機械設備工事必携 工事管理記録
（本 編）
大
総

目

次

則

································································· 総－ １

第１章

共通設備 ························································· １－ １

第２章

沈砂池設備 ······················································· ２－ １

第３章

主ポンプ設備 ····················································· ３－ １

第４章

送風機設備 ······················································· ４－ １

第５章

最初沈殿池設備 ··················································· ５－ １

第６章

反応タンク設備 ··················································· ６－ １

第７章

最終沈殿池設備 ··················································· ７－ １

第８章

消毒設備 ························································· ８－ １

第９章

用水設備 ························································· ９－ １

第 10 章

汚泥濃縮設備 ···················································· 10－ １

第 11 章

汚泥消化タンク設備 ·············································· 11－ １

第 12 章汚泥脱水設備 ···················································· 12－ １

第 13 章

流動床式汚泥焼却設備 ············································ 13－ １

第 14 章脱臭設備 ························································ 14－ １

第 15 章配管設備（ダクト設備を含む） ···································· 15－ １

目
総

次

則 ······································································· 総－１

第１節

共通事項 ························································ 総－１§１

目的 ·························································· 総－１§２

適用 ·························································· 総－１§３

本指針の概要及び管理の種類 ···································· 総－１§４

管理の実施 ···················································· 総－１§５

管理項目及び方法 ·············································· 総－２§６

基準値 ························································ 総－２§７

据付上の留意点 ················································ 総－２§８

あと施工アンカー（接着系）施工要領 ···························· 総－５§９簡易施工要領 ·················································· 総－21

目

第１章
第１節

次

共通設備 ························································· １－１
ポンプ設備 ······················································ １－１§１

無閉塞型汚泥ポンプ ············································ １－１§２

吸込スクリュ付汚泥ポンプ ······································ １－９§３

水中汚泥ポンプ ················································ １－９§４

吸込スクリュ付水中汚泥ポンプ ·································· １－15§５

床排水ポンプ ·················································· １－17§６給水ポンプ ···················································· １－19§７水中用水ポンプ ················································ １－21

§８

水中ミキサ ···················································· １－23§９圧力タンク式給水ユニット ······································ １－26

第２節

制水弁設備 ······················································ １－31

§１電動仕切弁 ···················································· １－31

§２

蝶形弁 ························································ １－39

§３

偏心構造弁 ···················································· １－41

§４

手動仕切弁 ···················································· １－41

§５

逆止弁（雨水・汚水用） ········································ １－41

§６

ソフトシール仕切弁 ············································ １－41

§７

テレスコープ弁 ················································ １－42

第３節

空気配管用弁設備 ················································ １－46§１

送気配管 ······················································ １－46

§２

逆止弁（空気用） ·············································· １－46§３電動仕切弁（空気用） ·········································· １－46

§４蝶形弁（空気用） ·············································· １－46

第４節
§１

ゲート設備 ······················································ １－47
鋳鉄製ゲート（沈砂池用） ······································ １－47

§２

鋳鉄製ゲート（水処理用） ······································ １－64

§３

鋳鉄製可動堰 ·················································· １－65

第５節

空気圧縮設備 ···················································· １－70

§１

可搬式小型空気圧縮機 ·········································· １－70

§２

空気槽 ························································ １－72

§３

除湿器（冷凍式） ·············································· １－75

§４

除湿器（分離膜式） ············································ １－77

第６節

搬出設備 ························································ １－79

§１

搬出ベルトコンベヤ ············································ １－79

§２

ホッパ ························································ １－83

第７節

クレーン設備 ···················································· １－87

§１電動式天井クレーン ············································ １－87

§２

ダブルレールホイスト式天井クレーン ···························· １－89

§３

シングルレールホイスト式天井クレーン ·························· １－89

§４手動式天井クレーン（クラブ式） ································ １－89

§５手動式天井クレーン（ギャードトロリーチェーンブロック式） ······ １－89

§６

ホイスト ······················································ １－89

§７－１

手動式チェーンブロック ········································ １－89

§７－２

電動式チェーンブロック ········································ １－89

目

第２章

次

沈砂池設備 ······················································· ２－１

第１節

ゲート設備 ······················································ ２－１

§１

第２節

鋳鉄製ゲート（沈砂池用） ······································ ２－１

除じん機械設備 ·················································· ２－１§１

スクリーン ···················································· ２－１§２

ロープ式けんすい型除じん機 ···································· ２－５§３

ロープ式台車型除じん機 ········································ ２－11§４連続式自動除じん機 ············································ ２－16§５間欠式自動除じん機（回転アーム型） ···························· ２－20§６間欠式自動除じん機（伸縮アーム型） ···························· ２－24

