Screwdriverinsertion slot

B-1940(6)To remove the cartridge, perform the work detailed in step 1.

Operating Temperature: -10 to +55°C (no freezing)
Storage Temperature: -25 to +70°C (no freezing)
Relative/Storage Humidity: 10 to 95%RH (no condensation),
Altitude or Air Pressure: 0 to 2,000 m (1,013 to 795hPa) during operation
0 to 3,000 m (1,013 to 701hPa) during transport,
Vibration Resistance: 5 to 8.4 Hz half amplitude 3.5 mm, 8.4 to 150 Hz,
acceleration 9.8 m/s2 (1 G), X, Y, Z directions, 2 hours,
Shock Resistance: 147 m/s2 (15 G), 11 ms, X, Y, Z, 3 axes,
6 directions, 3 times each
Installation Location: Inside cabinet (indoor use)
Maximum Surrounding Air Temperature: 55°C
Temperature Code: T4*See the user’s manual for more details on the product specifications.

voltage less than 30V DC is required to power the terminal.
● Attach or remove the cartridge straight to the unit. If the cartridge is

attached or removed when tilted, it may be damaged or cause operatingproblems. When not using Cartridge, attach the Cartridge cover.
● For UL/cUL, Horizontal mounting only.

5● For UL/cUL, use transistor outputs under resistive load and Limited energy.
● Use Use minimum 60°C wire copper conductor only.

7Dimensions

Applicable Cable / Recommended Ferrule /Recommended Screwdriver / Tightening TorqueThe recommended ferrule is made by IDEC, Weidmüller or Phoenix Contact.
To crimp the ferrules shown below, use a special crimping tool.
(S3TL-CR04T (S3TL-CR04T), PZ 6 Roto L (1444050000) or CRIMPFOX6(1212034))
To the terminal block, use the recommended screwdriver made by IDEC,
Weidmüller or Phoenix Contact and tighten terminal screws tightening torque.

44.6

3Parts Description

AWG24
UL1007/UL2464

Caution notices are used where inattention might cause personal injury ordamage to equipment.

AWG22
AWG20

(2)

12.5
17.8

34.8
● Turn off the power to the MICROSmart before starting installation,(1)

All dimensions in mm.

(1)

6Wiring

FC6A-PTK4: Fuse(1)Terminal
These terminals connect output devices, input devices or power.
(2)Connector
Connects to the cartridge slot 1 or 2 connector on the CPU module.

LL

10.2 to 28.8V DC

Connecting Cartridge

Step 1.
Insert two flathead screwdrivers into the screwdriver insertion slots in both
locations of the unit, and while pushing the tabs of the cartridge cover,remove the cartridge cover straight off of the unit.

Recommended ferrule
S3TL-H025-10WJ (S3TL-H025-10WJ),
AI 0,25-6 (3203040)
S3TL-H034-10WT (S3TL-H034-10WT),
AI 0,34-6 (3203053)
S3TL-H05-12WA (S3TL-H05-12WA),
AI 0,5-6 (3200687)

Screwdriver
Tighten torqueS3TL-D04-25-75 (S3TL-D04-25-75),
0.2 N･mSZS 0.4×2.5 (1205037)( ) indicates the Type No. of IDEC CORPORATION, Weidmüller Interface GmbH& Co. KG and PHOENIX CONTACT GmbH & Co. KG.
*See the user's manual for recommended tools and ferrules other than thoselisted above.

8Precaution for Disposal● Dispose of the FC6A Series MICROSmart as an industrial waste.

