Analog Signal Converters for Output Signals
MODEL

FA1-AT1B8Y1TE FA-ATS*M1Y*****
FA-ATFTMXY
FA-ATB8YTB
FA1-AT1B4Y1TE FA-Q6TCA
FA1-AT1B4Y1TB

User’s Manual(Detailed Edition)

Time and Wire Saving Devices

SAFETY PRECAUTIONS(Read these precautions before using the FA Goods products.)

Before using the products, please read this manual and the relevant manuals carefully, and pay full
attention to safety to handle the products correctly.
The precautions given in this manual are concerned with time and wire saving device only.
For the safety precautions of the programmable controller system, refer to the user's manual for the
programmable controller used.
If the equipment is used in a manner not specified by the manufacturer, the protection provided by theequipment may be impaired.
In this manual, the safety precautions are classified into two levels: "WARNINGCAUTIONWARNING" and "CAUTION".

Indicates that incorrect handling may cause hazardous
conditions, resulting in death or severe injury.
Indicates that incorrect handling may cause hazardous
conditions, resulting in minor or moderate injury orproperty damage.

Under some circumstances, failure to observe the precautions given under "CAUTION" may leadto serious consequences.
Observe the precautions of both levels because they are important for personal and system safety.

2

[Design Precautions]

WARNING●Configure safety circuits externally to ensure that the entire system operates safely even when a fault occurs in the external power
supply, the programmable controller, or the products. Failure to do so may result in an accident due to an incorrect output or
malfunction.
(1) Emergency stop circuits, protection circuits, and protective interlock circuits for conflicting operations (such as forward/reverse
rotations or upper/lower limit positioning) must be configured externally.
(2) Outputs may remain on or off due to a failure of a component such as a relay, transistor, and triac used for
digital signal converter outputs. Configure an external circuit for monitoring output signals that could cause a serious accident.
●In an output circuit for digital signal converter outputs, when a load current exceeding the rated current or an overcurrent caused
by a load short-circuit flows for a long time, it may cause smoke and fire. To prevent this, configure an external safety circuit, suchas a fuse.
●Configure a circuit so that the programmable controller is turned on first and then the external power supply. If the external power
supply is turned on first, an accident may occur due to an incorrect output or malfunction.

[Design Precautions]

CAUTION●Do not install the control lines or communication cables together with the main circuit lines or power cables. Keep a distance of100mm (3.94 inches) or more between them. Failure to do so may result in malfunction or failure due to noise.
●When using a terminal block conversion module for a high-speed counter module, do not install the control lines or communication
cables together with the main circuit lines or power cables. Keep a distance of 150mm (5.91 inches) or more between them.
Failure to do so may result in malfunction or failure due to noise.
●Keep a distance of 100mm (3.94 inches) or more between a thermocouple or RTD (Resistance Temperature Detector) and themain circuit line or AC control lines. Also, keep the thermocouple or RTD away from a circuit that includes harmonics, such as ahigh-voltage circuit and a load circuit of an inverter. If not, the thermocouple or RTD is more likely to be affected by noise, surges,
and induction.
●At power-on or power-off, a voltage may occur or a current may flow between output terminals for a moment. To use an analog
signal converter or analog terminal block conversion module, start the control after analog outputs become stable.
●Do not place an analog signal converter or analog terminal block conversion module near a device that generates magnetic noise.
●When a device such as a lamp, heater, or solenoid valve is controlled using a module for digital signal converter outputs, a large
current (approximately 10 times greater than normal) may flow when the output is turned from off to on. Therefore, select a module
for digital signal converter outputs that has a sufficient current rating.

[Installation Precautions]

WARNING●Shut off the external power supply (all phases) used in the system before installation. Failure to do so may result in electric shock
or damage to the products.

3

[Installation Precautions]

CAUTION●Use products in an environment that meets the general specifications in this manual. Failure to do so may result in electric shock,fire, malfunction, or damage to or deterioration of the products.
●Securely fix the products with a DIN rail or screws. Incorrect installation may cause malfunction, failure, or drop of the module.
When using the products in an environment of frequent vibrations, fix the products with screws.
●Tighten the screws within the specified torque range. Undertightening can cause drop of the screw, short circuit, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, or malfunction.
●Attach DIN rail stoppers on the right and left sides of the spring clamp conversion module (FA1-TESV**) to fix the module securely.
●Shut off the external power supply (all phases) used in the system before mounting or removing the products. Failure to do so may
result in damage to, malfunction of, or failure of the products.
●Do not directly touch any conductive parts and electronic components of the products. Failure to do so may cause malfunction or
failure of the products.
●Install the products in the correct orientation if it is specified. Failure to do so may result in damage to or deterioration of the
products.
●When drilling screw holes, be careful not to drop chips into the inside of the products or conductive parts. Such foreign matter cancause a fire, failure, or malfunction.
●When using modules for replacing digital signal converters or signal converters modules, use them correct combination. Incorrect
combination may cause failure.
●Shut off the power supply before installing/removing a module for replacing digital signal converters. Failure to do so may cause
failure or malfunction.
●Securely mount a module for replacing digital signal converters and signal conversion module on a digital signal converter andinstallation base. Failure to do so may cause damage to or drop of the products, or malfunction due to poor contact. Follow thecorrect procedure to install/remove them. Failure to do may cause damage to or drop of the products, or malfunction due to poor
contact.
●When a module for digital signal converters or signal conversion module is mounted on a digital signal converter or installationbase, hold the digital signal converter or installation base to transport them or install them to a panel. Holding the module for
digital signal converters or signal conversion module may cause drop or failure of the digital signal converter or installation base.

[Wiring Precautions]

WARNING●Shut off the external power supply (all phases) used in the system before wiring. Failure to do so may result in electric shock or
damage to the products.
●After wiring, attach the included terminal cover to the products before turning them on for operation. Failure to do so may result inelectric shock.
●Use copper conducters only a temperature rating of 75℃ or more.

4

[Wiring Precautions]

CAUTION●Use applicable solderless terminals and tighten them within the specified torque range. Failure to do so may cause failure, damage,or malfunction.
●Check the rated voltage and terminal layout before wiring to the products, and connect the cables correctly. Connecting a power
supply with a different voltage rating or incorrect wiring may cause a fire or failure.
●Do not install the control lines or communication cables together with the main circuit lines or power cables. Keep a distance of100mm or more between them. Failure to do so may result in malfunction due to noise.
●When using a terminal block conversion module for a high-speed counter module, do not install the control lines or communication
cables together with the main circuit lines or power cables. Keep a distance of 150mm (5.91 inches) or more between them.
Failure to do so may result in malfunction or failure due to noise.
●Keep a distance of 100mm (3.94 inches) or more between a thermocouple or RTD (Resistance Temperature Detector) and themain circuit line or AC control lines. Also, keep the thermocouple or RTD away from a circuit that includes harmonics, such as ahigh-voltage circuit and a load circuit of an inverter. If not, the thermocouple or RTD is more likely to be affected by noise, surges,
and induction.
●Do not place an analog signal converter or analog terminal block conversion module near a device that generates magnetic noise.
●Place the cables in a duct or clamp them. If not, dangling cable may swing or inadvertently be pulled, resulting in damage to the
products or cables or malfunction due to poor contact.
●Tighten the terminal screws within the specified torque range. Undertightening can cause short circuit, fire, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, or malfunction.
●Tighten the connector screws within the specified torque range. Undertightening can cause short circuit, fire, or malfunction.
Overtightening can damage the screw and/or products, resulting in drop, short circuit, fire, or malfunction.
●Securely connect connectors to the products. Failure to do so may cause malfunction.
●When disconnecting a cable from the products, do not pull the cable by the cable part. For the cable with connector, hold theconnector part of the cable. For the cable connected to the terminal block, loosen the terminal screw. Pulling the cable connectedto the products may result in malfunction or damage to the products or cable.
●Check the interface type and correctly connect the cable. Incorrect wiring (connecting the cable to an incorrect interface) may
cause failure of the products and external device.
●Prevent foreign matter such as dust or wire chips from entering the products. Such foreign matter can cause a fire, failure, or
malfunction.
●The products must be installed in control panels. Connect the main power supply to the products in the control panel through arelay terminal block. Wiring and replacement of the products must be performed by qualified maintenance personnel withknowledge of protection against electric shock.
●When connecting the products with a programmable controller, check that the product configuration is correct. An incorrect
configuration may cause failure or malfunction.
●Use the products with no force applied to their connectors. Applied force may cause failure or disconnection.
●Attach protective covers or signal conversion modules to unused connectors or empty slots of the products. Failure to do so may
cause a fire, failure, or malfunction due to foreign matter.
●When using modules for replacing digital signal converters or signal conversion modules, use them in the correct combination.
Incorrect combination may cause failure of a programmable controller, digital signal converter, installation base, or external device.
●Securely mount modules for replacing digital signal converters and signal conversion modules on a digital signal converter andinstallation base. Failure to do so may cause damage to or drop of the products, or malfunction due to poor contact. Follow thecorrect procedure to install/remove them. Failure to do so may cause damage to or drop of the products, or malfunction due topoor contact.
●Individually ground the FG terminal of the products with a ground resistance of 100 ohms or less. Failure to do so may result inelectric shock or malfunction.

