PLUG-IN TYPE
PROGRAMMABLE SIGNAL CONDITIONERSEWSERIES

INSTRUCTION MANUALPreface

Thank you for purchasing the SEW series Programmable Signal Conditioner.
This manual contains instructions for the mounting, functions, operations and notes when
operating the SEW series. To ensure safe and correct use, thoroughly read and understandthis manual before using this unit. To prevent accidents arising from the misuse of this
instrument, please ensure the operator receives this manual.

Notes• This instrument should be used in accordance with the specifications described in the manual.
If it is not used according to the specifications, it may malfunction or cause a fire.
• Be sure to follow the warnings, cautions and notices. If they are not observed, serious injury or
malfunction may occur.
• Specifications of the SEW series and the contents of this instruction manual are subject tochange without notice.
• Care has been taken to assure that the contents of this instruction manual are correct, but if there
are any doubts, mistakes or questions, please inform our sales department.
• This instrument is designed to be installed on a DIN rail within a control panel. If it is not, measures must
be taken to ensure that the operator does not touch power terminals or other high voltage sections.
• Any unauthorized transfer or copying of this document, in part or in whole, is prohibited.
• Shinko Technos Co., Ltd. is not liable for any damages or secondary damages incurred as a resultof using this product, including any indirect damages.
SAFETY PRECAUTIONS (Be sure to read these precautions before using our products.)
The safety precautions are classified into categories: “Warning” and “Caution”.
Depending on the circumstances, procedures indicated by
Caution may cause serious
results, so be sure to follow the directions for usage.
which may lead to dangerous conditions and cause
Warning Procedures
death or serious injury, if not carried out properly.

CautionProcedures which may lead to dangerous conditions and cause
superficial to medium injury or physical damage or may degrade or
damage the product, if not carried out properly.

Warning• To prevent an electric shock or fire, only Shinko or other qualified service personnel may
handle the inner assembly.
• To prevent an electric shock, fire or damage to the instrument, parts replacement may only
be undertaken by Shinko or other qualified service personnel.

Safety Precautions• To ensure safe and correct use, thoroughly read and understand this manual before using this
instrument.
• This instrument is intended to be used for industrial machinery, machine tools and measuring
equipment. Verify correct usage after purpose-of-use consultation with our agency or main
office. (Never use this instrument for medical purposes with which human lives are involved.)• External protection devices such as protective equipment against excessive temperature rise, etc.
must be installed, as malfunction of this product could result in serious damage to the system or
injury to personnel. Also proper periodic maintenance is required.
• This instrument must be used under the conditions and environment described in this manual.
Shinko Technos Co., Ltd. does not accept liability for any injury, loss of life or damage occurring
due to the instrument being used under conditions not otherwise stated in this manual.
Caution with respect to Export Trade Control Ordinance
To avoid this instrument from being used as a component in, or as being utilized in the
manufacture of weapons of mass destruction (i.e. military applications, military equipment,etc.), please investigate the end users and the final use of this instrument.
In the case of resale, ensure that this instrument is not illegally exported.
2

1. Installation Precautions

CautionThis instrument is intended to be used under the following environmental conditions(IEC61010-1): Overvoltage category , Pollution degree 2
Ensure the mounting location corresponds to the following conditions:• A minimum of dust, and an absence of corrosive gases• No flammable, explosive gases• No mechanical vibrations or shocks• No exposure to direct sunlight, an ambient temperature of -5 to 55(23 to 131 )that does not change rapidly, and no icing• An ambient non-condensing humidity of 35 to 85 %RH• No large capacity electromagnetic switches or cables through which large current is flowing• No water, oil or chemicals or where the vapors of these substances can come into
direct contact with the unit
• When installing this unit within a control panel, take note that the ambient temperatureof this unit – not the ambient temperature of the control panel - must not exceed 55(131 ), otherwise the life of the electronic components (especially electrolytic
capacitors) of the unit will be shortened.
Note: Avoid setting this instrument directly on or near flammable material eventhough the case of this instrument is made of flame-resistant resin.

2. Wiring Precautions

Caution• Do not leave wire remnants in the instrument, because they could cause a fire and/or amalfunction.
• When wiring terminals, use a solderless terminal with an insulation sleeve in which an
M3 screw fits.
• Tighten the terminal screw using the specified torque.
If excessive force is applied to the screw when tightening, the screw may be damaged.
• This instrument has no built-in power switch, circuit breaker or fuse.
Be sure to install a built-in power switch, circuit breaker or fuse near the instrument.
(Recommended fuse: Time-lag fuse, rated voltage 250 V AC, rated current 2 A)
• For wiring of AC power source, be sure to use exclusive terminals as described in thismanual. If AC power source is connected to incorrect terminals, the unit will burn out.
• For a 24 V DC power source, do not confuse polarity.
• Do not apply a commercial power source to the sensor connected to the input terminal
nor allow the power source to come into contact with the sensor.
• Use a thermocouple, compensating lead wire and 3-wire RTD according to the sensor
input specifications of this unit.
• When using DC voltage and current input, do not confuse polarity when wiring.
• Keep the input/output wires and power line separate.

3. Operation and Maintenance Precautions

Caution• Do not touch live terminals. This may cause electric shock or problems in operation.
• Turn the power supply to the instrument OFF when retightening the terminal andcleaning. Working on or touching the terminal with the power switched ON may result
in severe injury or death due to electric shock.
• Use a soft, dry cloth when cleaning the instrument.
(Alcohol based substances may tarnish or deface the unit.)• As the display section is vulnerable, do not strike or scratch it with a hard object or
put pressure on it.
3Model Explanation
Model names included in this manual are indicated below.
An individual model name will be used for individual explanations.
For common explanations, the model name SEW will be used.
Indication
SEW

Model
SEWU, SEWE, SEWR, SEWA, SEWV, SEWD, SEWD-F

Characters Used in This Manual
Indication
Number,

/

-1

0

1

2

3

4

5

6

7

8

9

A

B

C

D

E

F

G

H

I

J

K

L

M

N

O

P

Q

R

S

T

U

V

W

X

Y

Z

Indication
Alphabet
Indication
Alphabetmeans that no character is indicated (unlit) on the display.