EU Authorized Representative : APEM SAS
55, Avenue Edouard Herriot BP1, 82303 Caussade Cedex, France
UK Authorized Representative : APEM COMPONENTS LIMITEDDrakes Drive, Long Crendon, Buckinghamshire, HP18 9BA, UKL
L

4L : Load+ -removal, wiring, maintenance, or inspection on the MICROSmart.
Failure to turn off the power may cause damage, electrical shocks or fire
hazard.
● Emergency stop and interlocking circuits must be configured outside theMICROSmart. If such a circuit is configured inside the MICROSmart,failure of the MICROSmart may cause disorder of the control system,
damage, or accidents.
● SUITABLE FOR USE IN CLASS 1, DIVISION 2, GROUPS A,B,C AND DHAZARDOUS LOCATIONS, OR NONHAZARDOUS LOCATIONS ONLY.
● Cet appareil convient uniquement à ľemploi dans des zones dangereusesde classe 1, groupes A,B,C et D; ou dans des zones non dangereuses.
● WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT
EQUIPMENT WHILE THE CIRCUIT IS LIVE OR UNLESS THE AREA IS
KNOWN TO BE FREE OF IGNITABLE CONCENTRATIONS.
● Avertissement: risque d'explosion. Ne pas débrancher ľappareil tant quele circuit est sous tension, ou à moins ďêtre certain que lieu ďutilisationsoit exempt de concentrations inflammables.
● THIS EQUIOMENT IS AN OPEN -TYPE DEVICE MEANT TO BE
INSTALLED IN AN ENCLOSURE SUITABLE FOR THE ENVIRONMENTTHAT IS ONLY ACCESSIBLE WIHT THE USE OF A TOOL OR KEY.
● Cet appareil doit être installé dans un boîtier qui est adapté àľenvironnement ďutilisation et uniquement accessible avec un outilďouverture ou une clé.

NPNsensor● Use an isolated type or SELV power supply source when power supply

Applied cable
Warning notices are used to emphasize that improper operation may
cause severe personal injury or death.

Rating:
4 Inputs
12V DC 2.5mA/pt
24V DC 5mA/pt

Cartridge

Specification+PNP- 2wire +LLRating:
4 Transistor source outputs
12V DC 0.1A/pt
24V DC 0.1A/pt

Applicable model
FC6A Series MICROSmart CPU module
SmartAXIS Series FT1A Controller TOUCH (Display type)2

Rated load: 12-24VDC/0.1A

10.2 to 28.8VDC

L+-10.2 to 28.8VDC

Special expertise is required to use the MICROSmart.
● Read this instruction sheet and the user's manual to make sure ofcorrect operation before starting installation, wiring, operation,
maintenance, and inspection of the MICROSmart.
Keep this instruction sheet where it can be accessed by the end user.
● All MICROSmart modules are manufactured under IDEC's rigorous
quality control system, but users must add backup or failsafe provisions
to control systems use the MICROSmart in applications where heavy
damage or personal injury may be caused if the MICROSmart shouldfail.
● Install the MICROSmart according to the instructions described in thisinstruction sheet and the user's manual.
Improper installation will result in falling, failure, or malfunction of theMICROSmart.
● Make sure that the operating conditions are as described in the user’s
manual. If you are uncertain about the specifications, contact IDEC
before using the MICROSmart.
● In this instruction sheet, safety precautions are categorized in order ofimportance from Warning and Caution:

TYPE

sensorSafety Precautions

1

Transistor Sink out: FC6A-PTK4
Transistor Source out: FC6A-PTS4
DC input: FC6A-PN4+ 2wire -This sheet provides brief operating instructions of the MICROSmart
programmable controller. For details, see the FC6A Series MICROSmart
User’s Manual.

10.2 to 28.8V DC

Digital I/O Cartridge

Cartridge cover
Step 2.
Pay careful attention to the direction of the cartridge and attach it straightto the unit.

LL

FC6A Series

FC6A-PN4

Screwdriverinsertion slot- +INSTRUCTION SHEET● The MICROSmart is designed for installation in equipment. Do notinstall the MICROSmart outside of equipment.
● Install the MICROSmart in environments as described in the user'smanual. If the MICROSmart is used in places where it is subjected tohigh-temperature, high-humidity, condensation, corrosive gases,
excessive vibrations, or excessive shocks itwill result in electricalshocks, fire hazard, or malfunction.
● The environment rating for using the MICROSmart is “Pollution degree 2.”● Prevent metal fragments and pieces of wire from dropping inside theMICROSmart housing. Ingress of such fragments and chips may cause
fire hazard, damage, or malfunction.
● Use wires of a proper size to meet voltage and current requirements.
Tighten terminal screws to the proper tightening torque of 0.2 N･m.
● Do not disassemble, repair, or modify MICROSmart modules.