5

[Startup and Maintenance Precautions]

WARNING●Do not touch any terminal while power is on. Doing so will cause electric shock or malfunction.
●Shut off the external power supply (all phases) used in the system before cleaning the products or retightening the terminal screws,
connector screws, or products fixing screws. Failure to do so may result in electric shock or cause failure or malfunction of the
products. Undertightening can cause drop of the screw, short circuit, or malfunction. Overtightening can damage the screw and/or
products, resulting in drop, short circuit, or malfunction.

[Startup and Maintenance Precautions]

CAUTION●Do not disassemble or modify the products. Doing so may cause failure, malfunction, injury, or a fire.
●Use any radio communication device such as a cellular phone or PHS (Personal Handy-phone System) more than 25cm away inall directions from the programmable controller and products. Failure to do so may cause malfunction.
●Shut off the external power supply (all phases) used in the system before mounting or removing the products. Failure to do so may
cause failure or malfunction of or damage to the products.
●After the first use of the products, do not connect/remove the products and cables more than 50 times (IEC 61131-2 compliant).
Exceeding the limit may cause malfunction.
●Startup and maintenance of a control panel must be performed by qualified maintenance personnel with knowledge of protection
against electric shock. Lock the control panel so that only qualified maintenance personnel can operate it.
●Before handling the products, touch a conducting object such as a grounded metal to discharge the static electricity from thehuman body. Failure to do so may cause failure or malfunction of the products.
●The ESD susceptibility symbol shown below is placed on the products. This symbol products is susceptible static electricity passed.
Before handling the connector, touch a conducting object such as a grounded metal to release the static electricity from yourbody. Failure to do so may cause the products to fail or malfunction. Do not touch the connector when the products is powered.
Doing so may result in injury or cause the products to malfunction due to the static electricity in your body.

[Disposal Precautions]
CAUTION●When disposing of the products, treat them as industrial waste.

[Transportation Precautions]

CAUTION●Do not apply shock that exceeds the shock resistance described in the general specifications during transportation since theproducts are precision devices. Doing so may cause failure of the module.
●The halogens (such as fluorine, chlorine, bromine, and iodine), which are contained in a fumigant used for disinfection and pest
control of wood packaging materials, may cause failure of the products. Prevent the entry of fumigant residues into the productor consider other methods (such as heat treatment) instead of fumigation. The disinfection and pest control measures must be
applied to unprocessed raw wood.

EMC and Low Voltage Directives
Compliance with the EMC Directive, which is one of the EU directives, has been mandatory for products sold within EU
member states since 1996 as well as compliance with the Low Voltage Directive since 1997.
For products compliant to the EMC and Low Voltage Directives, their manufacturers are required to declare complianceand affix the CE marking.
In some other countries and regions, manufacturers are required to make their products compliant with applicable laws or
regulations and attach a certification mark on the products as well (such as UK Conformity Assessed (UKCA) marking in
the UK, and Korea Certification (KC) marking in South Korea).
(1) Sales representative in EU member states
The sales representative in EU member states is:Company: MITSUBISHI ELECTRIC EUROPE B.V.
Address: Mitsubishi-Electric-Platz 1, 40882 Ratingen, Germany(2) Method of ensuring complianceTo ensure that FA Goods products maintain EMC and Low Voltage Directives when incorporated into other machineryor equipment, certain measures may be necessary. Please refer to "EMC and Low Voltage Directives Compliant
Manual" (50D-FA9010-108).

6

REVISIONS*The manual number is given on the bottom left of the last page.
Print Date

Revision*Manual Number

January, 2013

50D-FA9010-123

First edition

March, 2013

50D-FA9010-123-A

May, 2015

50D-FA9010-123-B

March, 2018

50D-FA9010-123-C

November, 2021

50D-FA9010-123-D

May, 2022

50D-FA9010-123-E

November, 2023

50D-FA9010-123-F

Added or modified parts
SAFETY PRECAUTIONS
Added or modified parts
EMC and Low Voltage Directives, Table of contents, 2. GENERAL
SPECIFICATIONS, 3. PERFORMANCE SPECIFICATIONS, 8. CONNECTABLE
MODULES AND CABLES
Added or modified parts
Product addition: FA-Q6TCA,
SAFETY PRECAUTIONS, EMC and Low Voltage Directives, REVISIONS, 3.
PERFORMANCE SPECIFICATIONS, 4. CONNECTABLE MODULES AND CABLES,
5. EXTERNAL DIMENSIONS, 6. INSTALLATION ORIENTATION, 7. CONNECTINGMETHOD, 13.TRADEMARKS
Added or modified parts
Product addition：FA1-AT1B4Y1TE,FA1-AT1B4Y1TB
SAFETY PRECAUTIONS, Table of contents, 1. INTRODUCTION,
3. PERFORMANCE SPECIFICATIONS,
4. CONNECTABLE MODULES AND CABLES,
5. EXTERNAL DIMENSIONS, 6. INSTALLATION ORIENTATION,
7. CONNECTING METHOD,
8. APPLICABLE SOLDERLESS TERMINALS AND FERRULE
Added or modified parts
3. PERFORMANCE SPECIFICATIONS
Added or modified parts
Product addition：FA1-AT1B8Y1TE
Table of contents, 1. INTRODUCTION, 2. GENERAL SPECIFICATIONS,
3. PERFORMANCE SPECIFICATIONS, 4. CONNECTABLE MODULES AND
CABLES, 5. EXTERNAL DIMENSIONS, 6. INSTALLATION ORIENTATION,
7. CONNECTING METHODThis manual confers no industrial property rights or any rights of any other kind, nor does it confer any patent licenses. Mitsubishi
Electric Engineering cannot be held responsible for any problems involving industrial property rights which may occur as a result ofusing the contents noted in this manual.

