JIMGA-T-S/25/20

液化炭酸ガス取扱テキスト

本改訂版は、日本産業・医療ガス協会として編集していた JIMGA-T-S/25/15（2015 年 5 月改訂版）を見直し 2020 年 9 月改訂版としたものです。

保証免責についての注意書き
JIMGA の全ての技術的な刊行物は、それらの発行日時点での妥当な信頼できる情報源による最新の技術情報及び経験を基にしている。
JIMGA はメンバーがそれらの刊行物を参照若しくは使用することを強く推奨するが、それらは最終的に純粋に自主的判断によるものであり、拘束するものではない。
JIMGA は、JIMGA の刊行物に含まれる情報若しくは示唆のメンバーによるそれらの遵守実行或いは非実行、誤った解釈、適切または不適切な使用等に関していかなる管理もできない。
よって、JIMGA はその技術的な刊行物に含まれる情報若しくは示唆の参照或いは使用による信頼性若しくは妥当性および結果の保証をするものではなく、またそれらに関していかなる責任も負うものではない。
JIMGA の刊行物は定期的見直しにより内容が変更されるので最新版を参照のこと。

本文書の著作権は JIMGA にあります。複製には JIMGA の許可が必要です。

一般社団法人
日本産業・医療ガス協会

JIMGA (JAPAN INDUSTRIAL and MEDICAL GASES ASSOCIATION)〒105-0012 東京都港区芝大門 2 丁目 8 番 13 号
TEL：03-5425-2255 FAX：03-5425-2256
INTERNET： https://www.jimga.or.jp

JIMGA-T-S/25/20

目
第１章

次

炭酸ガスの性質

1.1

一 般 的 性 質 ·························································································· 11.2

各 種 定 数 ····························································································· 1

1.3

化 学 的 性 質 ·························································································· 2

1.4

環 境 影 響 ····························································································· 3

1.5

熱 力 学 的 性質········································································ 31.6

炭 酸 ガ ス の 状 態 ··················································································· 4

1.7

人 体 に 及 ぼ す 影 響················································································ 7

1.8

静 電 気 の 発生········································································ 9

1.9

液 封 に つ いて········································································ 9

第２章
2.1

2.2

2.3

第３章
3.1

3.2

炭酸ガスの製造法、用途及び品質
製 造 法 ······························································································· 10
2.1.1

製 造 の 歴史 ································································· 102.1.2

炭 酸 ガ ス 発 生 源 （ 産 業 用 原 料 ） ················································11

2.1.3

一 般 的 製 造 工 程 ········································································11

用途 ··························································································· 122.2.1

液 化 炭 酸 ガ ス の 用 途 ································································ 12

2.2.2

固 体 炭 酸 ガ ス （ ド ラ イ ア イ ス ） の 用 途····································· 13

品

質 ··························································································· 14

2.3.1

JIS 規格····································································· 14

2.3.2

食 品 添 加 物 規 格 ・ 医 薬 品 規 格 ·················································· 14

容器による貯蔵、消費継 目 な し 容器······································································· 15
造·················································································· 15

3.1.1

構

3.1.2

種 類 と 充 塡 量 ··········································································· 15

3.1.3

法 規 制·················································································· 16

3.1.4

容 器 の 形式 ································································· 17

3.1.5

容 器 弁·················································································· 18

3.1.6

容 器 内 液 化 炭 酸 ガ ス の 状 態 ······················································ 19

可 搬 式 超 低 温 容 器 （ LGC） ······················································ 20
3.2.1

構

造·················································································· 20iJIMGA-T-S/25/20

3.3

3.2.2

種 類 と 充 塡 量 ··········································································· 20

3.2.3

法 規 制·················································································· 20

3.2.4

容 器 の 形式 ································································· 21

消費 ··························································································· 22

