SPEC. SHEET

Digital Indicating Controller

Model:

BCS2, BCR2, BCD2

Model(e.g.) BCS2 R 0 0–1 3
Size: 48 x 48 x 68 mm (W x H x D) (Depth of control panel interior 60)
Control output: Relay contact
Power supply: 100 to 240 V AC
Input: Multi-range
Option 1: Event output EV2
Option 2: Event input (2 points) + Heater burnout alarm (20A)
Size

Control
OutputPower
SupplyInput(*1)

Option 1(*2)

Option 2(*2)

Specification

BCS2

48 x 48 x 68 mm (W x H x D) (Depth of control panel interior 60)

BCR2

48 x 96 x 68 mm (W x H x D) (Depth of control panel interior 60)

BCD2

96 x 96 x 68 mm (W x H x D) (Depth of control panel interior 60)
R

Relay contact: 1aS

Non-contact voltage (for SSR drive): 12 V DC 15%

A

Direct current: 4 to 20 mA DC
0100 to 240 V AC (Standard)

1

24 V AC/DC
0–

Multi-range (*1)
0

No option needed12

Event output EV2 (*3)
Heating/Cooling control output OUT2,
Non-contact voltage
Heating/Cooling control output OUT2,
Direct current
Insulated power output
Event output EV2 + Heating/Cooling control
output OUT2 Relay contact (*4)
Event output EV2 + Heating/Cooling control
output OUT2 Non-contact voltage (*4)
Event output EV2 + Heating/Cooling control
output OUT2 Direct current (*4)

3
4
5
6
7
0
1
2
3
4
5
6
7
8
9

No option needed
Event input (2 points) + Serial communication +Heater burnout alarm (20A) (*5) (*6)
Event input (2 points) + Serial communication +Heater burnout alarm (100A) (*5) (*6)
Event input (2 points) +Heater burnout alarm (20A) (*6)
Event input (2 points) +Heater burnout alarm (100A) (*6)
Event input (2 points) + External setting input +Transmission output (*7)
Serial communication
Heater burnout alarm (20 A) (*6)
Heater burnout alarm (100 A) (*6)
Event input (2 points)

EV2
DS
DA
P24
EV2+
DR
EV2+
DS
EV2+
DA
C5W (20A)
C5W (100A)
EIW (20A)
EIW (100A)
EIT
C5W (20A)W (100A)
EI(*1) Thermocouple, RTD, Direct current and DC voltage can be selected by keypad.
(*2) Only one option can be selected from Option 1 and Option 2 respectively.
(*3) Event output EV1 is standard.
The following outputs can be selected in [Event output EV1/EV2 allocation] by keypad:
Alarm output (12 alarm types and No alarm action), Heater burnout alarm output, Loop break alarm output, Time signal output,
Output during AT, Pattern end output, Output by communication command, Heating/Cooling control output OUT2 (for EV2 option only)
Event output EV1/EV2, Heater burnout alarm output and ‘Output by communication command’ are available only when C5W, EIW, C5 or W
option is ordered.
(*4) Available only for BCR2, BCD2.
If EV2+D and EIT options are ordered together, transmission output terminals will be used for EV2 output terminals.
Therefore, Transmission output will be disabled.
(*5) For BCS2, 2 points of Event input are not available.
(*6) For Direct current output type, C5W, EIW or W option cannot be ordered. The CT is sold separately.
(*7) For BCS2, 1 point of Event input is available.