© 2013 (2023) MITSUBISHI ELECTRIC ENGINEERING COMPANY LIMITED7

CONTENTS
CONTENTS··················································································································································· 8
1. INTRODUCTION ········································································································································· 9
2. GENERAL SPECIFICATIONS ······················································································································· 9
3. PERFORMANCE SPECIFICATIONS ············································································································ 10
3-1. Output type 8-channel installation base, spring clamp terminal block type (FA1-AT1B8Y1TE) ····························· 10
3-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB) ··········································· 11
3-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE) ····························· 12
3-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB) ······································ 13
3-5. Voltage output signal conversion module (current input) (FA-ATSAM1YV****) ················································· 14
3-6. Current input Signal conversion module (current input) (FA-ATSAM1YA****) ··················································· 15
3-7. Voltage output signal conversion module (voltage input) (FA-ATSVM1YV****) ················································· 16
3-8. Current input Signal conversion module (voltage input) (FA-ATSVM1YA****)··················································· 17
3-9. Pass-through module (FA-ATFTMXY) ····································································································· 18
3-10. Terminal block ↔ connector conversion adapter (FA-Q6TCA) ···································································· 18
4. CONNECTABLE MODULES AND CABLES ·································································································· 19
5. EXTERNAL DIMENSIONS ·························································································································· 22
5-1. Output type 8-channel installation base, spring clamp terminal block type (FA1-AT1B8Y1TE) ····························· 22
5-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB) ··········································· 22
5-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE) ····························· 23
5-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB) ······································ 23
5-5. Signal conversion module (FA-ATS*M1Y*****), pass-through module (FA-ATFTMXY) ······································· 24
5-6. Terminal block ↔ connector conversion adapter (FA-Q6TCA) ······································································ 24
6. INSTALLATION ORIENTATION ·················································································································· 25
6-1. Output type 8-channel installation spring clamp terminal block type (FA1-AT1B8Y1TE) ····································· 25
6-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB) ··········································· 25
6-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE) ····························· 26
6-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB) ······································ 26
7. CONNECTING METHOD ···························································································································· 27
7-1. Connection example with a terminal block module of a programmable controller ·············································· 27
7-1-1. When a cable with a terminal block is used ························································································· 27
7-1-2. When a terminal block to connector conversion adapter is used ······························································ 28
7-1-3. When a discrete cable is used ········································································································· 29
7-2. Connection example when an additional 4-channel base is used ·································································· 30
7-3. Mounting/removing a signal conversion module························································································· 31
7-4. Wiring to a spring clamp terminal block ···································································································· 32
8. APPLICABLE SOLDERLESS TERMINALS ··································································································· 35
9. PRECAUTIONS ········································································································································ 36
10. GRATIS WARRANTY TERMS AND GRATIS WARRANTY RANGE·································································· 37
11. REPAIRABLE PERIOD AFTER DISCONTINUATION OF PRODUCTION··························································· 37
12. EXCLUSION FROM LIABILITY FOR OPPORTUNITY LOSS AND SECONDARY LOSS ····························································· 37
13. TRADEMARKS ······································································································································· 37

81. INTRODUCTION
This manual describes the specifications and handling of the analog signal converter, which consistsof the installation base (FA1-AT1B8Y1TE, FA-ATB8YTB, FA1-AT1B4Y1TE, FA1-AT1B4Y1TB), thesignal conversion module (FA-ATS*M1Y*****) and/or the I/O signal pass-through module (FAATFTMXY), and the terminal block ↔ connector conversion adapter for MELSEC-Q series terminal
block module (FA-Q6TCA).
The analog signal converter includes the signal conversion module mounted to the installation base.
The analog signal converter insulates signals (1 to 5VDC, 4 to 20mADC) between input and output
terminals, and among the channels, converts them to analog output signals, and outputs the converted
signals.

2. GENERAL SPECIFICATIONS
Item
Operating surrounding air temperature
Storage ambient temperature
Operating ambient humidity
Storage ambient humidity
Compliance with standard
Under intermittent vibration
Vibration resistance
Under continuous vibration

5 to 8.4Hz
8.4 to 150Hz
Sweep count5 to 8.4Hz
8.4 to 150Hz
Sweep countShock resistanceOperating atmosphere
Operating altitude *1
Installation location
Overvoltage category *2
Pollution level *3Specifications
0 to 55°C-25 to 75°C
5 to 95% RH, non-condensing
5 to 95% RH, non-condensing
JIS B 3502, IEC 61131-2
Half amplitude: 3.5mm
Constant acceleration: 9.8m/s2 (1G)
10 times each in X, Y, and Z directions
Half amplitude: 1.75mm
Constant acceleration: 4.9m/s2 (0.5G)－
Compliant with JIS B 3502 and IEC61131-2(147m/s2 (15G), 3 times each in X, Y, and Z directions)
No corrosive gas
2,000m or lower
Inside the control panel *4, Indoor use
II or lower
2 or lower*1：Do not use or store the module under the atmospheric pressure greater than that at an altitude of 0m.
*2：Indicates the section of the power supply to which the equipment is assumed to be connected, between the public power gridand the machinery within the premises.
*3：This is a guideline indicating the degree of the generation of conducting substances in the environment in which a device isused.
*4：The enclosure is suitably designed for those specific environmental conditions, as applicable, and enclosure rate meets IP20
and minimum type 1 of UL 50.

93. PERFORMANCE SPECIFICATIONS
3-1. Output type 8-channel installation base, spring clamp terminal block type (FA1-AT1B8Y1TE)
Model

FA1-AT1B8Y1TE

Item
Number of slots

8
M3 screw, 7.62mm pitch, spring-up screw with finger protector cover
Tightening torque range: 58.8 to 88.2Nꞏcm (6 to 9kgfꞏcm, 5.22 to 7.5lbfꞏin),Terminal block screw
Terminal block
UL standard conformity tightening torque： 59Nꞏcm, 5.22lbfꞏinApplicable wire
22 to 14 AWG: 0.3 to 2.0mm2 (when solderless terminals are used)
M4 × 0.7mm × 27mm or more
Screw
Installation method
Tightening torque range: 78 to 118Nꞏcm (8 to 12kgfꞏcm, 7 to 10lbfꞏin)
DIN rail
Applicable DIN rail: TH35-7.5Fe, TH35-7.5Al (compliant with IEC 60715)
External power supply
24VDC±10%12mA or lessCurrent consumption (24VDC)(not including current consumption of the module, the programmable controller, and the monitor device)
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 250g
*1: Mount a dummy module onto an unused slot to allow no empty slot.
*2: When connecting a cable to the installation base, push the cable connector in until it is locked. Failure to do so may cause poor contact.
*3: When the output of the programmable controller is within a range of 4 to 20mA and the FA-ATFTMXY signal pass-through module is used, thevoltage value corresponding to the input resistance of the connected device is detected as a monitor output. The current value can be calculatedby dividing the detected voltage by the input resistance.

●Block diagram
Connector for signals
input from the
CON1
programmablecontroller

4

3

2

1

20

19

18

17

16

15

14

13

12

11

10

9

8

7

6

5

Connector for signal output
Connector for signals
CON1，CON2
CON2
Connector pin array chart output to monitor(Top view)

4

3

2

1

20

19

18

17

16

15

14

13

12

11

10

9

8

7

6

5

9

10

9

10

9

10

9

10

9

10

9

10

9

10

9

10

5

6

5

6

5

6

5

6

5

6

5

6

5

6

5

6

7

8

7

8

7

8

7

8

7

8

7

8

7

8

7

8

4

3

2

1

3

1

2

3

1

2

3

1

2

3

1

2

3

1

2

3

1

2

3

PW

CH8-

1A

FG

FUSE

24G

+24V
OUT
24G
OUT

+24V

+24V
OUT
24G
OUT

2

8B

CH7-

5

1

8C

7

6

3

Connector
for the signal
conversion device

CH8

8A

8

CH8+

2

CH7

7B

CH7+

1

CH6

7C

CH6-

CH5

7A

CH5-

9

CH4

6B

11

10

CH3

6C

12

CH6+

CH2

6A

CH5+

CH1

5B

CH4-

5C

13

5A

14

4B

CH4+

4C

CH3-

4A

15

3B

16

3C

CH3+

3A

CH2-

2B

CH2+

2C

CH1-

17

2A

19

18

1B

20

1C

CH1+

Spring clamp
terminal block

CH1 output CH2 output CH3 output CH4 output CH5 output CH6 output CH7 output CH8 output
For the external wiring for CH1 to CH8 signal outputs, refer to the signal conversion module block diagram.
24VDC
External power supply

Earth

Notes:●For a device connected to a monitor output, use a device with sufficiently large input resistance. (Input resistance of 1MΩ or more isrecommended.) The monitor output signal is 1 to 5V.
●Use shielded cables for external wirings.
●Use an output signal conversion device. Using an input signal conversion device incorrectly may damage the product.
●An external power supply is connected between CON1 and CON2.
When a power supply is not used, apply short-circuit protection.
･Power supply terminal
For 24V: Pin No.3 or 4 For 24G: pin No.1 or 2
･Short-circuit protection
1) Set the connector on the programmable controller and monitor device side to NC (No connection).
2) Insulate pins at wire end for NCs.