4

---

CONTENTS ---1. ModelPage
1.1 Model ---------------------------------------------------------------------------- 6
1.2 How to Read the Model Label --------------------------------------------- 6
2. Name and Functions of Sections ------------------------------------------- 7
3. Mounting
3.1 External Dimensions (Scale: mm) ---------------------------------------- 8
3.2 Mounting to a DIN Rail ------------------------------------------------------ 8
3.3 Removal from a DIN Rail -------------------------------------------------- 10
4. Wiring
4.1 Lead Wire Solderless Terminal ------------------------------------------ 12
4.2 Terminal Arrangement, Circuit Configuration ------------------------ 13
4.3 Wiring of Terminals
4.3.1 Power Source Wiring -------------------------------------------------- 14
4.3.2 Output Wiring ------------------------------------------------------------ 14
4.3.3 Input Wiring -------------------------------------------------------------- 15
5. Key Operation Flowchart ---------------------------------------------------- 16
6. Setup ------------------------------------------------------------------------------- 18
6.1 Indication after Power-on ------------------------------------------------- 19
6.2 Basic Operation of Setup ------------------------------------------------- 19
6.3 Setup6.3.1 Input 1/Output 1 Function Group ----------------------------------- 21
6.3.2 Output 2 Function Group --------------------------------------------- 23
6.3.3 Special Function Group ---------------------------------------------- 24
6.3.4 Using This Unit as a Standard Signal Conditioner ------------ 25
6.3.5 Using the Reverse Function ---------------------------------------- 25
6.3.6 Using the First Order Lag Filter Function ------------------------ 25
7. Adjustment
7.1 Basic Operation of Adjustment ------------------------------------------ 26
7.2 Adjustment
7.2.1 Output 1 Adjustment Group ----------------------------------------- 27
7.2.2 Output 2 Adjustment Group ----------------------------------------- 28
8. Operation
8.1 Indication after Power-on ------------------------------------------------- 28
8.2 Unit Operation --------------------------------------------------------------- 28
9. Specifications ------------------------------------------------------------------- 31
10. Troubleshooting
10.1 Indication -------------------------------------------------------------------- 34
10.2 Key Operation -------------------------------------------------------------- 34
10.3 Operation -------------------------------------------------------------------- 34
11. Character Table ----------------------------------------------------------------- 35
5

1. Model
1.1 Model
SEW SeriesSE

SignalConditioner
Type

-

-

WU
WE
WR
WA
WV
WD
WD

Socket2-output Universal (*1) (*2)
2-output Thermocouple
2-output RTD
2-output Direct current (*2)
2-output DC voltage
2-output Current Loop Supply
2-output Current Loop Supply(Suitable for Field communicator usage)
Finger-safe, Screw fall prevention(Only Y-type terminal usable)
Ring-type terminal usable
100 to 240 V AC
24 V AC/DCF
1
2Power supply

01(*1) SEWU accepts universal (all types of) inputs and outputs.
Types other than SEWU accept universal outputs only.
Input: Thermocouple, RTD, Direct current, DC voltage
Output: Direct current, DC voltage(*2) For Direct current input, a shunt resistor (sold separately) is required.
(e.g.) SEWU-1-0
Type: 2-output Universal transmitter
Socket: Finger-safe, Screw fall prevention (Only Y-type terminal usable)
Power supply: 100 to 240 V AC
Factory default: Input: 1 to 5 V DC
Output 1: 4 to 20 mA DC
Output 2: 4 to 20 mA DC
1.2 How to Read the Model Label
The model label is attached to the left side of the case.
Model (e.g. SEWU-1-0)
Input: Enter a range selected in [Input range].
Output 1: Enter a type selected in [Output type].
Output 2: Enter a type selected in [Output type].
Serial number(Fig. 1.2-1)

6

2. Name and Functions of Sections
(1)

(2)

(3)
(4)

(6)

(5)

(7)

(8)

(9)
(Fig. 2-1)

(1) Power indicator (Green): Lights when the power to the instrument is turned ON.
(2) Input Display (Red): Indicates the input value in RUN mode.
Indicates Output 1 value when ‘Output 1/Output 2 value’ is selected in [Display selection].
Indicates setting item characters in Setup mode.
Indicates adjustment item characters in Adjustment mode.
(3) Output Display (Red): Indicates Output 1 value (%) in RUN mode.
Indicates Output 2 value when ‘Output 1/Output 2 value’ is selected in [Display selection].
Indicates the set value in Setup mode.
Indicates the adjustment value in Adjustment mode.
(4) UP Key (): Increases the numeric value, or switches the selection items.

(5) DOWN Key (): Decreases the numeric value, or switches the selection items.

(6) MODE Key (): Selects or switches groups, and registers the set value.

(7) SUB-MODE Key
Turns the displays ON again while they are in OFF status. (The UP, DOWN or MODE Key
also turns the displays ON again while they are in OFF status.)(8) Console connector
By connecting to the USB communication cable (CMB-001, sold separately), the following
operations can be conducted from an external computer using the SWS-SE001M Console
software: Reading/setting of various set values, Reading of input values and action status(9) Light sensor
Automatically measures and controls brightness of the Input and Output Displays.

NoticeWhen setting the specifications and functions of this instrument, connect mains power
cable to terminals 13 and 14 first, then set them referring to “5. Key Operation Flowchart”
and “6. Setup” before performing “3. Mounting” and “4. Wiring”.
7

3. Mounting
3.1 External Dimensions (Scale: mm)
Socket85

DIN rail

(29)

3

79

30

108
(Fig. 3.1-1)

3.2 Mounting to a DIN Rail(1) Hook the upper part of the socket on the DIN rail, and mount it.
(A clicking sound is heard.)
Hook the upper part of thesocket on the DIN rail.

(Fig. 3.2-1)

CautionWire the instrument before inserting the unit into the socket.
For wiring, refer to Section “4. Wiring”.

8

3.3

(2) Confirm that the Lock Release is lowered.

Lock Release(Fig. 3.2-2)(3) Insert the SEW

series into the socket.

When inserting, be careful
about the position of pins
and slots.

(Fig. 3.2-3)

9

(4) Fix the SEW

series and the socket by pushing the Lock Release up.

Check that the SEW series
and the socket are locked bypushing the Lock Release up.

Lock Release(Fig. 3.2-4)

3.3. Removal from a DIN Rail(1) Turn the power supply to the unit OFF.
(2) Pull the Lock Release down, and release the SEW

series from the socket.

Check that the SEW series
and the socket are unlocked bypulling the Lock Release down.

Lock Release(Fig. 3.3-1)

10

(3) Separate the SEW

series from the socket.

(Fig. 3.3-2)(4) Remove the socket from the DIN rail by pulling the Socket Lock Release(at the bottom of the socket) down.

