Catalog 302
05 / 2019

Push Buttons and Pilot Lights, Ø 22,5 mm

Kraus & Naimer
The development of the Blue Line rotary switch and motor starter
product ranges is based on more than hundred years experience byKraus & Naimer in the design and manufacture of electrical switchgear.
Kraus & Naimer pioneered the introduction of the cam operated rotary switch
and continues to be recognized as the world leader in that product field.

BLUE LINE
Blue Line products are protected by numerous patents through-out theindustrial world. They are built to national and international standards anddesigned to withstand adverse temperatures and climates.

Blue Line products are accepted and universally recognized fortheir quality and workmanship. They are supported by a worldwide
sales and service organization.

The Kraus & Naimer Registered TrademarkWORLDWIDE SYMBOLFOR QUALITY SWITCHGEAR

Contents

Page

Programs and Description

4, 5Complete Standard Units

6, 7

Pre-assembled Front Elements

8, 9

Front Element Components

9, 10

Legend Plates

10, 11

Coupling Plate and Pilot Light Assemblies

11

Series Elements, Contact Blocks and Enclosures

12

Accessories

12-14

Front Plates for Push Buttons

15, 16

Front Plates for Mushroom Push Buttons

17

Color Caps for Pilot Lights

18

Design19

Dimensions

20-23

Technical Data24, 25

Blue Line Switchgear: Summary26

Programs
Push Buttons and Pilot Lights, 22,5 mm Ø
Push buttons and pilot lights by Kraus & Naimer represent an ideal combination of functional security and economical efficiency in amodular design.
Push Buttons• non-illuminated or illuminated• flush, extended or with extended front ring
• momentary or latched (for converting into spring return function)

Cam Switches• ON/OFF switches and double-throw switches• protection IP 65• for further cam switches, refer to Catalog 120

Pilot Lights• Standard units flush or conical• Solid pilot lights (direct wire)

Enclosures• plastic yellow or gray• with 1, 2, 3, 4 or 6 positions

Double-Push Buttons• non-illuminated or illuminatedLegend Options• front plates and color caps
• legend inserts

Emergency Stop Push Buttons• fool-proof• non-illuminated or illuminated• without and with key• optional mounting in enclosure

Accessories• a wide range of accessories are available, e.g. protection shrouds
and protection caps

Reset Push Buttons• incl. reset rod

Selection• complete units• pre-assembled front elements• individual components

Rotary Switches• non-illuminated or illuminated• without and with key• momentary (for converting into spring return function)
Front
Element

LegendPlate

Fixation
Ring

Front Elements• ergonomical design, front rings metallic colored or black• illuminated elements offer excellent brightest and contrast in alllight conditions• pilot lights with perfect light due to special lenses• any inscription, abrasion-resistant by laser• latched push buttons and rotary switches are convertible into spring
return function• mushroom push buttons with large points• high protection and food resistance: push buttons and pilot lights
IP 67/IP 69K, double-push buttons and rotary switches IP 66• for special operating available with protection caps
Legend Plates• for front elements and double-push buttons• with legend inserts• available with lasered or engraved inscription
Fixation Nut• is part of the front element• nut key for fixation nut as accessories
Coupling Plate• for contact blocks and LED pilot light assemblies• for max. 3 elements per contact level• up to 6 contacts on 2 contact levels are possible

4

Coupling
Plate

Contact Blocks
LED Pilot Light
Assemblies

Contact Blocks and LED Pilot Light Assemblies• finger-proof and open terminals (IP 20)• captive mounting screws• low overall depth, for mounting in commercial plaster depth box
Contact Blocks• available as N/C and N/O• high switching capacity, both in AC-15- and DC-13-operation(technical data see page 22)
LED Pilot Light Assemblies• in green, red and white color• long life (100 000 running hours) by especially low power consumption and vibration resistance• with only 2 voltage ranges the worldwide common applications
are covered• for decoupled function control LED series elements are available
Program Completion
For extensive and complicated switching programs we recommend
the use of cam switches size S00 described in Catalog 120. The
design and appearance closely match the described push buttons
and pilot lights.
Order Information
By changing the order text from P SN to P SB the unit will be
specified with black front ring.

< back to table of contents >Environmentally compatible Materials• cadmium and asbestos-free• recyclable

Potentiometer• incl. resistor

Description
Push Buttons and Pilot Lights, 22,5 mm Ø
The modular design of the series push buttons and pilot lights meets your personal requirements in every respect.

Front Elements
Push buttons non-illuminatedPush buttons illuminated
Front element
flush

Front plate
extended

Front element
extended

Front plate
flush

Mushroom push buttons< back to table of contents >Front plate
flush

Front element
flush

Front element
extended

Rotary switches

Front element
pre-assembled

Front plate

Front plate
extendednon-illuminated

Front elements
pre-assembled

illuminated

Front elements
pre-assembled

key operated

Double-push buttons

Front elements
pre-assembled

Emergency stop push buttons

Front element
pre-assembled

Front elements
pre-assembled

Complete Standard Units
Pilot lights

Solid pilot lights

Color caps
extended(conical)available withflush or extended
color cap

Color caps
flushContact Blocks and LED Pilot Light Assemblies

Potentiometerincl. resistor

LED pilot lightassembly

Cam switches

Couplingplate

LED series
elements

Contact block5Complete Standard Units
Push Buttons
Pilot Lights

Code

Push buttons flush, IP 67/IP 69K
non-illuminatedRotary Switches
Code
Double-Push Buttons, Potentiometer
Rotary switches, IP 66
non-illuminated, latched(changeable by coding pieces to spring return function)

13

P SN-WD0001

green
21

P SN-WD0002

red

P SN/WRK-K10

2 positions

14

13

0

22

14

13

green I

P SN/D/G/X1-K10
14
21

red h

P SN/D/R/X0-K01

P SN/WRK3-K20

3 positions
0

22

13 23

14 24

0

Pilot lights flush, IP 67/IP 69K
with LED element

P SN-WD0003

red
12 V-30 V AC/DC

P SN-WD0004

Double-push buttons, IP 66
with LED element, color cap opaque
85 V-264 V AC
13

green I
green
85 V-264 V AC

P SN-WD0005

red
85 V-264 V AC

P SN-WD0006

14
21

red h

P SN/DDL/GR/
X1-X0-K11

22

Solid pilot lights, IP 67/IP 69K
for direct wire (without bulb), bulb holder BA 9s
flush
green

P SN/LC/Gred

P SN/LC/R

yellow

P SN/LC/Y

blue

P SN/LC/B

1 kΩ

opaqueP SN/LC/W

4,7 kΩ

Potentiometer, IP 66
3 separate screw terminals, Pmax. = 0,5 W
P SN/R1K
P SN/R4K7
10 kΩ
P SN/R10K

extended (conical)
green

P SN/LCH/G

red

P SN/LCH/R

yellow

P SN/LCH/Y

blue

P SN/LCH/B

opaqueP SN/LCH/W

Other resistance values on request.

