SITEMANAGER 3439			
AINITIAL SETUP
DDIN Rail MountingPush the SiteManager from down andupwards to apply tension on thespring-lock, and in the same movement
push the SiteManager in, and over thetop of the DIN rail.

Release and ensure that theSiteManager it is firmly mounted

Applying UPLINK settings for accessing the Internet

The SiteManager requires being able to access the Internet via an Uplink port in order totarget a GateManager server. By default it will receive its IP address by DHCP, and you only
need to manually configure the Uplink if you will use a fixed IP on UPLINK1, or if you want to use
UPLINK2 as wireless Internet access.
Select one of the following 4 methods:

Using the Secomea Appliance Launcher.

1.

a.
b.

c.
d.

e.

Note: In order for this product to conform with the safety certifications, this product must be
installed in a Restricted Access Location.
B

Using the default IP address (10.0.0.1)

2.

POWER

a.
SiteManager must be fed 12 - 48V DC. Power consumption is max. 6W
Power should be applied to the GND and +V terminals only!

b.
c.
d.
e.
f.

Connect the DEV1 port of the SiteManager to the Ethernet port of your PC using astandard Ethernet cable.
Configure your PC’s Ethernet adapter to 10.0.0.2 subnet mask 255.255.255.0.
Power on the SiteManager and wait approx. 1 minute for it to become ready.
Type the following in your web browser: https://10.0.0.1
Login with user admin and the SiteManagers serial no. as password.
Enter menu System --> UPLINK1 to set the UPLINK1 address if you want to use afixed IP address, or enter menu UPLINK2 to set the SSID/WiFi Key for an optional
USB WiFi module, or PIN Code for the integrated broadband modem.

g.

Continue with section E to configure GateManager settings.

Using a DHCP server

3.

a.
b.

Note: Under-powering the SiteManager may result in external USB devices to fail.
It is recommended to connect the earth ground in order to reduce interference of noise.
Cc.
d.

Ethernet portse.
f.

Use a standard Ethernet patch cable (straight or cross over) to connect the UPLINK1 port to aswitch in a network that has access to the Internet.
The DEV port can be connected to an existing network separate from the UPLINK1 network, or
you can create a separate device network isolated from the UPLINK1 network. But you can also
just connect the UPLINK1 port, and only access equipment on the Uplink side.

g.

192.168.2.2/24

a.

Login to the GateManager Portal and locate the domain in which the SiteManager
should connect.

b.

Click the “USB Configuration” symbol , and set the UPLINK1 or UPLINK2 portsettings. If the SiteManager is connected to a local Intranet with a DHCP server,
you do not have to configure anything.
Click create to save the configuration file locally to your PC.
Copy the configuration file to a fat32 formatted USB memory stick.
Power ON the SiteManager and wait until the SiteManager is ready (Status hasstopped blinking)Insert the memory stick, and wait until the SiteManager has automatically rebooted. If the SiteManager has GateManager access, STATUS should turn green.
Remove the memory stick. No further configuraiton is needed.

c.
d.
e.

IP 10.0.0.2

f.

192.168.2.2/24

DO NOT CONNECT THE
DEV AND UPLINK1PORTS TO THE SAMEPHYSICAL NETWORKDO NOT ASSIGN DEVADDRESSES IN THE
SAME LOGICALNETWORK AS UPLINK1
192.168.2.5/24

Bernecker + Rainer Industrie-Elektronik Gesellschaft m.b.H.,
FN 111651 v, B&R-Straße 1, 5142 Eggelsberg, ÖsterreichConnect the UPLINK port of the SiteManager to your local network and power it on.
After approx. 1 minute the SiteManager should have received an IP address fromyour DHCP server.
Check the lease list of the DHCP server to see what the IP address is.
Type the IP address in your web browser preceded with  https:// (e.g.
https://192.168.41.13).
Login with user admin and the SiteManagers serial no. as password.
Enter menu System --> Uplink1 to set the UPLINK1 address if you want to set afixed IP address, or enter menu UPLINK2 to set the SSID/WiFi Key for an optional
USB WiFi module, or PIN Code for the integrated broadband modem.
Continue with section E to configure GateManager settings.

Using a USB memory stick

4.

