Small-sized Plug-in Transducer
Fine Series Installation base FWBA
1-output/2-output dual purpose type■ Application
FWBA-08DY-B00

A multiple unit installation base which can house
both small-sized transducers and plug-in alarm
setters in a lot. It widely used in all kinds of plants.

289×99×62mm/1.0kg■ Feature
1.
2.
3.
4.
5.
6.
7.
8.

It is possible for each unit to ON/OFF byFWBA-16DY-B00
power switch individually.
479×99×62mm/1.6kg
Wiring is reducible because the power supply isNote: Neither mass nor the size display include the transducers.
package supply.
There are two types can be chosen, 16 units storable and 8 units storable.
Two types of mountings are available. Wall mounting and DIN rail mounting.
An induced lightning detection arrester can be installed in an input terminal
and an output terminal.
A terminal is available for 2 unit transducers for earth terminal of a lightningarrester.
Small-sized plug-in alarm setter (FSDLC) can be mounting.
It became more compact than conventional mounting base (FSBS/FWBS)■ Specification●How to specifyTypename

Specification code

FWBA -Storable quantity
16 : 16 units
08 : 8 units

Way of mounting
P : Wall mounting
D : DIN rail mounting

Individual powerswitch
Y : with switch
N : none-Hard model
B : Hard model B

B00

Pattern of 1st output
0: Terminal block

Pattern of 2nd output
0: Terminal block

Note: If transducers of different withstand voltage were installed in a case, and a withstand voltage test was implemented, transducers may bedamaged by test voltage. Be careful enough, please.
Input/output withstand voltage test of small-sized transducers and installation base should be carried out individually or carry out
voltage test of devices of the same strength with test voltage that all devices can bear.
Terminal E (ground terminal) is connected with the ground terminal for all arrestors. However, the ground terminal and the base (frame)are insulated.

■ Terminal blockSpecifications
Terminal screw
Matching cable
Matching crimping terminal*

Power source (earth)*
M4×8L W sems
1.25mm2, 2mm2
1.25-42-4
1.25-5Arrester (earth)

Input
M3×8L W sems
1.25mm2
1.25-3

Output
M3×8L W sems
1.25mm2
1.25-3*Name of crimping terminal
1.25 -3Nominal diameter of screw usedSection area of nominal strand wire mm2Products List3

Small-sized Plug-in Transducer
Fine Series Installation base FWBA
■ Compatible model for installation■Fine series●All kinds of transducers
CautionPlease use installation base FWBA for the AC current transducer specification code.
FSAT-4□X□X□□0FWAT-4□X□□□□0●Dummy box FSDB
●Small-sized plug-in alarm setter FSDLC■Lightning detection arrester UV-2-1E1-1111
Used as input and output protection
Either storage 1st output or 2nd output in output circuit.

Products List

4

Small-sized Plug-in Transducer
Fine Series Installation base FWBA
■FWBA-16□□-B00■Dimensions (mm)■Connection diagram1.

E terminal is all inner-connected. And E terminal and base (flame earth) is insulation.

2.

One FSDLC uses 2 transducer units space.

Wall mounting

DIN rail mounting

Note (1) The case of mounting on a DIN rail of height 15mm.
Use a rail of DIN standard 35mm width (enhanced type), please.

Products List

5

Small-sized Plug-in Transducer
Fine Series Installation base FWBA
■FWBA-08□□-B00■Dimensions (mm)■Connection diagram

1. E terminal is all inner-connected. E terminal and base (flame earth) is insulation.
2. One FSDLC uses 2 transducer units space.

Wall mounting

DIN rail mounting

Note (1) The case of mounting on a DIN rail of height 15mm.
Use a rail of IEC, DIN standard 35mmwidth (enhanced type), please
Recommended: TH35-15AL by Fuji Electric

Products List6

Small-sized Plug-in Transducer
Fine Series Installation base FWBA
■ FWBA accessory/sell separately mounting dimensions(mm)Reference FWBA-08□□-B00

US-1: Shunt resistance unit for AC current transducer (FSAT, FWAT). (Accessory)
RJC: Cold junction compensation sensor for thermoelectric transducer (FSHT, FWHT). (Accessory)
UR-2: Precision resistance unit for isolator and high-speed isolator (FSTT, FWTT, FSHS, FWHS) (sell separately)
UV-2: For signal arrestor (2-wire signal) (UV-2-1E1-1111 “View arrestor”) (sell separately)■ FWBA installation dimensional drawing(mm)Note (1): In consideration of device heat radiation, please set metric spaces more than those mentioned above. In case ofusing accessory or sell-separately items, please refer to FWBA accessory/sell separately mounting dimensions and takeenough wring spaces into considerations.

Products List7