6< back to table of contents >green
12 V-30 V AC/DC

Complete Standard Units
Emergency Stop Push Buttons

CodeEmergency stop push buttons, IP 66/IP 69K
fool-proof acc. to ISO 13850/EN 418
reset by pullingcomplement max: 4 contact blocks

Cam Switches

Code

Cam switches, IP 65
ON/OFF switches

1 poleCG4 A200-600
FS1

21P SN/PV-K01

red
22
13 21

P SN/PV-K11

red

CG4 A290-600
FS1

14 22

reset by key operation
1 key, locking MS1

Double-throw switches
21

P SN/PVS-K01

red
22< back to table of contents >1 pole2 poleCG4 A210-600
FS1
CG4 A211-600
FS1

top yellow, bottom black
reset by pullingcomplement max: 3 contact blocks

Double-throw switches withspring return to center1 pole

13 21

P SN/PV-KC11-IY

red
14 22
11 21

P SN/PV-KC02-IY

red

CG4 A214-600
FS1

12 22

foot and palm switch, IP 67/IP 69K
top yellow, bottom black
reset by pulling

Double-throw switches withelectrically isolated contacts

1 pole21

P FT/R-V-KC01-IY

red
22

CG4 A710-600
FS1

For further cam switches, refer to Catalog 120.

7

Pre-assembled Front Elements
Push Buttons
Pilot Lights

Code

Push buttons, IP 67/IP 69K

Rotary Switches
Double-Push Buttons

Code

Rotary switches, IP 66
switching angle 60°, latched1

flush, non-illuminatedgreen

P SN/D/G

red

P SN/D/R

green I

P SN/D/G/X1

red h

P SN/D/R/X0

P SN/WRK

2 positions, non-illuminated

P SN/WKV

flush, illuminated
P SN/DL/Gred

P SN/DL/R

green I

P SN/DL/G/X1

red h

P SN/DL/R/X0

2 positions, illuminatedPush buttons, IP 67/IP 69K extended,
non-illuminatedgreen

P SN/DH/Gred

P SN/DH/R

3 positions, illuminatedextended, illuminatedgreen

P SN/DLH/G

red

P SN/DLH/R

green

P SN/WRLK/G

red

P SN/WRLK/R

yellow

P SN/WRLK/Y

blue

P SN/WRLK/B

opaqueP SN/WRLK/W

green

P SN/WRLK3/G

red

P SN/WRLK3/R

yellow

P SN/WRLK3/Y

blue

P SN/WRLK3/B

opaqueP SN/WRLK3/W

Rotary switches, key operated, IP 66
switching angle 60°, latched1
1 key, locking MS1
2 positions

Pilot lights, IP 67/IP 69K
flush
green

P SN/L/G

red

P SN/L/R

yellow

P SN/L/Y

blue

P SN/L/B

opaqueP SN/L/W

key can be removed in h I

P SN/WRS

key can be only removed in h

P SN/WRS/A1

3 positions

extended (conical)

key can be removed in I h II

P SN/WRS3

key can be only removed in h

P SN/WRS3/A1

Double-push buttons, IP 66
color cap opaquegreen

P SN/LH/G

red

P SN/LH/R

yellow

P SN/LH/Y

green

blue

P SN/LH/BIh

P SN/DDL/GR/X1-X0

red

opaqueP SN/LH/W

green

START

P SN/DDL/GR/GB1-GB0

red

STOP

green

P SN/DDL/GR

red

black

P SN/DDL/S/X7-X7

black
1

8

changeable by coding pieces to spring return function (40° switching angle)< back to table of contents >P SN/WRK3

3 positions, non-illuminatedgreen

Pre-assembled Front Elements
Emergency Stop Push Buttons
Reset Units

Front Element Components
Code

Emergency stop push buttons
IP 67/IP 69K (turning)
IP 66/IP 69K (pulling)fool-proof acc. to ISO 13 850/EN 418
complement max.: 4 contact blocks

Push Buttons
Front Plates

Code

Push buttons, IP 67/IP 69K
without front platewith flush front ring, non-illuminatedmomentary

P SN/D/X

latchedP SN/DR/X

non-illuminatedreset by pullingred

P SN/PV

reset by turningred

P SN/PVT

Push buttons, IP 67/IP 69K
without front platewith extended front ring, non-illuminated< back to table of contents >illuminatedreset by pullingred

P SN/PVL

reset by turningred

P SN/PVLT

momentary

P SN/DG/X

green

P SN/XD/G

red

P SN/XD/R

yellow

P SN/XD/Y

blue

P SN/XD/B

white

P SN/XD/W

black

P SN/XD/S

Front plates, flush

reset by key operation
1 key, locking MS1
P SN/PVS

red

legends see
page 13

Front plates, extended

Reset units, IP 67/IP 69K
non-illuminatedgreen

P SN/XDH/G

red

P SN/XDH/R

yellow

P SN/XDH/Y

blue

RESET

P SN/DZ/B/GB14

blue

P SN/XDH/B

blue

R

P SN/DZ/B/X6

white

P SN/XDH/W

black

P SN/XDH/Slegends see
page 13

9

Front Element Components and Legend Plates
CodeFront Plates, Pilot Lights
Color Caps, Emergency Stop Plates

CodeFront plates, flush

Mushroom push buttons, IP 67/IP 69K
without front plate
momentarygreen

P SN/DP/G/X

red

P SN/DP/R/X

yellow

P SN/DP/Y/X

black

P SN/DP/S/X

P SN/DRP/G/X

red

P SN/DRP/R/X

yellow

P SN/DRP/Y/X

black

P SN/DRP/S/X

P SN/XDP/G

red

P SN/XDP/R

yellow

P SN/XDP/Y

white

P SN/XDP/W

black

P SN/XDP/S

red

P SN/XDL/Ryellow

P SN/XDL/Y

blue

P SN/XDL/B

opaqueP SN/XDL/W

Front plates, extended

Front plates
green

P SN/XDL/Glegends see
page 14latched
green

green

green

P SN/XDLH/G

red

P SN/XDLH/R

yellow

P SN/XDLH/Y

blue

P SN/XDLH/B

opaqueP SN/XDLH/W

legends see
page 14
Pilot light, IP 67, IP 69K
flush, without color cap
P SN/L/X

legends see
page 15

Color caps

Push buttons, IP 67/IP 69K
without front platewith flush front ring, illuminatedmomentary

P SN/DL/X

latchedP SN/DRL/X

green

P SN/XL/G

red

P SN/XL/R

yellow

P SN/XL/Y

blue

P SN/XL/B

opaqueP SN/XL/W

legends see
page 16

Emergency stop plates, IP 66
rectangular
33 mm x 50 mm
Push buttons, IP 67/IP 69K
without front platewith extended front ring, illuminatedmomentary