3.3.1

サ イ フ ォ ン 管 の な い 継 目 な し 容 器 か ら 気 体 で 取 り 出 す 場 合······ 22

3.3.2

サイフォン管付き継目なし容器または
超 低 温 容 器 か ら 液 体 で 取 り 出 す 場 合 ··························· 22

3.3.3

3.4

取 扱 い 上 の 注 意 事 項 ································································ 22

送 ガ ス 蒸 発 器 （ 気 化 器 ） の 取 扱 い ····················································· 23
3.4.1

気 化 器 の 概 要 ··········································································· 23

3.4.2

取 扱 い 上 の 注 意 事 項 ································································ 24

3.5

減 圧 弁 ··························································································· 24

3.6

貯

蔵 ··························································································· 25

3.6.1

貯 蔵 の 方法 ································································· 25

3.6.2

異 常 時 の 応 急 処 置 ···································································· 25

第４章

移

動

4.1

移 動 に 関 す る 法 規 制 ·········································································· 26

4.2

容 器 に よ る 移 動 ················································································· 26

4.3

第５章

4.2.1

点 検 整 備·················································································· 26

4.2.2

移 動 上 の 注 意 事 項 ···································································· 26

4.2.3

移 動 に お け る 異 常 時 の 応 急 処 置 ··············································· 27

タ ン ク ロ ー リ に よ る 移動 ························································ 27
4.3.1

点 検 整 備·················································································· 27

4.3.2

移 動 上 の 注 意 事 項 ···································································· 28

4.3.3

携 行 品·················································································· 28

4.3.4

異 常 時 の 応 急 処 置 ···································································· 29

貯槽による貯蔵、消費

5.1

貯 槽 に 対 す る 法 規 制 ·········································································· 30

5.2

貯 槽 の 維 持 管 理 ················································································· 30

5.3

貯 槽 の 型 式 及 び 機 能 ·········································································· 31

5.4

5.3.1

CE（真 空 断 熱 貯 槽 ） の 例 ························································ 31

5.3.2

一 般 断 熱 貯 槽 の 例 ···································································· 31

附 属 機 器 （ 代 表 的 な も の の 例 ） ························································· 31ⅱ

JIMGA-T-S/25/20

5.4.1

一 般 用 操 作 弁 ··········································································· 33

5.4.2

安 全 弁·················································································· 33

5.4.3

ブ リ ー ダ ー 弁 （ 自 動 放 出 弁 ） ·················································· 33

5.4.4

液 面 計·················································································· 35

5.4.5

圧 力 計·················································································· 35

5.4.6

加 圧 自 動 弁 ・ 加 圧 蒸 発 器 ························································· 36

5.4.7

送 り ガ ス 自 動 弁 ······································································· 37

5.4.8

安 全 弁 元 弁 （ 三 方 弁） ··················································· 38

5.4.9

液 面 計 元弁 ································································· 39

5.4.10

附 属 冷 凍機 ································································ 40

5.5

タ ン ク ロ ー リ よ り の 受 入 れ ································································ 41

5.6

貯 槽 の 取 扱 い 上 の 注 意 事 項 ································································ 42

5.7

異 常 時 の 処置······································································· 43

第 6章

5.7.1

圧 力 の 異常 ································································· 43

5.7.2

安 全 弁 の 作 動 ··········································································· 44

5.7.3

緊 急 時 の 処 置 ··········································································· 44

5.7.4

事 故 災 害 時 の 措 置 ···································································· 44

保安管理

6.1

保 安 管 理 体制······································································· 45

6.2

危 害 予 防 規程······································································· 45

6.3

保 安 管 理 ··························································································· 45

第７章

教育訓練

7.1

保 安 教 育 実 施 上 の 要 点 ······································································· 47

7.2

教 育 訓 練 の 記 録 ················································································· 47

第 8章
8.1

8.2

安全活動
事 故 統 計 ··························································································· 48
8.1.1

事 故 統 計 の 意 義 ······································································· 48

8.1.2

事 故 原 因 の 分 析 と 対策 ··················································· 48

8.1.3

事 故 再 発 の 防 止 ······································································· 49

