Operator Interface

HG Series

Excellent visibility by super-bright LED
backlight even in well-lit surroundings.

Withstands harsh environments.
• See website for details on approvals and standards.

HG5G-VPage

L-085

HG3G-V(12.1 inch)(10.4 inch)

L-095

L-097

L-099

HG2G-V

HG2G-5T(5.7 inch)(4.3 inch)

L-101

L-103

L-105

(5.7 inch)Page

HG4G-V(15 inch)

HG1G

Operator Interfaces

From large to small size
		 For diverse applications

APEM
Switches &Pilot Lights
Control Boxes

Line up

Emergency
Stop Switches
Enabling
Switches

High-Performance Model

Safety Products
Explosion Proof

Version
up

15

inch

Version
up

12.1
inch

10.4
inch

Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers

Part No.

Operator
Interfaces

HG5G-V

HG4G-V

HG3G-VA

304.1 (W) ×228.1 (H) mm

245.8 (W) ×184.3 (H) mm

210.4 (W)×157.8 (H) mm

Display

TFT color LCD

TFT color LCD

TFT color LCD

Color / Shade

65,536 colors

65,536 colors

65,536 colors

Resolution

1024 (W) × 768 (H) pixels

1024 (W) × 768 (H) pixels

1024 (W) × 768 (H) pixels

View angle

Left/right/top/bottom: 85°

Left/right/top/bottom: 85°

Left/right/top/bottom: 85°

Display Size

Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG4G

Basic Model

High-Performance Model

Compact Model

HG4G
HG3G

Version
up

8.4

inch

4.3

5.7

inch

Part No.

5.7

Version
up

inch

inch

HG3G-V8

HG2G-V

HG2G-5T

HG1G

170.5 (W) ×127. 9 (H) mm

115.2 (W) ×86. 4 (H) mm

115.2 (W) × 86.4 (H) mm

95.0 (W) × 53.8 (H) mm

Display

TFT color LCD

TFT color LCD

TFT monochrome LCD /TFT color LCD

TFT color LCD

Color / Shade

65,536 colors

65,536 colors

65,536 colors

65,536 colors

Resolution

1024 (W) × 768 (H) pixels

640 (W) × 480 (H) pixels

320 (W) × 240 (H) pixels

480 (W) × 272 (H) pixels

View angle

Left/right/top/bottom: 85°

Left/right/top/bottom: 80°

Left/right/top/bottom: 80°(color type)Left/right: 70°, top: 60°,
bottom 65°

Display Size

HG2G
HG1G

L-086

Operator Interfaces

IoT

Harsh
environment

High performance IoT functionality
for the manufacturing floor

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Email function

Get notified via email

The data in the operator interface can be sent by CSV format or byscreen shot. Email settings can be configured to meet the requirementsof each customer.
Email function

Programmable
Operator Interfaces
Periphery
Equipment

HG4G
HG4G

FTP server / client function

Easy maintenance

FTP server function enables transfer of project data and helps
utilize data log easily. Easy maintenace from remote locations.

HG3G
HG2G
HG1G

Web server function

Confirm status of the system from an remote area

•The screen can be remotely monitored and operated from a PC,
tablet, or smartphone.
•No special software required. Accessible using an internet
browser.

Use a WEB PAGE EDITOR to create a your original monitor page without knowledge of Java or HTML.

L-087

Usability

Harshenvironment

Usability

Excellent environmental resistanceWithstands harsh environments

Operator Interfaces

IoT

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
MonitorFreezer : 1

Temp

Freezer : 2

Temp

Refrigerator : 1

Temp

Refrigerator : 2

Temp

Freezer : 1

HumidityFreezer : 2

Humidity

Refrigerator : 1

Humidity

Refrigerator : 2

HumidityFreezer : 1

Brightness

Freezer : 2

Brightness

Refrigerator : 1

Brightness

Refrigerator : 2

Brightness

Freezer : 1

Pressure

Freezer : 2

Pressure

Refrigerator : 1

Pressure

Refrigerator : 2

Pressure-18.5 ˚C -20.2-20.2 ˚C
30.5 %
200 lx50.0
50.0 %
170 lx170

10.0
10.0 ˚C
40.0
40.0 %

Explosion Proof

Refrigerator : 1

13.2
13.2 ˚C
73.2
73.2 %

202
202 lx

Terminal Blocks

185
185 lxRelays & Sockets

1,030 hPa 1,030
1,030hPa 1,030
1,030hPa 1,030
1,030hPa
21
18
15
12
9
6
3
0
-3
-6
-9
-12
-15
-18
-21
-24

250

200

150

Temp

Humidity

100

Freezer 1-18.5 ˚C

90

Freezer 1

30.5%

Freezer 2-20.2 ˚C

80

Freezer 2

50.0%

Refrigerator 1 10.0 ˚CRefrigerator 2 13.2 ˚C70

Refrigerator 1 40.0%

60Freezer 1
Run

Circuit
Protectors

Stop

Refrigerator 2 73.2%

50
40Freezer 2

30
20Power Supplies

10
0

Run

Brightness

Pressure

Freezer 1

200 lx

1,050

Freezer 2

170 lx

1,045

Refrigerator 1 202 lx
Refrigerator 2 185 lx

Freezer 1

1,030 hPa

Freezer 2

1,030 hPa

LED Illumination

Refrigerator 1

Refrigerator 1 1,030 hPa

1,040

Refrigerator 2 1,030 hPa

1,035

100

Stop

Run

Stop

Controllers

1,030
50

1,025

Refrigerator 2

1,020

0

SET

MENU

Run

Operator
Interfaces

Stop

Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

Wide Temperature range:-20 to +60°C
Suitable for use in a wide temperature range from cold
to hot. (-20 to +55°C for HG1G)

Waterproof / Oil resistantProtection against UV rays
Strong plastic material used for protecting the screen.
By using the optional protective sheet, UV protection isenhanced, and prevents degrading of the LCD (*2).
*2) UV protective material is used but operation is not guaranteed outdoors
or under direct sunlight.

HG4G
HG3G
HG2G
HG1G

(IP66F / IP67F / UL Type 4X, 12, and 13)

Touchscreens can be used on machines washed down
by water such as food machines. Also suitable for use
on food machines subject to oil spills.
(HG2G-5T: IP66F protection only)

HG4G

Marine standards
LR, DNV∙GL, ABS, ClassNK marine standards (*3)*3) Except HG2G-5T, HG1G

*Operation not guaranteed when used with certain types of oils.
See instructions on the back page.

Long-life, high-performance
LED backlight reduces
maintenance time

Rugged construction
Hard coating prevents damage to the screen.

48-level dimming control (*1) reduces cost and allows
for a wide range of uses.
(HG5G-V: Brightness 500cd/m2, backlight life: 100,000
hours)*1) 32-level for HG2G-T and HG1G.

L-088

Operator Interfaces

A wide variety of functionality for users

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches

Additional
I/O module

Safety Products
Explosion Proof

Expansion module

Terminal Blocks(64 I/O max.)

Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors

For bothdigital andanalog I/O
modules

Power input
terminal block(24VDC)

AUTO-ID

Terminal block (COM2)
RS232C/485 (422)Programmable
Operator Interfaces
Periphery
Equipment

D-sub9 pins (COM1)
RS232C/485 (422)
SD card

Audio output

USB-A

HG4G

Video input

USB mini-B(for PC)

HG4G
HG3G

Ethernet

HG2G
HG1G

3-seconds startup
Stress-free quick startup

USB autorun
Autorun menu on the USB memory enables easytransfer of data and settings.

Selectable memory

Multiprotocol

Data can be saved or transferred by using an SD card
(32GB max.) and USB memory. By saving user data on
an SD card or USB memory, back up of data is possible
and the user memory can be reduced.

Multiple machines using PLCs made by different
manufacturers can be controlled, configured, andmonitored by one operator interface.
Supports BACnet (*1) and Modbus TCP/RTU protocol.
*1) Except HG2G-5T, HG1T

L-089

Usability

Analog signals and contact signals can be sent and received byserial communication

Operator Interfaces

Harshenvironment

IoT

APEM

Complexwiring is time
consuming

Switches &Pilot Lights

Long wiring of
analog signals
may cause noiseand voltage drop

Control Boxes

Ethernet / Serial

Operator
interface

Emergency
Stop Switches
Enabling
Switches
Safety Products

Pilot
Light

Explosion Proof

Switch Buzzer

Terminal Blocks

Contact input
Analog input

Sensor

Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces

Saves
maintenancetime

Sensors

Ethernet / Serial

AUTO-ID

HG series
operator
interface

HG series
reduceswiringExpansion
moduleNoise resistantserialcommunication

Programmable
Operator Interfaces
Periphery
Equipment

HG4G

Pilot
Light

Buzzer

Switch

HG4G

Sensor

HG3G
HG2G
HG1G

Display image
Displays images on the screen from a camera.

Save image
Records and plays back images on the screen from acamera and saves the data to the SD card.

Play video

Record video

MPEG4 video files can be played back on the screen.
Work procedures can be shown on the screen, andwhen trouble occurs,it can be used as a video manual
for trouble shooting on-site.

When an alarm is set off, video images before and after
the start of the alarm can be recorded on an SD card.
This enables on-site analysis is of the trouble. Smoothand refined images can be recorded.

L-090

Operator Interfaces

Flexible and user-friendly programming

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion ProofOI Touchscreen
Programming Software
Flexible and easy to use
Easy programming enables efficiency

Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG4G

Create projects efficiently witha script debugger
The script debugger allows you to check the operation of thescript step by step during simulation mode.

HG4G
HG3G
HG2G
HG1G

Simple and useful manager fuctions
Several settings such as a text manager, picture manager, andscript managers can be controlled and displayed by a single
manager.

L-091

Harshenvironment

Usability

User communication function enables
use of complex protocols
User communication function allows the use of protocols notsupported by network drivers.

Operator Interfaces

IoT

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof

Error log helps specify problems easily

Terminal Blocks

The error check function displays incorrect setup or missed
items in a list. You can jump to the error from this list so
problems that occur in a large project can be solved quickly.

Circuit
Protectors

Relays & Sockets

Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Check operation of the PC using thesimulator
No need to download the project data to the operator interface
each time. Operation can be checked using a simulator.

Programmable
Operator Interfaces
Periphery
Equipment

HG4G
HG4G
HG3G
HG2G
HG1G

Check information of
the object at a glance

Extensive image library

Create documents
easily by print function

Information such as device
address and operating condition ofparts laid out on the screen can bechecked easily.

Drag & drop functionality allows
intuitive operation. Images can beimported from an image library of
10,000 parts.

Items selected from the project
data can be printed and used
as users manual or spec sheet.
The data can also be converted
to docx format and edited.

L-092

Operator Interfaces
APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches

HG5G-VPowerful visual presentation
Find all the information you need on asingle screen

Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG4G
HG4G
HG3G
HG2G
HG1G

Super bright, high resolution display
with outstanding performance
The bright display is visible from a distanceand in well-lit surroundings. (500cd/m2)

Lightweight construction
Plastic housing enables
lightweight structure. (3.2kg
approx.)

