Name & Function

3

Mount the FC6A MicroSmart as follows. To provide ample ventilation, ensure that there is sufficient space
between the FC6A MicroSmart and other devices, heat sources, and panel surfaces.

(1) Functional Button(10) LED Indicator[IN](11) Input Terminals(2) CAN PortLED Indicator[OUT](12) Cartridge Slot 2(3) SD Memory Card Slot
Power LED[PWR](13) Cartridge Slot 1(4) USB PortRun LED[RUN](5) Power Supply Terminals
Error LED[ERR](6) LINK LED
SD Memory Card Status LED[SD](7) ACT LED
Battery Status LED[BAT](8) Ethernet Port 1
Status LED[STAT](9) Output Terminals(13)(12) (11)
(14)

(17)

Top

(15)

FC6A Series
CPU module
CAN J1939 All-in-One type10

20mm minimum

Operating
Surrounding Air
Temperature
55 °C
maximum

40mm
minimum(1)

This sheet provides brief operating instructions of the MICROSmart programmable controller.
For details, see the FC6A Series MICROSmart User’s Manual.

DIN Rail

Available(3)

20mm minimum(9)

Right Side

(5) (6) (7) (8)
(22)
(23)

Operating
Surrounding Air
Temperature
35°C
maximum

Cable

11

Unavailable(19)

Available

2

2.9
[8.1]

163.0

2.7 [3.3]

AWG22

4.0
90.0

UL1007/ UL2464

AWG20

1. Grasp the battery holder and remove it from the module.* (a)2. Remove the old back up battery from the battery holder (c) bypulling the outside hook. (b)3. Install a new back up battery in the battery holder. Push the battery
in until the outsite hook (b) clicks.
4. Insert the battery holder into the module. (a)* The length of the battery holder is 36 mm.

AWG16

163.0
151.0±0.2

2-ø

4.3

UL1015

AWG20
AWG18
AWG16

Recommended ferrule
AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H0,25/10 HBL(9025740000), Ｈ0,25/12T GE (9021020000)
AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H0,34/10 TK(9025750000), H0,34/12 TK (9025770000)
AI 0,5-6 (3200687), AI 0,5-8 (3200014), AI-TWIN 2×0,5-8 (3200933),
H0,5/12D W(9019000000), H0,5/14D W (9019010000),
H0,5/14D ZH W (9037380000)
AI 0,75-6 (3200690), AI 0,75-8 (3200519), Al-TWIN 2×0,75-8 (3200807),
H0,75/12D GR (9019030000), H0,75/14D GR (9019040000),
H0,75/14D ZH GR (9037410000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)
AI 0,5-8 GB (1208966)
AI 1-8 (3200030), H1,0/14D R (9019080000)
AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

Type FC6A-C*4* (Push-in type)● Change the battery before the old battery expires.
● Do not change the battery when the MICROSmart is power ON. Doing so may damage the product.
● Change the battery within 1 minute of turning off the power supply, or the device value will be reset toits initial values.
● Battery May Explode If Mistreated. Do Not Recharge,Disassemble Or Dispose Of In Fire.
● La piles peut exploser en cas de mauvais usage. Ne pas recharger, démonter ou jeter la piles au feu.

Default Setting of the Function Switch● The default setting of the function switch is 0.
● The PLC will not run if the function switch is 0 when Run/Stop PLC by Function Switch isenabled in WindLDR and a program is downloaded with Automatic start after download
enabled. To run the PLC, the function switch must be set to 1.

* Enabled is the default setting for Run/Stop PLC by Function Switch in WindLDR.
* For details on the function switch, see the user's manual.

Mounting Modules

For details about mounting and removing modules, see the user’s manual.

35-mm-wide
DIN Rail(3)
Direct Mounting Hook
(FC6A-PSP1PN05)

DIN Rail Hook

.5

4
2-ø

* See the user’s manual for more details on the dimensions.
* Dimensions in brackets [ ] are for type numbers FC6A-C*4* (Push-in type).

(1) Pull out the DIN Rail Hook.
35-mm-wide (2) Put the groove of the module on the DIN Rail.
DIN Rail(3) Press the modules towards the DIN Rail.
(4) Push in the DIN Rail Hook.
(4)[Direct Mounting on Panel Surface]
Pull out the DIN Rail Hook on the back of themodule and insert the direct mounting Hook
Screw Hole(FC6A-PSP1PN05) into the slot.
Attach the module to the mounting plate using thescrew holes.
Attach the module to the mounting plate using M4tapping screws, as shown below, or make 5 to 6mm
mounting holes and secure the module using M4 panhead screws.
Always give sufficient consideration to operability,
Screw Holeease-of-maintenance, and environmental resistancewhen deciding on the mounting position.

