienstellen
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

Beleuchtung, Rollos oder von Beleuchtung und
Rollos programmiert werden.
• Unprogrammierte QS Bedienstellen, Sivoia® QS
Rollos, GRAFIK Eye® QS Steuergeräte undEnergi Savr NodeTM Geräte arbeiten alle
zusammen, solange sie nicht anderweitig
programmiert werden.
• Potentialfreie Eingänge ermöglichen Betrieb
mit Präsenzmeldern, Trennwänden u.a.
QS-Bus-Beschränkungen• Der verdrahtete QS-Kommunikationsbus ist auf
100 Geräte und 100 Zonen begrenzt. Jede QS
Bedienstelle zählt als 1 Gerät und 0 Zonen.
• QS Bedienstellen verbrauchen 1
Stromversorgungseinheit am QS-Bus. Weitere
Informationen zu Stromversorgungseinheiten
finden Sie im Datenblatt zu QS-BusStromversorgungseinheiten(Lutron-Bestell-Nr. 369405) und auf der Darstellung
auf der gegenüberliegenden Seite.

ArchitraveTM
Bedienstellen
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•

Hinweise••••• Lesen Sie alle Anweisungen sorgfältig durch,

bevor Sie mit der Installation beginnen.
• Lutron empfiehlt, dass die Bedienstellen
nur von Fachpersonal installiert werden.
• Nehmen Sie zur Reinigung der Abdeckungenausschließlich einen Lappen mit warmem
Wasser und mit Seifenlauge(keine chemischen Reinigungsmittel).
Installationsanweisungen

Beispiel zur Gruppierung der Stromversorgungen• QS Bedienstellen können zur Steuerung von

seeTouch®
Internationale
Bedienstellen
QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

Kompatible Komponenten
Die folgenden Geräte sind mit dem QS-Bus
kompatibel. Weitere Informationen finden
Sie auf www.lutron.com/qs
GRAFIK Eye® QS Steuergeräte
QS Bedienstellen
Sivoia® QS Rollos
QS-Schnittstellen (potentialfreie Kontakte,
Ethernet/RS232)
Quantum® System
Energi Savr NodeTM Gerät
QS-Sensormodul
QS-Schlüsselschalter

Am QS-Bus befinden sich Geräte, die Strom liefern, und Geräte, die Strom verbrauchen. Jedes Gerät hateine bestimmte Anzahl von Stromeinheiten, die es entweder liefert oder verbraucht. Eine Gruppe besteht
aus einem Gerät, das Strom liefert, und einem oder mehreren Geräten, die Strom verbrauchen. Jede
Leistungsgruppe darf nur ein stromlieferndes Gerät haben. Weitere Informationen zu Stromversorgungseinheiten
finden Sie im Datenblatt zu QS-Bus-Stromversorgungseinheiten (Lutron-Bestell-Nr. 369405).
Verbinden Sie innerhalb der Gruppen am QS-Bus alle 4 Klemmen (1, 2, 3 und 4), die in der Zeichnung mit
dem Buchstaben A gekennzeichnet sind. Verbinden Sie zwischen stromliefernden Geräten am QS-Bus nur
die Klemmen 1, 3 und 4 (NICHT Klemme 2), die in der Zeichnung mit dem Buchstaben B gekennzeichnet sind.
Der Anschluss kann sternförmig oder in Reihe vorgenommen werden.

A
LUTRONGRAFIK Eye® QS
Steuergerät
Liefert Stromversorgungseinheiten B(Klemme 2 nichtanschließen: 24 V )Benutzerexemplar

A

LUTRON

Steuer-Schnittstellen
Verbrauchen
Stromversorgungseinheiten

Bedienstellen
Verbrauchen
Stromversorgungseinheiten

B
LUTRON

Energi Savr NodeTM
B
Gerät
Liefert Stromversorgungs- (Klemme 2 nichtanschließen: 24 V
einheiten

LUTRON

LUTRON

Gruppe 3

Benutzerexemplar

Nur 3 Klemmen
zwischen Gruppen
anschließen:
1: Masse
3 und 4: Daten)

A

QS-Stromversorgungsgerät
Liefert Stromversorgungseinheiten

Alle 4 Klemmen
innerhalb einer
Gruppeanschließen:
1: Masse
2: 24 V
3 und 4: Daten

Gruppe 2A

Klemme 2 nichtanschließen:
24 V

LUTRON

B(Klemme 2 nichtanschließen: 24 V )2Gruppe 1

QS-Sensormodul mit Präsenzmelder
Verbrauchen Stromversorgungseinheiten
Quantum® Schaltschrank liefert
Stromversorgungseinheiten
3

InstallationsanweisungenLUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

Abzweig

LUTRON

LUTRON(2) 4,0 mm2(12 AWG)

LUTRON

Drahtquerschnitt< 153 mStromversorgung(Klemmen 1 und 2)2
1 1,0 mm -Leitungspaar (18 AWG)

Signature SeriesTM, ArchitraveTM
IEC-PELV/NEC® Class 2Steuerleitungen(2) 1,0 mm2 (18 AWG)
1: Masse
2: 24 V

Lutron-Kabel Bestell-Nr.

Daten (Klemmen 3 und 4)
2
1 abgeschirmtes verdrilltes 0,5 mm Leitungspaar (22 AWG)
Stromversorgung(Klemmen 1 und 2)2
1 4,0 mm -Leitungspaar (12 AWG)
Daten (Klemmen 3 und 4)
2
1 abgeschirmtes verdrilltes 0,5 mm Leitungspaar (22 AWG)

4

Datenverbindung

IEC-PELV/NEC® Class 2Steuerleitungen(2) 1,0 mm2 (18 AWG)
1: Masse
2: 24 V

Abschirmung

LUTRON

10 mm
Länge der QS-Bus-Verdrahtung

A

A

LUTRON

Abisolierte
Drahtlänge

B

B

LUTRON

LUTRON:C

seeTouch® Internationale
IEC-PELV/
NEC® Class 2Steuerleitungen

1

3

LUTRON

1

4

LUTRON

2

2

LUTRON

Leitungsquerschnitte (überprüfen Sie die Kompatibilität in Ihrer Region)

Installationsanweisungen

3

LUTRON

LUTRON

4. Vorbereitung der Leitungen. Entfernen Sie
von den Drähten 10 mm der Isolierung.

153 bis 610 m

4

IEC-PELV/
NEC® Class
2-SteuerleitungenC

2. Installation der UP-Dose. Stellen Sie sicher dierichtige Größe. Siehe “Montage” für Einzelheiten.
3. Vorbereitung der Bedienstellen. Nehmen Sie
die Frontplatte ab und legen Sie sie zur Seite.

LUTRON

Abschirmung

3(2) 4,0 mm2(12 AWG)

LUTRON

Datenverbindung

seeTouch®, seeTouch® Internationale
Datenverbindung: (1) abgeschirmtes
verdrilltes Leitungspaar
0,5 mm2 (22 AWG)
3: MUX
Abschirmung
4: MUX
4:

LUTRON

30 mA 30 mA

In Reihe

LUTRON

LUTRON

LUTRONOFF OFF OFF

ON
ON
ON

1. Schalten Sie den Strom
AUS. Schalten Sie die
Sicherungsautomaten ausoder entfernen Sie die
Sicherungen.

LUTRON

seeTouch®

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

LUTRON

LUTRON<153 m

153 bis 610 m

Mögliche Anschlusskonfigurationen

LUTRON

Schließen Sie für die Stromversorgung an Klemme
1 und 2 Leitungen an, die den richtigen Querschnitt
für die Länge der Verbindung haben(siehe gegenüberliegende Tabelle).

AC N
AC N
099 942 971 099 942 971• Die Systeminstallationsanleitung und Lutrons
Schaltpläne zur Verkabelung der Starkstromund Datenleitungen (Bus-Leitung) enthalten die
für die Verkabelung geltenden Grenzen undBeschränkungen.
• Die Bedienstelle muss innerhalb der UP-Dose derBedienstelle oder in einer Verteilerdose (bauseits) an
die Busleitung angeschlossen werden.
• Verwenden Sie Klemmen, die gesetzlich
vorgeschrieben sind.
Achtung! Stromschlaggefahr. Gefahr
schwerer oder tödlicher Verletzungen.
Vor allen Arbeiten muss immer derSicherungsautomat ausgeschaltet bzw.
die Hauptsicherung entfernt werden.

Verdrahtung des QS-Busses
Schließen Sie zwei abgeschirmte verdrillte 0,5-mm2Leitungspaare (22 AWG) an die Klemmen 3 und
4 des Busleitungsanschlusses an. Verbinden Sie
die Schirmleitungen der verdrillten Leitungspaare
wie gezeigt miteinander, aber verbinden Sie die
Schirmleitungen nicht mit Erde/Masse oder derBedienstelle und lassen Sie sie nicht die geerdete
Unterputzdose berühren.

1• Die Busleitungen dürfen nicht zusammen mit
Netzleitungen verlegt werden.
• Die Schirmleitung muss entlang der gesamten Busleitung
geführt werden. Verbinden Sie die Schirmleitung nicht
mit Erde/Masse, und achten Sie darauf, dass sie die
geerdete Unterputzdose nicht berührt.
• Schließen Sie Netzspannungsleitungen nie an
Niederspannungsklemmen an. Falsche Verdrahtung
kann zu Verletzungen von Personen führen undBeschädigungen der Steuerstelle oder anderer
Einrichtungen zur Folge haben.

2Anschluss/Installation

GRX-CBL-346S (nicht zur Verwendungin abgehängten Decken)
GRX-PCBL-346S (zur Verwendungin abgehängten Decken)

1

GRX-CBL-46L (nicht zur Verwendungin abgehängten Decken)
GRX-PCBL-46L (zur Verwendungin abgehängten Decken)

Datenverbindung: (1) abgeschirmtes
verdrilltes Leitungspaar
0,5 mm2 (22 AWG)
3: MUX
4: MUX

Signature SeriesTM, ArchitraveTM(2) 4.0 mm2(12 AWG)

Datenverbindung
1(2) 4.0 mm2(12 AWG)

2

IEC-PELV/NEC®
Class 2-Steuerleitungen2
3
4

Abschirmung

3
4

Benutzerexemplar

Benutzerexemplar

Abschirmung

5

Datenverbindung: (1)abgeschirmtes verdrilltes
Leitungspaar
0,5 mm2 (22 AWG)
3: MUX
4: MUX

IEC-PELV/NEC® Class 2Steuerleitungen(2) 1,0 mm2 (18 AWG)
1: Masse
2: 24 VInstallationsanweisungenseeTouch®

Signature SeriesTM
Adapterschrauben

seeTouch®
Montageschrauben

Montageschrauben

Adapterschrauben:

seeTouch® Internationale

Steuerstelle

Frontplatte
Frontplatte

B

2

1

AdapterA

3

Tastenkit

Tastenkit

C

Masse
Input 2
Input 1

Masse
Eingang 2
Eingang 1

Steuerstelle

Adapter

UP-Dose(3) 1,0 mm2(18 AWG)

4(18 AWG)

Montage
Bringen Sie die Bedienstelle wie abgebildet an
und richten Sie sie sorgfältig aus. Schrauben Sie dieobere und untere Montageschraube in Bedienstelleund Unterputzdose. Ersetzen Sie denAdapter(US Ausführungen mit Einsatz – mittels separater
Schrauben), bringen Sie das Tastenkit sowie
die Frontplatte in der gezeigten Reihenfolge an.

UP-DoseAC N
099 942 971(3) 1,0 mm2

Hinweis: Falls an einer Bedienstelle Geräte überpotentialfreie Eingänge angeschlossen sind, “bedient”
CCI1 die obere Taste und CCI2 “bedient” dieuntere Taste. Um dieses Verhalten zu ändern, sieheAnwendungshinweis 428 (erweiterter seeTouch®Programmiermodus) auf www.lutron.com.
Ausnahme: An einer 2-Tasten-Bedienstelle, die
für Trennwände, Panik oder Sequenzsteuerungkonfiguriert ist, folgt der Schließvorgang von Eingang
CCI1 auf Druck der oberen Tasteund der Öffnungsvorgang auf Druckder unteren Taste.

CO O P E R S BURG , P A 18036 US A

30 mA

Verdrahtung des potentialfreien Eingangs (CCI)
Die potentialfreien Eingängen können die folgenden
Signale verarbeiten: potentialfreie Kontakte, offener
Kollektor oder active-low (NPN)/active-high (PNP).
• Bei offenem npn-Kollektor oder active-low mussdie Spannung im Durchlasszustand unter 2 V liegenund 3,0 mA ziehen.
• Bei offenem pnp-Kollektor oder active-high mussdie Spannung im Durchlasszustand über 12 V liegenund 3,0 mA liefern.
• Die Ausgänge müssen mindestens 60 ms imgeschlossenen oder offenen Zustand bleiben, damit
die Bedienstelle den entsprechenden Zustand erkennt.
Falls Sie Zweifel haben, ob eine Komponente eines
anderen Herstellers mit diesen Spezifikationen
kompatibel ist, wenden Sie sich bitte an den Hersteller.

ArchitraveTM

seeTouch® Internationale

Montageschrauben
Montageschrauben
Adapterschrauben

UP-DoseSignature SeriesTM

Adapter(3) 1,0 mm2(18 AWG)
A
B
C

UP-Dose

Steuerstelle

ArchitraveTM(3) 1,0 mm2(18 AWG)

Eingang 1
Eingang 2
Masse

A
B
C

Eingang 1
Eingang 2
Masse

Steuerstelle

Tastenkit

Frontplatte

Frontplatte
Bedienstellentyps

UP-Dose größe(hoch x breit x tief)

Lutron Bestell-Nr.

seeTouch®
seeTouch®
Internationale
SignatureTM SeriesArchitraveTM

95 x 55 x 70 mm

24151975 x 75 x 35 mm

241683

Schalten Sie den Sicherungsautomaten ein odersetzen Sie die Hauptsicherung wieder ein.

113 x 39.x 71 mm
112 x 32 x 70 mm

WBOX-SA1-Q1
241399Die Installation ist damit abgeschlossen

Einschalten

Zu Programmierfunktionen siehe die Programmieranleitung
für QS Bedienstellen auf www.lutron.com/qs.
Installationsanweisungen

6

Benutzerexemplar

Benutzerexemplar

7

InstallationsanweisungenFehlersuche: LED-Funktionalität
Verhalten der LEDs

Fehlersuche: Rollofunktionen
Bedeutung und Abhilfe

Alle Bedienstellentypen
Rückwärtslaufend
Die LEDs leuchten nacheinander von unten nach oben auf, bis alle ansind. Dann gehen sie nacheinander von unten nach oben aus, bis alle
aus sind. Der Vorgang wird dann wiederholt.

Kommunikation am QS-Bus nicht möglich, oder allein am QS-Bus.
Bus-Verdrahtung überprüfen.

Überhaupt keine LED-Rückmeldungen, auch nicht bei Tastendruck.

Die Bedienstelle erhält keinen Strom. Netzverkabelung überprüfen.
Ein anderes Gerät am QS-Bus ist in Programmier- oder Zuordnungs-Modus.
Das betreffende Gerät aus dem Programmier-Modus nehmen oder diese Bedienstellein den Programmier-Modus versetzen und dann den Programmier-Modus
verlassen, wodurch der Programmier-Modus an allen Geräten abgeschaltet wird.

Alle LEDs blinken schnell.

Die Bedienstelle befindet sich im erweiterten Programmier-Modus. Zum Beenden
des erweiterten Programmier-Modus die obere und untere Taste 3 Sekundenlang gedrückt halten.

Rollo-Bedienstellen
Obere und untere LED blinken zusammen.

Die Bedienstelle ist im Zuordnungs-Modus. Zum Beenden des Zuordnungs-Modus
die obere und untere Taste 3 Sekunden lang gedrückt halten.

Alle LEDs blinken 3-mal, setzen aus, blinken erneut.

Die Bedienstelle befindet sich im Zuordnungs-Modus oder im Modus zum
Einstellen der Endlagen und kann keine Rollos finden, die dem QS-Bus zugeordnet
sind, bzw. mit ihnen kommunizieren. Die Rolloverdrahtung kontrollieren.
60 Sekunden warten, und die Bedienstelle kehrt automatisch zum normalen Modus
zurück (ohne Benutzereingriff). Oder die obere und untere Taste 3 Sekunden langgedrückt halten, um den Modus sofort zu verlassen.

