ESLONTM PLANT PIPE MATERIALSLARGE DIAMETER TS FITTINGSESLONTMLARGE DIAMETER TS FITTINGS
Suitable for pressurized pipes and drainage pipes at factories,
processing plants, and agricultural facilities.

PVC

Highly resistant to chemicals and corrosion.

HI-PVC

Compact size reduces construction costs.

HT（CPVC）■ Maximum Working Pressure

Maximum Working Pressure (MPa)■ Usage Temperature and Maximum Working Pressure
1.00.8HT FRP
reinforced piece

PVC・HI-PVC 0.75MPa● 0.75MPa at 20℃● FRPreinforced piece:
1.0MPa at 20℃

PVC・HI-PVC 0.6MPa0.20Material

PVC

HI-PVCHT（CPVC）

2000.75MPa

0.75MPa

0.6MPa250

0.75MPa

0.75MPa

0.6MPa300

0.6MPa0.6MPa0.6MPaSize● 0.6MPa at 20℃

0.60.4(Room Temperature)

Maximum
Working Pressure

PVC・HI-PVC FRP reinforced piece*All FRP reinforced pieces have a 1.0 MPa.

HT 0.6MPa

102030405060

Usage Temperature (℃)

708090℃

LARGE DIAMETER TS FITTINGS SPECIFICATIONS■ Socket Dimensions

Dd1td●200A〜300At●Reducing Blanch

Unit：㎜d1Size

Dd175A

10689.6

196100A134242150A

189

Size

Dd200A243

13.0 217.4 216.9

145

250A

300

14.5 268.6 268.1

175

300A

356

16.0 319.8 319.4

185288PVC
HT
HI-PVC*（CPVC）

d64

77

114.7

84102

166.0

132

146
Unit：㎜

Note: HT (C-PVC) 90°elbow is * dimension.

■ 90°Elbow

Unit：mm

H

Z200A
250A
300A

262
318355145
175185

PVCkg/unit

TS

HI

HT

6.6
10.8
15.5

TSL2H6K
TSL2F6K
TSL3H6K

HIL2H6K
HIL2F6K
HIL3H6K

HTL2H6K
HTL2F6K
HTL3H6K

HZ（*Dashed line shows 1.0MPa FRP specifications.

45Item No.

ReferenceweightSize）

FRP Reinforced Piece
TS

HIHT

FTSL2HFTSL2F
FTSL3HFHIL2HFHIL2F
FHIL3HFHTL2HFHTL2F
FHTL3HESLONTM PLANT PIPE MATERIALSLARGE DIAMETER TS FITTINGS■ 90°Bend

Unit：mm

Size
200A
250A
300A

H

Z

341428441

196253
256

R

Item No.

WeightPVC（kg/pc）

196242
242

7.6
14.4
20.3

FRP reinforced type

TSHI

HT

TSLL2H6TSLL2F6TSLL3H6HILL2H6HILL2F6HILL3H6HTLL2H6HTLL2F6HTLL3H6TSHIHTFTSLL2HFTSLL2FFTSLL3H

FHILL2H
FHILL2FFHILL3H

FHTLL2HFHTLL2F
FHTLL3H

HRZ゜90※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

■ 45°Elbow
H

Z

200A
250A
300A

205254280

607995Item No.

Weight
PVC
kg/pc

TS

HIHT

5.6
9.0
13.6

TS4L2H6TS4L2F6TS4L3H6HI4L2H6HI4L2F6HI4L3H6HT4L2H6HT4L2F6HT4L3H6（Size）

FRP reinforced type
TSHI

HT

FTS4L2H
FTS4L2F
FTS4L3H

FHI4L2H
FHI4L2F
FHI4L3H

FHT4L2H
FHT4L2F
FHT4L3HZ
H

45゜

Unit：mm※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

■ BushUnit：mmRL

Z

R

DWeight
PVC
kg/pc

250A×150A 344
300A×200A 374

3744242 267288 318

5.277.28

DSize

LZ（） TSTSRB2F2
TSRB3H2

Item No.
HIHT

HIRB2F2
HIRB3H2

HTRB2F2
HTRB3H2■ CouplingUnit：mm

L

Z

200A
250A
300A

300
384408103438Item No.