ヒ ヤ リ ハ ッ ト 、 Ｋ Ｙ 活動 ························································ 49
8.2.1

ヒ ヤ リ ハ ッ ト 活 動 ···································································· 49

8.2.2

Ｋ Ｙ 活 動·················································································· 49

iii

JIMGA-T-S/25/20

資料1

低 温 用 金 属 材 料 ·········································································· 51

資料2

真空断熱法における真空度の影響とCE 使用 時 の 内 圧 変 動 ····································· 52

資料3

静 電 気 の 発 生 ············································································· 53

資料4

炭 酸 ガ ス の 水 に 対 す る 溶 解 度 ····················································· 54

資料5

炭 酸 ガ ス の 温 暖 化 防 止 等 の 対策 ········································· 55

資料6

炭 酸 ガ ス 製 造 の 歴史 ························································ 56

資料72018 年 炭 酸 ガ ス 関 連 事 故 情 報 ···················································· 59

資料

資料

8

9

7.1

高 圧 ガ ス 保 安 法 事 故 情報 ·········································· 59

7.2

炭 酸 ガ ス 関 連 事 故 情 報 ····················································· 59

7.3

事 故 事 例 [災害 ]2018 年度 炭 酸 ガ ス 関係 ····················· 60

高圧ガス災害事故統計と解析
8.1

高 圧 ガ ス 災 害 事 故 件 数 の 推 移··············································· 65

8.2

産 業 ガ ス 関 係 事 故 区分別災害事故件数の推移 ························ 65

8.3

災害事故の原因別分析 ··························································· 66

8.4

CE 設 備 の 個 別 事 例······························································ 67

ヒ ヤ リ ハ ッ ト 事 例 ······································································ 68

資料 10 用 語 解 説等 ················································································· 71

図 5.1

CE 設 備 系 統 図 （ 例 ） ························································· 73

図 5.2

一 般 断 熱 貯 槽 設 備 系 統 図 （ 例 ） ·········································· 74

図 5.3

特 例 措 置 CE 設 備 系 統 図 ····················································· 75※印 を 付 し た 用 語 は 、 資 料 10（ P.71） 用 語 解 説 を ご 参 照 く だ さ い 。

ⅳ

JIMGA-T-S/26/19

高圧ガス保安法の要点

本改訂手引は、液化炭酸ガスを取り扱う関係者の「手引書」として高圧ガス保安法の要点をまとめ、日本産業ガス協会として編集していた
JIMGA-T-S/26/15（2015 年 5 月改訂版）を見直し 2019 年 12 月改訂版としたものです。

保証免責についての注意書き
JIMGA の全ての技術的な刊行物は、それらの発行日時点での妥当な信頼できる情報源による最新の技術情報及び経験を基にしている。
JIMGA はメンバーがそれらの刊行物を参照若しくは使用することを強く推奨するが、それらは最終的に純粋に自主的判断によるものであり、拘束するものではない。
JIMGA は、JIMGA の刊行物に含まれる情報若しくは示唆のメンバーによるそれらの遵守実行或いは非実行、誤った解釈、適切または不適切な使用等に関していかなる管理もできない。
よって、JIMGA はその技術的な刊行物に含まれる情報若しくは示唆の参照或いは使用による信頼性若しくは妥当性および結果の保証をするものではなく、またそれらに関していかなる責任も負うものではない。
JIMGA の刊行物は定期的見直しにより内容が変更されるので最新版を参照のこと。

本文書の著作権は JIMGA にあります。複製には JIMGA の許可が必要です。

一般社団法人
日本産業・医療ガス協会

JIMGA (JAPAN INDUSTRIAL and MEDICAL GASES ASSOCIATION)〒105-0012 東京都港区芝大門 2 丁目 8 番 13 号
TEL：03-5425-2255 FAX：03-5425-2256
INTERNET：https://www.jimga.or.jp

JIMGA-T-S/26/19

高圧ガス保安法の要点(液化炭酸ガス)