Obere und untere LED leuchten abwechselnd auf (obere LED leuchtet,
geht dann aus, untere LED leuchtet, geht dann aus, dann wird derVorgang wiederholt).

Die Bedienstelle befindet sich im Modus zum Einstellen der Endlagen oder ein
anderes Gerät amBus befindet sich im Modus zum Einstellen der Endlagen.
Die obere und die Heller-Taste 3 Sekunden lang gedrückt halten,
um den Modus zum Einstellen der Endlagen zu verlassen.

Obere und untere LED blinken langsam, und eine andere LED blinkt schnell.

Die Bedienstelle befindet sich im Voreinstellungs-Modus. Obere und untere Taste
gedrückt halten, um den Voreinstellungs-Modus zu verlassen.

Andere Bedienstellen
Eine einzige LED blinkt.

Die Bedienstelle ist entweder für Zonenumschaltung, Trennwände oder
Rolloumschaltung konfiguriert und befindet sich im Programmier-Modus. Die obere
und untere Taste gedrückt halten, um den Programmier-Modus zu verlassen.

Vorwärtslaufend
Die LEDs gehen nacheinander von oben nach unten an und aus.

Die Bedienstelle ist für Szene, Panik, Sequenz, Feinabstimmung oder Szenen/
Zonen-Verriegelung konfiguriert und befindet sich im Programmier-Modus.
Die obere und untere Taste gedrückt halten, um den Programmier-Moduszu verlassen.

Installationsanweisungen

8

Benutzerexemplar

Anzeichen

Mögliche Ursachen

Abhilfe

Die EDU (elektronische Antriebseinheit
des Rollos) bewegt sich nicht

Die EDU wird nicht mit Strom versorgt

Die Stromversorgung der EDU kontrollieren

Der Stoff des Rollos hängt irgendwo fest

Den Stoff überprüfen und ggf. lösen

Die EDU ist keiner Bedienstelle zugeordnet

Die EDU einer Bedienstelle zuordnen

Die Voreinstellungen sind falsch eingestellt

Die Heller/Dunkler-Tasten an der Bedienstelleausprobieren

Die Endlagen wurden falsch eingestellt

Die Endlagen richtig einstellen

Der Stoff des Rollos hängt irgendwo fest

Den Stoff überprüfen und ggf. lösen

Das Rollo bewegt sich in die
entgegengesetzte Richtung,wenn die Heller/Dunkler-Tasten
gedrückt werden

Die Endlagen beim Öffnen und Schließen wurdenvertauscht

Die Endlagen richtig einstellen

Die LEDs der Bedienstelle sind aus und
die Bedienstelle kann kein Rollo steuern

Die Bedienstelle erhält keinen Strom

Die Stromversorgung zur Bedienstelle kontrollieren
und herstellen

Die LEDs der Bedienstelle leuchten, aber
die Bedienstelle kann kein Rollo steuern

Alle Voreinstellungen befinden sich in der gleichen Höhe

Die Heller/Dunkler-Tasten an der Bedienstelleausprobieren

Der Kommunikationslink ist nicht an der EDU
angeschlossen

Den EDU-Link kontrollieren und herstellen

Die Zuordnung der EDU zur Bedienstelle wurde
aufgehoben

Die EDU der Bedienstelle neu zuordnen

Die EDU (elektronische Antriebseinheit
des Rollos) öffnet oder schließt nicht
vollständig

Die Bedienstelle steuert nicht allezugeordneten Rollos

Die Rollos in einem Raum bewegen sichvon selbst

Benutzerexemplar

Die Endlagen beim Öffnen und Schließen sind gleich

Die Endlagen richtig einstellen

Die Zuordnung der EDU zur Bedienstelle wurde
aufgehoben

Die EDU der Bedienstelle neu zuordnen

Alle Voreinstellungen befinden sich in der gleichen Höhe

Die Heller/Dunkler-Tasten an der Bedienstelleausprobieren

Die EDU ist nicht richtig verkabelt

Die EDU kontrollieren und neu verdrahten

Die Bedienstelle ist nicht richtig verkabelt

Die Bedienstelle kontrollieren und neu verdrahten

Die EDUs wurden einer Bedienstelle in einem anderen
Raum zugeordnet

Die EDU der richtigen Bedienstelle zuordnen

9InstallationsanweisungenFehlersuche
Anzeichen

Mögliche Ursachen

Keine Kommunikation mit dem GRAFIK Eye®-Steuergerät oder dem
Energi Savr NodeTM-Gerät.

Fehlerhafte Verdrahtung oder lose Verbindung der Datenleitungen3 und 4 der Busleitung.
Die Bedienstelle wurde nicht programmiert oder falsch programmiert.

Bedienstellentasten funktionieren nicht; LEDs reagieren nicht;
Bedienstellentasten funktionieren nicht wie vorgesehen.

Die Bedienstelle ist falsch angeschlossen.
Die Bedienstelle wird nicht mit Strom versorgt.
Die Bedienstelle ist nicht für die richtige Komponente programmiert.
Die Bedienstelle wurde nicht programmiert oder falsch programmiert.

Die LEDs leuchten nicht.

Fehlerhafte Verdrahtung oder lose Verbindung an den Bedienstellen oderam Prozessor in der Netz- oder Masseleitung der Busleitung (1 und 2).
Die Bedienstelle wurde falsch programmiert.

Eingänge mit potentialfreien Kontakten oder Sensoreneingänge führen
nicht zum gewünschten Ergebnis im System.

Fehlerhafte Verdrahtung oder lose Verbindung am Sensoren-/CCI-Anschluss
der Bedienstelle.
Die Bedienstelle wurde nicht programmiert oder falsch programmiert.

Internet: www.lutron.com
E-Mail: product@lutron.com
WELTWEITE ZENTRALE
USA
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TEL. +1.610.282.3800
FAX +1.610.282.1243
Gebührenfrei 1.888.LUTRON1
Technische Unterstützung 1.800.523.9466
Nord- und Südamerika
Technische Hotlines
USA, Kanada, Karibik: 1.800.523.9466
Mexiko: +1.888.235.2910
Mittel-/Südamerika: +1.610.282.6701

EUROPA-ZENTRALE
Großbritannien
Lutron EA Ltd.
6 Sovereign Close
LondonE1W 3JF United Kingdom
TEL. +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
GEBÜHRENFREI (Deutschland) 0800.1815.134
Technische Unterstützung +44.(0)20.7680.4481

Garantie: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code, NEC und NFPA sind eingetragene Warenzeichen der National Fire Protection Association, Inc.,
Quincy, Massachusetts.
Lutron, , Sivoia, seeTouch, Quantum und GRAFIK Eye sind eingetragene Warenzeichen und Energi Savr Node,Architrave und Signature Series sind Warenzeichen von Lutron Electronics Co., Inc.
© 2012 Lutron Electronics Co., Inc.

ASIEN-ZENTRALE
Singapur
Lutron GL Ltd.
15 Hoe Chiang Road
#07-03 Euro Asia Centre
Singapur 089316
TEL. +65.6220.4666
FAX +65.6220.4333
Asien, technische Hotlines
Nord-China: 10.800.712.1536
Süd-China: 10.800.120.1536
Hongkong: 800.901.849
Indonesien: 001.803.011.3994
Japan: +81.3.5575.8411
Macau: 0800.401
Singapur: 800.120.4491
Taiwan: 00.801.137.737
Thailand: 001.800.120.665853
Andere Länder: +65.6220.4666®

®

Lutron Electronics Co., Inc.
Bestell-Nr. 0301604 Rev. B 10/2012

Stations murales QS
Guide d’installation
IEC PELV/NEC® Class 2
24 V
30 mA

Veuillez lire attentivement

Exposé général................................................................................. 2
Exemple de câblage de groupe de puissance ................................... 3
Câblage/Installation.......................................................................... 4
Montage........................................................................................... 7
Dépistage de défauts........................................................................ 8

Pour la programmation, consulter le guide de programmationde station murale QS (P/N 0301639) au www.lutron.com/qs®

Les circuits de station murale sont classifiés IEC PELV/NEC® circuits Class 2. Les
circuits Class 2 sont conformes aux règlements du NFPA® 70, National Electrical Code®
(NEC®). Les circuits PELV sont conformes aux règlements du IEC 60364-4-41, VDE 0100
Partie 410, BS7671:1992 et à d’autres standards équivalents. Lors
de l’installation et du câblage de ces stations murales, vous devez suivre tous lesrèglements de câblage des codes nationaux et/ou locaux applicables. Les circuits
externes connectés aux entrées, aux sorties et autres terminaux de communication destations murales, doivent être fournis à partir de la source listée Class 2 ou être conforme
aux conditions pour les circuits PELV tel qu’appliqué dans notre pays.

Français

ContenuExposé général

Modèles de stations murales QS

Claviers
seeTouch®
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BD
Claviers
Signature SeriesTM
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

Claviers seeTouch®
Internationale
QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL• Les stations murales QS peuvent êtreprogrammées pour contrôler l’éclairage, les storesou l’éclairage et les stores.
• Les stations murales (hors de la boîte) QS non
programmées, les stores Sivoia® QS, les unitésde contrôle GRAFIK Eye® QS, les unités Energi
Savr NodeTM fonctionnent tous ensemble sauf si
programmés autrement.
• Les entrées à contact sec permettent
le fonctionnement des détecteurs de présence
et d’absence, de cloisonnement et plus encore.
Limites de la liaison QS• La liaison de communication câblée QS est limitéeà 100 dispositifs et à 100 zones. Chaque station
murale seeTouch® compte comme 1 dispositif
et 0 zone.
• Les stations murales QS utilisent 1 unité depuissance absorbée (PDU) sur la liaison QS.
Pour plus d’information concernant les unités depuissance absorbée, se référer aux spécifications
soumises pour les unités de puissance absorbéede liaison QS (Lutron P/N 369405) et au schéma àla page opposée.

Claviers
ArchitraveTM
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•
•
•
•
•

Remarques• Veuillez lire attentivement toutes les directives
avant de procéder à l’installation.
• Lutron recommande que les stations murales
soient installées par un électricien qualifié.
• Pour nettoyer les faces avants, utiliser uniquement
un linge avec de l’eau tiède et un savon doux
(aucun nettoyant chimique).
Directives d’installation

Composantes compatibles
Les dispositifs suivants sont compatibles avec
la liaison QS. Pour plus d’information sur chacun,se référer au www.lutron.com/qs
Unités de contrôle GRAFIK Eye® QS
Stations murales QSStores Sivoia® QS
Interfaces QS (contact sec, Ethernet/RS232)
Système Quantum®
Unités Energi Savr NodeTM
Module de détection QSInterrupteur à clé QS

Exemple de câblage de groupe de puissance

Sur la liaison QS, il y a des dispositifs qui consomment de l’énergie et des dispositifs qui en fournissent.
Chaque dispositif possède un nombre spécifique d’unités de puissance absorbée (PDU). Il fourni ou
consomme. Un groupe de puissance comprend un dispositif d’alimentation et un ou plusieurs dispositifs
de consommation; chaque groupe de puissance peut avoir qu’un seul dispositif d’alimentation. Se référer
aux spécifications soumises des unités de puissance absorbée de liaison QS (Lutron P/N 369405) pour plusd’information concernant les PDU.
Pour chaque groupe de puissance de liaison QS, connecter les 4 bornes de raccordement (bornes 1, 2,
3 et 4) identifiées par la lettre A sur le schéma. Pour les dispositifs qui servent d’alimentation de liaison QS,
ne raccorder que les bornes 1, 3 et 4 (ne PAS raccorder la borne 2) module indiqué par la lettre B
sur le schéma.
Le câblage peut être sous forme de branchement en T ou en cascade.

AGroupe de puissance 1

LUTRONGRAFIK Eye® QS
unité de contrôle
Fournitures
B
des PDU(Ne pas faire de connexion
à la borne 2 : 24 V ))Stations murales
PDU consommésGroupe de puissance 2

A

LUTRON

LUTRONB(Ne pas faire de connexion
à la borne 2 : 24 V )Groupe de puissance 3

A

Connecter
seulement
3 bornes deraccordement
entre les groupes
de puissance :1 : Commun
3 et 4 : Données

Bloc d’alimentation QSFournitures des PDU

LUTRON(Ne pas faire de connexion
à la borne 2 : 24 V )Copie de l’occupant

LUTRON

B

Appareil
Energi Savr NodeTM
Fournitures des PDU

Connecter les
4 bornes deraccordement
à l’intérieurd’un groupede puissance :1 : Commun
2 : 24 V
3 et 4 : Données

Module détecteur QS avec détecteurde présence
PDU consommés

B
2

A

LUTRONInterfaces de contrôle
PDU consommés

Copie de l’occupant

Ne pas faire deconnexion à laborne 2 : 24 V

Panneau Quantum®
Fournitures des PDU
3

Directives d’installation

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

Drain
4
3
2

4

Prise en T3(2) 4,0 mm2(12 AWG)

LUTRON

LUTRON

LUTRON

2
1

LUTRON

LUTRON

LUTRON

LUTRON

Longueur de dénudage
LUTRONA

LUTRONA

B

Liaison dedonnéesCâblage de contrôle IEC PELV/NEC®
Class 2, (2) 1,0 mm2 (18 AWG)
1 : Commun
2 : 24 V

LUTRONBC(2) 4,0 mm2(12 AWG)

LUTRONC

seeTouch® Internationale
Câblage decontrôle IEC PELV/
NEC® Class 2

LUTRON

LUTRON

1

Câblage decontrôle IEC PELV/
NEC® Class 2:

Liaison dedonnéesseeTouch®, seeTouch® Internationale
Liaison de données : (1) paire
torsadée, blindée 0,5 mm2 (22 AWG)
3 : MUX
4 : MUXDrain:

LUTRON

LUTRON

LUTRONOFF OFF OFF

ON
ON

LUTRON

30 mA 30 mA

LUTRON

LUTRON

seeTouch®

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

Guirlande

LUTRON

1. Couper l’alimentation
OFF. Couper le courant
au disjoncteur principal/
MCB (ou enlever le fusible).
2. Monter la boîte murale.
Assurez-vous que la dimension soit exacte. Voir“Montage” pour les détails.
3. Préparer les stations murales. Retirer la plaquemurale et mettre de côté.
4. Préparer les fils. Dénuder l’isolation des fils desorte que 10 mm (4 po) de fil nu soit exposé.
ON

LUTRON<153 m/500 pi

153 à 610 m/500 à 2 000 pi

Configurations de câblage admissibles
LUTRON

Connecter la grosseur de fil approprié aux bornes
1 et 2 pour l’alimentation, selon votre longueur deliaison (voir tableau ci-contre).

AC N
AC N
099 942 971 099 942 971•

Câblage de la liaison QS
Connecter deux paires de fils torsadés blindés de
0,5 mm2 (22 AWG) aux bornes 3 et 4 du connecteurde la barre de communication de la station murale.
Le blindage (drain) des câbles de paire torsadée doitêtre connecté ensemble tel que démontré mais ne
pas connecter le blindage à la mise à la terre ou lastation murale et ne permettez pas de contact avec
la mise à la terre de la boîte murale.

1

Avertissement! Choc électriquepouvant causer des blessures
graves, voire la mort. Toujours mettre
le disjoncteur/MCB (disjoncteur principal)
hors circuit ou enlever le fusible principal
de la ligne secteur avant d’effecteur tout travail.

•Le câblage de la barre de communication ne doit pasêtre tiré dans la même canalisation que celle du câbled’alimentation secteur.
Le fil de blindage ou de drain doit être continu sur toutela longueur de la barre de communication. Ne pas
connecter le blindage à la mise à la terre ou permettre
tout contact avec un boîtier mis à la terre.
Ne pas connecter l’alimentation haute tension à des bornes
de raccordement de basse tension. Un câblage inadéquat
peut résulter à des blessures corporelles ou des dommages
au contrôle ou à d’autres équipements.

