Ethernet I/O: BusWorks XT Series®

XT1230 Ethernet Analog Input Modules
22.5(0.89)

99.0(3.90)

EXAMPLE INPUT CONNECTIONSSOURCED DC CURRENT+DC CURRENTMILLIAMPS -IN0+

XT123x SIMPLIFIED I/O CHANNELISOLATEDNETWORK PORTS

CH0

RTN

IN0+

CH15

IN15+
TWO-WIRE CONNECTION+

IN0+

16-BIT
A/DµC &COMMS

114.5(4.51)

RTN
RTN+RTNUSB
Configured

ISOLATED
POWER

RTN

DIMENSIONS ARE IN MILLIMETERS (INCHES)

16-channel single-ended analog current input ◆ Modbus TCP/IP, Ethernet/IP, Profinet, or i2o communication

Description
The XT1230 offers an isolated Ethernet network
interface for up to to sixteen single-ended
current input channels. Single-ended inputs
enable a higher channel density to save space
and a lower cost per channel.
Rugged construction, high density design, andeasy USB-to-PC/Windows setup combine for avery effective and reliable module. These units
are ideal for remote monitoring, distributedcontrol, or SCADA applications.

Input Ranges
DC Current:
0 to 11mA, 0 to 20mA, 4 to 20mA, ±20mA.
0 to 20 amps AC (with optional AC sensor)
Ethernet Communication
Modbus TCP/IP, Ethernet/IP, Profinet,i2o® peer-to-peer, 10/100Base-T(X)PriorityChannel™ device determinism
Power Requirement
12 to 32V DC (2.8W)

Key Features & Benefits
■
■

■

■
■

■

■

■

■

Easy setup with Windows software via USB
Low input impedance (27 ohms) reducesloading on current loops
User-configurable sample averaging (1-200) on
a per-channel basis
10ms network updates for all 16 input channels
i2o peer-to-peer updates based on percent-ofchange and/or timed updates
High-resolution 16-bit Σ-Δ A/D converter
ensures precise, high accuracy measurements
High-Density 22.5mm wide package withpluggable, front-facing terminals
Dual Ethernet 10/100 ports (auto-negotiation)
reduce switch port requirements
1500V AC isolation (between I/O, power, andnetwork ports) and surge/transient protection■

Supports bussed/rail and redundant power■-40°C to +70°C wide temperature operation■

Withstands 25g shock and 4g vibration■

CE compliant. UL/cUL Class 1 Div 2 Zone 2
approvals. ATEX Certified.

BusWorks XT software (download free from www.acromag.com) allows you to configure I/O modules offline withUSB or save the configuration file and download settings into units later at your convenience.

Tel 248-295-0880 ■ sales@acromag.com ■ www.acromag.com ■ 30765 Wixom Rd, Wixom, MI 48393 USA
Bulletin #8400-797g

Ethernet I/O: BusWorks XT Series®

XT1230 Ethernet Analog Input Modules
Performance Specifications
IMPORTANT: To prevent damage or errors fromgrounded PCs and surges, Acromag strongly
recommends use of the USB-ISOLATOR when
configuring an XT1000 I/O module.
■ USB Interface
USB Connector
Type: USB Mini-B type socket, 5-pin
Data rate: 12Mbps. USB v1.1 and 2.0 compatible
Maximum cable length: 5.0 meters
USB Transient Protection
Transient voltage suppression on power and data lines
Driver
Not required. Uses Windows HID drivers■ Input
Accuracy±0.05% of span, typical for nominal input ranges
Analog to Digital Converter (A/D)
16-bit Σ-Δ converter. 1.476uA/bit resolution
Noise Rejection
Better than -110dB @ 60Hz
Input Filter Bandwidth-3dB at 25KHz, typicalInput Conversion Rate
10ms for all 16 input channels
Input Impedance
27.4 ohms■ Ethernet Communication
ProtocolsModbus TCP/IP, i2o peer-to-peer, Ethernet/IP, orProfinet depending on model number.
Ethernet Communication Controller
Innovasic RapID™ Platform with PriorityChannel™ fordeterminism at the device regardless of network load.
Modbus TCP/IP (slave)
Port 502 reserved. Supports up to 10 sockets
i2o Peer-to-Peer (master/slave)
Can map each of 16 analog input channels separately
to output channels. Timed (1-65535 sec) or percentof-change updates. Supports GPRS/GSM systems.
Ethernet/IP (adapter)
Supports 10 connections. EDS file on website
Profinet (server)Supports 1 connection. GSDML file on website
Connectors
Two shielded 8-pin RJ-45 sockets, 10BaseT/100BaseTX

