5106HART® transparent
repeaterNo. 5106V103-UK
From ser. no. 030459198

DK

PR electronics A/S tilbyder et bredt program af analoge og digitale
signalbehandlingsmoduler til industriel automation. Programmetbestår af Isolatorer, Displays, Ex-barrierer, Temperaturtransmittere,
Universaltransmittere mfl. Vi har modulerne, du kan stole på i selv
barske miljøer med elektrisk støj, vibrationer og temperaturudsving,og alle produkter opfylder de strengeste internationale standarder.
Vores motto »Signals the Best« er indbegrebet af denne filosofi – og
din garanti for kvalitet.

UKPR electronics A/S offers a wide range of analog and digital
signal conditioning devices for industrial automation. The productrange includes Isolators, Displays, Ex Interfaces, Temperature
Transmitters, and Universal Modules. You can trust our products inthe most extreme environments with electrical noise, vibrations andtemperature fluctuations, and all products comply with the mostexacting international standards. »Signals the Best« is the epitomeof our philosophy – and your guarantee for quality.

FRPR electronics A/S offre une large gamme de produits pour letraite­
ment des signaux analogiques et numériques dans tous
les domaines industriels. La gamme de produits s’étend destransmetteurs de température aux afficheurs, des isolateurs aux
interfaces SI, jusqu’aux modules universels. Vous pouvez compter
sur nos produits même dans les conditions d’utilisation sévères,p.ex. bruit électrique, vibrations et fluctuations de température.
Tous nos produits sont conformes aux normes internationales lesplus strictes. Notre devise »SIGNALS the BEST« c’est notre lignede conduite - et pour vous l’assurance de la meilleure qualité.

DEPR electronics A/S verfügt über ein breites Produktprogramm
an analogen und digitalen Signalverarbeitungsgeräte für die in­dustrielle Automatisierung. Dieses Programm umfasst Displays,Temperaturtransmitter, Ex- und galvanische Signaltrenner, undUniversalgeräte. Sie können unsere Geräte auch unter extremen
Einsatzbedingungen wie elektrisches Rauschen, Erschütterungen
und Temperaturschwingungen vertrauen, und alle Produkte von
PR electronics werden in Überein­stimmung mit den strengsteninternationalen Normen produziert. »Signals the Best« ist Ihre
Garantie für Qualität!
1408

HART ® TRANSPARENT REPEATER
PRetrans 5106
Table of contents
Warning........................................................................................................ 2
Symbol identification............................................................................. 3
Safety instructions.................................................................................. 3
How to demount system 5000......................................................... 5
Application.................................................................................................. 6
Technical characteristics....................................................................... 6
Mounting / installation.......................................................................... 6
Applications............................................................................................... 7
Order: 5106................................................................................................ 8Electrical specifications........................................................................ 8Connections............................................................................................... 11
Block diagram............................................................................................ 12Control Drawing 5106QU01............................................................... 145 106V1 0 3 - U K

1WARNING

GENERAL

This device is designed for connection to hazardous electricvoltages.
Ignoring this warning can result in severe personal injury ormechanical damage.
To avoid the risk of electric shock and fire, the safety instructionsof this manual must be observed and the guidelines fol­lowed.
The specifications must not be exceeded, and the device must
only be applied as described in the following.
Prior to the commissioning of the device, this manual must be
examined carefully.
Only qualified personnel (technicians) should install this device.
If the equipment is used in a manner not specified by themanufacturer, the protection provided by the equipment may beimpaired.

WARNING

Until the device is fixed, do not connect hazardous voltages tothe device.
The following operations should only be carried out on aHAZARD­OUS disconnected device and under ESD safe conditions:
VOLT­AGE
Dismantlement of the device for setting of DIP-switches
and jumpers.
General mounting, connection and disconnection of wires.
Troubleshooting the device.
Repair of the device and replacement of circuit breakers must
be done by PR electronics A/S only.

WARNINGINSTALLATION

2SYSTEM 5000 must be mounted on DIN rail according to DIN
46277.
The communication connector of SYSTEM 5000 is connected tothe input terminals on which dangerous voltages can occur, andit must only be connected to the programming unit Loop Link by
way of the enclosed cable.

5106V103- U K

SYMBOL IDENTIFICATION
Triangle with an exclamation mark: Warning / demand. Potentially le­thal
situations.
The CE mark proves the compliance of the device with the essential
requirements of the directives.
The double insulation symbol shows that the device is protected bydouble or reinforced insulation.
Ex devices have been approved for use in connection with installations in
explosive areas.

