９２０ＭＨｚ帯 無線ユニット［MODBUSⓇタイプ］
SWL90-R4MD

MODBUSⓇインタフェース編

このたびは，当社の 920MHz 帯無線ユニット[MODBUSⓇタイプ](以下:無線ユニット)をお買い上げいただき誠にありがとうございます。
無線ユニットを正しく安全にお使いいただくため，ご使用前に本書をよくお読みいただき，
無線ユニットの機能･性能を十分ご理解のうえ，正しくご使用くださるようお願いいたします。

ご注意
1. 許可なく,本ユーザーズマニュアルの無断転載をしないでください。
2. 記載事項は,お断りなく変更することがありますので,ご了承ください。
3. 本製品は,国内電波法にもとづく仕様となっておりますので
日本国外では使用しないでください。

◆ 使用上のご注意
R●無線ユニットは無線通信で MODBUS○機器のデータを収集します。
有線接続と違い通信時間が長くなりますので、無線部の通信時間、リトライ時間などを考慮した
R

データ要求周期・タイムアウト時間を設計し、MODBUS○-RTU マスタ機器に設定しご使用ください。

●無線ユニットを設置する際は、加工機周辺を避けるように設置してください。
ノイズ等の影響で通信不良になる可能性がございます。

◆ ソフトウェアバージョン対応表
MODBUSⓇインタフェース機能のソフトウェア対応状況を記載いたします。
○：取得可能、-：取得不可
無線ユニット[SWL90-R4MD]
S/W Ver.
1.03 以前
2.00～2.01
3.00 以降取得可能データ
子局 I/O データ
温湿度センサ子局データ
パルスカウント子局データ

-

○
○

○
○

-

-

○

【注意事項】
S/W Ver1.00～1.03 のユニットでは、無線ユニットのデータ取得は行えません【参考】無線ユニットソフトウェアバージョン確認方法
無線ユニットのバージョン（ソフトウェアバージョン）はユニット上部の定格銘板で確認が可能です。

子局の定格銘板の「SW Ver.」が無線ユニットのソフトウェアバージョンとなります。

920MHz Wireless Unit

SWL90-R4MD
12/24VDC 1.4W
SERIAL
00651
SW Ver. 3.00

TYPE

MADE IN JAPAN

定格銘板

A-1

◆ 目次
使用上のご注意 ·································································································································································································· A-1
ソフトウェアバージョン対応表 ········································································································································································ A-1

第1章

概要 ······························································································································································································· 1-1

1.1.

はじめに·············································································································································································································· 1-2

1.2.

システム構成 ···································································································································································································· 1-2

1.3.

取得可能データ······························································································································································································· 1-2

第2章
2.1.

通信仕様 ····················································································································································································· 2-1

RS485 通信仕様 ····························································································································································································· 2-2

第3章

伝文仕様 ····················································································································································································· 3-1

3.1.

伝文構成 ············································································································································································································ 3-2

3.2.

シリアル伝送バイトのビット構成 ······························································································································································ 3-3

3.3.

伝送タイミング ·································································································································································································· 3-3

第4章

要求/応答構成·········································································································································································· 4-1

4.1.

ファンクション一覧 ·························································································································································································· 4-2

4.2.

コイル・DO 読み出し(01H) ·········································································································································································· 4-3

4.3.

入力ステータス・DI 読み出し(02H)·························································································································································· 4-4

4.4.

保持レジスタ読み出し(03H) ······································································································································································· 4-5

4.5.

コイル・DO１点書き込み(05H) ··································································································································································· 4-6

4.6.

複数コイル・DO への一括書き込み(0FH)············································································································································ 4-7

4.7.

複数レジスタへの一括書き込み(10H) ·················································································································································· 4-8

第5章
5.1.

エラー時の応答伝文 ······························································································································································· 5-1

エラー処理、エラー発生時の応答伝文 ················································································································································ 5-2

第6章

レジスタ仕様 ··············································································································································································· 6-1

6.1.

データアドレス一覧 ························································································································································································ 6-2

6.2.

コイル・DO レジスタ一覧(0X) ····································································································································································· 6-6

6.3.

入力・DI レジスタ一覧(1X) ·········································································································································································· 6-9

6.4.

保持レジスタ一覧(4X) ·················································································································································································· 6-12

A-1

第

第1章

1章

概要

1.1. はじめに ··························································································1-2
1.2. システム構成 ·················································································1-2
1.3. 取得可能なデータ ·······································································1-2

1-1

1.1.

はじめに
R

本仕様書は 920MHｚ帯無線ユニット SWL90-R4MD(Ver2.00 以降)の無線ユニットデータを MODBUS○-RTU 通信にて取得する方法を記載します。

1.2.

システム構成以下に無線ユニット親局と MODBUS○R 通信をおこなう場合のシステム構成例に関して記載します。
上位機器

無線ユニット

下位機器
Modbusスレーブ

無線親局

無線子局

MODBUSマスタ
他社MODBUS機器

ﾊﾟｿｺﾝ

子局1

USB/RS485
変換機

RS485
(Modbus）

USB

RS485
(Modbus）

GOT

EcoMonitorLight
I/O
(入力)

子局最大64台
接続可能

子局2

シーケンサ

RS485
(SC製プロトコル)

子局3

RS485
(SC製プロトコル)

入出力
増設ユニットI/O（パルス）
ｴｱｰ・ｶﾞｽ流量計(無線センサ)

1.3.

取得可能データR

MODBUS○通信を使用することにより、無線ユニットより以下のデータが取得可能となります。
品名

形名取得可能データ

親局

SWL90-R4MD

I/O、パルス

MODBUS 子局

SWL90-R4MD

I/O、パルス、増設ユニットデータ(I/O、AI)

温湿度センサ子局

SWL90-TH1(E)

温度、湿度

パルスカウント子局

SWL90-PL3

パルス、I/O

1-2

アナログ
増設ユニット

第

第2章

2章

通信仕様

2.1.通信仕様 ···························································································2-2

2-1

2.1.

RS485 通信仕様
無線ユニットの RS485 通信仕様について下表に示します。

RS485 通信仕様
項目

仕様

伝送信号

RS-485 2 線式半二重伝送

電気的仕様

RS-485 に準拠

通信プロトコル

MODBUS○-RTU

伝送モード

RTU(バイナリデータ転送)

伝送方式

調歩同期

接続形態

マルチドロップ

R

2400 bps/4800 bps/9600 bps/14400 bps/19200 bps/38400 bps/※

伝送速度57600 bps/76800 bps/115200 bps/230400 bps/
(デフォルト：19200bps)
ビット長

伝送
フォーマット※ストップビット
パリティ※※

送信データサイズ
最大通信距離R(MODBUS○機器-無線ユニット間)

8 / 7(デフォルト：8)

1 / 2(デフォルト：1)

EVEN / ODD / NONE

(デフォルト：EVEN)

299Byte1000m

内蔵終端抵抗120Ω 1/2W

推奨ケーブルSPEV(SB)-MPC-0.2×3P (三菱電線工業株式会社製)※：伝送速度、伝送フォーマットはパラメータで設定可能。

2-2

第

第3章

3章

伝文仕様

3.1. 伝文構成 ·························································································3-2
3.2. シリアル伝送バイトのビット構成 ············································3-3
3.3. 伝送タイミング ···············································································3-3

3-1

3.1.