DC Sink Input Wiring-

SensorSensor(2 wires)(2 wires)-+24V 0V COM I0
Sensor Power

I5

I6+24V 0V COM I0
Sensor Power

I5

I6

12VDC Power Input

24VDC Power Input

100 to 240V AC
Power Input+12V 0V FE+24V 0V FE

L

N

L

+

-

+

Power Supply
10.2 to 18.0VDC

L

L: Fuse+--Power Supply
20.4 to 28.8VDC

L

Transistor Protect Source output

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(-) V0(+)

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(+) V0(-)

L

L

L

L

+

AI 0,5-8 GB (1208966)

AWG18

AI 1-12 (3200674), H1,0/16 GE (9025950000)

AWG16

H1,5/18D SW (9019140000)
Tighten torque0.51 N-m

Recommended ferrule

Type
Type
FC6A-C*1* FC6A-C*4*

－

－

Yes

AWG22

Al 0,34-10 (3241129)
AI 0,34-8 (3203066), H0,34/12 TK (9025770000)

Yes

－

－

Yes

Al 0,5-10 (3201275), H0,5/16D W (9019020000)
Al-TWIN2×0,5-10 (3203309),
H0,5/16D ZH W (9037390000)

Yes

Yes

AWG20

Yes

－

Al 0,75-10 (3201288), Al-TWIN 2×0,75-10 (3200975),
H0,75/16D GR (9019050000),
H0,75/16D ZH GR(9037420000)

Yes

Yes

AWG18

Yes

－

AWG20

AI 1,5-10 (3200195), H1,5/16D SW (9019130000)
Al 0,5-10 GB (3203150), H0,5/16 DS W (9202910000)

AWG18

AI 1-10 (3200182), H1,0/16D R (9019100000)

AWG16

AI 1,5-10 (3200195), H1,5/16D SW (9019130000)

Yes
Yes
Yes
Yes

Yes
Yes
Yes
Yes

Tighten torque0.49 N-m( ) indicates the Type No. of PHOENIX CONTACT GmbH & Co. KG and Weidmüller Interface GmbH & Co. KG.

Transistor Sink Output

L

H1,5/18D SW (9019140000)

AWG20

SZS 0,6×3,5 (1205053) , SDS 0,6×3,5×100 (9008330000)

Transistor Protect Source Output
WiringL

AWG16

Screwdriver: LoadPower Supply
85 to 264VAC

Transistor Sink Output
WiringL

AI 0,75-12 (3200849), Al-TWIN 2×0,75-10 (3200975),
H0,75/18 W (9025910000), H0,75/16D ZH GR (9037420000)

Yes

AWG16

Q1 Q2 Q3 COM1 Q4
L

AI 0,5-8 (3200014), H0,5/14D W (9019010000)

AWG18

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

Relay Output
COM0 Q0PE

AI 0,34-8 (3203066), H0,34/12 TK (9025770000)

AWG20

Al 0,25-10 (3241128)

AWG24

Relay Output
WiringAC Power
Wiring

AWG22

Applied cableI1 I2 I3 I4Input (24V DC)

100 to 240V AC power supply type: Support of sensor power which is in the circle area of above figure
is able to be used instead of 24V DC external power.
24V DC power supply type: No support of sensor power. Therefore 24V DC external power is required.
12V DC power supply type: No support of sensor power. Therefore 12V DC external power is required.
DC Power
Wiring

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

CAN Port :+I1 I2 I3 I4Input (24V DC)

Recommended ferrule

AWG24

Screwdriver
SZS 0,6×3,5 (1205053), SDS 0,6×3,5×100 (9008330000)

DC Source Input Wiring+L

UL1015

Wiring9[ Mounting on DIN Rail ]Use a 35-mm-wide DIN Rail and BNL6
mounting clips to secure the modules.

(2)

(1)

90.0
83.0±0.2

Alternative Batteries Compatible with BR2032
CR2032X or CR2032W
Murata
CR2032A or CR2032B
Panasonic

When an expansion module is not connected next,
don’t peel off the protection sticker.

