JCM_ID_F_PM_ver01.0

JCM Proposed Methodology Form
Cover sheet of the Proposed Methodology Form
Form for submitting the proposed methodology
Host Country

The Republic of Indonesia

Name of the methodology proponents

myclimate Japan Co., Ltd.

submitting this form
Sectoral scope(s) to which the Proposed

03. Energy Demand

Methodology applies
Title of the proposed methodology, andInstallation of a separate type fridge-freezer

version number

showcase by using natural refrigerant for grocery
store to reduce air conditioning load inside thestore, version 1.0

List of documents to be attached to this form

The attached draft JCM-PDD:(please check):

Additional information

Date of completion

30/04/2015

History of the proposed methodology
VersionDate

1.0

30/04/2015

Contents revisedFirst edition1

JCM_ID_F_PM_ver01.0

A. Title of the methodology
Installation of a separate type fridge-freezer showcase by using natural refrigerant for grocery
store to reduce air conditioning load inside the store, version 1.0

B. Terms and definitions
Terms

Definitions

Separate type fridge-freezer

Refrigeration or freezer system with natural refrigerant of

showcase

which condensing unit and showcase unit are separated andthe condensing unit is located outside the store. The system
includes the following:

Reach-in type fridge showcase or freezer showcase (astructure to interrupt display room from outside air byglass type door)

Open type fridge showcase (a structure to interrupt
display room from outside air by air curtain)

Walk in type fridge showcase (a structure which people
can go in and fill groceries from behind the display
shelves)Natural refrigerant

Natural refrigerant refers to naturally occurring substanceswith refrigeration capacity and with zero ozone depletion
potential (ODP) (e.g., CO2 and NH3).

Built-in type showcase

Refrigeration or freezer system of which condensing unit andshowcase unit are built in one unit.

Coefficient of Performance

Coefficient of Performance (COP) is the cooling capacity per(COP)

rated power consumption of the air conditioning system. The
values of cooling capacity and rated power consumption are
defined under specific temperature stated in ISO 5151:2010.

Energy efficiency

For the purpose of this methodology, energy efficiency of thefridge-freezer showcase is defined as the rated volume (L)divided by the rated electricity consumption (W) or the rated
cooling capacity (W) divided by the rated electricity
consumption (W).

2

JCM_ID_F_PM_ver01.0

C. Summary of the methodology
Items

Summary

GHG emission reduction

This methodology applies to the project that aims for saving total

measuresenergy of in-store showcase and air conditioning system byintroducing a separate type natural refrigerant fridge-freezer
showcase for grocery store in Indonesia, which leads to GHG
emission reductions, through reduction of air conditioning
demand by not releasing waste heat inside the store.

Calculation of reference

Reference emissions are GHG emissions from both the reference

emissionsbuilt-in type fridge-freezer showcase and the reference air
conditioning system.
[Built-in type fridge-freezer showcase]
Reference emissions from the reference fridge-freezer showcase
are calculated with:Electricity consumption of the project fridge-freezer
showcase;Energy efficiency of the project fridge-freezer showcase;Energy efficiency of the reference fridge-freezer
showcase; andCO2 emission factor for consumed electricity.

[Air conditioning system]
Reference emissions from the reference air conditioning system
due to waste heat from the reference fridge-freezer showcase arecalculated with:Electricity consumption of the project fridge-freezer
showcase;Energy efficiency of the project fridge-freezer showcase
in terms of the cooling capacity;Energy efficiency of the project fridge-freezer showcase
in terms of the volume;Energy efficiency of the reference fridge-freezer
showcase;

COP of the reference air conditioning system; andCO2 emission factor for consumed electricity.

Calculation of project[Separate type natural refrigerant fridge-freezer showcase]emissions

Project emissions are calculated with power consumption of3

JCM_ID_F_PM_ver01.0

installed separate type natural refrigerant fridge-freezer showcase
and CO2 emission factor for consumed electricity.
Monitoring parametersElectricity consumption of the project fridge showcase

Electricity consumption of the project freezer showcase

D. Eligibility criteria
This methodology is applicable to projects that satisfy all of the following criteria.
Criterion 1

The project is to install a separate type fridge-freezer by using natural refrigerantor replacing the existing at a grocery store which is equipped with wall mounted
type and/or ceiling cassette type air conditioning system and whose selling area isless than 400 (four hundred) m2. The project includes both new installation andreplacement of the existing fridge-freezer showcase.