§７

裏がき式連続自動スクリーン ···································· ２－24§８

ベルト走行式自動スクリーン ···································· ２－28

§９

背面降下前面かき揚げ式除じん機 ································ ２－32

§10脱水機構付裏かきスクリーンユニット ···························· ２－36

§11

脱水機構付ドラム状スクリーン ·································· ２－40

第３節

除砂機械設備 ···················································· ２－47

§１

バケットコンベヤ沈砂かき揚げ機 ································ ２－47

§２

噴射式揚砂装置 ················································ ２－52

§２－１

揚砂機 ······················································ ２－52

§２－２集砂装置 ···················································· ２－56

§２－３

噴射式揚砂機用沈砂分離機 ···································· ２－64

§２－４

加圧水ポンプ（陸上ポンプ） ·································· ２－68

§２－５

加圧水ポンプ（水中ポンプ） ·································· ２－68

§２－６

加圧水タンク（鋼板製） ······································ ２－70

§２－７加圧水タンク（パネルタンク） ································ ２－74

§３

スクリュ式沈砂かき寄せ機 ······································ ２－76

第４節

沈砂処理設備 ···················································· ２－81§１

洗浄装置付トラフコンベヤ ······································ ２－81

§２サイクロン ···················································· ２－85

§３

沈砂洗浄機（ドラム回転式） ···································· ２－85

§４沈砂・しさ洗浄機（機械攪拌式） ································ ２－89

第５節

しさ処理設備 ···················································· ２－91

§１

しさ洗浄機（機械攪拌式） ······································ ２－91

§２

しさ洗浄機（圧力水噴射式） ···································· ２－91

§３しさ脱水機（ローラ式） ········································ ２－91

§４しさ脱水機（スクリュ式） ······································ ２－92

§５しさ脱水機（二軸対向スクリュ式） ······························ ２－93

第６節

搬出設備 ························································ ２－97

§１

沈砂・しさ搬出ベルトコンベヤ ·································· ２－97

§２

スキップホイスト ·············································· ２－97

§３

沈砂・しさ貯留ホッパ ·········································· ２-100§４

鋼製しさコンテナ ·············································· ２-100§５

樹脂製しさコンテナ ············································ ２-100

第７節

その他設備 ······················································ ２-101§１－１

破砕機（二軸差動式） ·········································· ２-101§１－２

スクリーン付破砕機（二軸差動式） ······························ ２-108§２破砕機（ドラム回転式） ········································ ２-113

目

第３章

次

主 ポンプ 設 備 ··············································· ３ － １

第 １節

ポン プ設備 ················································· ３ － １§１

立 軸 渦巻 斜流 ポン プ ········································ ３ － １§２

立 軸 斜流 ポン プ ············································ ３ － 12§３

水 中 汚水 ポン プ（ 口 径 150mm 以上） ·························· ３ － 31

§４

水 中 汚水 ポン プ（ 口 径 150mm 未満 80mm 以 上 ） ················· ３ － 33

§５

吸 込 スク リュ 付水 中 汚 水ポ ン プ ······························ ３ － 35

§６

先 行 待機 型立軸 斜 流 ポン プ ·································· ３ － 37

第 ２節

制水 弁設備 ················································· ３ － 41§１

電 動 仕切 弁 ················································ ３ － 41§２

電 動 蝶形 弁 ················································ ３ － 41§３

逆 止 弁（ 雨水 ・汚 水 用 ） ···································· ３ － 41

§４

フ ラ ップ 弁 ················································ ３ － 41

第 ３節

電動 機設備 ················································· ３ － 42§１

電 動 機···················································· ３ － 42

§２

起 動 制御 装置 ·············································· ３ － 42§３

液 体 速度 制御 装置 ·········································· ３ － 47

第 ４節

内燃 機関設 備 ··············································· ３ － 50

§１

ポ ン プ駆 動用 ディ ー ゼ ル機 関 ································ ３ － 50

§２

ポ ン プ駆 動用 横 型 二 軸式 ガ スタービ ン ························ ３ － 50

§３

燃 料 貯留 タン ク ············································ ３ － 50

§４

燃 料 小出 槽 ················································ ３ － 50

第 ５節

減速 機設備 ················································· ３ － 50

§１

傘 歯 車減速機 ·············································· ３ － 50

§２

複 合 減速 機（ 液体 継 手 内蔵 型 傘歯車 減 速機 ） ·················· ３ － 51

第 ６節

天井 クレー ン 設 備 ··········································· ３ － 51

§１

電 動 式天 井ク レー ン ········································ ３ － 51

§２

ダ ブ ルレ ール ホイ ス ト 式天 井 クレー ン ························ ３ － 51

§３

シ ン グル レー ルホ イ ス ト式 天 井クレ ー ン ······················ ３ － 51

§４

手 動 式天 井ク レー ン （ クラ ブ 式） ···························· ３ － 51

§５

手 動 式天 井ク レー ン （ ギャ ー ドトロ リ ーチ ェ ーン ブ ロック 式 ） ·· ３ － 51

§６

ホ イ スト ·················································· ３ － 51

§７ － １ 手 動 式チ ェー ンブ ロ ッ ク ···································· ３ － 51
§７ － ２ 電 動 式チ ェー ンブ ロ ック ···································· ３ － 51

