Variable Speed Drive

High-performance Drive

Variable Speed Drive for Industry

Built-in Ethernet

Real Time ClockWeb Server

QR Code ®

Video Guidance

Remote Sensor
Monitoring

IoT / Industry 4.0 Ready
The high performance TOSHIBA VF-AS3 achieves high speed/real time network
communication via embedded Ethernet without any optional devices, ready to meet therequirement of modern automation with IoT and Industry 4.0.

Compatible with
the World’s Ma(EC Directive(CAlso, VF-AS3 with TOSHIBA excellent motor control technology and hardware design
helps for all your applications.

Applicable motor capacity (kW) : Multi ratings
Voltage class

HD

0.4

0.75

1.5

2.2

4.0

5.5

7.5

11

15

18.5

22

30

37

45

55

75

90

110

132

160

200

220

280

ND

0.75

1.5

2.2

4.0

5.5

7.5

11

15

18.5

22

30

37

45

55

75

90

110

132

160

220

250

280

315

3ph-240V class(IP20/IP00)
3ph-480V class(IP20/IP00)
3ph-480V class(IP55)

A1

A2

A3

A4

A5

A6

A1

A2

A3

A4

A5

A1E

A2E

A3E

A4E

A5E

A6

A7

A8

*A1 to A8 and A1E to A5E show frame size of the drives

Contents
Evolution to IoT-Ready drive.

P3

Standard specifications

P10

For drive users

P19

Ideal for various applications.

P5

External dimensions

P15

Peripheral devices

P23

All-in-One. Improvement in Usability.

P7

Standard connection diagrams

P17

Insert type options

P24

Basic functions

P9

Terminal functions

P18

Totally enclosed box type for IP55

P34

2

High-performance Drive

Evolution to
IoT-Ready drive.
The VF-AS3 is an IoT-Ready variable speed drive.
Using Internet, the VF-AS3 provides various
solutions to you.

Built-in Dual Ethernet PortWeb Server

QR Code ®

The VF-AS3 has an embedded Ethernet dual port adaptor that canbe used in the following Modbus TCP and EtherNet/IP. The adaptor
provides a set of services at the Ethernet and TCP/IP level.

The VF-AS3 has an embedded Web Server function, and it can beeasily accessed and manage the operating condition remotely fromyour PC or Smart Phone/tablet devices. It can be monitored bystandard web browser without any special software.

For the advanced information and the event of drive fault, VF-AS3
displays the QR Code ®(*1), which will provide immediate access to a
dedicated web link for support and maintenance.

The widgets can be customized easily. The integrated web server isideally suited for applications in which no special software or version
dependencies are desired.

Video Guidance

The dual Ethernet port adaptor offers an embedded Web serverwhich offers comfortable displaying and commissioning functions
directly from a standard web browser.
The VF-AS3 supports the following Automatic IP address assignment
via BOOTP and DHCP and Diagnostics and configuration via
integrated Web server.

Remote Sensor Monitoring
The sensor which is equipped in the machine and equipment, can beconnected with VF-AS3 and the status can be monitored by network
communication.

Dual Ethernet Port

The product supports the following functions on Web server:• Drive monitor• Drive parameters read/write• Trip history viewer• Network parameter setting• Administration function• TCP/IP statistics monitor(*1) QR Code ® is registered trademarks of DENSO WAVE INCORPORATED

For the installation, setup and maintenance, the video guidance isavailable with web support.

Video Guidance ImageQR Code® Example

Web Server Image

Motor & Sensor

Real Time Clock - Calendar/Time Stamp function
The VF-AS3 has RTC (Real Time Clock) built-in. The calendar (workday, holiday, etc.) can be easily set by parameters.
Output terminal signal is ON at the day of the week, hour and minuteset as "work day-time" by parameters.
The output terminal signal can be used as machine operation,
pattern operation, and my function in the drive.

IoT Systems Solution
Time Stamp Example-Ideal for Plant & Process Control Application
The VF-AS3 can be connected with various devices throughlocal area network, wireless network, and the Internet. It
achieves data collection to know operational status andanalyze system failure.
This IoT-Ready function increase productivity and reduce
total cost.

Local Area Network

Worldwide Network through the Internet

Wireless Network

Central Monitoring

Cloud ServerInternet

Big Data

Access point

Ethernet TCP/IP
PLC

Web Server

Ethernet TCP/IP
Webserverfunction with
controller

PLC
SensorSensor3

Sensor4

High-performance Drive

Ideal for various applications.
The VF-AS3 has various functions dedicated to various applications.
The VF-AS3 will be the ideal choice for a wide variety of uses.

For Oil & Gas / Mining Industry

For Water & Wastewater Industry

Jack pumps / Compressor / Conveyor / Crushers

Fan / Pump / Centrifuges
Torque characteristics

Multi ratings – excellent motor control performance

Multi pump control – maximum 10 pumps

300
275

The VF-AS3 has the multi ratings and can drive for various application with HD(150%60sec) and ND(120%-60sec). It is available for both heavy-load application and light-load
application.

225
200
175
150

Each pump is connected to commercial power via magnetic contactor which is controlled byrelay output signal of the drive.

125
100

The starting torque with sensor-less vector control is 200% with 0.3Hz or more. The VF-AS3
achieves high starting torque and high accuracy regenerative torque at low frequency.

75
50
25
-200

0
-25

0

200

400

600

800

1000

1200

1400

1600

1800

2000

2200

2400

2600

-50

Easy to set up with Auto-tuning function

System example of multi pump controller

The VF-AS3 can drive multiple pump motors (maximum ten pumps) and save the power ofwater pump system by controlling each pump appropriately, realizing great cost reduction.

250

-75
-100

There are 3 relay output terminals on the drive. Furthermore, two I/O extensions can beinserted to the drive. Each I/O extension has 3 relay output terminals, and thus a maximum of
9 relay output terminals can be used.

-125
-150

The VF-AS3 has the Auto-tuning function that automatically optimizes the drive parameters.

-175
-200
-225

The moment of inertia of machine and equipment can also be set easily by Auto-tuning
function.

-250
-275
-300

Drive: VFAS3-4022P

Motor: 480V-2.2kW-IE3

PM Motor

SPM

The VF-AS3 can drive both interior permanent magnetic motor (IPM) and surface permanent
magnetic motor (SPM).

Example of 4 PID applications

VF-AS3 has four built-in PID controllers: two for drives (motors) and other two for otherdevices including heaters and valves. The built-in PID controllers are available at the sametime for many purposes. It can help reduce cost and space because it can omit additional
external PID controllers.

PM motor drive
PM motor drive technology has been implemented in VF-AS3 as a standard feature. The VFAS3 can control both induction and permanent magnetic synchronous motors with/without
feedback sensor, allowing them to use for the variety of purposes.

Space-saving and cost reduction by four embedded PID controllers

The PID functions include temperature or pressure control of fan and pump, speed control ofa winder, stop position control, etc.

IPM

For Conveyor / Crane Industry

For Chemical / Pharmaceutical Industry

Transportation machine / Conveyor / Crushers / Compressor

Pumps / Mixers / Compressor / Centrifuges / Fans

Embedded positioning control

Enhanced environment resistance

VF-AS3 has sensor / sensor-less position control with point to point, Pulse input andOrientation, which is suitable for applications such as processing machine for high precisioncontrol.

• Comply with the chemicals (3C3)/dust (3S3) standards of
IEC60721-3-3. (Frame size A6 or smaller)

Excellent flexibility by My Function (logic function)• The inverter is operable at an ambient temperature of -15 to+60°C. (Frame size A7, A8: -10 to +60°C)

My function adds programming capability to the drive’s input/output signals without external
relays or PLC (programmable logic controller). The function makes it possible to reduce thespace and cost required for the system.
My function has the relay sequence function that combines logic operation functions. The
relay sequence function enables the drive to perform itself in 52 steps (4 steps x 7 units +24 steps) without PLC. The processing speed is faster than control with PLC as the functionuses internal data and signals directly.

5• Can be used at an altitude of up to 4800 m.
(Frame size A6 or smaller)• The design expectancy life time of the cooling fan,smoothing aluminum electrolytic capacitor for power circuit,and aluminum electrolytic capacitor for control circuit are ten
years. (Fan of frame size A7, A8: Five years)* Average ambient temperature 40°C, load factor 80% or less, 24-hour and
365 days operation

6

High-performance Drive

All-in-One. Improvement in Usability.
The VF-AS3 allows various functions without external options.
The VF-AS3 realizes improvement in usability and cost reduction.
Not necessary to prepare optional devices separately.

Reliable safety function

Mechanisms of STO function

The VF-AS3 has STO (Safe Torque Off) function as standard
and is highly reliable to cut off output in an emergency.
The STO function brings the machine safely into a no-torquestate and prevents it from starting accidentally.

In addition, the following safety functions are available asoptions:-SS2 (Safe Stop 2)-SBC (Safe Brake Control)-SLS (Safely-Limited Speed)

Detachable operation panel

Example of monitor mode

Example of error

The protection level of the keypad is enclosed type with door
mounting kit, which means dust-proof and wash-down capable.

Safety Module

The touch wheel has high sensitivity, which allows easy, smooth
operation.
Speed

NormalOperation-SS1 (Safe Stop 1)-SOS (Safe Operating Stop)

Touch wheel

The operation panel is detachable and easy to attach an
external control console with door mounting kit. The optional
panel is not required.

Emergency Stop

It complies with safety standard IEC 61800-5-2 and alsoachieves SIL3 level in IEC 61508 : 2010.

Detachable operation panel

STO function:safely clears the pulses of the drive

Ｖ

Motor
rotational
speed

Wide, multi-language LCD screen (HMI)

IEC 60204-1
Category 0(Under no control)

The drive is reliably
torque-free.

-SDI (Safe Direction)Time

The wide LCD screen (240 x 160 dots) displays multiple items
at the same time, allowing easy setting of parameters.
If the VF-AS3 trips, the panel will turn red in back light color,and it’s easy to recognize.
The panel can be displayed in multiple languages including
German, Italian, Spanish, French, Portuguese, Russian,Chinese and Japanese as well as English.

Harmonics reduction
The VF-AS3 is very friendly to a power supply systemand peripheral equipment. The built-in dual DC reactor (*1)
suppresses harmonic current and improves power factor.

Built-in DC Reactor

Example of input
current/voltage waveform

Detachable control terminal block

Detachable control terminal block

Detachable terminal block allows you to use the current control
wiring when replacing the drive. It also makes maintenancemuch easier.

VF-AS3 complies with IEC61000-3-12 and achieves total
harmonic distortion (THDi) ≦ 48% without external reactor.
(480V Class only)(*1) Frame size A7,A8: Attached DCL

High-frequency noise reduction

Built-in EMC Filter

Built-in UL Type1 kit

Various options

The built-in EMC filter suppresses high frequency noise. The
filter is ideal for sites such as commercial facilities, offices andfactories where attentions must be paid to peripheral devices.

Slots for options

If more additional options are required, cassette-type options for network, extended terminal block,sensor feedback, and safety function can be added easily.

The VF-AS3 complies with EMC directive of IEC61800-3
Category C2/C3 without external filter. (480V Class only)

Communication network:

In addition, the VF-AS3 has built-in UL Type 1 terminal box
integrated with EMC plate.

PROFINET (*1), PROFIBUS-DP (*1), DeviceNet™ (*2), EtherCAT ® (*3), CANopen® (*4)

Example of generated frequency noise data(*1) PROFINET and PROFIBUS-DP are registered trademarks of PROFIBUS and PROFINET International .
(*2) DeviceNet™ is a registered trademark of ODVA.
(*3) EtherCAT® is a registered trademark of Beckhoff Automation .
(*4) CANopen® is a registered trademark of CAN in Automation.

Inputs/Outputs:
Digital & Analog I/Os: 6-Digital Input, 2-Digital Output, 2-Analog Input
Relays: 3-Relay

Cassette-type options

Safety:Safety option (SS1, SOS, SS2, SBC, SLS, SDI)
Sensor feedback:Digital encoder: RS422 Line receiver
Resolver7

8

Basic functions

Standard specifications

Each “setup item” that determines the control characteristics of the drive is called a “parameter”.
For example, to change the acceleration time, you choose the acceleration time parameter (titled “ACC”).

■■Standard specifications

To enter the Easy mode, press theF1 to F4 key of Easy marking on the panel.
In this mode, you can set ten of the basic
parameters.

Setting mode
In this mode, you can set all parameters.
For details of parameters, refer to the Instruction Manual.

Title
CMOd
FMOd
ACC
dEC
UL
LL
tHrA
FM
F701
PSEL

Parameter nameRun command selectFrequency command select 1
Acceleration time 1
Deceleration time 1
Upper limit frequency
Lower limit frequency
Motor overload protection current 1
Terminal FM adjustment
Current, voltage units selectParameter mode selectParameter name

Adjustment Range

FC

Panel run frequency

LL-UL HzDefault setting

Title

Parameter name

Adjustment Range

AUH

History function

-

-

AUF

Guidance function

0:- 1:Embedded Ethernet setting 2:Preset speed operation 3:Analog frequency command 4:Motor 1,2 switching 5:Motor parameter0-

Default setting

6:PM motor parameter
AUA

Application easy setting

0:- 1:Initial easy setting 2:Conveyor 3:Material handling 4:Hoisting 5:Fan 6:Pump 7:Compressor

0

AUE

Eco-standby power setting

0:- +1:Embedded Ethernet OFF

0

AUL

Multi-rating select0:- 1:- 2:ND rating(120%-60s)(0 after execution) 3:HD rating(150%-60s)(0 after execution) 4-8:-0AU1Automatic Acc/Dec

0:Disabled 1:Automatic Acc/Dec 2:Automatic Acc only

0

AU2

Torque boost macro

0:Disabled 1:Automatic torque boost + offline auto-tuning 2:Vector control 1 + offline auto-tuning 3:Energy savings + offline auto-0

tuningRun command select0:Terminal 1:Operation panel, Extension panel 2:Embedded Ethernet 3:RS485 communication(connector 1) 4:RS485

0

communication(connector 2) 5:Communication option
FMOd

Frequency command select 1

0:- 1:Terminal RR 2:Terminal RX 3:Terminal II 4:Terminal AI4(option) 5:Terminal AI5(option) 6-9:- 10:Touch wheel 1(power off or press

1

OK to save) 11:Touch wheel 2(press OK to save) 12:Sr0 13-14:- 15:Terminal Up/Down frequency 16:Pulse train 17:High resolution

A2

A3

0.4

0.75

1.5

2.2

4.0

5.5

7.5

Applicable motor (HP)
Type
Form

0.5

1

2

3

5

7.5

10

3.0

4.3

7.1

9.7

12.5

Output capacity (kVA)*1

1.3

1.8

3.3

4.6

0.7

1.4

DC reactor
UL type1 kit

11

15

A5
18.5

22

30

A6
37

45

55

15
20
25
30
40
50
60
75
VFAS32004P 2007P 2015P 2022P 2037P 2055P 2075P 2110P 2150P 2185P 2220P 2300P 2370P 2450P 2550P

Output current (A)*2
Output voltage
Overload current rating
Dynamic braking circuit
Dynamic braking resistor
Voltage-frequency
Allowable fluctuation
Required power supply
capacity (kVA) *4
Degree of protection(IEC60529)
Cooling method
Color
Built-in filter
EMC filter(IEC61800-3) External filter *5Powersupply

Title

CMOd

A1

Specification
240 V class
A4

Applicable motor (kW)Elecalbraking■■Basic parameters

Item
Voltage class
Frame size

RatingEasy mode<240 V class: HD rating>

17.8

24.2

29.9

35.3

46.9

56.8

67.1

80.4

8.0
11.2
18.7
25.4
32.7
46.8
63.4
78.4
92.6
123
149
176
211
3-phase 200 V to 240 V (The maximum output voltage is equal to the input supply voltage)
150%-1 minute, 180%-2 s
Built-inOptional
External braking resistor (Optional)
3-phase 200 V to 240 V - 50/60 Hz
Voltage 170 V to 264 V*3, Frequency ± 5%
2.4

3.7

5.9

7.7

10.5

15.7

20.6

24.9

30.7

40.5

IP20

49.6

61.0

73.3

IP00

Forced air-cooled
RAL7016 / RAL7035
C2-50m (Carrier frequency: 4.0 kHz), C3-150m (4.0 kHz)
Built-inBuilt-inC2-50m (2.5 kHz), C3-150m (2.5 kHz)
Optional

pulse train(option) 18-19:- 20:Embedded Ethernet 21:RS485 communication(connector 1) 22:RS485 communication(connector 2)
0pump) 6:PM motor control 7:V/f 5-point setting 8:- 9:Vector control 2(speed/torque) 10:PG feedback control 11:PG feedback vector
control(speed/torque) 12:PG feedback PM motor control
vb

