PATLABOR™

INSTRUCTION MANUAL

CC-Link TOWER LIGHT(small size, 60 mm dia., 1 - 5 layers)

BEFORE USE ....
Thank you for choosing us. Before use, please check contents of the package you received as outlined below.
If you have any problems or questions with the product,
please contact our sales office or representatives.
■ PACKAGE INCLUDES:Tower Light..........................................................................(1)■ MODEL NO.
Confirm Model No. marking on the product to be exactly
what you ordered.
■ INSTRUCTION MANUALThis manual describes necessary points of caution whenyou use this product, including installation, connection andbasic maintenance procedures.

POINTS OF CAUTION■ CONFORMITY WITH EU DIRECTIVES• This equipment is suitable for Pollution Degree 3 andInstallation Category III (24V DC power model), or Pollution Degree 2 and Installation Category II (100 – 240V
AC power model). Reinforced insulation (network topower: 300V) is maintained. Prior to installation, checkthat the insulation class of this unit satisfies the system
requirements.
• Altitude up to 2000 meters.
• The equipment must be installed such that appropriate
clearance and creepage distances are maintained to conform to CE requirements. Failure to observe these requirements may invalidate the CE conformance.
• The actual installation environments such as panel configurations, connected devices, connected wires, may affect the protection level of this unit when it is integrated
in a panel system. The user may have to review the CE
requirements in regard to the whole system and employ
additional protective measures to ensure the CE conformity.
• The equipment is intended to be installed in a industrial
environment defined by EN 60947-5-1.

MODELIT60SRC■ POWER INPUT RATING & OPERATIONAL RANGE• Locate the power input rating marked on the product andconfirm its operational range as indicated below:		 100 – 240V AC rating: 85 – 264V, 47 – 66 Hz						approx. 7.5VA at 100V AC						approx. 10VA at 200V AC						approx. 11VA at 240V AC		 24V DC rating: 24V ±10%, approx. 5W■ GENERAL PRECAUTIONS• Before you remove the unit or mount it, turn off the power
supply for safety.
• The unit must not be subjected to external force.
• Do not rub the unit with organic solvent like paint thinner.
■ ENVIRONMENT• Indoor use.
• Do not install the unit where it is subjected to continuousvibration. Do not subject the unit to physical impact.
• Environmental temperature must be within -10 to +55°C(14 to 131°F) with relative humidity within 30 to 90% RH
in order to ensure adequate life span and operation.
• Mount the unit on a flat and robust plate.
• Lamps are omnidirectional.
• The buzzer sound is directional in front of the unit.
■ INGRESS PROTECTION (IP65)• The IP code is conformable when the unit is mounted vertically, and the control panel cover is locked. The compartment, where connectors are located, is not protected.
• When opening the control panel cover, avoid humidityand dust penetration. Dry and clean it if condensation isformed, and close the cover locking tightly.
• In order to protect ingress of water or dust into the bottom compartment, mount the unit on the flat plane, andbe sure that the gasket does not roll back or dust is noton the gasket.
■ WIRING• Do not install cables close to noise sources (relay drive
cable, high frequency line, etc.).
• Do not bind these cables together with those in which
noises are present. Do not install them in the same duct.
■ AND ....
• The unit is designed to function as soon as power is supplied, however, a warm up for 10 minutes is required forsatisfying complete performance described in the datasheet.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3

P. 1 / 6

IT60SRCCOMPONENT IDENTIFICATION■ FRONT VIEW (with the cover open)■ BOTTOM VIEW

Lamp 1
Lamp 2FRONTPower Error RDLamp 3

Terminator SWSDRunLamp 4→ON

Lamp 5

Mode

Status Indicator LED

CC-Link Connector

Power Error RDDIP SWRunSD

7 80 1

234 56

9Station No.
Rotary SW

90 1

7 82394 56

2 30 123456

90 1

7 8

90 1456

7 8

Baud Rate Setting
Rotary SW

2 3456

7 890 1

234 56

7 8Buzzer Aperture
Gasket■ STATION NO.
Station No. is selected between 1 and 64 in decimal. The
left switch determines the tenth place digit, while the rightswitch does the ones place digit of the address.
Station No. setting (×10)

90145690178

Station No. setting (×1)

23456

7823

■ BAUD RATEBaud Rate is selected with the rotary switch.
23456

0 : 156 kbps
1 : 625 kbps
2 : 2.5 Mbps
3 : 5 Mbps
4 : 10 Mbps

901

78

■ OPERATING MODE(*) Factory setting• Lamp blinking frequency
Mode-1OFFON

LAMP BLINKING FREQUENCY
Approx. 2 Hz (*)
Approx. 10 Hz• Buzzer intermittent frequency
Mode-2OFFON

BUZZER INTERMITTENT FREQUENCY
Approx. 2 Hz (*)
Approx. 10 Hz• Buzzer volume

Baud Rate Setting■ CC-Link CONNECTOR

Mode-3
OFFOFFONONMode-4OFFONOFFONBUZZER VOLUME
Quiet (*)
MiddleLoudMaximum• Output at the loss of communication
12345

1. FE
2. SLD
3. DG
4. DB
5. DA

FE
ShieldYellow
WhiteBlue

Mode-6OFFON

OUTPUT AT THE LOSS OF COMMUNICATION
Reset the output (turned off) (*)
Hold the output (maintains the last data
received normally)

Note 1: Blinking of lamps and buzzer intermittences are notsynchronized.
Note 2: Be sure to set unused Mode-5, -7 and -8 to OFF.