第 ７節

冷却 設備 ··················································· ３ － 52§１

管 内 クー ラ ················································ ３ － 52

目

第４章

次

送 風機設 備 ················································· ４ － １

第 １節

送風機設 備 ················································ ４ － １§１

直 結式 多段 タ ーボ ブ ロ ワ ··································· ４ － １§２

歯 車増 速式 単 段タ ー ボ ブロ ワ ······························· ４ － 10§３

ロ ータ リ（ ル ーツ 式 ） ブロ ワ ······························· ４ － 12§４鋼 板製 直結 式 多段 タ ー ボブ ロワ ····························· ４ － 15

§５高 速軸 浮上 式 ター ボ ブ ロワ ································· ４ － 18

第 ２節

電動機設 備 ················································ ４ － 20

§１

高 圧電 動機 ··············································· ４ － 20§２低 圧電 動機 ··············································· ４ － 20

第 ３節

集中強制 潤滑 設 備 ·········································· ４ － 21§１

潤 滑油 タン ク ············································· ４ － 21§２

潤 滑油 ポン プ ············································· ４ － 27

§３

潤 滑油 冷却 器 ············································· ４ － 27

§４

潤 滑油 ヘッ ド タン ク ······································· ４ － 27

第 ４節

冷却水設 備 ················································ ４ － 29

§１

冷 却水 ポン プ ············································· ４ － 29

§２

冷

却

塔 ··············································· ４ － 29

第 ５節

空気ろ過 設備 ·············································· ４ － 33§１

湿 式空 気ろ 過 器 ··········································· ４ － 33

§２

乾 式空 気ろ 過 器（ 自 動 巻取 型） ····························· ４ － 36

§３

乾 式空 気ろ 過 器（ ろ 材 自動 清掃型） ························· ４ － 38§４

乾 式空 気ろ 過 器（ 吹 き 流し 型） ····························· ４ － 40

第 ６節

配管弁設 備 ················································ ４ － 42§１

送 気配 管 ················································· ４ － 42

§２

逆 止弁 （空 気 用） ········································· ４ － 42§３電 動仕 切弁 ··············································· ４ － 42

