SB series

SPEC. SHEET

Current Loop Supply

Model:

SBD

Features
Simple wiring using a plug-in socket
Compact
3-port insulation (Input-Output-Power)

Model
SBD––Input
01: 4 to 20mA DC
Output
01: 4 to 20mA DC
02: 0 to 20mA DC
03: 0 to 12mA DC
04: 0 to 10mA DC

05: 0 to 1V DC
06: 0 to 5V DC
07: 1 to 5V DC
08: 0 to 10V DC

Power supply
0: 100 to 240V AC
1: 24V DC

2-wire transmitter power supply
Output voltage : 24 3V DC (when load current is 20mA)
Ripple voltage : 200mV DC or less (when load current is20mA)
Max. load current: 25mA DC

How to orderSpecify a model.
(e.g.) SBD-0101-0

Performance

Input specifications

Accuracy
Response time

DC current: 4 to 20mA DC
Shunt resistor: 50 built-in

Output specifications
When the output range lower limit is zero, (even if zeroadjustment results in a negative value), output value will
not indicate a negative value.
DC current

Allowableloadresistance
4 to 20mA DC 600 or more
0 to 20mA DC 600 or more
0 to 12mA DC 1k or less0 to 10mA DC 1k or less
Output range

DC voltage

Allowableloadresistance
0 to 1V DC 100 or more
0 to 5V DC 500 or more
1 to 5V DC 500 or more
0 to 10V DC 1k or more

Output range

Zeroadjustment
range-2.5 to 2.5%
0 to 2.5%
0 to 2.5%
0 to 2.5%

Spanadjustment
range
97.5 to 102.5%
97.5 to 102.5%
97.5 to 102.5%
97.5 to 102.5%

Zeroadjustment
range
0 to 2.5%
0 to 2.5%-2.5 to 2.5%
0 to 2.5%

Spanadjustment
range
97.5 to 102.5%
97.5 to 102.5%
97.5 to 102.5%
97.5 to 102.5%: Within 0.2%
: 1 sec. (090%)(Average 0.5 sec)
Temperature coefficient: 0.015%/
Insulation resistance : 10M or more, at 500V DC(Input-Output-Power)Dielectric strength: 2.0kV AC for 1 minute(Input-Output-Power)
Note: Input terminals: 1, 2, 3 (Power supply for 2-wiretransmitter included)

SBD
Instrument specifications

Mounting method

Case: Flame resistant resin Color: Light gray
Front panel: Polycarbonate
Spring type plug: Polyamide Color: Green
Adjustment: By the front potentiometer
Zero adjustment : 2.5%
Span adjustment : 2.5%
Indication:Power indicator (PWR): Green
Lights when the power is turned on.
Flashes in 500ms cycles when an error has occurredin non-volatile IC memory.
Error indicator (ERR): Red
Flashes in 250ms cycles when input is 110% or more.
Flashes in 500ms cycles when input is -10% or less.
Output status selection: Selects Normal or Reverse withthe DIP switch.
No.1 OFF: Normal, ON: Reverse
Momentary power failure: 30msec.
Self diagnosis:
The CPU is monitored by a watchdog timer, and whenan abnormal status is found on the CPU, the unit
restarts with the reset action.
Power indicator
Error indicator

Zero adjustment
Span adjustment

Power supplyOutput: DIN rail mounting
Be sure to use fastening plates atboth ends of the unit after the unit
is mounted to the DIN rail.
External dimensions : 17.5 (W) x 75 (H) x 85 (D) mm

Environmental specification
RoHS directive complianceFerrulesMade by Phoenix Contact GMBH & CO.
Insulation sleeve attached
ModelConductor cross section
2AI0.25-6BU
0.2 – 0.25mm
2AI0.34-8TQ
0.25 – 0.34mm
2AI0.5-8WH
0.34 – 0.5mm
2AI0.75-8GY
0.5 – 0.75mm
2AI1-8RD
0.75 – 1.0mm
2AI1.5-8BK
1.0 – 1.5mm
2AI2.5-8BU
1.5 – 2.5mm
Crimping pliers
CRIMPFOX ZA3CRIMPFOX UD6Circuit configuration, terminal arrangement++-6+

5Output+

Input +
Power supply for
2-wire transmitter +7Powercircuit

Power supply-

4+

3-

2Output
circuit50

Input
circuit

Input-Power supply for
2-wire transmitter+CPU

24V DCPowercircuit1-

32-wiretransmitter

2+

150

DIP switch
Spring type plug

External dimensions (Scale: mm)

Installation specifications
Power supply• 100 to 240V AC 50/60Hz
Allowable voltage range: 85 to 264V AC
Power consumption: Approx. 3.5VA• 24V DC
Allowable voltage range: 20 to 28V DC
Power consumption: Approx. 3.5W
Ambient temperature : -5 to 55
Ambient humidity: 35 to 85%RH (non-condensing)
Weight: Approx. 80g

DIN rail

SHINKO TECHNOS CO., LTD.

Tel: +81-72-727-6100
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technos.co.jp

20100624