FC6A-PTS4Rating:
4 Transistor sink outputs
12V DC 0.1A/pt
24V DC 0.1A/pt

L Rated load: 12-24V DC/0.1A

Manufacturer :IDEC CORPORATION
2-6-64,Nishimiyahara,Yodogawa-ku, Osaka,JapanMICROSmart User’s manual can be downloaded fromhttps://www.idec.com/FC6Amanuals

https://www.idec.com
2021.09

！

注意

46

注意NPN
PNP

センサ

FC6A-PTK4: ヒューズ

L : 負荷適合電線／推奨フェルール端子／推奨ドライバ／締付トルク

推奨のフェルール端子は弊社、ワイドミュラー社 またはフェニックス・コン
タクト社製品です。下記推奨フェルール端子を圧着する際には、専用の圧着工具 PZ 6 Roto L（1444050000）または CRIMPFOX 6（1212034）
をご使用ください。端子台に配線する際には、下記推奨ドライバをご使用ください。またねじ締め付けが必要な場合は、下記の推奨締付トルクで締め付けてください。

適合電線

UL1007／UL2464

LL+ -推奨フェルール端子
AWG24

S3TL-H025-10WJ (S3TL-H025-10WJ),
AI 0,25-6 (3203040)

AWG22

S3TL-H034-10WT (S3TL-H034-10WT),
AI 0,34-6 (3203053)

AWG20

S3TL-H05-12WA (S3TL-H05-12WA),
AI 0,5-6 (3200687)

推奨ドライバS3TL-D04-25-75 (S3TL-D04-25-75),
SZS 0.4×2.5（1205037）

ドライバ差込口

推奨締付トルク0.2 N･m（ ）内は 弊社、ワイドミュラー社または フェニックス・コンタクト社製品の発注形番
L 定格負荷：DC12～24V／ 0.1A

※上記以外の推奨工具・フェルール端子の詳細はユーザーズマニュアルをご覧ください。

8
FC6A-PTS4

廃棄上のご注意・本製品を廃棄するときは、産業廃棄物として扱ってください。

ドライバ
差込口

・本製品は装置内への組み込み設置専用です。装置外には設置しないでカートリッジカバーください。
・カタログ、ユーザーズマニュアルに記載の環境下で、ご使用ください。 手順2.
カートリッジの方向に注意して、本体にまっすぐ取り付けてください。
・高温、多湿、結露、腐食性ガス、過度の振動・衝撃のある所で使用すると、感電、火災、誤動作の原因となります。
・本製品の使用環境汚損度は「汚損度2」です。
・設置、配線作業時に配線くずやドリル加工による金属の切り粉などが、本製品内部に入らないように 注意してください。配線くずなどが本製品内部に入ると、火災、故障、誤動作の原因となります。
・配線は印加電圧、通電電流に適した電線サイズを使用し、端子ねじは推奨締付トルク 0.2 N･m で締め付けてください。
・分解、修理、改造等は行わないでください。

ユーザーサポート情報
最新のユーザーズマニュアルを、下記URLよりダウンロードして下さい。
https://jp.idec.com/downloads/fc6a

LL！

7

入出力配線

接続方法

・取り付け、取り外し、配線作業および保守・点検は必ず電源を切って行ってください。感電および火災の危険があります。
・非常停止回路やインタロック回路などはマイクロスマート以外の外部回路で構成してください。これらの回路をFC6A形、FT1A形のシステ
ムで構成するとFC6A形、FT1A形が故障した場合、機械の暴走、破損や事故のおそれがあります。