伝文構成

以下に要求伝文・応答伝文の伝文フォーマットを示します。

アドレス

ファンクション

データ

1Byte

1Byte

可変長

項目名
アドレス

内容

CRC
Lo
Hi
2Byte

入力可能範囲各スレーブに割り付けられた
アドレス

備考
00H（ブロードキャスト）

01～FFHは非対応

読み出し/書き込みする
ファンクション

データを指定する為の01～03H、05H、0F～10H

詳細は 4 章参照

R○

MODBUS ファンクション
データ

読み出し/書き込みデータ

CRC

エラーチェックコード

8 ビット HEX データ
アドレス～データまでの1615

算出方法に関しては
2

16 ビット CRC(X +X +X +1)

下記参照。

<参考>CRC 算出方法
１）CRC レジスタに FFFFH を入れる。
２）メッセージの最初の 1 キャラクタ目と CRC レジスタ下位バイトの XOR をとり、
CRC レジスタに格納
３）CRC レジスタを 1 ビット右にシフトする。
４）CRC レジスタの LSB が 0 であれば 1 になるまで CRC レジスタを 1 ビット右にシフトする。
CRC レジスタの LSB が 1 であれば、1 ビット右にシフトした後、CRC レジスタと生成多項式 A001H の XOR をとり、CRC レジスタに格納
５）４）を 8 ビットシフトするまで繰り返す。
６）2 キャラクタ目以降も同様に２）～５）を繰り返し、メッセージのすべてのバイトについて適用する。
７）最後に CRC レジスタに残った値が CRC となる。

3-2

3.2.

シリアル伝送バイトのビット構成

1 バイトのビット構成について以下に示します。
1 バイトは以下の順(左（Start)から右（Stop））に送られます。
・パリティあり(奇数又は偶数)、ストップビット 1 の場合
Start

1

2

3

4

5

6

7

LSB

8

Parity

Stop

8

Stop

MSB

・パリティなし、ストップビット 2 の場合
Start

1

2

3

4

5

6

7

LSB

3.3.

Stop

MSB

伝送タイミング
3.5ｷｬﾗｸﾀ以上

前回リプライ

3.5ｷｬﾗｸﾀ以上
1s以下

1.5ｷｬﾗｸﾀ以下

アドレス

ファンクション

CRC(Lo)CRC(Hi)

リプライ

伝送タイミング
各伝送テキストの前後は 3.5 キャラクタ以上のアイドリングを設けてください。
またクエリー（要求）受信後から 1s 以下で，レスポンス（応答）を送信します。（下表参照）
各データ間は 1.5 キャラクタ以下の間隔で送信します。
データ間隔が 3.5 キャラクタ以上空いた場合，伝送終了し，それまで受け取ったデータを破棄し，新たなクエリーの先頭アドレスと判断します。
＜参考値＞
データ間隔
3.5 キャラクタ
伝送速度

1.5 キャラクタ

ｽﾄｯﾌﾟﾋﾞｯﾄ：1

ｽﾄｯﾌﾟﾋﾞｯﾄ：1

ｽﾄｯﾌﾟﾋﾞｯﾄ：1

ｽﾄｯﾌﾟﾋﾞｯﾄ：1

ﾊﾟﾘﾃｨ：1

ﾊﾟﾘﾃｨ：なし

ﾊﾟﾘﾃｨ：1

ﾊﾟﾘﾃｨ：なし

2400 bps

16.04ms

14.58ms

6.88ms6.25ms4800 bps

8.02ms7.29ms3.44ms3.13ms9600 bps

4.01ms3.65ms1.72ms1.56ms

19200 bps

2.00ms1.82ms0.86ms0.78ms

38400 bps

1.00ms0.91ms0.43ms0.39ms

クエリー送信時間

応答時間※

リプライ送信時間

TOTAL 時間

1 レジスタ(2 バイト)

2.28ms2.34ms2.10ms6.72ms

10 レジスタ(20 バイト)

2.28ms4.14ms7.26ms

13.68ms

40 レジスタ(80 バイト)

2.28ms

14.02ms

24.60ms

40.90ms

伝送時間（伝送速度：38400bps）
一括モニタ
レジスタ(バイト)数

ストップビット：1,パリティビット 1,また,データ間隔は 0 と設定。
※：受信完了から送信開始までに無線ユニットが要する時間となります。
上記データは、あくまでも参考値であり、伝送時間を保障するものではありません。

3-3

第

第4章

4章
要求/応答構成

4.1. ファンクション一覧 ·······································································4-2
4.2. コイル・DO 読み出し (01H) ······················································4-3
4.3. 入力ステータス・DI 読み出し(02H) ········································4-4
4.4. 保持レジスタ読み出し(03H) ·····················································4-5
4.5. コイル・DO１点書き込み(05H) ·················································4-6
4.6. 複数コイル・DO への一括書き込み(0FH) ··························4-7
4.7. 複数レジスタへの一括書き込み(10H) ·································4-8

4-1

4.1.

ファンクション一覧

無線ユニットにてサポートしているファンクション一覧を以下に記載します。
サポートしているファンクション一覧
ファンクションコード

機能備考
無線ユニット・増設ユニットの01(0x01)

DO、コイルの読み出し

02(0x02)

DI、入力ステータスの読み出し

03(0x03)

保持レジスタ読み出し

05(0x05)

DO、コイルへの 1 点書き込み

15(0x0F)

複数 DO、コイルへの一括書き込み

16(0x10)

複数保持レジスタへの一括書き込み

出力状態確認に使用
無線ユニット・増設ユニットの入力状態確認に使用
パルスカウント、センサデータ、
アナログ増設ユニットのデータ確認に使用
無線ユニット・増設ユニットの出力指令に使用
無線ユニット・増設ユニットの出力指令に使用
パルスカウントの初期値設定に使用※RS485 トンネル機能で使用する場合にサポートしている伝文は異なります。

4-2

4.2.

