§ PLUG-IN TRANSDUCER §COMPENDIUM■ PLUG-IN 2-OUTPUT TYPE Signal/Sensor/AC transducer
ProductType code

Isolator
Distributor
Distributor withsquare root
extraction
Thermoelectric
temperaturetransducer
Resistancetemperaturetransducer
Potentiometertransducer
AC current
transducer
AC voltage
transducer
Frequencytransducer

Outlines

WHTP2 -□□□□□

Converts a DC input signal into a unified signal which wasisolated.
Supplies electric power to a 2-wire transmitter and converts
signal from the transmitter into a proportional DC signal.
Supplies electric power to a 2-wire transmitter and converts
signal from the transmitter into a DC signal which wasproportional to the square root of the signal.
Converts thermal electromotive force of a thermocouple into aDC signal which was proportional to temperature.

WRHTP2-□□□□□

Converts resistance of a 3-wire thermal resistance into a DC
signal which was proportional to temperature.

WTP2-

WDTP2-C7□□□□□□WSRDTP2-C7□□□

WRTP2-Z□□□

WAETP2 -□□□□
WVETP2 -□□□□
WFTP2 -□□□□□

Outputs a DC signal which was proportional to resistance of apotentiometer.
Outputs a DC signal which was proportional to RMS value ofan AC current input.
Outputs a DC signal which was proportional to RMS value ofan AC voltage input.
Outputs a DC signal which was proportional to frequency.

Withstandvoltage
AC2000V
AC2000V
AC2000V

AC2000V

AC2000V
AC2000V
AC2000V
AC2000V
AC2000V■ Soft spec type
Product

Type code

Adding/subtracting
transducer

CADTP1 -□□Multiplying/dividing
transducer

CMLTP1 -□□Temperature/pressure
correcting transducer

CLTP1-□□

Function generatingtransducer
Analog backup
transducer

CFGTP1 -□□CAMTP1 -□□CVFTP1 -□□Voltage pulse transducerOutlines
Does adding and subtracting of three inputs, and then outputs
a DC signal equivalent to the value.
Parameters can be changed by CCM-1.
Does multiplication and division of three inputs, and thenoutputs a DC signal equivalent to the value.
Parameters can be changed by CCM-1.
Processes temperature/pressure condition and converts it intoa DC signal which was proportional to flow rate.
Parameters can be changed by CCM-1.
Does broken line operation of a DC input 15 polygonal lines
maximum. Parameters can be changed by CCM-1
Provides output with a backup when a computer or a PID
controller was down. Follow-up movement and output backup
are settable by CCM-1.
Outputs a pulse of frequency which was proportional to a DCinput. Pulse frequency, pulse width and output cut against alow input are settable by CCM-1.

Withstandvoltage
AC1500V

AC1500V

AC1500V
AC1500V
AC1500V

AC1500V■ Alarm setter
ProductType code

Outlines

Alarm setter(digital % scale)
Alarm setter(actual scale)SDD-□-105□-□SD-□-105□-□

Alarm setter(LCD)

SDLC-105-□

Deviation alarm
setter (LCD)

SDDV-105-□

AC voltage alarmsetterProducts List

SVD-□-105□-□□Compares a preset value of digital % scale with a direct input
signal, and outputs a contact signal.
Compares value of an actual scale setter with a direct input
signal, and outputs a contact signal.
Compares a preset value with a direct input signal, and thenoutputs a contact signal. 4 digit LCD indication. Actual scaleindication is settable.
Compares deviation between two DC signal inputs anddeviation of each input with a preset value, and then outputs acontact signal.
Inputs AC voltage and outputs a contact signalWithstandvoltage
AC1500V
AC1500V
AC2000V

AC2000V
AC2000V

2§ PLUG-IN TRANSDUCER §COMMON STANDARD SPECIFICATION/TYPE CODE DESIGNATION■Common standard specifications●High quality/high reliability
Highly reliable electronic parts are adopted.
Aging tests of each part as well as burn-in aging test of the product under a high temperature areimplemented.
●PCB treatment
In order to reinforce insulation resistance stability of PCB surfaces and prevent the surfaces frominsulation deterioration, B side of the PCB was cleaned and coated with high humidity resistant varnish
after parts installation.
●Output limiter circuit
Even if an excessive input is applied, the product confines the output to about 1.5 times of rating andprotects the output side equipments.
Item

Specification

Tolerance% against output span

Influence of temperature

23±10℃ tolerance %Influence of frequency

45-65Hz tolerance %Characteristics

In conformity with JIS C 1111-1989 in tolerance(Reference) IEC, rated Hz±10% tolerance %Time it takes to fall within ±1% of the final steady-state when applied a stepped input.

Response timeStandard : ≦1.0. sec. (Insulation transducer only: ≦0.5 sec.)

