Product Specification Sheet
Model: MS5507
Plug-In Distributor with Isolated Single Output

MS5500DESCRIPTION

51

The MS5507 is a plug-in distributor that powers a two-wiretransmitter, converts its 4 to 20mA signals into commonlyused DC signals, and provides an isolated single output. Thismodel can also be used as an isolator.

SZ
EX POWER

85

ON OFFORDERING CODE

MS5507 --_Model
136.5

Power Supply
A: 100 to 240V AC (50 to 60Hz)
D: 24V DC
P: 100 to 240V DC(mm)SPECIFICATIONS

Input
4 to 20mA DC from 2-wire transmitters

OutputA: 4 to 20mA DC
D: 0 to 20mA DC
Z: Other DC current signals●POWER SECTION
PowerRequirements

1: 0 to 10mV DC
2: 0 to 100mV DC
3: 0 to 1V DC
4: 0 to 10V DC
5: 0 to 5V DC
6: 1 to 5V DC
0: Other DC voltage signals

Options
No code: None
/K: Fast response (0 to 90% response time: 10ms max.)/H: Polyurethane conformal coating/X: Others (Special order)* For non-standard options, ask MTT for availability.

100 to 240V AC: 85 to 264V AC (47to 63Hz)
24V DC: 24V DC±10%
100 to 240V DC: 85 to 264V DC
Power Sensitivity
Better than ±0.1% of span for eachpower supply range.
Power Line Fuse
160mA fuse
Maximum Power Consumption
Power100-240V AC 24V DC
100-240V DCApprox.
Approx.
Approx.
6.5VA
2.1W
7.2W

●INPUT SECTION
Input Signal
Input ResistanceTransmitter Power
SupplyORDERING INFORMATION
To place an order, please use the ordering code format
as shown above.
(e.g.) MS5507-A-A/K
Other Ordering Examples:
For an output code of “0”: MS5507-A-0 (Output: 2 to 5V)
For an option code of “X”: MS5507-A-A/X (Responsefrequency: 50Hz)
Note: If you wish to include multiple options in your order,
specify the option codes in series (e.g. /KX).

Limit Current for
Short-CircuitProtection
Permissible
Short-Circuit
Duration

4 to 20mA DC from 2-wiretransmitters
250Ω
Output voltage:
26.4V, typical. (0% input)
21.6V, typical. (100% input)
Maximum current: 22mA, typical.
40mA max.
Continuous.

●OUTPUT SECTION
Allowable Output Load
Voltage Output (DC) 1V span and up
2mA max.
10mV
10kΩ min.
100mV
100kΩ min.
Current Output (DC) 4 to 20mA
750Ω max.
Zero Adjustment
Approx. ±5% of span.
(Adjustable by the front-accessibletrimmer.)
Span Adjustment
Approx. ±5% of span.
(Adjustable by the front-accessibletrimmer.)Rev. 1.50

Page: 1/3

Product Specification Sheet

Model: MS5507

Plug-In Distributor with Isolated Single Output

Ranges Available
Current Signal
Voltage Signal
Output Range (DC)
0 to 20mA
0 to 10V
4 to 20mA
10mV to 10V
Output Span (DC)
Output Bias
0 to 100%
0 to 100%* For current output signals, the accuracy of any current
output smaller than 0.1mA is not guaranteed.
Output Spec. Ex. 1: For 4 to 20mA output, the output span is
16mA and the bias +25%.
Output Spec. Ex. 2: For 4 to 8V output, the output span is
4V and the bias +100%.

●PERFORMANCE
Accuracy Rating
Temperature
EffectResponse Time
CMRR
Isolation
Insulation
ResistanceDielectric Strength
Surge Withstand
Capability
Operating
Environment
Storage
Temperature

Better than ±0.1% of span (at25°C±5°C).
Better than ±0.2% of span per 10°C
change in ambient.
85ms max. (0 to 90%) with a step
input at 100%.
100dB min. (500V AC, 50/60Hz)
3-way isolation between input,output, and power.
100MΩ min. (@ 500V DC) between
input, output, and power.
Input / Output / Power: 2000V AC
for 1 minute (Cutoff current: 0.5mA)
Tested as per ANSI/IEEE
C37.90.1-1989.
Ambient temperature: -5 to 55°C
Humidity: 5 to 90% RH(non-condensing)-10 to 60°C

●MATERIAL
HousingSocket
Screw Terminal

ABS resin (UL 94V-0)
ABS resin (UL 94V-0)
Galvanized steel with trivalentchromate finish
Glass fabric, epoxy resin(FR-4: UL 94V-0)

Printed Circuit
Board

TERMINAL ASSIGNMENTS+ OUTPUT− OUTPUT− INPUTCOM
N.C.
+ INPUT
P (+)
N (−)

POWER

●PHYSICAL
Installation
Mounting Direction
Screwing TorqueWiring
ExternalDimensions
WeightWall/DIN rail mounting
Vertical
0.78 to 1.18 [Nm] * Recommended
M3.5 screw terminal connection
W51 × H85 × D136.5 mm(including the socket)
Main unit: 200g max.
Socket: 60g max.

Rev.1.50

Page: 2/3

Product Specification Sheet

Model: MS5507

Plug-In Distributor with Isolated Single Output

BLOCK DIAGRAM+INPUT−TRANSMITTERPOWER
SUPPLY

ZS

Amp.

250Ω

COM

POWER
SUPPLYP (+)

ISOLATIONISOLATION

CIRCUITCIRCUITOUTPUT
CIRCUITOUTPUT +OUTPUT −POWER
CIRCUITN (−)

When used as an isolator:

When used as a distributor:

2-WIRE
TRANSMITTER⊕ 4~20mA⊖

TRANSMITTERPOWER
SUPPLY

TRANSMITTERPOWER
SUPPLY250Ω

INPUT
SIGNAL⊕4~20mA⊖250Ω

Rev.1.50

Page: 3/3