Product Specification Sheet
Model: MS5510
Plug-In Potentiometer Transmitter with Isolated Single Output

DESCRIPTION

MS550051The MS5510 is a plug-in potentiometer transmitter thatdetects changes in the resistance of potentiometric sensors,converts them into commonly used DC signals and provides
an isolated single output.

SZ

85

ORDERING CODE

MS5510 --_Model
136.5

Power Supply
A: 100 to 240V AC (50 to 60Hz)
D: 24V DC
P: 100 to 240V DC
Input
Range between 0-100Ω and 0-10kΩ

OutputA: 4 to 20mA DC
D: 0 to 20mA DC
Z: Other DC current signals

1: 0 to 10mV DC
2: 0 to 100mV DC
3: 0 to 1V DC
4: 0 to 10V DC
5: 0 to 5V DC
6: 1 to 5V DC
3W: ±1V DC
4W: ±10V DC
5W: ±5V DC
0: Other DC voltage signals

Options
No code: None
/K: Fast response (0 to 90% response time: 10ms max.)/H: Polyurethane conformal coating/X: Others (Special order)* For non-standard options, ask MTT for availability.

ORDERING INFORMATION
To place an order, please use the ordering code format
as shown above.
(e.g.) MS5510-A-4/K* Factory adjustment of resistance range: Specify aresistance range if required (e.g. 0 to 1kΩ); otherwise,
products will be supplied with a factory-adjusted resistance
range of 0 to 10kΩ.
Other Ordering Examples:
For an output code of “0”: MS5510-A-0 (Output: 2 to 5V)
For a specific resistance range: MS5510-A-A (0 to 500Ω)(When you specify a resistance range, our factory performs
the test accordingly, the fact of which will be indicated in thelabel attached.)
For an option code of “X”: MS5510-A-A/X (Responsefrequency: 50Hz)
Note: If you wish to include multiple options in your order,
specify the option codes in series (e.g. /KX).

(mm)

SPECIFICATIONS●POWER SECTION
PowerRequirements

100 to 240V AC: 85 to 264V AC (47to 63Hz)
24V DC: 24V DC±10%
100 to 240V DC: 85 to 264V DC
Power Sensitivity
Better than ±0.1% of span for eachpower supply range.
Power Line Fuse
160mA fuse
Maximum Power Consumption
Power100-240V AC 24V DC 100-240V DC
Approx.
Approx.
Approx.
4.5VA
1.1W
4.8W

●INPUT SECTION
Input Signal
Measuring
VoltageAllowable LeadWire ResistanceRange between 0-100Ω and 0-10kΩ.
Approx. 0.5V
10% or less of total resistance perwire. (The resistance of all threewires must be equal.)●OUTPUT SECTION
Allowable Output LoadVoltage Output (DC) 1V span and up
2mA max.
10mV
10kΩ min.
100mV
100kΩ min.
Current Output (DC) 4 to 20mA
750Ω max.
Zero Adjustment
Approx. 0 to 50% of total resistance.
(Adjustable by the front-accessibletrimmer.)
Span Adjustment
Approx. 50 to 100% of totalresistance.
(Adjustable by the front-accessible
trimmer.)
Ranges Available
Current Signal
Voltage Signal
Output Range (DC)
0 to 20mA-10 to 10V
Output Span (DC)
4 to 20mA
10mV to 20V
Output Bias
0 to 100%-100 to 100%
* For current output signals, the accuracy of any current
output smaller than 0.1mA is not guaranteed.
Output Spec. Ex. 1: For 4 to 20mA output, the output span is
16mA and the bias +25%.
Output Spec. Ex. 2: For -1 to 4V output, the output span is
5V and the bias -20%.

Rev. 1.40

Page: 1/2

Product Specification Sheet

Model: MS5510

Plug-In Potentiometer Transmitter with Isolated Single Output●PERFORMANCE●MATERIAL

Accuracy Rating

HousingSocket
Screw Terminal

Temperature
EffectResponse Time
CMRR
Isolation
Insulation
ResistanceDielectric Strength
Surge Withstand
Capability
Operating
Environment
Storage
Temperature

Better than ±0.2% of span (at25°C±5°C).
Better than ±0.2% of span per 10°C
change in ambient.
170ms max. (0 to 90%) with a step
input at 100%.
100dB min. (500V AC, 50/60Hz)
3-way isolation between input,output, and power.
100MΩ min. (@ 500V DC) between
input, output, and power.
Input / Output / Power: 2000V AC
for 1 minute (Cutoff current: 0.5mA)
Tested as per ANSI/IEEE
C37.90.1-1989.
Ambient temperature: -5 to 55°C
Humidity: 5 to 90% RH(non-condensing)-10 to 60°C

Printed CircuitBoard

ABS resin (UL 94V-0)
ABS resin (UL 94V-0)
Galvanized steel with trivalentchromate finish
Glass fabric, epoxy resin(FR-4: UL 94V-0)

TERMINAL ASSIGNMENTS+ OUTPUT− OUTPUT
POT A
POT B
POT C
N.C.
P (+)
N (−)

POWER

●PHYSICAL
Installation
Mounting Direction
Screwing TorqueWiring
ExternalDimensions
WeightWall/DIN rail mounting
Vertical
0.78 to 1.18 [Nm] * Recommended
M3.5 screw terminal connection
W51 × H85 × D136.5 mm(including the socket)
Main unit: 200g max.
Socket: 60g max.







BLOCK DIAGRAM

ZA
POTB

S

REF.
VOLTAGE
Amp.

C

POWER
SUPPLY

P (+)
N (−)

ISOLATIONISOLATION

CIRCUITCIRCUITOUTPUT
CIRCUITOUTPUT +OUTPUT −POWER
CIRCUIT

Rev. 1.40

Page: 2/2