Insulate each pin so that the conductive part is not exposed.
Installation base side
Pin No.
Signal
4
24V
3
24V
2
24G
1
24G

Programmable controller/monitor side
NC
NC
NC
NC

10

3-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB)
Model

FA-ATB8YTB

Item
Number of slots

8
M3 screw, 7.62mm pitch, spring-up screw with finger protector cover
Tightening torque range: 58.8 to 88.2Nꞏcm (6 to 9kgfꞏcm, 5.22 to 7.5lbfꞏin),Terminal block screw
Terminal block
UL standard conformity tightening torque： 59Nꞏcm, 5.22lbfꞏinApplicable wire
22 to 14 AWG: 0.3 to 2.0mm2 (when solderless terminals are used)
M4 × 0.7mm × 20mm or more
Screw
Installation method
Tightening torque range: 78 to 118Nꞏcm (8 to 12kgfꞏcm, 7 to 10lbfꞏin)
DIN rail
Applicable DIN rail: TH35-7.5Fe, TH35-7.5Al (compliant with IEC 60715)
External power supply
24VDC±10%6mA or lessCurrent consumption (24VDC)(not including current consumption of the module, the programmable controller, and the monitor device)
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 320g
*1: Mount a dummy module onto an unused slot to allow no empty slot.
*2: When connecting a cable to the installation base, push the cable connector in until it is locked. Failure to do so may cause poor contact.
*3: When the output of the programmable controller is within a range of 4 to 20mA and the FA-ATFTMXY signal pass-through module is used, thevoltage value corresponding to the input resistance of the connected device is detected as a monitor output. The current value can be calculatedby dividing the detected voltage by the input resistance.

●Block diagram

Notes:●For a device connected to a monitor output, use a device with sufficiently large input resistance. (Input resistance of 1MΩ or more isrecommended.) The monitor output signal is 1 to 5V.
●Use shielded cables for external wirings.
●Use an output signal conversion device. Using an input signal conversion device incorrectly may damage the product.
●An external power supply is connected between CON1 and CON2.
When a power supply is not used, apply short-circuit protection.
･Power supply terminal
For 24V: Pin No.3 or 4 For 24G: pin No.1 or 2
･Short-circuit protection
1) Set the connector on the programmable controller and monitor device side to NC (No connection).
2) Insulate pins at wire end for NCs.

Insulate each pin so that the conductive part is not exposed.
Installation base side
Pin No.
Signal
4
24V
3
24V
2
24G
1
24G

Programmable controller/monitor side
NC
NC
NC
NC

11

3-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE)
Model name

FA1-AT1B4Y1TE

Item
Number of slots
Applicable wire

Terminal block4
0.2 to 1.5mm2 (24 to 16 AWG),
Copper wire with a temperature rating of 75°C or more
0.25 to 1.5mm2 (24 to 16 AWG),
Copper wire with a temperature rating of 75°C or more
10mm
M4 × 0.7mm × 22mm or greater
Tightening torque range: 78 to 118Nꞏcm (8 to 12kgfꞏcm)

When a ferrule is not used(stranded wire or solid wire)
When a ferrule is used(stranded wire)

Wire strip length
Mounting screws

Modulemounting

DIN rail
External supply power

Applicable DIN rail︓TH35-7.5Fe，TH35-7.5Al（compliant with IEC 60715）
24VDC±10% (ripple ratio: within 5%, SELV and LIM or CLASS 2)
6mA or less(not includeing current consumption by the conversion device,
the Signal through device, the programmable controller,
and the monitor equipment)
Between input/output/power supply: 500VAC for 1 minute, 10MΩ or more
About 160g

Current consumption (24VDC)

Withstand voltage/insulation resistance
Weight*1: Mount a dummy module onto an unused slot to allow no empty slot.
*2: When connecting a cable to the installation base, push the cable connector in until it is locked. Failure to do so may cause poor contact.
*3: When the output of the programmable controller is within a range of 4 to 20mA and the FA-ATFTMXY signal pass-through module is used, the voltage
value corresponding to the input resistance of the connected device is detected as a monitor output. The current value can be calculated by dividing thedetected voltage by the input resistance.

●Block diagram

11

CH5-

10

9

CH6-

CH7+

8

7

CH7-

CH8+

6

5

+24V
OUT
24G
OUT

4

3

2

1

CH8+24V
OUT
24G
OUT

1

20

19

18

17

16

15

14

13

11

10

9

8

7

6

5

12

11

10

9

8

7

6

5

NC NC NC NC NC NC NC NC
9

10

9

10

9

10

9

5

6

5

6

5

6

5

6

7

8

7

8

7

8

7

8

CH1
1

2

CH2
3

1

2

CH3
3

1

2

CH expansion terminal(CH5 to CH8)

10

Connector for Signal conversion device

CH4
3

1

2

PW

3

FUSE

4C

12

CH6+

2

12

(FG)

CH5+

3

4B

CH4-

4

4A

13

CON2

3C

14

Connector for signal
output to monitor

(FG)

CH4+

13

3B

CH3-

14

3A

15

15

2C

16

16

(FG)

CH3+

17

2B

CH2-

18

2A

17

19

1C

18

20

(FG)

CH2+

1

1B

CH1-

2

1A

19

3

FG

20

4

24G

CH1+

CON1

+24V

Connector for signal output
CON1，CON2
Connector pin array chart(Top view)

Connector for signal
output to PLC

Spring clamp terminal block

CH1 output CH2 output CH3 output CH4 output
24VDC
External power supply

For external wirings from the signal input CH1 to CH4, refer tothe block chart of the Signal conversion device.
Earth

Notes:●For a device connected to a monitor output, use a device with sufficiently large input resistance. (Input resistance of 1MΩ or more isrecommended.) The monitor output signal is 1 to 5V.
●Use shielded cables for external wirings.
●Use an output signal conversion device. Using an input signal conversion device incorrectly may damage the product.
●An external power supply is connected between CON1 and CON2.
When a power supply is not used, apply short-circuit protection.
･Power supply terminal
For 24V: Pin No.3 or 4 For 24G: pin No.1 or 2
･Short-circuit protection
1) Set the connector on the programmable controller and monitor device side to NC (No connection).
2) Insulate pins at wire end for NCs.

Insulate each pin so that the conductive part is not exposed.
Installation base side
Pin No.
Signal
4
24V
3
24V
2
24G
1
24G

Programmable controller/monitor side
NC
NC
NC
NC

12

3-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB)
Model name

FA1-AT1B4Y1TB

Item
Number of slots

4
M3 screw, Pitch of 7.62mm, Self tightening screw with finger protector cover
0.3 to 2.0mm2 (22 to 14 AWG),
Copper wire with a temperature rating of 75°C or more

Terminal screw
Applicable wire

Terminal
block

58.8 to 88.2N・m (6 to 9kgf・cm, 5.22 to 7.5lbf・in,

Tightening torque

UL standard conformity tightening torque：59N・m , 5.22 lbf・in.)M4 × 0.7mm × 22mm or greater
Tightening torque range: 78 to 118Nꞏm (8 to 12kgfꞏcm)

Mounting screws

Modulemounting

DIN rail
External supply power

Applicable DIN rail︓TH35-7.5Fe，TH35-7.5Al（compliant with IEC 60715）
24VDC±10% (ripple ratio: within 5%, SELV and LIM or CLASS 2)
6mA or lessCurrent consumption (24VDC)(not includeing current consumption by the conversion device, the Signal through device,
the programmable controller, and the monitor equipment)
Withstand voltage/insulation resistance
Between input/output/power supply: 500VAC for 1 minute, 10MΩ or more
WeightAbout 220g
*1: Mount a dummy module onto an unused slot to allow no empty slot.
*2: When connecting a cable to the installation base, push the cable connector in until it is locked. Failure to do so may cause poor contact.
*3: When the output of the programmable controller is within a range of 4 to 20mA and the FA-ATFTMXY signal pass-through module is used, the voltage
value corresponding to the input resistance of the connected device is detected as a monitor output. The current value can be calculated by dividing thedetected voltage by the input resistance.