§４

蝶

形

弁 ··············································· ４ － 42

第 ７節

天井クレ ーン 設 備 ·········································· ４ － 43

§１

電 動式 天井 ク レー ン ······································· ４ － 43

§２

ダ ブル レー ル ホイ ス ト 式天 井クレー ン ······················· ４ － 43

§３

シ ング ルレ ー ルホ イ ス ト式 天井クレ ー ン ····················· ４ － 43

§４

手 動式 天井 ク レー ン （ クラ ブ式） ··························· ４ － 43

§５

手 動式 天井 ク レー ン （ ギャ ードトロ リ ーチ ェ ーン ブロック 式 ） · ４ － 43

§６

ホ イス ト ················································· ４ － 43

§７ － １

手 動式 チェ ー ンブ ロ ッ ク ··································· ４ － 43

§７ － ２電 動式 チェ ー ンブ ロ ッ ク ··································· ４ － 43

目

第５章

次

最 初沈殿 池 設備 ············································· ５ － １

第1節

汚泥かき 寄せ 機 ············································ ５ － １§１ － １

汚 泥か き寄 せ 機（ ﾁｪｰﾝﾌﾗｲﾄ式： ｽﾃﾝﾚｽﾌﾞｼｭﾄﾞﾁｪｰﾝ） ············ ５ － １§１ － ２

汚 泥か き寄 せ 機（ ﾁｪｰﾝﾌﾗｲﾄ式：合 成樹 脂 ﾁｪｰﾝ） ··············· ５ － ９§２

汚 泥 かき 寄 せ機 （ 中 央駆 動懸垂 型） ························· ５ － 10§３

汚 泥 かき 寄 せ機 （ 中 央駆 動支柱 型） ························· ５ － 16

第2節

ゲート設 備 ················································ ５ － 19§１

鋳 鉄製 ゲー ト （水 処 理 用） ································· ５ － 19§２

鋳 鉄製 可動 堰 ············································· ５ － 19

第３節

スカム除 去設 備 ············································ ５ － 19

§１

矩 形池 用手 動 式パ イ プ スキ マ ······························· ５ － 19§２

矩 形池 用電 動 式パ イ プ スキ マ ······························· ５ － 23

§３

無 動力 式ス カ ム除 去 装 置 ··································· ５ － 24§４

円 形池 用自 動 反転 式 パ イプ スキマ ··························· ５ － 27§５

円 形池 用電 動 式パ イ プ スキ マ ······························· ５ － 27

第４ 節

ス カム分 離 設 備 ··········································· ５ － 28

§１

か ご式 スカ ム 分離 機 ······································· ５ － 28

§２

回 転ス クリ ー ン式 ス カ ム分 離機 ····························· ５ － 28

§３

脱 水機 構付 裏 掻ス カ ム ユニ ット ····························· ５ － 30

第５ 節

汚 泥ポン プ 設 備 ··········································· ５ － 34§１

無 閉塞 型汚 泥ポ ン プ ······································· ５ － 34

§２

吸 込ス クリ ュ 付汚 泥 ポ ンプ ································· ５ － 34

§３

手 動仕 切弁 ··············································· ５ － 34

§４

逆 止弁 （汚 水 用） ········································· ５ － 34

§５電 動仕 切弁 ··············································· ５ － 34

§６

偏 心構 造弁 ··············································· ５ － 34

§７

水 中汚 泥ポ ン プ ··········································· ５ － 34

§８

吸 込ス クリ ュ 付水 中 汚 泥ポ ンプ ····························· ５ － 34

第６ 節

雑 排水設 備 ··············································· ５ ― 34§１

床 排水 ポン プ ············································· ５ － 34

目

第６章

次

反 応タン ク 設備 ············································· ６ － １

第 １節

多孔性散 気設 備 ············································ ６ － １§１

散 気筒 ··················································· ６ － １§２

散 気板 ··················································· ６ － ６

第 ２節

全面曝気 式散 気 設備 ········································ ６ － 10

§１

全 面曝 気式 散 気設 備 ······································· ６ － 10

第 ３節

超微細気 泡散 気 設備 ········································ ６ － 12§１

メ ンブ レン パ ネル 式 散 気装 置 ······························· ６ － 12§２

低 圧損 型メ ン ブレ ン 式 散気 装置（全 面 曝気 式 ） ··············· ６ － 17§３

低 圧損 型メ ン ブレ ン 式 散気 装置（旋 回 流式 ） ················· ６ － 37

第 ４節

非多孔性 散気 設 備 ·········································· ６ － 45

§１ － １

散 気器 （Ａ 形 ） ··········································· ６ － 45

§１ － ２散 気器 （Ｂ 形 ） ··········································· ６ － 48

第 ５節

散気装置 吊上 設 備 ·········································· ６ － 49

§１

吊 上装 置 ················································· ６ － 49

第 ６節

消泡設備 ·················································· ６ － 49

§１

消 泡ノ ズル ··············································· ６ － 49

第 ７節

配管設備 ·················································· ６ － 49

§１

送 気配 管 ················································· ６ － 49

第 ８節

ゲート設 備 ················································ ６ － 49§１

鋳 鉄製 ゲー ト （水 処 理 用） ································· ６ － 49§２

鋳 鉄製 可動 堰 ············································· ６ － 49

第 ９節

機械式曝 気設 備 ············································ ６ － 50

§１

水 中撹 拌式 曝気 装 置 ······································· ６ － 50

§２