GermanP SN/XZK/D99

EnglishP SN/XZK/GB99

50 mm x 50 mm

P SN/XYK1P SN/DGL/Xsquare, in four languages

10< back to table of contents >Mushroom Push Buttons
Front Plates, Push Buttons

Legend Plates, Coupling Plate and Pilot Light Assemblies
Emergency Stop Plates
Legend Carrier, Legend Insert

CodeEmergency stop plates, IP 66
round, in four languages
Ø 90 mm

P SN/XAK1

Ø 60 mm

P SN/XBK1Legend Plates, Coupling Plate
LED Pilot Light Assemblies
Legend plates, IP 66
complete standard unit

		 0

I

P SB/ST/X88

0		 I

P SB/ST/X89

I

P SB/ST/X93

Legend carrier, IP 66
without platefor push buttons

0

II

STOP

P SB/ST/GB0

START

P SB/ST/GB1

Aus

P SB/ST/D5

OFF

P SB/ST/GB5

Ein

P SB/ST/D6

ON

P SB/ST/GB6

Störung

P SB/ST/D8

FAULT

P SB/ST/GB8

Betrieb

P SB/ST/D7

RUN

P SB/ST/GB7

P SB/ST/X

HAND		< back to table of contents >

Code

AUTO

P SB/ST/D11

MAN.		 AUTO

P SB/ST/GB11

Aus		

Ein

P SB/ST/D10

OFF		

ON

P SB/ST/GB10

HAND 0 AUTO

P SB/ST/D12

MAN. 0 AUTO

P SB/ST/GB12

Coupling plate
P SN/Afor double-pushbuttons

P SB/STDD/X

LED pilot light assemblies
front mounting
12 V-30 V AC/DC
green

P SN/LED/G

red

P SN/LED/R
1

white

P SN/LED/W

85 V-264 V AC
Legend insert
P SN/XSTgreen

P SN/LED230/G

red

P SN/LED230/R

white1

P SN/LED230/W

base mounting
12 V-30 V AC/DC
green

P SN/LEDC/G

red

P SN/LEDC/R
1

white

P SN/LEDC/W

85 V-264 V ACgreen

P SN/LEDC230/G

red

P SN/LEDC230/R

white1

P SN/LEDC230/W

1

can be combined with blue, yellow or white pilot lights

11Series Elements, Contact Blocks, Enclosures and Accessories
LED Series Elements
Contact Blocks, Enclosures

Code

LED series elements
for front mounting and base mounting

Enclosures
Blanking Plug, Lamps

Code

Plastic enclosure, IP 67/IP 69K
totally insulated, lid screws made of stainless steel

resistor element for
42 V-60 V AC/DC
for pilot lightassemblies
12 V-30 V AC/DC

top gray, bottom black
P SN/XLED60
control positions
Ø 22,5 mm
P SN/I1

1
LED test elements
for decoupled
operational test
for connecting to:
12 V-30 V AC/DC

P SN/XLED/T

85 V-264 V AC

P SN/XLED230/T

Contact blocks
front mounting

top gray, bottom black
3

P SN/K10

control positions
Ø 22,5 mm

41

2

P SN/I2

3

P SN/I3

4

P SN/I4

6

P SN/I6

2

for plastic enclosures

Blanking plug, IP 67/IP 69K
gray, for surplus control positions

3

P SN/KC10
4P SN/B

1

P SN/KC01
2

LED-lamps with 4 chips, BA 9s
with integrated bridge rectifier

24 V-28 V AC/DC

white

P SN/LW024

Plastic enclosure, IP 67/IP 69K
totally insulated, lid screws made of stainless steel

24 V-28 V AC/DC

red

P SN/LR024

top yellow, bottom black

24 V-28 V AC/DC

green

P SN/LG024

220 V AC/DC

white

P SN/LW220

220 V AC/DC

red

P SN/LR220

220 V AC/DC

green

P SN/LG220

110 V-120 V AC/DC

white

P SN/LW110

110 V-120 V AC/DC

red

P SN/LR110

110 V-120 V AC/DC green

P SN/LG110

control positions
Ø 22,5 mm
1

12

P SN/IY1< back to table of contents >P SN/K01

Accessories
Bulb Extractor
Protection Caps

Code

Bulb extractor
P SN/LGL

Protective Shrouds
Rod Link, Coding Pieces

CodeProtective shroud, IP 66
protection against accidental operation
for push buttons and rotary switches(cannot be combined with legend plates)
P SN/XGWK

Protection caps, IP 67
transparent, for aggravating environments(not in food areas)(cannot be combined with legend plates)

Protective shroud, IP 65
yellow, for emergency stop buttons(cannot be combined with legend plates)
P SN/XGPV< back to table of contents >push buttons, flush
pilot lights, flush

double-push buttons

P SN/T/DP SN/T/DD

Rod link
for operating the middle contact block of nonilluminated rotary switches with 3 positions
P SN/XW

Protection cap
prevents dirt and dust from getting into the keyhole (not food resistant)rotary switches,
key operated

Coding pieces
for rotary switches to convert the latched function
into spring return function (1 kit = 2 pieces)
P SN/XWSP SN/XC/Y

13

Accessories
Code

Track adapter
for tracks acc. to EN 60715
for front mounted units

Fixation Nut
Spare KeyCode

Fixation nut
for push buttons, pilot lights and rotary switches

P SN/IVS

Nut key
for push buttons, pilot lights and rotary switches

P SN/GRfor cam switches

P SN/MSS00 T170 10

for cam switches
Spare keylocking MS1
S00 T170 09

14

P SN/ES/MS1< back to table of contents >Track Adapter
Nut KeyFront Plates for Push Buttons< back to table of contents >Front Plates for Push Buttons
non-illuminatedSymbolMeaning

