Prototocol Implementation Conformance Statement

PICS
TROVIS 6610
Automation Station
Model 6610-0002
Software Version
SAMSON BACstack V2.0

TROVIS 6610

SAMSON AG
MESS- UND REGELTECHNIK
Weismüllerstraße 360314 Frankfurt am Main
Germany
http://www.samson.de
2014-08-26

EB 6610 - 09

Table of Contents

Table of Contents
DOCUMENT REVISION ............................................................................................................. 3
1.
BACnet Protocol Implementation Conformance Statement (PICS) ........................................... 4
1.1.
Product Description .....................................................................................................................5
1.2.
BACnet standardized device profile (Annex L) ............................................................................5
1.3.
BACnet interoperability building blocks supported (Annex K) .....................................................6
1.3.1. Data Sharing BIBBs .................................................................................................................... 6
1.3.2. Alarm and event management BIBBs ........................................................................................ 6
1.3.3. Sheduling BIBBs ......................................................................................................................... 6
1.3.4. Trending BIBBs ........................................................................................................................... 6
1.3.5. Device management BIBBs ........................................................................................................ 7
1.3.6. Network management BIBBs ..................................................................................................... 7
1.4.
Segmentation capability.............................................................................................................. 7
1.5.
Standard object types supported ................................................................................................ 8
1.5.1. Analog Input ................................................................................................................................ 9
1.5.2. Analog Output ........................................................................................................................... 10
1.5.3. Analog Value ............................................................................................................................ 11
1.5.4. Binary Input ............................................................................................................................... 12
1.5.5. Binary Output ............................................................................................................................ 13
1.5.6. Binary Value ............................................................................................................................. 14
1.5.7. Calendar ................................................................................................................................... 15
1.5.8. Device ....................................................................................................................................... 15
1.5.9. Event Enrollment ...................................................................................................................... 17
1.5.10. File ............................................................................................................................................ 17
1.5.11. Loop .......................................................................................................................................... 18
1.5.12. Multistate Input ......................................................................................................................... 20
1.5.13. Multistate Output ....................................................................................................................... 21
1.5.14. Multistate Value ........................................................................................................................ 22
1.5.15. Notification Class ...................................................................................................................... 23
1.5.16. Pulse Converter ........................................................................................................................ 24
1.5.17. Schedule ................................................................................................................................... 25
1.5.18. Trendlog .................................................................................................................................... 26
1.6.
Data Link Layer Options ........................................................................................................... 27
1.7.
Device Adress Binding.............................................................................................................. 27
1.8.
Network Options ....................................................................................................................... 27
1.9.
Character Sets Supported ........................................................................................................ 27

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

2

BACnet Protocol Implementation Conformance Statement (PICS)

DOCUMENT REVISION
Version

Date

Author Revision Information

0.1
1.0
1.1

2007-04-19
2007-09-25
2007-09-27

gkr
gkr
gkr

1.2

2008-02-25

gkr

1.3

2008-03-06

big

1.4

2008-04-07

gkr

1.5

2009-02-19

gkr

1.6

2011-02-22

gkr

EB 6610 - 9

Start
Event Enrollment / Event Type / only readable
Puls Converter / Update_Time / only readable
Binary Value / Minimum_Off _Time / not supported
Binary Value / Minimum_On _Time / not supported
Binary Input / Polarity writable
Binary Output / Polarity writable
All objects / Object_Name writable
Analog Output / Relinquish_Default / only readable
Analog Output / High_Limit supported
Binary Output / Relinquish_Default only readable
Multistate Output / Relinquish_Default only readable
Schedule / List_Of_Obj._Prop._References writable
Trendlog / Notification_Threshold writable
Object File / Line Record_Count removed
All Objects / Property Profile_Name removed
SAMSON BACstack v 1.3
Analog Value / Out_Of_Service / writable
Analog Value / Reliability / writable
Binary Value / Out_Of_Service / writable
Binary Value / Reliability / writable
Binary Value / Change _Of_State_Count / writable
Binary Value / Elapsed_Active_Time / writable
Multistate Value / Out_Of_Service / writable
Multistate Value / Reliability / writable
SAMSON BACstack v 1.6
Multistate Value / complement Priority_Array
Multistate Value / complement Relinguish_Default
Firmware Revision / complement
BACnet Protocol Revision / complement
Device /VT_Classes_Supported removed
Active_VT_Sessions removed
List_Of_Session_Keys removed
Max_Master removed
Max_Info_Frames removed
Slave_Proxy_Enable removed
Man_Slave_Addr_Binding removed
Auto_Slave_Discovery removed
Slave_ Address_Binding removed