(Fig. 3.3-3)

11

4. Wiring
Warning
Turn the power supply to the instrument off before wiring.
Working on or touching the terminal with the power switched ON may result
in severe injury or death due to electric shock.
4.1 Lead Wire Solderless Terminal
Use a solderless terminal with an insulation sleeve in which an M3 screw fits as follows.
For the sockets with finger-safe & screw fall prevention functions, the ring-type terminals
are unusable.
The torque should be 0.63 N•m.
Solderless
Manufacturer
Model
Terminal
Y-typeNichifu Terminal Industries CO., LTD.
TMEV1.25Y-3S
Nichifu Terminal Industries CO., LTD.
TMEV 1.25-3
Ring-type
Japan Solderless Terminal MFG CO., LTD.
V1.25-3(Scale: mm)(Fig. 4.1-1)

12

4.2 Terminal Arrangement, Circuit Configuration

+

RTD

mA DC

+

TC

mV DC (≦1V)

V DC (≦10V)

SEWU, SEWE, SEWR, SEWA, SEWV

A +

-

-

B B

1
2

Display/Setting
key circuit

Input
circuit3

13+Power supply

14-

Insulation circuit

4

+

Power
circuitOutputcircuit

CPU

5

9

+
Output 1

10-

Insulation circuit

6

Outputcircuit7

11

Output 2
12

8

+

-

DC voltage input:
mV DC( 1 V): 0 to 10 mV DC, -10 to 10 mV DC, 0 to 50 mV DC, 0 to 60 mV DC,
0 to 100 mV DC, 0 to 1 V DC
V DC( 10 V) : 0 to 5 V DC, 1 to 5 V DC, 0 to 10 V DC
(Fig. 4.2-1)

-

mA DC

SEWD
+ 1 50- 2

Power supply for
2-wire transmitter

+

Input
circuit

Display/Setting
key circuit

3

4

Power
circuit13
14

Insulation circuit
24V DC
Power
circuitOutputcircuitCPU

5

9Outputcircuit7
8(Fig. 4.2-2)

13

Power
supply+Output 1

10

Insulation circuit

6

+

11

+
Output 2

12-

mA DCSEWD-F+

1

50
Input circuit

-

2

4

Power circuit

240

24 V DCPower circuit

9CPU

Output circuit
Insulation circuit
116

Output circuit

7+
Output 1

105+Power supply

14
Insulation circuit

Power supply for 3
2-wire transmitter+

13

Display/Setting
key circuit+
Output 2

12-

8(Fig. 4.2-3)

4.3 Wiring of Terminals

Warning• For 100 to 240 V AC, if AC power source is connected to incorrect terminals,
this instrument will burn out.
• For a 24 V DC power source, do not confuse polarity when wiring.
4.3.1 Power Source Wiring
Use terminals 13 (+) and 14 (-) for the power supply to the instrument.
4.3.2 Output Wiring
Use terminals 9 (+) and 10 (-) for Output 1 wiring.
Use terminals 11 (+) and 12 (-) for Output 2 wiring.

14

4.3.3 Input Wiring
SEWU (thermocouple, RTD, DC voltage inputs), SEWE, SEWR, SEWV:
Terminals for wiring differ depending on the input specifications.
See (Fig. 4.2-1, p.13).
SEWU (Direct current input), SEWA:
Use terminals 1 (+), 2 (-) for input wiring and shunt resistor connection.
See (Table 4.3.3-1). (Shunt resistor: Sold separately)(Table 4.3.3-1)
Shunt Resistor
Input
Model
Model
Specification
4 to 20 mA DC
0 to 20 mA DC
0 to 16 mA DC
2 to 10 mA DC
0 to 10 mA DC
1 to 5 mA DC
0 to 1 mA DC(Y-type terminal)(Ring-type terminal)

RES-S06-050

RES-S01-050

50

0.1%

RES-S06-100

RES-S01-100

100

0.1%

RES-S06-200
RES-S06-01K

RES-S01-200
RES-S01-01K

200
1k

0.1%
0.1%

SEWD, SEWD-F: When using as a Current Loop Supply or as an Isolator, be sure
to wire the unit as follows. See (Fig. 4.3.3-1) to (Fig. 4.3.3-4).
SEWD
As a Current Loop Supply

-

+ 1
3

+

+4

+

50
Input
circuit- 2
2-wiretransmitter

As an Isolator
Input

-

1

50
Input
circuit2
3

24V DCpower
circuit

24V DCpower
circuit4(Fig. 4.3.3-1)(Fig. 4.3.3-2)

SEWD-FAs a Current Loop Supply

As an Isolator

-

+ 1

Input
circuit- 2
2-wiretransmitter

3

+

+ 4

+

50
Input

-

1

50
Input
circuit2
3

240

24V DCpower
circuit(Fig. 4.3.3-3)

4

240(Fig. 4.3.3-4)
15

24V DCpower
circuit5. Key Operation Flowchart
The Input Display indicates input type, and the Output Display indicates the Output 1
type for 3 sec after power is turned ON. See (Tables 5-1, 5-2).

POWER ON
RUN Mode
Output 1 Adjustment GroupOutput 2 Adjustment Group

Input 1/ Output 1
Function GroupOutput zero adjust

Output zero adjust

Input type (*1)

-5.00 to 5.00%-5.00 to 5.00%: Thermocouple: RTD

Output span adjust

Output span adjust-5.00 to 5.00%-5.00 to 5.00%: Direct current: DC voltage

Input range (*2)
See (Table 5-1).
(Table 5-1)
Item
Input Type & Range
K-200 to 1370

K-200 to 200

K

0 to 400

J-200 to 1000

J-200 to 200

J

0 to 400

R
S

Item

Input Type & Range
K-328 to 2498(*)

K

-328 to 392

(*)

(*)

K

32 to 752(*)

J

-328 to 1832(*)

J

-328 to 392

(*)

(*)

J

32 to 752(*)

-50 to 1760

R

-58 to 3200

-50 to 1760

S

-58 to 3200

B

0 to 1820

B

32 to 3308

E-200 to 800

E-328 to 1472

T

-200 to 400

T-328 to 752

N -200 to 1300(*)

N-328 to 2372

PL-

PL-

32 to 2534

0 to 1390: No decimal point: 1 digit after point: 2 digits after point: 3 digits after point

Output 0% value
Input range low limit to
Output 100% value
DC input: -1999 to
Output 100% value(*)

W5Re/W26Re 0 to 2315

W5Re/W26Re 32 to 4199

W3Re/W25Re 0 to 2315

W3Re/W25Re 32 to 4199

Pt100

-200 to 850

Pt100 -328 to 1562

Pt100

-100 to 100

(*)

Pt100

-148 to 212(*)

JPt100 -200 to 500

JPt100 -328 to 932

4 to 20 mA DC -1999 to 9999

0 to 10 mV DC -1999 to 9999

0 to 20 mA DC -1999 to 9999

-10 to 10 mV DC -1999 to 9999

0 to 16 mA DC -1999 to 9999

0 to 50 mV DC -1999 to 9999

2 to 10 mA DC -1999 to 9999

0 to 60 mV DC -1999 to 9999

0 to 10 mA DC -1999 to 9999

0 to 100 mV DC -1999 to 9999

1 to 5 mA DC -1999 to 9999

0 to 1 V DC

-1999 to 9999

0 to 1 mA DC -1999 to 9999

0 to 5 V DC

-1999 to 9999

1 to 5 V DC

-1999 to 9999

0 to 10 V DC

-1999 to 9999(*) ‘No decimal point’ or ‘1 digit after decimal point’ can be selected in[Decimal point place].
(Table 5-2)
Item

Decimal point place (*3)

Output 100% value
Output 0% value to
Input range high limit
DC input:
Output 0% value to 9999

Filter time constant
0.0 to 10.0 seconds

Sensor correction-100.0 to 100.0 ( )-1000 to 1000 (DC input)

Output typeSee (Table 5-2).