Accessories Sold Separately
Model
Terminal cover (for BCS2) (TC-ACS)
Terminal cover (for BCR2) (TC-BCR2)
Terminal cover (for BCD2) (TC-BCD2)
CT for 20A (CTL-6-S-H) (*)
CT for 100A (CTL-12-S36-10L1U) (*)
Tool cable CMD-001
USB cable (CUS-100)(*) Used for Heater burnout alarm (C5W, EIW, W options)RatingRated Scale
Input (TC)

Scale Range-200 to 1370
-328 to 2498
-200.0 to 400.0-328.0 to 752.0-200 to 1000
-328 to 1832
0 to 1760
32 to 3200
0 to 1760
32 to 3200
0 to 1820
32 to 3308
-200 to 800-328 to 1472
-200.0 to 400.0-328.0 to 752.0-200 to 1300
-328 to 2372
0 to 1390
32 to 2534
0 to 2315
32 to 4199

K
J
R
S
B
E
T
N
PLC(W/Re5-26)

Resolution
1 ( )0.1 ( )
1 ( )
1 ( )
1 ( )
1 ( )
1 ( )
0.1 ( )
1 ( )
1 ( )
1 ( )

Input (RTD)
Pt100
JPt100
Input (DC)
4 to 20 mA
0 to 20 mA
0 to 1 V
0 to 5 V
1 to 5 V
0 to 10 V

Scale Range-200.0 to 850.0-328.0 to 1562.0-200 to 850-328 to 1562
-200.0 to 500.0-328.0 to 932.0-200 to 500-328 to 932
Scale Range

Resolution
0.1 ( )1 ( )
0.1 ( )1 ( )Resolution-2000 to 10000 (*1)1(*1) Decimal point place change and scaling are possible.

Input
Thermocouple (TC)
RTD
Direct current (mA DC)

DC voltage (V DC)

K, J, R, S, B, E, T, N, PL- , C (W/Re5-26)
External resistance, 100
or less (However, B input: External resistance, 40
Pt100, JPt100, 3-wire type
Allowable input lead wire resistance: 10or less per wire
0 to 20 mA, 4 to 20 mA DC
Input impedance:
50
or less
Allowable input current: 50 mA or less0 to 1 V DC
Input impedance: 1 M or more
Allowable input voltage: 5 V DC or less
Allowable signal source resistance: 2 k or less0 to 5 V, 1 to 5 V, 0 to 10 V DC
Input impedance: 100 k or more
Allowable input voltage: 15 V DC or less
Allowable signal source resistance: 100
or less

Indicating Performance
Base accuracy
Thermocouple

RTD
Direct current
DC voltage
Effect of ambient temperature
Input sampling period
Time accuracy

At ambient temperature 23(for a single unit mounting)Within 0.2% of each input span 1 digit,
However, R, S inputs, 0 to 200 (32 to 392 ): Within 6 (12 )B input, 0 to 300 (32 to 572 ): Accuracy is not guaranteed.
K, J, E, T, N inputs, less than 0 (32 ): Within 0.4% of input span 1 digit
Within 0.1% of each input span 1 digit
Within 0.2% of each input span 1 digit
Within 0.2% of each input span 1 digit
Within 50 ppm/ of each input span
125 msWithin 1.0% of the setting time2or less)

Control PerformanceControl action

OUT1
proportional
band
Integral time
Derivative time
OUT1 proportional cycle
ARW
Manual reset

OUT1 ON/OFF
hysteresis
OUT1 high limit,
OUT1 low limit
Control output• PID control (with auto-tuning function)• PI control
When derivative time is set to 0
• PD control (with Auto-reset, Manual reset function)
When integral time is set to 0
• P control (with Auto-reset, Manual reset function)
When derivative time and integral time are set to 0.
• ON/OFF control
When proportional band is set to 0 (or 0.0)
Thermocouple, RTD inputs without decimal point: 0 to Input span [Factory default: 10
Thermocouple, RTD inputs with decimal point: 0.0 to Input span
Direct current, DC voltage inputs: 0.0 to 1000.0%
0 to 3600 sec (Factory default: 200 sec)
0 to 1800 sec (Factory default: 50 sec)