2019 年 12 月 改訂

目次

高圧ガス保安法の要点 ······································································ 1
付録
Ⅰ. 高圧ガスの製造をしようとするとき又は製造施設等を変更するときに必要な手続 ··········· 付 1
1. 都道府県知事等の許可 ··························································· 付 1(1)設置に対する立地条件 ························································· 付 2(2)申請手続 ····································································· 付 2
2. 完成検査 ······································································· 付 4(1)完成検査申請 ································································· 付 4(2)完成検査 ····································································· 付 4
3. 届出書類等 ····································································· 付 4(1)危害予防規程の届出 ··························································· 付 4(2)保安教育計画書の制定 ························································· 付 4(3)保安統括者等届出又は保安監督者届出 ··········································· 付 6(4)高圧ガス製造開始届 ··························································· 付 64. 製造のための施設等の変更手続 ··················································· 付 6(1)変更許可 ····································································· 付 6(2)完成検査を要しない変更工事の範囲 ············································· 付 6(3)軽微変更届 ··································································· 付 8(4)その他 ······································································· 付 8
5. 高圧ガス・石油コンビナート事故対応要領 ········································· 付 8

Ⅱ. 自主保安のための措置 ······························································ 付 121. 危害予防規程 ·································································· 付 122. 製造施設及び製造の方法の技術上の基準 ·········································· 付 12(1)設備管理の記録 ······························································ 付 12(2)運転管理 ···································································· 付 12(3)移動式製造設備(ローリ)受入充塡日誌 ·········································· 付 12(4)警戒標の確認 ································································ 付 12(5)保安物件に対する保安距離の確認 ·············································· 付 12(6)容器置場の保安上必要な措置 ·················································· 付 12
3. 保安教育の実施 ································································ 付 12
4. 都道府県知事等又は保安協会等の保安検査········································· 付 14
5. 定期自主検査 ·································································· 付 14
6. 危険時の措置 ·································································· 付 14

資料一 1

高圧ガス保安法の体系 ························································ 付 16

JIMGA-T-S/38/21

原料炭酸ガス製造フロー概説

本基準は、1998 年に旧炭酸ガス工業会・原料委員会で作成された「原料炭酸ガス製造フロー概説」を 2015 年 5 月に改訂し、JIMGA 基準として制定された。今回、最新の実績統計値の採用や各項目の見直しを行い改訂したものである。

保証免責についての注意書き
JIMGA の全ての技術的な刊行物は、それらの発行日時点での妥当な信頼できる情報源による最新の技術情報及び経験を基にしている。
JIMGA はメンバーがそれらの刊行物を参照若しくは使用することを強く推奨するが、それらは最終的に純粋に自主的判断によるものであり、拘束するものではない。
JIMGA は、JIMGA の刊行物に含まれる情報若しくは示唆のメンバーによるそれらの遵守実行或いは非実行、誤った解釈、適切または不適切な使用等に関していかなる管理もできない。
よって、JIMGA はその技術的な刊行物に含まれる情報若しくは示唆の参照或いは使用による信頼性若しくは妥当性および結果の保証をするものではなく、またそれらに関していかなる責任も負うものではない。
JIMGA の刊行物は定期的見直しにより内容が変更されるので最新版を参照のこと。

本文書の著作権は JIMGA にあります。複製には JIMGA の許可が必要です。

一般社団法人
日本産業・医療ガス協会

JIMGA (JAPAN INDUSTRIAL and MEDICAL GASES ASSOCIATION)〒105-0012 東京都港区芝大門 2 丁目 8 番 13 号
TEL：03-5425-2255 FAX：03-5425-2256
INTERNET：https://www.jiｍga.or.jp

目

１．総説

次

.........................................................................

１..............................

１................................................

３............................

４....................................................

５......................................................

５........................................................

５

１－１

産業設備分類別「原料炭酸ガス」出荷実績推移

１－２

液化炭酸ガス「生産拠点」

１－３

液化炭酸ガス

用途別需要比率・地区別需要比率

２．原料炭酸ガス製造フロー概説
２－１

アンモニアプラント（１）石油系原料

ＩＣＩ－ナフサスチームリフォーミング法（１例）（２）石炭系原料.......................................................