縦 軸型 オキ シ デー シ ョ ンデ ィッチ用 機 械式 曝 気装 置 ··········· ６ － 56

§３

水 中 プ ロ ペ ラ 付 縦 軸 型 オ キ シ デ ー シ ョ ン デ ィ ッ チ 用 機 械 式 曝 気 装 置 ·· ６ － 60

§４

水 中プ ロペ ラ 付オ キ シ デー ションデ ィ ッチ 用 散気 式曝気装 置 ··· ６ － 64

§４ －１

水中プ ロ ペ ラ ······································· ６ － 64

§４ －２

散気装 置 ··········································· ６ － 68

§５横 軸型 オキ シ デー シ ョ ンデ ィッチ用 機 械式 曝 気装 置 ··········· ６ － 72

§６

ス クリ ュ型 オ キシ デ ー ショ ンディッ チ 用機 械 式曝 気装置 ······· ６ － 76

第 10 節好気 性ろ床 設 備 ··········································· ６ － 80

§１

好 気性 ろ床 ··············································· ６ － 80

目

第７章

次

最 終沈殿 池 設備 ············································· ７ － １

第 １節

汚泥かき 寄せ 機 ············································ ７ － １§１ － １

汚 泥か き寄 せ 機 (ﾁｪｰﾝﾌﾗｲﾄ式 :ｽﾃﾝﾚｽﾌﾞｼｭﾄﾞﾁｪｰﾝ) ··············· ７ － １§１ － ２

汚 泥か き寄 せ 機 (ﾁｪｰﾝﾌﾗｲﾄ式 :合成樹 脂 ﾁｪｰﾝ) ·················· ７ － １§２

汚 泥か き寄 せ 機（ 中 央 駆動 懸垂形） ························· ７ － １§３

汚 泥か き寄 せ 機（ 中 央 駆動 支柱形） ························· ７ － １

第 ２節

ゲート設 備 ················································ ７ － １§１

鋳 鉄製 ゲー ト （水 処 理 用） ································· ７ － １§２

鋳 鉄製 可動 堰 ············································· ７ － １

第 ３節

スカム除 去設 備 ············································ ７ － ２§１

矩 形池 用手 動 式パ イ プ スキ マ ······························· ７ － ２§２矩 形池 用電 動 式パ イ プ スキ マ ······························· ７ － ２§３

無 動力 式ス カ ム除 去 装 置 ··································· ７ － ２§４円 形池 用自 動 反 転 式 パイ プ スキマ ··························· ７ － ２§５円 形池 用電 動 式パ イ プ スキ マ ······························· ７ － ２

第 ４節

スカム分 離設 備 ············································ ７ － ２§１

か ご式 スカ ム 分離 機 ······································· ７ － ２

第 ５節

汚泥ポン プ設 備 ············································ ７ － ３§１

無 閉塞 形汚 泥 ポン プ ······································· ７ － ３§２

吸 込ス クリ ュ 付汚 泥 ポ ンプ ································· ７ － ３§３

手 動仕 切弁 ··············································· ７ － ３§４

逆 止弁 ··················································· ７ － ３§５電 動仕 切弁 ··············································· ７ － ３§６

偏 心構 造弁 ··············································· ７ － ３

§７

水 中汚 泥ポ ン プ ··········································· ７ － ３§８

吸 込ス クリ ュ 付水 中 汚 泥ポ ンプ ····························· ７ － ３

目

第８章

次

消 毒設備 ··················································· ８ － １

第1節

次亜塩素 酸ソ ー ダ注 入 設備 ·································· ８ － １§１

次 亜塩 素酸 ソ ーダ 注 入 ポン プ ······························· ８ － １§２

次 亜塩 素酸 ソ ーダ 貯 槽 ····································· ８ － ５

第2節

その他設 備 ················································ ８ － 10§１

塩 素接 触装 置 （水 路 設 置型 ） ······························· ８ － 10

目

第９章

次

用 水設備 ··················································· ９ － １

第 １節

用水処理 設備 ·············································· ９ － １§１

圧 力式 砂ろ 過 器 ··········································· ９ － １§２

浮 上ろ 材ろ 過 器 ··········································· ９ － ６§３移 床式 連続 式 砂ろ 過 器 ····································· ９ － ９§４

自 動洗 浄ス ト レー ナ ······································· ９ － 11§５

水 中用 水ポ ン プ ··········································· ９ － 14

§６

回 転ド ラム 式 ろ過 器 ······································· ９ － 15

目

次

第 10 章

汚泥濃縮 設備 ·············································· 10－ １

第 １節

重力濃縮 設備 ·············································· 10－ １§１

汚 泥か き寄 せ 機（ 中 央 駆動 懸垂 型 ） ························· 10－ １§２

汚 泥か き寄 せ 機（ 中 央 駆動 支柱 型 ） ························· 10－ １

第 ２節

機械濃縮 設備 ·············································· 10－ １§１

遠 心濃 縮機 ··············································· 10－ １§２

ベ ルト 型ろ 過 濃縮 機 ······································· 10－ 6

第 ３節

常圧浮上 濃縮 設 備 ·········································· 10－ 10§１

常 圧浮 上濃 縮 装置 ········································· 10－ 10§２空 気圧 縮機 ··············································· 10－ 14§３除 湿機 ··················································· 10－ 14§４

起 泡用 水ポ ン プ ··········································· 10－ 14§５凝 集剤 注入 ポ ンプ ········································· 10－ 15§６凝 集剤 溶解 槽 ············································· 10－ 19§７

凝 集剤 供給 機 ············································· 10－ 23§８起 泡助 剤注 入 ポン プ ······································· 10－ 28§９起 泡助 剤希 釈 槽 ··········································· 10－ 29§10