Code

Code

Front Plates
flush

Front Plates
extended

Color

Legendblack

Zu

P SN/XD/S/D2

P SN/XDH/S/D2

Auf

P SN/XD/S/D3

P SN/XDH/S/D3

Ab

P SN/XD/S/D4

P SN/XDH/S/D4

red

Aus

P SN/XD/R/D5

P SN/XDH/R/D5

black

Ein

P SN/XD/S/D6

P SN/XDH/S/D6

blue

Entsperren

P SN/XD/B/D14

P SN/XDH/B/D14

black

Vorwärts

P SN/XD/S/D15

P SN/XDH/S/D15

Rückwärts

P SN/XD/S/D16

P SN/XDH/S/D16

Heben

P SN/XD/S/D17

P SN/XDH/S/D17

SenkenP SN/XD/S/D18

P SN/XDH/S/D18

red

STOP

P SN/XD/R/GB0

P SN/XDH/R/GB0

black

STOP

P SN/XD/S/GB0

P SN/XDH/S/GB0

green

START

P SN/XD/G/GB1

P SN/XDH/G/GB1

white

START

P SN/XD/W/GB1

P SN/XDH/W/GB1

black

CLOSE

P SN/XD/S/GB2

P SN/XDH/S/GB2

UP

P SN/XD/S/GB3

P SN/XDH/S/GB3

DOWN

P SN/XD/S/GB4

P SN/XDH/S/GB4

red

OFF

P SN/XD/R/GB5

P SN/XDH/R/GB5

black

ON

P SN/XD/S/GB6

P SN/XDH/S/GB6

TEST

P SN/XD/S/GB9

P SN/XDH/S/GB9

blue

RESET

P SN/XD/B/GB14

P SN/XDH/B/GB14

black

FORWARDP SN/XD/S/GB15

P SN/XDH/S/GB15

REVERSEP SN/XD/S/GB16

P SN/XDH/S/GB16

RAISE

P SN/XD/S/GB17

P SN/XDH/S/GB17

P SN/XD/S/GB18

P SN/XDH/S/GB18

P SN/XD/R/X0

P SN/XDH/R/X0

P SN/XD/S/X0

P SN/XDH/S/X0

P SN/XD/G/X1

P SN/XDH/G/X1

LOWER
red

h

black

h

green

I

black

I

P SN/XD/S/X1

P SN/XDH/S/X1

white

I

P SN/XD/W/X1

P SN/XDH/W/X1

green

II

P SN/XD/G/X2

P SN/XDH/G/X2

black

II

P SN/XD/S/X2

P SN/XDH/S/X2

blue
black

stop

start

+

increase

P SN/XD/S/X4

P SN/XDH/S/X4-

decrease

P SN/XD/S/X5

P SN/XDH/S/X5

R

reset

P SN/XD/B/X6

P SN/XDH/B/X6

guide motion

P SN/XD/S/X7

P SN/XDH/S/X7

P SN/XD/S/X8

P SN/XDH/S/X8

hand-control

P SN/XD/S/X9

P SN/XDH/S/X9

automatic cycle

P SN/XD/S/X10

P SN/XDH/S/X10

inching

P SN/XD/S/X11

P SN/XDH/S/X11

disengaging

P SN/XD/S/X12

P SN/XDH/S/X12

unlockP SN/XD/S/X13

P SN/XDH/S/X13

tighten

P SN/XD/S/X14

P SN/XDH/S/X14

releaseP SN/XD/S/X15

P SN/XDH/S/X15

liquidP SN/XD/S/X16

P SN/XDH/S/X16

horn

P SN/XD/S/X17

P SN/XDH/S/X17

15

Front Plates for Push Buttons

SymbolMeaning

Code

Code

Front Plates
flush

Front Plates
extended

Color

LegendopaqueZu

P SN/XDL/W/D2

P SN/XDLH/W/D2

Auf

P SN/XDL/W/D3

P SN/XDLH/W/D3

Ab

P SN/XDL/W/D4

P SN/XDLH/W/D4

red

Aus

P SN/XDL/R/D5

P SN/XDLH/R/D5

opaqueEin

P SN/XDL/W/D6

P SN/XDLH/W/D6

blue

Entsperren

P SN/XDL/B/D14

P SN/XDLH/B/D14

opaqueVorwärts

P SN/XDL/W/D15

P SN/XDLH/W/D15

Rückwärts

P SN/XDL/W/D16

P SN/XDLH/W/D16

Heben

P SN/XDL/W/D17

P SN/XDLH/W/D17

SenkenP SN/XDL/W/D18

P SN/XDLH/W/D18

red

STOP

P SN/XDL/R/GB0

P SN/XDLH/R/GB0

opaqueSTOP

P SN/XDL/W/GB0 P SN/XDLH/W/GB0

green

START

P SN/XDL/G/GB1

opaqueSTARTP SN/XDL/W/GB1 P SN/XDLH/W/GB1

CLOSE

P SN/XDL/W/GB2 P SN/XDLH/W/GB2

UP

P SN/XDL/W/GB3 P SN/XDLH/W/GB3

P SN/XDLH/G/GB1

DOWN

P SN/XDL/W/GB4 P SN/XDLH/W/GB4

red

OFF

P SN/XDL/R/GB5

opaqueON

P SN/XDL/W/GB6 P SN/XDLH/W/GB6

TEST

P SN/XDL/W/GB9 P SN/XDLH/W/GB9

blue

RESET

P SN/XDL/B/GB14 P SN/XDLH/B/GB14

opaqueFORWARDP SN/XDL/W/GB15 P SN/XDLH/W/GB15

REVERSEP SN/XDL/W/GB16 P SN/XDLH/W/GB16

RAISE

P SN/XDL/W/GB17 P SN/XDLH/W/GB17

LOWER

P SN/XDL/W/GB18 P SN/XDLH/W/GB18

redhopaque

h

green

I

stop

start

P SN/XDLH/R/GB5

P SN/XDL/R/X0

P SN/XDLH/R/X0

P SN/XDL/W/X0

P SN/XDLH/W/X0

P SN/XDL/G/X1

P SN/XDLH/G/X1

opaqueI

P SN/XDL/W/X1

P SN/XDLH/W/X1

green

II

P SN/XDL/G/X2

P SN/XDLH/G/X2

opaqueblue
opaque16

IIP SN/XDL/W/X2

P SN/XDLH/W/X2+

increase

P SN/XDL/W/X4

P SN/XDLH/W/X4-

decrease

P SN/XDL/W/X5

P SN/XDLH/W/X5

R

reset

P SN/XDL/B/X6

P SN/XDLH/B/X6

guide motion

P SN/XDL/W/X7

P SN/XDLH/W/X7

P SN/XDL/W/X8

P SN/XDLH/W/X8

hand-control

P SN/XDL/W/X9

P SN/XDLH/W/X9

automatic cycle

P SN/XDL/W/X10

P SN/XDLH/W/X10

inching

P SN/XDL/W/X11

P SN/XDLH/W/X11

disengaging

P SN/XDL/W/X12

P SN/XDLH/W/X12

unlockP SN/XDL/W/X13

P SN/XDLH/W/X13

tighten

P SN/XDL/W/X14

P SN/XDLH/W/X14

releaseP SN/XDL/W/X15

P SN/XDLH/W/X15

liquidP SN/XDL/W/X16

P SN/XDLH/W/X16

horn

P SN/XDL/W/X17

P SN/XDLH/W/X17< back to table of contents >Front Plates for Push Buttons
illuminatedFront Plates for Mushroom Push Buttons< back to table of contents >Front Plates for Mushroom Push Buttons