2

•

•

Pour connaître les limites et restrictions d’installation
des câbles d’alimentation et de données (barre decommunication), se référer au guide d’installation
du système et aux schémas de travail de Lutron.
Connecter la station murale à la barre de communication
à l’intérieur de la boîte murale de la station murale
ou dans une boîte de jonction (fournie par des tiers).
Utiliser un capuchon de connexion tel que requis
par le code local.

3•

Câblage/Installation

4

•

Drain

LUTRON

Signature SeriesTM, ArchitraveTM
Câblage de contrôle IEC PELV/NEC®
Class 2, (2) 1,0 mm2 (18 AWG)
1 : Commun
2 : 24 V

10 mm (4 po)

Grosseur de fil (vérifier la compatibilité dans votre région)
Longueur de câble deliaison QS

Calibre des fils

Moins de 153 m (500 pi)

Puissance (bornes
1 et 2)2
1 paire 1,0 mm (18 AWG)

153 à 610 m(500 à 2 000 pi)

Données (bornes 3 et 4)2
1 paire torsadée et blindée 0,5 mm(22 AWG)
Puissance (bornes
1 et 2)2
1 paire 4,0 mm (12 AWG)
Données (bornes 3 et 4)2
1 paire torsadée et blindée 0,5 mm(22 AWG)

Directives d’installation

Câble Lutron P/N

1

4

Câble GRX-CBL-346S (non-plenum)
Câble GRX-PCBL-346S (plenum)(2) 4,0 mm2(12 AWG)(2) 4,0 mm2(12 AWG)

2
3
4

Copie de l’occupant

Copie de l’occupant

Câblage de contrôle IEC PELV/
NEC® Class 2
Liaison dedonnées

1
2
3

Drain

4

Liaison de données : (1) paire
torsadée, blindée 0,5 mm2 (22 AWG)
3 : MUX
4 : MUXGRX-CBL-46L (non-plenum)
GRX-PCBL-46L (plenum)

Signature SeriesTM, ArchitraveTM

5

Liaison de données : (1) paire
torsadée, blindée
0,5 mm2 (22 AWG)
3 : MUX
4 : MUX

Drain

Câblage de contrôle IEC PELV/
NEC® Class 2(2) 1,0 mm2 (18 AWG)
1 : Commun
2 : 24 V

Directives d’installation

:

Signature SeriesTM
Vis
adaptatrices

Vis de montage

Vis adaptatricesBoîte murale

Face avant
Boutons

ArchitraveTM
Adaptateur

Vis de montage

Face avant
1

seeTouch® Internationale
Vis de montage

A

3

B

2

C

CommunEntrée 2
Entrée 1

CommunEntrée 2
Entrée 1

Vis adaptatricesBoîtemuraleSignature SeriesTM

BoîtemuraleArchitraveTM(3) 1,0 mm2(18 AWG)

A
B
C

Adaptateur(3) 1,0 mm2(18 AWG)

Entrée 1
Entrée 2
CommunA
B
C

Entrée 1
Entrée 2
CommunType deposte mural

Dimension deboîte murale(haut x large x profond)seeTouch®

95 x 55 x 70 mm
3,7 x 2,2 x 2,75 po
75 x 75 x 35 mm
3 x 3 x 1,4 po
113 x 39.x 71 mm
4,4 x 1,5 x 2,8 po
112 x 32 x 70 mm
4,4 x 1,25 x 2,75 po

ArchitraveTM
Copie de l’occupant

Boutons
Face avant

Signature SeriesTM

6Contrôle
Face avant

Contrôle

seeTouch®
Internationale

Directives d’installation

Boutons

Contrôle

Adaptateur

Contrôle

(3) 1,0 mm2(18 AWG)

Vis demontage

seeTouch®

Boîte murale

4(3) 1,0 mm2(18 AWG)

Montage
Monter soigneusement et aligner la station murale
tel que démontrée. Vissez la vis du haut et du bas
dans le contrôle de la boîte murale. Remplacerl’adaptateur (pour versions ancrage; visser
au contrôle), assemblage de bouton et la faceavant dans l’ordre démontré.

seeTouch® Internationale

AC N
099 942 971

seeTouch®

Remarque : Si une station murale a desdispositifs qui lui sont reliés via desentrées à contacts secs, CCI1
“appuie” sur le bouton du haut et
CCI2 “appuie” sur le bouton du bas.
Pour changer ce comportement, seréférer à la Note d’Application 428(seeTouch® Mode de Programmation
Advanced) au www.lutron.com.
Exception : Pour une station murale
à 2 boutons configurée pour lesfonctionnalités de cloisonnement,
panique ou de séquencement,
l’action de fermeture CCI1 suitle bouton du haut et l’action
d’ouverture suit le bouton du bas.

CO O P E R S BURG , P A 18036 US A

30 mA

Câblage d’entrée à contacts secs (CCI)
Les entrées à contacts secs doivent être à contacts
secs, semi-conducteur, collecteur ouvert, ou sortie
active à l’ état bas (NPN)/ à l’ état haut (PNP).
• La tension d’entrée du collecteur ouvert NPN ou
de l’entrée active à l’ état bas doit être inférieureà 2 V et baisser de 3,0 mA.
• La tension d’entrée du collecteur ouvert PNP
ou de l’entrée active à l’état haut doit être supérieurà 12 V et doit générer 3,0 mA.
• Les sorties doivent demeurer à l’état fermé
ou ouvert pendant au moins 60 msec afin d’être
reconnues par la station murale.
S’il y a des questions à savoir si le dispositif
d’un tiers qui génère ces sorties est compatible
avec les spécifications, communiquer avec
le fabricant.

Copie de l’occupant

Lutron P/N

Mettre sous tension
Activer le disjoncteur de contrôle, ou remettre
le fusible principal en place.
Installation est complétée
Pour les fonctions de programmation, se référer
au Guide de programmation de station murale QS
à www.lutron.com/qs

241519241683
WBOX-SA1-Q1
2413997

Directives d’installation

Dépistage de défauts : Fonctionnalité DEL

Dépistage de défauts : Fonctions stores

Comportement de la DEL

Symptôme

Causes possibles

Solution

L’unité EDU (unité de conduiteélectronique du store) ne bouge pas

L’unité EDU n’est pas alimentée

Vérifier l’alimentation de l’unité EDU

Le tissu du store est retenu par quelque chose

Vérifier et dégager le tissu du store

L’unité EDU n’est pas assignée à un clavier

Assigner l’unité EDU à un clavier

Les préréglages ont été réglés incorrectement

Essayer d’utiliser les boutons hausser/baisser
sur le clavier

Les limites ont été réglées incorrectement

Régler les limites correctement

Problème et solution

Tout type de clavier“Séquencement inversé”
Les DEL s’illuminent à partir du bas, en continuation jusqu’à
ce qu’elles soient toutes allumées; ensuite les DEL s’éteignent
en commençant par le bas, en continuation jusqu’à ce qu’elles
soient toutes éteintes. Ensuite, le cycle se répète.
Aucune rétroaction DEL du tout, même en appuyant sur le bouton.

Toutes les DEL clignotent rapidement.

Incapable de communiquer avec la liaison QS, ou seul sur la liaison QS.
Vérifier le câble de liaison.

Aucune puissance à la station murale. Vérifier le câblage de puissance.
Un autre dispositif sur la liaison QS est en mode de programmationou d’assignation. Sortir ce dispositif du mode de programmation,ou mettre ce clavier en mode de programmation et ensuite sortir
du mode de programmation, ce qui fera sortir du mode de programmation
tous les dispositifs.
La station murale est en mode de programmation advanced. Appuyer
et maintenir enfoncés les boutons haut et bas pendant 3 secondes afin
de sortir du mode de programmation advanced.

Claviers de store
Les DEL du haut et du bas clignotent ensemble.

Le clavier est en mode d’assignation. Pour sortir du mode d’assignation,
appuyer et maintenir enfoncés les boutons haut et bas pendant 3 secondes.
Toutes les DEL clignotent 3 fois, pausent, ensuite le cycle se répète. Le clavier est réglé en mode d’assignation ou de limite et ne peut trouver
ou communiquer avec aucun store assigné à la liaison QS. Vérifier le câblage
du store.
Attendre 60 secondes, et le clavier retournera automatiquement en mode
normal (sans l’intervention de l’utilisateur). Ou, appuyer et maintenir enfoncés
les boutons haut et bas pendant 3 secondes pour sortir immédiatement
de ce mode.
Les DEL du haut et du bas éclairent en alternance (DEL du haut
Le clavier est réglé en mode limite, ou un autre dispositif sur la liaison est
s’allume, ensuite s’éteint, ensuite la DEL du bas s’allume, ensuite
réglé en mode limite. Appuyer et maintenir enfoncés le bouton du haut et les’éteint; le cycle se répète).
bouton hausser pendant 3 secondes afin de sortir du mode de réglage limite.
Les DEL haut et bas clignotent lentement, et une autre DEL clignote Le clavier est en mode ajustement de préréglage. Appuyer et maintenir
rapidement.
enfoncés les boutons haut et bas pour sortir du mode ajustement
de préréglage.
Autres claviers
Une seule DEL clignote.
Le clavier est configuré en mode de bascule pour zone, cloisonnementou bascule pour store et est en mode de programmation. Appuyer
et maintenir enfoncés les boutons haut et bas pour sortir du modede programmation.
“Escalade séquentielle”
Le clavier est configuré pour scène, panique, séquence, précision,
Les DEL s’allument et s’éteignent en escalade de séquenceou verrouillage de scène/zone, et est en mode de programmation.
de haut en bas..
Appuyer et maintenir enfoncés les boutons haut et bas pour sortir
du mode de programmation.
Directives d’installation

8

Copie de l’occupant

L’unité EDU (unité de conduiteélectronique du store) ne peut
ni s’ouvrir, ni se fermer complètement

Le tissu du store est retenu par quelque chose

Vérifier et dégager le tissu du store

Le store se déplace dans la direction
opposée lorsque les boutons hausser/
baisser sont appuyés

Les limites d’ouverture et de fermeture ont été
inversées

Régler les limites correctement

Les DEL du clavier sont éteintes off
et le clavier ne contrôle aucun store

Aucune puissance ne se rend au clavier

Vérifier et effectuer le câblage d’alimentation
au clavier

Les DEL du clavier sont allumées(on) mais le clavier ne contrôle
aucun store

Tous les préréglages sont réglés à la mêmehauteur

Essayer d’utiliser les boutons hausser/baisser
sur le clavier

La liaison des communications n’est pas câblée
à l’unité EDU

Vérifier et effectuer le câblage de la liaison
de l’unité EDU

L’unité EDU a été non assignée au clavier

Réaffectation de l’unité EDU au clavier

Les limites ouvert et fermé sont identiques

Régler les limites correctement

L’unité EDU a été non assignée au clavier

Réaffectation de l’unité EDU au clavier

Tous les préréglages sont réglés à la mêmehauteur

Essayer d’utiliser les boutons hausser/baisser
sur le clavier

L’unité EDU n’est pas câblée correctement

Vérifier et refaire le câblage de l’unité EDU

Le câblage au clavier est incorrect

Vérifier et refaire le câblage du clavier

Les unités EDU sont assignées à un clavier
d’une autre pièce

Réaffecter l’unité EDU au bon clavier

Le clavier ne contrôle pas tous
les stores qui lui sont assignés

Les stores dans la pièce se déplacentpar eux-mêmes
Copie de l’occupant9

Directives d’installation

Dépistage de défauts
Symptôme

Causes possibles

Aucune communication avec l’unité de contrôle GRAFIK Eye® ou unité
Energi Savr NodeTM.

Mauvais raccordement ou connexion desserrée à la barrede communication des données des lignes 3 et 4.
La station murale n’a pas été programmée ou a été programmée
incorrectement.
Défaut de câblage à la station murale.

Les boutons de la station murale ne fonctionnent pas; les DEL ne
traquent pas; les boutons de la station murale ne fonctionnent pas telque prévu.

Station murale n’est pas alimentée.
Station murale n’est pas programmée au bon dispositif.
La station murale n’a pas été programmée ou a été programmée
incorrectement.

DEL ne s’allument pas.

Les entrées à contacts secs ou détecteurs d’entrée ne produisentpas le résultat désiré du système.

Mauvais raccordement ou connexion desserrée à la station(s) murale(s)ou le neutre du processeur de liaison de la barre de communication
et connexions d’alimentation 1 et 2.
Station murale n’est pas bien programmée.
Mauvais raccordement ou connexion desserrée au connecteurdu détecteur/CCI de la station murale.
La station murale n’a pas été programmée ou a été programmée
incorrectement.

Site Internet : www.lutron.com
Courriel : product@lutron.com
SIÈGE SOCIAL MONDIAL
États-Unis
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TÉL +1.610.282.3800
TÉLÉC. : +1.610.282.1243
Sans frais 1-888-LUTRON1
Assistance technique 1.800.523.9466
Amérique du nord et du sud
Lignes de support technique
États-Unis, Canada, Caraïbe : 1.800.523.9466
Mexique : +1.888.235.2910
Amérique Centrale/du Sud : +1.610.282.6701

SIÈGE EUROPÉEN
Royaume-Uni
Lutron EA Ltd.
6 Sovereign Close
Londres
E1W 3JF United Kingdom
TÉL +44.(0)20.7702.0657
TÉLÉC +44-(0)20-7480-6899
SANS FRAIS (U.K.) 0800-282-107
Support technique +44-(0)20-7680-4481

Garantie : www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code NEC et NFPA sont des marques déposées enregistrées du National Fire Protection Association, Inc.,
à Quincy, Massachusetts.
	Lutron, , Sivoia, seeTouch, Quantum, et GRAFIK Eye sont des marques de commerce déposées et enregistrées etEnergi Savr Node, Architrave et Signature Series sont des marques de commerce déposées de Lutron Electronics Co., Inc.
© 2012 Lutron Electronics Co., Inc.
®

®

SIÈGE ASIATIQUE
Singapour
Lutron GL Ltd.
15 Hoe Chiang Road
#07-03 Euro Asia Centre
Singapour 089316
TÉL : +65.6220.4666
TÉLÉC. : +65.6220.4333
Asie, Lignes de support technique
Chine du Nord : 10.800.712.1536
Chine du Sud : 10.800.120.1536
Hong Kong : 800.901.849
Indonésie : 001.803.011.3994
Japon : +81.3.5575.8411
Macau : 0800.401
Singapour : 800.120.4491
Taiwan : 00.801.137.737
Thaïlande : 001.800.120.665853
Autres pays : +65.6220.4666

Lutron Electronics Co., Inc.
P/N 0301604 Rev. B 10/2012

QS墙控站
安装指南
IEC PELV/NEC® Class 2
30 mA
24 V

请阅读

目录
概述..............................................2
电源组接线实例....................................3
接线/安装.........................................4
安装..............................................7
疑难排解..........................................8
中文

如需了解设置信息，请参阅www.lutron.com/qs
上的QS 墙控站设置指南(P/N 0301639)
墙控站回路分类为IEC PELV/NEC®2级回路。2级回路符合 NFPA® 70，
美国 National Electrical Code® (NEC®)的要求。PELV 回路符合欧洲IEC 60364-4-41，德国 VDE 0100 Part 410，英国 BS7671:1992 的要求和
其它同等的标准。当安装和接线到这些墙控器时，必须符合相应国家和/或当地的所有接线规定。连接到墙控器的输入、输出和其它通信端口的外接回路，
必须由名列在2级回路来源的供货商供货或符合该国家对 PELV 回路的要求。
®

概述

QS墙控站型号
seeTouch® 键控器
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BDSignature SeriesTM
键控器QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

电源组接线实例

• QS 墙控站可以进行设置，控制灯光、
窗帘或灯光和窗帘。
• 未设置的（出厂设置） QS墙控站、Sivoia® QS
窗帘、GRAFIK Eye® QS控制器和Energi Savr
NodeTM控制器可全部一起工作，直到有其他设置。
• 触点闭合输入允许与占用/空置传感器、分区和更多传感器一起操作。

seeTouch®
国际的键控器QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

QS 链路限制• QS接线通信链路限制为100个设备和100个光
区。每个QS 墙控站计数为1个设备和0个光区。
• QS墙控站使用QS链路上的1个用电单元（PDU）。关于用电单元的更多信息，请参考背页上的QS链路用电单元规格提交文件（路创P/N 369405）。