●Block diagram

CH5+

12

11

CH5-

CH6+

10

9

CH6-

CH7+

8

7

CH7-

CH8+

6

5

4

3

2

1

CH8-

2

1

20

19

18

17

16

15

14

13

12

11

10

9

8

7

6

5

12

11

10

9

8

7

6

5

NC NC NC NC NC NC NC NC
9

10

9

10

9

10

9

10

5

6

5

6

5

6

5

6

7

8

7

8

7

8

7

8

CH1
1

2

CH2
3

1

2

CH3
3

1

2

CH expansion terminal(CH5 to CH8)
Connector for
Signal conversion device

CH4
3

1

2

PW

3

FUSE

+24V
OUT
24G
OUT

+24V

+24V
OUT
24G
OUT

3

NC

CH4-

4

(FG)

13

CON2

4B

14

Connector for signal
output to monitor

4C

CH4+

13

3C

CH3-

14

4A

15

15

3A

16

16

3B

CH3+

17

2B

CH2-

18

2C

17

19

1C

18

20

2A

CH2+

1

1A

CH1-

2

1B

19

3

24G

20

4

(FG)

CH1+

CON1

FG

Connector for signal output
CON1，CON2
Connector pin array chart(Top view)

Connector for signal
output to PLC

Terminal block

CH1 output CH2 output CH3 output CH4 output

For external wirings from the signal input CH1 to CH4, refer to the block chart of the
Signal conversion device.
Earth

24VDC
External power supply

Notes:●For a device connected to a monitor output, use a device with sufficiently large input resistance. (Input resistance of 1MΩ or more isrecommended.) The monitor output signal is 1 to 5V.
●Use shielded cables for external wirings.
●Use an output signal conversion device. Using an input signal conversion device incorrectly may damage the product.
●An external power supply is connected between CON1 and CON2.
When a power supply is not used, apply short-circuit protection.
･Power supply terminal
For 24V: Pin No.3 or 4 For 24G: pin No.1 or 2
･Short-circuit protection
1) Set the connector on the programmable controller and monitor device side to NC (No connection).
2) Insulate pins at wire end for NCs.

Insulate each pin so that the conductive part is not exposed.
Programmable controller/monitor side
NC
NC
NC
NC

Installation base side
Pin No.
Signal
4
24V
3
24V
2
24G
1
24G

13

3-5. Voltage output signal conversion module (current input) (FA-ATSAM1YV****)
Model
Item
Number of points
Input(Programmable controller side)
Accuracy(to full-scale)

FA-ATSAM1YV05 FA-ATSAM1YV15 FA-ATSAM1YV010 FA-ATSAM1YV1010

1 point (1 channel)
4 to 20mA
250Ω
±0.1% or less (ambient temperature 25°C±5°C)±0.015% / °C or less0 to 5V
1 to 5V
0 to 10V-10 to +10V
2.5kΩ or more
OutputNone
Response speed*1
15ms or lessZero/span adjustment
Zero adjustment range: -2 to 2%, span adjustment range: 98 to 102%
Power supply
24VDC±10% (supplied from the installation base)
Current consumption (24VDC)
45mA or lessInsulation method
Transformer
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 40g
Approx. 40g
Approx. 40g
Approx. 40g*1: A time from when a startup pulse is input until the output level reaches 90%
Input range
Input resistance
Reference accuracy
Temperature characteristics
Output signal
Output allowable load resistance
Disconnection detection function●Block diagram

14

3-6. Current input Signal conversion module (current input) (FA-ATSAM1YA****)Model
FA-ATSAM1YA020
FA-ATSAM1YA420
Item
Number of points
1 point (1 channel)
Input range
4 to 20mA
Input(Programmable controller side) Input resistance250Ω
Reference accuracy±0.1% or less (Ambient temperature 25°C±5°C)
Accuracy(to full-scale)
Temperature characteristics±0.015% / °C or less
Output signal
0 to 20mA
4 to 20mA
Output allowable load resistance600Ω or less
OutputDisconnection detection function
None
Response speed*1
15ms or lessZero/span adjustment
Zero adjustment range: -2 to 2%, span adjustment range: 98 to 102%
Power supply
24VDC±10% (supplied from the installation base)
Current consumption (24VDC)
45mA or lessInsulation method
Transformer
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 40g
Approx. 40g*1: A time from when a startup pulse is input until the output level reaches 90%●Block diagram15

3-7. Voltage output signal conversion module (voltage input) (FA-ATSVM1YV****)
Model
Item
Number of points
Input(Programmable controller side)
Accuracy(to full-scale)

FA-ATSVM1YV05 FA-ATSVM1YV15 FA-ATSVM1YV010 FA-ATSVM1YV1010

1 point (1 channel)
1 to 5V
1MΩ or more
±0.1% or less (Ambient temperature 25°C±5°C)±0.015% / °C or less0 to 5V
1 to 5V
0 to 10V-10 to +10V
2.5kΩ or more
OutputNone
Response speed*1
15ms or lessZero/span adjustment
Zero adjustment range: -2 to 2%, span adjustment range: 98 to 102%
Power supply
24VDC±10% (supplied from the installation base)
Current consumption (24VDC)
45mA or lessInsulation method
Transformer
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 40g
Approx. 40g
Approx. 40g
Approx. 40g*1: A time from when a startup pulse is input until the output level reaches 90%
Input range
Input resistance
Reference accuracy
Temperature characteristics
Output signal
Output allowable load resistance
Disconnection detection function●Block diagram

16

3-8. Current input Signal conversion module (voltage input) (FA-ATSVM1YA****)Model
FA-ATSVM1YA020
FA-ATSVM1YA420
Item
Number of points
1 point (1 channel)
Input range
1 to 5V
Input(Programmable controller side) Input resistance1MΩ or more
Reference accuracy±0.1% or less (Ambient temperature 25°C±5°C)
Accuracy(to full-scale)
Temperature characteristics±0.015% / °C or less
Output signal
0 to 20mA
4 to 20mA
Output allowable load resistance600Ω or less
OutputDisconnection detection function
None
Response speed*1
15ms or lessZero/span adjustment
Zero adjustment range: -2 to 2%, span adjustment range: 98 to 102%
Power supply
24VDC±10% (supplied from the installation base)
Current consumption (24VDC)
45mA or lessInsulation method
Transformer
Withstand voltage, insulation resistance
750VAC for 1 minute, 10MΩ or higher between input/output/power supply
WeightApprox. 40g
Approx. 40g*1: A time from when a startup pulse is input until the output level reaches 90%●Block diagram17

3-9. Pass-through module (FA-ATFTMXY)
Model
FA-ATFTMXY
Item
Number of points
1 point (1 channel )Conversion type
When signals are passed throughWhen current is converted to voltage*1
Resistance
－
250Ω
Input
Resistor accuracy－±0.1% or less－Temperature characteristics of resistor±0.0025%/°C or less
Allowable I/O signal
Voltage: 10V or less, Current: 20mA or less
WeightApprox. 30g*1: When current is converted to voltage, short across terminals A and C of the installation base terminal block.

●Block diagram
Voltage/Current output: when signals are passed throughCurrent output: when current is converted to voltage

3-10. Terminal block ↔ connector conversion adapter (FA-Q6TCA)
Model

FA-Q6TCA

Item
Rated voltage, rated current

Voltage: 121VDC / 264VAC, Current: 2A (Terminal No.1 to 16) / 8A (Terminal No.17, 18)
66 to 89Nꞏcm (7 to 9kgfꞏcm, 6.08 to 7.81lbfꞏin)Tightening torque
WeightApprox. 80g