Criterion 2

In the case of replacing the existing fridge-freezer showcase with the project
fridge-freezer showcase, the existing one is a built-in type showcase.

Criterion 3

In the case of replacing the existing fridge-freezer showcase with the project
fridge-freezer showcase, plans to prevent release of refrigerants into theatmosphere are prepared for the existing fridge-freezer showcase replaced by the
project. Execution of the prevention plan is checked at the time of verification, inorder to confirm that refrigerant used for the existing one replaced by the project is
not released to the air.

E. Emission Sources and GHG types
Reference emissions
Emission sources

GHG types

Electricity consumption of the reference fridge showcase

CO2

Electricity consumption of the reference freezer showcase

CO2

Electricity consumption of the reference air conditioning system

CO2

Project emissions
Emission sources

GHG types

Electricity consumption of the project fridge showcase

CO2

Electricity consumption of the project freezer showcase

CO24

JCM_ID_F_PM_ver01.0

F. Establishment and calculation of reference emissions
F.1. Establishment of reference emissions
Reference emissions are GHG emissions from electricity consumption by both the reference
built-in type fridge-freezer showcase and the reference air conditioning system used for coolingthe exhaust heat from the reference fridge showcase.
Net emission reductions in this methodology are achieved by setting default values of “COP of
the reference air conditioning system” in a conservative manner, and also achieved by notincluding “leakage of HFCs from the reference fridge-freezer showcase” in the count ofemission reductions.
[COP of the reference air conditioning system]
The default values of COP of the reference air conditioning system are set in line with theapproved JCM methodology ID_AM004 Ver1.0.
If the air conditioning system equipped in the project store has higher COP values compared tothe table below within the respective cooling capacity range, the COP value of the air
conditioning system installed at the project store is used.
If multiple types of air conditioning system with different cooling capacity rage shown in thetable below are found in the project site, the highest value of COP is selected and applied to
calculate reference emissions in a conservative manner.

Cooling Capacity [kW]2.5 ＜ x ≦ 4.1
4.1 ＜ x ≦ 5.3
5.3 ＜ x ≦ 7.1
7.1 ＜ x ≦ 14.2

Reference COP
4.00
3.59
2.96
2.85

[Energy efficiency of the reference fridge-freezer showcase]
The default values of rated electricity consumption of the reference fridge and freezer showcase
are set ex ante in the table below.
The reference fridge showcase-Reach-in showcase

5

JCM_ID_F_PM_ver01.0

Range of volume (L)Energy efficiency (L/W)

z < 900

1.18

900 ≦ z < 1,200

1.07

1,200 ≦ z

2.24

-Open showcase
Range of volume (L)Energy efficiency (L/W)

z < 900

0.50

900 ≦ z < 1,200

0.65

1,200 ≦ z

0.73

The reference freezer showcase-Reach-in showcase
Range of volume (L)Energy efficiency (L/W)

z < 900

0.70

900 ≦ z < 1,200

0.70

1,200 ≦ z

1.01

Correspondence between project fridge-freezer showcase and reference fridge-freezer
showcase:
Pattern

Project fridge-freezer

Reference fridge-freezer

showcase

showcase

1

Reach-in type fridge showcase

Reach-in type fridge showcase

2

Open type fridge showcase

Open type fridge showcase

3

Walk-in type fridge showcase

Reach-in type fridge showcase

4

Reach-in type freezer showcase

Reach-in type freezer showcase

F.2. Calculation of reference emissionsRE୮‫܀‬۳‫܀ = ܘ‬۳܎‫܍܏܌ܑܚ‬,‫ ܘ‬+ ‫܀‬۳܎‫ܚ܍ܢ܍܍ܚ‬,‫ ܘ‬+ ‫܀‬۳‫ۯ‬۱,‫܌܌܉‬,܎‫܍܏܌ܑܚ‬,‫ ܘ‬+ ‫܀‬۳‫ۯ‬۱,‫܌܌܉‬,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܘ‬RE୤୰୧ୢ୥ୣ,୮RE୤୰ୣୣ୸ୣ୰,୮

RE୅େ,ୟୢୢ,୤୰୧ୢ୥ୣ,୮: Reference emissions during the period p [tCO2/p]: Reference emissions of the fridge showcase during the period p [tCO2/p]: Reference emissions of the freezer showcase during the period p[tCO2/p]: Reference emissions of the air conditioning system caused by the6