UL1007/UL2464／
UL1007b100.0±0.2

Applied cablecSpecification

AWG24

73.0

AWG18

● Warning: Replace Only The Battery With Panasonic BR2032, Or The
Alternative Batteries Compatible On The List As Below. Use of Another
Battery May Present A Risk of Fire Or Explosion.
● Avertissement: Remplacez uniquement la batterie par BR2032 de PANASONIC,ou par une batterie compatible de la liste ci-dessous. L'utilisation d'une autre
piles peut présenter un risque de feu ou d'explosion.

The
Side ofthe Battery Holder

6

ISO 11898/1993
120Ω

Applicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening TorqueAll dimensions in mm.

11.3[9.85]

2.9 [8.1]
13.6 [12.6]

aCPU module CAN J1939 All-in-One type (40-I/O Type)0.3mm² - 0.82mm² (AWG22-18)

Applied cable

Assembling Modules
The
Side ofthe Battery
Holder5

Cable TypePower supply Terminals, Input Terminals and Output Terminals :Type FC6A-C*1* (Screw fastened type)

Dimensions

8*1 No used with DC power supply types.
*2 FC6A-C*4* (Push-in type) does not have Power Supply Terminals Cover.

TYPE

Operating Temperature: -10 to +55°C(no freezing)
Expanded Operating Temperature: -25 to -10°C, +55 to 65°C (no freezing)* See the user's manual for details on use in Expanded Operating Temperatures.
Storage Temperature: -25 to +70°C(no freezing)
Relative / Storage Humidity: 10 to 95%RH (no condensation)
Altitude or Air Pressure: 1,013 to 795hPa (0 to 2,000 m) during operation, 1,013 to 701hPa (0 to 3,000 m) during transport
Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,
acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,
Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes, 6 directions, 3 times each
Installation Location : Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C / 65°C
Temperature Code: T4A* See the user's manual for more details on the product specifications.

(20) USB Port Cover(21) Power Supply Terminals Cover *2(22) Dummy Cartridges(23) Communication Connector Protection Sticker(24) Expansion Connecter Protect Sticker(14) Sensor Power Terminals *1(15) Communication Connector(16) Expansion Connector(17) Battery Holder(18) SD Memory Card Cover(19) Ethernet Port 1 CoverBattery
HolderOutput TypeType No.
FC6A-C40R*AEJ
Relay
FC6A-C40R*CEJ
Relay
FC6A-C40K*CEJTransistor Sink
24VDC
FC6A-C40P*CEJ
Transistor Protect Source
FC6A-C40R*DEJ
Relay
FC6A-C40K*DEJ
12VDC
Transistor Sink
FC6A-C40P*DEJ
Transistor Protect Source* 1: Screw fastened type, 4: Push-in type
Packing(Pcs/pack): FC6A Unit (1), Connector with analog input cable (1), Battery holder with battery (1)Instruction Sheet (this manual) (1).

For UL/cUL, Horizontal mounting only.

Right Side

Left Side● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE INSTALLED IN AN ENCLOSURE SUITABLE
FOR THE ENVIRONMENT THAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOL OR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté à ľenvironnement ďutilisation et uniquement
accessible avec un outil ďouverture ou une clé.
● WARNING - EXPLOSION HAZARD - THE USB PORT IS NOT FOR USE IN HAZARDOUS LOCATIONS.
● Avertissement: risque d'explosion. Le port USB ne doivent pas être utilisés dans des emplacements dangereux.

Power Supply Type
100-240VAC

J1939-11
J1939-15
Twisted pair Cable
Shielded
Unshielded

The recommended ferrule is made by Phoenix Contact or Weidmüller. To crimp the ferrules shown below,
use a special crimping tool. (CRIMPFOX6 (1212034) or PZ 6 Rote L (1444050000))To the terminal block, use the recommended screwdriver made by Phoenix Contact or Weidmüller andtighten terminal screws tightening torque.

(20)

4

*1 This port is connected to SG inside via
resistor and capacitor connected inseries. (R=1Ω, C=0.68µF)*2 This port is N.C. Not connect to inside.
*3 Use Termination resistors (120Ω, 0.5W
or higher) at the both ends of the network.

(24)

(18)

● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant que le circuit est sous tension, ou à
moins ďêtre certain que lieu ďutilisation soit exempt de concentrations inflammables.