0.5, or 1 to 120 sec (Factory default: Relay contact: 30 sec Non-contact voltage: 3 sec
Direct current: Not available)
0 to 100% (Factory default: 50%)
Proportional band (Factory default: 0.0)
For direct current, DC voltage input, it is possible to set up to ‘2-digits after decimal point’.
If the proportional band exceeds 100.0%, the setting range will be 100.00%
Thermocouple, RTD inputs: 0.1 to 1000.0 ( ) (Factory default: 1.0 )Direct current, DC voltage inputs: 1 to 10000 (The placement of the decimal point follows the selection)
0 to 100% (Direct current output: -5 to 105%)(Factory default: OUT1 low limit: 0%, OUT1 high limit: 100%)
Relay contact: 1aControl capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4),
Electrical life: 100,000 cycles
Minimum applicable load: 10 mA 5 V DC
Non-contact voltage (for SSR drive):
12 V DC 15%
Max. 40 mA (short circuit protected)
Direct current: 4 to 20 mA DC (Resolution: 12000)
Load resistance: Maximum 550

General Structure
Case material, Color

Flame-resistant resin, Black

Panel

Membrane sheet

Dust-proof/Drip-proof

Front panel: IP66, Rear case: IP20, Terminal section: IP00

Standards

EN61010-1 (Pollution degree 2, Overvoltage category )EMI: EN61326
Electric-field strength of radiated disturbance: EN55001 Group 1 Class A
Terminal noise voltage: EN55011 Group 1 Class A
EMS: EN61326
UL60730
File No. E159038

EN
EC
(EMC
directive)
UL(20 )]

3

Indication Structure
BCS2

BCR2

BCD2

(1)
(1)

(9)
(2)

(3)
(3)

(4)

(2)

(4)

(1)

(4)

(2)

(5)

(8) (5)

(8)

(5)

(8)

(6)

(7) (6)(7) (6)(7)

Display(1) PV Display

Indicates the PV (process variable) or setting characters in setting mode.

(2)

SV Display

Indicates the SV (desired value) or set data in setting mode. In Monitor mode, indicates MV (manipulated variable),remaining step time (Program control), step number (Program control) (*), or Set value memory number (Fixed value
control) (*). (*): For BCS2 only(3)

MEMO/STEP
Display

Indicates Set value memory number or Step number (Program control). (BCR2, BCD2)

Action Indicator(4)

O1

Lights up when control output OUT1 is ON. For direct current output type, flashes corresponding to the MV in 125 ms cycles.

O2

Lights up when control output OUT2 (EV2, DS, DA, EV2+D options) is ON.
For direct current output type, flashes corresponding to the MV (manipulated variable) in 125 ms cycles.

EV1

Lights up when Event output 1 is ON.

EV2

Lights up when Event output 2 (EV2, EV2+D options) is ON.
Turns off when 019 is selected in [Event output EV2 allocation].

AT

Flashes while AT, ‘AT on startup’ or Auto-reset is performing.

R/L

Lights up while in Remote action (EIT option).

T/R

Lights up during Serial communication (C5W option) TX (transmitting) output.

MEMO

Lights up when Set value memory number is indicated. (BCR2, BCD2)STEPLights up when Step number (Program control) is indicated. (BCR2, BCD2)

Keys, Connector(5)

UP keyIncreases the numeric value.
If this key is pressed for 1 second during program operation, the unit proceeds to the next step (Advance function).

(6)

DOWN keyDecreases the numeric value.

(7)

MODE key(8)

OUT/OFF
key

Selects the setting mode, and registers the set data.
In RUN mode, if this key is pressed for 3 seconds, the unit moves to Monitor mode.
OUT/OFF function: Turns the control output ON or OFF.
Auto/Manual control: Switches the Auto/Manual control.
Program control: Starts or stops the Program control.