JCM_ID_F_PM_ver01.0

electricity consumption due to exhaust heat from the reference fridge
showcase during the period p [tCO2/p]
RE୅େ,ୟୢୢ,୤୰ୣୣ୸ୣ୰,୮ : Reference emissions of the air conditioning system caused by theelectricity consumption due to exhaust heat from the reference freezer
showcase during the period p [tCO2/p]

RE୤୰୧ୢ୥ୣ,୮

PEC୤୰୧ୢ୥ୣ,୧,୮

ߟ୔୎,୤୰୧ୢ୥ୣ,୧

ߟୖ୉,୤୰୧ୢ୥ୣ,୧
EFୣ୪ୣୡ
iRE୤୰ୣୣ୸ୣ୰,୮

PEC୤୰ୣୣ୸ୣ୰,୨,୮

ߟ୔୎,୤୰ୣୣ୸ୣ୰,୨

ߟୖ୉,୤୰ୣୣ୸ୣ୰,୨
EFୣ୪ୣୡ

j‫܀‬۳܎‫܍܏܌ܑܚ‬,‫ = ܘ‬෍ ቆ‫۾‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫× ܘ‬ܑߟ‫۾‬۸,܎‫܍܏܌ܑܚ‬,ܑቇ × ۳۴‫܋܍ܔ܍‬ߟ‫܀‬۳,܎‫܍܏܌ܑܚ‬,ܑ: Reference emissions of the fridge showcase during the period p [tCO2/p]: Electricity consumption of the project fridge showcase i during the period p[MWh/p]: Energy efficiency of the project fridge showcase i in terms of the volume[L/W]: Energy efficiency of the reference fridge showcase i in terms of the volume[L/W]: CO2 emission factor for consumed electricity [tCO2/MWh]: Identification number of the fridge showcase [-]‫܀‬۳܎‫ܚ܍ܢ܍܍ܚ‬,‫ = ܘ‬෍ ቆ‫۾‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫× ܘ‬‫ܒ‬ߟ‫۾‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬ቇ × ۳۴‫܋܍ܔ܍‬ߟ‫܀‬۳,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬: Reference emissions of the freezer showcase during the period p [tCO2/p]: Electricity consumption of the project freezer showcase j during the period
p [MWh/p]: Energy efficiency of the project freezer showcase j in terms of the volume[L/W]: Energy efficiency of the reference freezer showcase j in terms of the volume[L/W]: CO2 emission factor for consumed electricity [tCO2/MWh]: Identification number of the freezer showcase [-]‫܀‬۳‫ۯ‬۱,‫܌܌܉‬,܎‫܍܏܌ܑܚ‬,‫܀ = ܘ‬۳۱‫ۯ‬۱,‫܌܌܉‬,܎‫܍܏܌ܑܚ‬,‫ × ܘ‬۳۴‫܋܍ܔ܍‬‫܀‬۳۱‫ۯ‬۱,‫܌܌܉‬,܎‫܍܏܌ܑܚ‬,‫ = ܘ‬෍ ۳۶‫܀‬۳,܎‫܍܏܌ܑܚ‬,ܑ,‫× ܘ‬ܑ૚ߟ‫܀‬۳,‫ۯ‬۱۳۶‫܀‬۳,܎‫܍܏܌ܑܚ‬,ܑ,‫ = ܘ‬۳۶‫۾‬۸,܎‫܍܏܌ܑܚ‬,ܑ,‫ = ܘ‬۶۵‫۾‬۸,܎‫܍܏܌ܑܚ‬,ܑ,‫ ܘ‬+ ‫܀‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫ܘ‬۶۵‫۾‬۸,܎‫܍܏܌ܑܚ‬,ܑ,‫۾ = ܘ‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫۾ߟ × ܘ‬۸,܎‫܍܏܌ܑܚ‬,‫ܘ܉܋‬,ܑ‫܀‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫۾ = ܘ‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫× ܘ‬

7ߟ‫۾‬۸,܎‫܍܏܌ܑܚ‬,ܑߟ‫܀‬۳,܎‫܍܏܌ܑܚ‬,ܑ

JCM_ID_F_PM_ver01.0

RE୅େ,ୟୢୢ,୤୰୧ୢ୥ୣ,୮: Reference emissions of the air conditioning system caused by theelectricity consumption due to exhaust heat from the reference fridge
showcase during the period p [tCO2/p]

