ORBIT 60 SERIES

Communication Gateway Module
Datasheet

Bently Nevada Machinery Condition Monitoring

137M0700 Rev. BDescription
The Communication Gateway Module (CGW) provides
information to external hosts including measurements,alarms, statuses, and system controls using standard
industrial protocols. The CGW is designed for integration withprocess control and other automation systems.
The Communication Gateway module occupies a single slot
and has two RJ-45 Ethernet ports supporting Modbus andEGD protocols.
The module OK LEDs indicate when the module is functioning
properly, and the LINK LED indicates when the module iscommunicating to the rest of the system.
The Comm Gateway Module includes two Ethernet ports
which provide TCP/IP communications capabilities. The
supported industrial protocols are:ll

Modbus TCP/IP: Modbus over Ethernet is available forconnection to HMI’s, unit control systems, or other plant
automation equipment. The module can only beconfigured as a server and supports configurable
Modbus addresses within the 40000 address range.
Ethernet Global Data (EGD): EGD is a GE protocol usedon Mark VI and Mark Vie controllers and by GE
Programmable Automation Controllers and certain 3rdparty automation equipment. Version 3.04 andbackward compatibility with previous versions issupported.

ORBIT 60 SERIES Communication Gateway Module
Datasheet

137M0700 Rev. B

Communications Gateway
Communications Gateway (CGW)Power Consumption
Maximum

10.2 Watts

Typical

6.8 Watts

Data Communications
2 Ethernet ports utility or rear side

Independent Ethernet
ports 1000/100/10 Base-T
Auto-negotiation

Connector

RJ-45

Cable Length

100 meters (328 feet) max

Updated RateModbus

50 ms

EDG

20 ms

Environmental Limits
ChassisOperatingTemperature
Range(indoor useonly)

ModuleTemperature
Rating
Certification

LEDs
Module OK LED

Indicates when themodule is functioning
properlySystemCommunication
LEDIndicates when themodule is communicating
to the rest of the system

1 SlotTemperatures over50°C (122°F) require
forced air convection
with a minimum
airspeed of 0.5 m/s.
-30°C to +70°C(-22°F to 158°F)
When using aBridge module,
temperatures over
58°C (136°F) require
forced airconvection with aminimum airspeedof 0.5 m/s.
You must still meet
the Chassis
OperatingTemperature Range
defined above.

Physical Characteristics
Required RackSpace

3U Chassis:-30°C to +70°C(-22°F to 158°F)
6U Chassis:-30°C to +65°C(-22°F to 149°F)

Storage
Temperature
Range-40°C to +85°C(-40°F to 185°F)

Relative
Humidity

0% to 95% rH non-condensing
operating and storageVibration

Without Isolators:
0 g to 0.35 g @ 57-500 Hz
With Isolators:
0 g to 5 g @ 57-500 Hz

Shock

ORBIT 60 SERIES Communication Gateway Module
2/6
Datasheet2” Incline DropORBIT 60 SERIES Communication Gateway Module
Datasheet

Environmental Limits< 2000 m (6,562 ft)

AltitudeHigher altitudes are
possible but are site
specificapplications.
Contact BentlyNevada
support if you
require higher
altitudes.
PollutionDegree

Pollution Degree 2

Installation
Category

Category II

Verify that temperature ratings on thewiring cables match the operating
temperature range.

CAUTIONLOCATION TEMPERATURE
AND HUMIDITY
While the system has beentested and capable of achieving
the design life when operating inenvironments up to 70°C,
whenever operating any
electronics system in elevatedhumidity or temperatures
exceeding 40°C, adding
environmental controls
maximizes the operational life ofthe system.

ORBIT 60 SERIES Communication Gateway Module
3/6
Datasheet137M0700 Rev. B

ORBIT 60 SERIES Communication Gateway Module
Datasheet

Compliance and Certifications
FCC

137M0700 Rev. B*Maritime
ABS Rules for Condition of Classification,
Part 1l

This device complies with part 15 of theFCC Rules. Operation is subject to thefollowing two conditions:llThis device may not cause harmfulinterference.
This device must accept any
interference received, includinginterference that may cause
undesired operation.