1

Signal wire
No.
SG
1
CAN_L
2
3 CAN_SHLD*¹
CAN_H
4(V+)*²
5Standards
Characteristic impedance(21)

This symbol mark means that batteries and accumulators, at their end-of life,
should be disposed of separately from your household waste.
If a chemical symbol is printed beneath the symbol shown above,this chemical
symbol means that the battery or accumulator contains a heavy metal at a certain
concentration. This will be indicated as follows:
Hg : Mercury (0.0005%) Cd : Cadmium (0.002%) Pb : Lead (0.004%)
In the European Union there are separate collection systems for used batteries and accumulators.
Please dispose of batteries and accumulators correctly in accordance with each country or local regulation.

1
2
3
4
5

Horizontal mounting

Left Side

Warning notices are used to emphasize that improper operation may cause severe personal injury or death.

● The MICROSmart is designed for installation in equipment. Do not install the MICROSmart outside of equipment.
● Install the MICROSmart in environments as described in the user's manual. If the MICROSmart is used in places
where it is subjected to high-temperature, high-humidity, condensation, corrosive gases, excessive vibrations, orexcessive shocks itwill result in electrical shocks, fire hazard, or malfunction.
● The environment rating for using the MICROSmart is “Pollution degree 2.”● Prevent metal fragments and pieces of wire from dropping inside the MICROSmart housing. Ingress of suchfragments and chips may cause fire hazard, damage, or malfunction.
● Use wires of a proper size to meet voltage and current requirements. Tighten terminal screws to the proper
tightening torque. (Power supply Terminals: 0.51 N-m, Input Terminals and Output Terminals: 0.28 N-m)
● Use an IEC60127-approved fuse on the power line and output circuit to meet voltage and current requirements.
(Recommended fuse: Littelfuse 5×20mm slow-blow type 218000 series/Type T)
This is required when exporting equipment containing MICROSmart to Europe.
● Use an EU-approved circuit breaker. This is required when exporting equipment containing MICROSmart to Europe.
● If relays or transistors in the MICROSmart output modules should fail, outputs may remain on or off.
For output signals which may cause heavy accidents, provide a monitor circuit outside of the MICROSmart.
● Do not disassemble, repair, or modify MICROSmart modules.

1
2
3
4
5

(10)

Special expertise is required to use the MICROSmart.
● Read this instruction sheet and the user's manual to make sure of correct operation before starting installation,
wiring, operation, maintenance, and inspection of the MICROSmart. Keep this instruction sheet here it can beaccessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorous quality control system, but users must add
backup or failsafe provisions to control systems use the MICROSmart in applications where heavy damage or
personal injury may be caused if the MICROSmart should fail.
● Install the MICROSmart according to the instructions described in this instruction sheet and the user's manual.
Improper installation will result in falling, failure, or malfunction of the MICROSmart.
● Make sure that the operating conditions are as described in the user’s manual. If you are uncertain about the
specifications, contact IDEC before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order of importance from Warning and Caution:● Turn off the power to the MICROSmart before starting installation, removal, wiring, maintenance, or inspection on
the MICROSmart. Failure to turn off the power may cause damage, electrical shocks or fire hazard.
● Emergency stop and interlocking circuits must be configured outside the MICROSmart. If such a circuit is configured
inside the MICROSmart, failure of the MICROSmart may cause disorder of the control system, damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND D HAZARDOUS LOCATIONS, OR
NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereuses de classe 1, groupes A,B,C et D;ou dans des zones non dangereuses.
● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT EQUIPMENT WHILE THE CIRCUIT IS LIVE OR
UNLESS THE AREA IS KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.

Type FC6A-C*4*(Push-in type)(4)

Safety Precautions

Caution notices are used where inattention might cause personal injury or damage to equipment.

CAN Port (SAE J1939)

Type FC6A-C*1*(Screw fastened type)

40mm
minimum(16)(2)● Use a Class 2 power supply source when power supply voltage less than 30V DC is required to power the terminal.
● Use copper conductor only.
● When the MICROSmart is used in a Surrounding Air Temperature of 65°C, reduce the I/O voltage and I/Outilization. See the user's manual for details.

UL2464

INSTRUCTION SHEET

Installation in Control Panel & Mounting Direction

7

Type FC6A-C*1* (Screw fastened type)

UL1015B-1818 (7)

L

L

L

L

L

L

L

12

Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.

L

MicroSmart User’s manual can be downloaded from http://www.idec.com/FC6Amanuals+-

http://www.idec.com*See the user's manual for more details on the wiring.