ArchitraveTM
键控器QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•
•
•
•
•

兼容组件
以下设备与QS链路兼容。更多信息，请参考
www.lutron.com/qs
GRAFIK Eye® QS控制器
QS 墙控站
Sivoia® QS窗帘QS接口（触点闭合，以太网/RS232）
Quantum®系统
Energi Savr NodeTM控制器
QS 传感器模块
QS 键开关

A

电源组1

LUTRONGRAFIKEye® QS
控制器
提供 PDUA

LUTRON

B

控制接口
消耗PDU

（不要连接端子2:24 V ）

墙控站
消耗PDU

1：共享
2：24 V
3和4：数据电源组2

A

B
LUTRON

LUTRON电源组间仅连接3
个端子：
1：共享
3和4：数据LUTRON

B

Energi Savr NodeTM
控制器。
提供 PDU

将所有4个端子连
接到一个电源组中不要连接
端子2: 24 V（不要连接端子2:24 V ）

电源组3A

注释• 开始安装前要仔细阅读所有的说明。
• 路创公司建议，墙控站应由合资格的电工来安装。
• 只能用蘸有温水和温性肥皂的布清洁面板（勿使用化学清洁剂）。

安装说明

在QS链路上，有供电设备，也有耗电设备。每个设备都有指定的用电单元（PDU）数。它们或是供电或是用电。 电源组包含一个供电设备或一个或多个用电设备；每个电源组可能都只有一个供电设备。 有关PDU 的
更多信息，请参阅QS链路用电单元规格提交文件（路创P/N 369405）。
在QS链路的电源组内，连接如示意图中的字母A所示的所有4个端子（1, 2, 3 和 4）。在 QS 链路上供应电力的设备之间，仅连接如示意图中的字母B所示的端子1, 3 和 4（不连接端子2）。
接线可以采用菊链式或T形抽头式连接。

QS电源
提供 PDU

LUTRON带占用传感器的 QS 传感器模块
消耗PDU

B
2

用户手册

（不要连接端子2:24 V ）

用户手册

Quantum® 面板向
PDU供电
3

安装说明

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

seeTouch®

T型抽头

4

3

(2) 12 AWG(4.0 mm2)

3

2

2

1

LUTRON

LUTRON

LUTRON(2) 12 AWG(4.0 mm2)

LUTRON

LUTRON

LUTRON

LUTRON

LUTRONIEC PELV/NEC® Class 2 接线(2) 18 AWG (1.0 mm2)
1: 共享
2: 24 V10 mm
线规不到 153 m

电源（端子1和2）
1 根1.0 mm2 (18 AWG)

153至610 m

电源（端子1和2）
1 根4.0 mm2 (12 AWG)
数据（端子 3 和 4）1根屏蔽双绞线，0.5 mm2 (22 AWG)

安装说明

1

路创线缆部件号数据（端子 3 和 4）1根屏蔽双绞线，0.5 mm2 (22 AWG)

4

A

Signature SeriesTM, ArchitraveTM

LUTRON

LUTRON接线尺寸（检查与您所在区域的兼容性）
QS 链路接线长度

A

B

剥线长度

数据
链路

B

C

IEC PELV/NEC® Class 2 接线(2) 18 AWG (1.0 mm2)
1: 共享
2: 24 V

LUTRONC

seeTouch® 国际的
IEC PELV/
NEC® Class
2 接线

LUTRON

LUTRON1

IEC PELV/
NEC® Class 2
接线

LUTRON

2. 安装墙盒。确保尺寸正确。详细说明请参阅“安装”。
3. 准备墙控站。卸下面板并放在一边。
4. 准备导线。 剥去导线的绝缘层使 10 mm
长的裸线露出。

:

数据链路
漏极

4

LUTRON

LUTRON:

LUTRON

30 mA 30 mA

菊链式

LUTRON

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

LUTRON

LUTRON<153 mseeTouch®, seeTouch® 国际的
数据链路 (1 根)屏蔽双绞线
0.5 mm2 (22 AWG)
3: MUX
4: MUX
漏极

AC N
AC N
099 942 971 099 942 971

LUTRON

LUTRON153 至 610 m

1

ON

ON

1. 切断电源。切断断路器（MCB）的电源（或取下保险丝）。

允许的接线配置
LUTRONOFF OFF OFF

ON

警告！触电危险。可能导致严重的受伤或死亡。 进入任何工作前，总是关闭断路器/MCB或从电源线上取下主保险丝。

根据链路长度，将相应规格的接线与端子1
和2相连供电（参见背面的表格）。

2• 有关电源电缆和数据电缆（控制器链路）的接线
限制，请参阅系统安装指南及路创的工作图。
• 墙控器与控制器链路之间的连接应在墙控器的墙盒内或在接线盒（由其它厂家提供）中进行。
• 使用当地法规规定的导线连接器。

接线QS 链路
连接两根0.5 mm2 (22 AWG)屏蔽双绞线到墙控站
的控制器链路连接器的接线端子 3 和 4 上。
必须如图所示将双绞线的屏蔽（漏极）连接在一起，但不要连接到地线或墙控站上，不允许与接地墙盒接触。

3• 控制器链路的走线 不得 与线电压的走线共用同一电缆管道。
• 所有控制器链路的漏极／屏蔽接线必须连接在一起。不要将屏蔽接线连接到地线上或允许与接地
墙盒接触。
• 不要将高压电源连接到低压端子上。不正确的接线会对人身构成伤害或造成控制器或其它设备的
损坏。

4

接线/安装

漏极
(2) 12 AWG(4.0 mm2)(2) 12 AWG(4.0 mm2)

Signature SeriesTM, ArchitraveTM

2

IEC PELV/NEC® Class 2
接线3

GRX-CBL-346S（非阻燃型）
GRX-PCBL-346S（阻燃型）

数据链路

4

1
2
3

数据链路 (1 根)屏蔽双绞线
0.5 mm2 (22 AWG)
3: MUX
4: MUXGRX-CBL-46L（非阻燃型）
GRX-PCBL-46L（阻燃型）

用户手册

用户手册

4

漏极

数据链路(1 根)屏蔽双绞线
0.5 mm2 (22 AWG)
3: MUX
4: MUX
5

漏极

IEC PELV/NEC® Class 2 接线(2) 18 AWG (1.0 mm2)
1: 共享
2: 24 V安装说明

注：如果墙控站有同触点闭合输入与之相连的设备，CCI1“按下”顶部按键，CCI2“按下”底部按键。如要更改此行为，请参考www.lutron.com上的应用说明428（seeTouch® 高级设置模式）。
例外：在配置用于分区、间隔空间、
应急模式或场景循环功能功能的2按键墙控站上，CCI1闭合动作受顶部按键控制，打开动作受底部按键控制。

seeTouch®

Signature SeriesTM
面板接口
安装螺
螺钉
钉

seeTouch®
面板接
口螺钉

安装螺钉

:

按键

控制器

面板接口
墙盒

seeTouch® 国际的

面板
控制器(3) 1.0 mm2

按键(18 AWG)

AC N
099 942 971

ArchitraveTM
面板接口

安装螺钉

2

B
A

3

C

共线
输入 2
输入 1

1

面板
共线
输入 2
输入 1

4

(3) 1.0 mm2(18 AWG)

安装如图所示，小心地装上墙控站并对齐。将顶部和
底部螺钉拧入控制器和墙盒。按以下顺序更换转接板（若嵌入式；装上控制器螺钉）、按键组
件和 面板。

墙盒CO O P E R S BURG , P A 18036 US A

30 mA

接线触点闭合输入(CCI)
触点闭合输入必须是干接触点闭合、固态、开
路集电极或低态有效(NPN)／高态有效(PNP)输
出。
• 开路集电极NPN或低态有效的通态电压必须小于
2 V 和 3.0 mA 灌入电流。
• 开路集电极 PNP 或高态有效的通态电压必须大于12 V 和 3.0 mA 源电流。
• 输出必须能保持在闭合状态或断开状态至少60毫
秒，以便墙控站识别。
如果对第三方设备产生的这些输出是否与这些规格兼容有疑问，请与制造商联系。

seeTouch® 国际的
安装螺钉
面板接口螺钉

墙盒
控制器面板

Signature SeriesTM

墙盒ArchitraveTM(3) 1.0 mm2(18 AWG)

A
B
C

安装说明

(3) 1.0 mm2(18 AWG)

输入 1
输入 2
共线

A
B
C

6

控制器
面板接口

按键
面板

输入 1
输入 2
共线

用户手册

墙控站类型

底箱尺寸
(高 x 宽 x 深)路创线缆部件号

seeTouch®
seeTouch® 国际的
Signature SeriesTM
ArchitraveTM

95 x 55 x 70 mm
75 x 75 x 35 mm
113 x 39.x 71 mm
112 x 32 x 70 mm

241519241683
WBOX-SA1-Q1
241399用户手册

通电
接通控制断路器的电源，或重新装上主保险丝。
安装完成
有关设置功能信息，请参见www.lutron.com/qs
上的QS墙控站设置指南。
7安装说明

疑难排解：窗帘功能疑难排解：LED功能
LED状态含义和解决办法

全部墙控器类型
“逆转瀑布”
LED从底部开始亮起，持续亮起，直至所有LED亮起，然后LED从底部开始熄灭，继续熄灭，直至所有LED熄灭，重复。
根本没有LED反馈，即使按键按下时。

无法与QS链路通信，或单独位于QS链路上。检查链路接线。

墙控站没有供电，检查电源接线。
QS链路上的其他设备处于设置或分配模式中。将该设备
退出设置模式或让墙控器进入设置模式，然后退出设置
模式，这将关闭所有设备上的设置模式。

所有LED灯快速闪烁。

墙控站在高级设置模式中，按住顶部和底部按钮3秒钟退出
高级设置模式。

表征

可能原因

解决办法

EDU（窗帘的电子驱动单元）不移动

EDU未通电

检查 EDU 的电源窗帘帘布被某个东西卡住

检查并解开窗帘帘布

EDU未指定给墙控器

将此EDU指定给墙控器

预设值的设置不正确

尝试使用墙控器的升／降按键极限的设置不正确

正确设置极限窗帘帘布被某个东西卡住

检查并解开窗帘帘布

按下升/降按键时窗帘在相反
的方向上移动

开启极限与关闭极限设反了正确设置极限墙控器的LED指示灯熄灭并
且墙控器无法控制任何窗帘墙控器无供电

检查并给墙控器接上电源墙控器的LED指示灯亮，但墙控器无法控制任何窗帘

所有预设值都设在同一高度

尝试使用墙控器的升／降按键通讯链路未连接至EDU检查并连接EDU链路EDU被从墙控器取消指定

重新将此EDU指定给墙控器

打开和关闭限制是相同的。

正确设置极限EDU被从墙控器取消指定

重新将此EDU指定给墙控器

所有预设值都设在同一高度

尝试使用墙控器的升／降按键EDU未正确接线

检查并重新给EDU接线控器未正确通电检查并重新给墙控器接线

EDU被指定给了另一房间内的某个墙控器

重新将此EDU指定给正确的墙控器

EDU（窗帘的电子驱动单元）不能完全开启或完全
关闭

窗帘墙控器
LED的顶部和底部一起闪烁。

墙控器在分配模式中。按住顶部和底部按钮3秒钟，退出分配模式。

所有LED闪烁3次，暂停然后重复。

墙控器处于分配或限制设置模式中，无法找到任何分配给
QS链路的窗帘或与其通信。检查窗帘接线。
等待60秒，墙控器将自动回到普通模式（无用户干预）。
或按住顶部和底部按钮3秒钟，立即退出该模式。

顶部和底部LED交替亮起（顶部LED亮起，熄灭，
然后底部LED亮起，熄灭，循环重复）。

墙控器在限制设置模式或链路上的其他设备处于限制设置
模式。按住顶部和上升按钮3秒钟，退出限制设置模式。

顶部和底部LED慢慢闪烁，另外一个LED快速闪烁。

墙控器在预设调节模式中，按住顶部和底部按钮退出预设
调节模式。
墙控器不能控制所有指定给
它的窗帘

其他墙控器
单个LED闪烁。
“前进瀑布”
LED从顶部到底部依次亮起和熄灭。

安装说明墙控器被配置用于区域切换、分区或窗帘切换，并处于设
置模式。按住顶部和底部按钮退出设置模式。
墙控器被配置用于场景、应急、循环、微调或场景/光区
锁定，并处于设置模式。按住顶部和底部按钮退出设置
模式。

8

用户手册

一个房间内的窗帘自行移动

用户手册

9

安装说明

疑难排解
表征

可能原因

没有与GRAFIK Eye® 控制器或Energi Savr NodeTM控制器通信。

控制链路的数据线 3 和 4 发生接线错误或连线松脱。

墙控站按钮不工作；LED没有跟踪；墙控站没有按要求工作。

墙控站接线有错。

墙控站未设置，或被错误地设置。

墙控未通电。
墙控站未设置到正确的设备。
墙控站未设置，或被错误地设置。

LED 指示灯不亮。

在墙控站或处理器上，控制器链路的共用和电源接线（1 和 2）发生接线错误或连线松脱。
墙控站设置不正确。

触点闭合输入或传感器输入未在系统中产生所期
望的结果。

墙控站的传感器／CCI 连接器发生接线错误或连线松脱。
墙控站未设置，或被错误地设置。

网址：www.lutron.com/asia
电子信箱：product@lutron.com
环球总部
美国
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
电话：+1.610.282.3800
传真：+1.610.282.1243
免费电话：1.888.LUTRON1
技术支援：1.800.523.9466
南美洲和北美洲
技术支持热线
美国、加拿大、加勒比：1.800.523.9466
墨西哥：+1.888.235.2910
中美洲／南美洲：+1.610.282.6701

欧洲总部
英国
Lutron EA Ltd.
6 Sovereign Close伦敦
E1W 3JF United Kingdom
电话：+44.(0)20.7702.0657
传真：+44.(0)20.7480.6899
免费电话（英国）：0800.282.107
技术支援：+44.(0)20.7680.4481

保修www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code, NEC 和 NFPA 是美国国家防火协会 (National Fire Protection
Association, Inc., Quincy, Massachusetts) 的注册商标。
Lutron、 、 Sivoia、seeTouch 、Quantum和GRAFIK Eye是路创电子公司的注册商标;Energi Savr Node, Architrave 和 Signature Series 是路创电子公司的商标。
© 2012 Lutron Electronics Co., Inc.

亚洲总部
新加坡
Lutron GL Ltd.
15 Hoe Chiang Road
#07-03 Tower Fifteen
Singapore 089316
电话：+65.6220.4666
传真：+65.6220.4333
亚洲技术支援热线
华北：10.800.712.1536
华南：10.800.120.1536
香港：800.901.849
印尼：001.803.011.3994
日本：+81.3.5575.8411
澳门：0800.401
新加坡：800.120.4491
台湾：00.801.137.737
泰国：001.800.120.665853
其它国家请拨打：+65.6220.4666®

®

Lutron Electronics Co., Inc.
P/N 0301604 Rev. B 10/2012

Acessórios de parede QS
Guia de instalação
IEC PELV/NEC® Class 2
30 mA
24 V

Leia com atenção

Conteúdo

Visão geral........................................................................................ 2
Exemplo de fiação do grupo de alimentação..................................... 3Fiação/Instalação.............................................................................. 4
Montagem........................................................................................ 7
Solução de problemas...................................................................... 8
Português

Para programação, consulte o Guia de programação
de acessórios de parede QS (P/N 0301639)
em www.lutron.com/qs®

Os circuitos dos acessórios de parede são classificados como circuitos IEC PELV/
NEC® Class 2. Como circuitos Class 2, eles devem atender aos requisitos
da NFPA® 70, Código Nacional de Eletricidade - National Electrical Code® (NEC®).
Como circuitos PELV, eles devem atender aos requisitos da IEC 60364-4-41,
VDE 0100 Parte 410, BS7671:1992 e outras normas equivalentes. Ao instalare conectar os acessórios de parede, siga todas as normas de fiação nacionais
e/ou locais aplicáveis. Circuitos externos conectados à entrada de fechamentode contato, saída e a outros terminais de comunicação do acessório de parededevem ser fornecidos por um fabricante de produtos Class 2 ou devem atender aos
requisitos dos circuitos PELV, conforme seu país.

