Smart Energy Controller
SUN2000-3-10KTL-M1 (High Current Version)

Active Safety

Higher Yields

Battery Ready

Flexible Communication

AI Powered
Active Arcing Protection

Up to 30% More Energy
with Optimizer 1

Plug & Play battery interface 2

WLAN, Fast Ethernet, 4GCommunication Supported

Efficiency Curve

Circuit Diagram

Efficiency [%]100%

DC
Switch

98%

PV1+

96%

PV1-

DC/AC
Converter

EMI
FilterOutputIsolation Relay

PV2L1

94%

PV2+
OutputFilter

92%EMI
Filter

L2
L390%

SPD0%

20%

40%
470 V

60%
600 VNPE

BAT+BAT-80%
850 VSPD100%

Load [%]

SUN2000-3/4/5/6/8/10KTL-M0/M1*1 Only applicable to SUN2000-3/4/5/6/8/10KTL-M1smart energy center.
*2. SUN2000-3/4/5/6/8/10KTL-M0 will be compatible with HUAWEI smart string ESS in Q1, 2021

11SOLAR.HUAWEI.COM/MEA

SUN2000-3/4/5/6/8/10KTL-M1 (High Current Version)

Technical Specification
Technical Specification

SUN2000-3KTL-M1

SUN2000-4KTL-M1

SUN2000-5KTL-M1

98.2%
96.7%

98.3%
97.1%

98.4%
97.5%

4,500 Wp

6,000 Wp

7,500 Wp

SUN2000-6KTL-M1

SUN2000-8KTL-M1

SUN2000-10KTL-M1

98.6%
97.7%

98.6%
98.0%

98.6%
98.1%

9,000 Wp

12,000 Wp

15,000 Wp

8,800 W

10,000 W

8,000 W
8,800 VA

10,000 W
11,000 VA 4

13.5 A

16.9 A

3,300 VA

3,300 VA

15 A

15 A

Efficiency
Max. efficiency
European weighted efficiency

Input (PV)
Recommended max. PV power 1
Max. input voltage 2
Operating voltage range 3
Start-up voltage
Rated input voltage
Max. input current per MPPT
Max. short-circuit current
Number of MPP trackers
Max. input number per MPP tracker

1,100 V
140 V ~ 980 V
200 V
600 V
13.5 A
19.5 A
21Input (DC Battery)
Compatible Battery
Operating voltage range
Max operating current
Max charge PowerMax discharge Power3,300 W

4,400 WHUAWEI Smart String ESS 5kWh – 30kWh
600 V ~ 980 V
16.7 A
10,000 W
5,500 W
6,600 W

Output (On Grid)
Grid connection
Rated output power
Max. apparent power
Rated output voltage
Rated AC grid frequency
Max. output current
Adjustable power factor
Max. total harmonic distortion

3,000 W
3,300 VA

4,000 W
4,400 VA

5.1 A

6.8 A

Three-phase5,000 W
6,000 W
5,500 VA
6,600 VA
220 Vac / 380 Vac, 230 Vac / 400 Vac, 3W / N+PE
50 Hz / 60 Hz
8.5 A
10.1 A
0.8 leading ... 0.8 lagging≤3%

Output (Off Grid)
Backup Box
Maximum apparent power
Rated output voltage
Maximum output current
Power factor range

3,000 VA

3,300 VA

13.6 A

15 A

Backup Box – B1
3,300 VA
3,300 VA
220 V / 230 V
15 A
15 A
0.8 leading ... 0.8 lagging

Features & Protections
Input-side disconnection device
Anti-Islanding protection
DC reverse polarity protection
Insulation monitoring
DC surge protection
AC surge protection
Residual current monitoring
AC overcurrent protection
AC short-circuit protection
AC overvoltage protection
Arc fault protection
Ripple receiver control
Integrated PID recovery 5
Battery reverse charging from grid

Yes
Yes
Yes
Yes
Yes, compatible with TYPE II protection class according to EN/IEC 61643-11
Yes, compatible with TYPE II protection class according to EN/IEC 61643-11
Yes
Yes
Yes
Yes
Yes
Yes
Yes
Yes

Operating temperature range
Relative operating humidity
Max. operating altitude
Cooling
Display
Communication
Weight (incl. mounting bracket)
Dimension (incl. mounting bracket)Degree of protection
Nighttime Power Consumption-25 ~ + 60 °C (-13 °F ~ 140 °F)
0 %RH～100 %RH
4,000 m (13,123 ft.) (Derating above 2000 m)
Natural convection
LED Indicators; Integrated WLAN + FusionSolar App
RS485; WLAN/Ethernet via Smart Dongle-WLAN-FE; 4G / 3G / 2G via Smart Dongle-4G (Optional)
17 kg (37.5 lb)
525 x 470 x 146.5 mm (20.7 x 18.5 x 5.8 inch)
IP65< 5.5 W 6General Data

Optimizer Compatibility
DC MBUS compatible optimizer

SUN2000-450W-P

Standard Compliance (more available upon request)
Certificate
Grid connection standards

EN/IEC 62109-1, EN/IEC 62109-2, IEC 62116
G98, G99, EN 50438, CEI 0-21, VDE-AR-N-4105, AS 4777, C10/11, ABNT, UTE C15-712, RD 1699, TOR D4, NRS 097-21, IEC61727, IEC62116, DEWA

*1 Inverter max input PV power is 20,000 Wp when long strings are designed and fully connected with SUN2000-450W-P power optimizers.
*2 The maximum input voltage is the upper limit of the DC voltage. Any higher input DC voltage would probably damage inverter.
*3 Any DC input voltage beyond the operating voltage range may result in inverter improper operating. *4 C10 / 11: 10,000 VA*5 SUN2000-3~10KTL-M1 raises potential between PV- and ground to above zero through integrated PID recovery function to recover module degradation from PID. Supported module types include: P-type (mono, poly).
*6. <10 W when PID recovery function is activated.

SOLAR.HUAWEI.COM/MEA

12