(9)Consoleconnector

Tool cable connector is at the top of the instrument (BCS2, BCR2, BCD2).
By connecting the tool cable (CMD-001, sold separately), the following operations can be conducted from an external
computer using the Console software SWC-BCx01M.
• Reading and setting of SV, PID and various set values • Reading of PV and action status • Function change

4Terminal Arrangement
BCS2

POWER SUPPLY
EV1
EV2
O2
P24
O1
TC
RTD
DC
CT1
CT2
RS-485EVENT INPUTEXT CONT
TRANSMIT OUTPUT

BCR2, BCD2

100 to 240 V AC or 24 V AC/DC
Event output 1
Event output 2 (EV2, EV2+D options)Control output OUT2 (EV2, DS, DA, EV2+D options)
24 V insulation voltage (P24 option)
Control output OUT1
Thermocouple input
RTD input
Direct current, DC voltage inputs
CT input 1 (C5W, EIW, W option)
CT input 2 (C5W, EIW, W option)
Serial communication RS-485 (C5W, C5 option)
Event input DI1 (BCS2: EIW, EIT, EI options, BCR2/BCD2: C5W, EIW, EIT, EI options)
Event input DI2 (BCS2: EIW, EI options,
BCR2/BCD2: C5W, EIW, EIT, EI options)
External setting input (EIT option)
Transmission output (EIT option) or Event output EV2 (EV2+D option)
For BCR2, BCD2, if EV2+D and EIT options are ordered together, transmission output terminals will be used forEV2 output terminals. Therefore, Transmission output will be disabled.

Standard Functions
EV1 Output
OutputRelay contact: 1aControl capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
Minimum applicable load:10 mA 5 V DC

Alarm Action
Alarm typeHigh limit alarm, Low limit alarm, High/Low limits alarm, High/Low limits independent, High/Low limit range, High/Low
limit range independent, Process high alarm, Process low alarm, High limit with standby alarm, Low limit with standby
alarm, High/Low limits with standby, High/Low limits with standby independent.
Energized/De-energized action are applied to the above alarms, totaling 24 alarm types. No alarm action can also be
selected.

ActionON/OFF action
0.1 to 1000.0 ( ) (Factory default: 1.0 )Direct current, DC voltage inputs: 1 to 10000 (The placement of the decimal point follows the selection)

Hysteresis
OutputAlarm value 0
Enabled/Disabled

EV1 or EV2 output for which Alarm output (000 to 012) is selected in [Event output EV1/EV2 allocation].
If ‘Enabled’ is selected in [Alarm value 0 Enabled/Disabled], the following alarm type activates even if alarm value isset to 0 (zero): High limit alarm, Low limit alarm, High/Low limits alarm, High/Low limits independent alarm, High/Low
limit range alarm, High/Low limit range independent alarm, High limit with standby alarm, Low limit with standby
alarm, High/Low limits with standby alarm, High/Low limits with standby independent alarm.
5Loop Break Alarm
Setting range

Loop break alarm time: 0 to 200 minutes
Loop break alarm span: TC, RTD inputs: 0 to 150 ( ), 0.0 to 150.0 ( )Direct current, DC voltage inputs: 0 to 1500 (The placement of the decimal point follows the selection)

OutputEV1 or EV2 output for which Loop break alarm (014) is selected in [Event output EV1/EV2 allocation].

Simplified Converter Function
For Direct current output type, the BCx2 can be used as a simplified converter.
Converts each input value to ‘4 to 20 mA DC’, and outputs it).

Optional Functions
Event Input (Option code: C5W, EIW, EIT, EI)
If ‘Set value memory function’ is selected in [Event input DI1/DI2 allocation], SV1 to SV4 can be switched.
Event input

2 points [For the BCS2, if the C5W option is ordered, Event input (2 points) is not available.
If the EIT option is ordered, Event input (1-point) is available.]