WiringAuto-crossover for MDI or MDI-X
IP Address
User-configurable. 192.168.1.100 default IP address
Data Rate
Auto-negotiated, 10Mbps or 100Mbps
ComplianceIEEE 802.3, 802.3u, 802.3x■ Environmental
Operating temperature-40 to 70°C (-40 to 158°F)
Storage temperature-40 to 85°C (-40 to 185°F)
Relative humidity
5 to 95% non-condensing.
MTBF: 463,547 hrs. at 25°C
345,200 hrs. at 40°C
Power Requirement
12 to 32V DC, 2.8W maximum(113mA maximum @ 24V)
Isolation
4-way isolation between I/O channels, network(each port), and power
Peak: 1500V AC, ANSI/ISA-82.01-1988
Continuous: 250V AC, 354V DC
Shock and Vibration Immunity
Vibration: 4g, per IEC 60068-2-64
Shock: 25g, per IEC 60068-2-27
Electromagnetic Compatibility (EMC) Compliance
Radiated Emissions: BS EN 61000-6-4, CISPR 16
RFI: BS EN 61000-6-2, IEC 61000-4-3
Conducted RFI: BS EN 61000-6-2, IEC 61000-4-6
ESD: BS EN 61000-6-2, IEC 61000-4-2
EFT: BS EN 61000-6-2, IEC 61000-4-4Surge Immunity: BS EN 61000-6-2, IEC 61000-4-5
Approvals
CE compliant. UL/cUL listed. ATEX Certified.
Designed for Class I; Division 2; Groups ABCD; Zone 2.
II 3 G Ex nA IIC T4 Gc -40°C < Ta < +80°C■ PhysicalGeneral
General purpose plastic enclosure for mounting on
35mm “T-type” DIN rail
Case Material
Self-extinguishing polyamide, UL94 V-0 rated, color
light gray. General purpose NEMA Type 1 enclosure.
Circuit Board
Military grade fire-retardant epoxy glass (IPC-4101/98)

I/O Connectors
Removable plug-in type terminal blocks rated for
12A/250V; AWG #26-12, stranded/solid copper wire
Dimensions
Width = 22.5mm (0.9 inches), Length = 114.5mm(4.51 inches), Depth = 99.0mm (3.90 inches)
Shipping Weight
0.5 pounds (0.22 Kg) packed

Ordering Information◆ Models
XT1231-000
16-channel single-ended current input module,
Modbus/TCP and i2o protocol
XT1232-000
16-channel single-ended current input module,
Ethernet/IP protocol
XT1233-000
16-channel single-ended current input module,
Profinet protocol◆ Software
XT-SIP (recommend one kit per customer)Software Interface Package. Includes software(XT-CONFIG), isolator (USB-ISOLATOR), two USB cables(4001-112, 4001-113), Ethernet cable (5035-360).

◆ Accessories
XT BUS-KIT
DIN rail bus power/excitation connector kit. Includes
one DIN rail bus connector (1005-070), one left-side
female connector terminal block (1005-220) and one
right side male connector terminal block (1005-221).
USB-ISOLATOR
USB-to-USB isolator, includes USB cable (4001-112)
5020-350
AC current sensor (toroidal transformer)
Converts 0-20A AC to 0-11.17mA DC
PS5R-VD24
Power supply (24V DC, 2.5A)
DIN RAIL 3.0
DIN RAIL 16.7
DIN rail strip, Type T, 3 inches (75mm) or16.7 (425mm)
20RM-16-DIN
19” rack-mount kit with DIN rail

Tel 248-295-0880 ■ sales@acromag.com ■ www.acromag.com ■ 30765 Wixom Rd, Wixom, MI 48393 USAAll trademarks are property of their respective owners. Copyright © Acromag, Inc. 2019. Data subject to change without notice. Printed in USA 10/2019.