Code

Color

LegendSymbolMeaningblack

Zu

P SN/XDP/S/D2

Auf

P SN/XDP/S/D3

Ab

P SN/XDP/S/D4

red

Aus

P SN/XDP/R/D5

black

Ein

P SN/XDP/S/D6

Vorwärts

P SN/XDP/S/D15

Rückwärts

P SN/XDP/S/D16

Heben

P SN/XDP/S/D17

SenkenP SN/XDP/S/D18

red

STOP

P SN/XDP/R/GB0

black

STOP

P SN/XDP/S/GB0

green

START

P SN/XDP/G/GB1

white

START

P SN/XDP/W/GB1

black

CLOSE

P SN/XDP/S/GB2

UP

P SN/XDP/S/GB3

DOWN

P SN/XDP/S/GB4

red

OFF

P SN/XDP/R/GB5

black

ON

P SN/XDP/S/GB6

TEST

P SN/XDP/S/GB9

FORWARDP SN/XDP/S/GB15

REVERSEP SN/XDP/S/GB16

RAISE

P SN/XDP/S/GB17

LOWER

P SN/XDP/S/GB18

red

h

black

h

green

I

black

I

P SN/XDP/S/X1

white

I

P SN/XDP/W/X1

green

II

P SN/XDP/G/X2

black

II

P SN/XDP/S/X2

stop

P SN/XDP/R/X0
P SN/XDP/S/X0

start

P SN/XDP/G/X1+

increase

P SN/XDP/S/X4-

decrease

P SN/XDP/S/X5

guide motion

P SN/XDP/S/X7
P SN/XDP/S/X8

hand-control

P SN/XDP/S/X9

automatic cycle

P SN/XDP/S/X10

inching

P SN/XDP/S/X11

disengaging

P SN/XDP/S/X12

unlockP SN/XDP/S/X13

tighten

P SN/XDP/S/X14

releaseP SN/XDP/S/X15

liquidP SN/XDP/S/X16

horn

P SN/XDP/S/X17

17

Color Caps for Pilot Lights
Color Caps for Pilot Lights
flush

Code

LegendMeaning

opaqueZu

P SN/XL/W/D2

Auf

P SN/XL/W/D3

Ab

P SN/XL/W/D4

red

Aus

P SN/XL/R/D5

opaqueEin

P SN/XL/W/D6

Vorwärts

P SN/XL/W/D15

Rückwärts

P SN/XL/W/D16

Heben

P SN/XL/W/D17

SenkenP SN/XL/W/D18

red

STOP

P SN/XL/R/GB0

opaqueSTOP

P SN/XL/W/GB0

green

START

P SN/XL/G/GB1

opaqueSTARTP SN/XL/W/GB1

CLOSE

P SN/XL/W/GB2

UP

P SN/XL/W/GB3

DOWN

P SN/XL/W/GB4

red

OFF

P SN/XL/R/GB5

opaqueON

P SN/XL/W/GB6

TEST

P SN/XL/W/GB9

FORWARDP SN/XL/W/GB15

REVERSEP SN/XL/W/GB16

RAISE

P SN/XL/W/GB17

LOWER

P SN/XL/W/GB18

redhopaque

h

green

I

opaqueI

P SN/XL/W/X1

green

II

P SN/XL/G/X2

opaqueIIP SN/XL/W/X2

stop

P SN/XL/R/X0
P SN/XL/W/X0

start

P SN/XL/G/X1+

increase

P SN/XL/W/X4-

decrease

P SN/XL/W/X5

guide motion

P SN/XL/W/X7
P SN/XL/W/X8

18

hand-control

P SN/XL/W/X9

automatic cycle

P SN/XL/W/X10

inching

P SN/XL/W/X11

disengaging

P SN/XL/W/X12

unlockP SN/XL/W/X13

tighten

P SN/XL/W/X14

releaseP SN/XL/W/X15

liquidP SN/XL/W/X16

horn

P SN/XL/W/X17< back to table of contents >SymbolFront Plates
flush

Color

Design
Programming and Circuit Design
Programming for converting the latched function into spring return function
Push buttons
Rotary switches

Rod link for operating the middle contact block of
non-illuminated rotary switches with 2 and 3 positions

B

P SN/XC/YA

P SN/XC/Y in B
O

I

O

I

II

II

P SN/XC/Y in A and B
Key cannot be removed in spring return positionUe ~/12 – 30 V ~/
R

R

1

R

2 1

2 1

2

X1

X2

H1
P SN/XLED60

P SN/XLED60

1x

2x

3x

4x

5x

6x

7x

Ue ≤

60 V

90 V

120 V

150 V

180 V

210 V

240 V

P SN/LED(C)/...

LED test element
P SN/XLED/T
13

13

K1

13

K2
14

12 – 30 V ~/

3

K3
14

2

ST

14

P SN/K(C)10

4

1

V1
2

1

V2
2
X1

H1

1

P SN/XLED/T
X1 V3

X1

H2

H3

X2

X2

P SN/LED(C)/...

X2

Ue ~

P SN/XLED230/T
P SN/K(C)10

85 – 264 V~,
50 – 60 Hz

L1
13

K1

13

K2
14

85 – 264 V ~/50 – 60 Hz< back to table of contents >LED resistor element
P SN/XLED60

13

K3
14

ST

14

3

1

4

2

P SN/K(C)01

C
1

C
2 1

2

P SN/XLED230/T

C1
2 1

C2
2 1

H1

X1 C3

X1

H2
X2

X2

H1

2 1

X1

X1

P SN/LED(C)230/...

P SN/XLED230/T

1x

2x

Ue ≤

400 V AC

500 V ACP SN/XLED230/T

H3
X2

X2

P SN/LED(C)230/...

N

19

mm
inch

Dimensions

Operating and Indicator Devices, Push Buttons, Rotary Switches, Rotary Switches key operated, Pilot Lights,
Push Buttons illuminated, Mushroom Push Buttons, Solid Pilot Lights, Emergency Stop Push Button, PotentiometerØ 29,5

1.16” dia

Ø 29,7
1.17” dia

Operating and indicator devices

29,7
1.17”

1–6
.04” – .24”
19
.75”

Push buttons
P SN/D

P SN/DG(L)P SN/DD

10
.39”

16,4
.65”

16,5
.65”

13,2
.52”

Rotary switches key operated
P SN/WRS

Ø 29,7
1.17” dia

Rotary switches
P SN/W(R)K...
P SN/W(R)LK...

Push buttons P SN/Dbase mounting

54,7
2.15”

Ø 29,7
1.17” dia

P SN/DH< back to table of contents >

10
.39”

20,6
.81”
47,75
1.88”

26,9
1.06”

P SN/LPush buttons illuminated
P SN/DLP SN/DLH

11,5
.45”

10
.39”

Mushroom push buttons
P SN/DPØ 36,5
1.44” dia

Pilot lights
P SN/LH

20

41
1.61”

22
.87”

22
.87”
11,5
.45”

Emergency stop push button
P SN/PV.
P SN/PVT.
P SN/PVL.
P SN/PVSP SN/LCH...

18
.71”

Potentiometer
P SN/R...K

35
1.38”

Solid pilot lights
P SN/LC...

23,6
.93”

16,4
.65”

41
1.61”
75,1
2.96”

47,9
1.89”

38
1.50”

18
.71”

29,2
1.15”

32,9
1.30”

Dimensions

mm
inch

Front Mounting
Pilot lights and illuminated push buttons

37
1.46”
.76”

19,3

21,5
.85”

Fixing adapter
P SN/A

30
1.18”

45
1.77”

30
1.18”

Track adapter

64,5
2.54”

54,5
2.15”
P SN/D...
P SN/L...
P SN/W...
P SN/P...