７

石炭ガス化法（１例）
２－２

石油精製プラント........................................................

９

ＩＣＩ－スチームリフォーミング法（１例）
２－３

製鉄プラント.........................................................

２－４エチレンオキサイドプラント

１１.............................................. １３

酸素酸化法（１例）
２－５

廃プラガス化法

２－６

燃焼排ガス

.......................................................... １５.............................................................. １７３．液化炭酸ガス製造フロー概説.................................................... １９４．原料炭酸ガス分離回収プロセス.................................................. ２０

４－１

化学吸収法

.............................................................. ２１

４－２

物理吸着法（ＰＳＡ）.................................................... ２２

JIMGA-T-S/24/21

液化炭酸ガスＣＥ設置事業所・ローリ運行事業所
関 係 基 準
本基準は 1967 年に旧炭酸ガス工業会で制定された危害予防規程規範の付属関係基準の見直し及び 2004 年 3 月に施行された省令改正を含んで、JIMGA
炭酸ガス分科会および技術保安 WG におけるタスクフォースにおいて検討し、JIMGA 基準として制定したものである。

保証免責についての注意書き
JIMGA の全ての技術的な刊行物は、それらの発行日時点での妥当な信頼できる情報源
による最新の技術情報及び経験を基にしている。
JIMGA はメンバーがそれらの刊行物を参照若しくは使用することを強く推奨するが、それらは最終的に純粋に自主的判断によるものであり、拘束するものではない。
JIMGA は、JIMGA の刊行物に含まれる情報若しくは示唆のメンバーによるそれらの遵守実行或いは非実行、誤った解釈、適切または不適切な使用等に関していかなる管理もできない。
よって、JIMGA はその技術的な刊行物に含まれる情報若しくは示唆の参照或いは使用による信頼性若しくは妥当性および結果の保証をするものではなく、またそれらに関していかなる責任も負うものではない。
JIMGA の刊行物は定期的見直しにより内容が変更されるので最新版を参照のこと。

本文書の著作権は JIMGA にあります。複製には JIMGA の許可が必要です。

一般社団法人
日本産業・医療ガス協会

JIMGA (JAPAN INDUSTRIAL and MEDICAL GASES ASSOCIATION)〒105-0012 東京都港区芝大門 2 丁目 8 番 13 号
TEL：03-5425-2255 FAX：03-5425-2256
INTERNET：https://www.jiｍga.or.jp

目

第１部

次

ＣＥ設置事業所関係基準

1-1

ＣＥ保安基準
１． 総
則 .......................................................................................................................
１．１ 目
的 ................................................................................................................

１................................................................................................................

１............................................................................................................

１.........................................................................................................

２
２

１．２

適

用

１．３

用語の定義

２．ＣＥの技術上の基準

１

２．１

設備の位置

............................................................................................................

２．２

設備の構造

............................................................................................................

４

２．３

そ

............................................................................................................

６.....................................................................................................

７

特例措置ＣＥの設置場所 .......................................................................................
３．ローリの停車位置等の基準 ..............................................................................................

７..................................................................................................

ローリの停車位置
４．ＣＥの保安管理 ................................................................................................................

８............................................................................................................

８...........................................................................................

８

４．３

日常点検及び月例点検
定期自主検査 .........................................................................................................

４．４

保安検査

................................................................................................................

９.........................................................................................................

９

２．４

の

他

ＣＥの設置場所

２．５

３．１

４．１
４．２

４．５

保安監督者

設備台帳管理８８９５．保全工事に関する管理 ..................................................................................................... ９
６．書類等の保管 ................................................................................................................ １０
付表１

ＣＥ設備台帳1-2

ＣＥ運転基準
１． 総
則 ....................................................................................................................
１．１ 目
的 .............................................................................................................

１３.............................................................................................................

