Isotop DSD
Steel spring isolators with integrated
high-performance dampers— Natural frequency from 4.2 Hz— Sylodamp® inside – ideal for machines with several start-stopcycles— Cathodic dip-coating (CDC) for increased corrosion protection— Secure connection between the plate and the spring thanks to
special adhesive— M 10 internal thread— Suitable base plate and/or height adjustment available— Base plate with damping element (FP/K) also isolates higher
frequencies— Simple load control thanks to open design— Spring design conforms to DIN EN 13906–1

Maximum loadin kgin N

DSD springelement KTL

Base plate FP/Kwith damping element for SD/DSD

Base plate FP forSD/DSD

Isotop DSD 1 KTL
Isotop DSD 2 KTL
Isotop DSD 3 KTL
Isotop DSD 4 KTL
Isotop DSD 5 KTL
Isotop DSD 6 KTL
Isotop DSD 7 KTL
Isotop DSD 8 KTL
Isotop DSD 9 KTL

24395787
140200
365
470
650

235
383559
853
1,373
1,962
3,581
4,611
6,377

Natural frequency
at maximum load

Packaging
unit

Order
number

5.6 Hz4.9 Hz4.8 Hz4.2 Hz4.8 Hz4.3 Hz5.2 Hz4.7 Hz4.6 Hz50 pcs.
50 pcs.
50 pcs.
50 pcs.
50 pcs.
50 pcs.
50 pcs.
50 pcs.
50 pcs.

39492
39493
39495
39496
39497
39157
39498
39499
39500

Isotop FP/K 1 — 9 KTL

for DSD 1 to 9

including screws1

50 pcs.

39158

Isotop FP 1 — 9 KTL

for DSD 1 to 9

without screws

50 pcs.

39537

50 pcs.

47321

Isotop NV 1 — 9M 10for DSD 1 to 9

Heightadjustment
for SD/DSD
M 10 connecting screws between base plate and spring

Isotop SD (unloaded)

Isotop FP/K

Isotop NV 1 - 9150120

120

20*9594957050

ø 70

Isotop FP150

ø 11

ø 28M 1012

ø 1121M 10171*Thread reach SD/DSD

200

8150

7100

6550

54080

6401517192123 25
Deflection in mm

700

8600

76500

17191517

19

1,500

101,300

91,1008900

75330042123 25
Deflection in mm

91113

93,00082,600762,200

Natural frequency in Hz
Force in N

103,400

15

17

19

5,000
4,600

10
94,20083,80073,40063,00052,60042,20031,800241,000

31,4001600

21,0000
9 10 11 12 13 14 15 16 17 18 19 20 21 22 23
Deflection in mm

1517192123 25
Deflection in mm

1005411131517192123 25
Deflection in mm

2,000101,80091,60081,40071,20061,0005800

46003240011131517192123 25
Deflection in mm

Isotop DSD 91,400

13695112002123 25
Deflection in mm

1,800

970

Isotop DSD 8

3,800300

Isotop DSD 6500

200894300

400

2123 25
Deflection in mm

65

Isotop DSD 7
Force in N

157004001313

Natural frequency in Hz
Force in N

9Force in N

10

Natural frequency in HzForce in N

9008001111

Isotop DSD 5

Isotop DSD 49496,400

86,0005,600

7Natural frequency in Hz
Force in N

139

Natural frequency in Hz

7500

5,200
64,8004,400

54,0003,600

43,2002,800

32,4002,000

Force in N
Natural frequency in Hz

AUSTRIA — Bürs GERMANY — Berlin — Munich — Stuttgart FRANCE — Paris — Lyon JAPAN — Tokyo
INDIA — Pune CHINA — Beijing USA — Charlotte AUSTRALIA — Melbourne
www.getzner.com

29 10 11 12 13 14 15 16 17 18 19 20 21 2223
Deflection in mm

Natural frequency in Hz12010DB Isotop en © Copyright by Getzner Werkstoffe GmbH l 09-2022 | All information and data is based on our current knowledge. It can be used in calculations and for reference purposes, but is subject to product-specific and application-specific manufacturing tolerances and does not represent warranted properties. Material properties and their tolerances vary depending on the type of application and load and are available fromGetzner on request. Subject to change without notice. For further general information, see VDI directive 2062 and glossary. Further characteristic values available on request.

98600

Natural frequency in Hz

250

160

Force in N

10

Natural frequency in Hz300

9Force in N

11200

11

Isotop DSD 3
12109

Isotop DSD 2350

11240

0

Roof-mounted recooler

400

280

Natural frequency in Hz

Force in N

Isotop DSD 1

Small combined heat and power plant