Circuit current whenclosedApprox. 16 mA

EV2 Output (Option code: EV2)
Same as standard EV1 output
Heater Burnout Alarm (Option code: C5W, EIW, W)
If C5W or EIW option is ordered, Heater burnout alarm is disabled for direct current output type.
For direct current output type, the W option cannot be ordered
20A, 100A (Must be specified)
Rated current
Single-phase: Detects burnout with CT1 input
3-phase: Detects burnout with CT1 and CT2 inputs
Setting range
Setting accuracy
Action point

20A: 0.0 to 20.0 A (Off when set to 0.0)
100A: 0.0 to 100.0 A (Off when set to 0.0)
5% of rated current
Set value

ActionON/OFF action

OutputEV1 or EV2 output for which Heater burnout alarm (013) is selected in [Event output EV1/EV2 allocation].

Heating/Cooling Control Output (Option code: DS, DA, EV2)
OUT2 proportional band Thermocouple, RTD input without decimal point: 0 to Input span [Factory default: 10
Thermocouple, RTD input with decimal point: 0.0 to Input span
DC voltage, current inputs: 0.0 to 1000.0%(20 )]

Integral time (I)Same as that of OUT1

Derivative time (D)Same as that of OUT1

OUT2 proportional
cycle

0.5 sec, or 1 to 120 sec [Factory default: DS option: 3 sec, EV2 option (When 019 is selected in [Event output EV2
allocation]): 30 sec, Direct current (DA option): Not available]

Overlap/Dead bandsetting range
OUT2 ON/OFF
hysteresis

Thermocouple, RTD inputs: -200.0 to 200.0 ( ),Direct current, DC voltage inputs: -2000 to 2000 (The placement of the decimal point follows the selection)
Thermocouple, RTD inputs: 0.1 to 1000.0 ( ) (Factory default: 1.0 )Direct current, DC voltage inputs: 1 to 10000 (The placement of the decimal point follows the selection)

OUT2 high limit,
OUT2 low limit

0 to 100% (Direct current output: -5 to 105%) (Not available for ON/OFF control)(Factory default: OUT2 low limit: 0%, OUT2 high limit: 100%)

OUT2 cooling method(1) Air cooling (linear characteristics) (Factory default: Air cooling)(2) Oil cooling (1.5th power of the linear characteristics)(3) Water cooling (2nd power of the linear characteristics)

OutputRelay contact 1a: EV2 option: When 019 is selected in [Event output EV2 allocation]
Control capacity: 3 A 250 V AC (resistive load)
1 A 250 V AC (inductive load cos =0.4)
Electrical life: 100,000 cycles
Non-contact voltage (for SSR drive):DS option
12 V DC 15%
Max. 40 mA (short circuit protected)
Direct current:
DA option
4 to 20 mA DC (Resolution: 12000)
Load resistance: Max. 550
6Serial Communication (Option code: C5W, C5)
Communication line

EIA RS-485

Communication method Half-duplex communication
Synchronization method Start-stop synchronization
Communication speed
Data bit/Parity
Stop bit
Response delay time
Data format

9600, 19200, 38400 bps Selectable by keypad (Factory default: 9600 bps)
Data bit: 7, 8
Parity: Even, Odd, No parity (Selectable by keypad) (Factory default: 7 bits/Even)
1, 2 (Selectable by keypad) (Factory default: 1)
0 to 1000 ms (Factory default: 10 ms)
Response from the controller can be delayed after receiving command from the host computer.
Communication
protocolStart bit

Shinko protocol

Modbus ASCII

Modbus RTU
1

1

1

Data bit7

7 or 8

8

ParityYes (Even)

Yes (Even, Odd) No parity

Yes (Even, Odd) No parity

Stop bit1

1 or 2

1 or 2External Setting Input (Option code: EIT)
Setting signal
4 to 20 mA DC
Allowable input
50 mA DC or less
Input impedance
50
or less
Input sampling period
125 msTransmission Output (Option code: EIT)
Converting the value (PV, SV, MV, DV) to analog signal every 125 ms, outputs the value in current. (Factory default: PV transmission)
Resolution
12000
Output4 to 20 mA DC (Load resistance, Max. 550 )Output accuracy
Within 0.3% of transmission output span
Insulated Power Output (Option code: P24)
Output voltage
24 3 V DC (when load current is 30 mA DC)
Ripple voltage
Within 200 mV DC (when load current is 30 mA DC)
Max. load current
30 mA DC