汚 泥供 給ポ ン プ ··········································· 10－ 32§11

脱 気槽 ··················································· 10－ 36

第 ４節

汚泥ポン プ設 備 ············································ 10－ 40§１

無 閉塞 形汚 泥 ポン プ ······································· 10－ 40§２

吸 込ス クリ ュ ー付 汚 泥 ポン プ ······························· 10－ 40§３

水 中汚 泥ポ ン プ ··········································· 10－ 40§４

吸 込ス クリ ュ ー付 水 中 汚泥 ポンプ ··························· 10－ 40§５手 動仕 切弁 ··············································· 10－ 40§６逆 止弁 （汚 水 用） ········································· 10－ 40

§７電 動仕 切弁 ··············································· 10－ 40§８偏 心構 造弁 ··············································· 10－ 40

第 ５節

その他設 備 ················································ 10－ 40§１

汚 泥貯 留槽 曝 気装 置 ······································· 10－ 40

目

次

第 11 章汚 泥消 化タ ンク 設 備 ·········································· 11－ １

第1節

センター ドー ム 設備 ········································ 11－ １§１

セ ンタ ード ー ム装 置 ······································· 11－ １§２

セ ンタ ード ー ム安 全 装 置 ··································· 11－ １§３

ガ ス撹 拌装 置 ············································· 11－ １§４機 械撹 拌装 置 ············································· 11－ ９§５低 速型 機械 撹拌 装 置 ······································· 11－ 16§６

蒸 気吹 込装 置 ············································· 11－ 22

第 ２節

汚泥ポン プ設 備 ············································ 11－ 25§１

無 閉塞 形汚 泥 ポン プ ······································· 11－ 25§２

吸 込ス クリ ュ 付汚 泥 ポ ンプ ································· 11－ 25§３

手 動仕 切弁 ··············································· 11－ 25§４

逆 止弁 ··················································· 11－ 25§５電 動仕 切弁 ··············································· 11－ 25§６

偏 心構 造弁 ··············································· 11－ 25

第 ３節

ガス撹拌 設 備 ·············································· 11－ 26§１

消 化ガ ス撹 拌ブ ロ ワ ······································· 11－ 26§２

消 化ガ ス安 全 装置 ········································· 11－ 31

第 ４節

脱硫設備 ·················································· 11－ 32§１連 続式 乾式 脱 硫装 置 ······································· 11－ 32§２間 欠式 乾式 脱 硫装 置 ······································· 11－ 32§３ク レー ン装 置 ············································· 11－ 37

第 ５節

ガス貯留 タン ク 設備 ········································ 11－ 38§１

乾 式低 圧ガ ス ホル ダ ······································· 11－ 38

第 ６節

加温設備 ·················································· 11－ 49§１

蒸 気ボ イラ ··············································· 11－ 49§２オ イル サー ビ スタ ン ク ····································· 11－ 56§３

軟 水装 置 ················································· 11－ 60§４

軟 水タ ンク ··············································· 11－ 64§５給 水ポ ンプ ··············································· 11－ 68§６

原 水タ ンク ··············································· 11－ 68§７

原 水ポ ンプ ··············································· 11－ 68§８

地 上定 置式 重 油タ ン ク ····································· 11－ 68§９

地 下重 油貯 蔵 タン ク ······································· 11－ 72§10

油 移送 ポン プ ············································· 11－ 79§11

煙 道 ····················································· 11－ 83§12

煙 突 ····················································· 11－ 83§13

ス チー ムヘ ッ ダ ··········································· 11－ 83§14

配 管（ ガス 、 蒸気 ） ······································· 11－ 83

第 ７節

温水器設 備 ················································ 11－ 84§１

温 水器 ··················································· 11－ 84§２オ イル サー ビ スタ ン ク ····································· 11－ 90§３

温 水ポ ンプ ··············································· 11－ 90§４

地 上定 置式 重 油タ ン ク ····································· 11－ 90§５地 下重 油貯 蔵タ ン ク ······································· 11－ 90§６

油 移送 ポン プ ············································· 11－ 90§７煙 道 ····················································· 11－ 90§８

煙 突 ····················································· 11－ 90

第 ８節

熱交換器 設備 ·············································· 11－ 91§１

二 重管 式汚 泥 熱交 換 器 ····································· 11－ 91§２

ス パイ ラル 式汚 泥 熱 交 換器 ································· 11－ 91

第 ９節

余剰ガス 燃焼 設 備 ·········································· 11－ 96§１

余 剰ガ ス燃 焼 装置 （ 炉 内燃 焼 型） ··························· 11－ 96

目

次

第 12 章汚泥脱水設備 ···················································· 12－１

第1節

加圧型脱水設備 ·················································· 12－１

§１

加圧ろ過機 ···················································· 12－１

§２

汚泥打込ポンプ ················································ 12－８

第2節
§１

遠心型脱水設備 ·················································· 12－９
遠心脱水機（標準型） ·········································· 12－９
遠心脱水機（高効率型） ········································ 12－９