コイル・DO 読み出し(01H)

要求伝文構成

**H

01H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

スタートアドレス

Lo

Hi

要求レジスタ数

項目名

内容

アドレス

スレーブアドレス

Lo
CRC

備考
パラメータで設定(０～２４７(00H～F7H))

R○

ファンクションMODBUS ファンクションコード

コイル・DO 読み出しは「01H」固定

スタートアドレス

データ読み出し開始アドレス『６． レジスタ一覧』参照

要求レジスタ数要求を行うデータ数

最大 144

CRC

エラーチェックコード

算出方法は『３．１ 伝文構成』参照

応答伝文構成
**H

01H

**H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

項目名
バイト数

・・・

1バイト目 2バイト目 3バイト目

Lo

Hi

データ

CRC

内容

備考

応答データサイズ

要求レジスタ数以上となった場合は残りの1Byte で 8 点分のデータを表す。

データに 0 を格納する。

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例＞子局 1 の出力状態及び IO 増設ユニット 1 の出力状態(合計 32 点)を取得する場合
・要求伝文構成
スタートアドレスに子局 1 データの開始アドレス「0100H」、レジスタ数に「0020H」を指定する。

**H

01H

アドレス

ﾌｧﾝｸｼｮﾝ

01H

00H

00H

スタートアドレス

20H

Lo

レジスタ数

Hi
CRC

・応答伝文構成
応答バイト数として「04H」が応答され、ON/OFF データが 4Byte 内に 32 点分のデータが格納される。
Y
7

Y
6

Y
5

Y
4

Y
3

Y
2

Y
1

Y
0

0 0 1 1 0 1 0 0
3

**H

01H

04H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

00H

01H

Y
F

Y
E

Y
D

Y
B

Y
A

Y
9

Y
8

0 0 0 1 0 0 1 0

4

1

34H

12H

1バイト目 2バイト目 3バイト目 4バイト目

4-3

Y
C

2

Lo

Hi
CRC

4.3.

入力ステータス・DI 読み出し(02H)

要求伝文構成
**H

02H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

スタートアドレスLo

Lo

要求レジスタ数

項目名

内容

アドレス

スレーブアドレス

Hi
CRC

備考
パラメータで設定

R○

ファンクションMODBUS ファンクションコード

入力ステータス・DI 読み出しは「02h」固定

スタートアドレス

データ読み出し開始アドレス『６． レジスタ一覧』参照

要求レジスタ数要求を行うデータ数

最大 144

CRC

エラーチェックコード

算出方法は『３．１ 伝文構成』参照

応答伝文構成
**H

02H

**H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

項目名
バイト数

・・・

1バイト目 2バイト目 3バイト目

Lo

データ

Hi
CRC

内容

備考

応答データサイズ

要求レジスタ数以上となった場合は残りの1Byte で 8 点分のデータを表す。

データに 0 を格納する。

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例 1＞子局 1 のデータ及び IO 増設ユニット 1 の入力状態(32 点)を取得する場合
・要求伝文構成
スタートアドレスに子局 1 データの開始アドレス「0100H」、レジスタ数に「0020H」を指定する。

**H

02H

アドレス

ﾌｧﾝｸｼｮﾝ

01H

00H

00H

スタートアドレス

20H

Lo

レジスタ数

Hi
CRC

・応答伝文構成
応答バイト数として「04H」が応答され、ON/OFF データが 4Byte 内に 32 点分のデータが格納される。
X
7

X
6

X
5

X
4

X
3

X
2

X
1

X
0

0 0 1 1 0 1 0 0
3

**H

02H

04H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

00H

01H

X
F

X
E

X
D

X
B

X
A

X
9

X
8

0 0 0 1 0 0 1 0

4

1

34H

12H

1バイト目 2バイト目 3バイト目 4バイト目

4-4

X
C

2

Lo

Hi
CRC

4.4.

保持レジスタ読み出し(03H)

要求伝文構成

**H

03H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

スタートアドレス

Lo

Lo

Hi

レジスタ数

CRC

項目名

内容

備考

アドレス

スレーブアドレスファンクションMODBUS○ファンクションコード

保持レジスタ読み出しは「03H」固定

スタートアドレス

データ読み出し開始アドレス『６． レジスタ一覧』参照

要求レジスタ数

読み込みデータ数

最大 125

CRC

エラーチェックコード

算出方法は『３．１ 伝文構成』参照

パラメータで設定

R

応答伝文構成
**H

03H

**H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

Hi

Lo

Hi

データ1

項目名

内容

バイト数

応答データサイズ

Lo

・・・

Lo

データ2

Hi
CRC

備考

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例 1＞温湿度センサ子局 1 のデータ(4 データ)を取得する場合
・要求伝文構成
スタートアドレスに温湿度センサ子局 1 データの開始アドレス「0010H」)、レジスタ数に「0004H」を指定する。

**H

03H

アドレス

ﾌｧﾝｸｼｮﾝ

00H

10H

00H

スタートアドレス

04H

レジスタ数

Lo

Hi
CRC

・応答伝文構成
応答バイト数として「08H」が応答され、データが 8Byte(4 データ分)格納される。
**H

03H

08H

アドレス

ﾌｧﾝｸｼｮﾝ

バイト数

01H

1BH

データ1

02H

14H

データ2

4-5

00H

00H

データ3

00H

00H

データ4

Lo

Hi
CRC

4.5.

コイル・DO１点書き込み(05H)

要求伝文構成

**H

05H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

出力アドレス

Lo

Lo

Hi

出力データ

項目名

内容

アドレス

スレーブアドレス

CRC

備考
パラメータで設定

R○

ファンクションMODBUS ファンクションコード

コイル・DO1 点書き込みは「05H」固定

出力アドレス

出力先のコイル・DO アドレス

『６． レジスタ一覧』参照

出力データ

コイル・DO に書き込む値

CRC

エラーチェックコード

FF00H：ON
0000H:OFF
算出方法は『３．１ 伝文構成』参照

応答伝文構成要求伝文構成のエコーバックを応答とする。

**H

05H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

出力アドレス

Lo

Lo

出力データ

Hi
CRC

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例 1＞子局 1 に接続された入出力増設 1 台目の Y1 を ON する場合
・要求伝文構成
スタートアドレスに子局 1 の入出力増設 1 のアドレス「0111H」、
出力データに「FF00H」を指定する。

**H

05H

アドレス

ﾌｧﾝｸｼｮﾝ

01H

11H

出力アドレス

FFH

00H

Lo

出力データ

Hi
CRC

・応答伝文構成
要求伝文に送信した伝文が応答伝文として返ってきます。

**H

05H

アドレス

ﾌｧﾝｸｼｮﾝ

01H

11H

出力アドレス

FFH

00H

出力データ

4-6

Lo

Hi
CRC

4.6.

複数コイル・DO への一括書き込み(0FH)

要求伝文構成
Hi

**H

0FH

アドレス

ﾌｧﾝｸｼｮﾝ

Lo

Hi

スタートアドレス

**H

Lo

Hi

バイト数

レジスタ数

Lo

Hi

データ1

Lo

・・・

Lo

データ2

項目名

内容

備考

アドレス

スレーブアドレスパラメータで設定

ファンクションMODBUS○ファンクションコード

スタートアドレス

データ書き込み開始アドレス『６． レジスタ一覧』参照

要求レジスタ数要求を行うデータ数

最大 144

バイト数

1Byte で 8 点分のデータを表す。

CRC

エラーチェックコード

複数コイル・DO への一括書き込みは「0FH」固

R

定

最大 18
(要求レジスタ数を 8 で割った切り上げ値)
算出方法は『３．１ 伝文構成』参照

応答伝文構成
**H

0FH

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

スタートアドレス

Lo

Lo

Hi

レジスタ数

CRC

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例 1＞子局 2 の入出力増設 3 の Y4 を ON, Y5 を OFF する場合
・要求伝文構成
要求伝文を以下のように指定します。
項目名

設定値

内容

スタートアドレス

02 34H子局 2 入出力増設 3、Y4 のアドレス

要求レジスタ数

2

2 レジスタ(Y4 から 2 ビット)指定

バイト数

1

要求レジスタ数 2 を 8 で割った切り上げ値

データ 1

01H

Y4 に 1(ON)、Y5 に 0(OFF)を指定。
要求データ以外は 0 で詰める。
Y
5

Y
4

0 0 0 0 0 0 0 1
0

**H

0FH

アドレス

ﾌｧﾝｸｼｮﾝ

02H

34H

スタートアドレス

00H

02H

レジスタ数

1

01H

01H

バイト数

データ1

Lo

Hi
CRC

・応答伝文構成
要求伝文のファンクション～レジスタ数までのデータが応答伝文として返ります。
**H

0FH

アドレス

ﾌｧﾝｸｼｮﾝ

02H

34H

スタートアドレス

00H

Hi
CRC

02H

レジスタ数

Lo

Hi
CRC

4-7

4.7.