+（単位：mm）

- +

警告

12.5
17.8

34.8

取り扱いを誤った場合、人が障害を負うか物的障害が発生する可能性があ 手順1.
マイナスドライバ2本を本体2箇所のドライバ差込口に差し込み、カートります。
リッジカバーのツメ部を押し込んだ状態で、カートリッジカバーをまっすぐ取り外してください。

！

DC10.2～28.8V

本製品の取り扱いには専門の知識が必要です。
・本製品の取り付け、配線作業、運転および保守・点検を行う前に、この取扱説明書およびユーザーズマニュアルをよくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管される②よう手配ください。
・本製品は弊社の厳しい品質管理体制のもとで製造されておりますが、万一本製品の故障により重大な故障や損害の発生するおそれがある用途
へご使用の際は、バックアップやフェールセーフ機能をシステムに追加してください。
①①
・取扱説明書、ユーザーズマニュアルに記載の指示に従って取り付けてください。取り付けに不備があると落下、故障、誤動作の原因となります。
・使用条件が、取扱説明書やユーザーズマニュアルの内容と相違ないことを必ずご確認ください。
内容に不明な点がある場合は、使用する前に弊社までご相談ください。 ①端子部
電源、および入力機器や出力機器を接続します。
・本取扱説明書では、誤った取り扱いをした場合に生じることが想定さ接続する機器は、デジタルＩ/Ｏカートリッジの種類によって異なります。
れる危険の度合いを「警告」「注意」として区別しています。
端子名の詳細は「6. 入出力配線」の項を参照ください。
それぞれの意味するところは以下のとおりです。
②接続コネクタ！ 警 告CPU モジュールのカートリッジスロット1 または2と接続します。
取り扱いを誤った場合、人が死亡または重傷を負う可能性があります。

！

44.6

名称と機能センサ

3+-LL

安全上のご注意

外形寸法

DC10.2～28.8V

5仕様

使用周囲温度：-10～+55℃（氷結なきこと）
ＦＣ６Ａ形
保存周囲温度：-25～+70℃（氷結なきこと）
使用/保存周囲湿度：10～95%RH（結露なきこと）
デジタル Ｉ/Ｏ カートリッジ
標高：動作時：0～2000ｍ（1013～795hPa）
輸送時：0～3000m（1013～701hPa）
この度は、弊社製品をお買い上げいただき、誠にありがとうございます。 耐振動：5 ～ 8.4Hz片振幅3.5mm 2
8.4 ～ 150Hz加速度9.8m/s （1G）XYZ各方向 2時間
ご注文の製品に間違いがないかを確認のうえ、この取扱説明書の内容を
耐衝撃：147m/s2（15G）11ms XYZ 3軸6方向各3回
よくお読みいただき、正しくご使用ください。また、この取扱説明書は最終ユーザー様で保管されるよう手配ください。
※電気的仕様に関する詳細はユーザーズマニュアルをご覧ください。

LL

2

カートリッジは本体に対してまっすぐに脱着してください。
傾いた状態で脱着すると、破損や動作不良の原因となる場合があります。
カートリッジを使用しないときは、カートリッジカバーを取り付けてください。

- 2線式 +適合機種
FC6A形マイクロスマート CPUモジュール
Smart AXISシリーズ FT1A形コントローラ Touch（ディスプレイタイプ）

FC6A-PN4

注意+ 2線式 -形番構成

DC10.2～28.8V

取扱説明書

1

トランジスタシンク出力：FC6A-PTK4
トランジスタソース出力：FC6A-PTS4
ＤＣ入力：FC6A-PN4

DC10.2～28.8V

B-1940(6)

取扱説明書にご不明な点がございましたら、製品問合せ窓口にお問い合わせください。

カートリッジカートリッジを取り外す場合は、手順1の要領で作業を行ってください。

L 定格負荷：DC12～24V／ 0.1A

製品問合せ窓口
2021.09