Output ripple≦1%p-p against output span

External adjustment of±5% adjustable

outputAuxiliary supply

AC100V or AC200V ±10% (50, 60Hz) (DC100/110V is manufacturable only for TP2)

Overvoltage

Input

2 times (10 sec.), 1.2 times (continuity) of rated voltage

Aux.supply

1.5 times (10 sec.), 1.1 times (continuity) of rated voltage
40 times (1 sec.), 20 times (4 sec.) 10 times (16 sec.),

AC transducer

Over current

1, 2 times (continuity) of rated current

Signal transducer

10 times (5 sec.)Between input terminal, output terminal, (auxiliary supply terminal) and outer case (earth)Insulation resistance≧50MΩ at DC500V. Non-insulation type: input terminal and output terminal conducted.

Material of outer caseFire-retardant ABS resin

Appearance color
Operating temperature/

Outer caseBlack (N 1.5)

Rating plate

Dark blue (5PB 2/6)

-10-＋55℃, 30-85%RH

humidity range
Storage temperature-40-＋70℃range■Type code designation

1 output type
●Signal transducer(1)

Products ListP

(2)

–(3)

(4)

(5)

3§ PLUG-IN TRANSDUCER §COMMON STANDARD SPECIFICATION/TYPE CODE DESIGNATION(1) Product (kind of conversion)
MarkProduct (kind of conversion)

TMark

Product (kind of conversion)

Isolator

CRT

Constant response (constant speed response)

Ultrahigh speed isolator

AMT

Analog memory

DT

Distributor

T***L

Isolator with lower limiter

LTLinearizer

RVT

Reverse isolator

SQT

Square

VFT

Analog pulse

RSignal switch

HST

SRT

Square root extraction

MT

Multiplying

UGT

Ultraslow pulse

DITDividing

PRTPulse rate

ALTAnalog limiter

PPTPulse isolator (2-output)

ADT

Adding(2) Dielectric strength voltage(3) / (4) / (5) Specification code

Mark

Dielectric strength voltage (50/60Hz)

None

Non-insulation

Input/output/auxiliary supply

1

AC1,500V between input/output, for 1 min.

2

AC2,000V between input/output, for 1 min.

●Sensor transducer

(1)

TP

(2)

–(3)

(4)

(5)

(1) Product (kind of input)
Mark(2) Dielectric strength voltage

Product (kind of input)

H

Thermoelectric temperature

RH

Resistance temperature

R

Potentiometer

MarkG

Revolution-speed (Frequency proportion)

GV

Revolution-speed (Voltage proportion)SSelsyn

SH

Thermoelectric alarm

SRH

Platinum alarm

Dielectric strength voltage (50/60Hz)

1

AC1,500V between input/output, for 1 min.

2

AC2,000V between input/output, for 1 min.

(3) / (4) / (5) Specification code
Kind of thermocouple, input, output, power source
Kind of thermal resistance, input, output, power source
Input, output, powerInput, normal operating voltage, output, power source●AC transducer

(1)

P2–

(2)

(3)

(4)

(1) Product (kind of input)

Dielectric strength voltage

MarkProduct (kind of input)

V

AC voltage (with waveform compensation, load fixation, need no power source)VT

AC voltage (with waveform compensation, need no power source)

VET

AC voltage (RMS value)A

AC current (with waveform compensation, load fixation, need no power source)AT

AC current (with waveform compensation, need no power source)

AET

AC current (RMS value)

FT

Frequency

AC2,000V(50/60Hz) between
input/output, for 1 min.

(2) / (3) / (4) Specification code
Input, output, power●DC power transducer

DWP1 – (1)

(2)

(3)

(4)

(5)

Dielectric strength voltage
AC1,500V(50/60Hz) between input/output, for 1 min.

(1) / (2) / (3) / (4) / (5) Specification code
Electric power, input 1, input 2, output, power source

Products List4§ PLUG-IN TRANSDUCER §COMMON STANDARD SPECIFICATION/TYPE CODE DESIGNATION

2-output type
●Signal transducer

W

(1)

P

(2)

–(3)

(4)

Product (kind of conversion)T(6)(2) Dielectric strength voltage(1)Product (kind of conversion)Mark(5)Isolator

DT

Distributor

SRDT

Square root extraction distributor

Mark

Dielectric strength voltage (50/60Hz)

2

AC2,000V between input/output, for 1 min.

(3) / (4) / (5) / (6) Specification code
Input, output, power source●Sensor transducer

W

(1)

P

(2)

-(3)

(4)

(5)

(6)

(7)

(1)Product (kind of input)
Mark(3) / (4) / (5) / (6) / (7) Specification code

Product (kind of input)

HT

Thermoelectric temperature

RHT

Resistance temperature

RT

Potentiometer

Kind of thermocouple, input, output, power source
Kind of thermal resistance, input, output, power source
Input, output, powerInput, normal operating voltage, output, power source(2)Dielectric strength voltage
Mark2

Dielectric strength voltage (50/60Hz)
AC2,000V between input/output, for 1 min.

●AC transducer

W

(1)

P

(2)

–

(3)

(4)

(5)

Product (kind of conversion)

VET

(7)

(2) Dielectric strength voltage(1)Product (kind of input)
Mark

(6)

AC voltage (RMS value)

AET

AC current (RMS value)

FT

Frequency

Mark

Dielectric strength voltage (50/60Hz)

2

AC2,000V between input/output, for 1 min.

