3

Closing the Front CoverName & Function

74.5
39.3±0.2

1. Close the front cover.
(4) CommunicationConnector(1) Front Cover

2. Push the access symbol until it clicks to lock the front cover.
Front Cover

90.0

INSTRUCTION SHEET

100.0±0.2

B-1778(3)(2) LCD

FC6A Series
HMI module

Front Cover(5) Operation Buttons(10) HMI-Ethernet Port

(6) LINK LED(7) ACT LED(8) Ground terminal

Safety Precautions

Caution notices are used where inattention might cause personal injury or damage to equipment.

● Turn off the power to the MICROSmart before starting installation, removal, wiring, maintenance, orinspection on the MICROSmart.Failure to turn off the power may cause damage, electrical shocks orfire hazard.
● Emergency stop and interlocking circuits must be configured outside the MICROSmart. If such a circuit
is configured inside the MICROSmart, failure of the MICROSmart may cause disorder of the controlsystem, damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND D HAZARDOUS
LOCATIONS, OR NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereuses de classe 1,groupes A,B,C et D; ou dans des zones non dangereuses.
● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT EQUIPMENT WHILE THE CIRCUITIS LIVE OR UNLESS THE AREA IS KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.
● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant que le circuit est sous tension,ou à moins ďêtre certain que lieu ďutilisation soit exempt de concentrations inflammables.
● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE INSTALLED IN AN ENCLOSURESUITABLE FOR THE ENVIRONMENT THAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOLOR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté à ľenvironnement ďutilisation etuniquement accessible avec un outil ďouverture ou une clé.

1

TYPE

4

3.9
Dummy Cartridge

Screwdriver Slot

73.0

3. Take care with the vertical orientation of the analog cartridge and firmly push the cartridge connector
onto cartridge slot 3 on the HMI module.

4.0

Cartridge Slot 3

Communication Connector
Protection Sticker

7Analog Cartridge

119.5
148.7

Mounting HMI Module

9For details about mounting and removing modules, see the user’s manual.
CPU module
2. Line up the HMI module alongside the FC6A Series MICROSmart CPU module.
3. Confirm that the HMI module eject button is depressed and push the HMI module until it clicks while
taking care with the position of the communication connector. If the eject button is not depressed,
push in the eject button until it clicks after the HMI module has been pushed onto the FC6A Series
MICROSmart CPU module. The HMI module is now locked on the FC6A Series MICROSmart CPUmodule.

[Mounting on DIN Rail]Use a 35-mm-wide DIN Rail and BNL6 mounting clips to secure the modules.

35-mm-wide DIN Rail

(1) Pull out the DIN Rail Hook(3) Press the modules
towards the DIN RailApplicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening Torque

Applied cable
35-mm-wide DIN Rail(4) Push in the DIN Rail Hook

UL1007/ UL2464

Specification
Eject Button

5

Opening and Closing Front CoverOpening the Front Cover
1. Push the access symbol until it clicks to unlock the front cover.

All dimensions in mm.

The recommended ferrule is made by Phoenix Contact or Weidmüller. To crimp the ferrules shown
below, use a special crimping tool. (CRIMPFOX6 (1212034) or PZ 6 Rote (9014350000))To the terminal block, use the recommended screwdriver made by Phoenix Contact or Weidmüller andtighten terminal screws tightening torque.

(2) put the groove of themodule on the DIN rail.

Communication Connector

Applicable model
FC6A Series MICROSmart CPU module

Operating Temperature: -10 to +55°C (no freezing),
Storage Temperature: -25 to +70°C (no freezing)
Relative/Storage Humidity: 10 to 95%RH (no condensation),Altitude or Air Pressure: 1,013 to 795hPa (0 to 2,000 m) during operation
1,013 to 701hPa (0 to 3,000 m) during transport,Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes, 6 directions, 3 times each
Installation Location: Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C
Temperature Code: T4A*See the user’s manual for more details on the product specifications.

7.3

Connecting HMI Module

HMI module
FC6A-PH12

74.5

1. Peel off the protection sticker applied to the communication connector on the FC6A Series
MICROSmart CPU module.

in places where it is subjected to high-temperature, high-humidity, condensation, corrosive gases,
excessive vibrations, or excessive shocks itwill result in electrical shocks, fire hazard, or malfunction.

proper tightening torque of 0.5 to 0.6 N-m.