複数レジスタへの一括書き込み(10H)

要求伝文構成
Hi

**H

10H

アドレス

ﾌｧﾝｸｼｮﾝ

Lo

Hi

スタートアドレス

**H

Lo

Hi

バイト数

レジスタ数

Lo

Hi

データ1

Lo

・・・

Lo

データ2

Hi
CRC

項目名

内容

備考

アドレス

スレーブアドレスパラメータで設定

ファンクションMODBUS○ファンクションコード

スタートアドレス

データ書込み開始アドレス

要求レジスタ数要求を行うデータ数

最大 4

バイト数

書きこみバイト数

要求レジスタの 2 倍となります。

CRC

エラーチェックコード

算出方法は『３．１ 伝文構成』参照

複数レジスタへの一括書き込みはR「10H」固定
パルスカウントのみ指定可能『６． レジスタ一覧』参照

応答伝文構成
**H

10H

アドレス

ﾌｧﾝｸｼｮﾝ

Hi

Lo

Hi

スタートアドレス

Lo

Lo

レジスタ数

Hi
CRC

エラー時応答伝文構成(エラー時の応答伝文詳細に関しては「6.エラー処理、エラー発生時の応答伝文」参照。)

**H

81H

**H

アドレス

エラー
ﾌｧﾝｸｼｮﾝ

エラー
コード

Lo

Hi
CRC

＜例 1＞子局 3 のパルスカウント１を 12345678D（１０進）＝００BC614EH（16 進）に設定する場合
・要求伝文構成
要求伝文を以下のように指定します。
項目名

設定値

内容

スタートアドレス

03 00H子局 3 パルスカウント Ch1 下位のアドレス

要求レジスタ数

2

2 レジスタ(パルスカウント Ch1 下位、上位)を指定

バイト数

4

要求レジスタ数 4 に 2 をかけた値

データ 1

61 4EH

パルスカウント値 Ch1 の下位データを指定

データ 2

00 BCH

パルスカウント値 Ch1 の上位データを指定

**H

10H

アドレス

ﾌｧﾝｸｼｮﾝ

03H

00H

00H

スタートアドレス

A

バイト数

レジスタ数

61H

A

04H

02H

4EH

00H

BCH

Lo

データ1
データ2
パルスカウント１

HiCRC

・応答伝文構成
要求伝文のファンクション～レジスタ数までのデータが応答伝文として返ります。

**H

10H

アドレス

ﾌｧﾝｸｼｮﾝ

03H

00H

スタートアドレス

00H

04H

レジスタ数

4-8

Lo

Hi
CRC

第

第5章

5章
エラー時の応答伝文

5.1. エラー処理、エラー発生時の応答伝文·······························5-2

5-1

5.1.

エラー処理、エラー発生時の応答伝文

以下に無線ユニットへの伝文送信時にエラーとして判別する内容と発生時の処理を記載します。

エラー項目

エラー内容

処理

無線ユニット
エラー表示

UART 受信バッファの内容を①フレーミングエラー

読み出す前に次のデータを受信した場合②オーバーランエラー

１バイトデータ長が正しくない③パリティエラー

パリティビットが正しくない④CRC チェックエラー

エラー応答は返さず，受信待ち状態となる。

CRC エラーチェックコードがEF.03 表示 ※2

正しくない⑤イリーガルファンクション 01～03H、05H、

エラーコード 01 を

ファンクション

0F～10H 以外を受信

レスポンス⑥レジスタアドレス

要求レジスタアドレスがエラーコード 02 を

エラー

存在しない

レスポンス

データが許容範囲外⑦データ値エラー

設定項目ワード数と設定値データのワード数が不一致の場合⑧無線無応答

無応答で失敗⑨ACK 未受信

ACK 未受信で失敗⑩キャリアセンス発生

キャリアセンスで失敗⑪送信失敗

送信タイムアウトで失敗⑫送信経路なし

中継経路なしで失敗⑬モジュールビジー

モジュールビジーで失敗⑭データフラッシュ異常⑮モジュール通信失敗⑯モジュール異常

EF.01 表示なし

エラーコード 03 をレスポンス
エラーコード 80 をレスポンス
エラーコード 95 をレスポンス
エラーコード 96 をE1.**を表示 ※1
E1.**を表示 ※1
ST.01 を表示

レスポンス
エラーコード 97 をE1.**を表示 ※1

レスポンス
エラーコード 98 をレスポンス
エラーコード 9A をレスポンス

データフラッシュ異常で失敗

エラーコード 9B をレスポンス
エラーコード 9C を否定応答で失敗

レスポンス
エラーコード 9D をRF 異常で失敗

レスポンス※1：**は子局番号※2：Ver4.10 以降のユニットをご使用の場合は『ST.23』が表示されます。
※⑧～⑯は Ver4.10 以降のユニットでのみ返答する応答伝文です。
※上記エラーコードは 3 回連続発生で親局に表示されます。

5-2

E7.**を表示 ※1
AH.01 を表示
なし
なし
なし

エラーコードをレスポンスするエラーにつきましては、下記のレスポンスを応答します。
レスポンス構成
**H

**H

**H

Lo

Hi

ｴﾗｰﾌｧﾝｸｼｮﾝ
ｴﾗｰｺｰﾄﾞ
ｺｰﾄﾞ

アドレス

CRC

・エラーファンクションコード ：各ファンクションコードの最上位ビットに 1 をセット。
＜参考＞エラーファンクションコード例
ファンクションコード

エラーファンクションコード

01H

81H

05H

85H

10H

90H

＜例 1＞子局 3 の複数レジスタへの一括書込みがサポートされていないアドレスに対して書きこみする場合
要求伝文構成スタートアドレスに「0310H」(子局 3 の書きこみサポートしていないアドレス)、要求レジスタ数に１バイト数に 2 を指定する。

**H

10H

アドレス

ﾌｧﾝｸｼｮﾝ

03H

10H

スタートアドレス

00H

01H

レジスタ数

応答伝文構成
**H
アドレス

90H

02H

ｴﾗｰﾌｧﾝｸｼｮﾝ
ｴﾗｰｺｰﾄﾞ
ｺｰﾄﾞ

Lo

Hi
CRC

5-3

02H
バイト数

00H

00H

データ1

Lo

Hi
CRC

第

第6章

6章

レジスタ仕様6.1. データアドレス一覧 ·····································································6-2
6.2. コイル・DO レジスタ一覧(0X) ···················································6-3
6.3. 入力・DI レジスタ一覧(1X) ························································6-5
6.4. 入力・DI レジスタ一覧(1X) ························································6-7

6-1

6.1.

