1-10. Elepon E.C.A.P. Corporation- ｐH Control Unit -I. Basic type ----Features-.Easy installation or movement.by unitization- Saving installation cost and economy- Easy maintenance by compacting equipment- Supporting neutralization treatment of acid wastewater- Grasping flow rate in terms of triangle sluice
Overview-.pH Control Unit of PB type is developed for site ofconstruction and engineering works and can be continuously
neutralized with stable pH control by addition on-site strong alkali wastewater to sulfuric acid,hydrochloric acid, etc., furthermore installed or moved easy by compacting equipment.
- The Unit treats within 5.8 - 8.6 as pH to various industrial wastewater contained acid/alkali, and has
the function of continuous record on pH value after neutralization in record tank.

Flow diagram of treatment system

Performance/Specifications- Specifications of PB series
Type(Standard treatmentcapacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemicalpump, pH electrode)
Recording tank volume(SS400+ Inside:epotal pH electrode)Sulfuric acid tank (PE tank)

PB-01

PB-03

PB-05

PB-10

PB-15

PB-20

PB-30

333333(30m /hr)(1m /hr)(3m /hr)

30.72 m30.3 m

0.25m

0.2 m

(5m /hr)

31.1 m30.48 m

(20m /hr)

32.4 m33.5 m34.8 m

37.0 m3

31.1 m31.5 m32.1 m33.0 m

3200 L (Round tank)
EPM-96(Digital) EPR-6S(1S)type

pH detector (pH electrode + holder)

Raw water pump(Submerge pump)(15m /hr)

350L (Square tank)Control panel (pH controller withindication, pH recorder)
Mixer MODEL of neutralization tank(Material: SUS 304)
Sulfuric acid pump
(Diaphragm pump PVC )(10m /hr)(Electrode+PK-50US)×2set
MFG-10H
0.1kW

MFG-20H
0.2kW

CRM-1225W

CR-2N
0.1kW

40A×0.25kW

50A×0.4KW

MFG-40H
0.4kW

MFG-75H
0.75kW

CR-2-2N
0.1kW
50A×
0.75kW

50A×
I.5kW

MFP-150H
I.5kW

CR-3N
0.1kW

CR-3-2N
0.1kW

65A×
2.2kW

80A×
2.2kW

| Wastewater treatment equipment

１３3- Handle PB-D type adapted to both acid and alkali, unit treated in capacity over 30 m /hr

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaning
factory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment[ Wastewater contained acid ]- Plating factory, metal surface treatment and electronics parts factory, etching factory, printing
factory, acid cleaning factory- Laboratory, hospital, steel/metal factory- Wastewater from scrubber, battery factory- Other various industrial wastewater contained acid
- Pretreatment/after treatment of wastewater treatment equipment
Others- Inquire below E-mail for information on PB-R of rack type (see right photo)
Reference
Elepon E.C.A.P. Corporation
24-3 Minamihanada-cho, Kita-ku, Sakai City, Osaka 591-8011, JAPAN
TEL：+81-72-256-2822
FAX：+81-72-256-2830
E-mail：osaka@elepon.co.jp
URL：http://www.elepon.co.jp

１４

Wastewater treatment equipment |II. Hexavalent chromium reduction treatment type ----Features- Reduction treatment function of hexavalent chromium- Easy installation or movement.by unitization- Saving installation cost and economy- Easy maintenance by compacting equipment- Grasping flow rate in terms of triangle sluice
Overview-.pH Control Unit of PB-Cr type can be continuously
neutralized with stable pH control because the unit, not only
neutralize alkali wastewater by sulfuric acid, hydrochloric acid, etc., also conduct reduction
treatment of hexavalent chromium by reduction solvent(ferrous sulfate etc.)- The Unit treats within 5.8 - 8.6 as pH and has the function of continuous record on pH value after
neutralization in record tank, and can be easily installed or moved in terms of compactification.

Flow diagram of treatment system

Performance/Specifications- Specifications of PB-Cr series
Type(Standard treatmentcapacity)
Specifications
Neutralization tank volume(SS400+Inside:epotal with chemicalpump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)PB-01Cr

PB-03Cr

PB-05Cr(1m /hr)3(3m /hr)

3(5m /hr)

30.72 m30.3 m

0.25m
0.2 m

1.1 m

30.48 m3(10m /hr)

3(15m /hr)

PB-20Cr

PB-30Cr3(30m /hr)

(20m /hr)3

32.4 m33.5 m34.8 m

37.0 m331.1 m31.5 m32.1 m33.0 m

3200 L (Round tank)
EPM-96(Digital) EPR-6S(1S)type

pH detector (pH electrode + holder)

Raw water pump(Submerge pump)

350L (Square tank)Control panel (pH controller withindication, recorder)
Mixer MODEL of neutralization tank(Material: SUS 304)
Sulfuric acid pump
(Diaphragm pump PVC )3

