RIK mV

333mV Rogowski Integrator Kit Datasheet

Specifications
RATED CURRENT
Current Range

2.5A - 60000A

Sensing Range

500A, 1000A, 2500A, 5000A, 10000A,25000A, 50000A
User Selectable

Integrator Output

0-333mVac

Integrator Accuracy±1% Full Scale Error

MECHANICAL/ENVIRONMENTAL

Integrator Kit Size

Single Phase:
62.7mm x 99.7mm x 114.6mm
2.46” x 3.93” x 4.52”
Three Phase:
146.3mm x 90.5mm x 100.0mm
5.76” x 3.56” x 3.94”

Input/Output Wire Connection

14 - 30 AWG

Operating Temperature-20°C ~ 55°C
-4°F ~ 131°F(RIK mV) is used to integrate Rogowski

Operating Humidity

Non-condensing, 0 to 95% RH

coils into any metering device that accepts

Integrator Enclosure Material

ABS, UL 94V-0

a 333mV input. Available in one or threeMounting

DIN TS-35/7.5 or 15 (DIN 43880) or Panel

Rogowski Coil and Power supply sold separately

The Accuenergy 333mV Rogowski Integrator

channels options, each channel can be
adjusted to accept one of seven field

Measurement Channels

1 (single-phase) or 3 (three-phase)

Channel Cross Talk<-60dB

Frequency Range

45Hz to 65Hz

Response Time

<10ms

Burden1.8VA/channel

Maximum Output Impedance

50mΩ

Available in either a three-phase orPower Supply

100-240Vac

single-phase & compatible with both

Supply Voltage

24Vdc ±5%50/60Hz systems

Supply Current

40mAdc @ 24Vdc

configurable CT ratios for added flexibility.
The Rogowski Integrator can be used onservices up to 60,000A AC.

Features••

Seven field-configurable CT ratios:
500A, 1kA, 2.5kA, 5kA, 10kA, 25kA, 50kA

•SAFETY/COMPLIANCE
Certifications

The 0-333mV rated output is compatiblewith any device with a 333mV nominal

ROGOWSKI COIL (Sold Separately)
Window Size

RCT16-1000 - 106.0mm (4.17’’)
RCT24-1000 - 178.0mm (7.01”)
RCT36-1000 - 271.0mm (10.67’’)
RCT47-1000 - 369.0mm (14.53’’)

Length of Coil

RCT16-1000 - 400.0mm (15.75’’)
RCT24-1000 - 600.0mm (23.62’’)
RCT36-1000 - 900.0mm (35.43’’)
RCT47-1000 - 1200.0mm (47.24’’)

Coil Material

Orange thermoplastic rubber
UL 94V-0 rated flame retardant

Lead Wires

1000V UL Style 20940, 26AWG

Wire Polarity

White=Positive, Brown=Negative,
Bare=ShieldPhase Orientation

Arrow Points Towards Loadcurrent transformer input•2.5A to 50,000A current sensing range
accommodates nearly any application•CE, RoHS, UL Listed (E359521)

The rope-style current transformer
flexes to fit into tight electrical panels•ELECTRICAL

CT ratios can be configured
independently for each channel

1Integrator’s Current Range Settings
PRIMARY INPUT (ARMS)SENSING RANGE (A)OUTPUT

CT RATIO

500

2.5 to 600

333mV@500A

500:333

1000

5 to 1200333mV@1000A

1000:333

2500

12.5 to 3000

333mV@2500A

2500:333

5000

25 to 6000333mV@5000A

5000:333

10000

50 to 12000

333mV@10000A

10000:33325000

125 to 30000

333mV@25000A

25000:33350000

250 to 60000

333mV@50000A

50000:333

Dimensions

SingleRogowskiIntegrator
SinglePhasePhase
RogowskiIntegrator
Kit
0.89” (22.7mm) 1.57” (40.0mm)

4.40”
4.40”(111.7mm)(111.7mm)

3.94”
3.94”(100(100.0.0mm)mm)

4.52”
4.52”(114.6mm)(114.6mm)

3.54”
3.54”(90.0mm)(90.0mm)

3.93”
3.93”(99.7mm)(99.7mm)100-240Vac to 24Vdc
Power Supply

3.93” (99.7mm)

4.52”
4.52”(114.6mm)(114.6mm)

0.89” (22.7mm) 1.57” (40.0mm)

1.37”(34.7mm)

3 Phase Rogowski Integrator
3 Phase Rogowski Integrator Kit
1.57”(40.0mm)

1.57” (40.0mm)

4.19” (106.3mm)
1.92” (50.6mm)

1.92” (50.6mm)

A-A ( 1 : 1 )2.44”
2.44”(62(62.0.0mm)mm)

3.94”
3.94”(100(100.0.0mm)mm)

2.44”
2.44”(62.0mm)(62.0mm)

3.54”
3.54”(90.0mm)(90.0mm)

3.56”
3.56”(90.5mm)(90.5mm)100-240Vac to 24Vdc
Power Supply

4.08” (103.7mm)

3.56” (90.5mm)* Power supply sold separatelyOrdering Information
Integrator

Model

Ordering Example

RIK

Integrator Output-RIKmVmV-313

Accuenergy Inc.
Los Angeles - Toronto - Pretoria
North America Toll Free: 1-877-721-8908
Web: www.accuenergy.com
Email: marketing@accuenergy.com

Channels

Power Supply Unit

Model

Ordering Example

AcuLink-RIK-PSU
AcuLink-RIK-PSU: 24Vdc Output

Revision Date: January 2024 Version: 1.0.3
Specs Subject To Change Without Notice.

2