Manual torque boost 1

0.00-30.00 %vLBase frequency 1

15.0-590 Hz

Depends on the capacity

vLv

Base frequency voltage 1

240V class:50-330 V 480V class:50-660 V

Depends on the setup menu

FH

Maximum frequency

30.0-590.0 Hz

Depends on the setup menu

UL

Upper limit frequency

0.0-FH Hz

LL

Lower limit frequency

0.0-UL Hz

ACC

Acceleration time 1

0.0-6000(600.0) sec

Depends on the capacitydEC

Deceleration time 1

0.0-6000(600.0) sec

Depends on the capacity

Sr0

Preset speed 0

LL-UL Hz

0.0

Sr1

Preset speed 1

LL-UL Hz

0.0

Sr2

Preset speed 2

LL-UL Hz

0.0

Sr3

Preset speed 3

LL-UL Hz

0.0

Sr4

Preset speed 4

LL-UL Hz

0.0

Sr5

Preset speed 5

LL-UL Hz

0.0

Sr6

Preset speed 6

LL-UL Hz

0.0

Sr7

Preset speed 7

LL-UL Hz

0.0

FPId

PID 1 set value

F368-F367 Hz

0.0

Fr

Panel Fwd/Rev run select0:Fwd run 1:Rev run 2:Fwd run(switchable F/R by panel) 3:Rev run(switchable F/R by panel)tHrA

Motor overload protection current 1

Depends on the capacity

OLM

Motor overload protection characteristic

0:Standard motor, OL2, No stall 1:Standard motor, OL2, Stall 2:Standard motor, No OL2 trip, No stall 3:Standard motor, No OL2

50.0/60.0

50.0/60.0
0.0

0Depends on the capacity
0

trip, Stall 4:Constant torque motor, OL2, No stall 5:Constant torque motor, OL2, Stall 6:Constant torque motor, No OL2 trip, No stall
7:Constant torque motor, No OL2 trip, Stall
FMSL

Terminal FM function

0-162

FM

Terminal FM adjustment

-

0
-

tyP

Default setting

0:- 1:50Hz setting 2:60Hz setting 3:Default setting 1 4:Clear past trips 5:Clear cumulative run time 6:Initialize type form 7:Store user

0

settings 8:Rewrite user settings 9:Clear numulative fan run time 10-11:- 12:Clear number of starting 13:Default setting 2(complete
initialization) 14:Clear number of external equipment stating 15:Clear cumulative overcurrent time
SEt

Region setting check

0:Setup menu starting 1:Japan(read only) 2:Mainly North America(read only) 3:Mainly Asia(read only) 4:Mainly Europe(read only)0

5:Mainly China(read only)
PSEL

Parameter mode select

0:Setting mode at power on 1:Easy mode at power on 2:Easy mode only

0

F1-- ～

Extended parameters

Set parameters in more detail-

F9-A---

Advanced parameters

Parameters with dedicated function are displayed

Communication parameters

Parameters with communication function are displayed-

Changed parameters search & edit--

For details on extended parameters, advanced parameters and communication parameters, please visit our
web site (http://www.inverter.co.jp/)

9-C--GrU<240 V class: ND rating>ItemSpecification
Voltage class
240 V class
Frame size
A1
A2
A3
A4
A5
A6
Applicable motor (kW)
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
Applicable motor (HP)
1
2
3
5
7.5
10
15
20
25
30
40
50
60
75
100
Type
VFAS3Form
2004P 2007P 2015P 2022P 2037P 2055P 2075P 2110P 2150P 2185P 2220P 2300P 2370P 2450P 2550P
Output capacity (kVA)*1
1.8
3.0
4.3
7.1
9.7
12.5
17.8
24.2
29.9
35.3
46.9
56.8
67.1
80.4
107
Output current (A)*2
4.6
8.0
11.2
18.7
25.4
32.7
46.8
63.4
78.4
92.6
123
149
176
211
282
Output voltage
3-phase 200 V to 240 V (The maximum output voltage is equal to the input supply voltage)
Overload current rating
120%-1 minute, 135%-2 s
Dynamic braking circuit
Built-inOptional
Dynamic braking resistor
External braking resistor (Optional)
Voltage-frequency
3-phase 200 V to 240 V - 50/60 Hz
Allowable fluctuation
Voltage 170 V to 264 V*3, Frequency ± 5%
Required power supply
1.2
2.3
3.3
5.9
7.8
10.3
15.0
20.6
24.9
29.4
40.5
49.3
59.6
73.3
98.1
capacity (kVA) *4
Degree of protection
IP20
IP00
(IEC60529)
Cooling method
Forced air-cooled
Color
RAL7016 / RAL7035
Built-in filter
EMC filter(IEC61800-3) External filter *5
C2-50m (Carrier frequency: 4.0 kHz), C3-150m (4.0 kHz)
C2-50m (2.5 kHz), C3-150m (2.5 kHz)DC reactor
Built-in
UL type1 kit
Built-inOptional
Rating

0:V/f constant 1:Variable torque 2:Automatic torque boost 3:Vector control 1 4:Energy savings 5:Dynamic energy savings(for fan andElectricalbraking

V/f PatternPowersupply23:Communication option
Pt*1: Capacity is calculated at 220 V for the 240 V class.
*2: Indicates rated output current setting when the PWM carrier frequency (parameter F300) is 4 kHz for frame size A1 to A5, 2.5 kHz for frame size A6.
*3: Lower limit of voltage for 240 V class is 180 V when the inverter is used continuously (load of 100%).
*4: Required power supply capacity varies with the value of the power supply side inverter impedance (including those of the input reactor and wires).
*5: Contact your Toshiba distributor for detail.

10

High-performance Drive<480 V class: HD rating><480 V class: ND rating>ItemSpecification

Voltage class

Item

480 V class

Frame size

A1

A2

A3

A4

480V class

Frame size

A1

A2

A3

A4

Applicable motor (kW)

0.4

0.75

1.5

2.2

4.0

5.5

7.5

11

15

18.5

22

30

37

Applicable motor (kW)

0.75

1.5

2.2

4.0

5.5

7.5

11

15

18.5

22

30

37

45

Applicable motor (HP)

0.5

1

2

3

5

7.5

10

15

20

25

30

40

50

Applicable motor (HP)

1

2

3

5

7.5

10

15

20

25

30

40

50

60

Type

VFAS34022PC

4037PC

4055PC

4075PC

4110PC

4150PC

4185PC

4220PC

4300PC

4370PC

Form

3.0

4.3

7.1

9.7

12.6

17.9

24.2

29.9

35.3

46.9

56.8

Output capacity (kVA)*1

1.7

3.0

4.3

7.1

9.7

12.6

17.9

24.2

29.9

35.3

46.9

56.8

67.1

Output current (A)*2

1.5

2.2

4.0

5.6

9.3

12.7

16.5

23.5

31.7

39.2

46.3

61.5

74.5

Output current (A)*2

2.2

4.0

5.6

9.3

12.7

16.5

23.5

31.7

39.2

46.3

61.5

74.5

88.0

Rating4015PC

1.73-phase 380 V to 480 V (The maximum output voltage is equal to the input supply voltage)

Output voltage

3-phase 380 V to 480 V (The maximum output voltage is equal to the input supply voltage)

Overload current rating

Dynamic braking circuit

Built-inDynamic braking circuit

Built-inDynamic braking resistor

External braking resistor (Optional)

Dynamic braking resistor

External braking resistor (Optional)

Electricalbraking

150%-1 minute, 180%-2 s

Voltage-frequency

3-phase 380 V to 480 V - 50/60 Hz

Allowable fluctuation

Voltage 323V to 528V*3 , Frequency ± 5%

Required power supply
capacity (kVA) *4

0.7

1.4

2.6

3.9

6.6

8.5

11.4

Degree of protection(IEC60529)

16.6

22.3

27.3

32.7

44.3

53.9

Power
supplyRating4004PC 4007PC 4015PC 4022PC 4037PC 4055PC 4075PC 4110PC 4150PC 4185PC 4220PC 4300PC 4370PC

4007PC

1.1

Overload current rating
Electricalbraking

VFAS3-

4004PC

Output voltage

PowersupplyType

Output capacity (kVA)*1

Form

120%-1 minute, 135%-2 s

Voltage-frequency

3-phase 380 V to 480 V - 50/60 Hz

Allowable fluctuation

Voltage 323 V to 528 V*3 , Frequency ± 5%

Required power supply
capacity (kVA) *4

1.2

2.4

3.4

6.1

8.3

10.9

15.6

Degree of protection(IEC60529)

IP20

21.3

Forced air-cooled

Cooling method

Forced air-cooled

Color

RAL7016 / RAL7035

Color

RAL7016 / RAL7035

C2-50m (Carrier frequency: 4.0 kHz), C3-150m (4.0 kHz)

Built-in filter
EMC filter(IEC61800-3) External filter *5

C2-150m (Carrier frequency: 4.0 kHz), C3-300m (4.0 kHz)DC reactor

Built-in

UL type1 kit

Built-in

UL type1 kit

Built-inSpecification

Frame size

A5

A6

Applicable motor (kW)

45

55

75

90

110

Applicable motor (HP)

60

75

100

125

150

A8
200

220

280

Applicable motor (kW)

55

75

90

110

132

200

250

300

350

450

Applicable motor (HP)

75

100

125

150

200

Type

4550PC

4750PC

4900PC

4110KPC

4132KPC

4160KPC

4200KPC

4220KPC

4280KPC

67.1

80.8

111

132

161

191

239

295

325

419

Output current (A)*2

88.0

106

145

173

211

250

314

387

427

550

3-phase 380 V to 480 V (The maximum output voltage is equal to the input supply voltage)
Built-in

150%-1 minute, 165%-2 s

Optional

Built-inOptional

Voltage-frequency

3-phase 380 V to 480 V - 50/60 Hz

3-phase 380 to 440 V - 50 Hz,
3-phase 380 to 480 V - 60 Hz

Allowable fluctuation

Voltage 323 V to 528 V*3, Frequency ± 5%

Voltage 323 to 484 V - 50 Hz,
323 V to 528 V - 60 Hz*3, Frequency ± 5%

Degree of protection(IEC60529)

65.6

79.5

108

133

155

181

IP20

225

275

308

379

250

280

315

250

350

400

450

500

4450PC

4550PC

4750PC

4900PC

80.8

111

132

161

191

230

325

367

419

469

Output current (A)*2

106

145

173

211

250

302

427

481

550

616

4110KPC 4132KPC 4160KPC 4200KPC 4220KPC 4280KPC

3-phase 380 V to 480 V (The maximum output voltage is equal to the input supply voltage)
120%-1 minute, 135%-2 s

Dynamic braking circuit

Built-inOptional

Dynamic braking resistor

Built-in3-phase 380 V to 480 V - 50/60 Hz

3-phase 380 to 440 V - 50 Hz,
3-phase 380 to 480 V - 60 Hz

Allowable fluctuation

Voltage 323 V to 528 V*3, Frequency ± 5%

Voltage 323 to 484 V - 50 Hz,
323 V to 528 V - 60 Hz*3, Frequency ± 5%

Required power supply
capacity (kVA) *4

77.0

103

125

155

181

214

IP20

Forced air-cooled

Cooling method

Forced air-cooled

Color

RAL7016 / RAL7035

Color

RAL7016 / RAL7035

C3-150m (2.5 kHz)

C3-50m (2.5 kHz)

C2-150m (2.5 kHz), C3-300m (2.5 kHz)

C2-100m (2.5 kHz)

Built-inAttached

DC reactor-

UL type1 kit

DC reactor
UL type1 kit

Built-inOptional*1: Capacity is calculated at 440 V for the 480 V class.
*2: Indicates rated output current setting when the PWM carrier frequency (parameter F300) is 4 kHz for frame size A1 to A5, 2.5 kHz for frame size A6 to A8.
*3: Lower limit of voltage for 480 V class is 342 V when the inverter is used continuously (load of 100%).
*4: Required power supply capacity varies with the value of the power supply side inverter impedance (including those of the input reactor and wires).
*5: Contact your Toshiba distributor for detail.

Built-in filter
EMC filter(IEC61800-3) External filter *5

296

335

379

C3-150m (2.5 kHz)

C3-50m (2.5 kHz)

C2-150m (2.5 kHz), C3-300m (2.5 kHz)

C2-100m (2.5 kHz)

Built-inAttached

Built-in

422

IP00

Cooling method
Built-in filter
EMC filter(IEC61800-3) External filter *5

Optional

External braking resistor (Optional)

Voltage-frequency

Degree of protection(IEC60529)

IP00

A8

220

Output capacity (kVA)*1

Overload current rating

External braking resistor (Optional)

A7
160
VFAS3-

Output voltage
Electricalbraking

150%-1 minute, 180%-2 s

Dynamic braking circuit

Required power supply
capacity (kVA) *4

Form
Rating

4450PC

Dynamic braking resistor

A6

160

Output capacity (kVA)*1

Overload current rating

A5

132

Form

63.2

480 V class

Frame size

VFAS3-

Output voltage
Electricalbraking

A7

52.4

Specification

Voltage classPower supply

RatingTypePower supply

Item

480 V class

42.0

C2-150m (Carrier frequency: 4.0 kHz), C3-300m (4.0 kHz)

Built-in

Item

31.4

C2-50m (Carrier frequency: 4.0 kHz), C3-150m (4.0 kHz)DC reactor

Voltage class

26.4

IP20

Cooling method
Built-in filter
EMC filter(IEC61800-3) External filter *5

11Specification

Voltage class

Optional-*1: Capacity is calculated at 440 V for the 480 V class.
*2: Indicates rated output current setting when the PWM carrier frequency (parameter F300) is 4 kHz for frame size A1 to A5, 2.5 kHz for frame size A6 to A8.
*3: Lower limit of voltage for 480 V class is 342 V when the inverter is used continuously (load of 100%).
*4: Required power supply capacity varies with the value of the power supply side inverter impedance (including those of the input reactor and wires).
*5: Contact your Toshiba distributor for detail.

12

High-performance Drive■■Common Specifications(Continued)

Protective function

Specification

Output voltage adjustment

Adjustable within the range of 50 - 330 V (240 V class) and 50 - 660 V (480 V class) by correcting
the supply voltage

Output frequency range

Setting between 0.01 - 590 Hz. Default max. frequency is set to 0.01 - 80 Hz.
Maximum frequency adjustment (30 to 590Hz)

Minimum setting steps of frequency

0.01 Hz: operation panel input (60 Hz base),0.03 Hz: analog input (60 Hz base, 11 bit/0 - 10 Vdc)

Frequency accuracy

Analog input: ±0.2% of the maximum output frequency (at 25±10°C)
Digital input: ±0.01%±0.022 Hz of the output frequency

Voltage/frequency characteristics

V/f constant, variable torque, automatic torque boost, vector control, PM motor control, basefrequency adjustment 1, 2, 3, and 4 (15 - 590Hz), V/f 5-point arbitrary setting, torque boost
adjustment (0 - 30%), start frequency adjustment (0 - 10 Hz), stop frequency adjustment (0 - 30 Hz)

Frequency setting signal

3 kΩ potentiometer (possible to connect to 1 - 10 kΩ-rated potentiometer)
0 - 10Vdc (input impedance Zin: 31.5 kΩ)-10 to +10 Vdc (Zin: 31.5 kΩ)
4 - 20 mAdc (Zin: 250 Ω)

Item

Display function

Sinusoidal PWM control

Specification

AlarmsStall prevention during run, overload limit, overload, undervoltage on power supply side, DC
circuit undervoltage, setting error, in retry, upper limit, lower limit.

Causes of failures

Overcurrent, overvoltage, overheat, short circuit on the load side, ground fault on the load side,
inverter overload, arm overcurrent at starting, overcurrent on the load side at starting, Cooling
fan fault, CPU fault, EEPROM fault, RAM fault, ROM fault, communication error, (braking resistor
overcurrent/overload), (emergency off), (undervoltage), (undercurrent), (overtorque), (motor
overload), (input phase failure), (output phase failure) The items in the parentheses are selectable.

Screen of LCD Monitoring function

Output frequency, frequency command, forward run/reverse run, output current, DC voltage,
output voltage, compensated frequency, terminal input/output information, CPU version, past trip
history, cumulative operation time, feedback frequency, torque, torque command, torque current,
exiting current, PID feedback value, motor overload factor, inverter overload factor, PBR overload
factor, PBR load factor, input power, output power, peak output current, peak DC voltage, RR
input, II input, RX input, AI4 input, AI5 input, FM output, AM output, expansion I/O card option
CPU version, integral input power, integral output power, communication option reception
counter, communication option abnormal counter.

Free unit display

Display of optional units other than output frequency (motor speed, line speed, etc), current
ampere/% switch, voltage volt/% switch

Automatic edit function

Searches automatically parameters that are different from the default setting parameters. Easy tofind changed parameters.

User default setting

User parameter settings can be saved as default settings. Allows to reset the parameters to theuser-defined parameter settings.

Terminal block frequency command

The characteristic can be set arbitrarily by two-point setting. Compliant with 7 types of input;
analog input (RR, RX, II, AI4, AI5), and pulse input (S4, S5)

Frequency jump

Three frequency can be set. Setting of jump frequency and width.

Upper and lower limit frequencies

Upper limit frequency: 0 to max. frequency, lower limit frequency: 0 to upper limit frequency

PWM carrier frequency

Frame size A1 to A4: adjustable between 1.0 - 16 kHz
Frame size A5 to A8: adjustable between 1.0 - 8.0 kHz

PID control

Adjustment of proportional gain, integral time, differential time and delay filter. Multi PID andexternal PID control.

