Flame Detection

FSL100 Series Flame Detectors
UV, UV/IR, IR3

UV, UV/IR, IR3 Flame Detectors
The FSL100 Series of flame detectors from Honeywell delivers robust, fast, andreliable detection of flaming fires in a wide range of applications.

The range consists of UV, UV/IR and IR3 flame detectors.
All utilize sophisticated sensing and signal analysis todetect fires quickly while also rejecting false alarms.
The FSL100 may be small and lightweight foreasy installation but it is designed to work intough indoor/outdoor environments, as wellas potentially explosive atmospheres.

With a large field of view it candetect a range of different typesof fire including hydrocarbon
and non-hydrocarbon sources.
Available in UV, UV/IR and 3IR wehave your application covered.

Suitable for Many Applications• UV, UV/IR and IR3 available• Hydrocarbon and non-hydrocarbon sources• Use in potentially explosive atmospheres• Indoor and outdoor operation• High visibility red or discrete white models available

Great Performance• Approved to EN54-10 and FM3260 flame
detector standards• Comprehensive automatic self test
•Remote manual self test option

Fast & Reliable• High speed sensors and microprocessor• Sophisticated analysis algorithms• Continuous health monitoring• False alarm rejection

Reduced Life Cost
• Long life elements• Pressure compensation to avoid contamination• 2 year warranty• Buy with confidence

Ease of Installation and Use• Relay and mA outputs as standard• Lightweight GRP housing• Pre-formed knockouts• Optional swivel mounting bracket• Long range test lamp available

FSL100-UV• Suitable for indoor applications; forexample fume hoods and hydrogenstorage areas• Effective solution for materials burningwith low temperatures, e.g. Sulphur• Alarms to fires from heavy hydrocarbons (wood,paper, petroleum, etc.), light hydrocarbons(methanol, methane, etc.), and hydrogen• Good resistance against theinfluences of:- Direct and reflected sunlight- Artificial light, such as fluorescenttubes and glass covered halogen lamps

FSL100-UV/IR• Analysis of the flame flicker-frequency
for improved false alarm rejection• Dual sensing methodology enables
a wide range of hydrocarbon andnon-hydrocarbon fires to beeffectively detected• Good resistance against the influences of:- Direct and reflected sunlight- Artificial light, such as fluorescent tubes
and glass covered halogen lamps- Arcs and electric discharges (staticor from e.g. electric motors)- The radiation from electric welding
provided that the electric welding takes
place at a distance more than 10 feet fromthe flame detector (a welding rod
contains organic compounds which
may produce a small flame)FSL100-IR3• Analysis of the flame flicker frequency
for improved false alarm rejection• Particularly suited to liquidhydrocarbon and dirty fires• Affected less by window
contamination or smoky fires• Good resistance against theinfluences of:- Direct and reflected sunlight- Artificial light, such as fluorescenttubes and glass covered halogen
lamps- Arcs and electric discharges (staticor from e.g. electric motors)- The radiation from electric welding
provided that the electric welding
takes place at a distance morethan 10 feet from the flame
detector (a welding rod contains
organic compounds which may produce a small flame)• Especially suitable fires that emitlarge amounts of smoke

APPLICATIONSAPPLICATION*

UVAircraft hangarsAtriums
Battery storage rooms / data communication✓BiogasCar, bus, tram and train parking
Clean rooms: semi-conductor, pharmaceutical, & hospital operating rooms✓

CNG filling/refilling for buses (public transportation)
Cold storage✓✓

Diesel engine rooms
Electric power transformers
Engine test cells/rooms
Fume hoods
Gas cabinets
Gas/Gasoline engine rooms
Heating rooms for chemicals
Indoor chemical, fuel, and solvent storage
Indoor hydrocarbon storage and processing
Indoor hydrogen storage and processingLaboratories✓✓✓
✓
✓
✓✓
✓
✓
✓✓
✓

Loading and unloading terminals: truck, rail, & marine
Monitoring of machinery✓

Oil and Gas pipe line and pumping stations
Outdoor chemical, fuel, paint, and solvent storage
Outdoor hydrogen storage and processing

UV/IRIR3

✓
✓
✓✓
✓
✓
✓✓
✓✓

✓✓
✓✓

✓
✓✓
✓✓
✓
✓✓
✓✓
✓
✓✓
✓
✓✓
✓✓
✓✓
✓✓
✓
✓
✓✓

Paint spray booths
Radio amplifier rooms / Isolators for antennas
Recycling and waste processing plants
Suitable ✓ Recommended ✓✓*Please contact your regional sales representative to discuss your application✓✓

✓

✓✓
✓✓
✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓✓

GENERAL SPECIFICATIONSPECIFICATIONS: FSL100 SERIES FLAME DETECTORSFSL100 Flame Detector types

