1 Filtration And Adsorption Unit

１Filtration And Adsorption Unit |1-1.

Elepon E.C.A.P. Corporation - Filtration and adsorption Unit -I.

Sand Filtration Unit / Activated Carbon Absorption Unit ----Features- Small size and light, safety by little installation area
- Operation by two methods of manual and fully automatic type
- Fully automatic type is easy to daily maintenance without complex
operation. The unit is excellent to operate with single five direction bulband multi bulb.
- The unit can operate continuously in long term by reverse washing filler
Inside filtration tower.
Overview

Pressuregauge

Window

Processingmater

Window

Raw water
Entrance volume

Processingmater

Filtration
Tower

Washingdrainage

Waste waterflowmeter

Washedwastewater

Influent

Waste waterflowmeter

Washedwastewater

Effluent

Influent

Effluent

Reversed washing water

Reversed washing water

Front view
Right Side view
Front view
Type of automatic simple five direction bulb
Type of automatic multi- direction bulb
Activated carbon absorption unit
Sand filtration unit

Influent
Reversed washing wastewater

Effluent
reversed washingwastewaterFiltration rawwater tank

To Raw water tank

Reversed washing pump

Treated watertank

Flow diagram of treatment| Filtration And Adsorption Unit

２

Structure of normal filter material ofsand filtration unit
- No adaptation in case of activated carbon absorption,
removal of iron/manganese, soft water generated fromhard waterNo.

name

⑥⑤④③
②
①

filter medium
filter medium
supporting bed No.4
supporting bed No.5
supporting bed No.6
supporting bed No.7

Specifications
anthracite 0.9mm
sand 0.5mm
gravel2～ 4mmgravel4～ 8mmgravel8～12mmgravel 12～20mm

Performance/Specifications- Specifications of RS，ARS，AR，RCS，ARCS，ARC series<Sand filtration unit / RS series: manual simple five direction bulb>
Main pipe caliber (mm)Capacity

Type3(m /hr)

Influent

Treatedwater

Reversedwashing

Product size(core parts)(mm)

Productroughweight(kg)Weight asoperation(kg)RS 40-15

1252540

φ400 × 1,525SH

140340RS 50-15

2252540

φ500 × 1,525SH

180480RS 60-15

3252540

φ600 × 1,525SH

210640RS 80-155404050

φ800 × 1,525SH

4401,510

RS 110-15

10404065

φ1,100 × 1,525SH6802,900RS 140-15

15505080

φ1,400 × 1,525SH

1,2004,800- Note: Capacity of treatment and specifications indicated above are different by water quality of wastewater.

< Activated carbon absorption unit / RCS series: manual simple five direction bulb>- Note: Capacity of treatment and specifications indicated above are different by water quality of wastewater.
Main pipe caliber (mm)Capacity

Type3(m /hr)

Influent

Treatedwater

Reversedwashing

Product size(core parts)(mm)

Productroughweight(kg)Weight asoperation(kg)RCS 40-24

1252540

φ400 × 2,440SH

170430

RCS 50-24

2252540

φ500 × 2,440SH

210510

RCS 60-24

3252540

φ600 × 2,440SH

250620

RCS 80-24

5404050

φ800 × 2,440SH

530

1,850

RCS 110-24

10404065

φ1,100 × 2,440SH

820

2,800

RCS 140-24

15505080

φ1,400 × 2,440SH

1,400

4,900

- Note: Capacity of treatment and specifications indicated above are different by water quality of wastewater.

３Filtration And Adsorption Unit |Applications/Experience- Many kinds of wastewater treatment equipment- Water supply, industrial water supply, processing water- pretreatment such as ion exchange resin equipment, etc.
- Pool, public bath, etc.

| Filtration And Adsorption Unit４

II.

Liquid Filtration Unit ‘Cocoon series’ ----Features- Bag or cartridge multi-use- Light weight and high corrosion resistance, economy by one body
molding of polypropylene- Clean filtration of water, acid, alkali, chemical product, medicine, oil,etc.
- Simple design without liquor accumulation- Saving space by compact unit
- Wide range for filtration accuracy from 1 micron to 800 micron- Easy maintenance by adoption of large cartridge and mud
possession capacity with 20 times as same as 10 inch cartridge as
standard- Molded mouth of filter bag contacted inside tank is sealed without
leakage.
- Design superior to cheap, light weight, simple structure and easy dealing
Overview

Treated water
Influent

Flow diagram of treatment
Performance/Specifications- Example for specifications<Unit specifications >- Max. treatment capacity: 18 m3/hr (as pure water)* Flow rate may decrease under loading state, however, treatment capacity: can be up by addition
to filter.
* Automatic stop control can be conducted by pressure meter to preserve pump.
- Body material: polypropylene(PP)- Pipe material: polyvinyl chloride(PVA)<Filter specifications >- Body E-100B(back filter type), E-100C(cartridge type)* Body: one body molding of polypropylene* Basket: molding of polypropylene* Leg part: resin
５Filtration And Adsorption Unit |* Pressure-resistant: 700kPa (43℃)* Product weigh: 45kg
* Contact caliber: 50A screw-in- Filter bag* Opening: poly-rock* Filter: polypropylene* Diameter: 152nm* Length: 508 nm*Surface area: 0.2 m2* Passing water volume: 150-200L/min- Cartridge* Seal part: poly-seal* Filter: polypropylene microfiber* Diameter: 140nm* Length: 590 nm*Volume: 8,200 m3* Passing water volume: 150L/min
Pressure-resistant(kPa)
Withstandpressure (Kpa)

Not available
range

vailaAvailable range
ble range

Temperature (℃)
Temperature (℃)

Cartridge

Differential

pressure (Kpa)

Flow rate (L/min)
Capacity (L/min)

Pressure difference
(kPa)

Bag

Differential

pressure (Kpa)

Pressure difference(kPa)

Pressure range for using filter container

Flow rate (L/min)
Capacity (L/min)

Applications/Experience- Machine work: Separation of suspend solid‐liquid (ceramic polishing solvent, printed board
polishing solvent, coolant solvent)- Surface preparation: Before/after- treatment of alkali removal of fat, various electric plating solvent,precious metal plating(activated carbon), no treatment solvent of activated carbon and zinc etc.
| Filtration And Adsorption Unit６

- Water treatment: Industrial water supply(ground water, reservoir/lake), drainage water, pre-filtration
etc.

Reference
Elepon E.C.A.P. Corporation
Shin-Daibiru Bidg, 1-2-1,Dojimahama,Kita-ku,Osaka,530-0004,Japan
E-mail：sales@elepon.co.jp
URL：http://www.elepon.co.jp

７

Filtration And Adsorption Unit |