L-093

The large screen and high-quality resolution makes it
easy to view precise data.
Display resolution: 1024 (W)×728 (H)View angle: Left/right/top/bottom 85°

Slim bezel
Slim bezel enables downsizingof the operator interface with alarge screen.

Energy-saving
Energy-saving 27W power
consumption.

Operator Interfaces
APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG4G
HG4G
HG3G
HG2G
HG1G

L-094

Operator Interfaces

15 ininchch

HGSeries XXXXXXXXXX
HG5G-V
Operator Interface
Lightweight with slim bezel.
Large size ideal for handling huge amount of information for the IoT era.
13 14

12

APEM
Switches &Pilot Lights

2

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products

11
10
3

9
8

Explosion Proof
Terminal Blocks

15

1

Relays & Sockets

No.

Name
Power LED
Display
Touchscreen
Power Supply Terminal
Serial Interface (COM2)
Serial Interface (COM1)
Audio Interface (AUDIO OUT)
Ethernet Interface (LAN)USB Interface (USB1)

Circuit
Protectors
Power Supplies

4

5

6

7 16 17

LED Illumination(for main unit only)

Controllers
Operator
Interfaces

No.

Name
USB Interface (USB2)
Memory Card Interface (SD)SD Memory Access LED
Expansion Module Interface (EXT)
Battery Cover
Terminal Resistor Switch
Video Interface (VIDEO IN1)
Video Interface (VIDEO IN2)

• See website for details on approvals and standards.

Sensors
AUTO-ID

HG5G-V Operator Interface
Display Screen

Programmable
Operator Interfaces
Periphery
Equipment

15-inchTFT color LCD
65,536 colors

Communication/
Memory Interface

Operation Style

COM1
COM2
LAN
USB1
USB2
SD
EXT

Touch Switch(analog resistive)

HG5G

Video/Audio
Interface

Housing/Bezel
Color

VIDEO IN1
VIDEO IN2
AUDIO OUT

Black

Part No.

HG5G-VFXT22MF-B

Approvals
Safety Standards:
UL61010-1, UL61010-2-201,
UL12.12.01
CSA C22.2 No.61010-1-12
CSA C22.2 No.61010-2-201
CSA C22.2 No.213
Ship Classification Standards:
LR, DNV∙GL, ABS, ClassNK

HG4G

HG2G

Dimensions

Panel Cut-out
33.0 (*1)

HG1G

351.5

10

364.5

352.0 +20

50

55

11.4

291.5

278.5

69.5

279.0 +20

HG3G

30

Panel Thickness: 2.0 to 5.0 mm
6.0

48.8
54.8

38.6

*1) Depth from the expansion
module mounting surface.

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG5G-V into a panel cut-out by tightening the six mounting clips (supplied with the HG5G-V) to a torque of 0.5 to 0.6 N·m.
Do not tighten with excessive force, otherwise the HG5G-V and screen may become distorted. Also waterproof characteristics may be lost.

L-095

All dimensions in mm.

HG5G-V Operator Interface
Operation Specifications

Rated Power Voltage

24V DC

Switching Element

Analog resistive membrane

Power Voltage Range

20.4 to 28.8V DC

Operating Force

3N maximum

27W maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer or audio output

Power Consumption

20W maximum when not using USB2 or EXT

Operator Interfaces

General Specifications

7W maximum when Backlight OFF
Allowable Momentary
10 ms maximum
Power Interruption
Inrush Current
30A maximum

Function Specifications

Dielectric Strength

Screen Types

1,000V AC, 10 mA, 1 minute between power and FG terminals

APEM

Electrostatic Discharge Contact ±6 kV, air ±8 kV (IEC/EN61131-2)

Power Failure Backup Data

Base screen, popup screen, system screen
Base screen: 3,000 max.
Popup screen: 3,015 max.
58 MB (including expansion fonts and kanji dictionary data)
Bit Button, Word Button, Goto Screen, Print Button, Key
Button, Multi Button, Keypad, Selector Switch, Potentiometer,
Numerical Input, Character Input, Pilot Lamp, Multi-State
Lamp, Picture Display, Message Display, Message Switching
Display, Alarm List Display, Alarm Log Display, Numerical
Display, Bar Graph, Trend Chart, Pie Chart, Meter, Calendar,
Bit Write Command, Word Write Command, Goto Screen
Command, Print Command, Timer, Screen Script Command,
Multi Command, Video Display
Year, Month, Day, Hour, Min., Sec., Day of Week
±60 sec per month (at 25°C)
Calendar, log data, keep internal relay, keep internal register

Corrosion Immunity

Free from corrosive gases

Battery

Recommended replacement: every 5 years (at 25°C)

Mounting
Degree of Protection(*1)
Dimensions

Panel mounting (Panel Thickness: 2.0 to 5.0 mm)
IP66F/IP67F (IEC 60529) (front part when mounted)
UL Type 4X, 12, and 13
364.5W × 291.5H × 54.8D mm

Weight (approx.)

3.2 kgOperating Temperature −20 to +60°C (no freezing)
Operating Humidity

10 to 90% RH (no condensation)

Storage Temperature−20 to +70°C (no freezing)

Storage Humidity

10 to 90% RH (no condensation)

Pollution Degree2

Vibration Resistance
Shock Resistance
Noise Immunity

5 to 8.4 Hz amplitude 3.5 mm, 8.4 to 150 Hz, acceleration 9.8 m/s2
10 cycles (100 minutes) on each of three mutually perpendicular axes
147 m/s2, 11 ms
5 shocks on each of three mutually perpendicular axes
Fast transient/burst test,
Power terminals: ±2 kV,Communication line: ±1 kV (IEC/EN61131-2)• Do not use the HG5G-V in an environment subject to strong ultraviolet rays, otherwise the
LCD quality will deteriorate.
*1) See instructions on L-111 for details.

No. of Screens
User Memory

Parts

Calendar

TFT Color LCD

Color/Shade

65,536 colors

Effective Display Area

304.1W × 228.1H mm

Display Resolution

1,024W × 768H pixels

View Angle

Left/right/top/bottom: 85°

Backlight

White LED

Backlight Life

100,000 hours minimum (*2)

Brightness

500 cd/m2 (*3)

Brightness Adjustment

48 levels

Backlight Replacement

1/4 size

Not possible
8 × 8 pixels (Western European language: ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)
16 × 16 pixels (Japanese JIS first and second level characters,
simplified Chinese, traditional Chinese, Korean)
32 × 32 pixels (Japanese JIS first level characters, Mincho font)
Width 8 to 128 dots (1/2 size fixed)(ISO 8859-1 western language, 7-segment)
128 characters × 96 lines

1/2 size

128 characters × 48 lines

Full size

64 characters × 48 lines

Double size

32 characters × 24 lines (Mincho font)

Display Character Size

1/4 size

1/2 size

Full size
Double size

Quantity of
Characters

Scalable

Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute
Graphics
Window Display

Blink (1 or 0.5 sec period), reverse, bold, shadowed
Straight line, polyline, rectangle, arc, pie,circle/ellipse,
equilateral polygons (3, 4, 5, 6, 8), picture, fill
3 popup screens + 1 system screen

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies

Interface Specifications
Electrical Characteristics

LED Illumination

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

D-sub 9-pin connector / socket

Electrical Characteristics

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

Detachable 9-pin terminal block

Ethernet
Interface (LAN)Interface

IEEE802.3u (10/100BASE-T) compliant

Connector

Modular connector (RJ-45)

Video Interface(VIDEO IN1)

Interface

NTSC/PAL

Connector

Pin jack

Video Interface(VIDEO IN2)Interface

NTSC/PAL

Connector

Pin jack

Audio Interface(AUDIO OUT)

InterfaceLINE OUT (stereo)

Connector

Mini jack connector (ø3.5 mm)

USB Interface(USB1)

InterfaceUSB 2.0

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput current

5V 500 mA

Interface

SD memory card, SDHC memory card

Connector

SD memory card socket

Interface

MicroSmart I/O module interface

Transmission Speed
Serial Interface(COM1)

Display Specifications
Display

Switches &Pilot Lights

Transmission Speed
Serial Interface(COM2)(*4)

USB Interface(USB2)
Memory Card
Interface (SD)Expansion
Module Interface Ouput Current(EXT)Max. No. of Units

Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

5V 130 mA, 24V 50 mA
4 units*4) RS232C and RS 422/485 can be used simultaneously*5) 187,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).
*6) RS232C only for hardware control• See instructions on L-111 for details.
• *2) T he backlight life is not guaranteed and refers to the time until the brightness reducesby half after use at 25°C. The actual life depends on operating environments andconditions.
*3) Brightness of the LCD only.

L-096

Operator Interfaces

12.1inch

HG4G-V Operator Interface
Compact housing with a versatile interface.
High performance operator interface with multimedia functions.
12

13

14

APEM
Switches &Pilot Lights

2

Control Boxes

11

Emergency
Stop Switches
Enabling
Switches
Safety Products

10
9

3

8

Explosion Proof
Terminal Blocks

1

15

Relays & Sockets
Circuit
Protectors

No.

Power Supplies

4

5

6

7

16 17

LED Illumination(for main unit only)

Controllers
Operator
Interfaces• See website for details on approvals and standards.

Name
Power LED
Display
Touchscreen
Power Supply Terminal
Serial Interface (COM2)
Serial Interface (COM1)
Audio Interface (AUDIO OUT)
Ethernet Interface (LAN)USB Interface (USB1)

No.

Name
USB Interface (USB2)
Memory Card Interface (SD)SD Memory Access LED
Expansion Module Interface (EXT)
Battery Cover
Terminal Resistor Switch
Video Interface (VIDEO IN1)
Video Interface (VIDEO IN2)

Sensors
AUTO-ID

HG4G-V Operator Interface
Operation Style

Communication/
Memory Interface

Touch Switch(analog resistive)

COM1
COM2
LAN
USB1
USB2
SD
EXT

Display Screen
Programmable
Operator Interfaces
Periphery
Equipment

12.1-inch
TFT color LCD
65,536 colors

HG5G

Video/Audio
Interface

VIDEO IN1
VIDEO IN2
AUDIO OUT

Housing/Bezel
Color

Part No.

Approvals

HG4G-VCXT22MF-B

Black

HG4G

Safety Standards:
UL61010-1
UL61010-2-201
UL12.12.01
CSA C22.2 No.61010-1-12
CSA C22.2 No.61010-2-201
CSA C22.2 No.213
Ship Classification Standards:
LR, DNV∙GL, ABS, ClassNK

HG3G

Dimensions

HG1G

Panel Cut-out
32.3 (*1)

301.0

10

314.0

301.5 +2.0
0

50

55

11.4

240.0

227.0

44.4

227.5 +2.00

HG2G*1) Depth from the expansion module mounting surface.

