Short String Inverter, for India
SE5K-INB
12 – 25YEARWARRANTY

INVERTERS

SolarEdge Home

The ideal solution for small-scale residential PV systems
Greater design flexibility by enabling
significantly shorter strings for low power threephase PV systems

Excellent reliability with standard 12-year
warranty (extendable to 20 or 25 years)

Optimized for installations with complex roofs(multi-facets and different orientations)

Advanced safety features, including touch-safe
DC voltage when the inverter is off ordisconnected

Supports optional smart energy devices andexpansion of system capabilities

Quick inverter commissioning directly from theSetApp smartphone appSingle vendor solution for seamless operationof all system components, and one address forwarranty and service issues

Suitable for outdoor or indoor installations

Built-in module-level monitoring for greater
visibility into system performancesolaredge.com

SolarEdge Home
Short String Inverter, for India
SE5K-INB
Applicable to inverters with part number

SE5K-INBTEBEN4

Unit

Rated AC Power Output

5000

VA

Maximum AC Power Output

5000

VAAC Output Line Connections

3-phase, 4-wire / PE (L1-L2-L3-N), TN, TT

OUTPUTAC Output Voltage – Line to Line / Line to Neutral (Nominal)
AC Output Voltage – Line to Line / Line to Neutral Range
AC Frequency Range

400/230

Vac320-478/180-264.5

Vac50/60 ± 5

Hz8A

Maximum Continuous Output Current (per Phase)
Grids Supported

3 / N / PE (WYE with Neutral)

Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds

Yes

INPUT
Maximum DC Power (Module STC)

6750

Transformer-less, UngroundedYes

Maximum Input Voltage

450

Vdc

Nominal DC Input Voltage

375

Vdc

Maximum Input Current

14

Ground-Fault Isolation Detection

W350 kΩ sensitivity

Maximum Inverter efficiency

97.8%

European Weighted Efficiency

96.3%

Reverse-Polarity Protection

Yes

Typical Nighttime Power Consumption<4W

ADDITIONAL FEATURES
Supported Communication Interfaces
Inverter Commissioning
Smart Energy Management

2 x RS485, Ethernet, Wi-Fi, Wireless SolarEdge Home Network (optional)
With the SetApp mobile application using built-in Wi-Fi station for local connection
Export Limitation, Home Energy Management (Device Control)

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Electromagnetic Compatibility (EMC)
Environmental

IEC-62109-1/2, IEC-62103 (EN50178)IEC 61727 & IEC 62116
EN/IEC 61000-6-1, EN/IEC 61000-6-2, EN/IEC 61000-6-3, EN/IEC 61000-6-4, EN 55011,
FCC Part 15, EN/IEC 61000-3-2, EN/IEC 61000-3-3
IEC-60068-2-1, IEC-60068-2-2, IEC-60068-2-14, IEC-60068-2-30, IEC-60529

RoHSYes

INSTALLATION SPECIFICATIONSAC Output

Cable gland diameter 15 – 21DC Input

2 x MC4 pairs

Dimensions (H x W x D)mm

540 x 315 x 260

mm

Weight25kg

Cooling

Fan (user replaceable)

Noise
Operating Temperature Range
Protection Rating
Mounting
Number of Power Optimizers per String< 50dBA-40 – +60ºC

IP65 - outdoor and indoor
Brackets provided
8(1)/9 to 20

Maximum Power per String

5625(1) When using S500B/S650B/P404/P485/P505 power optimizers only, a minimum of eight power optimizers are required per string.

© SolarEdge Technologies, Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge Technologies, Inc.
All other trademarks mentioned herein are trademarks of their respective owners. Date: June 21, 2023 DS-000195-IND. Subject to change without notice.