(3) / (4) / (5) / (6) / (7) Specification codeInput, rated voltage (current), output, power source

Soft spec. type
●Signal transducer

C(1)

P

(2)

–(3)

(4)

(1)Product (kind of conversion)
MarkProduct (kind of conversion)

ADT

Adding/subtracting

MLT

Multiplying/dividingLT

Temperature/pressure correction

FGT

Function generating

AMT

Analog backup

VFT

Voltage pulse(5)(2) Dielectric strength voltage
Mark

Dielectric strength voltage (50/60Hz)

1

AC1,500V between input/output, for 1 min.

(3) / (4) / (5) Specification code
Input, output, power source●Programming unit
CCM-1
Products List5§ PLUG-IN TRANSDUCER § 2-output

W series■Common standard specifications●High quality/high reliability
Highly reliable electronic parts are adopted.
Aging tests of each part as well as burn-in aging test of the product under a high temperature areimplemented.
●PCB treatment
In order to reinforce insulation resistance stability of PCB surfaces and prevent the surfaces frominsulation deterioration, B side of the PCB was cleaned and coated with high humidity resistant varnish
after parts installation.
●Output limiter circuit
Even if an excessive input is applied, the product confines the output to about 1.5 times of rating andprotects the output side equipments.

■Type code designation●Signal transducer

W

(1)

P

(1) Product (kind of conversion)
markT
DT
SRDT

(2)

―

(3)

(4)

(5)

(6)

(2)Dielectric strength voltage

product
isolator
distributor
Distributor with square root
extraction

mark2(3)〜(6)

Dielectric strength voltage
AC2,000V between input andoutput(3) input(4) 1st output(5) 2nd output(6) auxiliary supply●Sensor transducer
W

(1)

P(2)

―(3)

(4)

(5)

(6)

(7)

(1) Product (kind of conversion)(2)Dielectric strength voltage(3)〜(7)

markHTRHTRT

mark(3) Kind of thermocouple/
thermal resistance(4) input(5) 1st output(6) 2nd output(7) auxiliary supply

product
Thermoelectric temperature
Resistance temperature
Potentiometer

2

Dielectric strength voltage
AC2,000V between input
and output

Potentiometer does not need above
mentioned (3). They consist of (4)-(7)●AC transducerW(1)(1) Product (kind of conversion)
markAETVETFTproductAC current
AC voltage
FrequencyP

(2)

―(3)

(4)

(5)

(2)Dielectric strength voltage
mark2

Dielectric strength voltage
AC2,000V between input
and output

(6)

(7)

(3)〜(7)(3) input(4) rated voltage(5) 1st output(6) 2nd output(7) auxiliary supply
AC current/voltage does not need above
mentioned (4). They consist of (3).(5)-(7)Products List1

§ PLUG-IN TRANSDUCER § 2-output

W series■Standard specifications
ItemSpecification

Tolerance% against output span

Influence of temperature

23±10℃ tolerance %Influence of frequency

45-65Hz tolerance %Characteristics

In conformity with JIS C 1111-1989 in tolerance

Response time
Output ripple
External adjustment ofoutput
Auxiliary supply
Overvoltage
Over current
Insulation resistanceMaterial of outer caseAppearance color
Operating temperature/humidity rang
Storage temperature
range

Products List(Reference) IEC, rated Hz±10% tolerance %Standard ≦1 sec. (Signal transducer and AC transducer ≦0.5 sec.) Time it takes to fall within±1% of the final steady-state when applied a stepped input.
≦1%p-p against output span
±5% adjustable
Depends on individual specifications.
input

2 times (10 sec.), 1.2 times (continuity) of rated voltage

Aux.supply

1.5 times (10 sec.), 1.2 times (continuity) of rated voltage

AC transducer

20 times (1 sec.), 1, 2 times (continuity) of rated current

Signal transducer

10 times (5 sec.), 1, 2 times (continuity)

Between input terminal, output terminal, auxiliary supply terminal and outer case (earth)≧50MΩ at DC500V
Fire-retardant ABS resin
Outer caseBlack (N 1.5)

Rating plate

Dark blue (5PB 2/6)

-10-＋55℃, 5-90%RH(no condensation)-40-＋70℃2§ PLUG-IN TRANSDUSER §Dimension■ Dimensions (mm)Fig.1
●Main body

8-pin type

●Socket (Type code: 8PFA by OMRON)

Also compatible with the following socket:
Type code: 8PFA-W by Omron*1: accessory for thermoelectric
temperature transducer*2: diode unit for current transducer

Fig.2●Main body

8-pin type

●Socket (Type code: 8PFA by OMRON)

Also compatible with the following socket:
Type code: 8PFA-W by Omron

Fig.3●Main body

11-pin type
●Socket (Type code: 11PFA by OMRON)Also compatible with the following socket:
Type code: 11PFA-W by Omron*1: accessory for thermoelectric
temperature transducer*2: diode unit for current transducer■Multiple unit installation (mm)●Panel mounting●Rail mounting●Multiplier (DM-1)

In consideration ofradiation of heat by anatural convection of air,please establish metricspaces more than thosementioned above.

Use a DIN standard 35mm rail.

Products List1