データアドレス一覧

以下に無線ユニットから取得可能なデータのデータアドレスについて記載します。
親局・子局ごとにアドレスが分れておりますので、データを取得したいユニットのアドレスをご指定ください。
(レジスタマップは各レジスタの先頭からのオフセット値となります。)
また、温湿度センサ子局は親局にセンサ番号順にデータが格納されております。

6.1.1. レジスタアドレスマップ概要
レジスタマップ(オフセット値)
No.

アドレス

内容

参照項

1

0000H ～ 00FFH

親局・温湿度センサ子局データ

6.1.2 項2

0100H ～ 40FFHMODBUS(R)子局 1～64 データ

6.1.3 項※1

3
44100H ～ 64FFH
6500H ～ 68FFH

メーカ領域
パルスカウントユニットデータ※1

6.1.4 項-5

6900H 以降未使用※2
※1：メーカ領域エリアに要求がを行った場合、応答を返しません。
※2：未使用領域に要求を行った場合、エラーコード「03.H」が応答されます。

注意） 温湿度センサ子局、パルスカウント子局のデータは上記子局 1 から子局 64 のアドレスには格納されません。
※1 パルスカウント子局のデータは S/W Ver3.00 以降のユニットで取得可能です。

！！！注意事項！！！
●パルスカウントユニットのコイル・DO レジスタは 1 台ずつ書込み/読出しを行ってください。
複数台まとめての書込み/読出しは行えません。

6-2

6.1.2. 親局・温湿度センサ子局レジスタアドレス一覧
レジスタマップ(オフセット値)
No.

アドレス

内容

No.

アドレス

1
2

内容

0000H ～ 000FH

親局ユニットデータ

320088H ～ 008BH

温湿度センサ 31 台目データ

0010H ～ 0013H

温湿度センサ 1 台目データ

33008CH ～ 008FH

温湿度センサ 32 台目データ

30014H ～ 0017H

温湿度センサ 2 台目データ

340090H ～ 0093H

温湿度センサ 33 台目データ

40018H ～ 001BH

温湿度センサ 3 台目データ

350094H ～ 0097H

温湿度センサ 34 台目データ

5001CH ～ 001FH

温湿度センサ 4 台目データ

360098H ～ 009BH

温湿度センサ 35 台目データ

60020H ～ 0023H

温湿度センサ 5 台目データ

37009CH ～ 009FH

温湿度センサ 36 台目データ

70024H ～ 0027H

温湿度センサ 6 台目データ

38

00A0H ～ 00A3H

温湿度センサ 37 台目データ

80028H ～ 002BH

温湿度センサ 7 台目データ

3900A4H ～ 00A7H

温湿度センサ 38 台目データ

9002CH ～ 002FH

温湿度センサ 8 台目データ

40

00A8H ～ 00ABH

温湿度センサ 39 台目データ

100030H ～ 0033H

温湿度センサ 9 台目データ

4100ACH ～ 00AFH

温湿度センサ 40 台目データ

110034H ～ 0037H

温湿度センサ 10 台目データ

4200B0H ～ 00B3H

温湿度センサ 41 台目データ

120038H ～ 003BH

温湿度センサ 11 台目データ

4300B4H ～ 00B7H

温湿度センサ 42 台目データ

13003CH ～ 003FH

温湿度センサ 12 台目データ

4400B8H ～ 00BBH

温湿度センサ 43 台目データ

140040H ～ 0043H

温湿度センサ 13 台目データ

45

00BCH ～ 00BFH

温湿度センサ 44 台目データ

150044H ～ 0047H

温湿度センサ 14 台目データ

46

00C0H ～ 00C3H

温湿度センサ 45 台目データ

160048H ～ 004BH

温湿度センサ 15 台目データ

47

00C4H ～ 00C7H

温湿度センサ 46 台目データ

17004CH ～ 004FH

温湿度センサ 16 台目データ

48

00C8H ～ 00CBH

温湿度センサ 47 台目データ

180050H ～ 0053H

温湿度センサ 17 台目データ

49

00CCH ～ 00CFH

温湿度センサ 48 台目データ

190054H ～ 0057H

温湿度センサ 18 台目データ

50

00D0H ～ 00D3H

温湿度センサ 49 台目データ

200058H ～ 005BH

温湿度センサ 19 台目データ

51

00D4H ～ 00D7H

温湿度センサ 50 台目データ

21005CH ～ 005FH

温湿度センサ 20 台目データ

52

00D8H ～ 00DBH

温湿度センサ 51 台目データ

220060H ～ 0063H

温湿度センサ 21 台目データ

53

00DCH ～ 00DFH

温湿度センサ 52 台目データ

230064H ～ 0067H

温湿度センサ 22 台目データ

54

00E0H ～ 00E3H

温湿度センサ 53 台目データ

240068H ～ 006BH

温湿度センサ 23 台目データ

55

00E4H ～ 00E7H

温湿度センサ 54 台目データ

25006CH ～ 006FH

温湿度センサ 24 台目データ

56

00E8H ～ 00EBH

温湿度センサ 55 台目データ

260070H ～ 0073H

温湿度センサ 25 台目データ

57

00ECH ～ 00EFH

温湿度センサ 56 台目データ

270074H ～ 0077H

温湿度センサ 26 台目データ

58

00F0H ～ 00F3H

温湿度センサ 57 台目データ

280078H ～ 007BH

温湿度センサ 27 台目データ

59

00F4H ～ 00F7H

温湿度センサ 58 台目データ

29

007CH ～ 007FH

温湿度センサ 28 台目データ

60

00F8H ～ 00FBH

温湿度センサ 59 台目データ

30

0080H ～ 0083H

温湿度センサ 29 台目データ

61

00FCH ～ 00FFH

温湿度センサ 60 台目データ

310084H ～ 0087H

温湿度センサ 30 台目データ

6-3

6.1.3. MODBUS(R)子局レジスタアドレス一覧
レジスタマップ(オフセット値)
No.

アドレス

内容

No.

