Gas Detection

Sensepoint XCL
Fixed Gas Detector
Sensepoint XCL is a fixed point gas leak detector that is designed to meetthe needs of commercial and light industrial applications. With over 50years experience in gas leak detection, Honeywell offers a flexible rangeof highly-reliable sensing devices to meet those needs.
• Quicker installation• Rapid configuration• Simple to operate• Straightforward to maintain
Honeywell innovation enables customers to pair the gas detector with
their mobile phone, and then use an app to perform many tasks relatedto installation, commissioning and maintenance.

Flexible Output Options
Sensepoint XCL is available with either mA loop analog output orModbus RTU with the option for relays on both. The result is a flexible
solution that can easily be incorporated into legacy systems as well as
new installations.

Visual Integration

Faster Installation

Sensepoint XCL is designed with the needs ofbuilding architects in mind. Clean aesthetics
and a choice of colors mean that the detector
is ideal for public spaces like lobbies and retail
environments.

Everything you need for installation is in the box, including simple drilling
templates.

Typical Applications

Easy Control and Maintenance
Sensepoint XCL's smartphone interface makes for much faster
calibration, configuration and bump tests. Inspecting the status andsettings of individual Sensepoint XCL detectors is simple. Use themobile app to:• Read gas concentrations in real-time• Reconfigure settings• Check unit histories

Automated Reporting
Increase the efficiency of your operations and reduce administration
time. The app and Sensepoint XCL provides easy access to diagnostic
information and generates calibration reports at the touch of a screen.

Compatible System Controller• Kitchens and food processing• Manufacturing facilities and factories• Hospitals• Retail sites• Transportation and parking• Laboratories• Hotel and leisure• Apartments, accommodation blocks andcondominiums

Accessories• Calibration cap / flow housing• Duct mount kit for round or flat profile ducts

Touchpoint Plus is the perfect complement to Sensepoint XCL, providing
an intuitive, easy to operate gas detection solution to meet the needs ofyour business.

F E AT U R E S & B E N E F I T S• Choose from a range
of mA or Modbus
output versions forflexible system design
to meet thecustomers
requirements.
• Selectable source orsink current foranalog output
enables one detector
to be suitable for bothsystem
configurations.

• Optional relay output
for external control
systems or alarming
devices enables easy
integration and localindication.
• The ingress
protection of IP65
allows units to be
mounted in wash
down areas.

• Multi-color visualindicator to show
status makes it easier
to know the detector
status immediatelyand identify detectorsthat require attention
or are warning ofdanger.

• Gassing port foreasier bump test ofunits installed ininaccessible
locations. No need topurchase a separate
accessory and thus
saves money.

• Manage the detector
without making aphysical connection.
Remove the need forphysical access tohard-to-reachdevices.
• Simplified
maintenance withfamiliar smartphone
technology saves
money and time.

Sensepoint XCL Technical Specifications
PHYSICAL PROPERTIESCONNECTIONDIMENSIONSTYPE

WEIGHT
CASING MATERIAL
INGRESS PROTECTION RATING
LIFETIME

113 x 113 x 59 mm( 4.4 x 4.4 x 2.3 in )500 g (1.1 lb)
Polycarbonate (charcoal or white)
IP65, Type 4 (in accordance withNEMA 250)
10 years (excludes sensor)

USER INTERFACEVISUAL INDICATORAVAILABLE SENSORSFLAMMABLE, TOXIC GASES ANDOXYGEN RANGES• Combustible: 0 to 100 % LEL (factorycalibrated to Methane)• O₂: 0 to 25% vol• CO: 300 ppm (adjustable between 50and 1000 ppm)
• H₂: 1000 ppm• H₂S Low Range: 50 ppm (adjustablebetween 10 and 50 ppm)
• H₂S High Range: 100 ppm (adjustablebetween 50 and 200 ppm)
• NO₂: 20 ppm (adjustable between5 and 50 ppm)
• NH₃: 200 ppm (adjustable between50 and 200 ppm)
• CO2 (ppm range): 5,000 ppm(adjustable between 1,000 and 5,000ppm)• CO2 (% vol range): 5.0% vol(adjustable between 1.0 and 5.0%vol)

WIRELESS INTERFACENOMINAL AC INPUT VOLTAGE
MAXIMUM INRUSH CURRENTANALOG OUTPUTRELAY OUTPUT−20 to 50°C (−4 to 122 °F) 0 to 30°C

STORAGE TEMPERATURE(32 to 86 °F)

HUMIDITY

15 to 90% RH (non-condensing)
90 to 110 kPa

ATMOSPHERIC PRESSURE
APPROVALSELECTRICAL SAFETYRADIOOTHER§OUTPUT
DIGITAL OUTPUT

OPERATING TEMPERATURE

EMC

24 V DC†
24 V AC‡, 50/60 Hz
850 mAMODBUS VERSIONSRELAY VERSIONS

0 to 22 mA
Modbus RTU
2 relays rated at 24 V DC / 240 V AC, 5 A< 1.2 W (toxic), < 1.7 W (flammable and CO2)
< 0.7 W (toxic), < 1.2 W (flammable and CO2)
Additional 0.6 W total† mA versions: 11 to 32 VDC, Modbus versions: 9 to 32 VDC‡ All versions: 20 to 27 VAC

For more information

Asia Pacific, India

www.honeywellanalytics.com

Honeywell Analytics Asia PacificNorth Asia Tel: +82 (0) 2 6909 0300
South East Asia Tel: +65 6580 3662
India Tel: +91 124 4752700
China Tel: +86 10 5885 8788-3000

Europe, Middle East, AfricaLife Safety Distribution GmbH
Tel: 00800 333 222 44 (Freephone number)
Tel: +41 44 943 4380 (Alternative number)
Middle East Tel: +971 4 450 5800 (Fixed gas detection)
Middle East Tel: +971 4 450 5852 (Portable gasdetection)

Americas
Honeywell Analytics Distribution Inc.
Tel: +1 847 955 8200
Toll free: +1 800 538 0363
RAE Systems by Honeywell
Phone: 408.952.8200
Toll Free: 1.888.723.4800

EN/UL/IEC61010-1
CSA-C22.2 No. 61010-1-12
EN 50270
RED, FCCUL2075 (CO and CH4), AS 1668.2

LED behavior in normal condition can be changed by the user: solid green, green confidence
flash or off.

MAXIMUM POWER CONSUMPTIONmA VERSIONS

Multi-colour LED light ring
• Green: normal§• Flashing red: Alarm• Flashing green and yellow: Warning• Flashing yellow: Fault• Solid yellow: Inhibited• Flashing blue: Bluetooth pairing inprogress• Solid blue: Bluetooth connection
establishedBluetooth 4.0 (Bluetooth Low Energy).
Dedicated mobile app, enabling wirelessconfiguration and maintenance.
Connect up to 10 m away (mobiledevice dependent). Use a compatible
smartphone or other mobile device
running Android 4.3 or above.

OPERATING ENVIRONMENTPOWER SUPPLYNOMINAL DC INPUT VOLTAGE

Pluggable rising clamp style, 0.5 to
1.5 mm2, 20 to 16 AWG.

www.honeywell.com
DS_01178 | Rev. 01 | 05/2018© 2018 Honeywell International Inc.