EMC
European Community Directive:
EMC Directive 2014/30/EU
Standards:
EN 61000-6-2; Immunity for
Industrial Environments
EN 61000-6-4; Emissions forIndustrial Environments

Electrical SafetyEuropean Community Directive:
LV Directive 2014/35/EU
Standards:
EN 61010-1;
EN 61010-2-201;

RoHS
European Community Directive:
RoHS Directive 2011/65/EU

Cyber Security
Designed to meet IEC 62443-4-2

lSteel Vessels Rules
Offshore Units and Structures*Recorder Output module, Bridge
module, and 6U systems
approvals pending

Functional Safety
This component is non-interfering withthe safety system. The system SIL 2certification does not require thiscomponent be SIL certified.

Hazardous Area Approvals
For the detailed listing of country andproduct-specific approvals, refer tothe Approvals Quick Reference Guide(108M1756).
For additional technicaldocumentation, please log in to
bntechsupport.com and access theBently Nevada Media Library.

cNRTLusClass I, Zone 2: AEx/Ex ec nC IIC T4 Gc;
Class I, Zone 2: AEx/Ex nA nC IIC T4 Gc;
Class I, Division 2, Groups A, B, C, D T4;
Class I, Division 2, Groups A, B, C, D T4(N.I.);
T4 @ Ta= -30˚C to +70˚C (-22˚F to +158˚F)

ATEX/IECEx
II 3 G
Ex ec nC IIC T4 Gc
Ex nA nC IIC T4 Gc
T4 @ Ta= -30˚C to +70˚C (-22˚F to +158˚F)

ORBIT 60 SERIES Communication Gateway Module
4/6Datasheet

ORBIT 60 SERIES Communication Gateway Module
Datasheet

Ordering Information
For the detailed listing of country andproduct-specific approvals, refer tothe Approvals Quick Reference Guide(108M1756).
For additional technicaldocumentation, please log in to
bntechsupport.com and access theBently Nevada Media Library.

Communications Gateway Module
Ordering Option

Description

60R/CGW01-AAA-B • RJ-45 Ethernet Comm
Gateway
AAA – Hazardous Area Certifications
00

No Hazardous Area

01

CSA/NRTL/C (Class I,Div 2)

02

Multi (CSA, ATEX,IECEx)

XXXCountry SpecificApprovals

B – SIL Level
0No SIL

ORBIT 60 SERIES Communication Gateway Module
5/6Datasheet

137M0700 Rev. B

ORBIT 60 SERIES Communication Gateway Module
Datasheet

137M0700 Rev. B

Copyright 2024 Baker Hughes Company. All rights reserved.

Bently Nevada and Orbit Logo are registered trademarks of Bently Nevada, a Baker Hughes business, in the UnitedStates and other countries. The Baker Hughes logo is a trademark of Baker Hughes Company. All other product andcompany names are trademarks of their respective holders. Use of the trademarks does not imply any affiliation
with or endorsement by the respective holders.
Baker Hughes provides this information on an “as is” basis for general information purposes. Baker Hughes does notmake any representation as to the accuracy or completeness of the information and makes no warranties of any
kind, specific, implied or oral, to the fullest extent permissible by law, including those of merchantability and fitness
for a particular purpose or use. Baker Hughes hereby disclaims any and all liability for any direct, indirect,
consequential or special damages, claims for lost profits, or third party claims arising from the use of theinformation, whether a claim is asserted in contract, tort, or otherwise. Baker Hughes reserves the right to makechanges in specifications and features shown herein, or discontinue the product described at any time without
notice or obligation. Contact your Baker Hughes representative for the most current information.
The information contained in this document is the property of Baker Hughes and its affiliates; and is subject tochange without prior notice. It is being supplied as a service to our customers and may not be altered or its content
repackaged without the express written consent of Baker Hughes. This product or associated products may becovered by one or more patents. See Bently.com/legal.

1631 Bently Parkway South, Minden, Nevada USA 89423
Phone: 1.775.782.3611 (US) or Bently.com/support
Bently.com

6/6