第３節

ベルトプレス型脱水設備 ········································· 12－17§１

ベルトプレスろ過機（標準型） ·································· 12－17
ベルトプレスろ過機（高効率型） ································ 12－17

第４節

多重円板型脱水機設備 ··········································· 12－24§１

多重円板型脱水機 ·············································· 12－24

第５節

造粒調質設備（ベストシステム） ································· 12－29§１

造粒調質ユニット ·············································· 12－29§２無機凝集剤貯留タンク ·········································· 12－32§３無機凝集剤供給ポンプ ·········································· 12－33§４両性高分子凝集剤受入ホッパ及び供給機 ·························· 12－39§５両性高分子凝集剤溶解タンク ···································· 12－39§６両性高分子凝集剤供給ポンプ ···································· 12－41

第６節

多重板型スクリュプレス脱水機設備 ······························· 12－43§１

多重板型スクリュプレス脱水機 ·································· 12－43

第７節

圧入式スクリュプレス脱水機設備 ································· 12－48§１

圧入式スクリュプレス脱水機 ···································· 12－48

第８節

回転加圧脱水機設備 ············································· 12－53§１

回転加圧脱水機 ················································ 12－53

第９節

給泥設備 ······················································· 12－59§１

破砕ポンプ ···················································· 12－59§２

無閉塞型汚泥ポンプ ············································ 12－61§３

一軸ねじ式汚泥ポンプ ·········································· 12－61§４

汚泥サービスタンク ············································ 12－61§５

凝集混和タンク ················································ 12－63§６

汚泥貯留タンク用ミキサ ········································ 12－65

第 10 節

脱水汚泥搬送貯留設備 ·········································· 12－67§１

脱水汚泥搬送コンベヤ ·········································· 12－67§２

脱水汚泥移送ポンプ（一軸ねじ式） ······························ 12－67§３

脱水汚泥移送ポンプ（ピストン式） ······························ 12－69§４

脱水汚泥貯留ホッパ ············································ 12－71

第 11 節無機凝集剤用薬注設備 ·········································· 12－71§１

無機凝集剤貯留タンク ·········································· 12－71§２

塩鉄希釈タンク ················································ 12－72§３

薬液供給ポンプ ················································ 12－74§４消石灰サイロ ·················································· 12－76§５消石灰輸送コンベヤ ············································ 12－80§６

消石灰２次ホッパ ·············································· 12－82§７消石灰定量供給機 ·············································· 12－82§８

消石灰溶解タンク ·············································· 12－82

第 12 節高分子凝集剤用薬注設備 ········································ 12－84§１

薬品受入ホッパ及び供給機 ······································ 12－84§２

薬品溶解タンク ················································ 12－84§３

薬液供給ポンプ（一軸ねじ式） ·································· 12－86

第 13 節付帯設備 ······················································ 12－86§１

給水ポンプ ···················································· 12－86§２

空気圧縮機 ···················································· 12－86§３

空気槽 ························································ 12－86§４

除湿器 ························································ 12－86

目

次

第 13 章

流動床式汚泥焼却設備 ············································ 13－1

第1節

設計条件 ························································ 13－1

第2節

汚泥供給設備 ···················································· 13－1§１定量フィーダ ·················································· 13－1§２

計量コンベヤ ·················································· 13－3

第３節

焼却設備 ······················································· 13－4

§１

流動床焼却炉 ·················································· 13－4§２

補助燃料装置 ·················································· 13－8§３

脱水汚泥投入機 ················································ 13－8

第４節

空気予熱装置 ··················································· 13－9§１

空気予熱器 ···················································· 13－9§２

流動ブロワ ···················································· 13－11§３昇圧ブロワ（又はバーナーブロワ） ······························ 13－11

第５節

白煙防止設備 ··················································· 13－12§１

白煙防止予熱器 ················································ 13－12§２白煙防止ブロワ ················································ 13－12

第６節

集塵装置 ······················································· 13－13§１

バグフィルタ ·················································· 13－13§２サイクロン ···················································· 13－17§３サイクロン灰搬出機 ············································ 13－17§４

灰ホッパ ······················································ 13－17

第７節

排煙処理装置 ··················································· 13－18§１

排煙処理塔 ···················································· 13－18§２

苛性ソーダ貯槽 ················································ 13－20§３

苛性ソーダ供給ポンプ ·········································· 13－20§４洗浄水循環ポンプ ·············································· 13－20§５給水ポンプ ···················································· 13－20

第８節

排煙装置 ······················································· 13－21§１

誘引ファン ···················································· 13－21§２

煙突 ······················································ 13－21

第９節

燃料装置 ······················································· 13－21§１

燃料タンク ···················································· 13－21§２オイルポンプ ·················································· 13－21