Exemplo de fiação do grupo de alimentação

Modelos de acessórios de parede QS Visão geral

TecladosseeTouch®
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BD
Teclados
Signature SeriesTM
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

TecladosseeTouch® Internacional
QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

TecladosArchitraveTM
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

Limites da linha QS• A linha de comunicação QS conectada pode ter
até 100 dispositivos e 100 zonas. Cada acessório
de parede seeTouch® é considerado como
1 dispositivo e 0 zona.
• Os acessórios de parede QS usam 1 unidadede distribuição de energia (PDU) na linha QS.
Consulte a apresentação da especificação das
Unidades de distribuição de energia da linha
QS (Lutron PN 369405) e o diagrama no versoda página para obter mais informações sobre as
unidades de distribuição de energia.

•
•
•
•

Notas
• Leia todas as instruções de instalação atentamente
antes de iniciar a instalação.
• A Lutron recomenda que os acessórios de parede
sejam instalados por um eletricista qualificado.
• Use apenas um pano úmido com águamorna e sabão neutro para limpar as frentes(sem produtos químicos).
Instruções de instalação

• Os acessórios de parede QS podem ser
programados para controlar luzes, cortinas ou osdois simultaneamente.
• Acessórios de parede QS não programados(original), cortinas Sivoia® QS, unidades decontrole GRAFIK Eye® QS e unidades Energi
Savr NodeTM trabalharão juntos até que sejam
programados de outra forma.
• As entradas de fechamento de contato permitem
a operação com sensores de ocupação/vazio,
divisão e outros mais.

•
•
•
•

Componentes compatíveis
Os seguintes dispositivos são compatíveis com
a linha QS. Para obter mais informações sobrecada um deles, acesse www.lutron.com/qs
Unidades de controle GRAFIK Eye® QS
Acessórios de parede QS
Cortinas Sivoia® QS
Interfaces QS (fechamento de contato,
Ethernet/RS232)
Sistema Quantum®
Unidades Energi Savr NodeTM
Módulo do sensor QS
Chave seletora QS

Na linha QS, existem dispositivos que fornecem energia e dispositivos que consomem energia.
Cada dispositivo possui um número específico de unidades de distribuição de energia (PDUs)
que ele fornece ou consome. Um grupo de alimentação consiste em um dispositivo que fornece
energia e um ou mais dispositivos que consomem energia; cada grupo de alimentação podeter somente um dispositivo de fornecimento de energia. Consulte a especificação das Unidadesde distribuição de energia da linha QS (Lutron P/N 369405) para mais informações relacionadas às PDUs.
Dentro dos grupos de alimentação na linha QS, conecte todos os 4 terminais (1, 2, 3 e 4), mostrados pela
letra A no diagrama. Entre os grupos de alimentação na linha QS que fornecem energia, conecte apenasos terminais 1, 3 e 4 (NÃO o terminal 2), mostrados pela letra B no diagrama.
A fiação pode ser em série ou em T.

A
LUTRON

Unidade de controle
GRAFIK Eye® QSFornece PDUs
B

Cópia do usuário

A

LUTRONInterfaces de controle
Consomem PDUs

(Não conecteo terminal 2: 24 V )Acessórios de parede
Consomem PDUs

LUTRON

LUTRON

LUTRON

B

B

Unidade Energi
Savr NodeTM
Fornece PDUs

(Não conecteo terminal 2: 24 V)

Grupo de Alimentação 3

A

Fonte dealimentação QS
Fornece PDUs

Cópia do usuário

Conecte todos os
4 terminais dentro
de um grupo
de alimentação:1: Comum2: 24 V3 e 4: Dados

Grupo de Alimentação 2

A

Conecte apenas
3 terminais
entre os gruposde alimentação:1: Comum3 e 4: DadosNão conecteo terminal
2: 24 V

LUTRON

Módulo do sensor QS com sensor de ocupação
Consomem PDUs

B(Não conecteo terminal 2: 24 V )2Grupo de Alimentação 1

O painel Quantum®
fornece PDUs
3

Instruções de instalação

153 a 610 m/500 a 2 000 pés

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON(2) 4,0 mm2

LUTRON

LUTRONC
B

seeTouch® InternacionalFiação do controle
IEC PELV/
NEC® Class 2

LUTRON

LUTRON(2) 4,0 mm2(12 AWG)

LUTRONA

LUTRON

LUTRON

LUTRON

Signature SeriesTM, ArchitraveTMFiação do controle IEC PELV/
NEC® Class 2: (2) 1,0 mm2 (18 AWG)
1: Comum2: 24 VP/N do cabo Lutron

Alimentação (terminais
1 e 2)
2
1 par de 4,0 mm (12 AWG)

4

1

GRX-CBL-346S (não plenum)
GRX-PCBL-346S (plenum)

Dreno

Signature SeriesTM, ArchitraveTM(2) 4,0 mm2(12 AWG)(2) 4,0 mm2(12 AWG)

Linha de dados
2

3

3
4

4

Linha de dados: (1) par torcido eblindado, 0,5 mm2 (22 AWG)
3: MUX
4: MUX
Cópia do usuário

Cópia do usuárioFiação do controle IEC PELV/
NEC® Class 2

1

2

GRX-CBL-46L (não plenum)
GRX-PCBL-46L (plenum)

A

Comprimento da ponta descascada

Linha dedadosFiação do controle IEC PELV/
NEC® Class 2: (2) 1,0 mm2 (18 AWG)
1: Comum2: 24 V

LUTRON

Dados (terminais 23 e 4)
1 par de 0,5 mm (22 AWG), torcido e blindado

Instruções de instalação

1

1

LUTRON

Dados (terminais 23 e 4)
1 par de 0,5 mm (22 AWG), torcido e blindado
153 a 610 m(500 a 2 000 pés)2

(12 AWG)

LUTRON

2

B

Alimentação (terminais
1 e 2)
2
1 par de 1,0 mm (18 AWG)

3

C

Inferior a 153 m(500 pés)4Fiação docontrole IEC
PELV/NEC® Class 2

3

LUTRON

Tamanhos dos fios (verifique a compatibilidade em sua área)Bitola do fio

Linha de dados
Dreno

4

Em T

10 mm (4 pol)Comprimento da fiação
da linha QS

seeTouch®, seeTouch® Internacionale
Linha de dados: (1) par torcido eblindado, 0,5 mm2 (22 AWG)
3: MUX
4: MUX
Dreno:

LUTRON:

LUTRON

30 mA 30 mA

Em série

OFF OFF OFF

ON
ON

LUTRON

LUTRON

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

LUTRON

LUTRON

1. Desligue a alimentação
de energia. Desligue
a alimentação de energia
no quadro do disjuntor/
MCB (ou retire o fusível).
2. Instale caixas de embutir. Certifique-se dotamanho correto. Consulte a “Montagem” para
obter mais detalhes.
3. Prepare os acessórios de parede.
Remova o espelho frontal e deixe separado.
4. Prepare os fios. Remova o isolante dos fios
deixando uma ponta de 10 mm (4 pol) descascada.
ON

seeTouch®

Configuração de fiação permitida
LUTRON< 153 m/500 pés

1Aviso! Risco de choque. Risco deferimentos graves ou morte. Sempre
desligue a alimentação no disjuntor/MCB
ou remova o fusível principal da linha
de alimentação antes de fazer qualquer trabalho.

•

Conecte os fios de tamanho apropriado aos
terminais 1 e 2 para alimentação, de acôrdo
com o tamanho de sua linha (consulte tabela noverso).

2••Fiação da linha QS
Conecte pares de fios de 0,5 mm2 (22 AWG),
torcidos e blindados aos terminais 3 e 4
do conector de linha de controle do acessório
de parede. A blindagem (dreno) do par de fios
torcidos deve ser conectada junto conforme
exibido, mas não conecte a blindagem ao terra ou
ao acessório de parede e não permita queela contate a caixa aterrada.

3•

Consulte o guia de instalação do sistema e os desenhos
Lutron para conhecer as limitações e restrições de fiação
do cabo de alimentação de energia e cabo de dados(linha de controle).
Conecte o acessório de parede à linha de controle dentro
da caixa de embutir do acessório de parede ou em uma
caixa de derivação (fornecida por outro fabricante).
Use o conector especificado pelas normas locais.

A fiação da linha de controle não deve passar pelos
mesmos conduítes em que passa a alimentação da rede.
O fio blindado/dreno deve ser mantido através de toda
a linha de controle. Não conecte o blindado ao terraou permita o contato com a caixa de embutir aterrada.
Não conecte a alimentação de alta voltagem aos terminais
de baixa voltagem. A instalação inadequada pode causar
ferimentos pessoais ou danos ao dispositivo ou a outros
equipamentos.

4

•

•

AC N
AC N
099 942 971 099 942 971

Fiação/Instalação

Dreno

5

Linha de dados: (1) par torcido
e blindado, 0,5 mm2 (22 AWG)
3: MUX
4: MUX

DrenoFiação do controle IEC PELV/
NEC® Class 2: (2) 1,0 mm2 (18 AWG)
1: Comum2: 24 V
Instruções de instalação

:

seeTouch® Internacional

Parafusosde instalação

Parafusos
do adaptador

Caixa
de embutir

ControleBotõesArchitraveTM
ControleBotõesParafusos de instalação
Adaptador

Parafusos de instalação
Parafusos do
adaptadorCaixa
de embutir

ArchitraveTM(3) 1,0 mm2(18 AWG)
Entrada 1
Entrada 2
Comum

seeTouch® Internacional

A

3

B

2

C

1

Espelho frontal
Comum
Entrada 2
Entrada 1

Signature SeriesTM

ABC(3) 1,0 mm2(18 AWG)
Entrada 1
Entrada 2
Comum

Cópia do usuário

Controle
Espelhofrontal

AdaptadorBotõesEspelho frontal

Tamanho da caixa deembutir(altura x largura x profundidade)seeTouch®

95 x 55 x 70 mm
3,7 x 2,2 x 2,75 pol
75 x 75 x 35 mm
3 x 3 x 1,4 pol
113 x 39.x 71 mm
4,4 x 1,5 x 2,8 pol
112 x 32 x 70 mm
4,4 x 1,25 x 2,75 polArchitraveTM
6

Caixa
de embutir

Controle

Tipo deacessório deparedeseeTouch®
Internacional
Signature
SeriesTM
Instruções de instalação

Parafusos
Parafusos
do adaptador deinstalação

Adaptador(3) 1,0 mm2(18 AWG)

Comum
Entrada 2
Entrada 1

A
BC

Signature SeriesTM

seeTouch®

Caixa
de embutir

4(3) 1,0 mm2(18 AWG)

Montagem
Monte e alinhe cuidadosamente o acessório
de parede, conforme exibido. Fixe os parafusos
superior e inferior dentro do controle e da caixa
de embutir. Recoloque o adaptador (nas versões
embutidas; parafuse no controle), conjunto
de botões e espelho frontal na ordem exibida.

EspelhofrontalAC N
099 942 971

seeTouch®

Nota: Se um acessório de parede possuir
dispositivos conectados a ele atravésde entradas do fechamento de contato,a CCI1 “pressionará” o botão superior
e a CCI2 “pressionará” o botão inferior.
Para alterar este comportamento,
consulte a Nota de aplicação 428(Modo de programação avançada
seeTouch® ) em www.lutron.com.
Exceção: Em um acessório de parede
2-botões configurado para a funcionalidade
divisão, pânico ou sequenciamento,a ação do fechamento CCI1 seguiráo botão superior e ação de abertura
seguirá o botão inferior.

CO O P E R S BURG , P A 18036 US A

30 mA

Conectando a entrada do fechamentode contato (CCI)
As entradas do fechamento de contato devem serde fechamento de contato seco, no estado sólido,
coletor aberto, ou uma saída ativa baixa (NPN)/
ativa alta (PNP).
• O coletor aberto NPN ou a voltagem ativa baixa no
estado deve ter menos de 2 V e dissipar 3,0 mA.
• O coletor aberto PNP ou a voltagem ativa alta no
estado deve ser maior que 12 V e originar 3,0 mA.
• As saídas devem ficar nos estados fechadoou aberto por no mínimo 60 mseg para que
sejam reconhecidas pelo acessório de parede.
Se houver alguma dúvida quanto à compatibilidade
do dispositivo de terceiros que está gerando
essas saídas em relação a estas especificações,contate o fabricante.

Cópia do usuário

Lutron P/N241519241683
WBOX-SA1-Q1
241399
7

Alimentação
LIGUE o disjuntor do controle ou recoloqueo fusível.
A instalação está concluída
Para as funções de programação, consulteo Guia de programação de acessórios de parede
QS em www.lutron.com/qs.
Instruções de instalação

Solução de problemas: Funcionalidade do LED

Solução de problemas: Funções da cortina

Comportamento do LED

Sintoma

Causas possíveis

SoluçãoA EDU (Electronic Drive Unit - unidadede acionamento eletrônico da cortina)
não se move

A EDU não está alimentada

Verifique a alimentação da EDU

O tecido da cortina está preso em algo

Verifique e solte o tecido da cortina

A EDU não está atribuída a um teclado

Atribua a EDU a um teclado

As pré-programações não foram definidas
corretamente

Tente usando os botões aumentar/diminuir
no teclado

Os limites não foram definidos corretamente

Defina os limites corretamente

Significado e Solução

Todos os tipos de teclado“Cascata reversa”
Os LEDs começam a acender da parte inferior e continuam atéque todos estejam acesos; então os LEDs apagam começando
da parte inferior até que todos estejam apagados. O ciclo então
se repete.

Não é possível a comunicação com a linha QS, ou sozinho na linha QS.
Verifique a fiação da linha.

Não há resposta (feedback) do LED, mesmo quando um botão
é pressionado.

Não há energia no acessório de parede. Verifique a fiação de alimentação.

Todos os LEDs estão piscando rapidamente.

Outro dispositivo na linha Q está em modo de programação ou atribuição.
Retire este dispositivo do modo de programação ou, no teclado,
entre e depois saia do modo de programação. Isto desativará o modode programação de todos os dispositivos.
O acessório de parede está no modo de programação avançado.
Pressione e segure os botões superior e inferior por 3 segundos para sair.

A EDU (unidade de acionamento
eletrônico da cortina) não abreou fecha totalmente

O tecido da cortina está preso em algo

Verifique e solte o tecido da cortina

As cortinas se movem para direções
opostas quando os botões aumentar/
diminuir são pressionados

Os limites de abertura e fechamento foram
invertidos

Defina os limites corretamente

Os LEDs do teclado estão
desligados e o teclado
não controla nenhuma cortina

O teclado está sem alimentação de energia

Verifique e conecte a alimentação ao teclado

Os LEDs do teclado estão ligados,mas o teclado não controla
nenhuma cortina

Todas as pré-programações estão definidas
na mesma altura

Tente usando os botões aumentar/diminuir
no teclado

A linha de comunicação não está conectada à EDU

Verifique e conecte a fiação da EDU

A EDU teve a atribuição removida do teclado

Reatribua a EDU ao teclado

Os limites de abertura e fechamento são os mesmos

Defina os limites corretamente

A EDU teve a atribuição removida do teclado

Reatribua a EDU ao teclado

Todas as pré-programações estão definidas
na mesma altura

Tente usando os botões aumentar/diminuir
no teclado

A EDU não está conectada corretamente

Verifique e reconecte a EDU

O teclado não está conectado corretamente

Verifique e conecte o teclado novamente

As EDUs estão atribuídas a um teclado
em outro ambiente

Atribua a EDU ao teclado correto

Teclados da cortina
LEDs superior e inferior estão piscando juntos.

O teclado está no modo de atribuição. Pressione e segure os botões
superior e inferior por 3 segundos para sair.

Todos os LEDs piscam 3 vezes, pausam, e depois repetem a ação.

