1 Wastewater treatment equipment

１Wastewater treatment equipment |1-1.

Elepon E.C.A.P. Corporation - ｐH Control Unit -I. Basic type ----Features-.Easy installation or movement.by unitization- Saving installation cost and economy- Easy maintenance by compacting equipment- Supporting neutralization treatment of acid wastewater- Grasping flow rate in terms of triangle sluice
Overview-.pH Control Unit of PB type is developed for site ofconstruction and engineering works and can be continuously
neutralized with stable pH control by addition on-site strong alkali wastewater to sulfuric acid,hydrochloric acid, etc., furthermore installed or moved easy by compacting equipment.
- The Unit treats within 5.8 - 8.6 as pH to various industrial wastewater contained acid/alkali, and has
the function of continuous record on pH value after neutralization in record tank.

Raw watertankControl panel
Neutralization pH
Effluent Sulfuric acidtanktank
Recordingtank
Flow diagram of treatment system

Performance/Specifications- Specifications of PB series
Type(Standard treatment
capacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemicalpump, pH electrode)
Recording tank volume(SS400+ Inside:epotal pH electrode)Sulfuric acid tank (PE tank)

PB-01

PB-03

PB-05

PB-10

PB-15

PB-20

PB-30

(1m3/hr)(3m3/hr)(5m3/hr)(10m3/hr)(15m3/hr)(20m3/hr)(30m3/hr)

0.25m30.72 m3

1.1 m3

2.4 m3

3.5 m3

4.8 m37.0 m30.2 m3

0.3 m30.48 m3

1.1 m3

1.5 m3

2.1 m33.0 m350L (Square tank)Control panel (pH controller withindication, pH recorder)

200 L (Round tank)
EPM-96(Digital) EPR-6S(1S)type

pH detector (pH electrode + holder)
Mixer MODEL of neutralization tank(Material: SUS 304)
Sulfuric acid pump
(Diaphragm pump PVC )Raw water pump(Submerge pump)(Electrode+PK-50US)×2set
MFG-10H
0.1kW

MFG-20H
0.2kW

CRM-1225W

CR-2N
0.1kW

40A×0.25kW

50A×
0.4KW

MFG-40H
0.4kW

MFG-75H
0.75kW

CR-2-2N
0.1kW
50A×0.75kW

50A×I.5kW

MFP-150H
I.5kW

CR-3N
0.1kW

CR-3-2N
0.1kW

65A×2.2kW

80A×2.2kW| Wastewater treatment equipment２

- Handle PB-D type adapted to both acid and alkali, unit treated in capacity over 30 m3/hr

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaning
factory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment[ Wastewater contained acid ]- Plating factory, metal surface treatment and electronics parts factory, etching factory, printing
factory, acid cleaning factory- Laboratory, hospital, steel/metal factory- Wastewater from scrubber, battery factory- Other various industrial wastewater contained acid
- Pretreatment/after treatment of wastewater treatment equipment
Others- Inquire below E-mail for information on PB-R of rack type (see right photo)

３

Wastewater treatment equipment |II. Hexavalent chromium reduction treatment type ----Features- Reduction treatment function of hexavalent chromium- Easy installation or movement.by unitization- Saving installation cost and economy- Easy maintenance by compacting equipment- Grasping flow rate in terms of triangle sluice
Overview-.pH Control Unit of PB-Cr type can be continuously
neutralized with stable pH control because the unit, not only
neutralize alkali wastewater by sulfuric acid, hydrochloric acid, etc., also conduct reduction
treatment of hexavalent chromium by reduction solvent(ferrous sulfate etc.)- The Unit treats within 5.8 - 8.6 as pH and has the function of continuous record on pH value after
neutralization in record tank, and can be easily installed or moved in terms of compactification.

Water

Raw watertank

Effluent Sulfuric acid ReducingｐHNeutralization
agent tank
Recordingtanktanktank

Control panel

Flow diagram of treatment system

Performance/Specifications- Specifications of PB-Cr series
Type(Standard treatmentcapacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemicalpump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)

PB-20Cr(20m3/hr)

PB-30
Cr(30m3/hr)

2.4 m3

3.5 m3

4.8m3

7.0 m

3

1.1 m3

1.5 m3

2.1m3

3.0 m

3

PB-03Cr

PB-05Cr

PB-10Cr3(1m /hr)

3(3m /hr)

3(5m /hr)

3(10m /hr)