Insulation, Dielectric Strength
Circuit Insulation Configuration
BCS2
When the C5W or C5 option is ordered

When the EIW, EI or W option is orderedElectrically insulatedElectrically insulated
1
2

POWER
SUPPLY

3

7

13
14

CT1
CT2

6

2
CPU

16
EV2
OUT2

17

13
POWER
SUPPLY

9

EV1

5

8

15

4

1

OUT1

RS-485

10

9
CPU

EV1
4

16

11

5
18

12

6

8

15

3
TC
RTD
DC

14

7
OUT1

CT1
CT2

EV2
OUT2

17

DI1
DI2

TC
RTD
DC

18

10
11
12

5
P24

: When C5W option is ordered.

65: When W option is ordered.
P24

6: When EI option is ordered.

When the EIT option is orderedElectrically insulated
1
2

POWER
SUPPLY

3

CT1

6

8

15

4

9
TA

16

EV2
OUT2

17
18

If OUT1 is a non-contact voltage output or direct
current output, and if OUT2 is a non-contact voltage
output or direct current output, OUT1 is not electricallyinsulated from OUT2.

OUT1

14

EV1

5

7

13

EXT
CONT

CPU
TC
RTD
DC

10
11
12

5
P24
6

7

BCR2, BCD2
When the C5W or C5 option is ordered
8

9

10

11

When the EIW or W option is ordered
12

10

DI1
DI2
RS-485
13
14

11

OUT1
16
17

CPU

1

14

2

15

3

16

21

17

19
20

TC
RTD
DC

22

18

EV2
OUT2

23

19

24

20

POWER
SUPPLY

Electrically insulated
1
CT1
CT2

OUT1

2
3

CPU

21

EV1

EV1
18

12

DI1
DI2
13

CT1
CT2

15

9

RS-485

Electrically insulated

POWER
SUPPLY

8

12

EV2
OUT2

TC
RTD
DC

22
23
24

19

19

P24

P24

20

: When C5W option is ordered.

20: When EIW option is ordered.

When the EIT or EI option is ordered
8

9

12

6

DI1
DI2
13
14

POWER
SUPPLYTAElectrically insulated

15

EXT
CONT

OUT1
16
17

If OUT1 is a non-contact voltage output or direct
current output, and if OUT2 is a non-contact voltage
output or direct current output, OUT1 is not electricallyinsulated from OUT2.

7

CPU

4
5
21

EV1
18
19
20

TC
RTD
DC

EV2
OUT2

22
23
24

19
P24

: When EIT option is ordered.

20

Insulation resistance

10 M

Dielectric strength

Between input terminal and power terminal: 1.5 kV AC for 1 minuteBetween output terminal and power terminal: 1.5 kV AC for 1 minuteBetween output terminal (P24) and power terminal: 500 V AC for 1 minuteor more, at 500 V DC

8Attached Functions
Sensor correction coefficient, Sensor correction, Set value lock, Auto/Manual control, Auto/Manual after power ON, SV ramp, SV Rise rate/Fall rate,
Step time unit, Program start temperature, Program control start type, Power restore action, Pattern end output, Power failure countermeasure,Self-diagnosis, Automatic cold junction temperature compensation, Indication range/Control range, Input error (Overscale, Underscale), Burnout,
Warm-up indication, Console communication
Simplified Program Control
Number of patterns
Number of steps

1
9

Number of repetitions

0 to 10000

Program time range

00:00 to 99:59 Unit: Hours:Minutes or Minutes:Seconds (Factory default: Hours:Minutes)

Setting range

Scaling low limit value to Scaling high limit value (Factory default: 0 )Time accuracy

WithinWait value

0 to 20% of input span (For direct current, DC voltage inputs: 0 to 20% of scaling span)

1.0% of the setting timeError CodeError CodeError Contents

Occurance Status(*1)

Non-volatile IC memory (EEPROM) is defective.