30

48.1
54.1

Panel Thickness: 2.0 to 5.0 mm

37.9

6.0

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG4G-V into a panel cut-out by tightening the four mounting clips (supplied with the HG4G-V) to a torque of 0.5 to 0.6 N·m.
Do not tighten with excessive force, otherwise the HG4G-V and screen may become distorted. Also waterproof characteristics may be lost.

L-097

All dimensions in mm.

HG4G-V Operator Interface
Operation Specifications

Rated Power Voltage

24V DC

Switching Element

Analog resistive membrane

Power Voltage Range

20.4 to 28.8V DC
25W maximum
15W maximum when not using USB2 or EXT
7W maximum when Backlight OFF

Operating Force

3N maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer or audio output

Power Consumption

Allowable Momentary
10 ms maximum
Power Interruption
Inrush Current
30A maximum
Dielectric Strength

1,000V AC, 10 mA, 1 minute between power and FG terminals

Operating Temperature −20 to +60°C (no freezing)
Operating Humidity

10 to 90% RH (no condensation)

Storage Temperature−20 to +70°C (no freezing)

Storage Humidity

10 to 90% RH (no condensation)2
5 to 8.4 Hz amplitude 3.5 mm, 8.4 to 150 Hz, acceleration 9.8 m/s2
Vibration Resistance
10 cycles (100 minutes) on each of three mutually perpendicular axes
147 m/s2, 11 ms
Shock Resistance
5 shocks on each of three mutually perpendicular axes
Fast transient/burst test,
Noise Immunity
Power terminals: ±2 kV,Communication line: ±1 kV (IEC/EN61131-2)
Electrostatic Discharge Contact ±6 kV, air ±8 kV (IEC/EN61131-2)

Function Specifications
Screen Types

Power Failure Backup Data
Battery

Recommended replacement: every 5 years (at 25°C)

User Memory

Pollution Degree

Corrosion Immunity

Free from corrosive gases

Mounting
Degree of Protection(*1)
Dimensions

Panel mounting (Panel Thickness: 2.0 to 5.0 mm)
IP66F/IP67F (IEC 60529) (front part when mounted)
UL Type 4X, 12, and 13
314.0W × 240.0H × 54.1D mm

Weight (approx.)

2.1 kg• Do not use the HG4G-V in an environment subject to strong ultraviolet rays, otherwise the
LCD quality will deteriorate.
*1) See instructions on L-111 for details.

APEM

Base screen, popup screen, system screen
Base screen: 3,000 max.
Popup screen: 3,015 max.
58 MB (including expansion fonts and kanji dictionary data)
Bit Button, Word Button, Goto Screen, Print Button, Key
Button, Multi Button, Keypad, Selector Switch, Potentiometer,
Numerical Input, Character Input, Pilot Lamp, Multi-State
Lamp, Picture Display, Message Display, Message Switching
Display, Alarm List Display, Alarm Log Display, Numerical
Display, Bar Graph, Trend Chart, Pie Chart, Meter, Calendar,
Bit Write Command, Word Write Command, Goto Screen
Command, Print Command, Timer, Screen Script Command,
Multi Command, Video Display
Year, Month, Day, Hour, Min., Sec., Day of Week
±60 sec per month (at 25°C)
Calendar, log data, keep internal relay, keep internal register

No. of Screens

Parts

CalendarInterface Specifications
Electrical Characteristics

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

D-sub 9-pin connector / socket

Electrical Characteristics

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
AsynchronousTransmission Speed
Serial Interface(COM1)TFT Color LCD

Color/Shade

65,536 colors

Effective Display Area

245.76W × 184.32H mm

Display Resolution

1,024W × 768H pixels

View Angle

Left/right/top/bottom: 85°

Communication Method

Half or full duplex

Backlight

White LED

Control System

Hardware control or none (*6)

Backlight Life

100,000 hours minimum (*2)

Connector

Detachable 9-pin terminal block

Brightness

600 cd/m2 (*3)

IEEE802.3u (10/100BASE-T) compliant

Brightness Adjustment

48 levels

Ethernet
Interface (LAN)Interface
Connector

Modular connector (RJ-45)

Backlight Replacement

Video Interface(VIDEO IN1)

Interface

NTSC/PAL

Connector

Pin jack

Video Interface(VIDEO IN2)Interface

NTSC/PAL

Connector

Pin jack

Audio Interface(AUDIO OUT)

InterfaceLINE OUT (stereo)

Connector

Mini jack connector (ø3.5 mm)

USB Interface(USB1)

InterfaceUSB 2.0

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput current

5V 500 mA

1/4 size

Not possible
8 × 8 pixels (Western European language: ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)
16 × 16 pixels (Japanese JIS first and second level characters,
simplified Chinese, traditional Chinese, Korean)
32 × 32 pixels (Japanese JIS first level characters, Mincho font)
Width 8 to 128 dots (1/2 size fixed)(ISO 8859-1 western language, 7-segment)
128 characters × 96 lines

Interface

SD memory card, SDHC memory card

1/2 size

128 characters × 48 lines

Connector

SD memory card socket

Full size

64 characters × 48 lines

Interface

MicroSmart I/O module interface

Double size

32 characters × 24 lines (Mincho font)

Display Character Size

Full size
Double size

Quantity of
Characters

Scalable

Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute

Blink (1 or 0.5 sec period), reverse, bold, shadowed

Graphics

Straight line, polyline, rectangle, arc, pie,circle/ellipse,
equilateral polygons (3, 4, 5, 6, 8), picture, fill

Window Display

3 popup screens + 1 system screen

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors

LED Illumination

Display

1/2 size

Switches &Pilot Lights

Power Supplies

Display Specifications

1/4 size

Operator Interfaces

General Specifications

Transmission Speed
Serial Interface(COM2)(*4)

USB Interface(USB2)
Memory Card
Interface (SD)Expansion
Module Interface Ouput Current(EXT)Max. No. of Units

Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

5V 130 mA, 24V 150 mA
4 units*4) RS232C and RS 422/485 can be used simultaneously*5) 187,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).
*6) RS232C only for hardware control• See instructions on L-111 for details.
*2) The backlight life is not guaranteed and refers to the time until the brightness reduces byhalf after use at 25°C. The actual life depends on operating environments and conditions.
*3) Brightness of the LCD only.

L-098

Operator Interfaces

4, 8.4 ininchch
1100..4, 8.4

HG3G-V Operator Interface
Excellent visibility by super-bright LED backlight.
700 cd/m2 (10.4-inch), 800 cd/m2 (8.4-inch)
12

APEM

14

2
11

Switches &Pilot Lights

12

10

Control Boxes
Emergency
Stop Switches
Enabling
Switches

13

13 14

9
3

8

Safety Products

1

Explosion Proof

15

Terminal Blocks
Relays & Sockets

4

Circuit
Protectors

5

6

7

16 17

No.

Power Supplies
LED Illumination(for main unit only)

Controllers
Operator
Interfaces• See website for details on approvals and standards.

Name
Power LED
Display
Touchscreen
Power Supply Terminal
Serial Interface (COM2)
Serial Interface (COM1)
Audio Interface (AUDIO OUT)
Ethernet Interface (LAN)USB Interface (USB1)

No.

Name
USB Interface (USB2)
Memory Card Interface (SD)SD Memory Access LED
Expansion Module Interface (EXT)
Battery Cover
Terminal Resistor Switch
Video Interface (VIDEO IN1)
Video Interface (VIDEO IN2)

Sensors
AUTO-ID

HG3G-V Operator Interface
Display Screen

Programmable
Operator Interfaces
Periphery
Equipment

10.4-inch
TFT color LCD
65,536 colors

HG5G

8.4-inch
TFT color LCD
65,536 colors

Communication/
Memory Interface

Operation Style

Video/Audio
Interface

COM1
COM2
LAN
USB1
USB2
SD
EXT

Touch Switch(analog resistive)

VIDEO IN1
VIDEO IN2
AUDIO OUT

Housing/Bezel
Color

Part No.

Approvals

Light gray

HG3G-VAXT22MF-W

Black

HG3G-VAXT22MF-B

Light gray

HG3G-V8XT22MF-W

Black

HG3G-V8XT22MF-B

HG4G

Safety Standards:
UL61010-1
UL61010-2-201
UL12.12.01
CSA C22.2 No.61010-1-12
CSA C22.2 No.61010-2-201
CSA C22.2 No.213
Ship Classification Standards:
LR, DNV∙GL, ABS, ClassNK

HG3G

HG1G

HG3G-VA (10.4-inch)

All dimensions in mm

HG3G-V8 (8.4-inch)
30.9 (*1)
10

270.0

HG3G-VA (10.4-inch)
258.0 +2.0032.6 (*1)
257.5

218.5

231.0

44.4

15.2
20
163.5

219.0 +2.0
0

55

50
30

11.4

48.4
54.4

HG3G-V8 (8.4-inch)

38.2

30

55

50
52.7

36.5

46.7

6.0

11.4

30
35

176.0

212.0

199.5

40

6.0

Panel Cut-out

200.0 +2.00Dimensions

164.0 +2.00

HG2G*1) Depth from the expansion module mounting surface.
Panel Thickness: 2.0 to 5.0 mm

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG3G-V into a panel cut-out by tightening the four mounting clips (supplied with the HG3G-V) to a torque of 0.5 to 0.6 N·m.
Do not tighten with excessive force, otherwise the HG3G-V and screen may become distorted. Also waterproof characteristics may be lost.

L-99

HG3G-V Operator Interface

Model
Rated Power Voltage
Power Voltage Range

Power Consumption

Allowable Momentary
Power Interruption
Inrush Current
Dielectric Strength
Operating Temperature
Operating Humidity
Storage Temperature
Storage Humidity
Pollution Degree

HG3G-VA (10.4 inch)
24V DC
20.4 to 28.8V DC
25W maximum
15W maximum when notusing USB2 or EXT
7W maximum when
Backlight OFF

Operation Specifications
HG3G-V8 (8.4 inch)

22W maximum
15W maximum when notusing USB2 or EXT
7W maximum when
Backlight OFF

10 ms maximum

Switching Element

Analog resistive membrane

Operating Force

3N maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer or audio output

Function Specifications
Screen Types

30A maximum
1,000V AC, 10 mA, 1 minute between power and FG terminals−20 to +60°C (no freezing)
10 to 90% RH (no condensation)−20 to +70°C (no freezing)
10 to 90% RH (no condensation)2
5 to 8.4 Hz amplitude 3.5 mm,8.4 to 150 Hz, acceleration 9.8 m/s2
Vibration Resistance
10 cycles (100 minutes) on each of three mutually perpendicular axes
147 m/s2, 11 ms
Shock Resistance
5 shocks on each of three mutually perpendicular axes
Fast transient/burst test,
Noise Immunity
Power terminals: ±2 kV,Communication line: ±1 kV (IEC/EN 61131-2)
Electrostatic Discharge Contact ±6 kV, air ±8 kV (IEC/EN 61131-2)
Corrosion Immunity
Free from corrosive gases
Mounting
Panel mounting (Panel Thickness: 2.0 to 5.0 mm)
Degree of Protection
IP66F/IP67F (IEC 60529) (front part when mounted)(*1)
UL Type 4X, 12, and 13
270.0W × 212.0H × 52.7D mm 231.0W × 176.0H × 54.4D mm
Dimensions
Weight (approx.)1.65 kg
1.25 kg• Do not use the HG3G-V in an environment subject to strong ultraviolet rays, otherwise the
LCD quality will deteriorate.
*1) See instructions on L-111 for details.