O teclado está no modo de atribuição ou de definição de limite e não podeencontrar ou se comunicar com qualquer cortina atribuída à linha QS.
Verifique a fiação da cortina.
Aguarde 60 segundos, e o teclado voltará ao modo normal automaticamente(sem intervenção do usuário). Ou, pressione e segure os botões superior
e inferior por 3 segundos para sair do modo imediatamente.

Os LEDs superior e inferior se acendem em padrões alternados(o LED superior acende, depois apaga, então o inferior acende,depois apaga, e o ciclo se repete).

O teclado ou outro dispositivo na linha está no modo de definição de limite.
Pressione e segure os botões superior e inferior por 3 segundos para sair.

Os LEDs superior e inferior piscam lentamente, e um outro LED
pisca rapidamente.

O teclado está no modo de ajuste de pré-programação. Pressione e segure
os botões superior e inferior para sair.

O teclado não opera todas as cortinas
às quais está atribuído

Outros teclados
Um único LED está piscando.

O teclado está configurado para alternância de zona, divisão, ou alternância
de cortina e está no modo de programação. Pressione e segure os botões
superior e inferior para sair.

“Cascata”
Os LEDs acendem e apagam em sequência da parte superiorpara a parte inferior.

O teclado está configurado para cena, pânico, sequência, sintonia fina,
ou travamento de cena/zona, e está no modo de programação.
Pressione e segure os botões superior e inferior para sair.

Instruções de instalação

8

Cópia do usuário

As cortinas em uma salase movimentam sozinhas
Cópia do usuário

9

Instruções de instalação

Solução de problemasSintoma

Causas possíveis

Não há comunicação com a unidade de controle GRAFIK Eye®
ou com a unidade Energi Savr NodeTM.

Fiação errada ou conexão frouxa na linhas de dados 3 e 4 da linha de controle.

Os botões do acessório de parede não funcionam;
os LEDs não rastreiam; botões do acessório de paredenão funcionam como desejado.

O acessório de parede está conectado de forma incorreta.

O acessório de parede não foi programado ou foi programado incorretamente.

O acessório de parede não está alimentado.
O acessório de parede não está programado para o dispositivo correto.
O acessório de parede não foi programado ou foi programado incorretamente.

Os LEDs não acendem.

Fiação errada ou conexão frouxa no(s) acessório(s) de parede ou processador
nalinha de controle comum e conexões de alimentação 1 e 2.
O acessório de parede foi programado incorretamente.

As entradas de fechamento de contato ou a entrada do sensor
não produz o resultado desejado no sistema.

Fiação errada ou conexão frouxa no sensor do acessório de parede/conector CCI.
O acessório de parede não foi programado ou foi programado incorretamente.

Internet: www.lutron.com
E-mail: product@lutron.com
SEDES INTERNACIONAIS
EUA
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TEL +1.610.282.3800
FAX +1.610.282.1243
Ligue grátis 1.888.LUTRON1
Suporte técnico 1.800.523.9466
América do Norte e do Sul
Linhas de assistência técnica
EUA, Canadá, Caribe: 1.800.523.9466
México: +1.888.235.2910
América Central / do Sul +1.610.282.6701

SEDES EUROPÉIASReino Unido
Lutron EA Ltd.
6 Sovereign Close
Londres
E1W 3JF Reino Unido
TEL +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
LIGUE GRÁTIS (UK) 0800.282.107
Suporte técnico +44.(0)20.7680.4481

Garantia: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electrical Code, NEC e NFPA são marcas comerciais registradas da National Fire Protection Association,Inc., Quincy, Massachusetts.
Lutron, , Sivoia, seeTouch, Quantum, e GRAFIK Eye são marcas comerciais registradas e Energi Savr Node,Architrave, e Signature Series são marcas comerciais da Lutron Electronics Co., Inc.
© 2012 Lutron Electronics Co., Inc.

SEDES ASIÁTICAS
Cingapura
Lutron GL Ltd.
15 Hoe Chiang Road
07-03 Euro Asia Centre
Cingapura 089316
TEL +65.6220.4666
FAX +65.6220.4333
Linhas de Assistência Técnica na ÁsiaNorte da China: 10.800.712.1536
Sul da China: 10.800.120.1536
Hong Kong: 800.901.849
Indonésia: 001.803.011.3994
Japão: +81.3.5575.8411
Macau: 0800.401
Cingapura: 800.120.4491
Taiwan: 00.801.137.737
Tailândia: 001.800.120.665853
Outros países: +65.6220.4666®

®

Lutron Electronics Co., Inc.
P/N 0301604 Rev. B 10/2012

Tastierini QS
Guida di installazione
IEC PELV/NEC® Class 2
30 mA
24 V

Leggere con attenzione

IndiceInformazioni generali........................................................................ 2
Esempio di collegamento dell’alimentazione..................................... 3
Cablaggio/Installazione..................................................................... 4
Montaggio........................................................................................ 7
Individuazione ed eliminazione dei guasti.......................................... 8®

I circuiti elettrici dei tastierini sono classificati come IEC PELV/NEC® Class 2.
I circuiti Classe 2 sono conformi alla norma NFPA® 70, National Electrical Code® (NEC®).
I circuiti PELV sono conformi ai requisiti della normativa IEC 60364-4-41, VDE 0100
Parte 410, BS7671:1992 e altri standard equivalenti. Per l’installazione di questo
tipo di tastierini, occorre osservare le normative vigenti nazionali o locali sul cablaggio.
I circuiti esterni collegati a ingressi, uscite, e altri terminali di comunicazione dei tastierini,devono essere alimentati da sistemi compatibili con i requisiti Classe 2 o PELV,
secondo quanto previsto dalla normativa in vigore nel proprio paese.

Italiano

Per la programmazione, vedere la Guida di programmazionedel tastierino QS (codice 0301639) disponibile presso il
sito www.lutron.com/qs

Informazioni generali

Modelli di tastierini QS

Tastierini
seeTouch®
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BD
Tastierini
Signature SeriesTM
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD

Tastierini seeTouch®
Internazionale
QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

Limiti del link QS• Il link di comunicazione cablato QS è limitato a
100 dispositivi e 100 zone. Ai fini di questo limite,ogni tastierino QS vale come 1 dispositivo e 0zone.
• Ogni tastierino QS utilizza 1 unità di alimentazione(PDU) sul link QS. Per maggiori informazioni sulle
capacità di alimentazione del link QS, consultare
la scheda tecnica (codice Lutron 369405) e lo
schema alla pagina a fianco.

Tastierini
ArchitraveTM
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•
•
•
•
•

Note
• Leggere attentamente le istruzioni prima di effettuarel’installazione.
• Lutron raccomanda che l’installazione dei tastierini sia
effettuata da un tecnico qualificato.
• Per pulire il coperchio frontale utilizzare unicamente acqua
calda e sapone delicato (non applicare prodotti chimici).
Istruzioni per l’installazione

Esempio di collegamento dell’alimentazione• I tastierini QS possono essere programmati percontrollare luci, tende o entrambe.
• Non programmati (con impostazioni di fabbrica)
tastierini QS, tende Sivoia® QS, centraline
GRAFIK Eye® QS e unità Energi Savr NodeTM
comunicano tutti uno con l’altro finché non
programmati diversamente.
• I contatti di ingresso consentono di operare con
sensori di presenza, partizionamenti e molto altro.

Componenti compatibili
I seguenti dispositivi sono compatibili con il link QS.
Per ulteriori informazioni su di essi, consultare il sito
www.lutron.com/qs
Centraline GRAFIK Eye® QS
Tastierini QS
Tende motorizzate Sivoia® QS
Interfacce QS (a contatti, Ethernet/RS232)
Sistema Quantum®
Unità Energi Savr NodeTM
Modulo sensore QS
Interruttore a chiave QS

Il link QS comprende dispositivi in grado di alimentarne altri e dispositivi che assorbono energia. Ogni dispositivo
può essere descritto facendo riferimento a un numero specifico di PDU (unità alimentate direttamente) a cui fornisce
alimentazione elettrica o la “consuma”. Un gruppo di alimentazione è costituito da un dispositivo che fornisce
alimentazione e uno o più dispositivi che assorbono energia per funzionare; in ogni gruppo di alimentazione,l’alimentazione può essere fornita da un solo dispositivo. Per maggiori informazioni sulle unità alimentate direttamente(PDU), consultare la scheda tecnica QS Link Power Draw Units (codice Lutron 369405).
All’interno dei gruppi di alimentazione sul link QS, collegare i 4 morsetti (1, 2, 3 e 4) indicati dalla lettera A nello schema.
Tra i dispositivi sul link QS che erogano tensione, collegare solo i morsetti 1, 3 e 4 (NON il morsetto 2), indicati dalla
lettera B nello schema.

Il cablaggio puó essere realizzato in serie (daisy-chain) o in serie-parallelo.

A

Gruppo di alimentazione 1

LUTRON

Centralina GRAFIK
Eye® QS
Alimenta le PDU

B(Non collegare il morsetto
2: 24 V )Tastierini
Consuma PDU

B
LUTRON

Unità Energi Savr NodeTM
Alimenta le PDU

LUTRONB
Gruppo di alimentazione 3A

Non collegare
il morsetto
2: 24 V

LUTRON(Non collegare il morsetto
2: 24 V )Copia per l’utilizzatore

Collegare solo 3
morsetti tra gruppi
di alimentazione:
1: Comune
3 e 4: Dati

(Non collegare il morsetto
2: 24 V )Modulo sensore QS e sensore di presenza
Consuma PDU

B
Copia per l’utilizzatore

LUTRON

Collegare tutti e 4
i morsetti all’interno
di un gruppo dialimentazione:
1: Comune
2: 24 V3 e 4: Dati

Gruppo di alimentazione 2

A

Alimentatore QS
Alimenta le PDU

2A

LUTRONInterfacce
di controllo
Consuma PDU

Il quadro Quantum®
alimenta le PDU
3

Istruzioni per l’installazione

Collegamento in serie (daisy-chain)
LUTRON

LUTRON

LUTRON

LUTRON

Collegamento inserie-parallelo

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

Sezione del filo

Codice per il cavo Lutron

Dati (morsetti 3 e 4)2
1 coppia intrecciata e schermata da 0,5 mm (22 AWG)
153 m a 610 m

Alimentazione (morsetti
1 e 2)
2
1 coppia da 4,0 mm (12 AWG)
Dati (morsetti 3 e 4)2.
1 coppia intrecciata e schermata da 0,5 mm (22 AWG)

Istruzioni per l’installazione

4

Link
dati

:

A

A

Dimensione dei cavi (verificare la compatibilità nella vostra area)

Alimentazione (morsetti
1 e 2)
2
1 coppia da 1,0 mm (18 AWG)

B

seeTouch® Internazionale
Cablaggio di comando
IEC PELV/
NEC® Class 2

Massa

LUTRON

10 mm
Lunghezza max. link QS

C

B

LUTRON

1

C

LUTRON

2

1

Cablaggio di comando IEC PELV/
NEC® Class 2(2) 1,0 mm2 (18 AWG)
1: Comune
2: 24 V

LUTRON< 153 m2(2) 4,0 mm2(12 AWG)

LUTRON

Lunghezza di filo
messo a nudo

3

Cablaggio dicomando
IEC PELV/
NEC® Class 2

LUTRON

LUTRON

4. Preparare i fili. Togliere il rivestimento isolante
in modo da mettere a nudo 10 mm di filo.

43(2) 4,0 mm2(12 AWG)

LUTRON

LUTRON

2. Montare la scatola a muro. Assicurarsi che ilformato corretto. Per i dettagli consultare “Montaggio”.
3. Preparare i tastierini. Togliere la placca e riporlada parte.

LUTRON

LUTRON

Link dati
Massa:

LUTRON

30 mA 30 mA

LUTRON

seeTouch®, seeTouch® Internazionale
Link dati: (1) coppia di fili
intrecciata, schermata
0,5 mm2 (22 AWG)
3: MUX
Massa
4: MUX
4

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

LUTRON

LUTRON

seeTouch®

153 a 610 m

AC N
AC N
099 942 971 099 942 971

LUTRON

LUTRON<153 m1

Configurazioni di cablaggio consentite
LUTRONOFF OFF OFF

ON
ON

1. Togliere tensione. Toglieretensione all’interruttore
automatico/MCB (o togliere
il fusibile).

ON

Avvertenza! Pericolo di folgorazione.
Può causare gravi lesioni o morte.
Prima di effettuare qualsiasi intervento,
portare sempre l’interruttore automatico su
OFF o togliere il fusibile principale dalla linea
di alimentazione.

Collegare fili di dimensioni adeguate ai morsetti 1 e 2
per l’alimentazione, in base alla lunghezza del proprio
link (vedere la tabella nella pagina a fianco).

2• Per quanto concerne le restrizioni e le limitazioni relative
al cavo di alimentazione e al cablaggio delle linee dati(Control Link), consultare la guida all’installazionedel sistema e i disegni applicativi Lutron.
• Collegare il tastierino al link di comando all’internodella scatola a muro del tastierino o in una scatoladi derivazione (non fornita).
• Utilizzare il morsetto a cappuccio richiesto dalla
normativa locale.

Cablaggio del link QS
Collegare due fili intrecciati e schermati con sezione
0,5 mm2 (22 AWG) ai morsetti 3 e 4 del connettoredel link di comando del tastierino. La massa dei
fili intrecciati deve essere collegata insieme, comemostrato. Tuttavia, non è consentito il collegamentodella massa alla messa a terra o al tastierino, né ilcontatto con la scatola a muro di messa a terra.

3• Il cablaggio del circuito di controllo non deve essere
inserito nella stessa canalina contenente cavi a tensione
di linea.
• Il filo di massa deve essere presente lungo tutto il link dicomando. Non collegare il filo di massa a terra e nonconsentire il contatto con la scatola a muro di messa aterra.
• Non collegare alimentazione ad alta tensione nei
morsetti a bassa tensione. Un cablaggio scorretto può
provocare danni alle persone, ai dispositivi e ad altri
dispositivi.

4

Cablaggio/Installazione

GRX-CBL-346S (non plenum)
GRX-PCBL-346S (plenum)

Signature SeriesTM, ArchitraveTM
Cablaggio di comando IEC PELV/
NEC® Class 2(2) 1,0 mm2 (18 AWG)
1: Comune
2: 24 V
1

Signature SeriesTM, ArchitraveTM(2) 4,0 mm2(12 AWG)(2) 4,0 mm2(12 AWG)

2

Cablaggio di comando
IEC PELV/NEC® Class 2
Link dati

1
2
3
4

Massa

3
4

GRX-CBL-46L (non plenum)
GRX-PCBL-46L (plenum)

Copia per l’utilizzatore

Link dati: (1) coppia di fili
intrecciata, schermata
0,5 mm2 (22 AWG)
3: MUX
4: MUX
Copia per l’utilizzatore

Link dati: (1) coppia di fili
intrecciata, schermata
0,5 mm2 (22 AWG)
3: MUX
4: MUX

Massa

5

Cablaggio di comando IEC PELV/
NEC® Class 2 (2)1,0 mm2 (18 AWG)
1: Comune
2: 24 V
Istruzioni per l’installazione

seeTouch®

:Montaggio
Montare con attenzione e allineare il tastierino comemostrato. Avvitare la vite inferiore e superiore nel
dispositivo e nella scatola. Rimettere in posizionel’adattatore (per le versioni con inserto, avvitare
al dispositivo), il gruppo pulsanti e la placca,nell’ordine mostrato.
seeTouch®
Viti di fissaggio

PlaccaViti di fissaggio

Placca4

A

3

Viti di fissaggio

B

2

1

seeTouch® Internazionale
Viti dell’adattatore
Scatolaa muroA
B
C

Istruzioni per l’installazione

Dispositivo

ArchitraveTM(3) 1,0 mm2(18 AWG)
A
B
C

6Ingresso 1
Ingresso 2
ComuneCopia per l’utilizzatore

Dispositivo
PlaccaAdattatore

Pulsanti(3) 1,0 mm2(18 AWG)

Ingresso 1
Ingresso 2
ComunePulsanti

Dispositivo

ArchitraveTM

Adattatore

Scatolaa muroSignature SeriesTM

Viti difissaggio

Viti dell’adattatore

Dispositivo PulsantiC

ComuneIngresso 2
Ingresso 1

Viti
dell’adattatore

Adattatore(3) 1,0 mm2(18 AWG)

ComuneIngresso 2
Ingresso 1

Signature SeriesTM

Scatolaa muroScatolaa muroseeTouch® Internazionale

AC N
099 942 971(3) 1,0 mm2(18 AWG)

Nota: Se un tastierino ha dispositivi collegati,
un segnale sull’ingresso CCI1 equivale
alla pressione del pulsante superiore mentre
un segnale sull’ingresso CCI2 alla pressionedel pulsante inferiore. Per cambiare questo
comportamento, consultare la nota applicativa
428 (Modalità programmazione avanzatadel tastierino seeTouch® ), disponibile presso
il sito www.lutron.com.
Eccezione: sul tastierino a 2 pulsanti configurato
per funzionalità di partizionamenti, antipanicoo sequenza di scene, l’azione di chiusura
dell’ingresso CCI1 equivale alla pressionedel pulsante superiore mentre l’apertura allapressione del pulsante inferiore.