When power is turned ON(*1)

Data writing error when power failure occurs

When power is turned ON(*2)

When input value exceeds input range high limit value (Scaling high limit value for DC
input)

During usual operation(*2)

When input value drops below input range low limit value (Scaling low limit value for DC
input)

During usual operation(*2)

Input burnout, or input value is outside the control range or indication range.

During usual operation

Hardware malfunction, or in error status. Errors cannot be solved.

During usual operation

Indicated after 4 hours have passed since AT or ‘AT on startup’ is performed.
For ‘AT on startup’, delay time and slope cannot be measured correctly.

After AT or ‘AT on startup’ isperformed(*1)(*1) Errors can be cancelled with the MODE key.
(*2) Error codes are displayed when ‘Enabled’ is selected in [Error indication Enabled/Disabled].

Other
Power supply voltage(Must be specified
when ordering)

100 to 240 V AC, 50/60 Hz,
24 V AC/DC, 50/60 Hz,

Power consumption

100 to 240 V AC

Approx. 8 VA max. (When the maximum number of options are added: Approx. 11 VA max.)

24 V AC

Approx. 5 VA max. (When the maximum number of options are added: Approx. 8 VA max.)

24 V DC

Approx. 5 W max. (When the maximum number of options are added: Approx. 8 W max.)

100 to 240 V AC

Max. 14 to 34 A

24 V AC

Max. 34 A

Rush current

Allowable fluctuation range 85 to 264 V AC
Allowable fluctuation range 20 to 28 V AC/DC

24 V DC

Max. 34 A

Ambient temperature-10 to 55(Non-condensing, No icing)Ambient humidity

35 to 85 %RH (Non-condensing)

WeightBCS2: Approx. 110 g
BCR2: Approx. 160 g
BCD2: Approx. 220 g

Accessories included

Mounting frame 1 piece (BCS2), Screw type mounting bracket 1 set (BCR2, BCD2),
Instruction manual (excerpt) 1 copy

Accessories soldseparately

Terminal cover, CT (CTL-6-S-H) for Heater burnout alarm 20 A,
CT (CTL-12-S36-10L1U) for Heater burnout alarm 100 A, Tool cable CMD-001

Environmental
specification

RoHS directive compliant

Instruction manual

Please download the full Instruction Manual and Communication Instruction Manual from Shinko website:
http://www.shinko-technos.co.jp/e/9Dimensions (Scale: mm)
BCS2

Panel cutout (Scale: mm)
45 ＋0.50

Mounting framen×48-3＋0.5
0

45 ＋0.5
075

GasketTerminal cover(sold separately)

Horizontal close mounting
n: Number of units mounted

45 ＋0.5
0

BCR2

Screw type
mounting bracket

Terminal cover(sold separately)

Panel Cutout (Scale: mm)

13092＋0.80Gasket92＋0.80

n×48-3 ＋0.5
0Horizontal close mounting
n: Number of units mounted

45＋0.50

BCD2

GasketScrew type
mounting bracket

Terminal cover(sold separately)

130

92＋0.80Panel cutout (Scale: mm)□92＋0.8
0

n×96-3 ＋0.5
0Horizontal close mounting
n: Number of units mounted(*) When the terminal cover is used
CMD-001 (sold separately)

When connecting the USB cable CUS-100 (sold separately)
10.5

2000

200

3

60

34

Communication indicator
SHINKO TECHNOS CO., LTD.

Tool cable CMD-001

USB cable CUS-100

CUS-100: microUSB type B – USB Type A Full length 2 m(Commercially available USB cable can be used.)

2-5-1, Senbahigashi, Minoo, Osaka, 562-0035, Japan
TEL: +81-72-727-6100
FAX: +81-72-727-7006
URL: http://www.shinko-technos.co.jp/e/E-mail: overseas@shinko-technso.co.jp
20171003