Input/output terminal logic function

Possible to select positive logic or negative logic with programmable input/output terminal
function menu. 2 or 3 function can be assigned for some terminals. *1 *2(Default setting: positive logic)

Torque control

Voltage command input specification: -10 - +10 Vdc

Sink/source switching

Real Time Clock (RTC)

Current time (year, month, date, hour, minute), Timezone, Daylight saving time, 4 work days and
20 holidays can be set by parameters

Possible to switch between minus common (CC) and plus common (P24) for digital input terminal.
(Default setting: external power supply)

Failure detection signal

Acceleration/deceleration time

0.01 - 6000 sec. Selectable from among acceleration/deceleration. times 1, 2, 3 and 4. Automatic
acceleration/deceleration function. S-pattern acceleration/deceleration 1 and 2 pattern adjustable.

1c contact output (250Vac-2A (cosФ=1), 30Vac-2A (Resistive), 250Vac=1A (cosФ=0.4),
30Vdc=1A (L/R=7ms))

Relay output

DC braking

Adjustment of braking start frequency (0 - [FH]Hz), braking (0 - 100%) and braking time (0 - 25.5
sec.). With emergency off braking function and motor shaft fix control function.

2×1a contact output (250Vac-2A (cosФ=1), 30Vac-2A (Resistive), 250Vac=1A (cosФ=0.4),
30Vdc=1A (L/R=7ms))

Low speed, Acc/Dec completed signal
output *2

Digital output (24 Vdc, max. 50 mA)

Forward run/reverse run*1

Forward run with ON of the terminal [F], Reverse run with ON of the terminal [R] (Default setting).
Coast stop with OFF of the terminal assigned Stad-by function. Emergency off by panel operationor terminal.

Output for frequency meter/Output for
ammeter *3

Jog run*1

Jog run, if selected, allows jog operation from the operation panel
Jog run operation by terminal block is possible by setting the parameters.

Analog output for meter: 1 mA dc full-scale dc ammeter0 - 20 mA (4 - 20 mA) output: DC ammeter (allowable load resistance: 500 Ω or less)0 - 10 V output: DC voltmeter (allowable load resistance: 1 kΩ or more)

Pulse train frequency output

Pulse train output (Up to 30 kpps, duty 50%)

Preset speed operation*1

By changing the combination of the terminals [S1], [S2], [S3], [S4], [S5] set frequency + 31-speed
operation. Selectable between acceleration/deceleration time, torque limit and V/f by set
frequency.

Retry

Capable of restarting after a check of the power circuit elements in case the protective function is
activated. Max. 10 times selectable arbitrarily. Waiting time adjustment (0 - 10 sec.)

output signal

LED

Charge display

Communication function

Displays power circuit capacitor charging.

Ethernet standard 2-channel equipped (connector: RJ45)
IEEE802.3/IEEE802.3u (Fast Ethernet) (10/100Mbps: Auto negotiation)
RS485 standard 2-channel equipped (connector: RJ45)
PROFINET, DeviceNet, PROFIBUS-DP, EtherCAT are optional.

Use environments

Indoor use. Altitude: 4800m or less for frame size A1 to A6, 3000m or less for frame size A7 andA8 (current reduction necessary when above 1000 m *6 ). Place not exposed to direct sunlight andfree of corrosive and explosive gases.

Ambient temperature-15 to +60°C *5
Frame size A1 to A5: Current reduction, remove the top cover when above 50°C;
Frame size A6: Current reduction when above 50°C;
Frame size A7 and A8: Current reduction when above 50°C (HD), above 45°C (ND)

Soft stall

Automatic load reduction control at overloading. (Default: OFF)

Cooling fan ON/OFF

The cooling fan will be stopped automatically to assure long life when unnecessary.

Lockout key operation/Password setting

Lock or unlock the key operation and parameter setting.
Lock parameter setting with a password.

Regenerative power ride-through control

Possible to keep the motor running using its regenerative energy in case of a momentary power
failure. (Default: OFF)

Storage temperature-25 to + 70°C *7

Auto-restart operation

Possible to restart the motor in coasting in accordance with its speed and direction. (Default: OFF)

Relative humidity

5 to 95% (free from condensation)

Simplified pattern operation

Possible to select each 8 patterns in 2 groups from 15-speed operation frequency. Max. 16 typesof operation possible. Terminal operation/repeat operation possible.

Vibration

Frame size A1 to A5: 5.9 m/s2{0.6G} or less (10 - 55 Hz),
Frame size A6 to A8: 2.9 m/s2{0.3G} or less (10 - 55 Hz)

Commercial inverter switching

Possible to switch operation by commercial power supply or inverterLight-load high-speed operation

Increases the operating efficiency of the machine by increasing the rotational speed of the motor
when it is operated under light load.

Droop function

When two or more inverters are used to operate a single load, this function prevents load fromconcentrating on one inverter due to unbalance.

Override function

External input signal adjustment is possible to the operation frequency command value.

Protective function

Stall prevention, current limit, overcurrent, overvoltage, short circuit on the load side, ground fault
on the load side*4, undervoltage, momentary power failure (15 ms or more), non-stop control atmomentary power failure, overload protection, arm overload at starting, overcurrent on the loadside at starting, overcurrent and overload at braking resistor, overheat, emergency off

Electronic thermal characteristic

Switchable between standard motor/constant torque motor, adjustment of overload protection
and stall prevention level.

Reset

Reset by 1a contact closed (or 1b contact opened), or by operation panel. Or power supply OFF/ON. This function is also used to save and clear trip records.

Environments

Operation specifications

Control specifications

Item
Control system*1: 14 digital input terminals (of which 6 are options) are programmable digital input terminals, and they make it possible to arbitrarily select from 178 types of signals.
*2: Programmable ON/OFF output terminals make it possible to arbitrarily select from 256 types of signals.
*3: Programmable analog output terminals make it possible to arbitrarily select from 54 types of signals.
*4: This function protects inverters from overcurrent due to output circuit ground fault.
*5: -10 to 60°C for frame size A7 and A8. Remove operation panel of the inverter when above 50°C.
*6: Current must be reduced by 1% for each 100m over 1000m. e.g. 90% at 2000m, 80% at 3000m*7: Temperature applicable for a short term. e.g. during transportation(Continued overleaf)
13

14

High-performance Drive

External dimensions

4-φ24

W1(Mounting dimension)
W

11

15

6

5

(55)

2-

R5

2-

.7

R5
.7

7

8

2

8

7

A

15

8

15

8

A

R3

Input voltage
Class

3

R

7.5

H1(Mounting dimension)A

3-phase 240 V

2-

R

2-

R

3.
5

13.5

5

W1(Mounting dimension)(13.5)(75)(67.5)

3

6

(18)

6
D

11

10
A

R5

.5

11

8

13
2

13
15

13
A

R4

.75

17

15

R

12

3-phase 480 V
A

H1(Mounting dimension)
H

A

H

10

H1(Mounting dimension)

R

18

Frame Size A6
14

Frame Size A5

W1(Mounting dimension)
W

D

W

19

A

H

5

H1(Mounting dimension)

.5

H

10

.5

9

R

W1 (Mounting dimension)
W

D

7
D

Frame Size A4
14

Frame Size A3

3

D

D

W

3

150

H

(59.5)375
6

W1 (Mounting dimension)

R

4-φ24

H1 (Mounting dimension)

R
2-

2.
W

DCL

2

R1

75

R

2-

H1 (Mounting dimension)

H

H1(Mounting dimension)

9

5.
5
R

A

(15)

W1(Mounting dimension) 14

(14)

17

150

17
2

R1

H

A

598

8

8
H1(Mounting dimension)

9

5

5.

DCL

.7
R5

3

2.7

5

R

R5

.7

R

R

440

2

75

8

A

H

8

A

Frame Size A830

Frame Size A7
3

1

13

8

30

Frame Size A2

8

15

Frame Size A1

2R
4.
5

R

2-

W

22.5

6
D

(22.5)

W1(Mounting dimension)
W(17)

W1(Mounting dimension)

13

(175)

75

5.

(22.5)

22.5

7
D

Applicable motor capacity (kW)
HD
ND

0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
110
132
160
200
220
280

0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
110
132
160
220
250
280
315

Drive type-form

VFAS3-

VFAS3-

2004P
2007P
2015P
2022P
2037P
2055P
2075P
2110P
2150P
2185P
2220P
2300P
2370P
2450P
2550P
4004PC
4007PC
4015PC
4022PC
4037PC
4055PC
4075PC
4110PC
4150PC
4185PC
4220PC
4300PC
4370PC
4450PC
4550PC
4750PC
4900PC
4110KPC
4132KPC
4160KPC
4200KPC
4220KPC
4280KPC

W

H

Dimension (mm)
D
W1 *1

H1 *1

Frame
Size

130

326

202

102

263

A1

155

391.5

231

125

324

A2

195

534.5

232

168

460

A3

210

660

268

174

570

A4

265

908

313

220

718

A5

300

850

383

255

820

A6

130

326

202

102

263

A1

155

391.5

231

125

324

A2

195

534.5

232

168

460

A3

210

660

268

174

570

A4

265

908

313

220

718

A5

300

850

383

255

820

A6

430

1190

377

350

920

A7

585

1190

377

540

920

A8

Approx. mass
(kg)
4.3
4.3
4.5
4.6
7.7
13.8
13.8
27.3
27.3
27.3
57.6
57.6
57.6
82
82
4.5
4.5
4.5
4.6
4.7
7.7
7.7
13.6
14.2
14.3
28
28.2
28.7
57.5
59
59.5
82
82
82
110 (168)*2
138 (200)*2
140 (210)*2
140 (210)*2*1: W1 and H1 are the mounting dimensions of the drive.
*2: Value in ( ) includes attached DC reactor.

15

16

High-performance Drive

Standard connection diagrams

Terminal functions■■Standard connection diagram■■Power terminal■■Standard connection diagram: Sink logic (common : CC): Source logic (common : P24)＊

4
+DC -DC

＊

8

＊

5

＊

8

3

PA
＊
9
PC

F
R
RES
S1
S2
S3
S4
S5
P24

＊

9

＊

7

PO

PA/+

PB

PC/- BU+ BU-

＊

2

1

S/L2

U/T1
V/T2

Power
circuit

EMC
filterT/L3

SOURCE
SW1
＊
10

Motor

＊

R/L1

SINK

PLC

＊

MC

W/T3

FP

[R/L1] [S/L2] [T/L3]

Digital input

Fwd runRev runReset 1 ＊12
Preset speed switching 1

Default
Preset speed switching 2 setting
Preset speed switching 3

Pulse counter[PA/+] [P0][RO] [SO] [TO]

M

F
R
RES
S1
S2
S3
S4
S5
CC

RUN
+SU
CC
11 Control
circuit

＊

＊

13

ON
RUN

OFF

R1A/R2A＊

13

Grounding terminal.
Connected to an AC power supply.
240 V class: Three-phase 200 - 240 V-50/60 Hz
480 V class: VFAS3-4004PC to 4132KPC:Three-phase 380 - 480 V-50/60 Hz
VFAS3-4160KPC to 4280KPC: Three-phase 380 - 440 V- 50 Hz
Three-phase 380 - 480 V- 60 Hz
Connected to a three-phase motor.
Connected to a braking resistor.
Change the parameters [F304: Dynamic braking, OLr trip], [F308: Braking resistance], and [F309: Braking resistor
capacity] if necessary.
Inside the inverter. Connected to a braking unit (optional). Braking resistor (optional) is connected to a braking unit
terminals [PA] and [PB].
A DC power can be input.
For models of VFAS3-2110P to 2550P and VFAS3-4220PC to 4280KPC, a rush current suppression circuit (optional) is
required. Connected to a braking unit (Optional) for frame size A6.
Be sure to connect the attached DC reactor.
Inverter's cooling power input terminals. When using a DC power supply, connect three-phase power wires.

Frame size A4, A5, and A6

Fwd runRev runReset 1 ＊12
Preset speed switching 1

Default
Preset speed switching 2 setting
Preset speed switching 3
Preset speed switching 4
Preset speed switching 5
CommonInput/output

F

Input

R

Input

RES

Input

S1
S2
S3

Input
Input
Input

S4

Input

Function
Multifunction programmable digital input. In the default setting, forward run is performed with ON anddeceleration stop with OFF.
Multifunction programmable digital input. In the default setting, reverse run is performed with ON anddeceleration stop with OFF.
Multifunction programmable digital input. In the default setting, this inverter protective function is resetby ON → OFF. It has no effect when the inverter is in a normal condition.
Multifunction programmable digital input. In the default setting, preset speed operation is performed with ON
Multifunction programmable digital input. In the default setting, preset speed operation is performed with ON
Multifunction programmable digital input. In the default setting, preset speed operation is performed with ON
Multifunction programmable digital input. In the default setting, preset speed operation is performed
with ON. With [F146:Terminal S4 input select], digital input, pulse train input, and PG input can beswitched.

FP

SINK

PLC

PLC

SOURCE

FLC

RUN

All frame sizes

Pulse counter

Surge
absorberb-contact ofoverload relay

Digital input

P24

FLA
FLB

SW1

S5

10

Multifunction programmable digital input. In the default setting, preset speed operation is performed with
ON. With [F147: Terminal S5 input select], digital input, pulse train input, and PG input can be switched.

RX

II

RR

PP

Common to
input/output
Output+Frequency
meter−

Ammeter

*1:
*2:
*3:
*4:
*5:

Current signal: 4(0) to 20 mA

External potentiometer(or, input voltage signal of 0 - 10 V between the terminals [RR] and [CC])EMC filter is built in 480 V class.
The DC reactor is built in for models VFAS3-2004P to 2550P and VFAS3-4004PC to 4132KPC.
Be sure to mount the DC reactor for models VFAS3-4160KPC to 4280KPC. A circuit between the terminals [PA/+] and [PO] is not short circuited (at the time of shipping).
To input DC power, connect the inverter between the terminals [PA/+] and [PC/-]. It is not used in conjunction with the attached DC reactor for VFAS3-4160KPC to 4280KPC.
For models of VFAS3-2110P to 2550P and VFAS3-4220PC to 4280KPC, a rush current suppression circuit (optional) is required and please contact your Toshiba distributor for
information.
*6: When the inverter is used with a DC power supply, three-phase power input for cooling fan driving is required separately for models VFAS3-4160KPC to 4280KPC.
*7: External braking resistor (optional) for models VFAS3-2004P to 2370P and VFAS3-4004PC to 4750PC, VFAS3-4160KPC.
*8: When a braking resistor (optional) is mounted, a braking unit (optional) is also required. for models VFAS3-2450P, 2550P and VFAS3-4900PC to 4132KPC.
*9: When a braking resistor (optional) is mounted, a braking unit (optional) is also required. for models VFAS3-4200KPC to 4280KPC.
*10: With the slide switch [SW1] of the control terminal block, the setting of sink logic, source logic and external power supply sink logic of the digital input terminals [F], [R], [RES],
and [S1] - [S5] is switched. [SW1] is set to the PLC side in the default setting. This is the setting when the inverter external power supply is used.
*11: To supply control power from an external power supply for backing up the control power supplied from the inverter, an optional control power supply unit (CPS002Z) is
required. In this case, it is used in conjunction with the inverter internal power supply.
Set [F647: Control power option failure detection] to back up the control power supply.
*12: The reset signal is activated by ON → OFF trigger input.
*13: Connect to power to comply with OVC2 (Over Voltage Category 2). Isolation transformer is necessary when connecting to power supply (OVC3).

FP

Output

RR

Input

RX

Input

II

Input

FM

OutputAM

OutputOutput

PLC
Input

Frame size A8
All frame sizes
Frame size A7 and A8
Frame size A7 and A8Electrical specifications
Digital input.
•24 Vdc-5 mA or lessCompliant with IEC61131-2 logic type 1•Sink logic:ON < 10 V, 16 V < OFF•Source logic:OFF < 5 V, 11 V < ON
Sink logic and source logic can be switchedwith the slide switch [SW1]Digital input.
•24 Vdc-5 mA or lessCompliant with IEC61131-2 logic type 1•Sink logic:ON < 10 V, 16 V < OFF•Source logic:OFF < 5 V, 11 V <ON
Sink logic and source logic can be switchedwith the slide switch [SW1]

10 Vdc (allowable load current: 10 mAdc)
Digital output•24 Vdc-50 mA

Multifunction programmable digital/pulse train output. With [F669: Terminal FP switching], digital output
and pulse train output can be switched.
Analog input with 0 - 10 Vdc. It can be switched to PTC input, etc. with [F108: Terminal RR input select].
Analog input with -10 to +10 Vdc. With [F107: Terminal RX input voltage select], it can be swtiched to 0 10 Vdc.
Analog current input with 0 - 20 mAdc. The current can be changed to 4 - 20 mA, etc. with setting of theparameter.
Multifunction programmable analog output. 0 - 10 Vdc output with default setting. With [F681:Terminal
FM switching], meter option (0 - 1 mA), current (0 - 20 mA) output, and voltage (0 - 10 V) output can beswitched.
Multifunction programmable analog output. 0 - 20 mAdc output with default setting. With [F686: Terminal
AM switching], meter option (0 - 1 mA), current (0 - 20 mA) output, and voltage (0 - 10 V) output can beswitched.
When the slide switch [SW1] is set to the sink side or source side, it can be used as 24 Vdc power
output.
When the slide switch [SW1] is set to the PLC side, it can be used as a common terminal for digital input
terminal.