18

4. CONNECTABLE MODULES AND CABLES
Module model for a programmable controller

output range

Installation base

Signal conversion module

Cable model
FA-CBL**ATQ8YTMELSEC iQ-R series

R60DAI8

4 to 20mA
FA-CBL**ATQ8YA *1
FA-CBL**ATQ8YTMELSEC-Q series

Q68DAIN

4 to 20mA
FA-CBL**ATQ8YA *1

MELSEC-L series

L60DAIL8

4 to 20mA

FX3U-4DA
MELSEC-F series

4 to 20mA
FX3U-4DA-ADP

CC-Link IE TSN

NZGN2B-60DA4

FA-ATB8YTB
4 to 20mA

NZ2GFCE-60DAI8
CC-Link IE Field

4 to 20mA

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXY

FA-CBL**ATYF

NZ2GF2BN-60DA4
CC-Link

AJ65SBT2B-64DA

4 to 20mA

Programmable controllers
from various manufacturers

General-purpose analog
input module

4 to 20mA

Computers from various manufacturers

4 to 20mA

MELSEC iQ-R series

1 to 5V

FA-CBL**ATQ8YT
R60DAV8

FA-CBL**ATQ8YA *1
FA-CBL**ATQ8YTMELSEC-Q series

Q68DAVN

1 to 5V
FA-CBL**ATQ8YA *1

MELSEC-L series

L60DAVL8

1 to 5V

FA-CBL**ATYF

FX3U-4DA
MELSEC-F series

1 to 5V
FX3U-4DA-ADP
NZGN2B-60DA4

CC-Link IE TSN

FA3-AT1T8Y-01C

1 to 5V

FA1-AT1B8Y1TE
FA-ATB8YTB

FA3-AT1T8Y
NZ2GFCE-60DAV8
CC-Link IE Field

1 to 5V

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXY

NZ2GF2BN-60DA4

FA-CBL**ATYF

Use the cable that comeswith the product.
FA3-CB2L**MM1H20

FA-CBL**ATYF

AJ65SBT2B-64DA
CC-Link

FA3-AT1C8Y-01C

Use the cable that comeswith the product.

1 to 5V

FA3-AT1C8Y
Programmable controllers
from various manufacturers

General-purpose analog
input module

Computers from various manufacturers

FA3-CB2L**MM1H20
1 to 5V
FA-CBL**ATYF
1 to 5V*1: When the FA-Q6TCA is used on the MELSEC iQ-R series / MELSEC-Q series programmable controller side.

19

Module model for a programmable controller

Number ofchannels

Cable for
output range dispersed
installation

Installation base

Signal conversion module

Cable model
FA-CBL**ATQ8YT

R60DAI8

8
FA-CBL**ATQ8YA *1

MELSEC iQ-R series

4 to 20mA
R60DAH44

FA1-CB2L**AT4YA1T

R60DA4FA-CBL**ATQ8YTQ68DAIN

8
FA-CBL**ATQ8YA *1

MELSEC-Q series

4 to 20mA
Q64DAH
4
Q64DANMELSEC-L series

L60DA44

4 to 20mA

MELSEC iQ-F series

FX5-4DA44 to 20mA

4

4 to 20mA

4

4 to 20mA

4

4 to 20mA

4

4 to 20mA

FA1-AT1B4Y1TE,
FA1-AT1B4Y1TB―

FX3U-4DA
MELSEC-F series
FX3U-4DA-ADP

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXYNZ2GN2S-60DA4
CC-Link IE TSN

FA1-CB2L**AT4YA1T

FA-CBL**ATYF
FA2-CB2L**AT4YA1E

FA-CBL**ATYF

FA3-CB2L**AT4YA1E

NZ2GN2B-60DA4
CC-Link IE Field
CC-Link
Programmable controllers
from various manufacturers

NZ2GF2BN60DA4AJ65SBT2B64DA
General-purpose
analoginput module

Computers from various manufacturers

Differs
depending on
the module.
Differs
depending on
the computer.

FA-CBL**ATYF
4 to 20mA

4 to 20mA
FA-CBL**ATQ8YT

R60DAV88
FA-CBL**ATQ8YA *1

MELSEC iQ-R series

1 to 5V
R60DAH44

FA1-CB2L**AT4YV1T

R60DA4FA-CBL**ATQ8YTQ68DAVN

8
FA-CBL**ATQ8YA *1

MELSEC-Q series

1 to 5V
Q64DAH
4

FA1-CB2L**AT4YV1T

Q64DANMELSEC-L series

L60DA44

1 to 5V

MELSEC iQ-F series

FX5-4DA4

1 to 5V

4

1 to 5V

FA-CBL**ATYF

FX3U-4DA
MELSEC-F series
FX3U-4DA-ADP

FA1-AT1B4Y1TE,
FA1-AT1B4Y1TB―
FA3-AT1T8Y-01C
8
CC-Link IE TSN

FA3-AT1T8Y

1 to 5V

NZ2GN2S-60DA4

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXY

FA2-CB2L**AT4YV1E

FA-CBL**ATYF
Use the cable thatcomeswith the product.
FA3-CB2L**MM1H20
FA3-CB2L**AT4YV1E

4NZ2GN2B-60DA4
CC-Link IE Field

NZ2GF2BN60DA4
FA3-AT1C8Y01C

CC-Link

FA-CBL**ATYF
4

Use the cable thatcomeswith the product.

8
1 to 5V

FA3-AT1C8Y
AJ65SBT2B64DA
General-purpose
analoginput module

1 to 5V

FA3-CB2L**MM1H20

4

Differs
Programmable controllers
depending on
1 to 5V
from various manufacturers
the module.
Differs
Computers from various manufacturers
depending on
1 to 5V
the module.
*1: When the FA-Q6TCA is used on the MELSEC iQ-R series / MELSEC-Q series programmable controller side.

20

FA-CBL**ATYF

Module model for a programmable controller

Number ofchannels

Cable for
output range dispersed
installation

Installation base

Signal conversion module

Cable model
FA-CBL**ATQ8YTMELSEC iQ-R series

R60DAI8

8

4 to 20mA
FA-CBL**ATQ8YA *1

MELSEC-Q series

Q68DAIN

8

MELSEC-L series

L60DAIL8

Programmablecontrollers
from various
manufacturers

General-purpose Differs
depending on
analoginput module
the module.

4 to 20mA

Differs
depending on
the computer.

4 to 20mA

8

1 to 5V

Computers from various manufacturers

8

4 to 20mA

4 to 20mA

FA1-CB2L**AT4EX

FA1-AT1B4Y1TE × 2,
FA1-AT1B4Y1TB × 2

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXY

FA-CBL**ATQ8YT
FA-CBL**ATQ8YA*1

FA-CBL**ATYF

FA-CBL**ATQ8YTMELSEC iQ-R series

R60DAV8

FA-CBL**ATQ8YA *1
FA-CBL**ATQ8YTMELSEC-Q series

Q68DAVN

8

1 to 5V
FA-CBL**ATQ8YA *1

MELSEC-L series

L60DAVL8

8

1 to 5V

8

1 to 5V

FA3-AT1T8Y-01C
CC-Link IE TSN
FA3-AT1T8Y
FA3-AT1C8Y01C
CC-Link

FA1-AT1B4Y1TE × 2
FA1-AT1B4Y1TB × 2

8

FA3-AT1C8Y
AJ65VBTCU68DAVN

Programmablecontrollers
from various
manufacturers

FA1-CB2L**AT4EX

1 to 5V

Voltage output
FA-ATSAM1Y05,
FA-ATSAM1YV010,
FA-ATSAM1YV15,
FA-ATSAM1YV1010
Current output
FA-ATSAM1YA020,
FA-ATSAM1YA420
When signals are passed throughFA-ATFTMXY

FA-CBL**ATYF
Use the cable thatcomes with the product.
FA3-CB2L**MM1H20
Use the cable thatcomes with the product.
FA3-CB2L**MM1H20

4

General-purpose Differs
analogdepending on
input module
the module.

1 to 5V

FA-CBL**ATYF

Differs
depending on
1 to 5V
the computer.
*1: When the FA-Q6TCA is used on the MELSEC iQ-R series / MELSEC-Q series programmable controller side.