REC୅େ,ୟୢୢ,୤୰୧ୢ୥ୣ,୮: Electricity consumption of the reference air conditioning system due toexhaust heat from the reference fridge showcase during the period p[MWh/p]EFୣ୪ୣୡ

: CO2 emission factor for consumed electricity [tCO2/MWh]

EHୖ୉,୤୰୧ୢ୥ୣ,୧,୮

: Amount of exhaust heat from the reference fridge showcase i during theperiod p [MWh/p]ߟୖ୉,୅େ

: COP of the reference air conditioning system [-]EH୔୎,୤୰୧ୢ୥ୣ,୧,୮

: Amount of exhaust heat from the project fridge showcase i during theperiod p [MWh/p]

HG୔୎,୤୰୧ୢ୥ୣ,୧,୮

: Amount of cooling energy generated by the project fridge showcase iduring the period p [MWh/p]REC୤୰୧ୢ୥ୣ,୧,୮

: Electricity consumption of the reference fridge showcase i during theperiod p [MWh/p]ߟ୔୎,୤୰୧ୢ୥ୣ,ୡୟ୮,୧: Energy efficiency of the project fridge showcase i in terms of thecooling capacity [W/W]

PEC୤୰୧ୢ୥ୣ,୧,୮

: Electricity consumption of the project fridge showcase i during theperiod p [MWh/p]ߟ୔୎,୤୰୧ୢ୥ୣ,୧: Energy efficiency of the project fridge showcase i in terms of thevolume [L/W]ߟୖ୉,୤୰୧ୢ୥ୣ,୧: Energy efficiency of the reference fridge showcase i in terms of thei: Identification number of the fridge showcase [-]volume [L/W]‫܀‬۳‫ۯ‬۱,‫܌܌܉‬,܎‫ܚ܍ܢ܍܍ܚ‬,‫܀ = ܘ‬۳۱‫ۯ‬۱,‫܌܌܉‬,܎‫ܚ܍ܢ܍܍ܚ‬,‫ × ܘ‬۳۴‫܋܍ܔ܍‬૚‫܀‬۳۱‫ۯ‬۱,‫܌܌܉‬,܎‫ܚ܍ܢ܍܍ܚ‬,‫ = ܘ‬෍ ۳۶‫܀‬۳,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫× ܘ‬ߟ‫܀‬۳,‫ۯ‬۱‫ܒ‬۳۶‫܀‬۳,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫ = ܘ‬۳۶‫۾‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫ = ܘ‬۶۵‫۾‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫ ܘ‬+ ‫܀‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫ܘ‬۶۵‫۾‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫۾ = ܘ‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫۾ߟ × ܘ‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܘ܉܋‬,‫ܒ‬RE୅େ,ୟୢୢ,୤୰ୣୣ୸ୣ୰,୮‫܀‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫۾ = ܘ‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫× ܘ‬ߟ‫۾‬۸,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬ߟ‫܀‬۳,܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬: Reference emissions of the air conditioning system caused by theelectricity consumption due to exhaust heat from the reference freezer
showcase during the period p [tCO2/p]

REC୅େ,ୟୢୢ,୤୰ୣୣ୸ୣ୰,୮ : Electricity consumption of the reference air conditioning system due to8JCM_ID_F_PM_ver01.0

exhaust heat from the reference freezer showcase during the period p[MWh/p]EFୣ୪ୣୡ

EHୖ୉,୤୰ୣୣ୸ୣ୰,୨,୮
ߟୖ୉,୅େ

EH୔୎,୤୰ୣୣ୸ୣ୰,୨,୮

HG୔୎,୤୰ୣୣ୸ୣ୰,୨,୮
REC୤୰ୣୣ୸ୣ୰,୨,୮

ߟ୔୎,୤୰ୣୣ୸ୣ୰,ୡୟ୮,୨
PEC୤୰ୣୣ୸ୣ୰,୨,୮

ߟ୔୎,୤୰ୣୣ୸ୣ୰,୨

: CO2 emission factor for consumed electricity [tCO2/MWh]: Amount of exhaust heat from the reference freezer showcase j during
the period p [MWh/p]: COP of the reference air conditioning system [-]: Amount of exhaust heat from the project freezer showcase j during theperiod p [MWh/p]: Amount of cooling energy generated by the project freezer showcase jduring the period p [MWh/p]: Electricity consumption of the reference freezer showcase j during theperiod p [MWh/p]: Energy efficiency of the project freezer showcase j in terms of thecooling capacity [W/W]: Electricity consumption of the project freezer showcase j during theperiod p [MWh/p]: Energy efficiency of the project freezer showcase j in terms of thevolume [L/W]ߟୖ୉,୤୰ୣୣ୸ୣ୰,୨: Energy efficiency of the reference freezer showcase j in terms of thej: Identification number of the freezer showcase [-]volume [L/W]