アドレス

内容

1

0100H ～ 01FFH

子局 1 データ

33

2100H ～ 21FFH

子局 33 データ

20200H ～ 02FFH

子局 2 データ

34

2200H ～ 22FFH

子局 34 データ

3

0300H ～ 03FFH

子局 3 データ

35

2300H ～ 23FFH

子局 35 データ

4

0400H ～ 04FFH

子局 4 データ

36

2400H ～ 24FFH

子局 36 データ

50500H ～ 05FFH

子局 5 データ

37

2500H ～ 25FFH

子局 37 データ

6

0600H ～ 06FFH

子局 6 データ

38

2600H ～ 26FFH

子局 38 データ

70700H ～ 07FFH

子局 7 データ

39

2700H ～ 27FFH

子局 39 データ

80800H ～ 08FFH

子局 8 データ

40

2800H ～ 28FFH

子局 40 データ

90900H ～ 09FFH

子局 9 データ

41

2900H ～ 29FFH

子局 41 データ

10

0A00H ～ 0AFFH

子局 10 データ

42

2A00H ～ 2AFFH

子局 42 データ

110B00H ～ 0BFFH

子局 11 データ

43

2B00H ～ 2BFFH

子局 43 データ

120C00H ～ 0CFFH

子局 12 データ

44

2C00H ～ 2CFFH

子局 44 データ

13

0D00H ～ 0DFFH

子局 13 データ45

2D00H ～ 2DFFH

子局 45 データ

14

0E00H ～ 0EFFH

子局 14 データ46

2E00H ～ 2EFFH

子局 46 データ

15

0F00H ～ 0FFFH

子局 15 データ

47

2F00H ～ 2FFFH

子局 47 データ

16

1000H ～ 10FFH

子局 16 データ

48

3000H ～ 30FFH

子局 48 データ

17

1100H ～ 11FFH

子局 17 データ

49

3100H ～ 31FFH

子局 49 データ

18

1200H ～ 12FFH

子局 18 データ50

3200H ～ 32FFH

子局 50 データ

19

1300H ～ 13FFH

子局 19 データ

51

3300H ～ 33FFH

子局 51 データ

20

1400H ～ 14FFH

子局 20 データ

52

3400H ～ 34FFH

子局 52 データ

21

1500H ～ 15FFH

子局 21 データ

53

3500H ～ 35FFH

子局 53 データ

22

1600H ～ 16FFH

子局 22 データ

54

3600H ～ 36FFH

子局 54 データ

23

1700H ～ 17FFH

子局 23 データ

55

3700H ～ 37FFH

子局 55 データ

24

1800H ～ 18FFH

子局 24 データ

56

3800H ～ 38FFH

子局 56 データ

25

1900H ～ 19FFH

子局 25 データ

57

3900H ～ 39FFH

子局 57 データ

26

1A00H ～ 1AFFH

子局 26 データ

58

3A00H ～ 3AFFH

子局 58 データ27

1B00H ～ 1BFFH

子局 27 データ

59

3B00H ～ 3BFFH

子局 59 データ

28

1C00H ～ 1CFFH

子局 28 データ

60

3C00H ～ 3CFFH

子局 60 データ

29

1D00H ～ 1DFFH

子局 29 データ

61

3D00H ～ 3DFFH

子局 61 データ30

1E00H ～ 1EFFH

子局 30 データ

62

3E00H ～ 3EFFH

子局 62 データ

31

1F00H ～ 1FFFH

子局 31 データ

63

3F00H ～ 3FFFH

子局 63 データ

32

2000H ～ 20FFH

子局 32 データ

64

4000H ～ 40FFH

子局 64 データ6-4

6.1.4. パルスカウント子局レジスタアドレス一覧
レジスタマップ(オフセット値)
No.

アドレス

内容

No.

アドレス

内容

1

6500H ～ 650FH

パルスカウント 1 台目データ

33

6700H ～ 670FH

パルスカウント 33 台目データ

26510H ～ 651FH

パルスカウント 2 台目データ

346710H ～ 671FH

パルスカウント 34 台目データ

36520H ～ 652FH

パルスカウント 3 台目データ

356720H ～ 672FH

パルスカウント 35 台目データ

46530H ～ 653FH

パルスカウント 4 台目データ

366730H ～ 673FH

パルスカウント 36 台目データ

56540H ～ 654FH

パルスカウント 5 台目データ

376740H ～ 674FH

パルスカウント 37 台目データ

66550H ～ 655FH

パルスカウント 6 台目データ

386750H ～ 675FH

パルスカウント 38 台目データ

76560H ～ 656FH

パルスカウント 7 台目データ

396760H ～ 676FH

パルスカウント 39 台目データ

86570H ～ 657FH

パルスカウント 8 台目データ

40

6770H ～ 677FH

パルスカウント 40 台目データ

96580H ～ 658FH

パルスカウント 9 台目データ

416780H ～ 678FH

パルスカウント 41 台目データ

106590H ～ 659FH

パルスカウント 10 台目データ

426790H ～ 679FH

パルスカウント 42 台目データ

1165A0H ～ 65AFH

パルスカウント 11 台目データ

43

67A0H ～ 67AFH

パルスカウント 43 台目データ

1265B0H ～ 65BFH

パルスカウント 12 台目データ

44

67B0H ～ 67BFH

パルスカウント 44 台目データ

1365C0H ～ 65CFH

パルスカウント 13 台目データ

45

67C0H ～ 67CFH

パルスカウント 45 台目データ

14

65D0H ～ 65DFH

パルスカウント 14 台目データ

46

67D0H ～ 67DFH

パルスカウント 46 台目データ

15

65E0H ～ 65EFH

パルスカウント 15 台目データ

47

67E0H ～ 67EFH

パルスカウント 47 台目データ

16

65F0H ～ 65FFH

パルスカウント 16 台目データ

48

67F0H ～ 67FFH

パルスカウント 48 台目データ

176600H ～ 660FH

パルスカウント 17 台目データ

49

6800H ～ 680FH

パルスカウント 49 台目データ

186610H ～ 661FH

パルスカウント 18 台目データ

50

6810H ～ 681FH

パルスカウント 50 台目データ

196620H ～ 662FH

パルスカウント 19 台目データ

51

6820H ～ 682FH

パルスカウント 51 台目データ

206630H ～ 663FH

パルスカウント 20 台目データ

526830H ～ 683FH

パルスカウント 52 台目データ

216640H ～ 664FH

パルスカウント 21 台目データ

53

6840H ～ 684FH

パルスカウント 53 台目データ

226650H ～ 665FH

パルスカウント 22 台目データ

546850H ～ 685FH

パルスカウント 54 台目データ

236660H ～ 666FH

パルスカウント 23 台目データ

55

6860H ～ 686FH

パルスカウント 55 台目データ

246670H ～ 667FH

パルスカウント 24 台目データ

56

6870H ～ 687FH

パルスカウント 56 台目データ

256680H ～ 668FH

パルスカウント 25 台目データ

57

6880H ～ 688FH

パルスカウント 57 台目データ

266690H ～ 669FH

パルスカウント 26 台目データ

58

6890H ～ 689FH

パルスカウント 58 台目データ

27

66A0H ～ 66AFH

パルスカウント 27 台目データ

59

68A0H ～ 68AFH

パルスカウント 59 台目データ

28

66B0H ～ 66BFH

パルスカウント 28 台目データ

60

68B0H ～ 68BFH

パルスカウント 60 台目データ

29

66C0H ～ 66CFH

パルスカウント 29 台目データ

61

68C0H ～ 68CFH

パルスカウント 61 台目データ

30

66D0H ～ 66DFH

パルスカウント 30 台目データ

62

68D0H ～ 68DFH

パルスカウント 62 台目データ

31

66E0H ～ 66EFH

パルスカウント 31 台目データ

63

68E0H ～ 68EFH

パルスカウント 63 台目データ

32

66F0H ～ 66FFH

パルスカウント 32 台目データ

64

68F0H ～ 68FFH

パルスカウント 64 台目データ

6-5

6.2.