2020.11

B-1818(7)

3

名称と機能

7

FC6A形マイクロスマートは次のように取り付けてください。また、通気性が良くなるように、周囲の取付け物、発熱体および盤面から十分なスペースを確保して取り付けてください。

例）FC6A-C*1*形（ねじ締めタイプ）の場合(10) 入力表示 LED［IN］
出力表示 LED［OUT］
電源表示 LED［PWR］
運転表示 LED［RUN］
エラー表示 LED
［ERR］
SD メモリカードステータス LED［SD］
電池ステータス LED［BAT］
ステータス LED［STAT］(11) 入力端子部(12) カートリッジスロット 2(1) 機能スイッチ(2) CAN ポート(3) SD メモリカードスロット(4) USB ポート(5) 電源端子部(6) LINK LED(7) ACT LED(8) Ethernet ポート 1(9) 出力端子部

取扱説明書

(13)

(14)

ＦＣ６Ａ形
ＣＰＵモジュールＣＡＮ Ｊ1939 オールインワン タイプ

(15)

(9)

(23)

右側面

適合電線

動作周囲温度
35℃以下

(24)

(18)

取り付け可能推奨フェルール端子

AWG24

AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H0,25/10 HBL(9025740000), Ｈ0,25/12T GE (9021020000)

AWG22

AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H0,34/10 TK(9025750000), H0,34/12 TK (9025770000)

AWG20

AI 0,5-6 (3200687), AI 0,5-8 (3200014),
AI-TWIN 2×0,5-8 (3200933), H0,5/12D W(9019000000),
H0,5/14D W (9019010000), H0,5/14D ZH W (9037380000)

AWG18

AI 0,75-6 (3200690), AI 0,75-8 (3200519),
Al-TWIN 2×0,75-8 (3200807), H0,75/12D GR (9019030000),
H0,75/14D GR (9019040000), H0,75/14D ZH GR (9037410000)

AWG16

AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

AWG20

AI 0,5-8 GB (1208966)

AWG18

AI 1-8 (3200030), H1,0/14D R (9019080000)

AWG16

AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

(20)

右側面
(22) ダミーカートリッジ(23) 拡張コネクタ保護シール(24) 増設コネクタ保護シール(18) SD メモリカードカバー(19) Ethernet ポート 1 カバー(20) USB ポートカバー(21) 電源端子カバー *2

163.0

側

a

電池ホルダ

電池ホルダの* 電池ホルダの引き出し寸法は 36mm です。バックアップ用電池には、Panasonic 製 BR2032、もしくは下記のリストに記載されている互換電池のみ使用し、それ以外の電池は使用しないでください。

4.3

BR2032 互換バックアップ電池
CR2032X or CR2032W
Murata
CR2032A or CR2032B
Panasonicb

5

機能スイッチの出荷時の状態
・工場出荷時、機能スイッチは０の状態です。
・ WindLDR で［機能スイッチで PLC を RUN/STOP する］を有効にしている場合、［ダウンロード後、自動的に PLC を RUN スタートする］を有効にしてプログラムを
ダウンロードしても、機能スイッチが 0 では PLC は RUN しません。
RUN させるには、機能スイッチを 1 にする必要があります。

6

取付け

I2

DCソース入力配線例

+

-

2線式
センサ

2線式
センサ

I3

+

I4

I5

I6

+24V 0V COM I0

I1

電源出力

DC24Ｖ入力

DC24Ｖ入力

センサ用電源

出力仕様

形番

リレー出力
リレー出力
トランジスタシンク出力
トランジスタプロテクトソース出力
リレー出力
トランジスタシンク出力
トランジスタプロテクトソース出力

FC6A-C40R*AEJ
FC6A-C40R*CEJ
FC6A-C40K*CEJ
FC6A-C40P*CEJ
FC6A-C40R*DEJ
FC6A-C40K*DEJ
FC6A-C40P*DEJ

AC100-240V

DC24V

DC12V電源入力

DC24V電源入力

AC電源入力+12V 0V FE+24V 0V FE

L

１：ねじ締めタイプ、４：プッシュインタイプ

梱包内容（入り数）：本体ユニット（1）、アナログ入力用ケーブル付コネクタ（1）、電池ホルダ（電池付き 1）、取扱説明書（本書 1）。

仕様

使用周囲温度：-10～+55℃（氷結なきこと）
拡張使用周囲温度：-25～-10℃、+55～65℃（氷結なきこと）※拡張使用周囲温度で使用するための詳細は、ユーザーズマニュアルを参照ください。
保存周囲温度：-25～+70℃（氷結なきこと）
使用/保存周囲湿度：10～95%RH（結露なきこと）
標高または大気圧：動作時：1013～795hPa（0～2000ｍ）
輸送時：1013～701hPa（0～3000m）
耐振動：5 ～ 8.4Hz 片振幅3.5mm 8.4 ～ 150Hz加速度9.8m/s2（1G） XYZ各方向
耐衝撃：147m/s2（15G）11ms XYZ 3軸6方向各3回※電気的仕様に関する詳細はユーザーズマニュアルを参照ください。