G. Calculation of project emissions

PE୮PE୤୰୧ୢ୥ୣ,୮PE୤୰ୣୣ୸ୣ୰,୮PE୤୰୧ୢ୥ୣ,୮

PEC୤୰୧ୢ୥ୣ,୧,୮‫۾‬۳‫۾ = ܘ‬۳܎‫܍܏܌ܑܚ‬,‫ ܘ‬+ ‫۾‬۳܎‫ܚ܍ܢ܍܍ܚ‬,‫ܘ‬: Project emissions during the period p [tCO2/p]: Project emissions of the fridge showcase during the period p [tCO2/p]: Project emissions of the freezer showcase during the period p [tCO2/p]‫۾‬۳܎‫܍܏܌ܑܚ‬,‫ = ܘ‬෍൫‫۾‬۳۱܎‫܍܏܌ܑܚ‬,ܑ,‫ ܘ‬൯ × ۳۴‫܋܍ܔ܍‬ܑ: Project emissions of the project fridge showcase during the period p[tCO2/p]: Electricity consumption of the project fridge showcase i during the period p9

JCM_ID_F_PM_ver01.0[MWh/p]EFୣ୪ୣୡ
iPE୤୰ୣୣ୸ୣ୰,୮

PEC୤୰ୣୣ୸ୣ୰,୨,୮
EFୣ୪ୣୡ
j: CO2 emission factor for consumed electricity [tCO2/MWh]: Identification number of the fridge showcase [-]‫۾‬۳܎‫ܚ܍ܢ܍܍ܚ‬,‫ = ܘ‬෍൫‫۾‬۳۱܎‫ܚ܍ܢ܍܍ܚ‬,‫ܒ‬,‫ ܘ‬൯ × ۳۴‫܋܍ܔ܍‬‫ܒ‬: Project emissions of the project freezer showcase during the period p[tCO2/p]: Electricity consumption of the project freezer showcase j during the period
p [MWh/p]: CO2 emission factor for consumed electricity [tCO2/MWh]: Identification number of the freezer showcase [-]H. Calculation of emissions reductions

ER ୮

RE୮
PE୮

۳‫܀ = ܘ ܀‬۳‫ ܘ‬− ‫۾‬۳‫ܘ‬: Emissions reductions during the period p [tCO2/p]: Reference emissions during the period p [tCO2/p]: Project emissions during the period p [tCO2/p]

I. Data and parameters fixed ex ante
The source of each data and parameter fixed ex ante is listed as below.
Parameter

Description of Data

SourceEnergy efficiency of the reference fridge showcase i

Nominal value

in terms of the volume.

available on productcatalogs, specification
documents or-Reach-in showcase
ߟୖ୉,୤୰୧ୢ୥ୣ,୧

websites.

Range of volume (L)Energy efficiency (L/W)

z < 900

1.18

900 ≦ z < 1,200

1.07

The default values are

1,200 ≦ z

2.24

derived from the resultof survey on energy

10JCM_ID_F_PM_ver01.0

efficiency of fridge
showcase from-Open showcase
Range of volume (L)Energy efficiency (L/W)

manufacturers wellz < 900

0.50

known in the market.

900 ≦ z < 1,200

0.65

The default values

1,200 ≦ z

0.73

should be revised if
necessary from survey

When multiple types of showcases (Reach-in, Open,

result which is

and Walk-in) are connected to a condensing unit, theconducted by JC or

energy efficiency of Reach-in showcase above is

project participants

selected according to the total sum of rated coolingevery three years.

capacity (watt) of all showcases connected
corresponding to the “Range of volume” in the table.
Energy efficiency of the reference freezer showcase j

Nominal value

in terms of the volume.

available on productcatalogs, specification-Reach-in showcase

documents or
websites.