45
1.77”
71
2.80”

30
1.18”

3,1
.12”

56,7
2.23”

35,2
1.39”

4,5 (M4)
.18”

22,4
.88”

Plastic enclosureØ 943.70” dia

M20

M20

80

6,5 – 7,5
.26” – .30”

66.5

Foot and palm switches
P FT/R-V-KC01-IY

44

10 10 10.39” .39” .39”

101
3.98”

e

33

M4

b
a

18
.71”

17.8

¿

3xM20 (PG13,5)
1xM16 on base

M5x20

56

➀

M20/M2540
1.57”< back to table of contents >

37,2
1.46”

22,4
.88”

Push buttons with P SN/K...
Push buttons with P SN/LED... + P SN/XLED...

M20

M20

48

65
2.56”

85
3.35” sq

Type

Control apositionsbeCable entries

P SN/I (Y)1
P SN/I2		
P SN/I3		
P SN/I4		
P SN/I6		

1
2
3
4
6

42,6
85,6
118,6
151,6
217,6

58,5
106,5
139,5
172,5
238,5

2xM16 3xM20 2xM25
2xM20 3xM20 2xM25
2xM20 2xM25 4xM20
2xM20 2xM25 4xM20
2xM20 2xM25 4xM20

72
120
153
186
252

21

Dimensions

mm
inch

Legend Carrier
Legend carrier
P SB/ST

Mounting drilling with slot
P SB/STDD

24,1 +0.4
0
27,5
1.08”

.95” +.02”
0

47
1.85”

35
1.38”
.59”

30
1.18”

+0.4

22,3 030
1.18”

Grid dimension acc. to
IEC/EN 60947

1–6.04” – .24”+.02”.88” 0Grid dimension for different combinations

Protection cap with legend carriercannot be combined
Type

50
1.97”

B

P SN/...(IEC/EN 60947)
30
P SN/...
30
P SN/D... + P SN/T/D
33
38
P SN/D(R)P...
P SN/PV...
38
P SN/PV(L...)(S...) + P SN/D... 33
P SN/DDL...
30
P SN/DDL... + P SN/T/DD
33
30
P SB/STP SB/STDD
30
90
P SN/XAK...
P SN/XZK...
33
P SN/XBK...
60
50
P SN/XYK...

A

30
1.18”

Grid dimension for P SN/DD...

Grid dimension for P SN/DD...
with protection cap P SN/T/DD

22b ≥ 582.28”

b ≥ 46
1.81”

63
2.48”
75
2.95”

a ≥ 33
1.30”

30
1.18”

A≥		
mm inchProtection cap and protection shroud
with legend carrier cannot be combined

1.18
1.18
1.30
1.50
1.50
1.30
1.18
1.30
1.18
1.18
3.54
1.30
2.36
1.97

B≥
mm inch
50
40
40
40
40
40
55
58
50
75
90
52
60
50

1.97
1.57
1.57
1.57
1.57
1.57
2.17
2.28
1.97
2.95
3.54
2.05
2.36
1.97

< back to table of contents >

15

3,2
.13”

Dimensions

mm
inch

Blanking Plug, Protection Caps, Protective Shroud, Emergency Stop Plates, Cam Switches
Blanking plug
P SN/B

Protection cap
P SN/T/D

58
2.28”

17
.67”

29,5
1.16”

Protection cap
P SN/T/DD

33
1.30”

17
.67”

33
1.30”

23
.91”

Protective shroud
P SN/XGWK

20
.79”

R
1. 41
61
”

25
.98”

5
.2”

Ø 36
1.42” dia

12
.47”
78
3.07”

Emergency stop plates
P SN/XAK

Ø 25.98” dia50
1.97”

P SN/XBK...

33
1.30”

50
1.97”

12,5
.49”

.8

.65”

16,5

50
1.97”

Ø

d = 0,8.03”

P SN/XYK1

3,2
.13”

2
9” 2,5dia

P SN/XZK...

50
1.97”

Ø 60

2.36” dia

90
3.54”

Cam switches.638" .008"
0

+ 0.4

22,3 0+.878"+ .016"

B

C

D

M

28
1.1

5
.2

29,5
1.16

12,5
.49

+

.949" .016"
0

+ 0.4

0
+ .008"0

24,1 0++ 0.2

17,9 0

.126"

+ 0.2

16,2 0

+ 0.2

3,2

+ 0.2

1,7 0
+
.067" .008"0.705" .008"
0< back to table of contents >Protection cap
P SN/XWSP SN/XGPVL 1 stage

L 2 stages

38,5		
1.52		

50,5
1.99

0

23

Technical Data
Contact
BlocksGeneralStandards and requirements
Mechanical life
Max. operating frequency
Operating force
Operating torqueoperations

x 106
S/h
N
Nm

Protection IEC/EN 60529
Environmental resistanceLED
Elements

Push Buttons
Mushroom P/B
momentary

IEC/EN 60947, VDE 0660
5
5
–
3600
3600
–
≤5
≤5
–
≤ 0,8 (screw≤ 0,8 (screw–
terminals)
terminals)
IP 20
IP 20
IP 67/IP 69K
humidity, constant, acc. to IEC 60068-2-78
humidity, cyclic, acc. to IEC 60068-2-30

DoublePush Buttons

Rotary Switches
Rotary Switches
illuminated

0,2
3600
≤5
–

0,1
2000
–
≤ 0,3

IP 67/IP 69K

IP 66

Current Paths
Rated impulse withstand voltage Uimp
Rated insulation voltage Ui
Overvoltage category/
Pollution degree
Control circuit reliability at
24 V DC/5 mA
5 V DC/1 mA
Max. fuse size
Switching Capacity
Rated operational current Ie
AC-15
		115 V		230 V		400 V
		500 V
DC-13
		24 V		42 V
		60 V		110 V		220 VElectrical life
AC-15
		230 V/0,5 A
		230 V/1,0 A
		230 V/3,0 A
DC-13
		12 V/2,8 A

g-25/+70any> 30-25/+701
any> 30-25/+70any> 30-25/+70any> 30-25/+70
any
> 30

mm2
mm2

0,75-2,50,5-2,5

0,75-2,50,5-2,5

–
–

–
–

–
–

V
V

6000
500
III/3

6000
500
III/3

–
–
–

–
–
–

–
–
–

< 10 , < 1 failure per 10 operations< 5 x 10-6, < 1 failure per 5 x 106 operations
10
–
–

–

–

A
A
A
A

6
6
4
2

–
–
–
–

–
–
–
–

–
–
–
–

–
–
–
–

A
A
A
A
A

3
1,7
1,2
0,8
0,3

–
–
–
–
–

–
–
–
–
–

–
–
–
–
–

–
–
–
–
–

operations
operations
operations

x 106
x 106
x 106

1,6
1,0
0,7

–
–
–

–
–
–

–
–
–

–
–
–

operations

x 106

1,2

–

–

–

–

UL/CSA/GOST

UL/CSA/GOST

UL/CSA/GOST

UL/CSA/GOST UL/CSA/GOST

min./max.

min.-max.
min.-max.

fault frequency HFfault frequency HF
characteristic

Approvals
Technical data on request.