Output Normal/Reverse
Output Type

Item

Output Type

4 to 20 mA DC

0 to 1 V DC

0 to 20 mA DC

0 to 5 V DC

0 to 12 mA DC

1 to 5 V DC

0 to 10 mA DC

0 to 10 V DC

1 to 5 mA DC: Normal: Reverse

Burnout (*4): Upscale: Downscale16Output 2 Function GroupSpecial Function GroupOutput 0% value (*4)

Set value lock

Input range low limit to
Output 100% value: Unlock: Lock

Output 100% value (*4)

Input sampling period (Response time)

Output 0% value to
Input range high limit: 25 ms [65 ms(typ.)(0→90%)]: 125 ms [225 ms(typ.)(0→90%)]: 250 ms [425 ms(typ.)(0→90%)]

Output type
Auto-light function

See (Table 5-2).

: Disabled

Output Normal/Reverse: Enabled: Normal

Display Selection[Input Display]: Reverse: Input value: Input value: Output 1 value: No indication[Output Display]
Output 1 value
No indication
Output 2 value
No indication

Indication Time00.00 (Remains lit)
00.01 to 60.00 (Minutes.Seconds)[About Setting Items]

Output zero adjust-5.00 to 5.00%• Upper left (Input Display): Shows setting or
adjustment characters.
Lower left (Output Display): Shows factory default.
• Upper right: Shows setting or adjustment items.
Lower right: Shows setting range, selection items.
• Depending on the model, some items do not appear.
(*1) Available for the SEWU only.
(*2) Not available for the SEWD, SEWD-F.
(*3) Available if DC voltage or current is selectedin [Input type] or if (*) range for thermocouple
or RTD (Table 5-1) is selected.
(*4) Available for the thermocouple or RTD input.
[Key Operation]•, : This means that if theor
key ispressed, the unit proceeds to the next setting
mode.
• The
or
key sets the setting (or adjustment) items, and the
key registers the value.
• By pressing the
key for 3 sec, it is possible
to return to RUN mode from any setting (or adjustment) mode.

17

6. Setup
Setup [setting the Input type (SEWU), Input range, Output 0% value, Output 100% value,
Output type, etc.] should be done before using this unit, according to the user’s conditions.
Setup is performed in the Input 1/Output 1 function group, Output 2 function group andSpecial function group.
If the user’s specifications are the same as the factory default of the instrument, or if setup
has already been completed, it is not necessary to set up the instrument. Proceed to Section“7. Adjustment”.
Refer to factory defaults on (Tables 6-1, 6-2, 6-3).
(Table 6-1) Input 1/Output 1 Function Group
Setting Item
Factory Default
Input type
DC voltage (Available for the SEWU only)
1 to 5 V DC
-1999 to 9999 (SEWU, SEWV)
4 to 20 mA DC -1999 to 9999 (SEWA)
Input range (*)
K-200 to 1370 (SEWE)
Pt100 -200 to 850(SEWR)
Decimal point place
No decimal point-1999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)
Output 0% value-200(SEWE, SEWR)
9999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)
Output 100% value
1370 (SEWE)
850(SEWR)
Filter time constant
0.0 sec
0(SEWU, SEWA, SEWV, SEWD, SEWD-F)
Sensor correction
0.0(SEWE, SEWR)
Output type
4 to 20 mA DC
Output Normal/Reverse Normal
Burnout
Upscale (SEWE, SEWR)(*) Not available for the SEWD, SEWD-F.

(Table 6-2) Output 2 Function Group
Setting Item
Output 0% value

Factory Default-200 (SEWE, SEWR)
1370 (SEWE)
Output 100% value
850 (SEWR)
Output type
4 to 20 mA DC
Output Normal/Reverse Normal(Table 6-3) Special Function Group
Setting Item
Set value lock
Input sampling period(Response time)Auto-light function
Display selection
Indication time

Factory Default
Unlock
250 ms [425 ms (typ.) (0Disabled
Input value/Output 1 value
00.00 (Remains lit)
18

90%)]

6.1 Indication after Power-on
After power-on, the unit moves to warm-up status for approx. 3 sec as shown below(Fig. 6.1-1).

Indicates the input type.
Indicatesfor 1 to 5 V DC factory
default.

Lights whenpower-on.

Indicates Output 1 type.
Indicatesfor 4 to 20 mA DC
factory default.

(Fig. 6.1-1)
After that, the unit switches to RUN mode as shown below (Fig. 6.1-2).

Lights whenpower-on.

Input
value

Indicates the input value.

Outputvalue

Indicates Output 1 value as a percentage(%), corresponding to input value.

(Fig. 6.1-2)
6.2 Basic Operation of Setup
Setup is conducted in the Input 1/Output 1 function group, Output 2 function group andSpecial function group.
(e.g.) For the SEWU, to enter the Input 1/Output 1 function group:(1) In RUN mode, press the
key 3 times. (Fig. 6.2-1, p.20)(2) Press the
key while Input 1/Output 1 function group characters are indicated.
(Fig. 6.2-2, p.20)(3) The unit moves to the [Input type] item in the Input 1/Output 1 function group.
To set (or select) each item, use theorkey, and register the value
with thekey. (Fig. 6.2-3, p.20)
If thekey is pressed at the last setting item, the unit will revert to RUN mode.

19

(1) RUN Mode

Input
value
Outputvalue
In RUN mode, press the
3 times.

key(Fig. 6.2-1)(2) Input 1/Output 1 Function Group

Press thekey while Input 1/
Output 1 function group characters
are indicated.
(Fig. 6.2-2)(3) Selecting Input TypeTo set (or select)each item, use
these keys.

To proceed to each setting item or
to register the set (or selected) value,
use this key.