SiteManager 14xx and 34xx models:
192.168.2.100/24

Download and install the Appliance Launcher tool from here:
www.br-automation.com/appliance-launcher
Connect the DEV1 or UPLINK1 port of the SiteManager to the local network andpower it on. The SiteManager must be on the same Subnet as your PC. Alternatively connect the SiteManager with an Ethernet cable directly to your PC.
Power on the SiteManager and wait approx. 1 minute for it to become ready.
Start the Appliance Launcher and the SiteManager should be listed in the firstscreen. If it does not appear immediately, try pressing the Search button a coupleof times. (Note that the Appliance Launcher will only show the SiteManager if yourPC has a genuine private IP address (10.x.x.x, 172.16-31.x.x, 192.168.x.x or 169.254.x.x))
Follow the Wizard and set the UPLINK1  address if you want to use a fixed IP address, or continue the wizard to menu UPLINK2 to set the SSID/WiFi Key for an
optional USB WiFi module, or PIN Code for the integrated broadband modem.

g.
E

Applying settings for connecting to a GateManager server1.

In the SiteManager Web GUI enter the menu GateManager --> General (if using the Appliance Launcher, follow the wizard to the GateManager Parameters page).

2.

Enter the IP address of the GateManager server that the SiteManager should connectto, and a Domain Token for the domain where the SiteManager should appear. You shouldhave received this information from your administrator or from where you received theSiteManager.

3.

When the settings are entered, you should reboot the SiteManager. Observe that theStatus LED goes steady Green, which indicates that the SiteManager is connected to theGateManager.

4.

Once attached to the GateManager, you can use the GateManager Console or a LinkManager Client to get remote access to the SiteManager Web GUI to perform additional
configuration (DEV ports, Agents etc.)

5.

Detailed guides, new firmware etc. can be downloaded from: http://support.secomea.com

DOC: SM3439_BR_Initial contact_v02

FLED signalingJRefer to the following table. The Power LED is Green when power is supplied.

Internet access via broadband modem (UPLINK2)

The broadband modem connection is referred to as UPLINK2. The SiteManager will as default
always attempt to use the Ethernet connection (UPLINK1), and only use UPLINK2 if the Internet
connection is lost on UPLINK1. Once a connection is established on UPLINK2, switching to UPLINK1 will only be attempted at next reboot, or if the Internet connection on UPLINK2 is lost.

StateSTATUSCONNECTBooting

Steady RedBlink-GateManager Connectingor Disconnected

2 Red Blink-- Remote Management is disabled via
INPUT1 or SiteManager GUI-SiteManager in SMS Wakeup mode-long pause +2 Green Blink

GateManager Connected

On Green-- UPLINK is physically disconnected, or- GateManager configuration is missingin the SiteManager, or- No route to GateManager host due toits address being configured as DNS
name, and a DNS server is not configured or is not reachable/working.

On Red-LinkManager Connected-StateUPLINK2No SIM card detected

OffWhen enabling the WiFi client, the SiteManager will be by default attempt to connect with theSSID “sitemanager” and the MAC address of the SiteManager as WiFi Key.

Wrong or missing SIM Pin code

3 Green Blink

The SSID and WiFi Key can be configured in the System > UPLINK2 menu.

SIM PIN code OK, but no connection.
(Trouble shoot in SiteManager GUI)

2 Green BlinkGPRS connected (slow connection)

On Green +1 Green Blink

3G connected (fast connection)

On Green

SiteManager is in SMS Wakeup modelong pause +2 Green Blink

I the modem is using a SIM PIN code you should enter the PIN code in the System > UPLINK2
menu of the SiteManager. The SiteManager will automatically detect the APN (Access PointName) from an internal table, but can also be manually entered via the SiteManager GUI.
If your modem or SIM card does not have a PIN Code, you do not have to make any further
configuration of UPLINK2 in the SiteManager (The PIN Code can be removed from a SIM card byinserting it into a standard mobile phone, and use the remove SIM card function of the phone).
In order to reduce data traffic, you can configure UPLINK2 to let the broadband connection
enter sleep-mode if idle. The connection will be reestablished when sending an SMS to thephone number on the SIM card.
Note that when using a USB WiFi adapter as explained in the following, broadband uplink isdisabled.
KOn Green

Optional  Internet access via a USB WiFi adapter (UPLINK2)The SiteManager can connect to a WiFi access point using a Secomea USB WiFi adapter (p/n27101 or 27250).

Note that when using a USB broadband modem as explained in the foregoing, a USB WiFiadapter cannot be used concurrently.
LSIM card insertion

Slide the SIM card into the slot.