PB-10Cr PB-15Cr(Electrode+PK-50US)×2set
MFG-10H
0.1kW
CRM-1225W

MFG-20H
0.2kW
CR-2N
0.1kW50A×
40A×0.25kW
0.4KW

MFG-40H
MFG-75H
0.4kW
0.75kW
CR-2-2N
CR-3N
0.1kW
0.1kW
50A×
50A×
65A×0.75kW
I.5kW
2.2kW

| Wastewater treatment equipment

MFP-150H
I.5kW
CR-3-2N
0.1kW
80A×
2.2kW

１５

3- Handle unit treated in capacity over 30 m /hr- No removal for total chromium

Applications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaning
factory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment
Reference
Elepon E.C.A.P. Corporation
24-3 Minamihanada-cho, Kita-ku, Sakai City, Osaka 591-8011, JAPAN
TEL：+81-72-256-2822
FAX：+81-72-256-2830
E-mail：osaka@elepon.co.jp
URL：http://www.elepon.co.jp

１６

Wastewater treatment equipment |III. Touch panel type ----Features- Adoption of touch panel method for all process of operation, setting,adjustment, record- No chart and cost saving by paperless- Typical equipping from conventional function to proportional control function- Same price as conventional product in spite of high function specifications
Overview-. The unit typically equips high function such as touch panel method and proportional control.in
addition to the PB series
Performance/Specifications- Specifications of PB-T series
Type(Standard treatmentcapacity)

PBT-01

PBT-03

PBT-0533(5m /hr)(1m /hr)Specifications
Neutralization tank volume(SS400+Inside:epotal with chemical
pump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)

30.65 m31.0 m0.1 m

30.35 m30.5 m

50L (Square tank)

100L (Square tank)

0.2m

Control panel (pH controller withindication, recorder)

Touch panel method

pH detector (pH electrode + holder)
Mixer of neutralization tank(Material: SUS 304)
Sulfuric acid pump
(Fixed pump)
Raw water pump(Submerge pump)3(3m /hr)

33200L (Square tank)

Paperless record(Electrode+PK-50US)×2set
KVS-1008

0.1kW

MFG-20H

0.2kW

SPY-V60

18W

SPY-V300

30W

40A×0.25kW

50A×0.4kW- The unit can deal with various industrial wastewater (acid, alkyl etc.) , and treat within 5.8 - 8.6 as pH and has thefunction of continuous record on pH value after neutralization in record tankApplications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaningfactory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment
Reference
Elepon E.C.A.P. Corporation
24-3 Minamihanada-cho, Kita-ku, Sakai City, Osaka 591-8011, JAPAN
TEL：+81-72-256-2822
FAX：+81-72-256-2830
E-mail：osaka@elepon.co.jp
URL：http://www.elepon.co.jp| Wastewater treatment equipment

１７

IV. Touch panel and hexavalent chromium reduction treatment type ----Features- Adoption of touch panel method for all process of operation, setting,adjustment, record- No chart and cost saving by paperless- Typical equipping from conventional function to proportional control function- Same price as conventional product in spite of high function specifications
Overview-. The unit typically equips high function such as touch panel method and proportional control.in
addition to the PB-Cr series
Performance/Specifications- Specifications of PBT-Cr series
Type(Standard treatmentcapacity)

PBT-01Cr

PBT-03 Cr

PBT-05 Cr

33(5m /hr)

(1m /hr)Specifications
Neutralization tank volume(SS400+Inside:epotal with chemical
pump, pH electrode)
pH recording tank volume(SS400+Inside epotal, pH electrode)Sulfuric acid tank (PE tank)

30.65 m31.0 m0.1 m

30.35 m30.5 m

50L (Square tank)

100L (Square tank)

0.2m

Reduction solvent tank (PE tank)

50L (Square tank)Control panel (pH controller withindication, recorder)

Touch panel method

pH detector (pH electrode + holder)
Mixer MODEL of neutralization tank(Material: SUS 304)
Mixer MODEL of reduction solventtank(Material: SUS 304 + rubber lining)
Sulfuric acid pump MODEL(Solenoide pump)
Reduction solvent pump MODEL(Solrenoide pump)3(3m /hr)

33200L (Square tank)
100L (Square tank)

Paperless record(Electrode+PK-50US)×2set
KVS-1008

0.1kW

MFG-20H

0.2kW

KVS-0408

40W

KVS-0608

60W

SPY-V60

18W

SPY-V300

30W

SPY-V60

15WSPY-V60

18W

Raw water pump(Submerge pump)

40A×0.25kW

50A×0.4kW- The unit can be easily installed or moved in terms of compactification, and record on pH value after neutralization inrecord tankApplications/Experience[ Wastewater contained alkali ]- Ready-mixed concrete factory, second product factory from concrete, grindstone factory- Site of construction and engineering works, washing bottle factory, washing factory, Cleaning
factory, dyeing and fiber factory- Other various industrial wastewater contained alkali- Pretreatment/after treatment of wastewater treatment equipment
Reference
Elepon E.C.A.P. Corporation
24-3 Minamihanada-cho, Kita-ku, Sakai City, Osaka 591-8011, JAPAN
TEL：+81-72-256-2822
FAX：+81-72-256-2830
E-mail：osaka@elepon.co.jp
URL：http://www.elepon.co.jp
１８

Wastewater treatment equipment |