-

+

外部電源
DC10.2～18.0V① DINレールフック
を下げる

N

ねじ止め用穴2時間

DIN レールフック

L

L

（

L
: ヒューズ+-

外部電源
AC85～264V

L : 負荷トランジスタプロテクトソース出力

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(-) V0(+)

Q0 Q1 Q2 Q3 Q4 Q5 Q6 Q7 COM0(+) V0(-)

L

L

L

AI 0,5-8 GB (1208966)

AWG18

AI 1-12 (3200674), H1,0/16 GE (9025950000)

AWG16

H1,5/18D SW (9019140000)

推奨フェルール端子

L

L

L

+

推奨締付トルク
0.51 N・m

FC6A-C*1* FC6A-C*4*
形の場合
形の場合

Al 0,25-10 (3241128)
Al 0,34-10 (3241129)
AI 0,34-8 (3203066), H0,34/12 TK (9025770000)
Al 0,5-10 (3201275), H0,5/16D W (9019020000)

〇
－
〇
－
〇

－
〇
－
〇
〇

Al-TWIN2×0,5-10 (3203309),
H0,5/16D ZH W (9037390000)

〇

－

AWG18

Al 0,75-10 (3201288), Al-TWIN 2×0,75-10 (3200975),
H0,75/16D GR (9019050000),
H0,75/16D ZH GR(9037420000)

〇

〇

AWG16
AWG20

AI 1,5-10 (3200195), H1,5/16D SW (9019130000)
Al 0,5-10 GB (3203150), H0,5/16 DS W (9202910000)

AWG18
AWG16

AI 1-10 (3200182), H1,0/16D R (9019100000)
AI 1,5-10 (3200195), H1,5/16D SW (9019130000)

〇
〇
〇
〇

〇
〇
〇
〇

AWG22
AWG20

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

推奨ドライバ

トランジスタシンク出力L

H1,5/18D SW (9019140000)

AWG20

推奨締付トルクSZS 0,6×3,5 (1205053) , SDS 0,6×3,5×100 (9008330000)

Q1 Q2 Q3 COM1 Q4

トランジスタプロテクトソース出力
配線例

L

AI 0,75-12 (3200849), Al-TWIN 2×0,75-10 (3200975),
H0,75/18 W (9025910000), H0,75/16D ZH GR (9037420000)

CANポート:

リレー出力COM0 Q0

PE

-

外部電源
DC20.4～28.8V③ DINレールに沿わせる

直付け用取付けフック（FC6A-PSP2PN05）

I6

トランジスタシンク出力
配線例

35mm幅
DINレール④ DINレールフックを上げる

I5

リレー出力配線例

L

+

35mm幅
DINレール

I4

電源配線例［DINレール取付けの場合］取り付けには必ずDINレールを使用し、止め金具（BNL6）で固定してください。

② DINレールに
ひっかける

I3

センサ用電源詳しい取付け・取外し方法は、ユーザーズマニュアルをご参照ください。

ＣＡＮ Ｊ1939 オールインワン タイプ （入出力点数：40点）

I2

AC100～240V電源タイプの場合：外部DC24V電源を使用せず、上図丸部のセンサ用電源を使用することも出来ます。
DC24V電源タイプの場合：上図丸部のセンサ用電源はありません。外部DC24V電源が必要です。
DC12V電源タイプの場合：上図丸部のセンサ用電源はありません。外部DC12V電源が必要です。

DC12V

AI 0,5-8 (3200014), H0,5/14D W (9019010000)

AWG16

AWG24

電源出力

AI 0,34-8 (3203066), H0,34/12 TK (9025770000)

適合電線

DCシンク入力配線例

I1

AWG22

SZS 0,6×3,5 (1205053) , SDS 0,6×3,5×100 (9008330000)

入出力配線+24V 0V COM I0

AI 0,25-8 (3203037), H0,25/12T GE (9021020000)

推奨ドライバ※［ ］内は、FC6A-C*4* 形（プッシュインタイプ）の寸法。
※各カバーを開いたときの寸法は、マニュアルを参照してください。

2

・電池残量がなくなる前に、バックアップ用電池を交換してください。
・バックアップ用電池の交換作業は電源遮断後、１分以内に行ってください。
交換作業が長くなると、デバイス値が初期値に戻ります。
・通電状態では作業しないでください。製品が破損するおそれがあります。