Power Failure Backup Data
Battery

Recommended replacement: every 5 years (at 25°C)

User Memory

Parts

Calendar

HG3G-VA (10.4 inch)

Display Color
Color/Shade

Interface Specifications
Electrical Characteristics

Effective Display Area 210.4 W ×157.8 H mm
Display Resolution

1,024 W × 768 H pixels

Synchronization
Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

D-sub 9-pin connector / socket

Electrical Characteristics

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

Detachable 9-pin terminal block

Ethernet
Interface (LAN)Interface

IEEE802.3u (10/100BASE-T) compliant

Connector

Modular connector (RJ-45)

Video Interface(VIDEO IN1)

Interface

NTSC/PAL

Connector

Pin jack

Video Interface(VIDEO IN2)Interface

NTSC/PAL

Connector

Pin jack

Audio Interface(AUDIO OUT)

InterfaceLINE OUT (stereo)

Connector

Mini jack connector (ø3.5 mm)

USB Interface(USB1)

InterfaceUSB 2.0

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput current

5V 500 mA

Interface

SD memory card, SDHC memory card

Connector

SD memory card socket

Interface

MicroSmart I/O module interface

Transmission Speed
Serial Interface(COM1)

Transmission Speed

View Angle

Left/right/top/bottom: 85°

Backlight

White LED

Backlight Life

100,000 hours minimum (*2)

Brightness

700 cd/m2 (*3)
Brightness Adjustment 48 levels

170.496 W ×127.872 H mm

800 cd/m2 (*3)

Backlight Replacement Not possible

Quantity of
Characters

Display Character Size

1/4 size

1/2 size

8 × 8 pixels (Western European language: ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)

Full size

16 × 16 pixels (Japanese JIS first and second level characters,
simplified Chinese, traditional Chinese, Korean)

Double size

32 × 32 pixels (Japanese JIS first level characters, Mincho font)Scalable

Width 8 to 128 dots (1/2 size fixed)(ISO 8859-1 western language, 7-segment)

1/4 size

128 characters × 96 lines

1/2 size

128 characters × 48 lines

Full size

64 characters × 48 lines

Double size
32 characters × 24 lines (Mincho font)Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute
Blink (1 or 0.5 sec period), reverse, bold, shadowed
Graphics
Window Display

Straight line, polyline, rectangle, arc, pie,circle/ellipse,
equilateral polygons (3, 4, 5, 6, 8), picture, fill
3 popup screens + 1 system screen

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors

LED Illumination

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

HG3G-V8 (8.4 inch)

TFT Color LCD
65,536 colors

Switches &Pilot Lights

Power Supplies

Display Specifications
Model

APEM

Base screen, popup screen, system screen
Base screen: 3,000 max.
Popup screen: 3,015 max.
58 MB (including expansion fonts and kanji dictionary data)
Bit Button, Word Button, Goto Screen, Print Button, Key
Button, Multi Button, Keypad, Selector Switch, Potentiometer,
Numerical Input, Character Input, Pilot Lamp, Multi-State
Lamp, Picture Display, Message Display, Message Switching
Display, Alarm List Display, Alarm Log Display, Numerical
Display, Bar Graph, Trend Chart, Pie Chart, Meter, Calendar,
Bit Write Command, Word Write Command, Goto Screen
Command, Print Command, Timer, Screen Script Command,
Multi Command, Video Display
Year, Month, Day, Hour, Min., Sec., Day of Week
±60 sec per month (at 25°C)
Calendar, log data, keep internal relay, keep internal register

No. of Screens

Operator Interfaces

General Specifications

Serial Interface(COM2)(*4)

USB Interface(USB2)
Memory Card
Interface (SD)Expansion
Module Interface Ouput Current(EXT)Max. No. of Units

Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

5V 130 mA, 24V 150 mA
4 units*4) RS232C and RS 422/485 can be used simultaneously*5) 187,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).
*6) RS232C only for hardware control• See instructions on the L-111 for details.
*2) The backlight life is not guaranteed and refers to the time until the brightness reduces byhalf after use at 25°C. The actual life depends on operating environments and conditions.
*3) Brightness of the LCD only.

L-100

Operator Interfaces

5.7 inch 5.7 inch

HG2G-V Operator Interface (High Performance)
Excellent visibility by super-bright LED backlight.
800 cd/m2 (5.7-inch)
12

13

9

8

APEM
Switches &Pilot Lights

2

11
10

Control Boxes
Emergency
Stop Switches
Enabling
Switches

14

Safety Products

3

Explosion Proof

5

1

6

4

Terminal Blocks

No.

Relays & Sockets
Circuit
Protectors

7Power Supplies
LED Illumination(for main unit only)

Name
Power LED
Display
Touchscreen
Power Supply Terminal
Serial Interface (COM2)
Serial Interface (COM1)
Ethernet Interface (LAN)

No.

Name
USB Interface (USB1)
USB Interface (USB2)
Memory Card Interface (SD)SD Memory Access LED
Expansion Module Interface (EXT)
Battery Cover
Terminal Resistor Switch

Controllers
Operator
Interfaces• See website for details on approvals and standards.

Sensors
AUTO-ID

HG2G-V Operator Interface
Display Screen

Programmable
Operator Interfaces
Periphery
Equipment

5.7-inch
TFT color LCD
65,536 colors

Communication/
Memory Interface

Operation Style

COM1
COM2
LAN
USB 1
USB 2
SD
EXT

Touch Switch(analog resistive)

Housing/Bezel
Color

Part No.

Light gray

HG2G-V5FT22TF-W

Black

HG2G-V5FT22TF-B

Approvals
Safety Standards:
UL61010-1
UL61010-2-201
UL12.12.01
CSA C22.2 No.61010-1-12
CSA C22.2 No.61010-2-201
CSA C22.2 No.213
Ship Classification Standards:
LR, DNV∙GL, ABS, ClassNK

HG5G
HG4G
HG3G

Dimensions
167.2

Panel Cut-out
40

49.4

134.7

40

152.5

35

All dimensions in mm.

153.0 +2.0
0

121.0 +2.0
0

HG1G

120.0

HG2G

*1) Depth from the expansion

33.6 (*1)

Panel Thickness: 1.6 to 5.0 mm

40

5.0

module mounting surface.

54.4

50

55

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG2G-V into a panel cut-out by tightening the four mounting clips (supplied with the HG2G-V) to a torque of 0.2 to 0.3 N·m.
Do not tighten with excessive force, otherwise the HG2G-V and screen may become distorted. Also waterproof characteristics may be lost.

L-101

HG2G-V Operator Interface (High Performance)
Operation Specifications

Rated Power Voltage

24V DC

Switching Element

Analog resistive membrane

Power Voltage Range

20.4 to 28.8V DC

Operating Force

3N maximum

18W maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer or speaker output

Power Consumption

8W maximum when not using USB2 or EXT

Operator Interfaces

General Specifications

4W maximum when Backlight OFF
Allowable Momentary
10 ms maximum
Power Interruption
Inrush Current
30A maximum

Function Specifications

Dielectric Strength

Screen Types

1,000V AC, 10 mA, 1 minute between power and FG terminals

Power Failure Backup Data
Battery

Recommended replacement: every 5 years (at 25°C)

Operating Temperature −20 to +60°C (no freezing)

No. of Screens

Operating Humidity

10 to 90% RH (no condensation)

Storage Temperature−20 to +70°C (no freezing)User Memory

Storage Humidity

10 to 90% RH (no condensation)

Pollution Degree2
5 to 8.4 Hz amplitude 3.5 mm, 8.4 to 150 Hz, acceleration 9.8 m/s2
10 cycles (100 minutes) on each of three mutually perpendicular axes
147 m/s2, 11 ms
Shock Resistance
5 shocks on each of three mutually perpendicular axes
Fast transient/burst test,
Noise Immunity
Power terminals: ±2 kV,Communication line: ±1 kV (IEC/EN61131-2)
Electrostatic Discharge Contact ±6 kV, air ±8 kV (IEC/EN61131-2)
Vibration ResistanceCorrosion Immunity

Free from corrosive gases

Mounting
Degree of Protection(*1)
Dimensions

Panel mounting (Panel Thickness: 1.6 to 5.0 mm)
IP66F/IP67F (IEC 60529) (front part when mounted)
UL Type 4X, 12, and 13
167.2W × 134.7H × 54.4D mm

Weight (approx.)

Parts

CalendarInterface Specifications
Electrical Characteristics

Serial Interface(COM1)

Synchronization
Communication Method

Half or full duplex

Control System

Hardware control or none (*6)

Connector

D-sub 9-pin connector / socket

Electrical Characteristics

Synchronization

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Display

TFT Color LCD

Color/Shade

65,536 colors

Effective Display Area

115.2W × 86.4H mm

Display Resolution

640W × 480H pixels

Communication Method

Half or full duplex

View Angle

Left/right/top/bottom: 80°

Control System

Hardware control or none (*6)

Backlight

White LED

Connector

Detachable 9-pin terminal block

Backlight Life

100,000 hours minimum (*2)

Interface

IEEE802.3u (10/100BASE-T) compliant

Brightness

800 cd/m2 (*3)

Ethernet
Interface (LAN)

Connector

Modular connector (RJ-45)

Brightness Adjustment

48 levels

USB 2.0

Backlight Replacement

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput current

5V 500 mA

Interface

SD memory card, SDHC memory card

Connector

SD memory card socket

1/4 size

Not possible
8 × 8 pixels (Western European language: ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)
16 × 16 pixels (Japanese JIS first and second level characters,
simplified Chinese, traditional Chinese, Korean)
32 × 32 pixels (Japanese JIS first level characters, Mincho font)
Width 8 to 128 dots (1/2 size fixed)(ISO 8859-1 western language, 7-segment)
80 characters × 60 lines

USB Interface(USB1)

Interface

1/2 size

80 characters × 30 lines

Full size

40 characters × 30 lines

Double size

20 characters × 15 lines (Mincho font)

Display Character Size

1/2 size

Full size
Double size

Quantity of
Characters

Scalable

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors

LED Illumination

EIA RS232C, RS422/485 compliant
1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
AsynchronousTransmission Speed

Display Specifications

1/4 size

Switches &Pilot Lights

Power Supplies

0.65 kg• Do not use the HG2G-V in an environment subject to strong ultraviolet rays, otherwise the
LCD quality will deteriorate.
*1) See instructions on the L-111 for details.