コイル・DO レジスタ一覧(0X)

６．２．１ 親局コイル・DO レジスタ一覧
レジスタアドレス
オフセット値
0000H(0)0001H(1)0002H(2)～8FH(143)

親局 Y0
親局 Y1

親局出力端子 Y0 の出力状態。
親局出力端子 Y1 の出力状態。

メーカ設定用メーカ設定用領域となります。

90H(144)～
FFH(255)

未使用

未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

データ名称

データ内容

６．２．２ 子局コイル・DO レジスタ一覧※：nn は子局番号(16 進数)、m は子局番号(10 進数)を示しています。
レジスタアドレス
オフセット値※

データ名称

データ内容

nn00H(256×m)
nn01H(256×m +1)
nn02H(256×m +2)～
nn0FH(256×m +15)
nn10H(256×m +16)
nｎ11H((256×m）+17)
nｎ12H((256×m）+18)
nｎ13H((256×m）+19)
nｎ14H((256×m）+20)
nｎ15H((256×m）+21)
nｎ16H((256×m）+22)
nｎ17H((256×m）+23)
nｎ18H((256×m）+24)
nｎ19H((256×m）+25)
nｎ1AH((256×m）+26)
nｎ1BH((256×m）+27)
nｎ1CH((256×m）+28)
nｎ1DH((256×m）+29)
nｎ1EH((256×m）+30)
nｎ1FH((256×m）+31)

子局 Y0
子局 Y1

子局出力端子 Y0 の出力状態。
子局出力端子 Y1 の出力状態。

メーカ設定用メーカ設定用領域となります。

入出力増設 1 台目 Y0
入出力増設 1 台目 Y1
入出力増設 1 台目 Y2
入出力増設 1 台目 Y3
入出力増設 1 台目 Y4
入出力増設 1 台目 Y5
入出力増設 1 台目 Y6
入出力増設 1 台目 Y7
入出力増設 1 台目 Y8
入出力増設 1 台目 Y9
入出力増設 1 台目 YA
入出力増設 1 台目 YB
入出力増設 1 台目 YC
入出力増設 1 台目 YD
入出力増設 1 台目 YE
入出力増設 1 台目 YF

子局 m に接続されている入出力増設ユニット
1 台目の各出力端子の出力状態。

Nn20H(256×m +32)～
nn7FH(256×m +127)

入出力増設 2～7 台目
Y0～YF

nn80H(256×m +32)～
nn8FH(256×m +47)

入出力増設 8 台目
Y0～YF

nｎ90H((256×n）+144)～nｎFFH((256×n）+255）

未使用

子局 m に接続されている入出力増設ユニット
2～7 の台目各出力端子の出力状態。
データの順番は子局 1 と同様に増設番号の小さい増設
ユニットのデータから順に並びます。
子局 m に接続されている入出力増設ユニット
8 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

注意）入出力増設ユニットは増設ユニットのうち、入力増設ユニットもしくは入出力増設ユニットと設定されたもの
から順に前詰で入出力増設ユニット台数が認識されます。
例）増設 1～4(P501～508)にアナログ入力増設ユニットを、増設 5(P505)に入出力増設ユニットを設定した場合、増設 5(P505)の入出力増設ユニットが「入出力増設ユニット 1 台目」となります。

6-6例）子局 3 のレジスタ一覧
子局 3 の場合、前ページで示した nn=03、m=3 となり、以下に示すようなレジスタマップとなります。
レジスタアドレス
オフセット値※

データ名称

データ内容

0300H(768)0301H(769)0302H(770)～
030FH(783)0310H(784)0311H(785)0312H(786)0313H(787)0314H(788)0315H(789)0316H(790)0317H(791)0318H(792)0319H(793)031AH(794)031BH(795)031CH(796)031DH(797)031EH(798)031FH(799)

子局 Y0
子局 Y1

子局出力端子 Y0 の出力状態。
子局出力端子 Y1 の出力状態。

メーカ設定用メーカ設定用領域となります。

入出力増設 1 台目 Y0
入出力増設 1 台目 Y1
入出力増設 1 台目 Y2
入出力増設 1 台目 Y3
入出力増設 1 台目 Y4
入出力増設 1 台目 Y5
入出力増設 1 台目 Y6
入出力増設 1 台目 Y7
入出力増設 1 台目 Y8
入出力増設 1 台目 Y9
入出力増設 1 台目 YA
入出力増設 1 台目 YB
入出力増設 1 台目 YC
入出力増設 1 台目 YD
入出力増設 1 台目 YE
入出力増設 1 台目 YF

子局 3 に接続されている入出力増設ユニット
1 台目の各出力端子の出力状態。

0320H(800)～
032FH(815)

入出力増設 2 台目
Y0～YF

0330H(816)～
033FH(831)

入出力増設 3 台目
Y0～YF

0340H(832)～
034FH(847)

入出力増設 4 台目
Y0～YF

0350H(848)～
035FH(863)

入出力増設 5 台目
Y0～YF

0360H(864)～
036FH(879)

入出力増設 6 台目
Y0～YF

0370H(880)～
037FH(895)

入出力増設 7 台目
Y0～YF

0380H(896)～
038FH(911)

入出力増設 8 台目
Y0～YF

0390H(912)～
03FFH(1023)

未使用

子局 3 に接続されている入出力増設ユニット
2 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
3 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
4 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
5 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
6 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
7 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
8 台目の各出力端子の出力状態。
データの順番は子局 1 と同様になります。
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

6-7

６．２．３ パルスカウント子局 コイル・DO レジスタ一覧※：nn は 16 進数、m は 10 進数でパルスカウントユニット番号を示しています。
レジスタアドレス
オフセット値※
6500H + (nn-1)0H(25856+ 16 × (m-1) )6500H + (nn-1)1H ～6500H + (nn-1)FH ～(25857+ 16 × (m-1) ～25871+ 16 × (m-2))

データ名称

データ内容

パルスカウントユニット Y0

パルスカウントユニット出力端子 Y0 の出力状態。

メーカ設定用メーカ設定用領域となります。

例）パルスカウント子局 2 台目、3 台目のレジスタ一覧
パルスカウント子局 2 台目、3 台目の場合、前ページで示した nn、m は以下の値となり、下表に示すようなレジスタマップとなります。
2 台目 ： nn = 02、m = 2
3 台目 ： nn = 03、m = 3
レジスタアドレス
オフセット値※

データ名称

データ内容

6510H(25872)

パルスカウントユニット 2 台目
Y0

パルスカウントユニット 2 台目の出力端子 Y0 の出力状態。

6511H(25873) ～651FH(25887)

メーカ設定用メーカ設定用領域となります。

6520H(25888)

パルスカウントユニット 3 台目
Y0

パルスカウントユニット 3 台目の出力端子 Y0 の出力状態。

6521H(25889) ～652FH(25903)

メーカ設定用メーカ設定用領域となります。

注意）パルスカウント子局のコイル・DO レジスタは複数のパルスカウント子局を跨いでの書込み/読出しはできません。
パルスカウント子局のコイル・DO レジスタに対し、書込み/読出しを行う場合は 1 台ずつ行ってください。

6-8

6.3.

