JCM_LA_F_PDD_ver02.0Criterion 2Criterion 3

Criterion 4

Criterion 5

The container is highly air-tightwith IEC60529 value of IP-54 orhigher based on manufacturer’sinspection results.
The project DC installs ITequipment that has operatingtemperaturerecommendedbymanufacturer with upper limit of 40degrees C or higher.
Ozone Depletion Potential (ODP)of the refrigerant used for theproject DC is zero.
A plan for not releasing refrigerantused for project DC is prepared.

The container is highly air-tight withIEC60529 value of IP-54 based onmanufacturer’s inspection results.
The project DC installs IT equipment thatis capable of stable operation at 40degrees C.

The refrigerant used for the project DC isR410a, whose ODP is zero.
A plan for not releasing refrigerant usedfor project DC is prepared. Refrigerantleakage from the project DC will beprevented by conducting periodical checkin linewith "Guideofsimplified

fluorocarbons leak check" correspondingto "Act on rational use and propermanagement of fluorocarbons" to preventrelease of refrigerant used for project DC.

C. Calculation of emission reductionsC.1. All emission sources and their associated greenhouse gases relevant to the JCM projectReference emissionsEmission sources

GHG type

Electricity consumption by reference DCCO2

Project emissionsEmission sources

GHG type

Electricity consumption by project DC

CO2

C.2. Figure of all emission sources and monitoring points relevant to the JCM project3

JCM_LA_F_PDD_ver02.0Electricity from the grid

Datacenter

Monitoring Point (1)Electricity meter for the DC(monitoring point for ECPJ,p)Power receiving facility

UPSUPS

1 2 3 4 5ITIT

6 7 8ITIT

910 11 12 13ITITUPSUPS

14 15 16ITIT

17 18 19 20 21 22 23 24

IT

IT

IT

Unit1

IT

25 26 27 28 29 30

IT

IT

ITUPSUPS

31 32

33 34

IT

IT

35 36

37 38

39 40

41 42

43 44

45 46

47 48

ITIT

IT

IT

IT

IT

IT

otherfacility

Unit3

Unit2i ：Electricity meter i (monitoring point for ECIT, i,p ） for Monitoring point (2)C.3. Estimated emissions reductions in each yearYear

Estimated

Reference Estimatedemissions (tCO2e)

Project EstimatedEmissions (tCO2e)

Emission

Reductions (tCO2e)

2013

---

2014

---

2015

---

2016

---

2017

833

533

300

2018

1,609

1,030

579

2019

1,931

1,236

6952020

1,931

1,236

695

Total

6,304

4,035

2,269(tCO2e)

D. Environmental impact assessmentLegal requirement of environmental impact assessment for Nothe proposed project4

JCM_LA_F_PDD_ver02.0E. Local stakeholder consultationE.1. Solicitation of comments from local stakeholdersTo solicit comments from local stakeholders, a consultation meeting was planned by the projectparticipant, and the project participant invited various stakeholders.

Details of the local

stakeholders consultation meeting is summarized as follows:Date and Time: 18th August 2016, 10:50 – 12:05Venue: Subnakhone Hotel (SNK Hotel)Address: ASEAN road, Sibounheuang Village Chanthabuli District, Vientiane Capital, Lao PDRThe following organization from Lao side participated to the consultation meeting:·Department of Disaster Management and Climate Change (DDMCC), Ministry of NaturalResource and Environment (MONRE)·International Relation Division, Lao Women Union·REDD Office, Department of Forestry, Ministry of Agriculture and Forestry (MAF)·Department of Industry and Handicraft, Ministry of Industry and Commerce (MOIC)·Institute of Public Work and Transport, Ministry of Public Works and Transport (MPWT)·Ministry of Health·Ministry of Education and Sport·Renewable Energy Institute, Ministry of Science and Technology (MOST)·Renewable Energy Promotion Institute, Ministry of Energy and Mines (MEM)·Department of Information and Technology, Ministry of Science and Technology (MOST)·E-Government Center, Ministry of Post and Telecommunication·Electricite Du Laos (EDL)·ESL Sole, Co. Ltd.
At the meeting, a brief introduction about JCM procedures was provided first. The details ofthe proposed JCM project and the technology introduced by the project were explained byrepresentative of Internet Initiative Japan (IIJ) who is in charge of the technical design of theproject, followed by a Q and A session. Total of twenty one attendees to the meeting from Laoside actively expressed their comments to the proposed JCM project at the consultationmeeting.

In general, the proposed project was received positively by the attendees to theconsultation meeting. Many stakeholders showed their interest to the JCM scheme. At themeeting, no negative comments toward the proposed project were expressed by the attendees.
The received comments from the local stakeholders, along with the responses/action to thecomments, are listed in the following section.
5

JCM_LA_F_PDD_ver02.0E.2. Summary of comments received and their considerationStakeholdersDirector

Comments received

Consideration of comments receivedof As similar to the CDM, it is my The

maximum

durationoftheDivision

understanding that the length of the crediting period for a JCM project isDDMCC,crediting period affects the amount of determined by the project lifetime.

MONRE

emission reduction generated from The project lifetime for a JCMthe project.

How long is the project is often defined as thecrediting period for the proposed technicalproject?

lifetimeoftheequipment/system installed by theproject.

However, as a JCM

demonstration project, the creditingperiod for the LEED project needs tobe decided among relevant entities,including

NEDO

andproject

participants prior to the projectregistration.
No further action is necessary.
Technical

Does the capacity of data center Based on the result of the feasibility

officer

implemented by the proposed project study, the capacity of the data center

DDMCC,

cover the demand of the government installed by the proposed project

MONRE

and the private sector?

covers the demand of the governmentand the private sector for the nearfuture (from 5 to 10 years), providedthat the demand projection of the LaoPDR used in the FS is valid.
No further action is necessary.

TechnicalParticipant of the proposed JCM Firstofficer

project

DDMCC,

government agency. If any private claim emission reductions achieved

MONRE

sector candidate start using the data by the use of the data center

fromLaoPDR

isofall,

onlytheprojecta participants of the LEED project cancenter of the proposed project, can implemented by the LEED project.
theprivate

sectorentityclaim Emission reduction achieved by theemission reduction due to the use of use of the project data center will bethe energy efficient data center? Or, counted as the reduction by thiscan it be considered as a sub-JCM proposed JCM project, regardless of6

JCM_LA_F_PDD_ver02.0project?

the types of the data center users.
To avoid double counting of GHGemission reduction by the project, theJCM prohibits double registration ofthe same project in other climatemitigation mechanism. Therefore, theprivate sector entity is not allowed toclaim emission reduction due to theuse of the energy efficient data centerinstalled by the LEED project.
No further action is necessary.

TechnicalItissuggested

thatproject The project participants understandofficer

proponents conduct a cost-benefit the importance of marketing for theDDMCC,analysis for the private sector who private sector in Lao PDR and willMONRE

may be interested in the container study how to conduct the marketingdatacenter.

which includes the cost benefitanalysis.
No further action is necessary.

Senior Officer

Who will manage the project?

The project will be managed byDDMCC,Japan side until the end of the JCM

MONRE

demonstration project, which ends in2018. After 2018, the project willbe handed to Lao PDR.
No further action is necessary.

F. ReferencesN/AReference lists to support descriptions in the PDD, if any.

AnnexN/A

7

JCM_LA_F_PDD_ver02.0Revision history of PDDVersionDate

Contents revised

01.019/12/2016

First Edition

02.020/02/2017

Second Edition8