APEM

Base screen, popup screen, system screen
Base screen: 3,000 max.
Popup screen: 3,015 max.
58 MB (including expansion fonts and kanji dictionary data)
Bit Button, Word Button, Goto Screen, Print Button, Key
Button, Multi Button, Keypad, Selector Switch, Potentiometer,
Numerical Input, Character Input, Pilot Lamp, Multi-State
Lamp, Picture Display, Message Display, Message Switching
Display, Alarm List Display, Alarm Log Display, Numerical
Display, Bar Graph, Trend Chart, Pie Chart, Meter, Calendar,
Bit Write Command, Word Write Command, Goto Screen
Command, Print Command, Timer, Screen Script Command,
Multi Command, Video Display
Year, Month, Day, Hour, Min., Sec., Day of Week
±60 sec per month (at 25°C)
Calendar, log data, keep internal relay, keep internal register

Transmission Speed
Serial Interface(COM2)(*4)

USB Interface(USB2)
Memory Card
Interface (SD)Interface
Expansion
Module Interface Ouput Current(EXT)Max. No. of Units

Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

MicroSmart I/O module interface
5V 130 mA, 24V 150 mA
2 units*4) RS232C and RS 422/485 can be used simultaneously*5) 187,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).
*6) RS232C only for hardware control

Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute
Graphics
Window Display

Blink (1 or 0.5 sec period), reverse, bold, shadowed
Straight line, polyline, rectangle, arc, pie,circle/ellipse,
equilateral polygons (3, 4, 5, 6, 8), picture, fill
3 popup screens + 1 system screen• See instructions on L-111 for details.
*2) The backlight life is not guaranteed and refers to the time until the brightness reduces byhalf after use at 25°C. The actual life depends on operating environments and conditions.
*3) Brightness of the LCD only.

L-102

Operator Interfaces

5.7 inch

5.7 inch

HG2G-5T Operator Interface (Basic)
Enhanced visibility and user-friendly
Supports a wide range of operating temperatures achieving high environmental resistance.
HG2G-5TT (Color)

HG2G-5TN (Monochrome)

2

APEM

3

2

3

Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches

1

1

Safety Products
Explosion Proof

6

Terminal Blocks

6

Relays & Sockets

No.

9

Circuit
Protectors

9Power Supplies
LED Illumination
Controllers

4

Operator
Interfaces
Sensors

5 10 7 8

4

5 10 7

8

Name
Power LED
Display
Touchscreen
Power Supply Terminal
Serial Interface 1 (SERIAL1)
Ethernet Interface (LAN)USB Interface (USB)
USB Interface (USB2)
Battery Cover
Terminal Resistor Switch(for main unit only)

AUTO-ID• See website for details on approvals and standards.

Programmable
Operator Interfaces
Periphery
Equipment

HG2G-5T Operator Interface
Display Screen
5.7-inch
TFT color LCD
65,536 colors

HG5G
HG4G

5.7-inch
TFT Monochrome LCD
16 shades

Operation Style

Touch Switch(analog resistive)

Communication/Memory
Interface

Housing/Bezel
Color

SERIAL1
LAN
USB
USB2

Light gray
Dark graySilverLight gray
Dark graySilver

HG3GPart No.
HG2G-5TT22TF-W
HG2G-5TT22TF-B
HG2G-5TT22TF-S
HG2G-5TN22TF-W
HG2G-5TN22TF-B
HG2G-5TN22TF-SApprovals
Safety Standards:
UL508
CSA C22.2 No.142
CSA C22.2 No.213
ANSI/ISA 12.12.01

HG2G

Dimensions

Panel Cut-out
53

152.5

All dimensions in mm.

153.0 +2.0
0

121.0 +2.0
0

35.9

134.7

167.2

120.0

HG1G

Panel Thickness: 1.0 to 5.0 mm

5.0

50

45

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG2G-5T into a panel cut-out by tightening the four mounting clips (supplied with the HG2G-5T) to a torque of 0.2 to 0.3 N·m.
Do not tighten with excessive force, otherwise the HG2G-5T and screen may become distorted. Also waterproof characteristics may be lost.

L-103

HG2G-5T Operator Interface (Basic)
Operation Specifications

Model
Rated Power Voltage
Power Voltage Range

Switching Element

Analog resistive membrane

Operating Force

3N maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer or speaker output

Display Specifications
Model
Display
Color/Shade
Effective Display
Area
Display Resolution
View Angle
Backlight
Backlight Life
Brightness
Brightness Adjustment
Backlight Replacement

HG2G-5TT (Color)
TFT color LCD
65,536 colors

Screen Types

Power Failure Backup Data
Battery

Recommended replacement: every 5 years (at 25°C)

No. of Screens
User Memory

Parts

CalendarInterface Specifications

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors

LED Illumination

Electrical
Characteristics

EIA RS232C compliant

Controllers

Transmission Speed

1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Operator
Interfaces

Synchronization

Sensors

Communication Method Half or full duplex
Serial Interface 1(SERIAL1)(*4)

Control System

Hardware control or none

Transmission Speed
Synchronization

1200, 2400, 4800, 9600, 19200, 38400,
57600, 115200, 187500 bps (*5)
Asynchronous

Communication Method Half or full duplex
Control System

Connector

Detachable 9-pin terminal block

Ethernet
Interface (LAN)Interface

IEEE802.3u(10BASE-T/100BASE-TX) compliant

Connector

Modular connector (RJ-45)

USB Interface(USB1)

InterfaceUSB 2.0

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput Current

5V 500 mA

USB Interface(USB2)

AUTO-ID

Electrical Characteristics EIA RS422/485 compliant

Control System

115.2W × 86.4H mm*4) R S232C and RS 422/485 can be used simultaneously*5) 1 87,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

Quantity of
Characters

Display Character Size

Switches &Pilot Lights

Power Supplies

HG2G-5TN (Monochrome)
TFT Monochrome LCD
16 shades

320W × 240H pixels
Right and left 80°, up 80°, down 80° Right and left 65°, up 80°, down 60°
White LED
100,000 hours minimum (*2)
1100 cd/m2 (*3)
500 cd/m2 (*3)
32 levels
Not possible
8 × 8 pixels (Western European language: ISO 8859-1, Central
1/4 size
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
1/2 size
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)
16 × 16 pixels (Japanese JIS first and second level characters,
Full size
simplified Chinese, traditional Chinese, Korean)
Double size 32 × 32 pixels (Japanese JIS first level characters, Mincho font)
1/4 size
40 characters × 30 lines
1/2 size
40 characters × 15 lines
Full size
20 characters × 15 lines
Double size 10 characters × 7 liness (Mincho font)Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute Blink (1 or 0.5 sec period), reverse, bold, shadowed
Straight line, polyline, rectangle, arc, pie,circle/ellipse,
Graphics
equilateral polygons (3, 4, 5, 6, 8), picture, fill
Window Display
3 popup screens + 1 system screen

APEM

Base screen, popup screen, system screen
Base screen: 3,000 max.
Popup screen: 3,015 max.
5 MB (including expansion fonts)
Bit Button, Word Button, Goto Screen, Print Button, Key
Button, Multi Button, Keypad, Selector Switch, Potentiometer,
Numerical Input, Character Input, Pilot Lamp, Multi-State
Lamp, Picture Display, Message Display, Message Switching
Display, Alarm List Display, Alarm Log Display, Numerical
Display, Bar Graph, Trend Chart, Pie Chart, Meter, Calendar,
Bit Write Command, Word Write Command, Goto Screen
Command, Print Command, Timer, Screen Script Command,
Multi Command, Video Display
Year, Month, Day, Hour, Min., Sec., Day of Week
±60 sec per month (at 25°C)
Calendar, log data, keep internal relay, keep internal register

RS232C• Do not use the HG2G-5T in an environment subject to strong ultraviolet rays, otherwise
the LCD quality will deteriorate.
*1) See instructions on the L-111 for details.

Function Specifications

RS422 / 485

HG2G-5TT (Color) / HG2G-5TN (Monochrome)
12V DC/24 V DC
10.2 to 28.8V DC
8W maximum
Power Consumption
4W maximum when not using USB interface (USB2)
Allowable Momentary 10ms maximum (Voltage 20.4 to 28.8V DC)
Power Interruption
1ms maximum (Voltage 10.2 to 20.4V DC)
Inrush Current
40A maximum
Dielectric Strength
1000V AC, 10 mA, 1 minute between power and FG terminals
Operating−20 to +60°C (no freezing)
Temperature
Operating Humidity
10 to 90% RH (no condensation)
Storage Temperature −20 to +70°C (no freezing)
Storage Humidity
10 to 90% RH (no condensation)
Pollution Degree2
5 to 8.4 Hz amplitude 3.5 mm,
8.4 to 150 Hz, acceleration 9.8 m/s2
Vibration Resistance
10 cycles (100 minutes) on each of three mutually perpendicularaxes
147 m/s2, 11 ms
Shock Resistance
5 shocks on each of three mutually perpendicular axes
Fast transient/burst test,
Power terminals: ±2 kV,
Noise Immunity
Communication line: ±1 kV(IEC/EN 61131-2, IEC/EN 61000-4-4)
Electrostatic
Contact ±6 kV, air ±8 kV (IEC/EN 61131-2, IEC/EN 61000-4-2)
Discharge
Corrosion Immunity
Free from corrosive gases
Mounting
Panel mounting (Panel Thickness: 1.0 to 5.0 mm)
IP66F (IEC 60529) (front part when mounted)
Degree of Protection
UL Type 4X, 12, and 13(*1)
IP65F when panel thickness is below 1.5mm
Dimensions
167.2 W ×134.7 H × 40.9 D mm
Weight (approx.)
0.5 kgOperator Interfaces

General Specifications• See instructions on L-111 for details.
*2) The backlight life is not guaranteed and refers to the time until the brightness reduces byhalf after use at 25°C. The actual life depends on operating environments and conditions.
*3) Brightness of the LCD only.

L-104

Operator Interfaces

44..33ininchch

HG1G Operator Interface
Maintenance time reduced by IoT monitoring.
Enhanced visibility and user-friendly.
1

3

2

8

6

7

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof

5

Terminal Blocks

4

Relays & Sockets
Circuit
Protectors

No.

Power Supplies(for main unit only)

LED Illumination
Controllers

Name
Display
Touchscreen
Power Supply Terminal
Serial Interface (COM)

No.

Name
Ethernet Interface (LAN)USB Interface (USB1)
USB Interface (USB2)
Battery Cover• See website for details on approvals and standards.

Operator
Interfaces
Sensors
AUTO-ID

HG1G Operator Interface
Display Screen

Programmable
Operator Interfaces
Periphery
Equipment

4.3-inch
TFT color LCD
65,536 colors

Operation Style

Touch Switch(analog resistive)

Communication/Memory
Interface

Housing/Bezel
Color

COM
LAN
USB1
USB2

Black

HG1G-4VT22TF-B

Silver

HG1G-4VT22TF-SPart No.