(Fig. 6.2-3)

20

6.3 Setup
6.3.1 Input 1/Output 1 Function GroupTo enter the Input 1/Output 1 function group, follow the procedure below.
(1)(2)

In RUN mode, press the
key 3 times.
Press thekey. For the SEWU, ‘Input type’ item appears.
For the SEWA, SEWV, SEWE, SEWR, each Input range item appears.
For the SEWD, SEWD-F, ‘Decimal point place’ item appears.

Set up the unit referring to the explanation of each item.
Display
IN

OUT

IN

OUT

Name, Function, Setting Range
Input type
Selects an input type.
Available for the SEWU only.
: Thermocouple: RTD: Direct current: DC voltage
Thermocouple input range
Selects thermocouple input range.
Available for thermocouple input.
: K -200 to 1370
:K-200 to 200 (*1):K
0 to 400 (*1)
: J -200 to 1000
:J-200 to 200 (*1):J
0 to 400 (*1):R
-50 to 1760
:S
-50 to 1760
:B
0 to 1820:E-200 to 800:T-200 to 400 (*1)
: N -200 to 1300
: PL0 to 1390
: W5Re/W26Re 0 to 2315
: W3Re/W25Re 0 to 2315
: K -328 to 2498
:K
-328 to 392 (*1):K
32 to 752 (*1)
: J -328 to 1832
:J
-328 to 392 (*1):J
32 to 752 (*1):R
-58 to 3200
:S
-58 to 3200
:B
32 to 3308
: E -328 to 1472
:T
-328 to 752 (*1)
: N -328 to 2372
: PL- 32 to 2534
: W5Re/W26Re 32 to 4199
: W3Re/W25Re 32 to 4199
21

Factory Default
DC voltage

K -200 to 1370

DisplayName, Function, Setting Range
Factory Default
RTD input range
Pt100 -200 to 850
Selects RTD input range.
OUT
Available for RTD input.
: Pt100-200 to 850: Pt100-100 to 100 (*1)
: JPt100 -200 to 500: Pt100 -328 to 1562
: Pt100-148 to 212 (*1)
: JPt100-328 to 932
IN
Direct current input range
4 to 20 mA DC -1999 to 9999
Selects Direct current input range.
OUT
Available for Direct current input.
: 4 to 20 mA DC -1999 to 9999
: 0 to 20 mA DC -1999 to 9999
: 0 to 16 mA DC -1999 to 9999
: 2 to 10 mA DC -1999 to 9999
: 0 to 10 mA DC -1999 to 9999
: 1 to 5 mA DC -1999 to 9999
: 0 to 1 mA DC -1999 to 9999
IN
DC voltage input range
1 to 5 V DC -1999 to 9999
Selects DC voltage input range.
OUT
Available for DC voltage input.
: 0 to 10 mV DC -1999 to 9999
: -10 to 10 mV DC -1999 to 9999
: 0 to 50 mV DC -1999 to 9999
: 0 to 60 mV DC -1999 to 9999
: 0 to 100 mV DC -1999 to 9999
: 0 to 1 V DC
-1999 to 9999
: 0 to 5 V DC
-1999 to 9999
: 1 to 5 V DC
-1999 to 9999
: 0 to 10 V DC
-1999 to 9999
IN
Decimal point place
No decimal point
Selects the decimal point place.
OUT
Available for DC voltage, current input.
When (*1) range (pp. 21, 22) is selected in [Thermocouple input range] & [RTD
input range], ‘No decimal point’ or ‘1 digit after decimal point’ can be selected.
: No decimal point: 1 digit after decimal point: 2 digits after decimal point: 3 digits after decimal point-1999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)
IN
Output 0% value-200(SEWE, SEWR)
OUT• Thermocouple, RTD input:
Sets the temperature at 0% output.
Setting range: Input range low limit to Output 100% value (*2)
• DC voltage, current input or SEWD, SEWD-F:
Sets the value (indicated on the Input Display) at 0% output.
Setting range: -1999 to Output 100% value(*2) The minimum input span is 50 (100 ).
22
INDisplayName, Function, Setting Range
Factory Default
9999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)
Output 100% value
1370 (SEWE)
OUT850(SEWR)• Thermocouple, RTD inputs:
Sets the temperature at 100% output.
Setting range: Output 0% value to Input range high limit value (*2)
• DC voltage, current inputs or SEWD, SEWD-F:
Sets the value (indicated on the Input Display) at 100% output.
Setting range: Output 0% value to 9999
IN
Filter time constant
0.0 seconds
Sets the filter time constant.
OUT
Reduces input fluctuation caused by noise.
Setting range: 0.0 to 10.0 seconds
IN
0(SEWU, SEWA, SEWV, SEWD, SEWD-F)
Sensor correction
0.0(SEWE, SEWR)
OUT
Sets the sensor correction value.
Input value = Current input value + (Sensor correction value)
Setting range:
Thermocouple, RTD inputs: -100.0 to 100.0 ( )DC voltage, current inputs, or SEWD, SEWD-F: -1000 to 1000
IN
Output type
4 to 20 mA DC
Selects the output type.
OUT: 4 to 20 mA DC: 0 to 20 mA DC: 0 to 12 mA DC: 0 to 10 mA DC: 1 to 5 mA DC: 0 to 1 V DC
: 0 to 5 V DC
: 1 to 5 V DC
: 0 to 10 V DC
IN
Output Normal/Reverse
NormalSelects either Output Normal mode (0.0 to 100.0%) or Reverse mode
OUT
(100.0 to 0.0%), corresponding to the input.
: Normal,: ReverseIN
Burnout
UpscaleSelects Upscale (110.0%) or Downscale (-10.0%) output when input
OUT
indicates burnout.
Available for thermocouple, RTD input.
: Upscale,: Downscale(*2) The minimum input span is 50 (100 ).
IN

6.3.2 Output 2 Function GroupTo enter the Output 2 function group, follow the procedure below.
(1)
In RUN mode, press thekey 4 times(2)
Press thekey. ‘Output 0% value’ item appears.
For the SEWU, if DC voltage or current input is selected, ‘Output type’ item appears.
For the SEWA, SEWV, SEWD, SEWD-F, ‘Output type’ item appears.
Set up the unit referring to each item.
23

DisplayName, Function, Setting Range
Factory Default-200(SEWE,
SEWR)
Output 0% value
Sets the temperature at 0% output.
OUT
Available for the thermocouple, RTD input.
Setting range: Input range low limit to Output 100% value (*)
IN
Output 100% value
1370 (SEWE)
850(SEWR)
OUT
Sets the temperature at 100% output.
Available for the thermocouple, RTD input.
Setting range: Output 0% value to Input range high limit value (*)
IN
Output type
4 to 20 mA DC
Selects the output type.
OUT: 4 to 20 mA DC: 0 to 20 mA DC: 0 to 12 mA DC: 0 to 10 mA DC: 1 to 5 mA DC: 0 to 1 V DC
: 0 to 5 V DC
: 1 to 5 V DC
: 0 to 10 V DC
IN
Output Normal/Reverse
NormalSelects either Output Normal mode (0.0 to 100.0%) or Reverse mode
OUT
(100.0 to 0.0%), corresponding to the input.
: Normal: Reverse(*) The minimum input span is 50 (100 ).
IN

6.3.3 Special Function GroupTo enter the Special function group, follow the procedure below.
(1)(2)

In RUN mode, press thekey 5 times.
Press thekey. ‘Set value lock’ item appears.