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

3

BACnet Protocol Implementation Conformance Statement (PICS)

1.7

2013-06-11

gkr

Supplements AMEV/Certification BACnet
Standard 12 (DIN EN ISO 16484-5:2007)

1.8

2013-09-02

gkr

Multistate Value
Number_Of_States added

1.9

2013-09-17

gkr

Trendlog
Logging_Type added
Allign_Intervals addedInterval_Offset added

2.0

2014-08-26

gkr

Binary Value
Time_Delay writable

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

4

BACnet Protocol Implementation Conformance Statement (PICS)

1. BACnet Protocol Implementation Conformance Statement (PICS)
Date:
Vendor Name:

2013-09-17
SAMSON AG (BACnet Vendor ID 51)

Product Name:TROVIS 6610 Automation Station

Product Model Number:

6610-0002

Application Software Version:
Firmware Revision:
BACnet Protocol Revision:

2.0
2.0 (SAMSON BACstack 2.0)
BACnet Standard 135-2010 Rev 12

1.1.

Product Description

Autonomous automation station for control and monitoring purposes

1.2.

BACnet standardized device profile (Annex L)

BACnet Operator Workstation (B-OWS)
BACnet Advanced Operator Workstation (B-AWS)
BACnet Operator Display (B-OD)
BACnet Building Controller (B-BC)
BACnet Advanced Application Controller (B-AAC)
BACnet Application Specific Controller (B-ASC)
BACnet Smart Sensor (B-SS)
BACnet Smart Actuator (B-SA)

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

5

BACnet Protocol Implementation Conformance Statement (PICS)

1.3.

BACnet interoperability building blocks supported (Annex K)

1.3.1.

Data Sharing BIBBs

Data Sharing ReadProperty-A
Data Sharing ReadProperty-B
Data Sharing ReadProperty-Multiple-A
Data Sharing ReadProperty-Multiple-B
Data Sharing WriteProperty-A
Data Sharing WriteProperty-B
Data Sharing WriteProperty-Multiple-B
Data Sharing COV-A
Data Sharing COV-B
Data Sharing COVP-A
Data Sharing COVP-B
Data Sharing COV - Unsolicited-A
Data Sharing COV - Unsolicited-B
1.3.2.

DS-RP-A
DS-RP-B
DS-RPM-A
DS-RPM-B
DS-WP-A
DS-WP-B
DS-WPM-B
DS-COV-A
DS-COV-B
DS-COVP-A
DS-COVP-B
DS-COVU-A
DS-COVU-B

Alarm and event management BIBBs

Alarm and Event - Notification-Internal-B
Alarm and Event - Notification-External-B
Alarm and Event - Acknowledge-B
Alarm and Event - AlarmSummary-B
Alarm and Event - EnrollmentSummary-B
Alarm and Event - Information-B
1.3.3.

AE-N-I-B
AE-N-E-B
AE-ACK-B
AE-ASUM-B
AE-ESUM-B
AE-INFO-B

Sheduling BIBBs

Scheduling - Internal-B
Scheduling - External-B
1.3.4.

SCHED-I-B
SCHED-E-B

Trending BIBBs

Trending - Viewing and Modifying Trends-Internal-B
Tending – Viewing and Modifying Trends-External-B
Trending - Automated-Trend-Retrieval-B

EB 6610 - 9

T-VMT-I-B
T-VMT-E-B
T-ATR-B

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

6

BACnet Protocol Implementation Conformance Statement (PICS)

1.3.5.