■ TERMINATING RESISTOR
To use the terminating resistor, turn the switch ON, andOFF to invalidate. (Factory setting OFF)MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3P. 2 / 6

IT60SRC

INDICATORS■ STATUS INDICATOR
PowerRunError

SD*1

RD

STATUS*2

ONONBLBL

ON

Communicates normally with occasional CRC errors due to noise interference.

ONONBLBL

ON

Communicates normally but the Baud Rate and/or Station Address switches failed. Error
indicator blinks approximately in 0.5 seconds intervals.

ONONBLBLOFF----ONONBLOFFON

CRC error found in the received data. Unable to respond.

ON

ON

BL

OFF

OFF

----

ON

ON

OFF

BL

ON

Normal communication

ON

ON

OFFBL

OFF

----

ON

ON

OFF

OFF

ON

Unable to receive data addressed to the station.

ON

ON

OFF

OFF

OFF

----

ON

OFF

BL

BL

ON

Performs the interval-timed responses but CRC error found in receiving the refresh data.

ON

OFF

BL

BL

OFF

----

ON

OFF

BL

OFF

ON

CRC error found in the data addressed to the station.

ON

OFF

BL

OFF

OFF

----

ON

OFF

OFF

BL

ON

Link is not started.

ON

OFF

OFF

BL

OFF

----

ON

OFF

OFF

OFF

ON

No data addressed to the station. Or unable to receive data addressed to the station due
to noise interference. (Missing parts of the data sent from the master)OFF

Unable to receive data due to wire breakdown

ONOFF

OFFOFFONOFFONOFF ON/OFF Faulty Baud Rate and/or Station Address setting

OFFOFF

OFF

OFF

OFF

Power input removed. Or power supply failure.

OFF = OFF, ON = ON, BL = Blinking*1. SD LED may look not blinking but ON with high baud rate and fewer connected modules.
*2. LEDs indicated with “----” in STATUS rarely occurs in normal operation. (LED failure or the like as possible cause).

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3

P. 3 / 6

IT60SRCDATA ALLOCATION
0Interval-timed Response (X)Refresh Data (Y)0

RY (n + 0) F to RY (n + 0) 0
F Unused

F

1F

1F

UnusedI/O DATA DESCRIPTIONS■ OUTPUT DATA
150Output 0
Output 1::
Output 15

OutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutputOutput0123456789101112131415

Lamp 1
Lamp 2
Lamp 3Lamp 4Lamp 5
Buzzer0: Off,0: Off,0: Off,
0: Off,0: Off,0: Off,

1: On
1: On
1: On
1: On
1: On
1: Continuous

Lamp 1
Lamp 2
Lamp 3
Lamp 4Lamp 5
Buzzer0: Off,0: Off,0: Off,0: Off,0: Off,0: Off,

1: Blinking
1: Blinking
1: Blinking
1: Blinking
1: Blinking
1: Intermittent

Note: If “On” (Continuous) and “Blinking” (Intermittent)
are set simultaneously for a single lamp (buzzer),“Blinking” (Intermittent) is disabled.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3P. 4 / 6

IT60SRCTERMINAL CONNECTIONSConnect the unit as in the diagram below.
■ EXTERNAL DIMENSIONS unit: mm
60±1.5dia.

A±4Control Panel Cover1 – 6 lengths*1

Lamp Layers
12345

A
224
256288320352

Approx.1500

3 Bolts and Nuts (M4)

Lead wires

60±1.5 dia.
5±1.

43.
dia(30 dia.)■ CONNECTION DIAGRAM.

*1. Consult us for other bolt length.

■ MOUNTING REQUIREMENTS unit: mm.*DA

To other CC-Link devices

5DB4DG3SLD2FE1leirW

FE

Hodia

43 dia.

Gray U(+)
POWERing

30Black V(−)

3 Holes (5 dia.)

Green/Yellow FE1120°

Front*Protect wires to prevent scratching them at the edge of thecompartment.

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3P. 5 / 6IT60SRC

COMMUNICATION CABLE CONNECTIONS■ MASTER CONNECTION
Master UnitTERMINATOR

blueDA
white
DB
yellow
DG
SLDFG

Remote Unit

Remote Unit

DA
DB
DG
SLD
FE

DA
DB
DG
SLD
FE

TERMINATOR

Be sure to connect the terminating resistor across DA and DB at both ends of communication line.
When this unit is located at an end, turn the terminating resistor SW ON.
The Master Unit can be located at not only both ends but also any node of the of communication line.

WIRING INSTRUCTIONS■ TENSION-CLAMP TERMINAL
Applicable wire size: 0.2 to 1.25 mm2Stripped length: 10 mm
Recommended solderless terminal• AI0,5−10WH 0.5 mm2 (Phoenix Contact)• AI0,75−10GY 0.75 mm2 (Phoenix Contact)

MG CO., LTD. www.mgco.jp
5-2-55 Minamitsumori, Nishinari-ku, Osaka 557-0063 JAPANEM-2383 Rev.3

P. 6 / 6