Approvals
Safety Standards:
UL508
CSA C22.2 No.142
CSA C22.2 No.213
ANSI/ISA 12.12.01• Models with a coated board that can be used in harsh environments are also available.
HG5G

Dimensions

Panel Cut-out

HG3G

43.2

50

117.0

118.0 +1
–0

91.0

102.0

+1

128.0

HG2G
HG1G

All dimensions in mm.

52.2

92.0 –0

HG4G

34.5

4.0

27.8

Panel Thickness: 1.0 to 5.0 mm

Note 1: Dimensions in blue show the mounting dimensions of the cable.
Note 2: Dimensions in the figure may vary depending on the type of cable connected.
Note 3: Install the HG1G into a panel cut-out by tightening the two mounting clips (supplied with the HG1G) to a torque of 0.3 to 0.35 N·m.
Do not tighten with excessive force, otherwise the HG1G and screen may become distorted. Also waterproof characteristics may be lost.

L-105

HG1G Operator Interface

Electrical Specifications

Operation Specifications

Rated Power Voltage 12/24 V DC

Switching Element

Analog resistive membrane

Power Voltage Range 10.2 to 28.8V DC

Operating Force

3N maximum

Mechanical Life

1,000,000 operations

Acknowledgement Sound

Electronic buzzer

Power Consumption

8W maximum
4W maximum when not using USB interface (USB2)

Allowable Momentary 10ms maximum (voltage 20.4 to 28.8V DC)
Power Interruption
1ms maximum (voltage 10.2 to 20.4V DC)
Inrush Current

40A maximum

Dielectric Strength

1,000V AC, 10 mA, 1 minute between power and FG terminals

Operating Temperature −20 to +55°C (no freezing)
Operating Humidity 10 to 90% RH (no condensation)

Structure

Environmental Specifications

Storage Temperature −20 to +70°C (no freezing)
Storage Humidity

10 to 90% RH (no condensation)

Pollution Degree2

Vibration Resistance

5 to 8.4 Hz amplitude 3.5 mm, 8.4 to 150 Hz, acceleration 9.8 m/s
10 cycles (100 minutes) on each of three mutually perpendicular axes

Shock Resistance

147 m/s2, 11 ms
5 shocks on each of three mutually perpendicular axes

Noise Immunity

Fast transient/burst test,
Power terminals: ±2 kV,Communication line: ±1 kV (IEC/EN 61131-2, IEC/EN 61000-4-4)

Electrostatic
Discharge

Contact ±6 kV, air ±8 kV(IEC/EN 61131-2, IEC/EN 61000-4-2)

Function Specifications
Screen Types

Base screen, popup screen, system screen

No. of Screens

Base screen: 3,000 max.
Popup screen: 3,015 max.

User Memory

12 MB (including expansion fonts)

Parts

Bit Button, Word Button, Goto Screen,Print Button Key Button,
Multi Button, Keypad, Selector Switch, Potentiometer, Numerical
Input, Character Input, Pilot Lamp, Multi-State Lamp, Picture Display,
Message Display, Message Switching Display, Alarm List Display,
Alarm Log Display, Numerical Display, Bar Graph, Trend Chart,
Pie Chart, Meter, Calendar, Bit Write Command, Word Write Command,
Goto Screen Command,Print Command Screen Script Command,
Multi Command,Timer2

CalendarYear, Month, Day, Hour, Min., Sec., Day of Week
±90 sec per month (at +25°C)

Corrosion Immunity Free from corrosive gases

Power Failure
Backup Data

Calendar, log data, keep internal relay, keep internal register

Mounting

Panel mounting (panel thickness: 1.0 to 5.0 mm)

Battery

Recommended replacement time: every 5 years (at +25°C)

Degree ofProtection (*1)

IP66F/IP67F (IEC 60529) (front part when mounted)
UL Type 4X, 12, and 13
IP65F/IP67F when panel thickness is below 1.5mm

Dimensions

128 W ×102 H × 31.8 D mm

Weight (approx.)

300g

Interface Specifications

Color/Shade

65,536 colors
Effective Display Area 95.04 W × 53.836 H mm
Display Resolution

480 W × 272 H pixels

View Angle

Right and left 70°, up 60°, down 65°

Backlight

White LED

Backlight Life

70,000 hours (*2)

Brightness

800 cd/m2 (*3)

Brightness
Adjustment

32 levels

Backlight Replacement Not possible

Quantity of
Characters

Display Character Size

1/4 size

1/2 size

8 × 8 pixels (Western European language: ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
8 × 16 pixels (Western European language ISO 8859-1, Central
European language: ANSI 1250, Baltic: ANSI 1257, Cyrillic:
ANSI1251, Japanese katakana and symbols: JIS 8-bit code)
16 × 32 pixels, 24 × 48 pixels, 32 × 64 pixels(Western European language: ISO 8859-1)

Full size

16 × 16 pixels (Japanese JIS first and second level characters,
simplified Chinese, traditional Chinese, Korean)

Double size

32 × 32 pixels (Japanese JIS first level characters, Mincho font)

1/4 size

60 characters × 34 lines

1/2 size

60 characters × 17 lines

Full size

60 characters × 17 lines

Double size

15 characters × 8 lines (Mincho font)

RS232C
RS422/485

TFT color LCD

Serial Interface (COM) (*4)

Display

APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies• Do not use the HG1G in an environment subject to strong ultraviolet rays, otherwise the
LCD quality will deteriorate.
*1) See instructions on L-111 for details.

Display Specifications

Operator Interfaces

General Specifications

Electrical
Characteristics

EIA RS232C compliant

Transmission
Speed

1200, 2400, 4800, 9600, 19200, 38400, 57600,
115200, 187500 bps (*5)

Synchronization

Asynchronous

Communication
MethodHalf or full duplex

Control System

Hardware control or none

Electrical
Characteristics

EIA RS422/485 compliant

Transmission
Speed

1200, 2400, 4800, 9600, 19200, 38400, 57600,
115200, 187500 bps (*5)

Synchronization

Asynchronous

Communication
MethodHalf or full duplex

Control System

None

Connector

Detachable 9-pin terminal block

LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G

Ethernet
Interface(LAN)

Interface

IEEE802.3u (10BASE-T/100BASE-TX) compliant

HG4G

Connector

Modular connector (RJ45)

HG3G

USB
Interface(USB1)

InterfaceUSB 2.0

Connector

USB Type Mini-B connector

InterfaceUSB 2.0

Connector

USB Type A connector

Ouput Current

5V 500 mA (*6)

USBInterface(USB2)

HG2G
HG1G*4) RS232C and RS 422/485 can be used simultaneously.
*5) 187,500 bps is available only with SIEMENS SIMATIC S7-300/400 series(MPI port direct connection).
*6) When using USB2 at 151mA min., the operating temperature is –20 to 50° C.

Character Magnification 0.5, 1 to 8 vertically and horizontally (except for scalable fonts)
Character Attribute
Graphics
Window Display

Blink (1 or 0.5 sec period), reverse, bold, shadowed
Straight line, polyline, rectangle, arc, pie,circle/ellipse,
equilateral polygons (3, 4, 5, 6, 8), picture, fill
3 popup screens + 1 system screen• See instructions on L-111 for details.
*2) The backlight life is not guaranteed and refers to the time until the brightness reduces byhalf after use at 25°C. The actual life depends on operating environments and conditions.
*3) Brightness of LCD when operating condition is 25°C.

L-106

HG Series Operator Interface
Operator Interfaces

Options
Name
Application Software

Package
Quantity

Part No.
SW1A-W1C

USB Maintenance Cable HG9Z-XCM42
APEM
Switches &Pilot Lights
Control Boxes

PLC Connection Cable

Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets

USB panel-mountextension cable
Protective Cover

Circuit
Protectors
Power Supplies
LED Illumination

Protective Sheet (*1)

Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

Expansion Module
Clamp (*2)

User’s Manual

Description

Applicable Model
HG5G HG4G HG3G HG3G HG2G HG2G HG1G
-V
-V
-VA
-V8
-V
-5T

1

Automation Organizer (includes WindO/I-NV4)















1

USB Cable (2m), USB-miniB















HG9Z-XC295

1

For IDEC MicroSmart (5m), Mini DIN 8-pin (Dsub 9-pin)











–

–

HG9Z-XC305

1

For Mitsubishi FX series (5m), Mini DIN 8-pin (Dsub 9-pin)











–

–

HG9Z-XC315

1

For Mitsubishi Q series (5m), Mini DIN 6-pin (Dsub 9-pin)











–

–

HG9Z-XC275

1

For IDEC MicroSmart (5m), Mini DIN 8-pin (loose wire)















FC2A-KP1C

1

For IDEC MicroSmart (2.4m), Mini DIN 8-pin (loose wire)















FC6A-KC1C

1For IDEC MicroSmart (FC6A) (5m), RJ45 connector (loose wire)















FC6A-KC2C

1For IDEC MicroSmart (FC6A) (5m), RJ45 connector (Dsub 9-pin)









–

–

–

HG9Z-XCE11

1

For USB-A port (1m)















HG9Z-XCE21

1

For USB-mini B port (1m)















HG9Z-2E2PN03

3

For 5.7 inch (3 pcs/pack)(used to cover the front side of the operator interface)

–

–

–

–





–

HG9Z-1D4PN05

5

For 4.3 inch (5 pcs/pack) (used to protect the LCD)

–

–

–

–

–

–



HG9Z-2D5PN05

5

For 5.7 inch (5 pcs/pack) (used to protect the LCD)

–

–

–

–





–

HG9Z-3D8PN02

2

For 8.4-inch (2 pcs/pack)

–

–

–



–

–

–

HG9Z-3DA2PN02

2

For 10.4-inch (2 pcs/pack)

–

–



–

–

–

–

HG9Z-4DCPN02

2

For 12.1 inch (2 pcs/pack)

–



–

–

–

–

–

HG9Z-5DFPN01

1

For 15.0 inch (1 pcs/pack)



–

–

–

–

–

–











–

–











–

–









–

–

–















HG9Z-XJ3PN05

5

HG9Z-XJ4PN05

5

HG9Z-XJ5PN05

5

HG9Y-B1701

1

For installing the expansion modules on the back of the operator
interface (short). For total width 17.6 to 41.1 mm.
For installing the expansion modules on the back of the operator
interface (long). For total width 47.0 to 69.4 mm.
For installing the expansion modules on the back of the operator
interface (XL). For total width 70.5 to 93.0 mm.
English*1) The protective sheet is UV resistant, however, resistance against direct sunlight in outdoor usage is not guaranteed.
Used to protect the display screen.
*2) Use the expansion module clamp when using expansion modules.
Order the module clamp by referring to the width of the module shown in the dimensions of each module.