Pulse train output•Up to 30 kpps (duty 50%)
0 - 10 Vdc (input impedance: 31.5 kΩ)-10 to +10 Vdc (input impedance: 31.5 kΩ)
0 - 20 mAdc (input impedance: 250 Ω)
0 - 10 Vdc(allowable load resistance: 1 kΩ or more)
4 - 20 mAdc (0 - 20 mAdc)(allowable load resistance: 500 Ω or less)
24 Vdc-200 mA (200 mA in total with P24)
Compliant with IEC61131-2-

P24

Output24 Vdc power output.

24 Vdc-200 mA (200 mA in total with PLC)
Compliant with IEC61131-2

+SU

Input

DC power input to operate the control circuit. Connect a control power supply option or 24 Vdc power
supply between [+SU] and [CC].

24 Vdc- current 1A or more

STOA

Input

STOB

Input

FLA
FLB
FLC
R1A
R1C

R2C

At the time of shipping, the terminals [STOA]-[STOB]-[PLC] are shorted by the shorting bar. This is aterminal with STO function that complies with the safety standard IEC61800-5-2. For details, refer to
Safety Function Manual. This terminal is not programmable digital input.

OutputMultifunction programmable relay contact output. Operation of the protection function of the inverter
is detected in the default setting. The contact across [FLA]-[FLC] is closed and [FLB]-[FLC] is opened
during protection function operation.

OutputMultifunction programmable relay contact output. A low-speed signal is output in the default setting.

OutputMultifunction programmable relay contact output. It is not assigned in the default setting. The function
can be set with [F134: Terminal R2 function].

R2A

17

Frame size A1, A2, A3, A4, A5, and A7

An equipotential terminal of the control circuit. It is allocated in three positions.

PP−

Ammeter or voltmeterAll frame sizes

10 Vdc power output for analog input setting.

Voltage signal: -10 to +10V+

All frame sizes

Pulse train input•Up to 30 kpps (duty 50%)

STOB
CC

FM AM CC

Input

STOA

＊

R1C/R2C

Applicable frame size

Grounding terminal for inverter case.

■■Control terminal
Terminal
symbolDC/DC

TO

Optional control
power supply unit＊
11

[BU+] [BU-][PA/+] [PC/-]

Fan

MC

[PA/+] [PB]

Preset speed switching 5

6
RO
SO

[U/T1] [V/T2] [W/T3]

Preset speed switching 4＊

480/240 V
transformer

Function[PE]

Power supply
240V class:
VFAS3-2004P to VFAS3-2550P:
3-phase, 200 to 240V-50/60Hz
480V class:
VFAS3-4004PC to VFAS3-4132KPC: 3-phase, 380 to 480V-50/60Hz
VFAS3-4160KPC to VFAS3-4280KPC: 3-phase, 380 to 440V-50Hz
3-phase, 380 to 480V-60Hz

MCCB

Terminal symbol

Refer to Safety Function Manual.
Compliant with IEC61131-2 logic type 1• Activate < 5 V, 11 V < Deactivate
Not coast stop
Maximum contact capacity•250 Vac-2 A(cosφ=1)•30 Vdc-2 A (at resistive load)•250 Vac-1 A (cosφ=0.4)•30 Vdc-1A (L/R=7 ms)
Minimum contact capacity•24 Vdc-5 mA
Life•100000 times

18High-performance Drive

For drive users
When studying how to use our drives

Notes

Note) In the case of this drive, the PWM carrier frequency can be decreased to 1.0kHz.
However, that it should not be set to less than 2.0kHz during vector control.
Decreasing the carrier frequency results in an increase in electromagnetic noise from the motor.

Leakage current
This drive uses high-speed switching devices for PWM control.
When a relatively long cable is used for power supply to a drive, current may leakfrom the cable or the motor to the ground because of its capacitance, adversely
affecting peripheral equipment. The intensity of such a leakage current depends on
the PWM carrier frequency, the lengths of the input and output cables, etc., of thedrive. To prevent current leakage, it is recommended to take the following measures.

[Effects of leakage current]
Leakage current which increases when a drive is used may pass through thefollowing routes:
Route (1) ... Leakage due to the capacitance between the ground and the noise filter
Route (2) ... Leakage due to the capacitance between the ground and the drive
Route (3) ... Leakage due to the capacitance between ground and the cableconnecting the drive and the motor
Route (4) ... Leakage due to the capacitance of the cable connecting the motor
and a drive in another power distribution line
Route (5) ... Leakage through the grounding line common to motors
Route (6) ... Leakage to another line because of the capacitance of the ground
Leakage current which passes through the above routes may cause the following
trouble.
• Malfunction of a earth leakage circuit breaker (ELCB) in the same or anotherpower distribution line
• Malfunction of a ground-relay installed in the same or another power distributionline• Noise produced at the output of an electronic device in another power distribution
line• Activation of an external thermal relay installed between the drive and the motor,
at a current below the rate current

Power supply(5) If the drive has a high-attenuation EMC filter, turn off the grounding capacitor
detachment switch to reduce the leakage current. Note that doing so leads to a
reduction in the noise attenuating effect.

ELCB

Noise filter

motor

Drive
1

2

Vibration

Before begining operation, thoroughly check the wiring between the motor and thedrive for incorrect wiring or short circuits. Do not ground the neutral
point of any star-connected motor.

Radio interference

Installing a magnetic contactor [MC] [primary side]

When a motor is operated with an industrial drive, it experiences more vibrations
than when it is operated by the commercial power supply. The vibration can be
reduced to a negligible level by securing the motor and machine to the base firmly.
If the base is weak, however, the vibration may increase at a light load due toresonance with the mechanical system.

[Noise produced by drives](1) To prevent an automatic restart after the power interruption or overload relay has
tripped, or actuation of the protective circuit, install a magnetic contactor in the
power supply.
(2) The drive is provided with a failure detection relay (FL), so that, if its contacts areconnected to the operation circuit of the magnetic contactor on the primary side,
the magnetic contactor will be opened when the protective circuit of the drive isactivated.
(3) The drive can be used without a magnetic contactor. In this case, use an MCCB
(equipped with a voltage tripping device) for opening the primary circuit when thedrive protective circuit is activated.
(4) Avoid turning the magnetic contactor on and off frequently to turn on/off the
motor.
(5) To turn on/off the motor frequently, ON/OFF the control terminals F (or R)-CC.

Since this drive performs PWM control, it produces noise and sometimes affects
nearby instrumental devices, electrical and electronic systems, etc. The effects
of noise greatly vary with the noise resistance of each individual device, its wiringcondition, the distance between it and the drive, etc.

[Measures against noises]
According to the route through which noise is transmitted, the noises produced by adrive are classified into transmission noise, induction noise and radiation noise.

[Examples of protective measures]• Separate the power line from other lines, such as weak-current lines and signallines, and install them apart from each other.
• Install a noise filter in each drive. It is effective for noise prevention to install
noise filters in other devices and systems, as well.
• Shield cables and wires with grounded metallic conduits, and cover electronicsystems with grounded metallic cases.
• Separate the power distribution line of the drive from that of other devices andsystems.
• Install the input and output wires of the drive apart from each other.
• Use shielded twisted pair wires for wiring of the weak-current and signal circuits,
and always ground one of each pair of wires.
• Ground the drive with grounding wires as large and short as possible, separatelyfrom other devices and systems.
On 480V models, noise can be greatly reduced as they have a built-in EMC noise
filter on their input side.

Ground-fault relay

M
5

Noise filter

ElectronicsystemDrive[Measures against effects of leakage current]

19

Install the wires 30 cm or moreapart from each other.
When the wires are installed in thesame duct, separate the weak-current
ine and the strong-current line with ametallic separator.
Use twisted wires for weak-current lines.

Exclusive grounding,if necessary

Leakage current flow routes

The measures against the effects of leakage current are as follows:
1) Measures to prevent the malfunction of ELCBs(1) Decrease the PWM carrier frequency of the drive. Note)(2) Use radio-frequency interference-proof ELCBs as ground-fault interrupters in
not only the system into which the drive is incorporated but also other systems.
When ELCBs are used, the PWM carrier frequency needs to be increased tooperate the drive.
(3) When connecting multiple drives to a single ELCB, use an ELCB with a highcurrent sensitivity or reduce the number of drives connected to the ELCB.
2) Measures against malfunction of ground-fault relay:(1) Decrease the PWM carrier frequency of the drive. Note)(2) Install ground-fault relays with a high-frequency protective function in both thesame and other lines. When ELCBs are used, the PWM carrier frequency needs
to be increased to operate the drive.
3) Measures against noise produced by other electric and electronic systems:(1) Separate the grounding line of the drive from that of the affected electric andelectronic systems.
(2) Decrease the PWM carrier frequency of the drive. Note)
4) Measures against malfunction of external thermal relays:(1) Remove the external thermal relay and use the electronic thermal function of thedrive instead of it. (Unapplicable to cases where a single drive is used to drive
more than one motor. Refer to the instruction manual for measures to be taken
when thermal relays cannot be removed.)(2) Decrease the PWM carrier frequency of the drive. Note)
5) Measures by means of wiring and grounding(1) Use a grounding wire as large as possible.
(2) Separate the drive's grounding wire from that of other systems or install thegrounding wire of each system separately to the grounding point.
(3) Ground (shield) the power circuit wires with metallic conduits.
(4) Use the shortest possible wires to connect the drive to the motor.

Application to standard motors(1) Install ELCB or MCCB with an electric leak detector on the drive's power supply
input to protect the wiring.
(2) Avoid turning the ELCB or MCCB on and off frequently to turn on/off the motor.
(3) To turn on/off the motor frequently, ON/OFF the control terminals F (or R)-CC.

3

6

Wiring precautions

When changing the motor speed

Installing a molded-case circuit breaker [MCCB]

Ground fault

M

4

When wiring the drive

Exclusive grounding
Noise filter
Control panel enclosure
Sensor signal
Control signal

Ground every
shielded cable
at one point

Metallic conduit,
Plica tube,
shielded cable, etc

motorInstalling a magnetic contactor [MC] [secondary side](1) As a rule, if a magnetic contactor is installed between the drive and the motor,
do not turn of ON/OFF while running. (If the secondary-side contactor is turnedof ON/OFF while running, a large current may flow in the drive, causing drive
damage and failure.)(2) A magnetic contactor may be installed to change the motor or change to thecommercial power supply when the drive is stopped. Always use an interlock
with the magnetic contactor in this situation so that the commercial power supply
is not applied to the drive's output terminals.

External signal(1) Use a relay rated for low currents. Mount a surge absorber on the excitation coilof the relay.
(2) When wiring the control circuit, use shielded wires or twisted pair cables.
(3) Because all of the control terminals except FLA, FLB, FLC, R1A, R1B, R2A andR2B are connected to electronic circuits, insulate these terminals to prevent themfrom coming into contact with the power circuit.

Installing an overload relay(1) The drive has an electronic-thermal overload protective function.
However, in the following cases, the thermal relay operation level must be
adjusted or an overload relay matching the motor's characteristics must be
installed between the drive and the motor.
(a) When operating a motor that is smaller than applied motor capacity.
(b) When driving several motors simultaneously.
(2) When using the drive to control the operation of a constant-torque motor, change
the protective characteristic of the electronic thermal relay according to thesetting of constant torque motor.
(3) In order to adequately protect a motor used for low-speed operation, we
recommend the use of a motor equipped with a embedded thermal relay.

Reduction gear, belt, chain
Note that the lubrication capability of a reducer or a converter used as the interfaceof the motor and the load machine may affected at low speeds.
When operating at a frequencies over 60 Hz, power transmission mechanisms suchas reduction gear, belts and chains, may cause problems such as production ofnoise, a reduction in strength, or shortening of service life.

Frequency
Before setting the maximum frequency to 60 Hz or more, confirm that this operating
range is acceptable for the motor.

Application to special motors
Braking motor
When using a braking motor, if the braking circuit is directly connected to the drive's
output terminals, the brake cannot be released because of the lowered starting
voltage. Therefore, when using a braking motor, connect the braking circuit to thedrive's power supply side, as shown on the below. Usually, braking motors produce
larger noise in low speed ranges.
MC2
Power
supply

B

MC1
F

CC

P24

FP

LOW
Start/stop

Non-excitation
action type brake

IM
LOW

MC2

Gear motor
When using an industrial drive to drive a gear motor, inquire of the motor
manufacturer about its continuous operation range, since low-speed operation of agear motor may cause insufficient lubrication.

Toshiba Premium Gold Motor (High-efficiency power-saving motor)
Drive operation of Toshiba Premium Gold Motor is the best solution for savingenergy. This is because these motors have improved efficiency, power factor, andnoise/vibration reduction characteristics when compared to standard motors.

Pole-changing motor
Pole-changing motors can be driven by this drive. Before changing poles, however,be sure to let the motor come to a complete stop.

Hight-pole-count motors
Power factor improvement capacitors
Do not install a power factor improvement capacitors on the input or output side ofthe drive.
Installing a power factor improvement capacitor on the input or output side causes
current containing harmonic components to flow into the capacitor, adversely
affecting the capacitor itself or causing the drive to trip. To improve the power
factor, install an input AC reactor on the primary side of the drive.

Note that hight-pole count motors(8 or more poles), which may be used for fans,etc.,
have higher rated current than 4-pole moters.
The current ratings of multipole motors are relatively high. So, when selecting adrive, you must pay special attention to its current rating so that the current rating of
the motor is below that of the drive.

Single-phase motor
Because single-phase motors are equipped with a centrifugal switch and capacitors
for starting, they cannot be driven by a drive.

Installation of input AC rectors
These devices are used to improve the input power factor and suppress highharmonic currents and surges. Install an input AC reactor when using this drive
under the following conditions:(1) When the power supply capacity is 500kVA or more, and when it is 10 times ormore greater than the drive capacity.
(2) When the drive is connected the same power distribution system as a thyristorcommitted control equipment.
(3) When the drive is connected to the same power distribution system as that of
distorted wave-producing systems, such as arc furnaces and large-capacity
drives.

20

High-performance Drive

For drive users■■Selecting peripheral and wiring sizes devices for HD rating

Voltage
class

240V

480V

Applicable
motor
(kW)

Drive
type-form

0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
110
132
160
200
220
280

VFAS3-2004P
VFAS3-2007P
VFAS3-2015P
VFAS3-2022P
VFAS3-2037P
VFAS3-2055P
VFAS3-2075P
VFAS3-2110P
VFAS3-2150P
VFAS3-2185P
VFAS3-2220P
VFAS3-2300P
VFAS3-2370P
VFAS3-2450P
VFAS3-2550P
VFAS3-4004PC
VFAS3-4007PC
VFAS3-4015PC
VFAS3-4022PC
VFAS3-4037PC
VFAS3-4055PC
VFAS3-4075PC
VFAS3-4110PC
VFAS3-4150PC
VFAS3-4185PC
VFAS3-4220PC
VFAS3-4300PC
VFAS3-4370PC
VFAS3-4450PC
VFAS3-4550PC
VFAS3-4750PC
VFAS3-4900PC
VFAS3-4110KPC
VFAS3-4132KPC
VFAS3-4160KPC
VFAS3-4200KPC
VFAS3-4220KPC
VFAS3-4280KPC

Input
current
(A)

1.7
3.3
6.0
9.0
15.1
20.1
27.3
40.0
53.2
64.8
78.3
104.7
128.4
157.6
189.0
0.9
1.8
3.2
4.9
8.3
10.9
14.7
21.4
28.9
35.4
42.1
57.1
69.9
84.8
103.3
139.8
170.2
203.5
240.3
290.0
360.0
395.0
495.0

Molded-case circuit breaker(MCCB) or Earth leakage
circuit breaker (ELCB)
Note 1),2)

Magnetic contactor(MC) Note 1),3),4),5)

Rated current(A)

Operational
current (A)
AC1

3
5
10
15
20
30
40
50
75
100
100
150
175
200
250
3
3
5
10
10
15
20
30
40
50
60
75
100
125
125
175
225
250
300
350
500
500
700

20
20
20
20
20
32
32
50
60
80
80
150
200
260
260
20
20
20
20
20
20
20
32
32
50
50
60
80
100
135
200
260
260
260
350
450
450
660

■■Selecting peripheral and wiring sizes devices for ND rating
Drive Terminal
Screw size

Wire size (mm2) Note 6),7),9)Power circuit
Input terminal Output terminal(R, S, T)(U, V, W)
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
2.5
4
4
6
6
10
10
16
16
25
25
35
35
50
50
70
70
95
95
120
120
70x2
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
2.5
2.5
4
4
6
6
10
10
10
16
16
25
25
25
35
35
35
50
50
95
95
120
120
70x2
70x2
70x2
70x2
120x2
95x2
150x2
120x2
150x3
120x2
150x3
185x2