FSL100-UV, FSL100-UVIR and FSL100-IR3; Choice of red or white housings

Range

110 ft /35 m (IR3), 25 m/80 ft (UV, UV/IR) alarming within 10 seconds to a 1 ft2(0.1 m2)n-heptane fireCone of vision

90˚minimum horizontal and verticalPower

10-28 VDC (12-24 VDC nominal)
Continuous green: normal operation
Continuous yellow: fault
Flashing yellow: Fault and guide to repeat self-test after a self-test failure
Continuous red: alarm

Local LEDs

Current output

Standard available 4–20 mA (stepped, sinking, non-isolated)•0 mA power fault / microprocessor fault•
2 mA optical fault•
4 mA normal operation•>20 mA alarm

Relay output:- Alarm relay- Fault relay

De-energized during normal operation, no alarm, SPDT, 30 VDC – 2 A, 60 W max. Energised during normal operation, no fault,SPDT, 30 VDC – 2 A, 60 W max.

Cable gland & terminals

Cable entry M20 clearance. Supplied with gland suitable for cable diameter from 0.2” (5.5mm) to 0.5”(13mm). Terminals
suitable for 0.5mm2 (20AWG) to 1.5mm2 (15AWG) wireStart up times<10 sec

Alarm response time

8 to 30 sec

Alarm output settings

Selectable LEDs and relays latching/non-latching; factory setting: latching

Automatic & manual Self-Test

Automatic Sensor Test (built in Self-Test) and manual Self-Test

Operating current normal

25 mA at 24 VDC

Current in alarm, at 24 VDC±75 mA at 24 VDC

Connections to:•••End of line and alarm resistor

To be adjusted to the fire control panel; free terminals are dedicated to the resistors
Note: the alarm and EOL resistor must be rated 2 W min. each and the total power dissipation of both alarm and EOL resistor
should not exceed 2 W

Housing

Glass Reinforced Polyester (GRP), Non-incendive. UV resistant, Self-Extinguishing V–0 (UL-94)

Swivel Mount

PA66, UV resistant; Stainless Steel fixings; 280 g (0.62 lb)

Pressure compensating element

PCE (Pressure Compensating Element) avoids moisture build-up in the detector housing due to changes in ambient air-pressure

Dimensions

4.9 x 3.15 x 2.25 in (125 x 80 x 57 mm)

Weight1.05 lb (465 g)

Ingress protection

IP65

Temperature, operating–40 ˚F to +158 ˚F (–40 ˚C to +70 ˚C)Temperature, ambient ATEX and FM class 3611

–13 ˚F to +158 ˚F (–25 ˚C to +70 ˚C)Fire control panels using end of line (EOL) and alarm resistors (current increase)
Devices that operate via relay switched outputs
PLCs with 4–20 mA inputs

Honeywell Analytics Gas Detection
Honeywell Analytics is able to provide gas detection solutions to meet the requirements of all applications and industries.
Contact us in the following ways:

HEADQUARTERS
Europe, Middle East, AfricaLife Safety Distribution GmbH
Javastrasse 28604 Hegnau
Switzerland
Tel: +41 (0)44 943 4300
Fax: +41 (0)44 943 4398
gasdetection@honeywell.com
Customer Service:
Tel: 00800 333 222 44 (Freephone number)
Tel: +41 44 943 4380 (Alternative number)
Fax: 00800 333 222 55
Middle East Tel: +971 4 450 5800 (Fixed Gas Detection)
Middle East Tel: +971 4 450 5852 (Portable Gas Detection)

Americas
Honeywell Analytics Distribution Inc.
405 Barclay Blvd.
Lincolnshire, IL 60069
USA
Tel: +1 847 955 8200
Toll free: +1 800 538 0363
Fax: +1 847 955 8210
detectgas@honeywell.com
RAE Systems by Honeywell
Phone: 408.952.8200
Toll Free: 1.888.723.4800
Fax: 408.952.8480

TECHNICAL SUPPORTEMEA: HAexpert@honeywell.com
US: ha.us.service@honeywell.com
AP: ha.ap.service@honeywell.com

www.honeywellanalytics.com
www.raesystems.com
Please Note:
While every effort has been made to ensure accuracy in this publication, noresponsibility can be accepted for errors or omissions. Data may change, as wellas legislation, and you are strongly advised to obtain copies of the most recently
issued regulations, standards, and guidelines. This publication is not intended toform the basis of a contract.
13475_H_FSL100_DS01155_V2_AMER
11/16© 2016 Honeywell Analytics

Asia Pacific
Honeywell Analytics Asia Pacific
7F SangAm IT Tower,
434, Worldcupbuk-ro, Mapo-gu,
Seoul 03922,
Korea
Tel: +82 (0) 2 6909 0300
Fax: +82 (0) 2 2025 0328
India Tel: +91 124 4752700
China Tel: +86 10 5885 8788 3000
analytics.ap@honeywell.com