Note that it may take some time for the Status LED to reflect a new state. For instance a GM
Disconnect may take up to 4 minutes to be reflected, depending on the Keep-alive Interval
setting on the GateManager.
GUSB ports (USB cable not included)

The USB port can be used for attaching selected USB equipped PLCs and for connecting a
optional WiFi adapter to use as Internet connection (UPLINK2). See details in the next sections.
HIO Ports

Digtial Input port 1 and 2
In “OFF” (inactive) state at 2.34 V or above, and in the “ON” (active) state at  0.16 V or below. Thebehavior for input voltages between 0.16 V and 2.34 V is undefined.
There is an internal 10 kohms pull-up resistor to 3.3 V, so an unconnected input port is in the“OFF” state. Input port 1 is by default assigned to toggle GateManager Access. By connecting asimple on/off switch you can control when remote service should be allowed.
Digital Output 1 and 2
Output ports are “single pin” ports, which is pulled towards GND when ON, and is highimpedance when OFF. The port is an “open drain” kind, which means that (just like a switch) novoltage is output by the port itself, but must be supplied either from an external source (max24 V) or from the Vout (5V) pin. In the “OFF” (inactive) state, the impedance is min 24 Mohms; inthe “ON” (active) state, the impedance is max 0.5 ohms.
Maximum sink current is 0.2 A.
Refer to the guide “Working with IO ports” for application scenarios.
I

Serial ports (Serial cables not included)

Use a sharp object, such as a screwdriver,  to push
the SIM card further into the slot (approx 2 mm), until
you hear the click of the spring lock.

The SIM card is properly inserted when it is level with
the SiteManager cabinet.

SiteManager is equipped with a RS232 Serial port with full flow control support. The pinout of
the DB9 connector corresponds to the standard Serial COM port of a PC. You should be able touse an ordinary NUL-modem cable for most equipment.
- For Omron PLCs use the cable XM2S-09.
- For Siemens MPI- or PPI connection use either a RS232-to-MPI adapter,  a USB-to-MPI adapter or an Ethernet-to-MPI/PPI adapter (Secomea p/n 26940)- For other devices refer to their documentation about special Serial pinout.

M

Regulation Notices

This product has been tested for compliance with:   • CE (EN 61000-6-2, EN 61000-6-4, EN 61000-3-2/-3-12, EN 61000-3-3/-3-11) • FCC 47 cfr part 15 * • IC-Tick N29451 • RCM Compliant • IEC CB certified (DK-30193-UL) • UL Listed (file #E358541, ITE 4ZP8)* NOTE: This equipment has been tested and found to comply with the limits for a Class A digital device, pursuant to Part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference when the equipment is operated in acommercial environment. This equipment generates, uses, and can radiate radio frequency energy, and if it is not installed and used in accordance with the instruction manual, it may cause harmful interference to radio communications. Operation of this equipment in a
residential area is likely to cause harmful interference, in which case the user will be required to correct the interference at his own expense.. Operation is subject to the following conditions:
1.
This device may not cause harmful interference.
2.
his device must accept any interference received, including interference that may cause undesired operation.
Specific to the integrated broadband module:
1.
The module is PTCRB and FCC approved. To fully comply to FCC/IC the following conditions must be met: a) At least 20 cm separation distance between the antenna and the user’s body must be maintained at all times. b) The maximum gain of a connected
antenna including cable loss in a mobile-only exposure condition must not exceed 3.5 dBi in the cellular band.
2.
The module is in conformity with the essential requirements and other relevant requirements of the R&TTE Directive (1999/5/EC).
3.
The module is in conformity with the following standards and/or normative documents: Safety: EN 60950-1:2006+A11:2009, EMC: EN 301 489-1/-7/-24, Radio: EN 301 511, EN 301 908-1/-2
第十二條 經型式認證合格之低功率射頻電機，非經許可，公司、商號或使用者均不得擅自變更頻率、加大功率或變更原設計之特性及功能。 第十四條 低功率射頻電機之使用不得影響飛航安全及干擾合法通信；經發現有干擾現象時，應立即停用，並改善至無干
擾時方得繼續使用。 前項合法通信，指依電信法規定作業之無線電通信。 低功率射頻電機須忍受合法通信或工業、科學及醫療用電波輻射性電機設備之干擾。