DC
terminal
2.5
2.5
2.5
2.5
2.5
4
6
10
16
25
35
50
70
95
120
2.5
2.5
2.5
2.5
2.5
2.5
2.5
4
6
10
10
16
25
35
50
70
95
70x2
70x2
150x2
150x3
150x3
150x4

Braking resistor/
Grounding
Braking unit
wire
(optional) Note 8)
1.5
1.5
1.5
1.5
1.5
1.5
2.5
4
6
10
16
25
35
50
50
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
2.5
2.5
4
6
10
16
16
35
35
50
70
95
150
150
150

2.5
2.5
2.5
2.5
4
6
10
16
16
16
25
35
50
70
95
2.5
2.5
2.5
2.5
2.5
2.5
2.5
4
10
10
16
16
16
16
25
50
70
95
95
120
150
150
120x2

Power
terminal

GroundingTerminal

M4

M5

M4

M5

M5

M5

Voltageclass

Applicable
motor
(kW)

Drive
type-form

0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
110
132
160
220
250
280
315

VFAS3-2004P
VFAS3-2007P
VFAS3-2015P
VFAS3-2022P
VFAS3-2037P
VFAS3-2055P
VFAS3-2075P
VFAS3-2110P
VFAS3-2150P
VFAS3-2185P
VFAS3-2220P
VFAS3-2300P
VFAS3-2370P
VFAS3-2450P
VFAS3-2550P
VFAS3-4004PC
VFAS3-4007PC
VFAS3-4015PC
VFAS3-4022PC
VFAS3-4037PC
VFAS3-4055PC
VFAS3-4075PC
VFAS3-4110PC
VFAS3-4150PC
VFAS3-4185PC
VFAS3-4220PC
VFAS3-4300PC
VFAS3-4370PC
VFAS3-4450PC
VFAS3-4550PC
VFAS3-4750PC
VFAS3-4900PC
VFAS3-4110KPC
VFAS3-4132KPC
VFAS3-4160KPC
VFAS3-4200KPC
VFAS3-4220KPC
VFAS3-4280KPC

240V
M8

M6
M8

M12

M8
M12

M10

M8
M10

M4

M5

M4

M5

M5

M5

M8

M6
M8

M12

M8
M12

M10

M8
M10

M10/M12

M12

M12

M12

Note 1) Selections for use of the Toshiba 4-pole standard motor with power supply voltage of 200V/400V-50Hz.
Note 2) Choose the MCCB or ELCB according to the power supply capacity.
For comply with UL and CSA standard, use the fuse certified by UL and CSA.
Note 3) When the motor is driven by commercial power supply switching, for example, use a magnetic contactor that is matched to AC-3 class motor rated current.
Note 4) Attach surge absorber to the magnetic contactor and exciting coil of the relay.
Note 5) In the case the magnetic contactor (MC) with 2a-type auxiliary contacts is used for the control circuit, raise the reliability of the contact by using 2a-type contacts inparallel connection.
Note 6) The recommended wire size is that of the wire (e.g. 600V class, HIV cable) with continuous maximum permissible temperature of 75°C. Ambient temperature is 50°C orless and the wiring distance is 30m or less.
The wire size comply with IEC60364-5-52 (Grounding wire: IEC60364-5-54).
It does not comply with UL Standard.
Note 7) For the control circuit, use shielded wires whose size (cross-section) is 0.75 mm2 or more.
Note 8) Choose the wiring size according to the braking resistor value.
Note 9) Use Crimp-style terminals for VFAS3-2450P,2550P, 4900PC to 4280KPC.

480V

Input
current
(A)

3.0
5.9
8.5
15.1
20.2
27.1
39.3
53.0
65.1
76.0
104.7
128.0
154.7
191.9
256.0
1.6
3.1
4.5
8.0
10.8
14.4
20.8
28.3
34.9
41.4
55.9
69.0
83.4
101.9
138.0
165.1
203.5
240.3
284.2
395.0
444.0
495.0
555.0

Molded-case circuit breaker(MCCB) or Earth leakage
circuit breaker (ELCB)
Note 1),2)

Magnetic contactor(MC) Note 1),3),4),5)

Rated current(A)

Operational
current (A)
AC1

5
10
15
20
30
40
50
75
100
100
150
175
200
250
350
3
5
10
10
15
20
30
40
50
50
75
100
125
125
175
200
250
300
350
500
500
700
1000

20
20
20
20
32
32
50
60
80
80
150
200
260
260
350
20
20
20
20
20
20
32
32
50
50
60
80
100
135
200
260
260
260
350
450
450
660
660

Drive Terminal
Screw size

Wire size (mm2) Note 6),7),9)Power circuit
Input terminal Output terminal(R, S, T)(U, V, W)
1.5
1.5
1.5
1.5
1.5
1.5
2.5
4
4
6
6
10
10
16
16
25
25
35
35
50
50
70
70
95
95
120
70x2
70x2
95x2
95x2
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
1.5
2.5
2.5
4
4
6
6
10
10
10
10
16
16
25
25
35
35
35
50
50
70
95
95
120
50x2
50x2
70x2
70x2
95x2
95x2
150x2
150x2
150x2
150x2
150x3
120x3
150x3
150x3

DC
terminal

Braking resistor/
Grounding
Braking unit
wire
(optional) Note 8)

2.5
2.5
2.5
2.5
4
6
10
16
25
35
50
70
95
50x2
70x2
2.5
2.5
2.5
2.5
2.5
2.5
4
6
10
10
16
25
35
50
70
95
70x2
70x2
95x2
150x2
185x2
150x3
150x3

1.5
1.5
1.5
1.5
1.5
2.5
4
6
10
16
25
35
50
50
70
1.5
1.5
1.5
1.5
1.5
1.5
1.5
2.5
2.5
4
6
10
16
16
35
35
35
50
70
95
150
150
150

2.5
2.5
2.5
4
6
10
16
16
16
25
35
50
70
95
120
2.5
2.5
2.5
2.5
2.5
2.5
4
10
10
16
16
16
16
25
50
70
95
95
120
150
150
120x2
120x2

Power
terminal

GroundingTerminal

M4

M5

M4

M5

M5

M5

M8

M6
M8

M12

M8
M12

M10

M8
M10

M4

M5

M4

M5

M5

M5

M8

M6
M8

M12

M8
M12

M10

M8
M10

M10/M12

M12

M12

M12

Note 1) Selections for use of the Toshiba 4-pole standard motor with power supply voltage of 200V/400V-50Hz.
Note 2) Choose the MCCB or ELCB according to the power supply capacity.
For comply with UL and CSA standard, use the fuse certified by UL and CSA.
Note 3) When the motor is driven by commercial power supply switching, for example, use a magnetic contactor that is matched to AC-3 class motor rated current.
Note 4) Attach surge absorber to the magnetic contactor and exciting coil of the relay.
Note 5) In the case the magnetic contactor (MC) with 2a-type auxiliary contacts is used for the control circuit, raise the reliability of the contact by using 2a-type contacts inparallel connection.
Note 6) The recommended wire size is that of the wire (e.g. 600V class, HIV cable) with continuous maximum permissible temperature of 75°C. Ambient temperature is 50°C orless and the wiring distance is 30m or less.
The wire size comply with IEC60364-5-52 (Grounding wire: IEC60364-5-54). It does not comply with UL Standard.
Note 7) For the control circuit, use shielded wires whose size (cross-section) is 0.75 mm2 or more.
Note 8) Choose the wiring size according to the braking resistor value.
Note 9) Use Crimp-style terminals for VFAS3-2450P,2550P, 4900PC to 4280KPC.

Selecting the Capacity (model) of the Drive
selection
Capacity

Refer to the applicable motor capacities listed in the standard specifications.
When driving a high-pole motor, special motor, or multiple motors in parallel, select such a drivethat the sum of the motor rated current multiplied by 1.05 to 1.1 is less than the drive's rated output
current value.

Acceleration/deceleration times

The actual acceleration and deceleration times of a motor driven by a drive are determined by thetorque and moment of inertia of the load, and can be calculated by the following equations.
The acceleration and deceleration times of a drive can be set individually. In any case, however, theyshould be set longer than their respective values determined by the following equations.
Acceleration time

(JM+JL) x ΔN
ta = 9.56 x (TM–TL) (sec.)

Deceleration time

(JM +JL) x ΔN
ta = 9.56 x (TB+TL) (sec.)

Conditions

JM : Moment of inertia of motor (kg.m2)
JL : Moment of inertia of load (kg.m2) (converted into value on motor shaft)
ΔN : Difference in rotating speed between before and after acc. or dce. (min.–1)
TL : Load torque (N.m)
TM : Motor rated torque x 1.1 (N.m) ... V/f control: Motor rated torque x 1.2 (N.m) ... Vector operation control
TB : Motor rated torque x 0.2 (N.m)
When a braking resistor or a braking resistor unit is used:
Motor rated torque x 0.8-1.0 (N.m)(

21

Allowable torque characteristics

When a standard motor is combined with a drive to perform variable speed operation, the motor
temperature rises slightly higher than it normally does during commercial power supply operation.
This is because the drive output voltage has a sinusoidal (approximate) PWM waveform. In addition,
the cooling becomes less effective at low speed, so the torque must be reduced according to thefrequency.
When constant-torque operation must be performed at low speeds, use a constant-torque motor
designed specifically for use with drives.

Starting characteristics

When a motor is driven by a drive, its operation is restricted by the drive’s overload current rating, so
the starting characteristic is different from those obtained from commercial power supply operation.
Although the starting torque is smaller with a drive than with the commercial power supply, a highstarting torque can be produced at low speeds by adjusting the V/f pattern torque boost amount orby employing vector control. When a larger starting torque is necessary, select a drive with a larger
capacity and examine the possibility of increasing the motor capacity.

)22High-performance Drive

Insert type options

Peripheral devices

This drive is equipped with two optin slots (A, B) as standard. The option adaptor (option) can be mounted.

■■Table of optional devices■■Insert type options
Power supply

Molded-case circuit breaker MCCB
or Earth leakage circuit breaker (ELCB)

Name

A,B,C

I/O extension 1

This option is covenient for adding on I/O terminals.(Type:ETB013Z)

A,B,C

I/O extension 2

This option is covenient for adding on I/O terminals.(Type:ETB014Z)

B

Digital encoder

Closed loop operation is possible by combining with a motor equipped with a sensor.(Type:VEC008Z)

B

Resolver

Closed loop operation is possible by combining with a motor equipped with a sensor.(Type:VEC010Z)

C

Safety option

This option enables adding on more safety functions. (Type:SFT001Z)A

PROFINET

This option enables PROFINET connectivity with a host controller or other PLC. (Type:PNE001Z)A

PROFIBUS-DP

This option enables PROFIBUS-DP connectivity with a host controller or other PLC.
(Type:PDP003Z)A

DeviceNet

A

EtherCAT

This option enables EtherCAT connectivity with a host controller or other PLC. (Type:IPE003Z)

CANopen

This option enables CANopen connectivity with a host controller or other PLC.
(Type:CAN001Z,CAN002Z,CAN003Z)

A

Magnetic contactor MC

Function/Purpose, etc

Refer to24

This option enables DeviceNet connectivity with a host controller or other PLC. (Type:DEV003Z)■■External options
No.

1 Input AC reactor

Name

Slot

①

Name

2 DC reactor

B C

Surge Voltage
restriction

Input AC reactor

EnabledEnabledEnabledDC reactor

Enabled (large)

Enabled (large)

Disabled

A DC reactor is a reactor to connect with the DC terminal, and used for improving input power
factor and reducing harmonics. It has better power factor improvement effect than an input ACreactor. When a facility applying the drive requires high reliability, it is recommended to use withan input AC reactor that has surge voltage restriction effect.
However, the frame size A1 to A6 of the drive has a built-in DC reactor as standard, and theframe size A7 and A8 attached with a DC reactor, no option is available.

EMC filter

When installing an EMC filter and wire properly, it can comply with EMC Directive.
480 V model of the drive has the built-in EMC filter as standard; however, if an EMC filter
is added externally, noise reduction becomes more effective. Please contact your Toshiba
distributor for details.

④

Braking resistor
Braking unit

It is a resistor to consume regenerative energy from a motor.
When making frequent rapid deceleration and stop, it is used to shorten deceleration time withload in large inertia. A braking unit is necessary in addition to a braking resistor for the frame
size A6 and A8.

28 to 30⑤

Motor-end
surge voltage
suppression
filter(Only 480V class)

When operating a 480 V class general purpose motor with a voltage type PWM control drivethat uses high speed switching element (IGBT, etc.), surge voltage exceeding the insulation levelof motor winding is generated depending on power supply voltage, motor wire length and its
laying method, and type. When the condition is repeatedly applied for a long time, it may cause
deterioration of insulation on the motor.
Such measures as installation of an AC reactor, surge voltage suppression filter, sinusoidal
filter on the drive output side (secondary side), and use of a high insulation strength motor arenecessity.

27⑥

Control power
supply unit

Control power need not be input separately as it is supplied internally on the drive from thepower circuit power supply.
Use this option when backing up only by the control power supply when the power circuit isshut off. This is +24 VDC output common to both 240 and 480 V models. (Type : CPS002Z)⑦

USB
communications
conversion unit

It enables to set and manage parameters on a personal computer.
Connect between the RS485 communication connector 2 of the drive and a personal computer.
Use the specific cable for the drive side, and a commercial USB cable (USB 1.1/2.0 compatible
A-B connection type) for a personal computer side. Software PCM002Z for parameter
management is required. (Type: USB001Z, Specific cable Type: CAB0011 (1 m), CAB0013 (3 m),
CAB0015 (5 m))

32⑧

Door mounting kit
for Operation panel

The operation panel can be mounted on a cabinet surface by means of an door mounting kit.
(Type:SBP010Z, Specific cable Type:CAB0071 (1 m), CAB0073 (3 m), CAB0075 (5 m),
CAB00710 (10 m))

32⑨

LED extension
panel

It is an extension panel for LED display. A specific cable is used to connect between the driveand LED panel. (Type: RKP002Z, Specific cable Type: CAB0011 (1 m), CAB0013 (3 m), CAB0015(5 m); Type: RKP007Z, Specific cable Type: CAB0071 (1 m), CAB0073 (3 m), CAB0075 (5 m))

32⑩

Flange mounting kit

This allows heat generated inside panels to be reduced.

31⑪

Operation panel

Has a built-in frequency type, frequency setter and RUN-STOP (forward run, reverse run) switch.
(Type: CBVR-7B1)

33

5 Motor-end surge voltage--

Multifunction programmable open
collector output

Harmonics are defined as sinusoidal waves that is multiple frequency ofcommercial power supply (base frequency: 50Hz or 60Hz). Commercial
power supply including harmonics has a distorted waveform.
Some electrical and electronic devices produce distorted waves in their
rectifying and smoothing circuits on the input side. Harmonics produced bya device influence other electrical equipment and facilities in some cases (forexample, overheating of phase advancing capacitors and reactors).

23

ETB013Z

A, B, CETB014Z
VEC008Z
VEC010Z
SFT001Z
PNE001Z
IPE003Z
PDP003Z
DEV003Z
CAN001Z
CAN002Z
CAN003Z

A, B ,C
B
B
C
A
A
A
A
A

DisableDisableMultifunction programmablerelay contact output: 3 relay(1a)250 Vac-2A(cosφ=1), 30 Vdc-2A (at resistive load)
250 Vac-1A(cosφ=0.4), 30 Vdc-1A (L/R=7 ms)

DisableAnalog input

Differential analog input: 2 points
Voltage input: -10Vdc to +10Vdc
Impedance: 20kohm
Current input: 0 to 20mA
Impedance: 250ohm

Disable■■Function sensor feedback
Type-form

33

ETB014Z

Multifunction programmable contact input : 6 points
Logic type selected by DICC wiring.
Sink logic:ON<10V, 16V<OFF
Source logic:OFF<5V, 11V<ON
Multifunction programmable open collector output : 2 points
Logic Type selected by DQCC wiring
Max. switching voltage<= 30V
Max. switching current<= 100mA
Voltage drop at 100mA load <= 3V

Multifunction programmable relay
contact output

VEC008Z

VEC010Z

Sensor type

Incremental rotary encoder

Specification

Signal interface: differential line driver (TIA/EIA RS422)
Pulse frequency: 300kHz or less (Duty: 50% ±10%)
Maximum load of power supply for encoder:
24V 100mA, 12V 100mA, 5V 250mA

Connector

D subminiature connector (DE-15 / HD15)

ResolverSignal interface:Ref+, Cos-, Sin+, Cos+, Sin-, RefExcitation Carrier:3 to 12kHz
Pole pairs number = 1
Transformation ratio = 0.5
Reference (Excitation voltage): 7Vrms
D subminiature connector (DE-9)■■How to install
Option slot A, B

Option Slot C

Control terminal
block

Note1) Ethernet cable: LAN cable comply with ANSI/TIA/EIA-568-B.2 (CAT5E or successor)
Note2) A lithium battery for internal real time clock of the operation panel (equipped as standard at the time of shipping): CR2032EC(Toshiba)

Harmonic current and influence to power supply

Slot avaiability

ETB013Z

Multifunction programmable contact
input

③

6 Control power supply unit

M

Harmonics
reduction

DC reactor

4 Braking unit

suppression filter (Only 480V class)Power factor
improvement

Type-form

26

②

Drive

4 Braking resistor

Type

Type-form■■Function of I/O extension

EffectA

I/O extension 2
Digital encoder
Resolver
Safety option
PROFINET
EtherCATPROFIBUS-DP
DeviceNet

Refer toInput AC reactor is used for improving input power factor on the drive power side (primary side),
reducing harmonics or restriction of surge voltage.
It is also installed when the power supply capacity is 500 kVA or more and is 10 times or moreof the drive capacity, and when devices that cause distorted waves (a device with thyristor, etc.)
and a large capacity drive is connected on the same power distribution line. Install an input ACreactor between the power supply and the drive (primary side).