Computers from various manufacturers

21

5. EXTERNAL DIMENSIONS
5-1. Output type 8-channel installation base, spring clamp terminal block type (FA1-AT1B8Y1TE)[Unit：mm]
134

25

6.5

CON1 CON2

30.2

24.5

20

RJC

170.5

RJC

RJC

RJC

35.5

RJC

RJC

(5)

RJC

22.8
39.9

8.5

PW

RJC

74.2

2-φ4.52-φ847.5

5-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB)[Unit：mm]22

5-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE)[Unit：mm]
１２３

４.５
１３

ＲＪ Ｃ

ＲＪ Ｃ

１３２

８.５

ＲＪ Ｃ

５

ＲＪ Ｃ

３５.５

ＰＷ

７４.２

ＣＯＮ１ ＣＯＮ２

６５.２

４.２

(３０.２)

２-φ４.５×５.１Long hole

１７.７
２５.８

１３

６４.４

5-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB)[Unit：mm]
４.５
１３

３５.５

５

ＰＷ

７４.２

ＣＯＮ１ ＣＯＮ２

６５.２

４.２

(３０.２)

２-φ４.５×５.１Long hole

１３２

１７.７
４１.４

１３

８１

23

８.５

１２３

5-5. Signal conversion module (FA-ATS*M1Y*****), pass-through module (FA-ATFTMXY)[Unit：mm]

42.1
39.3

Connector pin layout(bottom view)

5-6. Terminal block ↔ connector conversion adapter (FA-Q6TCA)[Unit：mm]
When the Q68DAVN is connected24

6. INSTALLATION ORIENTATION
6-1. Output type 8-channel installation spring clamp terminal block type (FA1-AT1B8Y1TE)
Horizontal installation

Vertical installation

RJC

RJC

PW

CON1 CON2

CON1 CON2

PW

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC
RJC

RJC
RJC

RJC
RJC

RJC
RJC

RJC

Upward installation

RJC
PW

CON1 CON2

RJC

6-2. Output type 8-channel installation base, screw terminal block type (FA-ATB8YTB)
Horizontal installation

Vertical installation

Upward installation25

6-3. Output type 4-channel installation base, spring clamp terminal block type (FA1-AT1B4Y1TE)
Vertical installation

ＣＯＮ１ ＣＯＮ２

ＲＪＣ

ＣＯＮ１ ＣＯＮ２

ＰＷ

Horizontal installation

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＰＷ

ＲＪＣ

ＲＪＣ

ＲＪＣ
ＲＪＣ
ＲＪＣ

ＣＯＮ１ ＣＯＮ２

ＲＪＣ

Upward installation

ＰＷ

6-4. Output type 4-channel installation base, screw terminal block type (FA1-AT1B4Y1TB)
Vertical installation
ＣＯＮ１ ＣＯＮ２

ＰＷ

Horizontal installation
ＣＯＮ１ ＣＯＮ２

ＰＷ

ＰＷ

26

ＣＯＮ１ ＣＯＮ２

Upward installation

7. CONNECTING METHOD
7-1. Connection example with a terminal block module of a programmable controller
7-1-1. When a cable with a terminal block is used

Connect the terminal block securely tothe programmable controller moduleusing installation screws.
Programmablecontroller
*1

Cable

Insert the connector fully to
fix it securely.
*1

Ground the FG wires to the panel(Ground both ends of the cable).
CON1 CON2

FA1-AT1B8Y1TE
PW

FA-ATB8YTB

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

ＣＯＮ１ ＣＯＮ２

FA1-AT1B4Y1TE

ＰＷ

FA1-AT1B4Y1TB

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

*1: Ground the FG wires of the cable to the panel.
If the values retrieved by the programmable controller vary greatly due to noise, install a ferrite core(such as the ESD-SR-250 manufactured by TOKIN Corporation) on the unshielded part of the cable.
*2: Instead of a 8-channel analog unit, two 4-channel bases can be used. To connect two bases, refer to 7-2.

27

7-1-2. When a terminal block to connector conversion adapter is used

Connect
the theadapterConnect
adaptersecurely
securely toto
theprogrammablecontroller
the programmable controller
moduleusing
installation screws.
screws.
moduleusing
installation

Insert the connector fully to
fix it securely.

Programmablecontroller*1
Terminal block toconnector conversion
adapter

Cable

Insert the connector fully to
fix it securely.
*1

Ground the FG wires to the panel(Ground both ends of the cable).
CON1 CON2

FA1-AT1B8Y1TE
PW

FA-ATB8YTB

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

ＣＯＮ１ ＣＯＮ２

FA1-AT1B4Y1TE

ＰＷ

FA1-AT1B4Y1TB

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

*1: Ground the FG wires of the cable to the panel.
If the values retrieved by the programmable controller vary greatly due to noise, install a ferrite core(such as the ESD-SR-250 manufactured by TOKIN Corporation) on the unshielded part of the cable.
*2: Instead of a 8-channel analog unit, two 4-channel bases can be used. To connect two bases, refer to 7-2.

28

7-1-3. When a discrete cable is used
CC-Link module, non-Mitsubishi
programmable controller, or others[FA-CBL**ATYF pin assignment]

Wire the cable securely to theterminal block of the
programmable controller module.

Signal name
CH1+
CH1CH2+
CH2CH3+
CH3CH4+
CH4CH5+CH5CH6+
CH6CH7+
CH7CH8+CH824V
24V
24G
24G

Cable

*1

Ground the FG wires to the panel.

Insert the connector fully to
fix it securely.

Cable color
Pink
YellowWhite
GrayOrangePink
YellowWhite
GrayOrange

Dot
2
2
2
2
2
2
2
2
2
2
1
1
1
1
1
1
1
1
1
1

Dot
color
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red
Black
Red

CON1 CON2

FA1-AT1B8Y1TE
FA-ATB8YTB

PW

RJC

RJC

RJC

RJC

RJC

RJC

RJC

RJC

ＣＯＮ１ ＣＯＮ２

FA1-AT1B4Y1TE
FA1-AT1B4Y1TB

ＰＷ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

*1: Ground the FG wires of the cable to the panel.
If the values retrieved by the programmable controller vary greatly due to noise, install a ferrite core(such as the ESD-SR-250 manufactured by TOKIN Corporation) on the unshielded part of the cable.
*2: Instead of a 8-channel analog unit, two 4-channel bases can be used. To connect two bases, refer to 7-2.

29

7-2. Connection example when an additional 4-channel base is used
Connect the base as shown in the figure below.

Expansion cable
FA1-CB2L**AT4EX(*1)
the installation base 1
FA1-AT1B4Y1TE,
FA1-AT1B4Y1TB

the installation base 2
FA1-AT1B4Y1TE,
FA1-AT1B4Y1TB

ＣＯＮ１ ＣＯＮ２

ＣＯＮ１ ＣＯＮ２

ＰＷ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＰＷ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

ＲＪＣ

24VDC

*1: When the base is added, note that CH1 to CH4 and CH5 to CH8 change places with each other.
(Refer to the following table.)
Monitor display
Order of channels displayed on the monitor
When a 8-channel base is used When a 4-channel base is used When two 4-channel bases are used*1
CH1
CH1
CH5
CH2
CH2
CH6
CH3
CH3
CH7
CH4
CH4
CH8
CH5
―
CH1
CH6
―
CH2
CH7
―
CH3
CH8
―
CH4
*1: When two 4-channel bases are used, channels of the added base are displayed first.

30

7-3. Mounting/removing a signal conversion module(1) How to mount the module to theinstallation base(2) How to remove the module from theinstallation base1) Align the signal conversion module with a slot of
the installation base.

1) Hold both sides of the mounting/removing
hooks.

Attaching/removing
hook2) Insert the signal conversion module until themounting/removing hooks are locked (until
they click).

2) Pull out the signal conversion module while
holding the hooks.

Attaching/removing
hook

Note
Use an output type signal conversion module (the one with a orange line). Using an input type signal conversion module (theone with an purple line) incorrectly may cause failure of the products.
Points(1) Hold the installation base, not the signal conversion module, when transporting the installation base with the signal conversion
module mounted or when installing it to a panel.
(2) Mount a dummy module (FA-ATNDM) onto an empty slot of the installation base for dust prevention.

31

7-4. Wiring to a spring clamp terminal block(1) Wires routing(a) Fabrication on cable insulator
Strip the wire as follows. If the length of the sheath peeled is too long, a short circuit may occur withneighboring
wires. If the length is too short, wires might come off. Wire the stripped cable after twisting it to prevent it frombecoming loose. In addition, do not solder it.

