SE series

SPEC. SHEET

Potentiometer Transmitter

Model:SE1P(with indication function)■ Model

SE1P - □ - □Socket
1: Finger-safe(For Y terminal)
2: For Ring terminal
Power supply
0: 100 to 240V AC
1: 24V AC/DC■ How to orderSpecify the model (e.g.) SE1P-1-0
Default value
Output4 to 20mA DC■ Performance■ Accessories (sold separately)
Communication cable for the console software: CMB-001■ Input specification
Potentiometer
Excitation: 100 to 10k
Reference voltage: 1.0V DC■ Output specification
When the output range lower limit is zero, (even if zeroadjustment results in a negative value), the output value
will not be negative.
DC current
Zero
Span
Allowable load
Output range
adjustment
adjustment
resistance
range
range
4 to 20mA DC
700 or less
-5 to 5%95 to 105%
0 to 20mA DC
700 or less0 to 5%95 to 105%
0 to 12mA DC
1.2k or less0 to 5%95 to 105%
0 to10mA DC
1.2k or less0 to 5%95 to 105%
1 to 5mA DC
2.4k or less
-5 to 5%95 to 105%
DC voltage
Output range

Allowable load
resistance

0 to 1V DC
0 to 5V DC1 to 5V DC
0 to 10V DC

100 or more
500 or more
500 or more
1k or more

Zeroadjustment
range
0 to 5%0 to 5%-5 to 5%0 to 5%

Spanadjustment
range
95 to 105%
95 to 105%
95 to 105%
95 to 105%

Accuracy (When ambient temperature is 23 ):Input: Within 0.1%
Output: Within 0.1%
Indication accuracy: Within input accuracy 1 digit
Input sampling period: 25ms, 125ms, 250ms (Selectable by keypad)
Response time: 65ms (typ.) (0→90%) (Input sampling period 25ms)
225ms (typ.) (0→90%) (Input sampling period 125ms)
425ms (typ.) (0→90%) (Input sampling period 250ms)(Selectable by keypad)
Temperature coefficient: 0.015%/ or lessInsulation resistance: 10M or more, at 500V DC(Input – Output – Power supply)
Dielectric strength: 2.0kV AC for 1 minute(Input – Output – Power supply)■ General structure
Case: Flame-resistant resin, Color: Light gray
Front panel: Membrane sheet
Setting: By the front keypad
Connector for console software: Only for CMB-001
Indication: Input display: 7-segment, Red LED display 4-digit
Character size 10x4.6mm (HxW)
Output display: 7-segment, Red LED display 4-digit
Character size 10x4.6mm (HxW)Power indicator: Green LED
CH1 indicator: Yellow LED
CH2 Indicator: Yellow LED

Console connector

SE1P■ Installation specifications■ Solderless terminal

Power supply: 100 to 240V AC 50/60Hz, 24V AC/DC 50/60Hz
Allowable voltage range: 85 to 264V AC, 20 to 28V AC/DCPower consumption: Approx. 6VA
Ambient temperature: -5 to 55
Ambient humidity: 35 to 85%RH (Non-condensing)
Mounting: DIN rail mounting
External dimensions: W30xH88xD108mm (including the socket)
Weight: Approx. 190g (including the socket)

Y typeRing type■ Circuit configuration and terminal arrangement■ Attached functions

Potentiometer

Auto-light function: Display brightness is controlled in accordancewith the surrounding area. Unnecessary brightness is reduced,
saving energy.
Power failure countermeasure: The data is backed up in nonvolatile IC memory..
Self diagnosis: The CPU is monitored by a watchdog timer, andwhen an abnormal status is found on the CPU, the unit isswitched to warm-up status with tuning all outputs off.

123CH1
input
circuit

Display/Setting
key circuit

Powercircuit

13+14-

Power
supplyInsulation circuit

4CPU
5CH1output
circuit9+Output

10-678■ Environmental specification

1112RoHS directive compliance■ External dimensions (Scale: mm)■ Settings
Function keys
(1) UP Key: Increases the numeric value.
(2) DOWN Key: Decrease the numeric value.
(3) MODE Key: Selects the setting mode.
(4) SUB-MODE Key: Turns the displays ON again when they
are in OFF status.
(The UP, DOWN or MODE Key also turns the displays ON again
when they are in OFF status.)■ Displays and indicators
Input display: Indicates the input value
Indication of -2000 or less (for DC input):
The minus (-) sign and input value light alternately.
Indication of 10000 or more:The lower 4 digits flash.
Under range: “” flashes on the Input display.
Over range: “” flashes on the Input display
Warm-up indication: For approx. 3sec. after the power to theinstrument is turned on, the input type of CH1
is indicated on the Input display, the input
type of CH2 is indicated on the Output
display.
Output display: Indicates output volume in percentage (%) form.
Power indicator: The green LED lights when the power to the
instrument is turned on.

SHINKO TECHNOS CO., LTD.

Tel: 81-72-727-6100

URL: http://www.shinko-technos.co.jp/e/ E-mail: overseas@shinko-technos.co.jp

20120106