0.25m30.72 m3

1.1 m30.2 m3

0.3 m30.48 m3

50L (Square tank)Control panel (pH controller withindication, recorder)

200 L (Round tank)
EPM-96(Digital) EPR-6S(1S)type

pH detector (pH electrode + holder)
Mixer MODEL of neutralization tank(Material: SUS 304)

PB-15Cr(15m3/hr)

PB-01Cr(Electrode+PK-50US)×2set
MFG-10H
0.1kW

MFG-20H
0.2kW

MFG-40H
0.4kW

MFG-75H
0.75kW| Wastewater treatment equipment

MFP-150H
I.5kW

４

Sulfuric acid pump
(Diaphragm pump PVC )Raw water pump(Submerge pump)CRM-1225W
40A×0.25kW

CR-2N
0.1kW
50A×0.4KW

CR-2-2N
0.1kW
50A×0.75kW

50A×I.5kW

CR-3N0.1kW
65A×2.2kW

CR-3-2N
0.1kW
80A×2.2kW- Handle unit treated in capacity over 30 m3/hr- No removal for total chromium

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaningfactory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment

５Wastewater treatment equipment |III. Touch panel type ----Features- Adoption of touch panel method for all process of operation, setting,adjustment, record- No chart and cost saving by paperless- Typical equipping from conventional function to proportional control function- Same price as conventional product in spite of high function specifications
Overview-. The unit typically equips high function such as touch panel method and proportional control.inaddition to the PB seriesPerformance/Specifications- Specifications of PB-T series
Type(Standard treatmentcapacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemicalpump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)

PBT-01

PBT-03

PBT-05(1m3/hr)(3m3/hr)(5m3/hr)

0.2m3

0.65 m3

1.0 m30.1 m30.35 m3

0.5 m350L (Square tank)

100L (Square tank)

200L (Square tank)Control panel (pH controller withindication, recorder)

Touch panel method Paperless record

pH detector (pH electrode + holder)
Mixer of neutralization tank(Material: SUS 304)
Sulfuric acid pump
(Fixed pump)
Raw water pump(Submerge pump)(Electrode+PK-50US)×2set
KVS-1008 0.1kW

MFG-20H 0.2kW

SPY-W60

SPY-W300 30W

18W
40A×0.25kW

50A×0.4kW- The unit can deal with various industrial wastewater (acid, alkyl etc.) , and treat within 5.8 - 8.6 as pH and has thefunction of continuous record on pH value after neutralization in record tank

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaning
factory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment| Wastewater treatment equipment

６IV. Touch panel and hexavalent chromium reduction treatment type ----Features- Adoption of touch panel method for all process of operation, setting,adjustment, record- No chart and cost saving by paperless- Typical equipping from conventional function to proportional control function- Same price as conventional product in spite of high function specifications
Overview-. The unit typically equips high function such as touch panel method and proportional control.in
addition to the PB-Cr series
Performance/Specifications- Specifications of PBT-Cr series
Type(Standard treatmentcapacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemical
pump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)

PBT-01Cr

PBT-03 Cr

PBT-05 Cr(1m3/hr)(3m3/hr)(5m3/hr)

0.2m3

0.65 m3

1.0 m30.1 m30.35 m30.5 m3

50L (Square tank)

100L (Square tank)

200L (Square tank)

Reduction solvent tank (PE tank)

50L (Square tank)Control panel (pH controller withindication, recorder)

Touch panel method Paperless record

pH detector (pH electrode + holder)
Mixer MODEL of neutralization tank(Material: SUS 304)
Mixer MODEL of reduction solventtank(Material: SUS 304 + rubber lining)
Sulfuric acid pump MODEL(Solenoide pump)
Reduction solvent pump MODEL(Solrenoide pump)

100L (Square tank)(Electrode+PK-50US)×2set
KVS-1008 0.1kW

MFG-20H 0.2kW

KVS-0408 40WKVS-0608 60W

SPY-W60

18W

SPY-V300 30W

SPY-W60

15W

SPY-W60

Raw water pump(Submerge pump)

40A×0.25kW

18W
50A×0.4kW- The unit can be easily installed or moved in terms of compactification, and record on pH value after neutralization inrecord tank

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaningfactory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment

７

Wastewater treatment equipment |- Reference
Elepon E.C.A.P. Corporation
Shin-Daibiru Bidg, 1-2-1,Dojimahama,Kita-ku,Osaka,530-0004,Japan
E-mail：sales@elepon.co.jp
URL：http://www.elepon.co.jp| Wastewater treatment equipment８