Set up the unit referring to the explanation of each item.
Display
IN

OUT

IN

OUT

Name, Function, Setting Range
Factory Default
Set value lock
UnlockLocks the set values to prevent setting errors.
: Unlock: Lock (None of the set values or adjusted values can be changed.)
Input sampling period (Response time) 250 ms [425 ms (typ.)(090%)]
Selects input sampling period (response time).
: 25 ms [65 ms (typ.) (090%)]: 125 ms [225 ms (typ.) (090%)]: 250 ms [425 ms (typ.) (0
90%)]
24

Display
IN

OUT

IN

OUT

IN

OUT

Name, Function, Setting Range
Factory Default
Auto-light function
Disabled
Selects Auto-light Enabled/Disabled.
: Disabled: Enabled
Display selection
Input value/Output 1 value
Selects items to be indicated on the Input and Output Displays.
Item
Input Display
Output Display
Input value
Output 1 value
Input value
No indication
Output 1 value
Output 2 value
No indication (*)
No indication (*)(*) Only the Power indicator is lit.
Indication time
00.00 (Remains lit)
Sets the indication time of the display after the final key operation.
Available when any item except
is selected in [Display selection].
The displays turn OFF (only the Power indicator is lit) after indication time
has passed.
If the,,or SUB-MODE Key is pressed while displays are in OFF
status, or if the power is turned ON again, the displays will light again.
Setting item:
00.00: Remains lit
00.01 (1 sec) to 60.00 (60 minutes) (Minutes.Seconds)

6.3.4 Using This Unit as a Standard Signal Conditioner
Set the Filter time constant to 0.0 seconds (p.23), and set the Output Normal/Reverse(p.23) to “Normal”.
6.3.5 Using the Reverse Function
This function reverses the output (100 to 0%) that corresponds to the input (0 to 100%).
Set the Output Normal/Reverse (p.23) to “Reverse”.
6.3.6 Using the First Order Lag Filter Function
The value is outputted by performing the first order lag computation using the Filter time
constant “T”. (Fig. 6.3.6-1)
Set the filter time constant (p.23) to a random value (0.0 to 10.0 seconds).

Input
Time

OutputT

Time(Fig. 6.3.6-1)
25

7. Adjustment
Performs the Output Zero and Span Adjustments for Output 1, Output 2 respectively.
Connect an mV generator or Dial resistor to the input terminals of this instrument.
Connect a Digital multimeter to the output terminals.
7.1 Basic Operation of Adjustment
Perform adjustment in the Output 1 and Output 2 adjustment groups.
(e.g.) To enter Output 1 adjustment group on the SEWU
(1) In RUN mode, press the
key. (Fig. 7.1-1)(2) Press the
key while Output 1 adjustment group characters are indicated.
(Fig. 7.1-2)(3) The unit will proceed to the “Output Zero Adjustment” in Output 1 adjustment group.
For Output Zero and Span adjustment, use theorkey, and register the value
with thekey. (Fig. 7.1-3, p.27)
If thekey is pressed at the last adjustment item, the unit will revert to RUN mode.

(1) RUN Mode
Input
value
Outputvalue
In RUN mode, press the
once.

key

(Fig. 7.1-1)(2) Output 1 Adjustment Group

Press thekey while Output 1
adjustment group characters areindicated.
(Fig. 7.1-2)
26

(3) Output Zero Adjustment

To proceed to each adjustment
item in Adjustment mode, andto register the adjusted value,please use this key.

Please use
these keys
for adjustment.

(Fig. 7.1-3)
7.2 Adjustment
7.2.1 Output 1 Adjustment GroupTo enter Output 1 adjustment group, follow the procedure below.
(1)
In RUN mode, press the
key once.
(2)
Press thekey. ‘Output Zero Adjustment’ item appears.
Adjust the unit referring to the explanation of each item.
DisplayIN

OUT

Name, Function, Setting Range
Factory Default
0.00%
Output Zero Adjustment
Adjusts Output Zero.
Input the value corresponding to 0% output, then adjust the value with theor
key while viewing the output value (on the Digital multimeter).
When the output range lower limit is Zero, (even if Zero Adjustment
results in a negative value), the output value will not be negative.
Setting range: -5.00 to 5.00%(Effective range of adjustment differs depending on the output type.)
Output Type
4 to 20 mA DC
0 to 20 mA DC
0 to 12 mA DC
0 to 10 mA DC
1 to 5 mA DC
0 to 1 V DC
0 to 5 V DC
1 to 5 V DC
0 to 10 V DC

IN

OUT

Effective Adjustment Range-5 to 5%0 to 5%0 to 5%0 to 5%-5 to 5%0 to 5%0 to 5%-5 to 5%0 to 5%

Output Span Adjustment
0.00%
Adjusts Output Span.
Input the value corresponding to 100% output, then adjust the value withtheor
key while viewing the output value (on the Digital multimeter).
Setting range: -5.00 to 5.00%
Effective range of adjustment is 95 to 105%.
27

7.2.2 Output 2 Adjustment GroupTo enter Output 2 adjustment group, follow the procedure below.
(1)
In RUN mode, press the
key twice.
(2)
Press thekey. ‘Output Zero Adjustment’ item appears.
Setting items are the same as those of Section “7.2.1 Output 1 Adjustment Group”.
Adjust Output zero and span referring to Section “7.2.1 Output 1 Adjustment Group”.

8. Operation
8.1 Indication after Power-on
After power-on, the unit moves to warm-up status for 3 seconds as shown below(Fig. 8.1-1).

Indicates the input type.
(Fig. 8.1-1) (p.29)
Indicatesfor 1 to 5 V DC
factory default.

Lights after
power-on.

Indicates Output 1 type.
(Fig. 8.1-2) (p.29)
Indicatesfor 4 to 20 mA
DC factory default.
(Fig. 8.1-1)
8.2 Unit Operation
The unit enters RUN mode after 3-second warm-up. (Fig. 8.2-1)
The input selected in [Input type] is converted to the output selected in [Output type].