HG5G
HG4G
HG3G

Maintenance Parts

HG2G

Name

Package
Quantity

SLD-K02PN10

10Four clips are supplied.

–

–

–

–





–

HG9Z-4K2PN04

4Four clips are supplied.
(Two clips supplied with HG1G)

–







–

–



HG9Z-4K2PN06

6

Six clips are supplied.



–

–

–

–

–

–

HG9Z-XT09V

1

One plug (terminal block type) is supplied.

–

–

–

–







HG9Z-XT09

1

One plug (terminal block type) is supplied.









–

–

–

HG9Z-XR1

1

Lithium battery CR2032 (one battery is supplied)

–

–

–

–

–





HG9Z-XR2

1

Lithium battery CR2032W (one battery is supplied)











–

–

HG9Z-XU1PN05

5Used to lock USB cable (for USB2).















Description

HG1G

Mounting Clip

Serial Interface Connector(Detachable 9-pin terminal block)
Replacement Battery
USB Cable Lock Pin

L-107

Applicable Model

Part No.

HG5G HG4G HG3G HG3G HG2G HG2G HG1G
-V
-V
-VA
-V8
-V
-5T

HG Series Operator Interface

Input Modules
Input

Part No.

Dimensions(L × W × H mm)

Connector

Consumption Current (mA)
5V
24V

Operator Interfaces

Expansion Modules (Cannot be used for expansion with HG2G-5T and HG1G)

8 points/DC Input

FC6A–N08B1

Removable, 5.08mm pitch
11-pin, screw fastened type connector

90.0 × 23.6 × 73.030

0

16 points/DC Input

FC6A–N16B1

Removable, 3.81mm pitch
10-pin, screw fastened type connector

90.0 × 23.6 × 73.0

40

0

APEM

16 points/DC Input

FC6A–N16B3

90.0 × 17.6 × 73.0

400

Switches &Pilot Lights

32 points/DC Input

FC6A–N32B3

90.0 × 30.2 × 73.06508 points/AC Input

FC6A–N08A11

90.0 × 23.6 × 73.040020-pin MIL connector

Removable, 5.08mm pitch
11-pin, screw fastened type connector

Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products

Output Modules

Explosion Proof

OutputPart No.

Dimensions(L × W × H mm)

Connector

8 points/Relay Output

FC6A–R081

Removable, 5.08mm pitch
11-pin, screw fastened type connector

16 points/Relay Output

FC6A–R161

Removable, 3.81mm pitch
10-pin, screw fastened type connector

8 points/Transistor Sink Output

FC6A–T08K1

8 points/Transistor Source Output

FC6A–T08P1

Removable, 5.08mm pitch
11-pin, screw fastened type connector

Consumption Current (mA)
5V
24V

90.0 × 23.6 × 73.0

35

50

Relays & Sockets

90.0 × 23.6 × 73.0

50

100

Circuit
Protectors

90.0 × 23.6 × 73.0

25

15

90.0 × 23.6 × 73.0

25

15

Controllers

90.0 × 23.6 × 73.0

30

25Operator
Interfaces

Power Supplies

16 points/Transistor Sink Output

FC6A-T16K1

Removable, 3.81mm pitch
10-pin, screw fastened type connector

16 points/Transistor Sink Output

FC6A–T16K3

20-pin MIL connector

90.0 × 17.6 × 73.0

30

25

16 points/Transistor Source Output

FC6A-T16P1

Removable, 3.81mm pitch
10-pin, screw fastened type connector

90.0 × 23.6 × 73.0

30

25

16 points/Transistor Source Output

FC6A–T16P3

90.0 × 17.6 × 73.030

25

32 points/Transistor Sink Output

FC6A–T32K3

90.0 × 30.2 × 73.0

45

50

32 points/Transistor Source Output

FC6A–T32P3

90.0 × 30.2 × 73.0455020-pin MIL connector

24V DC(Sink/Source)

Output240V AC, 2A
30V DC, 2A

Sensors

Programmable
Operator Interfaces
Periphery
Equipment

HG5G

Dimensions(L × W × H mm)

Consumption Current (mA)
5V
24V

Part No.

Connector

4 points/DC Input
4 points/Relay Output

FC6A–M08BR1

Removable, 5.08mm pitch,
11-pin, screw fastened type connector

90.0 × 23.6 × 73.0

30

25

16 points/DC Input
8 points/Relay Output

FC6A-M24BR1

Removable, 3.81mm pitch
11-pin, screw fastened type connector
17-pin, screw fastened type connector

90.0 × 39.2 × 73.0

55

50

I/O Points

LED Illumination

AUTO-ID

Digital Combination I/O Modules
Input

Terminal Blocks

HG4G
HG3G
HG2G
HG1G

L-108

HG Series Operator Interface
Operator Interfaces

Analog I/O Modules
Name

Part No.

I/O Points

FC6A–J2C1

2 inputs

FC6A–J4A1

4 inputs

FC6A–J8A1

8 inputs

Input

Dimensions(L × W × H mm)

OutputTerminal—

Removable, 5.08mm pitch
11-pin, screw fastened type connector

Consumption
Current (mA)
5
24
40

0

—

45

0

—

40

0

50

0

50

0

45

0

40

0

50

0

Removable, 3.81mm pitch
10-pin, screw fastened type connector

55

0Removable, 5.08mm pitch
11-pin, screw fastened type connector

55

0

APEM
Switches &Pilot Lights

Voltage (0 to 10V, −10 to +10V)
Current (0 to 20mA, 4 to 20mA)

Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof

Analog Input Module

Control Boxes

FC6A-J4CN1

4 inputs

Voltage (0 to 10V, −10 to +10V)
Current (0 to 20mA, 4 to 20mA)
Thermocouple(K, J, R, S, B, E, T, N, C)
Resistance Thermometer(Ni100, Ni1000, Pt100, Pt1000)

FC6A-J4CH1Y

Isolated
betweenchannels
4 inputs

Thermocouple(K, J, R, S, B, E, T, N, C)

FC6A-J8CU1

8 inputs

Thermocouple(K, J, R, S, B, E, T, N, C)
NTC/PTC Thermistor

FC6A–K2A1

2 outputs—

FC6A–K4A1

4 outputs—

FC6A-L06A1

4 inputs/
2 outputs

Voltage (0 to 10V, −10 to +10V)
Current (0 to 20mA, 4 to 20mA)

2 inputs/
1 output

Voltage (0 to 10V, −10 to +10V)
Current (0 to 20mA, 4 to 20mA)
Thermocouple(K, J, R, S, B, E, T, N, C)
Resistance Thermometer(Ni100, Ni1,000, Pt100, Pt1000)

Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers——

Removable, 3.81mm pitch
10-pin, screw fastened type connector

90.0 × 23.6 × 73.0—

Sensors
AUTO-ID

Analog Output Module

Operator
Interfaces

HG5G
HG4G

Analog I/O Module

Programmable
Operator Interfaces
Periphery
Equipment

FC6A-L03CN1

HG3G
HG2G
HG1G

Voltage(0 to 10V, −10 to +10V) Removable, 5.08mm pitch
11-pin, screw fastened type connector
Current(0 to 20mA, 4 to 20mA)

Voltage(0 to 10V, −10 to +10V)
Current(0 to 20mA, 4 to 20mA)• IDEC PLC MicroSmart expansion I/O modules can be used.
When connecting expansion modules to the HG5G-V, HG4G/3G-V, and HG2G-V, note the limits shown below:
No. of Connectable
Expansion Modules

Total width of expandable modules
when more than two are used

Current flow rate at 5V

Current flow rate at 24V

HG5G-V

4 max.

93.0 mm max.

130 mA max.

50 mA max.

HG4G/3G-V

4 max.

93.0 mm max.

130 mA max.

150 mA max.

HG2G-V

2 max.

70.0 mm max.

130 mA max.

150 mA max.

Part No.

• Use the expansion module clamp when using expansion modules.
Order the module clamp by referring to the width of the module shown in the dimensions of each module.
• See catalog or instruction manual (http://www.idec.com/language/) for details on MicroSmart expansion modules.

L-109

HG Series Operator Interface

Note: HG2G-5T and HG1G cannot communicate using Ethernet/IP (Logix Native Tag)
Manufacturer

SeriesManufacturer

MICROSmart FC6A (Ethernet)
IDEC

Mitsubishi

SmartAXIS FT1A Pro/Lite (Ethernet)
MICROSmart FC6A / FC5A / FC4A

Modbus RTU Slave (*2)
ModiconModbus TCP Client (*1)

MELSEC-A (link unit)

Modbus TCP Server (*2)

MELSEC-QnA (link unit)

Schneider Electric

Twido

MELSEC-Q (link unit)

Panasonic

FP Series

MELSEC-Q (Ethernet)

Yaskawa Electric

DirectLOGIC 05
DirectLOGIC 06

SYSMAC-CJ1

Koyo

DirectLOGIC 205

Safety Products

KOSTAC SZ

Explosion Proof
Terminal Blocks

Power Mate

Relays & Sockets

CompactLogix (Full Duplex)
FlexLogix (Full Duplex)

Fanuc
Yokogawa Electric

SeriesFA-M3

Circuit
Protectors

FA-M3 (Ethernet)

Power Supplies

FREX-PC
Fuji Electric

MICREX-F

LED Illumination

MICREX-SXControllers

ControlLogix (Ethernet/IP, Ethernet/IP (Logix Native Tag))

MICREX-SX (Ethernet)

CompactLogix (Ethernet/IP, Ethernet/IP (Logix Native Tag))PROSEC T Series

Operator
Interfaces

PLC-5 (Ethernet/IP)
SLC 500 (Ethernet/IP)
MicroLogix (Ethernet/IP)
S7-200Toshiba
LS Industrial Systems
VIGOR

V Series

Sensors

MASTER-K

AUTO-ID

VB
VH

S7-300 (connects to CPU)

EmersonFloBoss

S7-300 (link unit)

Hitachi Industrial
Equipment Systems

EH

S7-400S7-1200 (Ethernet)
KV-700/1000/3000/5000
KV NanoKZ
KVKV (Ethernet)

GE Fanuc Automation

Emergency
Stop Switches
Enabling
Switches

KOSTAC SU (Ethernet)

ControlLogix (Full Duplex)

Toshiba Machine
Works

Control Boxes

SYSMAC-CP1

MicroLogix (Full Duplex)

JTEKT

Switches &Pilot Lights

KOSTAC SU

SLC-500 (Half Duplex)

HitachiAPEM

SYSMAC-CJ2

PLC-5 (Half Duplex)

KeyenceMP (Ethernet)

SYSMAC-CSYSMAC (Ethernet)

SIEMENSMP

MELSEC-FX (Ethernet)
SYSMAC-CS

Allen-Bradley

Modbus ASCII Master (*1)

SmartAXIS FT1A Pro/Lite

MELSEC-FX

OMRON

SeriesModbus RTU Master (*1)

Operator Interfaces

Compatible PLCs

S10mini
S10V
TOYOPUC-PC2J
TOYOPUC-PC3J

EH (Ethernet)• The compatible PLC information is for reference only (except for IDEC PLCs), and
IDEC does not guarantee the operation of any other manufacturers’ PLC. Whenusing other manufacturers’ PLCs, read their specifications and instruction manual
carefully. The PLC must be operated correctly under the user’s responsibility.
• The company names and product names are registered trademarks or brandnames.