１３

１．２

適

１．３

用語の定義

.........................................................................................................

１３

２．ＣＥの系統と機能.........................................................................................................

１３........................................................................................

ＣＥの系統と弁の名称
機能 .............................................................................................................

１３...............................................................................................

１４................................................................................................................

１５

４．１

運転開始（長期間（３日以上）停止後の運転開始） .............................................

１５

４．２

１６

４．３

正常運転 ................................................................................................................
運転停止（長時間（３日以上）運転を停止するとき） .........................................

４．４

一時運転停止及び運転開始 ....................................................................................

１６

２．１
２．２

用

１３

３．ＣＥ運転の技術上の基準

４．ＣＥ運転要領

1

１４

１６

短期間（３日未満）運転停止及び運転開始 ...........................................................
運転停止中の作業 ..................................................................................................

４．５
４．６

１６
１７

巡回点検 ................................................................................................................
５．ローリからの受入充塡作業 ...........................................................................................

２１........................................................................................

２１

５．２

充塡作業員及び立合人
充塡準備・点検 ..................................................................................................

５．３

充塡作業

.............................................................................................................

２２........................................................................................

２３

４．７

５．１

５．４

充塡作業修了後の処置
点検記録 .............................................................................................................

５．５

１７

２１

２３

６．運転作業上の一般的注意事項 ...........................................................................................
６．１ ドライアイス生成防止 ........................................................................................

２３
２３

６．２

凍傷防止

.............................................................................................................

２３

６．３

液封防止

.............................................................................................................

２３

酸欠防止

.............................................................................................................

２３

許容濃度 .............................................................................................................
７．故障時の処置 ....................................................................................................................

２３
２４....................................................................................................................

２４

気化器 .................................................................................................................
８．応急処置 ...........................................................................................................................

２５
２５....................................................................................................................

２５

６．４
６．５

７．１

貯槽

７．２
８．１

漏洩

８．２

圧力の上昇

.........................................................................................................

２５

８．３

圧力の降下

.........................................................................................................

２６

８．４

安全弁の作動......................................................................................................

２６

８．５

弁・配管等の破損...............................................................................................

２７

気化器からの液噴出 ...........................................................................................
９．緊急時の措置 ....................................................................................................................

２７
２７

９．１

通報連絡

.............................................................................................................

２７

９．２

２７

９．３

応急処置 .............................................................................................................
退避 ....................................................................................................................

９．４...........................................................................................

緊急時の連絡の周知
事故災害の記録 ..................................................................................................

２７...........................................................................................................................

２８

８．６

９．５
１０．記録

２７
２７

１０．１

液化炭酸ガスＣＥ設備運転日誌
２８

１０．２

液化炭酸ガスＣＥ運転日誌（特例措置ＣＥ） ................................................
液化炭酸ガス受入充塡日誌 .............................................................................

１１．ＣＥのヒヤリハット ..................................................................................................
１２．ＣＥの事故事例 .........................................................................................................

２８

表－１

液化炭酸ガス受入充塡日誌表－２－１

液化炭酸ガスＣＥ運転日誌

表－２－２

液化炭酸ガスＣＥ運転日誌（特例措置ＣＥ）

2

２８
２９

別図１－１

ＣＥ設備系統図

別図１－２

特例措置ＣＥ設備系統図

別図２

運転準備（長期間（３日以上）停止後の運転準備）

別図３

運転開始（長期間（３日以上）停止後の運転開始）

別図４

正常運転

別図５

運転停止（長期間（３日以上）停止する時）

別図６

一時運転停止及び運転開始

別図７

運転停止（短期間（３日未満）停止する時）

別図８

運転開始（短期間（３日未満）停止後、運転開始）

別図９

運転停止中の作業

別図 10

日常点検

別図 11

月例点検

第２部

ローリ運行事業所関係基準

2-1

ローリ取扱基準
１． 総
則 ....................................................................................................................
１．１ 目 的 ................................................................................................................

４５................................................................................................................