1> 200 V AC/60 Hz: -25/+55 °C

24

°C

-7

A

gG

7

< back to table of contents >Ambient temperature			
open
Mounting position
Shock withstand acc. to IEC 60068-2-27
Shock period 11 ms, 1/2 sinus wave
Max. permissible wire gage
single core
stranded wire

Technical Data
RotarySwitches
key operated
GeneralStandards and requirements
Mechanical life
Max. operating frequency
Operating force
Operating torqueProtection acc. to IEC/EN 60529

operations

x 106
S/h
N
Nm

< back to table of contents >Push Buttons
Push Buttons, illuminatedMushroom P/B, latched

Emergency
Stop Push
Buttons

> 0,1
1800
≤5

> 0,1
600
≤ 50

IP 67/IP 69K

reset by turning
IP 67/IP 69K
reset by pulling
IP 66/IP 69K-25/+70any> 30-25/+70any> 30-25/+70
any> 50

UL/CSA/GOST

UL/CSA/GOST

UL/CSA/GOST

Pilot Lights

IEC/EN 60947, VDE 0660
> 0,1
100
≤ 0,5
IP 66

IP 67/IP 69K
IP 66(Potentiometer)
IP 67/IP 69K(pilot light)
humidity, constant, acc. to IEC 60068-2-78
humidity, cyclic, acc. to IEC 60068-2-30

Environmental resistanceAmbient temperature			
open
Mounting position
Shock withstand acc. to IEC 60068-2-27
Shock period 11 ms, 1/2 sinus wave
Max. permissible wire gage
single core
stranded wire

Potentiometer
Solid Pilot
Lightsmin./max.

°Cgmin.-max.
min.-max.

Current Paths
Rated impulse withstand voltage Uimp
Rated insulation voltage Ui
Overvoltage category/
Pollution degree-25/+70any> 30-25/+70
any
> 30

mm2
mm2

0,5-1,50,5-1,5

V
V

4000
250
III/3

Approvals
Technical data on request.

UL/CSA/GOST

UL/CSA/GOSTFoot and Palm Switches
latchedGeneralStandards and requirements
Mechanical life
Max. operating frequency
Operating force
Protection acc. to IEC/EN 60529
Environmental resistanceAmbient temperature
Mounting position
Shock withstand acc. to IEC 60068-2-27
Shock period 11 ms, 1/2 sinus wave

operations

x 106
S/h
N

min./max.

°Cg

IEC/EN 60947, VDE 0660
> 0,1
≤ 600
≤ 60
IP 67, IP 69K
humidity, constant, acc. to IEC 60068-2-78
humidity, cyclic, acc. to IEC 60068-2-30-25/+40any> 15

Cam Switches CG41

GeneralStandards and requirements
Rated impulse withstand voltage Ue2
2
Rated insulation voltage Uimp
Rated thermal current Iu/Ith
Rated operational current Ie			
220 V-240 V
			
380 V-440 V
Max. fuse sizegG-characteristic
Max. permissible wire gage
single core or stranded wire
flexible wireApprovals
Technical data on request.

AC-21A
AC-15
AC-15

V
V
A
A
A
A
A
mm2
mm2

IEC/EN 60947, VDE 0660
440
4000
10
10
2,5
1,5
10
2 x 1,5
2 x 1,5

UL/CSA/GOST/CCC 3

1

For further cam switches, refer to Catalog 120. 2Valid for lines with grounded common neutral termination, overvoltage category III, pollution degree 3.
If this approval is required, please request when ordering.

3

25

The Range of “Blue Line” Switchgear
Technical literature covering the following products is available on request.

Catalog
NumberMain Switches and Main Switches with Emergency Function 16 A-315 A
Maintenance Switches 20 A-315 A
Switch Disconnectors 20 A-315 A

500

According to IEC 60947-3, EN 60947-3, VDE 0660 part 107, IEC 60204, EN 60204 and VDE 0113

CL Switches 10 A-20 A
C, CA and CAD Switches 10 A-315 A and L Switches 350 A-2400 A
C, CA and CAD switches are designed for universal application. They are recommended for instrument, isolator,
double-throw and motor control.
L switches are designed for load and off-load applications. They are used to switch resistive or low inductive
loads.

100

Optional Extras and Enclosures
The complete product line, a large number of optional extras is available, including door interlocks, push-pull
devices, cylinder and padlock attachments, control and indicator devices, AC motor drives, as well as
enclosures, both insulated and metal.

101

A and AD Switches 6 A-25 A
A and AD switches have 4 contacts in each switching stage. These switches provide an extensive range of switch
functions and require a minimum mounting depth. Up to 36 switching positions are possible, with availability of
48 contacts per 12 stage switch column.

110

CG, CH and CHR Switches 10 A-25 A
Ultra compact CG, CH and CHR switches are ideally suited for control and instrumentation applications.
Switch terminals are “finger-proof” and conveniently accessible for wiring and are delivered open. All CG4 switches offer specially designed gold plated contacts or H-bridges with “cross-wire” contact systems, which facilitates their use in electronic circuitry and chemically aggressive environments.

120

DH, DHR, DK and DKR Switches 6 A-16 A
DH, DHR, DK and DKR switches incorporate unique corrosion resistant contacts that permit operation on system
voltage as low as 1 V. They have fully enclosed and protected contacts which can be operated either by rotary
and/or lateral handle movement. D switches are used in calibration and semiconductor circuits. They are also
used for relay and contactor control.

X Switches 80 A-630 A
X switches can be applied for load, tap and gang switching duties. They incorporate 6 contacts in each switchingstage. Their compact design provides a minimum length dimension for mounting purposes.

130
140

KG Switches 20 A-315 A and KH and KHR Switches 16 A-80 A
KG, KH and KHR switches are excellent circuit interruptors. They have high through fault and fault making
capacities and are especially designed for use as isolators and safety switches for machine tools, distribution
panels and switchboards. KG ON/OFF switches offer unusually high dimensioned air and creepage distances
between terminals which are designed for time saving “straight-line” wiring. ON/OFF switches are available withup to 8 poles and double-throw switches are available with up to 4 poles.

Push Buttons and Pilot Lights, 22,5 mm Ø
A complete range of state-of-the-art push buttons and pilot lights represent an ideal combination of functional
security and economical efficiency in a modular design.

150
302

We reserve the right to make technical and dimensional changes without prior notice.