第 10 節空気圧縮設備 ··················································· 13－22§１

空気圧縮機 ···················································· 13－22

§２

空

気

槽 ···················································· 13－25

§３

除

湿

器 ···················································· 13－25

第 11 節電気集塵装置 ··················································· 13－26§１－１

乾式電気集塵機 ················································ 13－26§１－２

湿式電気集塵機 ················································ 13－29§２

灰輸送コンベヤ ················································ 13－29

第 12 節

排煙ダクト及び配管 ············································· 13－29§１

排煙ダクト ···················································· 13－29§２

配管 ························································ 13－29

第 13 節電気計装設備 ··················································· 13－29§１

計装設備 ······················································ 13－29

目

次

第 14 章脱臭設備 ·················································· 14－ １

第 １節

設計条件 ·················································· 14－ １

第 ２節

臭気ガス 吸引 装 置 ·········································· 14－ １§１

吸 引フ ァン ··············································· 14－ １§２

換 気用 風道 及 びダ ン パ ー ··································· 14－ ６

第 ３節

薬液洗浄 脱臭 装 置 ·········································· 14－ ６§１

立 型薬 液洗 浄 塔 ··········································· 14－ ６§２横 型薬 液洗 浄 塔 ··········································· 14－ ９§３

薬 液貯 留タ ン ク ··········································· 14－ 12§４薬 液注 入ポ ン プ ··········································· 14－ 14§５

循 環タ ンク ··············································· 14－ 16§６

循 環ポ ンプ ··············································· 14－ 18§７中 和タ ンク ··············································· 14－ 23

第 ４節

オゾン及 び薬 液 脱臭 装 置 ···································· 14－ 23

第 ５節

残留オゾ ン除 去 装置 （ 薬液洗浄 ） ···························· 14－ 23

第 ６節

残留オゾ ン除 去 装置 （ 接触分解 槽） ·························· 14－ 23

第 ７節

吸着脱臭 装置 ·············································· 14－ 24§１

吸 着塔 ··················································· 14－ 24

第 ８節

土壌脱臭 装置 ·············································· 14－ 29§１

土 壌脱 臭床 ··············································· 14－ 29

第９ 節

充 填塔式 生 物 脱臭 装 置 ····································· 14－ 31§１

充 填塔 式生 物 脱臭 装 置 ····································· 14－ 31

目

次

第 15 章配管設備 ·················································· 15－ １

第 １節

共通事項 ·················································· 15－ １§１

配 管設 備の 区 分 ··········································· 15－ １§２

材 料の 規格 ··············································· 15－ １§３

弁 類 ····················································· 15－ １§４配 管支 持及 び 基礎 ········································ 15－ １

第 ２節

配管ダク ト施 工 一般 フ ローチャ ート ·························· 15－ ３§１

一 般配 管 ················································· 15－ ３§２ダ クト 施工 一 般フ ロ ー チャ ート ····························· 15－ ６

第 ３節

管材別施 工要 領 ············································ 15－ ８§１

ダ クタ イル 鋳 鉄管 配 管 ····································· 15－ ８§２鋼 管配 管 ················································· 15－ 29§３

ス テン レス 鋼管 、 配 管 ····································· 15－ 32§４塩 化ビ ニー ル 管 ··········································· 15－ 34§５ラ イニ ング 鋼 管 ··········································· 15－ 36§６

銅 及び 銅合 金 継目 無 管 ····································· 15－ 38

第 ４節

使用目的 別配 管 施工 要 領 ···································· 15－ 40§１

下 水用 配管 ··············································· 15－ 40§２

汚 泥配 管 ················································· 15－ 42§３

空 気配 管 ················································· 15－ 46§４雑 用水 配管 ··············································· 15－ 47§５上 水用 配管 ··············································· 15－ 48§６

蒸 気配 管、 温 水配 管 、 シー ル水配管 ························· 15－ 50§７

油 用配 管､集 中 給油 管 ······································ 15－ 52§８

消 化ガ ス配 管 ············································· 15－ 58§９

脱 水汚 泥圧 送管 ··········································· 15－ 61

§10

薬 液配 管 ················································· 15－ 62

第 ５節

試験 ······················································ 15－ 65§１

一 般配 管試 験 （水 圧 、 空気 圧、通水 （ 気） 試 験） ············ 15－ 65

第 ６節

基礎サポ ート 施 工要 領 ······································ 15－ 74§１

基 礎サ ポー ト 施工 要 領 ···································· 15－ 74§２

標 準サ ポー ト と垂 直 荷 重に よるサポ ー ト選 定 ················· 15－ 78

今 年 度 版で の 改 定個所は 、 ゴ シッ ク で 示す。