10mm(b) Using a ferrule terminal
Insert wires to a ferrule terminal and crimp it. Make sure that core wire slightly comes out of the ferrule.
Check the condition of the ferrule terminal after crimping. Do not use a ferrule terminal of which the crimping is
inappropriate, or the face is damaged.
Refer to chapter 9 for the applicable ferrule terminal.
* Ferrule terminals crimped onto one wire are applicable to the terminal block of this product.
If multiple wires need to be installed (such as for the power supply), provide an external common terminal.
(For example, ABCOM of a high-speed counter module or COM of a simple motion module)32(c) Inserting wires
The wire with ferrule or solid cable can be inserted into the wire insertion hole. Afterinserting, pull the wire lightly to confirm that the wire is surely connected.
For the correct terminal insertion direction, refer to the figure below.
When binding twisted wires, press the push button using the screw driver, then insert the twisted wires
into the wire insertion hole.
* Make sure to insert the wire straight as far as it will go.

(Push button)

Cable insert ion holeFerrule terminals

33

(2) Wires removal
Press the push button all the way using the screw driver, then pull out the wire.

(Push button)

Cable insertion hole

Use the screw driver shown in the table below.
Manufacturer
PHOENIX CONTACT

Recommended tool (screw driver)Model
SZS 0,4×2,5 VDE

34

Blade edge size
2.5x0.4mm

8. APPLICABLE SOLDERLESS TERMINALS● Solderless terminal dimensions[Unit：mm]

Round non-insulated solderless terminal

Round insulated solderless terminal

Y-shaped non-insulated solderless terminal

Y-shaped insulated solderless terminal● Terminal block shape[Unit：mm]

35

● Applicable solderless terminals (ferrule)Type
Manufacturer

Applicable wire size

PHOENIX CONTACT

0.25 ㎟ (AWG24)
0.34 ㎟ (AWG22)
0.5 ㎟ (AWG20)
0.75 ㎟ (AWG18)
1.0 ㎟ (AWG18)
1.5 ㎟ (AWG16)

Applicable ferrule

Crimp tool

AI 0,25-10 YE
AI 0,34-10 TQ
AI 0,5-10 WH
AI 0,75-10 GY
AI 1-10 RD
AI 1,5-10 BKCRIMPFOX 6

9. PRECAUTIONS(1) Allow the product to warm up for 10 minutes or more as a precautionary measure though this product works at the same time as powering
it on.
(2) Since the signal conversion module had been calibrated at the factory, calibration at the site is not necessary. However, when thecalibration is required for the conformity between the signal conversion module and other connected device, make the zero/span
adjustment as follows:(Trimmer operation… Turning to the right (in clockwise) for increasing a value,
Turning to the left (in counterclockwise) for decreasing a value)
1) Allow the product to warm up for 10 minutes or more after powering it on.
2) Input the signal equivalent to 0% in the input range, and adjust output signal to 0% by using the zero adjustment trimmer.
3) Input the signal equivalent to 100% in the input range, and adjust output signal to 100% by using the span adjustment trimmer.
4) Complete the zero/span adjustment by repeating the operation in Step 2 and 3.
5) Input the signal of 25%, 50%, and 75% in the input range, and check the output linearity(3) When the monitor output is used, the handling is different depending on the usage condition of the module. The following table lists
the handling of each module.
Programmable
Signal conversion module,
Installation baseMonitor output*1, *2
controller analog
Pass-through module
terminal block
output signal
Output signals that
4 to 20mA
1 to 5V
differ depending on
FA-ATS*M1Y*****
the signal
1 to 5V
1 to 5V
conversion modules
When signals are passed through4 to 20mA*3
4 to 20mA
FA-ATFTMXY when current is converted to voltage
1 to 5V
1 to 5V
1 to 5V
When signals are passed through1 to 5V
1 to 5V*1: For a measuring device connected to a monitor output, use a device with sufficiently large input resistance.
(Input resistance of 1MΩ or more is recommended.)*2: Do not short across connector pins No.1 to 4 for monitor output of the installation base FA-ATB8YTB (output type) since the pins
are assigned to 24V/24G.
*3: The voltage value corresponding to the input resistance (R) of the connected external device is detected. The current value (I)can be calculated with the monitor output voltage (V) and the input resistance (R) by the following formula.
I=V/R
Example) When R (the input resistance of the connected external device) = 500Ω, and V (the measured
voltage value) = 5V, the formula for I (the detected current) is as below.
5V / 500Ω = 10mA

36

10. GRATIS WARRANTY TERMS AND GRATIS WARRANTY RANGE
If any fault or defect (hereinafter referred to as "Failure") attributable to Mitsubishi Electric Engineering should occur within the gratis
warranty period, Mitsubishi Electric Engineering shall replace the product free of charge via the distributor from whom you made yourpurchase.
● Gratis warranty period
The gratis warranty period of this product shall be one (1) year from the date of purchase or delivery to the designated place.
● Gratis warranty range(1) The gratis warranty range shall be limited to normal use based on the usage conditions, methods and environment, etc., defined by
the terms and precautions, etc., given in the instruction manual, user’s manual, and caution labels on the product.
(2) In the following cases, a repair fee shall be applied even if within the gratis warranty period.
1) Failure resulting from inappropriate storage or handling, carelessness or negligence by the user, or Failure caused by the user's
hardware or software design.
2) Failure caused by unapproved modifications, etc., to the product by the user.
3) Failure that could have been avoided if, when the Mitsubishi Electric Engineering product was assembled into the user's device,safeguards defined by legal regulations applicable to the user's device or functions or structures considered standard by theindustry had been provided.
4) Failure recognized as preventable if the consumed products specified in instruction manuals, etc., were normally maintained or
replaced.
5) Replacement of consumable parts (relays, etc.).
6) Failure caused by external factors beyond anyone's control such as fires or abnormal voltage, and Failure caused by Force
Majeure such as earthquakes, lightning, or wind and water damage.
7) Failure caused by reasons unpredictable by scientific technology standards at the time of shipment from Mitsubishi ElectricEngineering.
8) Any other failure not attributable to Mitsubishi Electric Engineering or found by the user to not be attributable to Mitsubishi ElectricEngineering.

11. REPAIRABLE PERIOD AFTER DISCONTINUATION OF PRODUCTION(1) The period in which product repair (fee applied) is available is seven (7) years after product discontinuation.
Discontinuation of production shall be reported by the distributor.
(2) Product supply (including spare parts) is not possible after production has been discontinued.

12. EXCLUSION FROM LIABILITY FOR OPPORTUNITY LOSS AND SECONDARY LOSS
Regardless of the gratis warranty period, Mitsubishi Electric Engineering shall not be liable for compensation for damages arising from causes not
attributable to Mitsubishi Electric Engineering, opportunity losses or lost profits incurred by the user due to Failures of Mitsubishi Electric Engineering
products, damages or secondary damages arising from special circumstances, whether foreseen or unforeseen by Mitsubishi Electric Engineering,compensation for accidents, compensation for damages to products other than Mitsubishi Electric Engineering products, or compensation for
replacement work, readjustment of onsite machinery and equipment, startup test runs or other duties carried out by the user.

13. TRADEMARKSMELSEC, MELSEC iQ-R, MELSEC iQ-F, CC-Link, CC-Link IE, CC-Link IE/field, CC-Link IE/TSN and CC-Link/LT are trademarks or registeredtrademarks of Mitsubishi Electric Corporation. Other company names and product names in the text are trademarks or registered trademarks of eachcompany.
In some cases, trademark symbols such as '™' or '®' are not specified in this manual.

FOR SAFE OPERATIONS● This product has been manufactured as a general-purpose part for general industries, and has
not been designed or manufactured to be incorporated in a device or system used in purposes
related to human life.
● Before using the product for special purposes such as nuclear power, electric power, aerospace,
medicine or passenger movement vehicles, consult with Mitsubishi Electric Engineering.
● This product has been manufactured under strict quality control. However, when installing the
product where major accidents or losses could occur if the product fails, install appropriate backup
or failsafe functions in the system.

37

NAGOYA ENGINEERING OFFICE

50D-FA9010-123-F(2311)MEE

1-9, Daiko-Minami, 1-Chome, Higashi-ku, Nagoya, Aichi 461-0047 Japan
Phone +81-52-6495 URL:https://www.mitsubishielectricengineering.com/

New publication, effective Nov. 2023.
Specifications subject to change without notice.