SAFETY INSTRUCTIONSDEFINITIONS
Hazardous voltages have been defined as the ranges: 75 to 1500 Volt DC, and
50 to 1000 Volt AC.
Technicians are qualified persons educated or trained to mount, operate, and also
troubleshoot technically correct and in accordance with safety regulations.
Operators, being familiar with the contents of this manual, adjust and operate
the knobs or potentiometers during normal operation.
RECEIPT AND UNPACKING
Unpack the device without damaging it. The packing should always follow thedevice until this has been permanently mounted. Check at the receipt of thedevice whether the type corresponds to the one ordered.
ENVIRONMENT
Avoid direct sunlight, dust, high temperatures, mechanical vibrations and shock,as well as rain and heavy moisture. If necessary, heating in excess of the statedlimits for ambient temperatures should be avoided by way of ventilation.
All devices fall under Installation Category II, Pollution Degree 2, and Insulation
Class II.
MOUNTING
Only technicians who are familiar with the technical terms, warnings, andinstructions in the manual and who are able to follow these should connect thedevice.

5 106V1 0 3 - U K

3

Should there be any doubt as to the correct handling of the device, please contact
your local distributor or, alternatively,
PR electronics A/S
www.prelectronics.com
Mounting and connection of the device should comply with national legislation
for mounting of electric materials, i.e. wire cross section, protective fuse, andlocation. Descriptions of input / output and supply connections are shown in theblock diagram and side label.
The following apply to fixed hazardous voltages-connected devices:
The max. size of the protective fuse is 10 A and, together with a powerswitch, it should be easily accessible and close to the device. The powerswitch should be marked with a label telling it will switch off the volt­age to the device.
Year of manufacture can be taken from the first two digits in the serial number.
CALIBRATION AND ADJUSTMENT
During calibration and adjustment, the measuring and connection of external
volt­ages must be carried out according to the specifications of this manual. The
technician must use tools and instruments that are safe to use.
NORMAL OPERATION
Operators are only allowed to adjust and operate devices that are safely fixed inpanels, etc., thus avoiding the danger of personal injury and damage. This means
there is no electrical shock hazard, and the device is easily accessible.
CLEANING
When disconnected, the device may be cleaned with a cloth moistened withdistilled water.
LIABILITY
To the extent the instructions in this manual are not strictly observed, thecustom­er cannot advance a demand against PR electronics A/S that would
otherwise exist according to the concluded sales agreement.

45106V103- U K

HOW TO DEMOUNT SYSTEM 5000First, remember to demount the connectors with hazardous voltages.
Picture 1:
By lifting the bottom lock, the device
is detached from the DIN rail.

Picture 2:
Then, by lifting the upper lockand pulling the front plate
simultaneously, the PCB is removed.
Switches and jumpers can now beadjusted.

5 106V1 0 3 - U K

5

HART ® TRANSPARENT REPEATER
PRetrans 5106
• 3- / 5-port 3.75 kVAC galvanic isolation• Low response time
• 2-wire supply > 17 V
• 1- or 2-channel version• Universal AC or DC supplyApplication• Power supply and signal isolator with 2-way HART® communication for 2-wiretransmitters.
• Signal isolator with 2-way HART® communication for supplied current
transmitters.
• Signal isolator with low response time on analogue current signals.

Technical characteristics• PR5106 primarily processes current signals of 4...20 mA.
• PR5106 is based on microprocessor technology for gain and offset. The
analogue signal is transmitted at a response time of less than 25 ms.
• Inputs, outputs, and supply are floating and galvanically separated.
• The output can be connected either as an active current transmitter or as a2-wire transmitter.

Mounting / installation• Mounted vertically or horizontally on a DIN rail. As the devices can be mount­
ed without distance between neighbouring units, up to 84 channels can bemounted per metre.
• PR5106B is recommended as Ex safety barrier for 5335D and 6335D.

65106V103- U K

APPLICATIONS
2-wire transmitter
OutputSupplyCurrent, mA
OutputSupply5 106V1 0 3 - U K

7

Order: 5106

TypeVersion

Input

Output5106

Standard:A[EEx ia] II C : B

4…20 mA : B

4…20 mA : 220...4 mA : 9Channels
SingleDoubleElectrical specifications
Specifications range:-20 to +60°C
Common specifications:
Supply voltage universal....................................... 21.6...253 VAC, 50...60 Hz or
19.2...300 VDCInternal consumption.............................................. ≤ 2 W (2 channels)
Max. consumption..................................................... ≤ 3 W (2 channels)
Fuse................................................................................ 400 mA SB / 250 VAC
Isolation voltage, test / operation..................... 3.75 kVAC / 250 VAC
Signal / noise ratio................................................... Min. 60 dB (0...100 kHz)
Response time (0...90%, 100...10%)................. < 25 ms
Calibration temperature......................................... 20...28°C
Effect of supply voltagechange (24...250 V)................................................. < ±10 µA
Accuracy, the greater of general and basic values:

General values
Input type

Absolute
accuracy≤ ±0.1% of spanmA

Temperature
coefficient≤ ±0.01% of span / °C

Basic values
Input typemA

8Basicaccuracy≤ ±16 µA

5106V103- U K

Temperature
coefficient≤ ±1.6 µA/°C:A:B

EMC immunity influence................................................... < ±0.5% of span
Extended EMC immunity:
NAMUR NE 21, A criterion, burst.................................. < ±1% of span
Auxiliary supply:
2-wire supply (pin 44...42 & 54...52)................ 25...17 VDC / 0...20 mA
Max. wire size............................................................. 1 x 2.5 mm2 stranded wire
Screw terminal torsion........................................... 0.5 Nm
Relative humidity..................................................... < 95% RH (non-cond.)
Dimensions (HxWxD)............................................... 109 x 23.5 x 130 mm
DIN rail type................................................................ DIN 46277
Protection degree..................................................... IP20
Weight........................................................................... 246 g

Current input:
Measurement range................................................. 4...20 mA
Min. measurement range (span)......................... 16 mA
Input resistance:
Supplied unit.............................................................. Nom. 10 Ω
Non-supplied unit..................................................... Rshunt = ∞, Vdrop < 4 V
Current output and 2-wire 4...20 mA output:
Signal range (span).................................................. 4...20 mAMin. signal range (span)......................................... 16 mA
Load (max.).................................................................. 20 mA / 600 Ω / 12 VDC
Load stability.............................................................. ≤ 0.01% of span / 100 Ω
Current limit................................................................ ≤ 28 mA
Ripple on HART® communication........................ < 3 mVRMS
Max. external 2-wire supply................................ 29 VDC
Effect of external 2-wire supply
voltage change.......................................................... < 0.005% of span / V
EEx / I.S. approval - 5106B:
DEMKO 00ATEX127483........................................

II (1) GD[EEx ia] IIC
Applicable for............................................................. Zone 0, 1, 2, 20, 21 or 22
UL.................................................................................... IS, Cl. I, Div. 1, Group A, B, C, D
IS, Cl. I, zone 0 and 1, Group IIC
IS, Cl. II, Div. 1, Group E, F,GUL control drawing no................................... 5106QU01

5 106V1 0 3 - U K

9Ex / I.S. data:
Terminal 31...33
Um................................................................................... : 250 V
Terminal 44 to 42, 41 (54 to 52, 51)
Uo.................................................................................... : 28 VDC
Io...................................................................................... : 91 mADC
Po..................................................................................... : 0.65 W
Lo..................................................................................... : 3.0 mH
Co..................................................................................... : 80 nF
Terminal 41 to 42 (51 to 52)
Uo.................................................................................... : 10 VDC
Io...................................................................................... : 2 mADC
Po..................................................................................... : 5 mW
Lo..................................................................................... : 1 H
Co..................................................................................... : 3 µF
GOST R approval:
VNIIM & VNIIFTRI, Cert. no................................... See www.prelectronics.com
Observed authority requirements:
Standard:
EMC 2004/108/EC................................................... EN 61326-1
LVD 2006/95/EC....................................................... EN 61010-1
PELV/SELV................................................................... IEC 364-4-41
and EN 60742
ATEX 94/9/EC............................................................. EN 50014, EN 50020 andEN 50281-1-1
UL.................................................................................... UL 913, UL 508
Of span = of the presently selected range

105106V103- U K

CONNECTIONSConnections:

Connections are identicalfor channel 1 and channel 2.

Supply:3124...230 VAC &24...250 VDC
33Inputs:
Input

Input

Current

41 / 51

42 / 52

42 / 52

43 / 53

43 / 53

44 / 54

44 / 54

C O M M U N I C AT I O N F O U N D AT I O NC O M M U N I C AT I O N F O U N D AT I O N

Outputs:

Activeoutput

DCS / PLC

14 / 24

Activeoutput

DCS / PLC

14 / 24

13 / 23

13 / 23

12 / 22250 Ω

2-wire transmitter

41 / 51

OutputInput

Z

11 / 21Z

12 / 22Output

250 ΩInput

11 / 21

C O M M U N I C AT I O N F O U N D AT I O N

C O M M U N I C AT I O N F O U N D AT I O N

If the input impedance Z is 250 Ω or higher

If the input impedance Z is < 250 Ω

Passiveoutput

DCS / PLC

14 / 24

Passiveoutput

DCS / PLC

14 / 24Input

ZInput13 / 23

13 / 2312 / 2212 / 22250 ΩOutput

11 / 21250 ΩOutput

Z

11 / 21C O M M U N I C AT I O N F O U N D AT I O N

C O M M U N I C AT I O N F O U N D AT I O N

If the input impedance Z is 250 Ω or higher

If the input impedance Z is < 250 Ω5 106V1 0 3 - U K

1112Tx-+

5106V103- U K

CH 2515254

41-Input -, I4244

Input +, I+2-wire supply

Ex barrier, only 5106BCH 11VPTCVreg.

5106 Channel 25106 Channel 11213mAI+, Output

mA2-wire
installation

Supply21222324+

24...230 VAC &24...250 VDC

11 I -, Output

250 Ω0...20mA

143133 Supply

BLOCK DIAGRAMAPPENDIX

Control Drawing 5106QU01

5 106V1 0 3 - U K

13

CONTROL DRAWING 5106QU01

Hazardous (Classified) Location

Nonhazardous

Class I, Division 1, Group A,B,C,D
Class I , Zone 0 and 1, Group IIC
Class II, Division 1 Group E, F, G

Current input

T-Supply

24....230VAC &24....230VDC

314433+14mA43134212mA+-2-wiretransmitter

The sum of capacitance andinductance of cable and intrinsic safe equipment must be
less or equal to Ca and La+

Current input

Vmax. (Ui) ≥ Vt (Uo)Imax. (Ii) ≥ It (Io)Pi ≥ PoCa ≥ Ccable + Ci
La ≥ Lcable + Li

2-wiretransmitter

Intrinsically safe apparatus
entity parameters:

SupplyAssociated apparatus
Galvanically Isolated+V-

41

11

CH1

54

24

53

23

52

22+
mA

mA+

-51

CH25106B

5106B Associated apparatus parameters
CH1Terminals 44 to 41,42
CH2
Terminals 54 to 51,52
Vt (Uo)28 VIt (Io)93 mA
Po
0.65 W
IIC / grp. A, B IIB / grp. C IIA / grp.DCa (Co)
0.06 μF
0.52 μF1.72 μF
La (Lo)
2.4 mH
12 mH
20 mH

21

Terminals 41 to 42
Terminals 51 to 52
10V
2 mA
5 mW
IIC / grp. A, B
3.0 μF
1.0 H

Installation notes:
1)
The maximum nonhazardous location voltage is 250VAC/DC.
2)
The installation shall be in accordance with the National Electrical CodeNFPA 70, Articles 504 and 505.
3)
The terminals of the two individual channels shall not be interconnected in anyway.
4)
Install in Pollution degree 2 or better5)
Use 60 / 75 °C copper conductors with wire size AWG: (26 – 14).
6)
Warning: Substitution of components may impair intrinsic safety.

145106V103- U K

Displays
Programmable displays with a wide selectionof inputs and outputs for display of temperature, volume andweight, etc. Feature linearization, scaling, and difference
measurement functions for programming via PReset software.
Interfaces for analog and digital signals
Ex interfaces
as well as HART® signals between sensors / I/P converters /frequency signals and control systems in Ex zone 0, 1 & 2 andfor some devices in zone 20, 21 & 22.
Galvanic isolators for analog and digital signals
Isolation
as well as HART® signals. A wide product range with bothloop-powered and universal isolators featuring linearization,inversion, and scaling of output signals.
Temperature
A wide selection of transmitters for DIN form
B mounting and DIN rail devices with analog and digital bus
communication ranging from application-specific to universal
transmitters.
UniversalPC or front programmable devices with
universal options for input, output and supply. This range offers
a number of advanced features such as process calibration,linearization and auto-diagnosis.

 www.prelectronics.fr
 sales-fr@prelectronics.com
 www.prelectronics.de sales-de@prelectronics.com
 www.prelectronics.es
 sales-es@prelectronics.com
 www.prelectronics.it
 sales-it@prelectronics.com
 www.prelectronics.se sales-se@prelectronics.com
 www.prelectronics.co.uk
 sales-uk@prelectronics.com
 www.prelectronics.com
 sales-us@prelectronics.com
 www.prelectronics.cn
 sales-cn@prelectronics.com

Head officeDenmark

PR electronics A/S
Lerbakken 10DK-8410 Rønde

www.prelectronics.com

sales-dk@prelectronics.com
tel. +45 86 37 26 77
fax +45 86 37 30 85