Dimensions

90.0(1) Front Cover
Remove the front cover when using the operation buttons.
(2) LCDDisplays operation menus, status, and settings of the MicroSmart.
(3) Cartridge Slot 3
For connecting an optional cartridge. You cannot connect a communication cartridge to cartridge
slot 3.
(4) Communication Connector
Connects to the CPU modules.
(5) Operation Buttons
For operating the menus displayed on the LCD to access functions. There are six operationbuttons.
(6) LINK LED
Turns on when the CPU module is connected to another network device using a LAN cable.
(7) ACT LED
Flashes when the CPU module sends or receives data from the Ethernet port.
(8) Ground terminalfunctional ground terminal(9) Dummy Cartridge
Remove the HMI connector cover when using an optional HMI module.
(10) HMI-Ethernet PortThis port is used for Ethernet connection.

● The environment rating for using the MICROSmart is “Pollution degree 2.”● Do not disassemble, repair, or modify MICROSmart modules.

8(9) Dummy Cartridge

equipment.

of such fragments and chips may cause fire hazard, damage, or malfunction.

1. Unlock and open the front cover of the HMI module.

Bottom● Install the MICROSmart in environments as described in the user's manual. If the MICROSmart is used

● Use wires of a proper size to meet voltage and current requirements. Tighten terminal screws to the.5

Connecting Cartridge

2. Insert a flathead screwdriver into each of the screwdriver slots (two locations) on the HMI moduleand remove the dummy cartridge straight off the HMI module by pushing in the dummy cartridge tabs.

● The MICROSmart is designed for installation in equipment. Do not install the MICROSmart outside of● Prevent metal fragments and pieces of wire from dropping inside the MICROSmart housing. Ingress

ø466.5Warning notices are used to emphasize that improper operation may cause severe personal injury or death.

6All dimensions in mm.

2-Access Symbol

5.0

Special expertise is required to use the MICROSmart.
● Read this instruction sheet and the user's manual to make sure of correct operation before starting
installation, wiring, operation, maintenance, and inspection of the MICROSmart.
Keep this instruction sheet where it can be accessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorous quality control system, but usersmust add backup or failsafe provisions to control systems use the MICROSmart in applications where
heavy damage or personal injury may be caused if the MICROSmart should fail.
● Install the MICROSmart according to the instructions described in this instruction sheet and the user'smanual. Improper installation will result in falling, failure, or malfunction of the MICROSmart.
● Make sure that the operating conditions are as described in the user’s manual. If you are uncertain
about the specifications, contact IDEC before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order of importance from Warning andCaution:● For UL/cUL, Horizontal mounting only.
● Use copper conductor only.

(3) Cartridge Slot 3[Direct Mounting on Panel Surface]
Pull out the DIN Rail Hook on the back of the module and insert the direct mounting Hook
(FC6A-PSP1PN05) into the slot. Attach the module to the mounting plate using the screw holes.
Attach the module to the mounting plate using M4 tapping screws, as shown below, or make 5 to 6mmmounting holes and secure the module using M4 pan head screws.
Always give sufficient consideration to operability, ease-of-maintenance, and environmental resistancewhen deciding on the mounting position.

UL1015

Direct mounting Hook
(FC6A-PSP1PN05)

Recommended ferrule

AWG24

AI 0,25-6 (3203040), AI 0,25-8 (3203037),
H0,25/10 HBL(9025740000), Ｈ0,25/12T GE (9021020000)

AWG22

AI 0,34-6 (3203053), AI 0,34-8 (3203066),
H0,34/10 TK(9025750000), H0,34/12 TK (9025770000)

AWG20

AI 0,5-6 (3200687), AI 0,5-8 (3200014), AI-TWIN 2×0,5-8 (3200933),
H0,5/12D W(9019000000), H0,5/16D W (9019020000),
H0,5/14D ZH W (9037380000)

AWG18

AI 0,75-6 (3200690), AI 0,75-8 (3200519), Al-TWIN 2×0,75-8 (3200807),
H0,75/12D GR (9019030000), H0,75/14D GR (9019040000),
H0,75/14D ZH GR (9037410000)

AWG16

AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)

AWG20
AWG18

AI 0,5-8 GB (1208966)
AI 1-8 (3200030), H1,0/14D R (9019080000)

AWG16

AI 1,5-6 (3200755), Al 1,5-8 (3200043),
H1,5/14D SW (9019120000)
Screwdriver

SZS 0,6×3,5 (1205053) , SDS 0,6X3,5X100 (9008330000)

2. The front cover will open.

Tighten torque
0.5 to 0.6 N-m( ) indicates the Type No. of PHOENIX CONTACT GmbH & Co. KG and Weidmüller Interface GmbH & Co. KG.

Front CoverScrew Hole

10Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.

DIN Rail Hook
Front Cover
Access Symbol

MicroSmart User’s manual can be downloaded from http://www.idec.com/FC6Amanuals
Screw Hole

http://www.idec.com
2019.07