Device management BIBBs

Device Management - Dynamic Device Binding-A
Device Management - Dynamic Device Binding-B
Device Management - Dynamic Object Binding-B
Device Management - Device Communication Control
Device Management -TimeSynchronization-A
Device Management -TimeSynchronization-B
Device Management - UTCTimeSynchronization-A
Device Management - UTCTimeSynchronization-B
Device Management - Automatic Time Synchronization-A
Device Management - ReinitializeDevice-B
Device Management - Backup and Restore-B
Device Management – Restart-A
Device Management - Restart-B
Device Management - List Manipulation-B
Device Management - Object Creation and Deletion-B

1.3.6.

Network management BIBBs

Network Management - ConnectionEstablishment-A
1.4.

DM-DDB-A
DM-DDB-B
DM-DOB-B
DM-DCC-B
DM-TS-A
DM-TS-B
DM-UTC-A
DM-UTC-B
DM-ATS-A
DM-RD-B
DM-BR-B
DM-R-A
DM-R-B
DM-LM-B
DM-OCD-B

NM-CE-A

Segmentation capability

Able to transmit segmented messages Window size : 16
Able to to receive segmented messages Window size : 16

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

7

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.

Standard object types supported

ObjectAccumulator
Analog Input
Analog Output
Analog Value
Averaging
Binary Input
Binary Output
Binary ValueCalendarCommandDeviceEvent Enrollment(Event Log)
File
(Global Group)
Group
Life Safety Point
Life Safety Zone
Loop
Multistate Input
Multistate Output
Multistate Value
Notification Class
Programm
Pulse Converter
Schedule
Trendlog(Trendlog Multiple)

EB 6610 - 9

Supported

CreateDeleteE72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

8

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.1.

Analog Input

Optional properties
Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Typ
Status_Flags
Event_State
Reliability
Out_Of_Service
Update_Interval
Units
Min_Pres_Value
Max_Pres_Value
Resolution
COV_Increment
Time_Delay
Notification_Class
High_Limit
Low_Limit
Deadband
Limit_Enable
Event_Enable
Acked_Transition
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions*** These properties are writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

9

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.2.

Analog Output

Optional properties
Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Type
Status_Flags
Event_State
Reliability
Out_Of_Service
Units
Min_Pres_Value
Max_Pres_Value
Resolution
Priority_Array
Relinquish_Default
COV_Increment
Time_Delay
Notification_Class
High_Limit
Low_Limit
Deadband
Limit_Enable
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions** This property is writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

10

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.3.

Analog Value

Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Status_Flags
Event_State
Reliability
Out_Of_Service
Units
Priority_Array
Relinquish_Default
COV_Increment
Time_Delay
Notification_Class
High_Limit
Low_Limit
Deadband
Limit_Enable
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

*
**
***

supported

Writable properties

roperty range restrictions

*

**

***
***

This property is writable when “parameter”
This property is writable when Out_Of_Service is TRUE
These properties are commandable with FB BAC-A

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

11

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.4.

Binary Input

Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Type
Status_Flags
Event_State
Reliability
Out_Of_Service
Polarity
Inactive_Text
Active_Text
Change_Of_State_Time
Change_Of_State_Count
T_Of_State_Count_Reset
Elapsed_Active_Time
T_Of_Active_Time_Reset
Time_Delay
Notification_Class
Alarm_Value
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions*** These properties are writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

12

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.5.

Binary Output

Optional properties

supported

Writable properties

Property range restrictions

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Type
Status_Flags
Event_State
Reliability
Out_Of_Service
Polarity
Inactive_Text
Active_Text
Change_Of_State_Time
Change_Of_State_Count
T_Of_State_Count_Reset
Elapsed_Active_Time
T_Of_Active_Time_Reset
Minimum_Off_Time
Minimum_On_Time
Priority_Array
Relinquish_Default
Time_Delay
Notification_Class
Feedback_Value
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

13

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.6.

Binary Value

Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Status_Flags
Event_State
Reliability
Out_Of_Service
Inactive_Text
Active_Text
Change_Of_State_Time
Change_Of_State_Count
T_Of_State_Count_Reset
Elapsed_Active_Time
T_Of_Active_Time_Reset
Minimum_Off_Time
Minimum_On_Time
Priority_Array
Relinquish_Default
Time_Delay
Notification_Class
Alarm_Value
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

*
**
***

supported

Writable properties

Property range restrictions

*

**

***
***
***
***

This property is writable when “parameter”
This property is writable when Out_Of_Service is TRUE
These properties are commandable with FB BAC-B

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

14

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.7.