3 EMC filter

I/O extension 1

CANopen
Function/Purpose, etc

Input AC reactor

Specification
6x digital input
2x digital output
2x analog input
3x 1a relay
RS422 Line receiver
ResolverSS1, SS2, SOS, SBC, SLS, SDI
PROFINET interface
EtherCAT interface
PROFIBUS-DP interface
DeviceNet interface
CANopen interface : RJ45
: D-sub: Open style

Option adaptor (option): SBP011Z

Measures for suppressing higher harmonics
No.

Measures

Description

1

Connecting a reactor

The leakage of a harmonic current from a drive can be restricted byconnecting an input AC reactor (ACL) on the input side of the drive or a DC
reactor (DCL) to the DC section of the drive.

2

Connecting a higher
harmonic suppressingunit

A PWM converter that shapes the waveform of an input current into asubstantially sinusoidal waveform. The leakage of a harmonic current from a
power supply can be restricted by connecting a harmonic suppressing unit.

3

Connecting a higher
harmonic suppressing
phase advancing
capacitor

A harmonic current can be absorbed by the use of a phase advancing
capacitor unit composed of a phase advancing capacitor and a DC reactor.

4

Multi-pulse operation oftransformation

For delta-delta connection and delta-Y connection transformers, the effect of
12 pulses can be obtained by distributing the load evenly, and thus currents
containing fifth-order and seventh-order harmonics can be suppressed.

5

Other measures

Harmonic currents can also be suppressed by the use of passive (AC) andactive filters.

Option slot

Cassette
optionCassette
optionAdaptor coverNote) The depth of the drive increases about 44mm
when the option is mounted.

24

High-performance Drive■■External options for HD rating
Braking resistor

Motor-end surge voltage
suppression filter

Input AC reactor
Flange mounting kit

0.4

VFAS3-2004P

PFL-2005S

PBR-2007

0.75

VFAS3-2007P

PFL-2005S

PBR-2007

FOT018Z

1.5

VFAS3-2015P

PFL-2011S

PBR-2022

FOT018Z

2.2

VFAS3-2022P

PFL-2011S

PBR-2022

FOT018Z

4.0

VFAS3-2037P

PFL-2018S

PBR-2037

FOT019Z

5.5

VFAS3-2055P

PFL-2025S

PBR7-004W015

FOT020Z

7.5

VFAS3-2075P

PFL-2050S

PBR7-004W015

FOT020Z

11

VFAS3-2110P

PFL-2050S

15

VFAS3-2150P

PFL-2100S

PBR7-008W7R5

FOT021Z

18.5

VFAS3-2185P

PFL-2100S

PBR7-008W7R5

FOT021Z

22

VFAS3-2220P

PFL-2100S

PBR7-017W3R7

FOT022Z30

VFAS3-2300P

PFL-2150S

PBR7-017W3R7

FOT022Z

37

VFAS3-2370P

PFL-2150S

PBR7-035W1R8

FOT022Z

45

VFAS3-2450P

PFL-2200S

PB7-4132K

PBR7-035W1R8

PB7-4132K

PBR7-035W1R8

Built-inBuit-in

PBR7-008W7R5

FOT018Z-

VFAS3-2550P

PFL-2300S

VFAS3-4004PC

PFL-4012S

PBR-2007

MSF-4015Z

FOT018Z

0.75

VFAS3-4007PC

PFL-4012S

PBR-2007

MSF-4015Z

FOT018Z

1.5

VFAS3-4015PC

PFL-4012S

PBR-2007

MSF-4015Z

FOT018Z

VFAS3-4022PC

PFL-4012S

PBR-2007

MSF-4037Z

FOT018Z

4.0

VFAS3-4037PC

PFL-4012S

PBR-4037

MSF-4037Z

FOT018Z

5.5

VFAS3-4055PC

PFL-4025S

PBR7-004W060

MSF-4075Z

FOT019Z

VFAS3-4075PC

PFL-4025S
PFL-4025S

15

VFAS3-4150PC

PFL-4050S

18.5

VFAS3-4185PC

PFL-4050S

Built-inBuilt-in

PBR7-004W060

MSF-4075Z

FOT019Z

PBR7-008W030

MSF-4150Z

FOT020Z

PBR7-008W030

MSF-4150Z

FOT020Z

PBR7-008W030

MSF-4220Z

FOT020Z

22

VFAS3-4220PC

PFL-4050S

PBR7-017W015

MSF-4220Z

FOT021Z30

VFAS3-4300PC

PFL-4100S

PBR7-017W015

MSF-4370Z

FOT021Z

37

VFAS3-4370PC

PFL-4100S

PBR7-017W010

MSF-4370Z

FOT021Z45

VFAS3-4450PC

PFL-4100S

PBR7-017W7R5

MSF-4550Z

FOT022Z

55

VFAS3-4550PC

PFL-4150S

PBR7-017W7R5

MSF-4550Z

FOT022Z75

VFAS3-4750PC

PFL-4150S

PBR7-017W3R7MSF-4750Z

FOT022Z90

VFAS3-4900PC

PFL1-4260

PB7-4132K

DGP600W-B2M/C2M

FOT023Z110

VFAS3-4110KPC

PFL1-4260

PB7-4132K

DGP600W-B2M/C2M

FOT023Z

132

VFAS3-4132KPCPFL1-4350

PB7-4132K

DGP600W-B2M/C2M

160

VFAS3-4160KPC

PFL1-4350

Built-in

DGP600W-B2M/C2M

200

VFAS3-4200KPC

PFL1-4455

PB7-4200K

DGP600W-B3M/C3M

220

VFAS3-4220KPC

PFL1-4455

PB7-4200K

DGP600W-B3M/C3M

FOT014Z/FOT015Z

280

VFAS3-4280KPC

PFL1-4800

PB7-4200K

DGP600W-B4M/C4M

FOT014Z/FOT015Z

Braking unit

Braking resistor

Attached as
standard

Fig.B

Terminal box with coverD

VF-AS3AC reactor

FOT023Z

2.2

VFAS3-4110PC

Fig.A

Power
supply

U

X

V

Y

W

Z

R

U

S

V

T

W

M

FOT023Z

55

11■■Connection diagram

FOT021Z

0.4

7.5■■External dimensions

H

Braking unit

Refer to P.27 for selectionof Motor-end surge voltage
suppression filter.

A
W

A
W

D

4-φF holes

Fig.C

4-φF holes

Fig.D

D

VF-AS3

D

MCCB
Power
supplyA
W

A
W

4-φF holes

AC reactor
U
X
V
W

MC

Y
Z

Control power
supply unitH

DC reactor
(DCL)

H

Input AC reactor (ACL)

H2

480V

Drive type-form

H

240V

Applicablemotor (kW)

H2

Voltageclass

Groundingterminal
M6 screw

R

U

S
T

V
W

M

+SU
CC

In case of using control power supply
unit (option)
E

FOT023Z
FOT013Z
FOT014Z/FOT015Z

Fig.E

D
140
φ18

240V

480V

25

Applicablemotor(kW)Drive type-form

Input AC reactor (ACL)

0.75

VFAS3-2004P

PFL-2005S

PBR-2007

FOT018Z

1.5

VFAS3-2007P

PFL-2011S

PBR-2022

FOT018Z

2.2

VFAS3-2015P

PFL-2011S

PBR-2022

FOT018Z

4.0

VFAS3-2022P

PFL-2018S

PBR-2037

FOT018Z

5.5

VFAS3-2037P

PFL-2025S

PBR7-004W015

FOT019Z

7.5

VFAS3-2055P

PFL-2050S

PBR7-004W015

FOT020Z

11

VFAS3-2075P

PFL-2050S

15

VFAS3-2110P

PFL-2100S

18.5

VFAS3-2150P

PFL-2100S

PBR7-008W7R5

FOT021Z

22

VFAS3-2185P

PFL-2100S

PBR7-008W7R5

FOT021Z30

VFAS3-2220P

PFL-2150S

PBR7-017W3R7

FOT022Z

37

VFAS3-2300P

PFL-2150S

PBR7-035W1R8

FOT022Z

45

VFAS3-2370P

PFL-2200S

PBR7-035W1R8

FOT022Z

55

VFAS3-2450P

PFL-2300S

PB7-4132K

PBR7-035W1R8

FOT023Z

PB7-4132K

DGP600W-B1M/C1M

Built-inBuit-in

Motor-end surge voltage
suppression filter

PBR7-008W7R5
PBR7-008W7R5

Flange mounting kit

VFAS3-2550P

PFL1-2350

VFAS3-4004PC

PFL-4012S

PBR-2007

MSF-4015Z

FOT018Z

1.5

VFAS3-4007PC

PFL-4012S

PBR-2007

MSF-4015Z

FOT018Z

2.2

VFAS3-4015PC

PFL-4012S

PBR-2007

MSF-4037Z

FOT018Z

VFAS3-4022PC

PFL-4012S

PBR-4037

MSF-4037Z

FOT018Z

5.5

VFAS3-4037PC

PFL-4025S

PBR7-004W060

MSF-4075Z

FOT018Z

7.5

VFAS3-4055PC

PFL-4025S

PBR7-004W060

MSF-4075Z

FOT019Z

VFAS3-4075PC

PFL-4025S
PFL-4050S

18.5

VFAS3-4150PC

PFL-4050S

22

VFAS3-4185PC

PFL-4050S

30

VFAS3-4220PC

PFL-4100S

Built-inBuilt-in

PBR7-008W030

MSF-4150Z

FOT019Z

PBR7-008W030

MSF-4150Z

FOT020Z

PBR7-008W030

MSF-4220Z

FOT020Z

PBR7-008W030

MSF-4220Z

FOT020Z

PBR7-017W015

MSF-4370Z

FOT021Z

37

VFAS3-4300PC

PFL-4100S

PBR7-017W015

MSF-4370Z

FOT021Z45

VFAS3-4370PC

PFL-4100S

PBR7-017W010

MSF-4550Z

FOT021Z55

VFAS3-4450PC

PFL-4150S

PBR7-017W7R5

MSF-4550Z

FOT022Z75

PBR7-017W3R7MSF-4750Z

FOT022Z

VFAS3-4550PC

PFL-4150S

90

VFAS3-4750PC

PFL1-4260

DGP600W-B2M/C2M

FOT022Z110

VFAS3-4900PC

PFL1-4260

PB7-4132K

DGP600W-B2M/C2M

FOT023Z

132

VFAS3-4110KPC

PFL1-4350

PB7-4132K

DGP600W-B2M/C2M

160

VFAS3-4132KPCPFL1-4350

PB7-4132K

DGP600W-B2M/C2M

220

VFAS3-4160KPC

PFL1-4455

250

VFAS3-4200KPC

PFL1-4800

280

VFAS3-4220KPC

PFL1-4800

315

VFAS3-4280KPC

PFL1-4800

Attached as
standard

Model

Rating

FOT023Z

4.0

VFAS3-4110PC

Groundingterminal
M6 screw

E

FOT021Z

75

11

A
W

FOT020Z
-

0.75

15

58

DC reactor (DCL)320

Voltage
class

H■■External options for ND rating

Refer to P.27 for selectionof Motor-end surge voltage
suppression filter.

PFL-2005S

3φ-230V-5.5A-50/60Hz

PFL-2011S

3φ-230V-11A-50/60Hz

PFL-2018S
PFL-2025S

3φ-230V-18A-50/60Hz
3φ-230V-25A-50/60Hz

PFL-2050S

3φ-230V-50A-50/60Hz

PFL-2100S

3φ-230V-100A-50/60Hz

PFL-2150S

3φ-230V-150A-50/60Hz

PFL-2200S
PFL-2300S
PFL1-2350

3φ-230V-200A-50/60Hz
3φ-230V-300A-50/60Hz
3φ-230V-350A-50/60Hz

PFL-4012S

3φ-460V-12.5A-50/60Hz

FOT023Z
FOT023Z

Built-in

DGP600W-B3M/C3M

PB7-4200K

DGP600W-B4M/C4M

PB7-4200K

DGP600W-B4M/C4M

FOT014Z/FOT015Z

PB7-4200K

DGP600W-B4M/C4M

FOT014Z/FOT015Z

PFL-4025S

3φ-460V-25A-50/60Hz

FOT013Z
FOT014Z/FOT015Z

PFL-4050S

3φ-460V-50A-50/60Hz

PFL-4100S

3φ-460V-100A-50/60Hz

PFL-4150S

3φ-460V-150A-50/60Hz

PFL1-4260

3φ-460V-260A-50/60Hz

PFL1-4350

3φ-460V-350A-50/60Hz

PFL1-4455

3φ-460V-455A-50/60Hz

PFL1-4800

3φ-460V-800A-50/60Hz

Drive type-form
VFAS3-2004P(HD)、2007P(HD)VFAS3-2004P(ND)
VFAS3-2015P(HD)、2022P(HD)VFAS3-2007P(ND)、2015P(ND)
VFAS3-2037P(HD)、VFAS3-2022P(ND)
VFAS3-2055P(HD)、VFAS3-2037P(ND)
VFAS3-2075P(HD)、2110P(HD)VFAS3-2055P(ND)、2075P(ND)
VFAS3-2150P(HD)、2185P(HD)、2220P(HD)VFAS3-2110P(ND)、2150P(ND)、2185P(ND)
VFAS3-2300P(HD)、2370P(HD)VFAS3-2220P(ND)、2300P(ND)
VFAS3-2450P(HD)、VFAS3-2370P(ND)
VFAS3-2550P(HD)、VFAS3-2450P(ND)
VFAS3-2550P(ND)
VFAS3-4004PC(HD) ～ VFAS3-4037PC(HD)VFAS3-4004PC(ND) ～ VFAS3-4022PC(ND)
VFAS3-4055PC(HD) ～ VFAS3-4110PC(HD)VFAS3-4037PC(ND) ～ VFAS3-4075PC(ND)
VFAS3-4150PC(HD) ～ VFAS3-4220PC(HD)VFAS3-4110PC(ND) ～ VFAS3-4185PC(ND)
VFAS3-4300PC(HD) ～ VFAS3-4450PC(HD)VFAS3-4220PC(ND) ～ VFAS3-4370PC(ND)
VFAS3-4550PC(HD)、4750PC(HD)VFAS3-4450PC(ND)、4550PC(ND)
VFAS3-4900PC(HD)、4110KPC(HD)VFAS3-4750PC(ND)、4900PC(ND)
VFAS3-4132KPC(HD)、4160KPC(HD)VFAS3-4110KPC(ND)、4132KPC(ND)
VFAS3-4200KPC(HD)、4220KPC(HD)VFAS3-4160KPC(ND)
VFAS3-4280KPC(HD)VFAS3-4200KPC(ND) ～ VFAS3-4280KPC(ND)

Dimensions(mm)
W

H

D

H2

A

E

F

105

115

72.5

－

90

55

5

130

140

85

－

115

60

5

130
125

140
130

85
100

－
－

115
50

60
83

5
7

155

140

115

－

50

95

7

230

210

150

－

60

90

8

175

290

160

220

60

110

8

195
235
260

320
370
330

170
200
165

240
280
255

65
75
85

115
128
121

10
10

125

130

95

－

50

79

7

－

50

155

155

110

－

External
dimension
diagram

Terminals

Approx.
mass(kg)

Terminal block M3.5

1.2

A

2.3
Terminal block M4

B

C
D

2.5
2.6

Terminal block M6

3.4

Terminal block M8

8.2

Ring terminal 60-10

11.3

Ring termina 80-10
Ring terminal 150-10
Ring terminal 100-12

15.1
23.1
19
2.3

Terminal block M4
94

7

4.9
B

155

165

140

－

50

112

7

Terminal block M6

6.6

235

250

170

－

75

105

10

Terminal block M8

17.6

235

360

190

280

75

115

10

Ring terminal 80-10

20.3

260

380

170

295

85

126

－

Ring terminal 80-12

22

260

380

185

295

85

141

－

Ring terminal 100-12

28

360

470

165

370

125

121

－

Ring terminal 150-16

37

360

400

220

－

125

136

－

φ18

62

C

D

E

26

High-performance Drive

Motor end surge voltage suppression filter (Only 480V class)

Braking resistor■■Braking resistor (PBR)

4-φ12 holes

Terminal
block

E (Mounting dimension)

Name
plate

E (Mounting dimension)

4-φ12 holes

2-Hanging
bolts

Fig.A

Fig.B

4-φ12 holes

Groundingterminal M5
Terminal
block

Groundingterminal M5

B

D ( Mounting
dimension )Wire opening

Name plate

E (Mounting dimension)

ON

Fig.C

D (Mounting dimension)
A

C

E

PB

Note)

MSF-4037Z
MSF-4075Z
MSF-4150Z
MSF-4220Z
MSF-4370Z
MSF-4550Z
MSF-4750Z

VFAS3-4004PC(HD) to VFAS3-4015PC(HD)VFAS3-4004PC(ND), 4007PC(ND)
VFAS3-4022PC(HD), 4037PC(HD)VFAS3-4015PC(ND), 4022PC(ND)
VFAS5-4055PC(HD), 4075PC(HD)VFAS3-4037PC(ND), 4055PC(ND)
VFAS3-4110PC(HD), 4150PC(HD)VFAS3-4075PC(ND), 4110PC(ND)
VFAS3-4185PC(HD), 4220PC(HD)VFAS3-4150PC(ND), 4185PC(ND)
VFAS3-4300PC(HD), 4370PC(HD)VFAS3-4220PC(ND), 4300PC(ND)
VFAS3-4450PC(HD), 4550PC(HD)VFAS3-4370PC(ND), 4450PC(ND)
VFAS3-4750PC(HD)VFAS3-4550PC(ND)

9.5External dimension
diagram

D (Mounting dimension)A

Approx.
mass (kg)

A

B

C

D

E

F

G

310

255

300

200

270

55

189

M4

12

310

255

300

200

270

55

209

M4

20

310

315

350

200

320

55

249

M5

30

330

355

400

200

370

65

289

M6

40

330

405

400

200

370

65

279

M6

52

426

372

512

260

490

83

349.5

M8

75

450

395

632

260

610

95

372.5

M10

110

M10

120

A

B

C

2-φ7 holes

400W class
1.5kW class
5kW class

Wiring port dimension
83
1.5
R1

70

Wiring port
Grounding terminal (M5 screw)Note) Wiring port of PBR7-052W□□□ is different.