Lights after
power-on.

Input
value

Indicates the input value.

Outputvalue

Indicates Output 1 value
as a percentage (%),
corresponding to input value.

(Fig. 8.2-1)

28

(Table 8.1-1)
Input
K
K
K
J
J
J
R
S
B
E
T
N
PLW5Re/W26Re
W3Re/W25Re
Pt100
Pt100
JPt1004 to 20 mA DC
0 to 20 mA DC
0 to 16 mA DC
2 to 10 mA DC
0 to 10 mA DC
1 to 5 mA DC
0 to 1 mA DC
0 to 10 mV DC-10 to 10 mV DC

0 to 50 mV DC
0 to 60 mV DC
0 to 100 mV DC

0 to 1 V DC
0 to 5 V DC
1 to 5 V DC
0 to 10 V DC
(Table 8.1-2)
Output4 to 20 mA DC
0 to 20 mA DC
0 to 12 mA DC
0 to 10 mA DC
1 to 5 mA DC
0 to 1 V DC
0 to 5 V DC
1 to 5 V DC
0 to 10 V DC

Input Display: -200 to 1370
: -200 to 200:
0 to 400: -200 to 1000
: -200 to 200:
0 to 400: -50 to 1760
: -50 to 1760:
0 to 1820: -200 to 800: -200 to 400: -200 to 1300:
0 to 1390:
0 to 2315:
0 to 2315: -200 to 850: -100 to 100: -200 to 500: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999
: -1999 to 9999

:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:
:

Output Display

29-328 to 2498
-328 to 392
32 to 752
-328 to 1832
-328 to 392
32 to 752
-58 to 3200
-58 to 3200
32 to 3308
-328 to 1472
-328 to 752-328 to 2372
32 to 2534
32 to 4199
32 to 4199
-328 to 1562
-148 to 212-328 to 932

• Indication when input value is -200.0 (-2000) or less
When the range has a decimal point: For the indication of -200.0 or less (up to –10%
output), the input value and the minus (-) sign are indicated alternately.
For DC voltage or current input, the indication of -2000 or less is the same as the above.
(e.g.) Indication of -200.0
IN
IN• Indication when input value is 10000 or more
When DC voltage or current input is selected: For the indication of 10000 or more (up to
110% output), the lower 4 digits of input value are flashing.
(e.g.) Indication of 10020
IN
Flashes.

• Under-range, Over-range and Sensor Burnout Indication
The following will be indicated whatever setting item is selected in [Display selection].
(p.25)
Under-range: "" flashes on the Input Display.
Over-range: "" flashes on the Input Display.

• Indication Time Setting
If indication time (p.25) is set, the displays will go off after the indication time has elapsed.
(Only the Power indicator remains lit.)
If power is turned ON again, or if any of the keys,,
or the SUB-MODE Key
is pressed while displays are unlit, the displays will light again.

30

9. Specifications
Input Specifications
SEWU (Thermo- Input resistance: 1 M min.
External resistance: 100
max. However, B: 40
max.
couple)Burnout:
Upscale,Downscale(Selectablebykeypad)SEWE
Input:
Thermocouple
Input Range
K-200 to 1370
-328 to 2498
J-200 to 1000
-328 to 1832
R
-50 to 1760
-58 to 3200
S
-50 to 1760
-58 to 3200
B
0 to 1820
32 to 3308
E-200 to 800-328 to 1472
T
-200 to 400-328 to 752
N-200 to 1300
-328 to 2372
PL0 to 1390
32 to 2534
W5Re/W26Re
0 to 2315
32 to 4199
W3Re/W25Re
0 to 2315
32 to 4199
The minimum input span is 50 (100 ).
SEWU (RTD),
Input detection current: Approx. 0.2 mA
Allowable lead wire resistance: 10
max. per wire
SEWR
Burnout: Upscale, Downscale (Selectable by keypad)
Input:
RTD
Input Range
Pt100-200 to 850-328 to 1562
JPt100-200 to 500-328 to 932
The minimum input span is 50 (100 ).
SEWU (Direct
current),
SEWA

SEWU (DCvoltage),
SEWV

Input
Shunt Resistor
4 to 20 mA DC
0 to 20 mA DC
50
0 to 16 mA DC
2 to 10 mA DC
100
0 to 10 mA DC
1 to 5 mA DC
200
0 to 1 mA DC
1k
Connect a shunt resistor (sold separately) between input terminals.
Input

Input
Resistance

0 to 10 mV DC-10 to 10 mV DC
0 to 50 mV DC
0 to 60 mV DC
0 to 100 mV DC
0 to 1 V DC
0 to 5 V DC
1 to 5 V DC
0 to 10 V DC

1M

31

Allowable signal
source resistance
20
max.
40
max.
200

max.

2k

max.

1k

max.

SEWD, SEWD-F

Input
4 to 20 mA DC

Shunt Resistor
50
built-in

Output Specifications
When the output range lower limit is zero, (even if Zero Adjustment results in anegative value), the output value will not be negative.
Direct current
Allowable load Zero adjustment Span adjustment
Outputresistance
range
range
4 to 20 mA DC
0 to 20 mA DC
0 to 12 mA DC
0 to 10 mA DC
1 to 5 mA DC
DC voltage
Output0 to 1 V DC
0 to 5 V DC
1 to 5 V DC
0 to 10 V DC

700
700
1.2 k
1.2 k
2.4 k

max.
max.
max.
max.
max.

-5 to 5%0 to 5%0 to 5%0 to 5%-5 to 5%95 to 105%
95 to 105%
95 to 105%
95 to 105%
95 to 105%

Allowable load Zero adjustment Span adjustment
resistance
range
range

100
500
500
1k

min.
min.
min.
min.

0 to 5%0 to 5%-5 to 5%0 to 5%95 to 105%
95 to 105%
95 to 105%
95 to 105%

Power supply for 2-wire transmitter (SEWD, SEWD-F)
Output voltage
Ripple voltage
Max load current
Output impedance(SEWD-F)
Performance
Basic accuracy(at 23 )Cold junction
compensation
accuracy

24 to 28 V DC (when load current is 20 mA DC)
Within 200 mV DC (when load current is 20 mA DC)
25 mA DC240
(Suitable for Field communicator usage)

SEWU (thermocouple input), SEWE:
Within 0.1% of each input span
R, S inputs -50 to 200 (-58 to 392 ): Within 6 (12 )B input 0 to 300 (32 to 572 ): Accuracy is not guaranteed.
K, J, E, T, N inputs, less than 0 (32 ): Within 0.4% of each
input span
SEWU (RTD input), SEWR:
Within 0.1% of each input span
SEWU (DC voltage, current inputs), SEWA, SEWV, SEWD, SEWD-F:
Within 0.1%
Output: Within 0.1%
Within 1 at -5 to 55 [SEWU (thermocouple input), SEWE]

32

Indication accuracy Within Basic accuracy (input)

Input sampling
periodResponse time
Temperature
coefficient

1 digit
25 ms, 125 ms, 250 ms (Selectable by keypad)
65 ms (typ.) (090%) (Input sampling period 25 ms)
225 ms (typ.) (090%) (Input sampling period 125 ms)
425 ms (typ.) (090%) (Input sampling period 250 ms)
0.015%/ max.