Calendar

Optional properties

supported

Writable properties

Property range restrictions

supported

Writable properties

Property range restrictions

Object_Identifier
Object_Name
Object_Type
Description
Present_Value
Date_List

1.5.8.

DeviceOptional properties

Object_Identifier
Object_Name
Object_Type
System_Status
Vendor_Name
Vendor_Identifier
Model_Name
Firmware_Revision
App_Software_Version
Location
Description
Protocol_Version
Protocol_Revision
Prot_Services_Supported
Prot_Obj_Types_Supp
Object_List
Max_APDU_Length_Acc
Segmentation_Supported
Max_Segments_Accepted
Local_Time
Local_Date
UTC_Offset
Daylight_Savings_Status
APDU_Segment_Timeout
APDU_Timeout
Nu_Of_APDU_Retries
Time_Synch_Intervall

EB 6610 - 9****

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

15

BACnet Protocol Implementation Conformance Statement (PICS)

T_Synch_Recipients
UTC_Time_Synch_Recipients
Align_Intervals
Interval_Offset
Device_Address_Binding
Database_Revision
Configuration_Files
Last_Restore_Time
Backup_Failure_Timeout
Backup_Preperation_Time
Restore_Preparation_Time
Restore_Completion_Time
Active_COV_Subscriptions
Restart_Notification_Recipients

****
****
****
****

**** This property is writable when device is Time_MasterEB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

16

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.9.

Event Enrollment

Optional properties

supported

Writable properties

Property range restrictions

supported

Writable properties

Property range restrictions

Object_Identifier
Object_Name
Object_Type
Description
Event_Type
Notify_Type
Event_Parameters
Obj_Property_Reference
Event_State
Event_Enable
Acked_Transitions
Notification_Class
Event_Time_Stamps
Event_Message_Texts

1.5.10. File
Optional properties

Object_Identifier
Object_Name
Object_Type
Description
File_Type
File_Size
Modification_Date
Archive
Read_Only
File_Access_Method

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

17

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.11. Loop
Optional properties

supported

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Status_Flag
Event_State
Reliability
Out_Of_Service
Update_Interval
Output_Units
Manipulated_Variable_Reference
Controlled_Variable_Refenrence
Controlled_Variable_ValueControlled_Variable_Units
Setpoint_Reference
Setpoint
Action
Proportional_Constant
Proportional_Constant_Units
Integral_ConstantIntegral_Constant_Units
Derivative_Constant
Derivative_Constant_Units
Bias
Maximum_Output
Minimum_Output
Prioritity_For_Writing
COV_Increment
Time_Delay
Notification_Class
Error_Limit

EB 6610 - 9

Writable properties

Property range restrictions

*

**
**
***
***
****
****

*****
******************

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

18

BACnet Protocol Implementation Conformance Statement (PICS)

Optional properties

Deadband
Event_Enable
ACK_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts
Profile_Name

supported

Writable properties

Property range restrictions**************************************

These properties are writable when Out_Of_Service is TRUE**

If one of these optional properties is present, then both of these properties shall be present***

If one of these optional properties is present, then both of these properties shall be present****

If one of these optional properties is present, then both of these properties shall be present***** This property is required if the object supports COV reporting****** These properties are required if the object supports intrinsic reporting******* This property, if present, is required to be read only

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

19

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.12. Multistate Input
Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Type
Status_Flags
Event_State
Reliability
Out_Of_Service
Number_Of_States
State_Text
Time_Delay
Notification_Class
Alarm_Values
Fault_Values
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions*** These properties are writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

20

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.13. Multistate Output
Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Device_Type
Status_Flags
Event_State
Reliability
Out_Of_Service
Number_Of_States
State_Text
Priority_Array
Relinquish_Default
Time_Delay
Notification_Class
Feedback_Value
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions** This property is writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