415

700

260

678

95

392.5

A

B

C

D

E

G

Approx.
mass(kg)

External
dimension
diagramConnection
diagram

42

182

20

4.2

172

-

0.28

A

D

120
240
395

320
430
616

115
190
190

110
190
320

230
414
600

48
52
52

3.4
10
29

B

Dimensions (mm)Model
PBR-2007
PBR-2022
PBR-2037
PBR-4037
PBR7-004W □□□PBR7-017W □□□PBR7-052W □□□■■Braking resistor (DGP600)
Fig.F

Fig.G

VF-AS3Power
supplyMCCBMC■■Connection diagram

MC
Note 1)R
S
T

Reactor
U1 U2
V1 V2
W1 W2

U
V
W

FLB
FLC

Braking
resistor(DGP600W)

1

TH1
TH2

M

IM

PA

4-19 holes

B1

Note 2)B2

L1 2 T1

95

6 T3 5 L3

96

e

b

Power
supplyFN filter

U
V
W

MC

E

OFF E

a
VF-AS3

R
S
T
PB

ON

■■External dimensions

E

C

Note 1) □□□ in the type-form are numeric character. Please refer to the “Selection of braking resistor” in the next
page.
Note 2) The rating shows the synthetic resistor value (Ohm) and the synthetic resistor power (Watt). The word in theparentheses shows the composition of resistor elements.
Note 3) The allowable continuous regenerative power differs on the resistor value or power tolerance. Please refer
the “Selection of braking resistor” in the next page.

C
450

Braking resistor
TH2Note) In case of 480V class, please apply
the 200V to the operation circuit byusing control transformer or 200V
power supply.

G

Terminal screwStandard

G

MSF-4015Z

Dimensions (mm)Drive type-form

Type

NP

Note 1) To be installed floor horizontal mounting.
Note 2) To be used that carrier frequency is 15kHz or less, and output frequency is 60Hz or less.

Model

TH1

TH1
TH2

44

At the system of operation of the 480V class motor by the voltage type PWM drive with using superhigh-speed switching device(ex.IGBT). the degradation of insulation of motor wiring may be occurredby the length conditions of the cable, laid down of the cable and the constants of the cable.
In this case, the following countermeasures are suggested.
1) Use of the enhanced insulation type of motor2) Suppress the surge voltage by AC reactors in the load side or surge suppression filter.

M

PA

5
R3

MC

IM

PA

FLB
FLC

23

X
Y
Z

PB

OFF E

2-φ19

B

U
V
W

U
V
W

U
V
W

MC

Wiring port (Rubber bushing)E (Mounting dimension)

R
S
T

R
S
T

Power
supplyR6PowersupplyMSF filter

IM

PA/+

VF- AS3MCN P■■Countermeasure of motor end surge voltage

VF-AS3V

Fig.E

Name plate

to center)
G ( ofHeight
wiring port■■Connection diagram

U
W

Braking resistor

Wiring port
to center)
G ( Heightof wiring port

R
S
T

PB

C

D ( Mounting
dimension )Wiring port

VF-AS3Power
supply500 (Length of lead wire)

D ( Mounting
dimension )Fig.D

4-φ5 holes

B

Fig.C
4-Hangingbolts

A
D (Mounting dimension)

Fig.B

E (Mounting dimension)

Fig.A

E (Mounting dimension)■■External dimensions

Th-Ry

M

c
c1

f

For VFAS3-2550P, 4900PC to 4132KPC, 4220KPC to 4280KPC,
in requires the braking unit.

CapacitorHG

2-φ13.5 holes
2-φ13.5 holesKJ

6-φ9 holesLdApplicable
Motor (kW) Note 1)
90
110
132
160
200
220
250
280

27

Note 1) Approximately 10% of voltage drop is generated by the filter, depending on the outpur current and the motor power factor.
Motor should be selected with this voltage drop in consideration.
Note 2) Select the drive with the capacity that is larger than the motor, due to the carrier frequency limitation of the filter and the current reduction of the drive.
Refer to "E6582116: Instruction manual for load reduction" for detail of current reduction.
Note 3) Set the parameter [F316: Carrier frequency control] to "4" or "5" (sinusoidal filter usage).
([F300: Carrier frequency] and [Pt: V/f pattern] are limited, refer to Instruction manual for detail.)
Note 4) Use the filter under the condition that the drive output frequency is 100Hz or less and the ambient temperature is -10 to 50°C.
Drive type-form Note 2) 3)

HD rating
VFAS3-4110KPC
VFAS3-4132KPC
VFAS3-4160KPC
VFAS3-4200KPC
VFAS3-4220KPC
VFAS3-4280KPC-

ND rating
VFAS3-4900PC
VFAS3-4110KPC
VFAS3-4132KPC
VFAS3-4160KPC
VFAS3-4160KPC
VFAS3-4200KPC
VFAS3-4220KPC
VFAS3-4280KPC

Model Note 4)

FN5040-410-99

Dimensions (mm)
a

b

c

c1

G

H

M

d

e

f

J

K

L

Approx.mass
(kg)

490

600

240

355

430

194

10.6x18.6

170

240

328

150

300

150

177

FN5040-480-99

510

618

270

410

430

195

13x27

270

220

328

150

300

250

220

FN5040-750-99

660

670

290

468

570

220

13x26

375

200

555

255

510

350

455

Note 1) In case of 480 V class, please apply the 200V to the operation circuit by using control transformer or 200V power supply.
Note 2) Please twist the wire by 10 cm pitch. The distance between resistor power wiring and the control wiring should be over 20 cm.
Note 3) Please make a short circuit between the 2/T1 and 6/T3 of the thermal relay.

Standard
DGP600W-B1
DGP600W-B2

Model
With cover Note 1)
DGP600W-C1
DGP600W-C2

DGP600W-B3

DGP600W-C3

DGP600W-B4

DGP600W-C4

Rating1.7Ω-3.4kW
3.7Ω-7.4kW
1.9Ω-8.7kW
2.5Ω-10.5kW5Ω-10kW
1.4Ω-14kW
1.7Ω-10kW

A/A1
283/303493/513

Dimensions (mm) Note 2)
D/D1
E/E1
207/192
620/700
417/402620/700

F/F1
725/780725/780703/723

627/612620/700

725/780

913/933

837/822620/700

725/780

External dimension
diagramF

Connection
diagram

G

Thermal relay (Th-Ry)
Setting value (A)
46
44
71
65
45
110
77

Approx. mass
(kg)
50
100
150
150
150
200
200

Note 1) The braking resistors are designed for indoor type. Please use them with drip cover in case of water drop. But please note it is not for water proof protection type.
Note 2) A,D,E,F are the dimensions of standard type. A1,D1,E1,F1 are the dimensions of those with drip cover type.

28

High-performance Drive■■Selection of braking resistor

ND ratingThis is used for the quick deceleration, the frequent deceleration stop or shortening the deceleration time at the large inertia load. This resistor consumes the regenerative energy when regenerative braking operation.
In case of over 3% ED, please select the allowable continuous regenerative power (Watt) in the following table.
1) The continuous regenerative load likes an elevator2) Deceleration stops at large inertia machine3) Frequent deceleration stop by using braking resistors

Voltageclass

HD rating
Voltageclass

Applicable
motor
(kW)
0.4
0.75

240V

480V

Drive
type-form
VFAS3-2004P
VFAS3-2007P

Minimumallowable
resistance (Ω)

Model
PBR

7.9
7.9

PBR-2007(90W-200Ω)
PBR-2022(90W-75Ω)

1.5

VFAS3-2015P

7.9

2.2

VFAS3-2022P

7.9

PBR-2037(90W-40Ω)

4.0

VFAS3-2037P

7.9

5.5
7.5
11
15
18.5
22
30
37
45
55
0.4
0.75
1.5
2.2

VFAS3-2055P
VFAS3-2075P
VFAS3-2110P
VFAS3-2150P
VFAS3-2185P
VFAS3-2220P
VFAS3-2300P
VFAS3-2370P
VFAS3-2450P
VFAS3-2550P
VFAS3-4004PC
VFAS3-4007PC
VFAS3-4015PC
VFAS3-4022PC

5.3
5.3
5
5
4.5
1
1
1
1
1
78
78
78
31.2

4.0

VFAS3-4037PC

31.2

5.5
7.5
11
15
18.5
22
30

VFAS3-4055PC
VFAS3-4075PC
VFAS3-4110PC
VFAS3-4150PC
VFAS3-4185PC
VFAS3-4220PC
VFAS3-4300PC

22.3
22.3
15.6
15.6
15.6
12
12

PBR7-008W030(270W-30Ω)37

VFAS3-4370PC

7.9

45
55

VFAS3-4450PC
VFAS3-4550PC

2.5
2.5

75

VFAS3-4750PC

2.5

90
110
132
160
200
220

VFAS3-4900PC
VFAS3-4110KPC
VFAS3-4132KPC
VFAS3-4160KPC
VFAS3-4200KPC
VFAS3-4220KPC

280

VFAS3-4280KPC

PBR7-004W015(130W-15Ω)
PBR7-008W7R5(270W-7.5Ω)PBR7-017W3R7(540W-3.75Ω)PBR7-035W1R8(1080W-1.87Ω)PBR-2007(90W-200Ω)
PBR-4037(90W-160Ω)

DGP600-800W class
PBR7-008W060(270W-60Ω)

10kW class---

PBR7-035W030(1080W-30Ω)

PBR7-008W015(270W-15Ω)

PBR7-017W015(540W-15Ω)

PBR7-035W015(1080W-15Ω)

PBR7-017W7R5(540W-7.5Ω)PBR7-035W7R5(1080W-7.5Ω)PBR7-052W7R5(1620W-7.5Ω)-PBR7-035W3R7(1080W -3.75Ω)PBR7-052W3R7(1620W-3.75Ω)-PBR7-052W1R8(1620W-1.87Ω)DGP600W-B4M/C4M(10kW-1.7Ω)--PBR7-052W060(1620W-60Ω)--PBR7-008W060(270W-60Ω)PBR7-017W010(540W-10Ω)-

PBR7-017W7R5(540W-7.5Ω)PBR7-017W060(540W-60Ω)PBR7-017W030(540W-30Ω)-

PBR7-035W060(1080W-60Ω)PBR7-035W030(1080W-30Ω)

PBR7-052W015(1620W-15Ω)

PBR7-052W030(1620W-30Ω)

-

-

-

PBR7-035W015(1080W-15Ω)--

PBR7-035W010(1080W-10Ω)

PBR7-052W010(1620W-10Ω)

-

-

-

PBR7-035W7R5(1080W-7.5Ω)PBR7-052W7R5(1620W-7.5Ω)

-

-

-

-

-

PBR7-035W3R7(1080W-3.75Ω)-PBR7-052W3R7(1620W-3.75Ω)-DGP600W-B3M/C3M(10.5kW-2.5Ω)

-

-

-

-

-

1.9
1.9
1.9
1.9
1
1

PBR7-017W3R7(540W-3.75Ω)-DGP600W-B2M/C2M(7.4kW-3.7Ω)

1-

DGP600W-B4M/C4M(14kW-1.4Ω)DGP600W-B3M/C3M(8.7kW-1.9Ω)

240V

-

PBR7-017W030(540W-30Ω)-

PBR7-017W015(540W-15Ω)

5kW class-

PBR7-008W030(270W-30Ω)-

PBR7-004W060(130W-60Ω)High frequency type
3.5kW class
PBR7-017W060
PBR7-035W060(540W-60Ω)(1080W-60Ω)
1.5kW class-

PBR7-052W015(1620W-15Ω)

DGP600W-B3M/C3M(10kW-5Ω)

DGP600W-B4M/C4M(10kW-1.7Ω)480V

Applicable
motor
(kW)

Drive
type-form

Minimumallowable
resistance (Ω)

0.75

VFAS3-2004P

7.9

1.5
2.2

VFAS3-2007P
VFAS3-2015P

7.9
7.9

4.0

VFAS3-2022P

7.9

5.5
7.5
11
15
18.5
22
30
37
45
55
75
0.75
1.5
2.2

VFAS3-2037P
VFAS3-2055P
VFAS3-2075P
VFAS3-2110P
VFAS3-2150P
VFAS3-2185P
VFAS3-2220P
VFAS3-2300P
VFAS3-2370P
VFAS3-2450P
VFAS3-2550P
VFAS3-4004PC
VFAS3-4007PC
VFAS3-4015PC

7.9
5.3
5.3
5
5
4.5
1
1
1
1
1
78
78
78

4.0

VFAS3-4022PC

31.2

5.5
7.5
11
15
18.5
22
30
37

VFAS3-4037PC
VFAS3-4055PC
VFAS3-4075PC
VFAS3-4110PC
VFAS3-4150PC
VFAS3-4185PC
VFAS3-4220PC
VFAS3-4300PC

31.2
22.3
22.3
15.6
15.6
15.6
12
12

45

VFAS3-4370PC

7.9

55

VFAS3-4450PC

2.5

75

VFAS3-4550PC

2.5

Model
PBR

DGP600

PBR-2007(90W-200Ω)
PBR-2022(90W-75Ω)PBR-2037(90W-40Ω)PBR7-004W015(130W-15Ω)
PBR7-008W7R5(270W-7.5Ω)PBR7-017W3R7(540W-3.75Ω)PBR7-035W1R8(1080W-1.87Ω)PBR-2007(90W-200Ω)

DGP600W-B1M/C1M-

PBR-4037(90W-160Ω)PBR7-004W060(130W-60Ω)-PBR7-008W030(270W-30Ω)
PBR7-017W015(540W-15Ω)
PBR7-017W010(540W-10Ω)
PBR7-017W7R5(540W-7.5Ω)PBR7-017W3R7(540W-3.75Ω)90

VFAS3-4750PC

2.5

-

110
132
160

VFAS3-4900PC
VFAS3-4110KPC
VFAS3-4132KPC

1.9
1.9
1.9

-

220

VFAS3-4160KPC

1.9

-

250
280
315

VFAS3-4200KPC
VFAS3-4220KPC
VFAS3-4280KPC

1
1
1

-

800W class

1.5kW classHigh frequency type
3.5kW class

5kW class

10kW class

-

-

-

PBR7-035W060(1080W-60Ω)--PBR7-008W060(270W-60Ω)PBR7-017W060(540W-60Ω)PBR7-008W030(270W-30Ω)

PBR7-017W030(540W-30Ω)

PBR7-035W030(1080W-30Ω)

PBR7-008W015(270W-15Ω)-

PBR7-017W015(540W-15Ω)

PBR7-035W015(1080W-15Ω)

PBR7-017W7R5(540W-7.5Ω)PBR7-035W7R5(1080W-7.5Ω)PBR7-052W7R5(1620W-7.5Ω)-PBR7-035W3R7(1080W -3.75Ω)-PBR7-052W3R7(1620W-3.75Ω)-PBR7-052W1R8(1620W-1.87Ω)DGP600W-B4M/C4M(10kW-1.7Ω)--PBR7-008W060(270W-60Ω)PBR7-017W060(540W-60Ω)

-

-

-

-

-

-

-

-

-

-

-

PBR7-035W060(1080W-60Ω)-PBR7-052W060(1620W-60Ω)PBR7-017W030(540W-30Ω)

PBR7-035W030(1080W-30Ω)

PBR7-052W030(1620W-30Ω)-

PBR7-035W015(1080W-15Ω)
PBR7-035W010(1080W-10Ω)

PBR7-052W015(1620W-15Ω)
PBR7-052W010(1620W-10Ω)

PBR7-035W7R5(1080W-7.5Ω)PBR7-052W7R5(1620W-7.5Ω)PBR7-052W3R7(1620W-3.75Ω)
-

-

-

-

-

PBR7-035W3R7(1080W-3.75Ω)-DGP600W-B3M/C3M(8.7kW-1.9Ω)

-

-

-

-

DGP600W-B4M/C4M(14kW-1.4Ω)

-

-

-

-

DGP600W-B2M/C2M(7.4kW-3.7Ω)-PBR7-052W015(1620W-15Ω)-

DGP600W-B3M/C3M(10kW-5Ω)

DGP600W-B3M/C3M(10.5kW-2.5Ω)DGP600W-B4M/C4M(10kW-1.7Ω)-Note 1) For VFAS3-2550P, 4900PC to 4132KPC, 4220KPC to 4280KPC, it requires the braking unit.
Note 2) The figures in the parentheses show the synthetic resistor value (Ohm) and the allowable continuous regenerative power (Watt).
Note 3) The guideline of the maximum braking at the standard type.
Note 4) The necessary power in case of deceleration from 60Hz at one time per 120 seconds periods at 30 seconds deceleration time for the 10 times of the motor inertia. please contact our agency when large inertia or quick
deceleration.
Note 5) The braking resistors are designed for indoor type. Please use them with drip cover in case of water drop. But please note it is not for water proof protection type.