推奨フェルール端子

AWG24
UL1007 AWG20/UL2464
AWG18

.5
-ø4

9

注意

！

適合電線

UL1015側c

FC6A-C*4*形（プッシュインタイプ）の場合

90.0
163.0
151.0±0.2

2-ø100.0±0.2

電池ホルダの

73.0

UL1015

2.7 [3.3]

2.9 [8.1]
13.6 [12.6]

バックアップ用電池の交換手順
1. 電池ホルダの両端をつまみ、引き抜きます。*（a）2. 電池ホルダから使用済みのバックアップ用電池を取り外します。
外側のツメ（b）を引きながら、下からバックアップ用電池を押します（c）。
3. 新しいバックアップ用電池を電池ホルダに取り付けます。
外側のツメ（b）にカチッと音がするまで押し込みます。
4. 電池ホルダを元の位置に差し込み（a）、奥までしっかり押し込みます。

（単位：mm）

11.3[9.85]

4.0

DC 電源タイプにはありません。
FC6A-C*4* 形（プッシュインタイプ）には、電源端子カバーはありません。

* WindLDR の初期設定では［機能スイッチで PLC を RUN/STOP する］は有効です。
* 機能スイッチに関する詳細はユーザーズマニュアルを参照ください。

形番構成

外形寸法

／ UL2464
UL1007

左側面

8

2.9
[8.1]

(21)

UL1015◆EU加盟国でのバッテリおよびバッテリ組込み機器の取扱いについての注意事項
注）右のシンボルマークは欧州連合域内の国においてのみ有効です。
このシンボルマークは電池及び蓄電池を廃棄する際、一般ゴミとは分別して処理する必要があるということを意味します。上記のシンボルマークの下に元素記号が表示されている場合、電池または蓄電池に基準以上の重金属が含有されていることを意味します。
濃度の基準は次のとおりです。
Hg : 水銀 (0.0005%)
Cd : カドミウム (0.002%)
Pb : 鉛 (0.004%)
電池および蓄電池は各国や地域の条例に従って、正しく廃棄してください。

UL1007/UL2464

取り付け不可(19)4・本製品は装置内への組み込み設置専用です。装置外には設置しないでください。
・カタログ、ユーザーズマニュアルに記載の環境下で、ご使用ください。
・高温、多湿、結露、腐食性ガス、過度の振動・衝撃のある所で使用すると、感電、火災、誤動作の原因となります。
・本製品の使用環境汚損度は「汚損度2」です。
・設置、配線作業時に配線くずやドリル加工による金属の切り粉などが、本製品内部に入らないように注意
してください。配線くずなどが本製品内部に入ると、火災、故障、誤動作の原因となります。
・配線は印加電圧、通電電流に適した電線サイズを使用し、端子ねじは推奨締付トルク（0.51N・mまたは0.49N・m）で締め付けてください。詳細は「11. 適合電線／推奨フェルール端子／推奨ドライバ／締付トルク」の項を参照ください。
・本製品の電源ライン、出力モジュールの出力ラインには印加電圧、通電電流に適したIEC60127承認ヒューズをご使用ください。（推奨:リテル社5×20mmスローブロー型218000シリーズ／タイプT）（マイクロスマートを組み込んだ機器を欧州に出荷する場合に適用）
・サーキットブレーカをご使用の場合は、EU承認品をご使用ください。
（マイクロスマートを組み込んだ機器を欧州に出荷する場合に適用）
・出力モジュールのリレー、トランジスタなどの故障により出力がONまたはOFFの状態になったままになることがあります。重大事故の可能性のある出力信号については外部に状態を監視する回路を設けてください。
・センサ電源は、マイクロスマートに接続するセンサの電源供給以外の用途では使用しないで下さい。
・分解、修理、改造等は行わないでください。

* 端子仕様20mm以上(22)

注意DC12V電源タイプ

DINレール

内部で抵抗とコンデンサを直列に経由してSGに接続されています。
（R=1Ω, C=0.68μF）*2 N.C. です。内部に接続されていません。
*3 ネットワークの両端に終端抵抗（120Ω、0.5W以上）を接続してください。