Range of volume (L)Energy efficiency (L/W)

z < 900

0.70

900 ≦ z < 1,200

0.70

The default values are

1,200 ≦ z

1.01

derived from the resultof survey on energy
efficiency of fridge

ߟୖ୉,୤୰ୣୣ୸ୣ୰,୨

showcase frommanufacturers wellknown in the market.
The default values
should be revised if
necessary from survey
result which is
conducted by JC or
project participants
every three years.

ߟ୔୎,୤୰୧ୢ୥ୣ,ୡୟ୮,୧Energy efficiency of the project fridge showcase i in

The specifications ofterms of the cooling capacity.

the project fridge

The value of rated cooling capacity (watt) and rated

showcase andelectricity consumption (watt) used in calculation ofcondensing unit for11

JCM_ID_F_PM_ver01.0

energy efficiency prepared by manufacturer isquotation or theapplied.

factory acceptance test
data by manufacturer.

When multiple showcases are connected to acondensing unit, the energy efficiency is calculated asa ratio between the total sum of rated cooling capacity(watt) of all showcases connected and the rated
electricity consumption (watt) of condensing unit.

ߟ୔୎,୤୰୧ୢ୥ୣ,୧Energy efficiency of the project fridge showcase i in

The specifications ofterms of the volume.

the project fridge

The value of rated volume and rated electricity

showcase andconsumption used in calculation of energy efficiency

condensing unit for

prepared by manufacturer is applied.

quotation or thefactory acceptance test

When multiple showcases are connected to adata by manufacturer.

condensing unit, the energy efficiency is calculated asa ratio between the total sum of rated volume (little)of all showcases connected and the rated electricity
consumption (watt) of condensing unit.

ߟ୔୎,୤୰ୣୣ୸ୣ୰,ୡୟ୮,୧Energy efficiency of the project freezer showcase j in

The specifications ofterms of the cooling capacity.

the project fridge

The value of rated cooling capacity and rated

showcase for quotationelectricity consumption used in calculation of energy

or the factory

efficiency prepared by manufacturer is applied.

acceptance test data by
manufacturer.

When multiple showcases are connected to acondensing unit, the energy efficiency is calculated asa ratio between the total sum of rated cooling capacity(watt) of all showcases connected and the rated
electricity consumption (watt) of condensing unit.

ߟ୔୎,୤୰ୣୣ୸ୣ୰,୨Energy efficiency of the project freezer showcase j in

The specifications ofterms of the volume.

the project fridge

The value of rated volume and rated electricity

showcase for quotation

consumption used in calculation of energy efficiency

or the factory

prepared by manufacturer is applied.

acceptance test data by
manufacturer.

When multiple showcases are connected to a12

JCM_ID_F_PM_ver01.0

condensing unit, the energy efficiency is calculated asa ratio between the total sum of rated volume (little)of all showcases connected and the rated electricity
consumption (watt) of condensing unit.

EFelecCO2 emission factor for consumed electricity.

[Grid electricity]

When project air conditioning system consumes only

Updates on Grid

grid electricity or captive electricity, the project

Electricity Emission

participant applies the CO2 emission factor

Factors (calculated in

respectively.

year 2013), National

When project air conditioning system may consume

Committee on Clean

both grid electricity and captive electricity, the project

Development

participant applies the CO2 emission factor with

Mechanism,

lower value.

Indonesia, unlessotherwise instructed[CO2 emission factor]

by the Joint

For grid electricity: The most recent value available

Committee

from the source stated in this table at the time ofvalidation[Captive electricity]

For captive electricity: 0.8* [tCO2/MWh]

CDM approved small*The most recent value available from CDM

scale methodology

approved small scale methodology AMS-I.A at the

AMS-I.A

time of validation is applied.
Default COP values of the reference air conditioning

The approved JCM

system.

methodology

If multiple types of air conditioning system with

ID_AM004 Ver1.0

different cooling capacity, which means different
COP values, are found in the project site, the highest
value of COP is selected.
ߟ୅େ,ୖ୉

When an air conditioning system with higher COP
value than that of the reference COP withcorresponding cooling capacity set in the table isinstalled at the project site, ߟ୅େ,ୖ୉ is revised to the

COP value of installed one.

Default COP of Reference
Air Conditioning System (ߟ୅େ,ୖ୉ )13

JCM_ID_F_PM_ver01.0

Cooling Capacity [kW]2.5 ＜ x ≦ 4.1
4.1 ＜ x ≦ 5.3
5.3 ＜ x ≦ 7.1
7.1 ＜ x ≦ 14.2

Reference COP
4.00
3.59
2.96
2.85

14