■■Braking unit

Maximum DC voltage
240V class
480V class

Maximum braking power

PB7-4200K
758V
825V
420kW

11

11

13
2

External dimensions
PB7-4132K is mechanically mounted on the bottom side of the drive.
Approx. mass 23kg

PB7-4200K is mechanically mounted on the left-hand side of the drive.
Approx. mass 30kg

8

75

598

DCL

3

PB7-4132K
379V
758V
820V
93kW
220kW

240V class
480V class17

75 150.7R530Specification
Threshold voltage

H1 (Mounting dimension)
H

.7

5

.
R5

2x

48
126
350
353

4xφ10.5

75

38

29

W1 (Mounting
dimension)
W
340

22.5
42.5
38

2-

R5

7

H

R5

4-φ24

Braking unit
(optional)
H1 (Mounting dimension)

2x

Braking unit
(optional)

2

R1

.7

D

W1 (Mounting dimension)
75

7

D

W

30

High-performance Drive

Flange mounting kit

Door mounting kit

This options enable the heatsink parts of the backside of drive that generate much heat to be located at the outside of the panel.
This is effective for the small sizing of the totally-enclosed box by reducing the heat values inside the box.

FOT021Z
FOT022Z
FOT023Z
FOT013Z
FOT014Z
FOT015Z

Fig.A

Fig.B

FOT018Z

FOT019Z

A

1.3

B

1.5

C

1.9

D

6.8

E

9.4

F

15.5

G
H

4.4
4.7

H

4.9

12.5

133.5

10

Note) Operation panel juts out about 26mm from the cabinet surface when the option is mounted on the cabinet surface.

LED Extension panel

502.5

200

555

130
375

420

133.5

165

9-φ7.5 holes

180
265

30
230

9-φ7.5 holes

Type-form: RKP002Z (It has parameter copy function)

Type-form: RKP007Z■ Dimension■ Dimension■ Panel cutout dimension■ Panel cutout dimension

50

115

162.5

17.5

235

φ4 mm

φ4 mm

252

215

307.5

360

175

Panel cable (option)
Type-form: CAB0071(1m)CAB0073(3m)
CAB0075(5m)
CAB00710(10m)

12.5
9

165

190

7-φ7.5 holes

135

FOT020Z

15

10Operation panel
Operation panel

10

12.5

12.5

φ22.5 mm

φ22.5 mm

Door mounting kit
Door mounting kit

162.5

120

11.5
11.5

105

120

Panel cutout dimension
Panel cutout dimension

Cabinet surface
Cabinet surface

Fig.C
135

105

■■Mounting on the cabinet

34
4-φ4

20

8
φ2

Fig.F

15

6-φ8 holes

145

413
70

98±0.3

2.3
16.2

50
227

Communication cable Type-form: CAB0011 (1m), CAB0013 (3m),CAB0015 (5m)

135
270
45
360

3-φ8 holes
12-φ7.5 holes

Type-form: USB001Z
Drive can be management and setting on a PC

380
435

26.5

10

325
385

227

330

31
21

237.5

190
12-φ7.5 holes

15

Communication cable Type-form: CAB0071 (1m), CAB0073 (3m),CAB0075 (5m)

USB communication conversion unit

227

190

235

12-φ10 holes■ Connection

Fig.G

45

180
150
120

10
8-φ8 holes

190
160
130

■ Dimension

50

28-φ8 holes

60
16

19.6
3.2
hole

1

31.6

180
195

112

*1

90

8-φ10 holes

(G1)

G1
G

G1

Dimensions (mm)
a1
G
610
645
685
720

G1
215
240

5

280
8-φ8 holes

FOT014Z
FOT015Z

D1
90
165

9

*1: USB communication conversion unit cable. Type-form (drive side): CAB0011 (1m),CAB0013 (3m),
CAB0015 (5m)
*2: Cable is USB cable (USB1.1/2.0 A-B connect type) for PC side.

2.8

3.2
hole

27.1

490

Model

19.6

245

60

60
6-φ8 holes

（245）

*2

1

17.5

280

a1

280

15

970

460

280

970

88

8-φ10 holes

280

280

19.9

120

20

120

20

50

210
50

210

FOT014Z/FOT015Z
180
195

FOT013Z

Fig.H

D1

Unit: mmApprox mass: 39g

7.7

1417
1305

975

920

227

235

9.2

227

237.5

13.5
190
190
733

800

Unit: mmApprox mass: 0.11kg

29.4

5

FOT023Z

15.1

FOT022Z（17.5）

17.5

202.5
12.5

12.5

FOT021Z

175
12.5

20

175

202.5

190

Fig.E

15

Fig.D

10.4

54

70

16.4

80

17.5

4-φ4

4.6

63±0.3

295

31

29.2

FOT020Z

Approx. mass
(kg)

25 mm

FOT019Z

VFAS3-2004P to VFAS3-2022P
VFAS3-4004PC to VFAS3-4037PC
VFAS3-2037P
VFA3-4055PC, 4075PC
VFAS3-2055P, 2075P
VFAS3-4110PC to VFA3-4185PC
VFAS3-2110P to VFAS3-2185P
VFAS3-4220PC to VFAS3-4370PC
VFAS3-2220P to VFAS3-2370P
VFAS3-4450PC to VFAS3-4750PC
VFAS3-2450P, 2550P
VFAS3-4900PC to 4132KPC
VFAS3-4160KPC
VFAS3-4200KPC to VFAS3-4280KPC
VFAS3-4200KPC to VFAS3-4280KPC
with using PB7-4200K

External dimension
diagram15

FOT018Z

Drive type-form

25 mm

Model

Type-form: SBP010Z

45°
13.2

31

Unit: mm32

High-performance Drive

Control power supply unit (Model: CPS002Z)■■External dimensions

Totally enclosed box type for IP55 / UL type 12■■Connection diagram
3.5

41
.25

φ8

IP55 / UL type 12 protection for direct mounting on wall.

20.5
5

R2

VF-AS3HDND
3ph-480V class (IP55)

R
S
T

Power
supply

150

140

5

Voltage class

Control
power
supply
unit

R2

.25

U
V
W

M

1.5
2.2

2.2
4.0

Item

HD
ND

Applicable motor (kW)
Type
Form

Type-form: CPS002Z* CPS002Z can be used forboth 240V and 480V class.

Output capacity (kVA) *1
RatingOutput current (A) *2

HD
ND
HD
ND

Output voltage
HD
Overload current rating
ND
Voltage/frequency
Power
Tolerance
Required power supply HD
supplyND
capacity (kVA) *4
Output frequency range
Electrical
Dynamic braking circuit
Dynamic braking resistor
braking
Degree of protection
Cooling method
Color
EMC filter
DC reactor
Use environments
AltitudeChemical class
Mechanical class
Environments
Ambient temperature
Storage temperature
Relative humidity
Vibration

Operation panel (Model: CBVR-7B1)■■Connection diagram

R2.5(Mounting
hole M4)

VF-AS3

Panel cutout dimension

φ10.5
Frequency meter

Mounting holes
2-φ4(M3)

90(Mounting dimension)

Potentiometer
JIS mark N1.5
Operation
switch

R/L1
S/L2
T/L3

OperationPanel(option)FM
φ5 hole

Motor
M

U/T1
V/T2
W/T3

(a)

PP

PP

RR
CC

RR
CC

FM

Forward F

FM
(a)

F

Reverse R
Note)

(a)

Rubber bushing(φ34)Note) The wire length should be 30m or lessthe drive and the operation panel.

Color: JIS mark 5Y7/1(Panel front N1.5)
Approx. mass: 0.7kg

37
45

45
55

55
75

75
90

*1: Capacity is calculated at 440V for 480V class.
*2: Indicates rated output current setting when the PWM carrier frequency (parameter F300) is 4 kHz.
*3: Lower limit of voltage for 480V class is 342V when inverter is used continuously (load of 100%).
*4: Current derating by 1% for each 100m above 1000m. For example, 90% at 2000m.
*5: Required power supply capacity varies with the value of the power supply side impedance (including input reactor and cables).
*6: Temperature applicable for a short term. e.g. during transportation*7: UL type1 without the top cover

R

Panel

Applied motor capacity(kW) : Dual rating
5.5 7.511
15 18.5 22
30
7.5
11
15 18.5 2230
37Specification
480 V class
A1E
A2E
A3E
A4E
A5E
0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
VFAS34004PCE 4007PCE 4015PCE 4022PCE 4037PCE 4055PCE 4075PCE 4110PCE 4150PCE 4185PCE 4220PCE 4300PCE 4370PCE 4450PCE 4550PCE 4750PCE
1.1
1.7
3.0
4.3
7.1
9.7
12.6
17.9
24.2
29.9
35.3
46.9
56.8
67.1
80.8
111
1.7
3.0
4.3
7.1
9.7
12.6
17.9
24.2
29.9
35.3
46.9
56.8
67.1
80.8
111
132
1.5
2.2
4.0
5.6
9.3
12.7
16.5
23.5
31.7
39.2
46.3
61.5
74.5
88.0
106
145
2.2
4.0
5.6
9.3
12.7
16.5
23.5
31.7
39.2
46.3
61.5
74.5
88.0
106
145
173
3-phase 380V to 480V (The maximum output voltage is equal to the input supply voltage)
150%-1 minute, 180%-2 s
120%-1 minute, 135%-2 s3-phase 380 to 480V, 50/60Hz
Voltage: 323V to 528V *3, Frequency: +/-5%
0.7
1.4
2.6
3.7
6.6
8.5
11.4
16.6
22.3
27.3
32.7
44.3
53.9
65.6
79.5
108
1.2
2.4
3.4
6.1
8.3
10.9
15.6
21.3
26.4
31.4
42.0
52.4
63.2
77.0
103
125
0.01 to 590Hz (Default setting 0.01 to 80.0Hz)
Built-inExternal braking resistor (Optional)
IP55 (IEC60529) / UL type 12 *7
Forced air-cooled
RAL7016
Built-inBuilt-inIndoor use. Place not exposed to direct sunlight and free of corrosive gas, explosive gas, flammable gas, oil mist, or dust.
4800m or less (Current reduction necessary when above 1000m) *4
3C3 (IEC/EN60721)
3S3 (IEC/EN60721)-15 to +50°C (Current reduction necessary when above 40°C) *5-25 to +70°C *6
5 to 95% (Free from condensation)
5.9m/s2 or less (10 - 55Hz)

Voltage class
Frame size

20.5■■External dimensions

4.0
5.5

■■Standard specification

+SU
CC

4.5

100.7

0.4 0.75
0.75 1.5

Grounding (M5)

45
22.5

33

108

15

R1
2

314.5

17

105

12

262

Input
voltageclass

ole
3-Phase
480V

ND

0.4
0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75

0.75
1.5
2.2
4.0
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90

H1 (Mounting dimension)

H

D

HD

(15)

H

17

(22.5)

Applicable motor (kW)(H2)

H1 (Mounting dimension)

dimension).7

Potentiometer knob<K-3>0h

10 holeW1 (Mounting
W

Screw

Panel cutout dimension
3.2 hole

375

R5

22.5

White mark

φ2

15
162.5

2x

Potentiometer panel

15

R3

Unit: mm

FRH-KIT
Potentiometer<RV30YN-20S-B302>

R1
0

4x

(10)

2-φ3.5holes
24±0.2 24±0.2(H2)

Approx. mass: 75g.5(Rear)

15

R4(Side)

24

135

H2

24

Fig.C

340

15

H

.5
53

30
17

15

2x

(Front)

25.5

7

(6.5)

13

φ

24
10
60

Fig.B

Color: N1.5
H1 (Mounting dimension)

24

Mountingscrew (M3)

φ52

QS60T

60

0

80

80Hz-1mAdc

24±0.2 24±0.2

Terminal cover

60

Hz

9

20

Panel cutout dimension

227.5

103

9

Terminal (M4)
40

11
10.5

R7

7

115

7

11

.
R5

R3

.5

Fig.A

R4

Frequency meter <QS-60T (80Hz-1mAdc)>

65.5■■External dimensions

Drive type-form
VFAS3-4004PCE
VFAS3-4007PCE
VFAS3-4015PCE
VFAS3-4022PCE
VFAS3-4037PCE
VFAS3-4055PCE
VFAS3-4075PCE
VFAS3-4110PCE
VFAS3-4150PCE
VFAS3-4185PCE
VFAS3-4220PCE
VFAS3-4300PCE
VFAS3-4370PCE
VFAS3-4450PCE
VFAS3-4550PCE
VFAS3-4750PCE

20W1 (Mounting
dimension)

(17)

W

(20)

D

26
(17)

Dimension (mm)
W

H

D

W1

H1

H2

250
250
250
250
250
250
250
250
250
250
290
290
290
345
345
345

678
678
678
678
678
678
678
678
678
678
910
910
910
1250
1250
1250

271
271
271
271
271
301
301
301
301
301
340
340
340
375
375
375

205
205
205
205
205
205
205
205
205
205
250
250
250
293
293
293

661
661
661
661
661
661
661
661
661
661
888
888
888
1220
1220
1220

19
19
19
19
19
19
19
40
40
40
26
26
26
30
30
30

W1 (Mounting
dimension)

(26)

D

W

Frame
Size

External
dimension
diagramApprox.mass
(kg)

A1E
A1E
A1E
A1E
A1E
A2E
A2E
A3E
A3E
A3E
A4E
A4E
A4E
A5E
A5E
A5E

A
A
A
A
A
A
A
A
A
A
B
B
B
C
C
C

13.2
13.2
13.4
13.6
13.7
17.1
17.4
21.3
21.8
21.9
51.5
51.5
52.5
89
91
91

34

For users of the products : Our variable speed drives are designed to control the speeds of three-phase motors for general industry.
Precautions* Please read the instruction manual before installing or operating the drive unit.
* This product is intended for general purpose uses in industrial application. It cannot be used applications where may cause big impact on public
uses, such as power plant and railway, and equipment which endanger human life or injury, such as nuclear power control, aviation, space flightcontrol, traffic, safety device, amusement, or medical.
It may be considerable whether to apply, under the special condition or an application where strict quality control may not be required. Pleasecontact our headquarters, branch, or local offices printed on the front and back covers of this catalogue.
* When exporting Toshiba variable speed drive separately or combined with your equipment, please be sure to satisfy the objective conditions
and inform conditions listed in the export control policies, so called Catch All restrictions, which are set by the Ministry of Economy, Trade andIndustry of Japan, and the appropriate export procedures must also be taken.
* Please use our product in applications where do not cause serious accidents or damages even if product is failure, or please use in environment
where safety equipment is applicable or a backup circuit device is provided outside the system.
* Please do not use our product for any load other than three-phase motors.
* None of Toshiba, its subsidiaries, affiliates or agents, shall be liable for any physical damages, including, without limitation, malfunction, anomaly,
breakdown or any other problem that may occur to any apparatus in which the Toshiba variable speed drive is incorporated or to any
equipment that is used in combination with the Toshiba variable speed drive. Nor shall Toshiba, its subsidiaries, affiliates or agents be liable forany compensatory damages resulting from such utilization, including compensation for special, indirect, incidental, consequential, punitive or
exemplary damages, or for loss of profit, income or data, even if the user has been advised or apprised of the likelihood of the occurrence of suchloss or damages.
For further information, please contact your nearest Toshiba Representative or International Operations-Producer Goods.
The information in this brochure is subject to change without notice.

Global Sales Group Motor Drive Division
10th Floor, LAZONA Kawasaki TOSHIBA building, 72-34, Horikawa-cho, Saiwai-ku, Kawasaki-shi, Kanagawa 212-8585, Japan
Tel : +81-44-520-0828 Fax : +81-44-520-0508
http://www.toshiba-tips.co.jp/en/

CKVJ-1304
2021-11

AB