電源端子部、入力端子部、出力端子部：
FC6A-C*1*形（ねじ締めタイプ）の場合

警告

DC24V電源タイプ

取り付け可能*1

11 適合電線／推奨フェルール端子／推奨ドライバ／締付トルク(10)・取り付け、取り外し、配線作業および保守・点検は必ず電源を切って行ってください。
破損のおそれ、感電および火災の危険があります。
・非常停止回路やインタロック回路などはマイクロスマート以外の外部回路で構成してください。
これらの回路をマイクロスマートのシステムで構成するとマイクロスマートが故障した場合、機械の暴走、破損や事故のおそれがあります。

2

(16)

信号線
SG
CAN_L
CAN_SHLD *¹
CAN_H(V+) *²

推奨のフェルール端子はフェニックス・コンタクト社またはワイドミュラー社製品です。
下記推奨フェルール端子を圧着する際には、専用の圧着工具（CRIMPFOX 6（1212034）またはPZ 6
Rote L（1444050000）をご使用ください。
端子台に配線する際には、下記推奨ドライバをご使用ください。またねじ締め付けが必要な場合は、下記の推奨締付トルクで締め付けてください。

(4)

*1
*2

注意

AC100-240V電源タイプ

天面

90.0
83.0±0.2

警告

電源仕様

40mm
以上

No.
1
2
3
4
5

1
2
3
4
5

1
2
3
4
5

(5) (6) (7) (8)取扱いを誤った場合、人が障害を負うか物的障害が発生する可能性があります。

1

(11)

左側面

取扱いを誤った場合、人が死亡または重傷を負う可能性があります。

！

40mm
以上

(3)

安全上のご注意！

20mm以上動作周囲温度
55℃以下

(17)

(2)

本製品の取り扱いには専門の知識が必要です。
・本製品の取り付け、配線作業、運転および保守・点検を行う前に、この取扱説明書およびユーザーズマニュ
アルをよくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管されるよう手配ください。
・本製品は弊社の厳しい品質管理体制のもとで製造されておりますが、万一本製品の故障により重大な故障や損害の発生するおそれがある用途へご使用の際は、バックアップやフェールセーフ機能をシステムに追加してください。
・取扱説明書、ユーザーズマニュアルに記載の指示に従って取り付けてください。
取り付けに不備があると落下、故障、誤作動の原因となります。
・使用条件が、取扱説明書やユーザーズマニュアルの内容と相違ないことを必ずご確認ください。
内容に不明な点がある場合は、使用する前に弊社までご相談ください。
・本取扱説明書では、誤った取り扱いをした場合に生じることが想定される危険の度合いを「警告」「注意」
として区別しています。それぞれの意味するところは以下のとおりです。

！

(13) カートリッジスロット 1(14) センサ用電源端子部 *1(15) 拡張コネクタ(16) 増設コネクタ(17) 電池ホルダ(1)

この度は、弊社製品をお買い上げいただき、誠にありがとうございます。本製品を安全に正しくお使いいただくために、この取扱説明書およびFC6A形マイクロスマートユーザーズマニュアルをよくお読みください。この取扱説明書は最終ユーザー様で保管されるよう手配ください。

！

(12)

［FC6A-C*4*形［FC6A-C*1*形（ねじ締めタイプ）の場合］ （プッシュインタイプ）の場合］

取付け方向

0.49 N・m）内はフェニックス・コンタクト社またはワイドミュラー社製品の発注形番

12 廃棄上のご注意
・本製品を廃棄するときは、産業廃棄物として扱ってください。

ユーザーサポート情報
最新のユーザーズマニュアルを、下記URLよりダウンロードして下さい。
https://jp.idec.com/c/MicroSmart_FC6A

L

L

L

L

L

L

L

L
+
-

［直付け取付けの場合］
本体の裏面のDIN レールフックを引き出し、直付け用取付けフック（④保守部品：
FC6A-PSP2PN05）を本体に取り付け、ねじ止め用穴を使用して取付板に取り付けます。
左図のように取付板に、FC6A 形マイクロスマートをM4 ナベねじで取り付けます。
操作性、保守性、耐環境性を十分考慮して取付け位置を決定してください。

ねじ止め用穴※出力配線時の電源仕様に関する詳細は、ユーザーズマニュアルを参照ください。

10 ＣＡＮポート（ＳＡＥ Ｊ１９３９）
電線形態
ケーブル
適用規格
特性インピーダンス

J1939-11
J1939-15
ツイストペアケーブル
シールドあり シールドなし
0.3mm² - 0.82mm² (AWG22-18)
ISO 11898/1993
120Ω

2020.11