FINE SERIESPLUG-IN ALARM SETTER

PLUG-IN ALARM SETTERHigh & Low Limit Alarm of Various Sensor Inputs.

FSDEL

FEATURE■ COMPACT SIZE
- 2 output alarm setter with space saving plug-in type (width: 29.5mm).
■ DISPLAY FUNCTION- Adopted with organic EL display (OLED) for setting and measuring.
■ OUTPUT OPERATION LAMP (AL1/AL2)- Output operation can be check by output monitor lamp (red).
■ TEST FUNCTION- Output operation alarm can be checked without adding input.

SPECIFICATIONItems
Quantity
DC Voltage Input

Input

DC Current Input
Contact Composition &Output Points

Alarm Output

ContactCapacity

Maximum Switching Load

Minimum Switching Load
Mechanical Life
Electric Life

Auxiliary Supply

Auxiliary Supply Range(Power Consumption)
Inrush Current(Time Constant)Speciﬁcations
1 Circuit
DC60mV to 60V
DC±60mV to ±60V
DC1 to 50mA
DC±1 to ±50mA
1 Output: Change-over break before make contact (N.O. / N.C.)
2 Outputs: Both make Contact (N.O.) / Both break contact (N.C.)/ Make Contact (N.O.), break contact (N.C.)
AC125V 0.5A (load resistance)
DC110V 0.5A (load resistance)
AC125V 0.1A (inductive load cosφ=0.4)
DC110V 0.1A (inductive load L/R=7ms)
DC30V 0.5A (inductive load L/R=7ms)
DC10mV 10μA
More than 100,000,000 times (ON/OFF: 36,000 times/hour)
AC: More than 100,000 times (ON/OFF: 1,800 times/hour)
DC: More than 100,000 times (ON/OFF: 1,200 times/hour)
AC80 to 264V (rated AC110V 4.0VA , AC200/220V 5.5VA)
DC80 to 264V (rated DC110V 2.5W) AC/DC common use
DC19 to 30V (rated DC24V 2.0W)
AC110V below 1.6A (below 1.3ms), AC220V below 3.2A (below 1.3ms),
DC110V below 1.1A (below 1.3ms), DC24V below 1.9A (below 3.3ms)

RELAY CONTACT OPERATIONOutput Point:
Contact Composition
Auxiliary Supply OFF
orRelay Non-Excitation
Figures are
terminal number.*

Relay Excitation
Figures are
terminal number.** When socket (FW11) is attached.

1 Alarm Output:
N.O. / N.C.

2 Alarm Output:
Both N.O.

2 Alarm Output:
Both N.C.

2 Alarm Output:
N.O. (AL1), N.C. (AL2)

ORDERING INFORMATION Please specify the specification code at below.
TypeSpeciﬁcation CodeFSDEL -Input (Input Resistance)
DC1 to 5V (approx. 1MΩ)DC4 to 20mA (approx. 100Ω)(special speciﬁcation)ZZZ Other
Please specify when ordering.

0A80C7123450g
DIMENSIONS Weight: body approx. 105g, socket approx.
Unit: mm

Alarm Output
Output 1 Output 2
N.O. / N.C.
N.O.
N.O.
N.C.
N.C.
N.O.
N.C.

Auxiliary Supply
AC80 to 264V
F
DC80 to 264V
DC19 to 30V
5Power Fuse
1 Without Fuse
2 With Fuse

- Socket is a standard accessory (type: FW11). Please specify“without socket”, if socket is unnecessary.
- Please specify “socket type: FW11-W”, if M3 screw (with springwasher and plate washer) for socket terminal is desired.

MOUNTING METHODS

Unit : mm

Please use IEC DIN standard rail
35mm width (high strength type).
Recommended: Fuji Electric Co.,
Ltd. (type: TH35-15AL).

Screw Mounting
Rail Mounting(Possible to install side by side closely)SIDE
FRONT (Top: Body / Bottom: Socket)
Socket is standard accessory(type: FW11), and standard
terminal screw in socket is M3screw (with square washer).
The socket is unnecessary for thefine series installation base (type:FWBA).

CONNECTION DIAGRAM

The diagrams are part of specification example.

1 Output (N.O. / N.C.)

2 Outputs (2x N.O.)

2 Outputs (2x N.C.)

2 Outputs (1x N.O., 1x N.C.)

Socket(FW11)

SAFETY PRECAUTIONSHEAD OFFICETo ensure safety, technical knowledge is necessary when using this product. Please refer to manual instruction
for correct operation. Please check connection diagram carefully before performing connections. Please DO NOT
work with live wires. There is a risk of electric shock, device malfunction or fire.

11-13, Hitotsuya 1-chome,Adachi-ku, Tokyo 121-8639 Japan
TEL: +81-3-3885-2411
FAX: +81-3-3858-3966

http://www.daiichi-ele.co.jp/

NOTE: Reserves the right to update the specification without notification.

No.1803-0