CO O P E R S BURG , P A 18036 US A

30 mA

Cablaggio dell’ingresso a contatti (CCI)
Gli ingressi a contatti devono essere a contatti puliti,
a stato solido, a collettore aperto o uscite attivo basso(NPN)/attivo alto (PNP).
• Nel caso di collettore aperto NPN o collegamento attivo
basso, la tensione allo stato di conduzione deve essere
inferiore a 2 V (con un assorbimento di 3,0 mA).
• Nel caso di collettore aperto PNP o attivo alto,la tensione allo stato di conduzione deve essere
superiore a 12 V (con un’erogazione di 3,0 mA).
• Le uscite devono rimanere chiuse o aperte per almeno
60 msec affinché il segnale sia riconosciuto
dal tastierino.
In caso di domande relative alla compatibilità
di dispositivi prodotti da terzi, con il tipo di uscitarichiesto, contattare il produttore.

PlaccaTipo ditastierino

Dim. Scatola(altezza x larghezza x profondità)

Codice Lutron

seeTouch®
seeTouch®
Internazionale
Signature SeriesTM
ArchitraveTM

95 x 55 x 70 mm

24151975 x 75 x 35 mm

241683113 x 39.x 71 mm
112 x 32 x 70 mm

WBOX-SA1-Q1
241399

Copia per l’utilizzatore

7

Accensione
Portare l’interruttore automatico in posizione ONo rimettere in posizione il fusibile principale.
Installazione completata
Per la programmazione, vedere la Guida alla
programmazione del tastierino QS disponibile presso il
sito www.lutron.com/qs.
istruzioni d’installazione

Individuazione ed eliminazione dei guasti: Funzione LED

Individuazione ed eliminazione dei guasti: Funzioni per tendeComportamento del LED

Significato e misura correttiva

Problema

Possibili cause

AzioneL’EDU non è alimentata.

Verificare l’alimentazione dell’EDU“Cascata inversa”
I LED si accendono a partire dal basso, finché tutti non sonoaccesi, quindi si spengono, a partire dal basso, finché tutti
non sono spenti. Quindi il ciclo si ripete.

Impossibile comunicare sul link QS; o nessun altro dispositivo è presente
sul link QS. Controllare il cablaggio del link.

L’EDU (unità di azionamento
elettronica del sistema di oscuramento
finestre) non si sposta

Il telo della tenda è rimasto intrappolato in qualcheostacolo

Controllare e liberare il telo della tenda dall’ostacolo

L’EDU non è assegnata ad un tastierino

Assegnare l’EDU a un tastierino

I LED non mostrano alcuna reazione, anche quando si preme
un pulsante.

Tastierino non alimentato. Controllare il cablaggio di alimentazione.

I livelli predefiniti non sono stati impostati
correttamente

Provare ad usare i pulsanti alza e abbassadel tastierino

I limiti non sono stati impostati correttamente

Impostare correttamente i limiti

Il telo della tenda è rimasto intrappolato in qualcheostacolo

Controllare e liberare il telo della tenda dall’ostacolo

La tenda si sposta nella direzione
opposta quando si premono i pulsantialza/abbassa

I limiti di apertura e chiusura sono stati invertiti

Impostare correttamente i limiti

I LED dei tastierini sono spenti, ma
il tastierino non comanda nessuna
tenda

Il tastierino non è alimentato

Verificare e collegare l’alimentazione al tastierino

I LED del tastierino sono accesi,
ma il tastierino non comanda
nessuna tenda

Tutti i livelli predefiniti sono stati impostati alla
stessa altezza

Provare ad usare i pulsanti alza e abbassadel tastierino

Il link di comunicazione non è collegato all’EDU

Verificare e collegare il link EDU

L’assegnazione dell’EDU al tastierino è stataannullata

Riassegnare l’EDU al tastierino

I limiti di apertura e chiusura sono gli stessi

Impostare correttamente i limiti

L’assegnazione dell’EDU al tastierino è stata annullata

Riassegnare l’EDU al tastierino

Tutti i livelli predefiniti sono stati impostatialla stessa altezza

Provare ad usare i pulsanti alza e abbassadel tastierino

L’EDU non è collegata correttamente

Verificare i collegamenti e ricollegare l’EDU

Il tastierino non è collegato correttamente

Verificare i collegamenti e ricollegare il tastierino

Le EDU sono assegnate a un tastierino in un altro
ambiente

Riassegnare l’EDU al tastierino corretto

Tutti i tipi di tastierini

Tutti i LED lampeggiano rapidamente.

Un altro dispositivo sul link QS è in modalità programmazione o assegnazione.
Fare uscire questo dispositivo dalla modalità programmazione o portare
il tastierino in modalità programmazione e quindi uscire da tale modalità:
questa azione determinerà l’uscita di tutti i dispositivi dalla modalità
programmazione.
Il tastierino si trova in modalità programmazione avanzata. Tenere premuto
i pulsanti superiore e inferiore per 3 secondi per uscire dalla modalità
programmazione avanzata.

L’EDU non apre o chiude
completamente

Tastierini per tende motorizzate
I LED superiore e inferiore lampeggeranno contemporaneamente.

Il tastierino si trova in modalità assegnazione. Tenere premuto i pulsantisuperiore e inferiore per 3 secondi per uscire dalla modalità assegnazione.

Tutti i LED lampeggiano 3 volte seguite da una pausa,
quindi la sequenza si ripete.

Il tastierino è in modalità assegnazione o impostazione limiti e non riesce
a rilevare o a comunicare con le tende motorizzate assegnate al link QS.
Controllare il cablaggio delle tende motorizzate.
Attendere 60 secondi e il tastierino tornerà automaticamente alla modalità
normale (senza intervento dell’utente). In alternativa, premere i pulsanti superiore
e inferiore per 3 secondi per uscire immediatamente da tale modalità.

I LED superiore e inferiore si accendo secondo uno schema
alternato (prima si accende e si spegne il LED superiore, poi
si accende e si spegne quello inferiore, quindi il ciclo si ripete).

Il tastierino è in modalità impostazione limiti o un altro dispositivo sul linkè in tale modalità. Tenere premuto i pulsanti superiore e alza per 3 secondi
per uscire dalla modalità impostazione limiti.

I LED superiore e inferiore lampeggiano lentamente e un altro LED
lampeggia rapidamente.

Il tastierino si trova in modalità regolazione delle posizioni preimpostate.
Tenere premuto i pulsanti superiore e inferiore per tre secondi per uscireda tale modalità.

Altri tastierini
Un LED singolo lampeggia.
“Cascata diretta”
I LED si accendono e si spengono in sequenza dall’alto al basso.

Istruzioni per l’installazione

Il tastierino non comanda tutte letende assegnate

Il tastierino è configurato per il controllo zone, il controllo partizionamenti
o il controllo tende motorizzate e si trova in modalità programmazione.
Tenere premuto i pulsanti superiore e inferiore per uscire da tale modalità.
Il tastierino è configurato per il controllo scene, modalità antipanico,sequenza scene, regolazione fine o esclusione scena/zona e si trova
in modalità programmazione. Tenere premuto i pulsanti superiore
e inferiore per uscire da tale modalità.
8

Copia per l’utilizzatore

Le tende del locale si muovono senza
controllo

Copia per l’utilizzatore

9

Istruzioni per l’installazione

Individuazione ed eliminazione dei guasti
Problema

Possibili cause

Nessuna comunicazione con la centralina GRAFIK Eye®
o con l’unità Energi Savr NodeTM.

Cablaggio errato o collegamento lento sulle linee dati 3 e 4 del link
di comando.
Il tastierino non è stato programmato oppure è stato configurato
in modo errato.

I pulsanti dei tastierini non funzionano; i LED non riflettono i comandi;
i pulsanti dei tastierini non funzionano come previsto.

Il collegamento elettrico del tastierino non è corretto.
Il tastierino non è alimentato.
Il tastierino non è assegnato al dispositivo corretto.
Il tastierino non è stato programmato oppure è stato configurato
in modo errato.

I LED non si accendono.

Errore di cablaggio o collegamento lento del tastierino o del processore
sulla linea di alimentazione o sul comune 1 e 2 del circuito di comando.
Il tastierino non è stato programmato correttamente.

Gli ingressi a contatti o l’ingresso del sensore non producono
il risultato desiderato nel sistema.

Errore di cablaggio o collegamento lento del connettore dell’ingresso
a contatti/sensore.
Il tastierino non è stato programmato oppure è stato configurato
in modo errato.

Sito Internet: www.lutron.com
E-mail: product@lutron.com
SEDE PRINCIPALE
USA
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA
18036-1299
TEL +1.610.282.3800
FAX +1.610.282.1243
Numero verde 1.888.LUTRON1
Assistenza tecnica 1.800.523.9466
America settentrionale e meridionale
Numero verde Assistenza Tecnica e Informazioni
U.S.A., Canada, zona caraibica: 1.800.523.9466
Messico: +1.888.235.2910
America centrale/meridionale: +1.610.282.6701

SEDE IN EUROPA
Regno Unito
Lutron EA Ltd.
6 Sovereign Close
LondraE1W 3JF Regno Unito
TEL +44.(0)20.7702.0657
FAX +44.(0)20.7480.6899
NUMERO VERDE (UK) 0800.282.107
Assistenza tecnica +44.(0)20.7680.4481

Garanzia: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
National Electric Code, NEC, e NFPA sono marchi registrati di National Fire Protection Association, Inc.,
Quincy, Massachusetts.
Lutron, , Sivoia, seeTouch, Quantum, e GRAFIK Eye sono marchi registrati e Energi Savr Node, Architrave, eSignature Series sono marchi di Lutron Electronics Co., Inc.
© 2012 Lutron Electronics Co., Inc.

SEDE IN ASIA
Singapore
Lutron GL Ltd.
15 Hoe Chiang Road
#07-03 Euro Asia Centre
Singapore 089316
TEL +65.6220.4666
FAX +65.6220.4333
Assistenza Tecnica - Asia
Cina settentrionale: 10.800.712.1536
Cina meridionale: 10.800.120.1536
Hong Kong: 800.901.849
Indonesia: 001.803.011.3994
Giappone: +81.3.5575.8411
Macao: 0800.401
Singapore: 800.120.4491
Taiwan: 00.801.137.737
Tailandia: 001.800.120.665853
Per gli altri paesi: +65.6220.4666®

®

Lutron Electronics Co., Inc.
Cod. 0301604 Rev. B 10/2012

QS補助コントロール
取付説明書
IEC PELV/NEC® Class 2
30 mA
24 V

必ずお読みください

目次

概要...................................................................................2
電源配線例.........................................................................3
配線/取り付け....................................................................4
取付方法............................................................................7
トラブルシューティング...................................................8

プログラム方法については、QS 補助コントロール プ
ログラミング ガイド をご参照くださいP/N 0301639,
www.lutron.com/qs。
日本語®

補助コントロールは、低電圧機器IEC PELV/NEC®として分類されます。これら
は NFPA® 70、米国国家電気規制® (NEC®) に準拠しています。また、これらはIEC 60364-4-41, VDE 0100 パート 410, BS7671:1992, およびその他の同等な標準に準拠しています。これらの補助コントロールに取り付けおよび配線を実施する際には、すべての適用可能な国内および地域の配線法規に準ずる必要があります。補助コントロールの無電圧接点入力、出力、その他の通信端子に接続される外部回路は、ご使用の国および地域で適用可能な低電圧電源、または低電圧機器向けに準拠する電源から供給する必要があります。

概要

QS補助コントロール モデル

seeTouch®
キーパッド
QSWS2-1B
QSWS2-2B
QSWS2-3B
QSWS2-5B
QSWS2-7B
QSWS2-2BRL
QSWS2-3BRL
QSWS2-5BRL
QSWS2-2BRLIRQSWS2-3BRLIRQSWS2-5BRLIRQSWS2-1RLDQSWS2-2RLDQSWS2-3BDSignature SeriesTM
キーパッド
QSWAS-1B
QSWAS-2B
QSWAS-3B
QSWAS-5B
QSWAS-7B
QSWAS-2BRL
QSWAS-3BRL
QSWAS-5BRL
QSWAS-1RLDQSWAS-2RLDQSWAS-3BD• QS 補助コントロールは、照明・シェードを個別、または同時に制御するためにプログラムすることができます。
• プログラムされていないQS 補助コントロール
は、Sivoia® QS シェード、GRAFIK Eye® QS コ
ントロールユニット、Energi Savr NodeTM ユニ
ット等の接続されている機器をプログラムされるまで一括で制御します。
• 無電圧接点入力は、人感センサー、パーティシ
ョン等のプログラムが可能です。

seeTouch® 国際
キーパッド
QSWE-2B
QSWE-3B
QSWE-4B
QSWE-5BRL
QSWE-5BRLIRQSWE-6BRL
QSWE-7BRL
QSWE-8BRL
QSWE-8BRLIRQSWE-10BRL

QS リンクの上限• QSリンクは 100 個のデバイスもしくは 100
個のゾーンが上限となります。QS 補助コント
ロールは、1 個のデバイスおよび 0 個のゾーンとして計算します。
• QS 補助コントロールは、QS リンク上で 1 電源ユニット (PDU) を使用します。
電源ユニットに関する詳細については、QS
リンク電源ユニット仕様書と次ページ配線図を参照ください。

ArchitraveTM
キーパッド
QSWA-KP5-DN
QSWA-KP5-DW
QSWA-KP7-DN
QSWA-KP7-DW

•
•
•
•
•
•
•
•

注意
• 本説明書をよくお読みいただき、正しく設置してください。
• 補助コントロールの取り付けは、各国の関連法規にしたがい設置ください。
• フェースプレートを拭く場合は、必ず低刺激性の石鹸水 (ぬるま湯) を使用します。(化学洗浄剤
は使用しないでください)。
取付説明書

互換性のある機器
次の機器は QS リンクと互換性があります。
GRAFIK Eye® QS コントロールユニット
QS 補助コントロール
Sivoia® QS シェード
QS インターフェース (接点、Ethernet/RS232)
Quantum® システム
Energi Savr NodeTM ユニット
QS センサー モジュール
QS キースイッチ

電源配線例

QS リンク上に、電力を供給する機器及び電力を消費する機器があります。それぞれの機器は、消費電力に応じ予め設定された電源ユニット (PDU) があります。1つの電源グループは電源を供給する 1 台の機器および電力を消費する 1 台以上の機器から構成されており、それぞれの電源グループには、 1台のみの電源供給機器が設置してあります。QS リンク上の電源グループ内では、配線図内の文字 A で示されている、すべての 4 端子 (1、2、3、4) を接続します。電源を供給する QS リンク上の各機器間では、配線図内で文字B で示されている、端子 1、3、4 (端子 2 は未接続) のみを接続します。
配線は T タップまたは一筆書き配線にしてください。

A
LUTRONGRAFIK Eye®
シリーズ コント
ロールユニット•
電源（PDU）
B
を供給します)を接(端子2 (24 V
続しないこと)お客様保管用A

LUTRON

コントロールインタ 補助コントロールーフェース
電源(PDU)を消費します
電源(PDU)を消費します

B
LUTRON

LUTRON

LUTRON

B

Energi Savr NodeTM
ユニット
電源（PDU）を供給します(端子2 (24V
しないこと)