21

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.14. Multistate Value
Optional properties

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Status_Flags
Event_State
Reliability
Out_Of_Service
Number_Of_States
Update_Interval
State_Text
Priority_Array
Relinquish_Default
Time_Delay
Notification_Class
Alarm_Values
Fault_Values
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

*
**
***

supported

Writable properties

Property range restrictions

*

**

***
***

This property is writable when “parameter”
This property is writable when Out_Of_Service is TRUE
These properties are commandable with FB BAC-M

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

22

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.15. Notification Class
Optional properties

supported

Writable properties

Property range restrictions

Object_Identifier
Object_Name
Object_Type
Description
Notification_Class
Priority
Ack_Required
Recipient_List

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

23

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.16. Pulse Converter
Optional properties

Object_Identifier
Object_Name
Object_Type
Description
Present_Value
Input_Reference
Status_Flags
Event_State
Reliability
Out_Of_Service
Units
Scale_Factor
Adjust_ValueCount
Update_Time
Count_Change_Time
Count_Before_Change
COV_Increment
COV_Period
Notification_Class
Time_Delay
High_Limit
Low_Limit
Deadband
Limit_Enable
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

supported

Writable properties

Property range restrictions*** These properties are writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

24

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.17. Schedule
Optional properties

supported

Object_Identifier
Object_Name
Object_Type
Present_Value
Description
Effective_Period
Weekly_Schedule
Exception_Schedule
Schedule_Default
List_Of_Obj._Prop._References
Priority_For_Writing
Status_Flags
Reliability
Out_Of_Service

Writable properties

Property range restrictions*** These properties are writable when Out_Of_Service is TRUE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

25

BACnet Protocol Implementation Conformance Statement (PICS)

1.5.18. Trendlog
Optional properties

supported

Writable properties

Object_Identifier
Object_Name
Object_Type
Description
Log_Enable
Start_Time
Stop_Time
Log_DeviceObjectProperty
Log_Interval
COV_Resubscription_Interval
Client_COV_Increment
Stop_When_Full
Buffer_Size
Log_Buffer
Record_Count
Logging_Type
Align_Intervals
Interval_Offset
Trigger
Status_Flags
Reliability
Total_Record_Count
Notification_Threshold
Records_Since_Notification
Last_Notify_Record
Event_State
Notification_Class
Event_Enable
Acked_Transitions
Notify_Type
Event_Time_Stamps
Event_Message_Texts

Property range restrictions** This property is writable when Log_Enable is FALSE

EB 6610 - 9

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

26

BACnet Protocol Implementation Conformance Statement (PICS)

1.6.

Data Link Layer Options

BACnet IP, (Annex J)
BACnet IP, (Annex J), Foreign Device
ISO 8802-3, Ethernet (Clause 7)
ANSI/ATA 878.1, 2.5 Mb. ARCNET (Clause 8)
ANSI/ATA 878.1, RS-485 ARCNET (Clause 8)
MS/TP master (Clause 9), baud rate(s):MS/TP slave (Clause 9), baud rate(s):Point-To-Point, EIA 232 (Clause 10), baud rate(s): 115200 bit/s
Point-To-Point, modem, (Clause 10), baud rate(s): max. Modem
LonTalk, (Clause 11), medium:
Other:

1.7.

Device Adress Binding

Is static device binding supported?
1.8.

Yes

No

Network Options

Router, Clause 6, BACnet IP / BACnet PTP)
Annex H, BACnet Tunneling Router over IP
BACnet/IP Broadcast Management Device (BBMD)
Does the BBMD support registrations by foreign devices?
(Max. list foreign devices = 128)
Does the BBMD support network address translation)?

1.9.

Yes

No

Yes

No

Character Sets Supported

Indicating support for multiple character sets does not imply that they can all be supported
simultaneously.
ISO 10646 (UTF-8)
IBM / Microsoft DBCS
ISO 8859-1

EB 6610 - 9

ISO 10646 (UCS-2)
ISO 10646 (UCS-4)
JIS C 6226

E72 / gkr · TROVIS 6610 – V2.0 / 2014-08-26

27