*1) H
 G series can be connected as a master to the slave/server device.
*2) H G series is connected as a slave to the master/client device.
An updated listing of compatible PLCs can be found at the following website.
http://www.idec.com/oi/drivers

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

TC200
TCmini
Series90-30
VersaMax

L-110

HG Series Operator Interface
Operator Interfaces
APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G

Operating Instructions
Be sure to read this manual carefully before performing installation, wiring, or maintenance work.
• This product has been manufactured under strict quality control.
However, if you intend to use this product in applications where
failure of this equipment may result in damage to property or injury,
ensure that it used in conjunction with appropriate fail-safe backup
equipment.
• When using the HG series in applications which require high reliability
and safety, such as nuclear equipment, railways, aircraft, medical
equipment, and vehicles, add a failsafe or backup functionality andverify an adequate level of safety using the product specifications.
• Turn off the power to the HG series before installation, removal,
wiring, maintenance, and inspection of the HG series. Failure to turnpower off may cause electrical shock or fire hazard.
• Emergency and interlocking circuits must be configured outside of
the HG series.
• Do not use touch switches and the function keys for an emergency
circuit or an interlocking circuit. If the HG series fails, external
equipment connected to the HG series will no longer be protected,
and serious injury to operators and equipment damage may becaused.
• Although the screen will not be visible if the backlight of the HG series
burns out, the touch panel will remain functional. Incorrect touch
panel operation will occur when operating the touch panel when thebacklight appears to be turned off but is actually burnt out. Becausesuch erroneous operation could result in damage, the touch panel
should not be used after the backlight has burned out.
• When more than one button is pressed at the same time, due to thedetection characteristics of an analog type touch panel, only thegravity center of the pressed area is sensed and the unit assumes
that only one button is pressed. Therfore, do not operate the HG
series by pressing more than one button simultaneously.
• Use the product within the environmental limits given in the catalog
and manual. Use of the product in high-temperature or high-humidity
environments, or in locations where it is exposed to condensation,
corrosive gas or large shock loads, can create the risk of electricalshock or fire.
• The HG series is designed for use in pollution degree 2. Use the HG
series in environments of pollution degree 2. (based on the IEC606641 rating)

HG3G
HG2G
HG1G

SAPEN01A_HG_November 2022

L-111

• Install the HG series according to the instructions in the User’s
Manual. Improper installation will result in falling, failure, electricalshock, fire hazard, or malfunction of the HG series.
• Use a power supply of the rated value. Using a incorrect power supply
may cause fire.
• The HG series uses “PS2 of EN61131” as DC power supply. (based on
the IEC / EN61131 rating)• When exporting the HG series to Europe, use an EN60127 (IEC60127)
approved fuse on the power line outside the HG series.
• When exporting the HG series to Europe, use an EU-approved circuit
protector.
• The touch panel of the HG series is made of glass, and will break if
exposed to excessive shock. Be careful when handling the HG series.
• Do not press or scratch the touch panel and protection sheet with ahard object such as a tool.
• Do not install the HG series in areas subject to strong ultraviolet rays,
as ultraviolet rays may impair the quality of the LCD.
• Note that small black and bright dots may show up on LCD Screen:
this is not a failure or malfunction.
• The backlight life is not guaranteed and refers to the time until thebrightness reduces by half after use at 25°C. The actual life depends
on operating environments and conditions.
• Protection degree refers to the front of the surface after mounting.
Although the protection structure satisfies various testing conditions,operation is not guaranteed under certain environments. IP66F/IP67F
oilproof structure satisfies oilproof test conditions. Conditions arelisted in the appendix of Japanese Industrial Standard JIS C 0920.
Operation is not guaranteed when using oil for a long period of timeor oil that does not satisfy standards. Please test/check before use.
• Do not attempt to disassemble, repair or modify the HG series. Thiscan create the risk of fire or elecrical shock.
• When using HG2G-5T and HG1G, to satisfy specifcations forunnecessary radiation, attach a ferrite core to the power andcommunication cable connected to the main unit.

HG Series Operator Interface
Operator Interfaces
APEM
Switches &Pilot Lights
Control Boxes
Emergency
Stop Switches
Enabling
Switches
Safety Products
Explosion Proof
Terminal Blocks
Relays & Sockets
Circuit
Protectors
Power Supplies
LED Illumination
Controllers
Operator
Interfaces
Sensors
AUTO-ID

Programmable
Operator Interfaces
Periphery
Equipment

HG5G
HG4G
HG3G
HG2G
HG1G

L-112

Ordering Terms and Conditions
Thank you for using IDEC Products.
By purchasing products listed in our catalogs, datasheets, and the like (hereinafter referred to as “Catalogs”) you agree to be bound by these terms and conditions. Please readand agree to the terms and conditions before placing your order.

1. Notes on contents of Catalogs

3. Inspections(1) Rated values, performance values, and specification values of IDEC products
listed in this Catalog are values acquired under respective conditions in
independent testing, and do not guarantee values gained in combined
conditions.
Also, durability varies depending on the usage environment and usage
conditions.
(2) Reference data and reference values listed in Catalogs are for reference
purposes only, and do not guarantee that the product will always operate
appropriately in that range.
(3) The specifications / appearance and accessories of IDEC products listed in
Catalogs are subject to change or termination of sales without notice, for
improvement or other reasons.
(4) The content of Catalogs is subject to change without notice.

2. Note on applications(1) If using IDEC products in combination with other products, confirm theapplicable laws / regulations and standards.
Also, confirm that IDEC products are compatible with your systems, machines,
devices, and the like by using under the actual conditions. IDEC shall bear no
liability whatsoever regarding the compatibility with IDEC products.
(2) The usage examples and application examples listed in Catalogs are forreference purposes only. Therefore, when introducing a product, confirm theperformance and safety of the instruments, devices, and the like before use.
Furthermore, regarding these examples, IDEC does not grant license to use
IDEC products to you, and IDEC offers no warranties regarding the ownershipof intellectual property rights or non-infringement upon the intellectual
property rights of third parties.
(3) When using IDEC products, be cautious when implementing the following.
i. Use of IDEC products with sufficient allowance for rating and 		
performanceii.	Safety design, including redundant design and malfunction prevention
design that prevents other danger and damage even in the event that an
IDEC product failsiii.	Wiring and installation that ensures the IDEC product used in yoursystem, machine, device, or the like can perform and function according
to its specifications(4) Continuing to use an IDEC product even after the performance has
deteriorated can result in abnormal heat, smoke, fires, and the like due toinsulation deterioration or the like. Perform periodic maintenance for IDEC
products and the systems, machines, devices, and the like in which they areused.
(5) IDEC products are developed and manufactured as general-purpose products
for general industrial products. They are not intended for use in the following
applications, and in the event that you use an IDEC product for theseapplications, unless otherwise agreed upon between you and IDEC, IDEC shallprovide no guarantees whatsoever regarding IDEC products.
i.	Use in applications that require a high degree of safety, including nuclear
power control equipment, transportation equipment (railroads / airplanes/ ships / vehicles / vehicle instruments, etc.), equipment for use in outerspace, elevating equipment, medical instruments, safety devices, or
any other equipment, instruments, or the like that could endanger life or
human healthii.	Use in applications that require a high degree of reliability, such asprovision systems for gas / waterworks / electricity, etc., systems that
operate continuously for 24 hours, and settlement systems
iii.	Use in applications where the product may be handled or used deviatingfrom the specifications or conditions / environment listed in the Catalogs,
such as equipment used outdoors or applications in environments
subject to chemical pollution or electromagnetic interference
If you would like to use IDEC products in the above applications, be sure
to consult with an IDEC sales representative.

Head Office
USA
EMEA

We ask that you implement inspections for IDEC products you purchase without
delay, as well as thoroughly keep in mind management/maintenance regarding
handling of the product before and during the inspection.

4. Warranty(1) Warranty period
The warranty period for IDEC products shall be one (1) year after purchase ordelivery to the specified location. However, this shall not apply in cases where
there is a different specification in the Catalogs or there is another agreementin place between you and IDEC.
(2) Warranty scope
Should a failure occur in an IDEC product during the above warranty period
for reasons attributable to IDEC, then IDEC shall replace or repair that
product, free of charge, at the purchase location / delivery location of the
product, or an IDEC service base. However, failures caused by the following
reasons shall be deemed outside the scope of this warranty.
i. The product was handled or used deviating from the conditions / 		environment listed in the Catalogs
ii. The failure was caused by reasons other than an IDEC productiii. Modification or repair was performed by a party other than IDEC
iv. The failure was caused by a software program of a party other than 		IDEC
v. The product was used outside of its original purposevi.	Replacement of maintenance parts, installation of accessories, or the like
was not performed properly in accordance with the user’s manual and
Catalogs
vii. The failure could not have been predicted with the scientific and 		technical standards at the time when the product was shipped from 		
IDEC
viii.	The failure was due to other causes not attributable to IDEC (including
cases of force majeure such as natural disasters and other disasters)
Furthermore, the warranty described here refers to a warranty on the IDEC
product as a unit, and damages induced by the failure of an IDEC product are
excluded from this warranty.

5. Limitation of liability
The warranty listed in this Agreement is the full and complete warranty for IDEC
products, and IDEC shall bear no liability whatsoever regarding special damages,
indirect damages, incidental damages, or passive damages that occurred due to an
IDEC product.

6. Service scope
The prices of IDEC products do not include the cost of services, such as dispatching
technicians. Therefore, separate fees are required in the following cases.
(1) Instructions for installation / adjustment and accompaniment at test operation(including creating application software and testing operation, etc.)(2) Maintenance inspections, adjustments, and repairs(3) Technical instructions and technical training(4) Product tests or inspections specified by you
The above content assumes transactions and usage within your region. Please
consult with an IDEC sales representative regarding transactions and usage outsideof your region. Also, IDEC provides no guarantees whatsoever regarding IDEC
products sold outside your region.

www.idec.com

6-64, Nishi-Miyahara-2-Chome, Yodogawa-ku, Osaka 532-0004, JapanIDEC Corporation
APEM SAS

Singapore
ThailandIndia

IDEC Izumi Asia Pte. Ltd.
IDEC Asia (Thailand) Co., Ltd.
IDEC Controls India Private Ltd.

Specifications and other descriptions in this brochure are subject to change without notice.
2022 IDEC Corporation, All Rights Reserved.

China
TaiwanIDEC (Shanghai) Corporation
IDEC Izumi (H.K.) Co., Ltd.
IDEC Taiwan CorporationJapan

IDEC Corporation