Weight
PVCkg/pc

TS

HI

HT

3.4
6.9
9.1

TSS2H6K
TSS2F6K
TSS3H6K

HIS2H6K
HIS2F6K
HIS3H6KHTS2H6KHTS2F6KHTS3H6K（Size）FRP reinforced type
TS

HIHT

FTSS2HFTSS2FFTSS3H

FHIS2HFHIS2F
FHIS3HFHTS2HFHTS2F
FHTS3H※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

ZL46

ESLONTM PLANT PIPE MATERIALSLARGE DIAMETER TS FITTINGS■ Reducing Coupling

Unit：mmSize

L

200A×150A※250A×150A
250A×200A※300A×150A※300A×200A
300A×250A

368557400605601435

Z

Item No.

WeightPVC（kg/pc） TS

91
250
80
288
271
75

TSS2H16TSS2F26
TSS2F16TSS3H36
TSS3H26
TSS3H163.9
12.1
6.1
35.1
16.4
9.1

HIHIS2H16HIS2F26HIS2F16HIS3H36HIS3H26HIS3H16HTFRP reinforced type
TSHIHTS2H16 FTSS2H1 FHIS2H1HTS2F26 FTSS2F2 FHIS2F2HTS2F16 FTSS2F1 FHIS2F1HTS3H36 FTSS3H3 FHIS3H3HTS3H26 FTSS3H2 FHIS3H2HTS3H16 FTSS3H1 FHIS3H1HTFHTS2H1FHTS2F2FHT2F1FHTS3H3FHTS3H2FHTS3H1※With Bushing
ZLZL●With Bushing※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

■ Tee

Unit：mmSizeHH2LZ

200A
250A
300A

267355410267355375533710820

122180225

Item No.

Weight
PVCkg/pc（） TSHIHT

FRP reinforced typeTS

TST2H6K HIT2H6K HTT2H6K FTST2H
TST2F6K HIT2F6K HTT2F6K FTST2F
TST3H6K HIT3H6K HTT3H6K FTST3H

HIHTFHIT2H
FHIT2FFHIT3H

FHTT2HFHTT2F
FHTT3H

H28.618.8
30.4

ZH

L

※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

■ Reducing Tee

Unit：mm

Z2
Z2

H2H2Size

ZL

ZH

H

L

●With Bushing

200A×75A
200A×100A
200A×150A
250A×75A
250A×100A※250A×150A
250A×200A
300A×75A
300A×100A※300A×150A※300A×200A
300A×250A※With Bushing※Dashed Shape for Fiber Reinforced 1.0MPa fitting.

47

H2 Z2Weight
PVCkg/pc

201 56 402 180 116
218 73 436 200 116
245 100 490 257 125
246 71 492 210 146
267 92 534 225 141
355 180 710 524 392
335 160 670 335 190
260 75 520 236 172
266 81 532 257 173
375 190 750 561 429
410 225 820 599 454
375 190 750 392 217

5.6
6.5
8.4
8.8
9.8
24.1
16.1
12.9
13.4
30.8
37.7
25.5

HZ

L

（Item No.

） TS
TST2H46
TST2H36
TST2H16
TST2F56
TST2F46
TST2F26
TST2F16
TST3H66TST3H56TST3H36TST3H26TST3H16HIHIT2H46HIT2H36HIT2H16HIT2F56HIT2F46HIT2F26HIT2F16HIT3H66HIT3H56HIT3H36HIT3H26HIT3H16HTFRP reinforced typeTSHTT2H46 FTST2H4HTT2H36 FTST2H3HTT2H16 FTST2H1HTT2F56 FTST2F5HTT2F46 FTST2F4HTT2F26 FTST2F2HTT2F16 FTST2F1HTT3H66 FTST3H6HTT3H56 FTST3H5HTT3H36 FTST3H3HTT3H26 FTST3H2HTT3H16 FTST3H1HIHTFHIT2H4FHIT2H3FHIT2H1FHIT2F5FHIT2F4FHIT2F2FHIT2F1FHIT3H6FHIT3H5FHIT3H3FHIT3H2FHIT3H1FHTT2H4FHTT2H3FHTT2H1FHTT2F5FHTT2F4FHTT2F2FHTT2F1FHTT3H6FHTT3H5FHTT3H3FHTT3H2FHTT3H1