26
24

SALES AND SERVICE ORGANIZATION
Australia
Kraus & Naimer Pty. Ltd.
379 Liverpool Road, ASHFIELD, N.S.W. 2131
P: 1800 567 948
E: sales-au@krausnaimer.com
Austria
Kraus & Naimer GmbH
Schumanngasse 39
1180 WIEN
P: +43 1 404 06 0
E: sales-at@krausnaimer.com
Belgium, Luxembourg
Kraus & Naimer B.V.
Ikaros Business Park
Ikaroslaan 21930 ZAVENTHEM
P: +32 2 757 0141
F: +32 2 757 1640
E: sales-be@krausnaimer.com

Great Britain
Kraus & Naimer Ltd.
115 London RoadNEWBURY/BERKSHIRE RG14 2AH
P: +44 1635 262626
F: +44 1635 37807
E: sales-uk@krausnaimer.com
Greece
KALAMARAKIS-SAPOUNAS S. A.
Ionias & Neromilou Str., P. O. Box 46566
13671 ACHARNES/ATHENS
P: +30 2 10 240 6000 6
F: +30 2 10 240 6007
E: kalamarakis.sapounas@ksa.gr
Hungary
GANZ KK KFT.
X. Kõbányal út 41/c, Postfach 871475 BUDAPEST
P: +36 1 261 5479
E: ganzkk@ganzkk.hu

BrazilCentral and South America
Kraus & Naimer Ind. Com. Ltda.
Rua Santa Monica, 1061
Parque Industrial San Jose
P: +55 11 2198 1288
F: +55 11 2198 1251
E: knbrasil@krausnaimer.com.br

Iceland
JOHAN RÖNNING LTD.
Klettagarðar 25
104 REYKJAVIK
P: +354 5200 800
E: ronning@ronning.is

CanadaKraus & Naimer Ltd.
219 Connie Crescent, Unit 13A
CONCORD, Ontario, L4K 1L4
P: +1 905 738 1666
E: sales-ca@krausnaimer.com

Republic of Ireland
Kraus & Naimer Ltd.
4235 Atlantic Avenue
Westpark Business Campus
Shannon, Co. Clare
P: +353 61 704700
F: +353 61 471084
E: sales-ie@krausnaimer.com

CyprusELECTROMATIC CONSTRUCTIONS LTD.
72, Evagoras Pallikarides Str., 2235 LATSIA-Nicosia
P. O. Box 12630, 2251 LATSIA-Nicosia
P: +357 2 48 41 41
F: +357 2 48 57 47
E: electromatic@cytanet.com.cy
Czech Republic
OBZOR, výrobní družstvo Zlín
Na Slanici 378
763 02 ZLÍNP: +420 577 195 150
F: +420 577 195 152
E: odbyt@obzor.cz
Denmark
THIIM A/S
Transformervej 31
2860 SOEBORG
P: +45 4485 8000
F: +45 4485 8005
E: thiim@thiim.com
FinlandKraus & Naimer Oy
Kiitoradankuja 801530 VANTAA
P: +358 9 825 424 0
E: sales-fi@krausnaimer.com
FranceKraus & Naimer s.a.s.
33, rue Bobillot
75013 PARIS
P: +33 1 58 40 80 80
E: sales-fr@krausnaimer.com
Germany
Kraus & Naimer GmbH
Wikingerstraße 20-28, 76189 KARLSRUHE
Postfach 10 01 24, 76231 KARLSRUHE
P: +49 721 59 88 0
E: sales-de@krausnaimer.com

Italy
Kraus & Naimer s.r.l.
Via Terracini, 924047 TREVIGLIO (BG)
P: +39 0363 30 11 12
E: sales-it@krausnaimer.com
Japan
Kraus & Naimer Ltd.
Yoshiwada Building 2F
1-11-6 Hamamatsucho
Minato-Ku, TOKYO 105-0013
P: +81 3 3436 6151
F: +81 3 3436 6325
E: sales-jp@krausnaimer.com
MexicoJC INGENIERÍA Y CONTROL, SA DE CV.
Ángel Gaviño 30.
C. Satélite, C. Medicos,
Naucalpan Edo. de Mexico, C.P. 53100
P: +52 55 55 62 75 77
F: +52 55 55 62 04 34
E: ventas@jcingenieriaycontrol.com
Netherlands
Kraus & Naimer B.V.
Wegtersweg 38-40, Postbus 199
7556 BR HENGELO (Ov.)
P: +31 74 291 9441
F: +31 74 291 98380
E: sales-nl@krausnaimer.com
New ZealandKraus & Naimer Ltd.
42 Miramar Avenue, WELLINGTON 6022
P. O. Box 15-009, WELLINGTON 6243
P: + 64 0800 736 522
E: sales-nz@krausnaimer.com
NorwayKraus & Naimer AB Avd. Norge
Postboks 27 Vollebekk
0516 Oslo
P: +47 22 64 44 20
E: sales-no@krausnaimer.com

PolandASTAT LOGISTYKA SP. Z O.O.
Dąbrowskiego 441
60451 POZNAŃ
P: +48 61 849 80 89
E: k.swiderski@astat.pl
Portugal
ELECTRICOL-DAMAS, FERREIRA & DAMASCENO, LDA.
Apartado 1063, S. Ant. Cavaleiros
2670 LOURES
P: +351 21 989 8939
F: +351 21 988 6464
E: electricol@electricol.pt
Singapore, India, Middle East – UAE
Kraus & Naimer Pte. Ltd.
115A, Commonwealth Drive#03-17/23
SINGAPORE 149 596
P: +65 6473 8166
E: sales-sg@krausnaimer.com
Slovenia
SCHRACK TECHNIK D.O.O.
Pameče 175
SI-2380 SLOVENJ GRADEC
P: +386 2 88 392 00
F: +386 2 88 434 71
E: d.goljat@schrack.si
Republic of South Africa
Kraus & Naimer Pty. Ltd.
7 Village Crescent, Linbro Village
Linbro Business Park, SANDTON 2065
P. O. Box 511, KELVIN 2054
P: +27 11 608 6060
E: sales-za@krausnaimer.com
Spain
Kraus & Naimer B.V.
P: +34 662 696 014
E: sales-es@krausnaimer.com
SwedenKraus & Naimer AB
Dr. Widerströms Gata 11, Hägersten
Box 42097, 126 14 STOCKHOLM
P: +46 8 97 00 80
E: sales-se@krausnaimer.com
Switzerland
AWAG Elektrotechnik AG
Sandbüelstraße 2CH-8604 VOLKETSWIL
P: +41 44 908 19 19
E: info@awag.ch
TurkeyKARDES ELEKTRIK SANAYI VE TICARET A.S.
Yassioren Mah. Hifa Sok. No: 434277 Arnavutkoy-Istanbul-Turkey
P: +90 212 624 92 04 118
F: +90 212 592 48 10
E: info@unalkardes.com.tr
USA
Kraus & Naimer Inc.
760 New Brunswick RoadSOMERSET, NJ 08873
P: +1 732 560 1240
E: sales-us@krausnaimer.com

Contact us:
www.krausnaimer.com