すべての 4 個の端子を 1 個の電源グ
ループ内で接続します:
1: コモン
2: 24 V
3 および 4: データ

電源グループ 2A

3 個の端子のみを
電源クループ間で接続します:
1: コモン
3 および 4: データ)を接続

電源グループ 3

A

QS リンク電源
電源（PDU）
を供給します2

電源グループ 1

端子2 (24 V )は接続しません。

LUTRONQS センサー モジュール＋人感センサ
電源(PDU)を消費します

B)を接続(端子2 (24 V
しないこと)
お客様保管用Quantum® パネル
は 電源(PDU)を供
給します。

3

取付説明書

LUTRON

LUTRON

LUTRONOFF OFF OFF

ON
ON

1.	電源をオフにする。
ブレーカーをオフにします。

ON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

LUTRON

Tタップ
LUTRON

LUTRON2

LUTRON

A

低電圧電源
配線

1
LUTRON:B

LUTRON4(2) 4.0 mm2

A

データ
リンク

LUTRON

LUTRON

LUTRONドレイン

LUTRON

低電圧電源配線
1: コモン

1.0 mm2

2: 24 V

LUTRON

LUTRON

10 mm

Signature SeriesTM, ArchitraveTM
低電圧電源配線 1.0 mm2
1: コモン

ルートロン ケーブル部品番号

2: 24 V

Signature SeriesTM, ArchitraveTM(2) 4.0 mm2
1

1

GRX-CBL-346S

電源（端子１および２）2
4.0 mm x 2本

低電圧電源配線データ リンク

2
3
4

ドレイン

3
4

GRX-CBL-46L

データ線 (端子 3 および 4)
2
ツイストペアシールド線 0.5 mm
4(2) 4.0 mm22

データ線 (端子 3 および 4)
2
ツイストペアシールド線 0.5 mm

取付説明書

C

seeTouch® 国際

B

電源（端子１および２）2
1.0 mm x 2本

(2) 4.0 mm2

LUTRON

1

C

電線径

2

低電圧電源
配線

LUTRON

電線サイズ (ご使用地域における互換性をご確認ください)
153 m以下

3

3

被覆を剥く長さ

QS リンクの配線の長さ

4seeTouch®, seeTouch® 国際
データ リンク: (1) ツイスト
ペアシールド線
0.5 mm2
3: MUXドレイン
4: MUX
4

LUTRON

2. スイッチボックスを取付ける。 正しいサイズを確認してください。詳細は “取付方法”を参照。
3. 補助コントロールを準備する。フェースプ
レートを取り外し、取付準備をしておきます。
4. 電線を準備する。 被覆を 10 mm むき、裸線を露出させます。

153 m 以上～ 610 m以下

ドレイン

153 – 610 m

LUTRON

LUTRON:

LUTRON

LUTRON

データ
リンク
30 mA 30 mA

筆書き配線（送り配線）

seeTouch®

CO O P E R S BURG
US , AP A 18036 US A
CO ,OPPAE 18036
R S BURG

配線例
LUTRON<153 m

AC N
AC N
099 942 971 099 942 971

警告! 深刻な人身事故につながる可能性がありますので、取り付けのさいは必ずブレーカーをオフにしてください。

ご使用になる信号線の長さに応じ(前ページの表を参照)、電源用の端子 1 および 2 へ適切な径の電線を接続してください。

1• 電源ケーブルおよびデータケーブル (コントロー
ルリンク) 配線上の注意点や制限については、コントロールユニット取扱説明書および仕様書を参照して下さい。
• 補助コントロールと信号線の接続には、スイッチボックス等をご使用ください。
• 使用地域で定められた規格にて、信号線を接続
してください。

QS リンクの配線
ツイストペアシールド線0.5 mm2 を、補助コン
トロールのコネクター端子 3 および 4 に接続します。シールド線（ドレイン線）は図示されるように一緒に接続されている必要があります
が、このシールド線（ドレイン線）をアース/接地側に、または補助コントロールに接続したり、または接地されたスイッチボックスに接続することを、絶対に行なわないでください。

2• コントロールリンクは、電源と同じ配管内には絶対に設置しないでください。誤動作の原因となります。
• ドレイン/シールド線はコントロールリンクに沿って敷設されます。この線をアース/接地側に絶対に接続しないでください。
• 高電圧側電源配線を低電圧用端子に接続しないでください。不適切な配線は、人身事故や、コントロールユニットをはじめとする各機器への損傷につながる恐れがあります。

3

配線/取り付けお客様保管用

データ リンク:
(1) ツイスト
ペアシールド線
0.5 mm2
3: MUX
4: MUX

お客様保管用

データ リンク: (1) ツイスト
ペアシールド線
0.5 mm2
3: MUX
4: MUX

ドレイン

5

低電圧電源配線

1.0 mm2

1: コモン

2: 24 V

取付説明書

メモ: 補助コントロールの接点入力に機器が接続されている場合、CCI1 が表面の一番上のボタンを「押す」、および CCI2 が表面の一番下のボタンを「押す」となります。この動作を変更するには、アプリ
ケーション ノート 428 (seeTouch®
アドバンスド プログラミング モード)
を www.lutron.com にてご参照ください。
パーティション、非常時、またはシーケ
ンス機能向けに構成された、2ボタンコ
ントロールの場合、CCI1 の閉動作が上のボタンに従い、開動作が下のボタンに従います。

seeTouch®

:

取付方法
補助コントロールを下図のように取り付けます。
コントロール本体をスイッチボックスを上下のネジでとめ、ボタン部、フェースプレート取付
板、フェースプレートを取り付けます。

スイッチ
ボックス

コント
ロール

ボタン部
取付板

(3) 1.0 mm2
2
3

A

4

B

A
B
C

ArchitraveTM

取付説明書

コント
ロール

取付板

ボタン部

(3) 1.0 mm2

入力 1
入力 2
コモン

A
B
C

6

ボタン部
取付板
フェース
プレート
取り付けネジ

フェースプ
レート

取付板用ネジスイッ
チボッ
クス(3) 1.0 mm2

コント
ロール

ArchitraveTM

スイッチ
ボックス

Signature SeriesTM

取り付
けネジ

取り付けネジC

1

seeTouch® 国際
コモン
入力 2
入力 1

取付板
用ネジ

取付板
用ネジ

取り付けネジ

seeTouch® 国際

コモン
入力 2
入力 1

Signature SeriesTM

seeTouch®

スイッチ
ボックス

AC N
099 942 971(3) 1.0 mm2

CO O P E R S BURG , P A 18036 US A

30 mA

無電圧接点入力 (CCI) の配線
入力は、無電圧接点、ソリッドステート、オー
プンコレクター、アクティブ・ロー (NPN)/アクティブ・ハイ (PNP) によるものに限ります。
• - NPN オープンコレクター またはアクティブ・
ローのオン状態電圧は 2 V 以下、シンク電流は3.0 mA 以下。
• - PNP オープンコレクターまたはアクティブ・
ハイのオン状態電圧は 12 V 以上、ソース電流
は 3.0 mA 以上。
• 各出力は、補助コントロールにより認識されるために、最低 60 ミリ秒間クローズまたは
オープン状態を保持する必要があります。
他社製機器の出力と上記の仕様内容との互換性に関するご質問については、その製造元にお問い合わせください。

入力 1
入力 2
コモン

お客様保管用

コント
ロール

フェース
プレート

フェース
プレート

補助コントロールタイプ

スイッチボックスのサイズ(高さ x 幅 x 奥行き)

ルートロン
ケーブル部
品番号

seeTouch®
seeTouch® 国際
Signature SeriesTM
ArchitraveTM

95 x 55 x 70 mm
75 x 75 x 35 mm
113 x 39.x 71 mm
112 x 32 x 70 mm

241519241683
WBOX-SA1-Q1
241399

電源投入
ブレーカーをオンにします。
取り付け完了プログラミング機能については、QS 補助コン
トロール プログラミング ガイドを参照くださ
い。

7

取付説明書

お客様保管用トラブルシューティング: LED 機能
LED 動作

トラブルシューティング: シェード機能
エラー識別および対処方法

すべてのキーパッド タイプ「LED が上方向への循環点滅を繰り返す」
すべての LED がオンになるまで、下から点灯し始めてから、すべての LEDが オフになるまで下からが消灯していきます。一巡してから反復します。

QS リンクと通信できない、または QS リンク上で孤立している。
リンク配線を確認します。

ボタンが押された場合でも、LED の応答が全くない。

補助コントロールに電源が供給されていない。電源配線を確認します。
QS リンク上の別の機器がプログラミングモードまたは割り当てモードになっています。その機器をプログラミング モード
から解除させるか、またはこの機器をプログラミングモードに入れることによって、他のすべての機器をプログラミング モードから解除することが出来ます。

すべての LED が早く点滅している。

補助コントロールがアドバンスト プログラミング モードになっています。上と下のボタンを押してそのまま 3 秒間押したままにして、アドバンスト プログラミング モードを終了します。

シェードキーパッドタイプ
上と下の LED が同時に点滅している。

キーパッドが割り当てモードになっています。上と下のボタンを押し、 3 秒間保持し、割り当てモードを終了します。

すべての LED が 3 回点滅し、一時停止してから、これを繰り返す。

キーパッドが割り当てモードか、または上下限設定モードになっているか、または QS リンクに割り当てられた任意のシェードと通信しています。
60 秒間待機し、キーパッドが自動的に通常モードに復帰するようになります (操作は不要です)。または、上と下のボタンを押し、3 秒間保持し、プログラミングモードを終了します。

上と下の LED が交互のパターンで点灯している(上のLED が点灯し消灯してから、下の LED が点灯しこれが消灯する、これを繰り返します)。

キーパッドが上下限設定モードになっているか、またはこのリ
ンク上の別のデバイスが上下限設定モードになっています。
上と下のボタンを押し、3 秒間保持し、上下限設定モードを終了します。

上と下の LED がゆっくり点滅し、その他の 1 個の LED
早く点滅している。

キーパッドがプリセット調整モードになっています。上と下のボタンを押し、3秒間保持し、プリセット調整モードを終了します。

その他のキーパッドタイプ
1 個の LED が点滅している。

「LED が下方向への循環点滅を繰り返す」
LED が上から下まで順番に点灯し消灯します。

取付説明書

キーパッドは、ゾーン トグル、パーティション、またシェー
ド トグル用に構成されており、プログラミング モードになっています。上と下のボタンを押し、3秒間保持し、プログラミ
ング モードを終了します。
キーパッドは、シーン、非常時、シーケンス、ゾーンの微調
整、またはシーン/ゾーン ロック等に構成されており、プログ
ラミング モードになっています。上と下のボタンを押し、3秒間保持し、プログラミング モードを終了します。.
8

お客様保管用問題

考えられる原因

対処方法

接続されたシェードが動作しない。

シェードに電源が供給されていない。

電源を確認します。

シェード素材が何かに引っかかっている。

引っかかっているシ
ェード素材をほどきます。

シェードがキーパッドに割り当てられていない。

任意のシェードをキーパッドに割り当てます。

プリセットが正しく設定されていない。

キーパッド上の上昇/下降ボタンを試してみます。

上下限が正しく設定されていない。

上下限を正しく設定します。

シェード素材が何かに引っかかっている。

引っかかっているシェード素材をほどきます。

上昇/下降ボタンが押されると、シェードがそれとは逆の方向に動く。

オープンとクローズの上下限が逆になっています。

上下限を正しく設定します。

キーパッドのLEDが消灯状態で接続されたシェードが動かない。

電源がキーパッドに供給されていない。

キーパッドへの電源線を確認します。

キーパッド LED はオンですが、キーパッドがどのシ
ェードをもコントロールできない。

すべてのプリセット値が同じ高さに設定されている。

キーパッド上の上昇/下降ボタンを試してみます。

データ線がシェードに配線されていない。

シェードにデータ線を接続します。

シェードが任意のキーパッドに割り当てられていない。

シェードを任意のキーパッドに再度割り当てします。

シェードが完全に開かないか、
または完全に閉じない。

キーパッドが、それに割り当てられているすべてのシェードを操作できない。

部屋のシェードが勝手に動く。

お客様保管用上下限が同じになっている。

上下限を正しく設定します。

シェードがキーパッドから割り当てを解除されている。

その シェード を任意のキーパッドに再度割り当てます。

すべてのプリセット値が同じ高さに設定されている。

キーパッド上の上昇/下降ボタンを試してみます。

シェードが正しく配線されていない。

シェードを再度配線します

キーパッドが正しく配線されていない。

キーパッドを再度配線します。

シェードが別の部屋にあるキーパッドに割り当てられている。

その シェードを正しいキーパッドに再度割り当てます。

9

取付説明書

トラブルシューティング
問題

考えられる原因

GRAFIK Eye® コントロール ユニット、またはEnergi Savr NodeTM ユニットが全く通信しない。

コントロールリンクのデータ線 3 および 4 が誤配線か、または接続不良。
補助コントロールがプログラムされていない、または正しくプログラミングされていない。

補助コントロールのボタンが動作しない。LED が応答しない。補助コントロールのボタンがに機能しない。

補助コントロールが誤配線されている。
補助コントロールに電源が供給されていない。
補助コントロールが正しいコントロールユニットに対してプログラミングされていない。
補助コントロールがプログラムされていない、または正し
くプログラミングされていない。

LEDが点灯しない。

補助コントロール (複数)か、プロセッサーにて、電源接続
端子 1もしくは 2の、誤配線かまたは接続不良。
補助コントロールが正しくプログラムされていない。

接点入力が正しい動作をしない。

補助コントロールの接点入力コネクター の誤配線かまたは接続不良。
補助コントロールがプログラムされていない、または正し
くプログラミングされていない。

インターネット： www.lutron.com/japan
電子メール： asuka@lutron.com
国際本社
米国
Lutron Electronics Co., Inc.
7200 Suter Road
Coopersburg, PA 18036-1299
TEL： +1-610-282-3800 (米国電話番号)
FAX: +1-610-282-1243 (米国電話番号)
米国フリーダイヤル 1-888-LUTRON1(米国内のみ)テクニカル サポート: 1-800-523-9466(米国内限定)欧州本社英国Lutron EA Ltd.
6 Sovereign Close
ロンドン
E1W 3JF United Kingdom
TEL: +44-(0)20-7702-0657 (現地電話番号)
FAX: +44-(0)20-7480-6899 (現地電話番号)
英国フリーダイヤル (UK): 0800-282-107(英国限定)
テクニカル サポート: +44-(0)20-7680-4481(英国電話番号)

南北アメリカテクニカル ホットライン
米国、カナダ、カリブ諸国: +1-800-523-9466(現地電話番号)
メキシコ: +1-888-235-2910 (現地電話番号)
中米/南米: +1-610-282-6701 (現地電話番号)
保証情報: www.lutron.com/TechnicalDocumentLibrary/Warranty_CommercialSystems.pdf
米国電気記号体系、NEC および NFPA はNational Fire Protection Association, Inc., Quincy,
Massachusetts の商標です。
Lutron、 、Sivoia、GRAFIK Eye, Quantum は Lutron Electronics Co., Inc. の登録商標です;
Energi Savr Node, ArchitraveとSignature Seriesはの登録商標です。© 2012 Lutron Electronics Co., Inc.

アジア本社
シンガポールLutron GL Ltd.
15 Hoe Chiang Road
#07-03 Euro Asia Centre
シンガポール 089316
TEL: +65-6220-4666 (現地電話番号)
FAX: +65-6220-4333 (現地電話番号)
アジア テクニカル ホットライン
華北地域: 10-800-712-1536 (中国電話番号)
華南地域: 10-800-120-1536 (中国電話番号)
香港 SAR: 800-901-849 (現地電話番号)
インドネシア: 001-803-011-3994 (現地電話番号)
日本: 0120-083-417
マカオ SAR: 0800-401 (現地電話番号)
シンガポール: 800-120-4491 (現地電話番号)
台湾: 00-801-137-737 (現地電話番号)
タイ: 001-800-120-665853 (現地電話番号)
その他の国・地域: +65-6220-4666(シンガポール電話番号)®

®

Lutron Electronics Co., Inc.
P/N 0301604 改定 B 10/2012