４５
４５

１．２

適

用

４５

１．３

用語の定義

.........................................................................................................

１．４

関連法規

.............................................................................................................

４５......................................................................................................

４５

２．１

車両の構造基準..................................................................................................

４５

２．２

搭載設備その他の技術上の基準 .........................................................................
搭載設備の系統 ..................................................................................................

４５........................................................................................................................

４８................................................................................

４８

３．２

運行開始及び終了時の点検受入作業 .............................................................................................................

３．３......................................................................................................

５０.........................................................................................................

５１

保安監督者

.........................................................................................................

５１

設備台帳

.............................................................................................................

５１

４．３

日常管理

.............................................................................................................

５１

４．４

５２

４．５

定期自主検査 ......................................................................................................
保安検査 .............................................................................................................

４．６.............................................................................................................

５２

５．保全工事に関する管理 ..................................................................................................
６．一般的注意事項 .............................................................................................................

５２....................................................................................

不活性ガスに対する注意
圧力に対する注意 ...............................................................................................

５２

低温に対する注意 ...............................................................................................
その他 .................................................................................................................

５３

２．ローリの構造と系統

２．３

３．作業基準３．１

送り出し作業

４．ローリの保安管理
４．１
４．２

６．１
６．２
６．３
６．４

保安教育

3

４８

４８

５２

５２
５２
５３

７．故障時の処理................................................................................................................

５３

８．異常時の処置................................................................................................................

５４

８．１

漏洩時の処置......................................................................................................

５４

８．２

火災時の処置 ......................................................................................................
通報連絡 .............................................................................................................

５４........................................................................................................................

５４.............................................................................................................

５４......................................................................................................

５４

事故災害記録 ......................................................................................................
10．書類の保管 ....................................................................................................................

５４

８．３
９．記

録

９．１
９．２

作業日誌

日常点検記録９．３

付図１

ローリ系統図（例）

付表１

ローリ設備台帳

付表２

作業日誌

付表３

搭載設備日常点検記録表

付表４

事故災害記録表

５４

５５

2-2

ローリ運行基準
１． 総
則 ....................................................................................................................
１．１ 目 的 ................................................................................................................

６１................................................................................................................

６１

１．２

適

１．３

用語の定義

.........................................................................................................

６１

１．４

関連法規 .............................................................................................................
行 ........................................................................................................................

６１
６２

２．２

注意書面(イエローカード) ................................................................................
仕業点検 .............................................................................................................

２．３................................................................................

６２

２．４

運行開始及び終了時の点検
安全運転 .............................................................................................................

２．５

禁.............................................................................................................

６３.........................................................................................................

６３..................................................................................................

６３

２．８

ガード下の通過
駐車 .............................................................................................................

２．９.........................................................................................................

６４...............................................................................................

緊急時の連絡通報
行 品 ....................................................................................................................

６４....................................................................................................................

６４.........................................................................................................

６４

２．運
２．１

２．６
２．７

２．10
３．携
３．１
３．２

用

６１

煙

踏切の通過

容器の保安

書類

６２
６２
６３

６３

６４

資材（例）
工具等 .................................................................................................................

６４

備........................................................................................................................

６５

４．１

車

体

.............................................................................................................

６５

４．２

搭載設備

.............................................................................................................

６５..................................................................................................

６５..................................................................................................

６５

３．３
４．整

５．運行中の異常時の措置
５．１

漏えい時の措置

4

５．２
５．３

容器内圧異常時の処置 ........................................................................................
火災時の処置 ......................................................................................................

６．ローリのヒヤリハット ..................................................................................................
７．ローリの事故事例 .........................................................................................................
表－１

ローリ検査項目及び検査期間

表－２

容器再検査期間

６５
６６
６７
６８

付属書 外ねじ式及び内ねじ式長軸玉形弁のねじはめ輪磨耗量測定方法（例）解説１ ..................................................................................................................................

解１

解説２

..................................................................................................................................

解３

解説３

..................................................................................................................................

解４

解説４

..................................................................................................................................

解５5