Insulation
Input – Output – Power: 10 M min., at 500 V DC
resistanceDielectric strength Input – Output – Power: 2.0 kV AC for 1 minute

General Structure
Case
Front panel
Setting

Flame-resistant resin, Color: Light gray
Membrane sheet
Setting by the front keypadConsole connector For the CMB-001 (USB communication cable)
Input Display: 7-segment 4-digit Red LED display
Displays,
Character size:10 x 4.6 mm (H x W)
Indicator
Output Display: 7-segment 4-digit Red LED display
Character size: 10 x 4.6 mm (H x W)
Power indicator: Green LED

Installation Specifications
Power supply
100 to 240 V AC 50/60 Hz, 24 V AC/DC 50/60 Hz
Allowable
85 to 264 V AC，20 to 28 V AC/DC
voltage range
Power
Approx. 8 VA
consumption
Ambient-5 to 55 (23 to 131 )temperature
Ambient humidity 35 to 85%RH (Non-condensing)
WeightApprox. 190 g (Socket included)
Mounting
DIN rail
Dimensions
30 (W) x 88 (H) x 108 (D) mm (Socket included)
Attached Function
Auto-lightfunction

Power failurecountermeasureSelf-diagnosis

Cold junction
temperaturecompensation

Display brightness is controlled from the front light sensor after
measurement, saving energy.
The setting data is backed up in the non-volatile IC memory.
The CPU is monitored by a watchdog timer, and if an abnormal status
is found on the CPU, the unit is switched to warm-up status.
At this time all outputs are turned OFF.
This detects the temperature at the connecting terminal between thethermocouple and the instrument, and always maintains it at the same
status as if the reference junction location temperature was at 0 (32 ).
Available for the SEWU (thermocouple input), SEWE.

33

10. Troubleshooting
10.1 Indication
Problem
The Input Display is
flashing "
" or
"
".

Possible Cause
The sensor may be burnt out.

Solution
Replace the sensor.

The sensor is not securely
connected to the input terminalsof the instrument.

Ensure that the sensor
terminals are securely
connected to the input
terminals of the instrument.
Check the input signal
source.
Ensure that they are wired
correctly.

Input signal is not normal.

The indication of the
Input Display isirregular or unstable.

Polarity of thermocouple orcompensating lead wire is notcorrect.
Codes (A, B, B) of the RTD do
not match the instrument
terminals.
Sensor input and temperatureunit ( / ) selections are notcorrect.
Sensor correction value is notsuitable.
AC leaks into the sensor circuit.
There may be equipment thatinterferes with or makes noise
near the unit.

10.2 Key Operation
ProblemPossible Cause‘Lock’
isselected in [Set value
Setting or adjustment islock].
not possible.
10.3 Operation
Problem
Input value does notchange.

No output

Ensure that sensor type andtemperature unit ( / ) areselected correctly.
Set it to a suitable value.
Use an ungrounded typesensor.
Keep the unit clear of any
potentially disruptive
equipment.

Solution
Select ‘Unlock’.

Possible Cause
The sensor may be out of order.
Input and output wires are notsecurely connected to the I/O
terminals of the instrument.
Wiring of input and output is notcorrect.

Solution
Replace the sensor.
Ensure that input and output
wires are securely connectedto the I/O terminals.
Wire the input and output
correctly.

Output 100% value and Output
0% value are not set to suitablevalues.
Output type and Output
Normal/Reverse are not selected
correctly.

Set them to a suitable value.

34

Select Output type andOutput Normal/Reverse
correctly.

11. Character Table

Factory defaults are indicated in the following tables.

Input 1/Output 1 Function Group
Display

Setting Item
Input type
Thermocouple input range
RTD input range
Direct current input range
DC voltage input range
Decimal point place
Output 0% value
Output 100% value

Filter time constantSensor correction
Output typeOutput Normal/Reverse
Burnout

Factory Default

Data

DC voltage (SEWU)
K -200 to 1370 (SEWE)
Pt100 -200 to 850 (SEWR)
4 to 20 mA DC -1999 to 9999 (SEWA)
1 to 5 V DC -1999 to 9999 (SEWU, SEWV)No decimal point-1999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)-200(SEWE, SEWR)
9999 (SEWU, SEWA, SEWV, SEWD, SEWD-F)
1370 (SEWE)
850(SEWR)
0.0 sec
0(SEWU, SEWA, SEWV, SEWD, SEWD-F)
0.0(SEWE, SEWR)
4 to 20 mA DC
NormalUpscale (SEWE, SEWR)

Output 2 Function Group
Display

Setting Item
Output 0% value
Output 100% value
Output typeOutput Normal/Reverse

Factory Default

Data-200 (SEWE, SEWR)
1370 (SEWE)
850 (SEWR)
4 to 20 mA DC
NormalSpecial Function Group
Display

Setting Item
Set value lock
Input sampling period(Response time)Auto-light function
Display selection
Indication time

Factory Default
Unlock
250 ms [425 ms (typ.) (0

Data

90%)]

Disabled
Input value/Output 1 value
00.00 (Remains lit)

Output 1, Output 2 Adjustment GroupOutput 1 and Output 2 have respective setting items.
Display

Setting Item
Output zero adjustment
Output span adjustment

Factory Default
0.00%
0.00%
35

Data

****** Inquiries ******For any inquiries about this unit, please contact the vendor where youpurchased the unit or our agency after checking the following.
(e.g.)• Model ........................………. SEWU-1-0• Serial number ….................... No. 104F05000
In addition to the above, please let us know the details of malfunction,or discrepancy, and the operating conditions.

SHINKO TECHNOS CO., LTD.
OVERSEAS DIVISION

Head Office: 2-5-1, Senbahigashi, Minoo, Osaka, Japan
http://www.shinko-technos.co.jp
URL:
Tel: +81-72-727-6100
E-mail:overseas@shinko-technos.co.jp
Fax: +81-72-727-7006
No.SEWx1E2 2014.08