入力・DI レジスタ一覧(1X)

６．３．１ 親局入力・DI レジスタ一覧
レジスタアドレス
オフセット値
0000H(0)0001H(1)0002H(2)～8FH(143)

親局 X0
親局 X1

親局入力端子 X0 の入力状態。
親局入力端子 X1 の入力状態。

メーカ設定用メーカ設定用領域となります。

90H(144)～
FFH(255)

未使用

未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

データ名称

データ内容

６．３．２ 子局入力・DI レジスタ一覧※：nn は子局番号(16 進数)、m は子局番号(10 進数)を示しています。
レジスタアドレス
オフセット値※
nn00H(256×m)
nn01H(256×m +1)
nn02H(256×m +2)～
nn07H(256×m +7)
nn08H(256×m +8)
nn09H(256×m +9)
nn0AH(256×m +10)
nn0BH(256×m +11)
nn0CH(256×m +12)
nn0DH(256×m +13)
nn0EH(256×m +14)
nn0FH(256×m +15)
nn10H(256×m +16)
nｎ11H((256×m）+17)
nｎ12H((256×m）+18)
nｎ13H((256×m）+19)
nｎ14H((256×m）+20)
nｎ15H((256×m）+21)
nｎ16H((256×m）+22)
nｎ17H((256×m）+23)
nｎ18H((256×m）+24)
nｎ19H((256×m）+25)
nｎ1AH((256×m）+26)
nｎ1BH((256×m）+27)
nｎ1CH((256×m）+28)
nｎ1DH((256×m）+29)
nｎ1EH((256×m）+30)
nｎ1FH((256×m）+31)

データ名称

データ内容

子局 X0
子局 X1

子局入力端子 X0 の入力状態。
子局入力端子 X1 の入力状態。

メーカ設定用メーカ設定用領域となります。

増設 1 通信エラー
増設 2 通信エラー
増設 3 通信エラー
増設 4 通信エラー
増設 5 通信エラー
増設 6 通信エラー
増設 7 通信エラー
増設 8 通信エラー
入出力増設 1 台目 X0
入出力増設 1 台目 X1
入出力増設 1 台目 X2
入出力増設 1 台目 X3
入出力増設 1 台目 X4
入出力増設 1 台目 X5
入出力増設 1 台目 X6
入出力増設 1 台目 X7
入出力増設 1 台目 X8
入出力増設 1 台目 X9
入出力増設 1 台目 XA
入出力増設 1 台目 XB
入出力増設 1 台目 XC
入出力増設 1 台目 XD
入出力増設 1 台目 XE
入出力増設 1 台目 XF

Nn20H(256×m +32)～
Nn8FH(256×m +143)

入出力増設 2～8 台目
X0～XF

nｎ90H((256×n）+144)～nｎFFH((256×n）+255）

未使用

子局に接続されてる増設ユニットの通信エラーが格納されます。
増設番号は P500 系に登録されている順番になります。
（P501 が増設 1、P508 が増設 8 になります。）

子局 m に接続されている増設ユニット 1 の各入力端子の入力状態。

子局 m に接続されている増設ユニット 2～8 の各入力端子の入力状態。
データの順番は入出力増設 1 台目と同様に増設番号の小さい増設ユニットのデータから順に並びます。
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

6-9

例）子局 3 のレジスタ一覧
子局 3 の場合、前ページで示した nn=03、m=3 となり、以下に示すようなレジスタマップとなります。
レジスタアドレス
オフセット値※
0300H(768)0301H(769)0302H(770)～
0308H(775)0308H(776)0309H(777)030AH(778)030BH(779)030CH(780)030DH(781)030EH(782)030FH(783)0310H(784)0311H(785)0312H(786)0313H(787)0314H(788)0315H(789)0316H(790)0317H(791)0318H(792)0319H(793)031AH(794)031BH(795)031CH(796)031DH(797)031EH(798)031FH(799)

データ名称

データ内容

子局 X0
子局 X1

子局入力端子 X0 の入力状態。
子局入力端子 X1 の入力状態。

メーカ設定用メーカ設定用領域となります。

増設 1 通信エラー
増設 2 通信エラー
増設 3 通信エラー
増設 4 通信エラー
増設 5 通信エラー
増設 6 通信エラー
増設 7 通信エラー
増設 8 通信エラー
入出力増設 1 台目 X0
入出力増設 1 台目 X1
入出力増設 1 台目 X2
入出力増設 1 台目 X3
入出力増設 1 台目 X4
入出力増設 1 台目 X5
入出力増設 1 台目 X6
入出力増設 1 台目 X7
入出力増設 1 台目 X8
入出力増設 1 台目 X9
入出力増設 1 台目 XA
入出力増設 1 台目 XB
入出力増設 1 台目 XC
入出力増設 1 台目 XD
入出力増設 1 台目 XE
入出力増設 1 台目 XF

0320H(800)～
032FH(815)

入出力増設 2 台目
X0～XF

0330H(816)～
033FH(831)

入出力増設 3 台目
X0～XF

0340H(832)～
034FH(847)

入出力増設 4 台目
X0～XF

0350H(848)～
035FH(863)

入出力増設 5 台目
X0～XF

0360H(864)～
036FH(879)

入出力増設 6 台目
X0～XF

0370H(880)～
037FH(895)

入出力増設 7 台目
X0～XF

0380H(896)～
038FH(911)

入出力増設 8 台目
X0～XF

0390H(912)～
03FFH(1023)

未使用

子局に接続されてる増設ユニットの通信エラーが格納されます。
増設番号は P500 系に登録されている順番になります。
（P501 が増設 1、P508 が増設 8 になります。）

子局 3 に接続されている入出力増設ユニット
1 台目の各入力端子の入力状態。

子局 3 に接続されている入出力増設ユニット
2 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
3 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
4 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
5 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
6 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている入出力増設ユニット
7 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
子局 3 に接続されている増設ユニット 8 台目の各入力端子の入力状態。
データの順番は子局 1 と同様になります。
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

6-10

６．３．３ パルスカウント子局 入力・DI レジスタ一覧※：nn は 16 進数、m は 10 進数でパルスカウントユニット番号を示しています。
レジスタアドレス
オフセット値※
6500H + (nn-1)0H(25856+ 16 × (m-1) )6500H + (nn-1)1H(25857+ 16 × (m-1) )6500H + (nn-1)2H(25858+ 16 × (m-1) )6500H + (nn-1)3H ～6500H + (nn-1)FH(25859+ 16 × (m-1) ～25871+ 16 × (m-2))

データ名称

データ内容

パルスカウントユニット X0

パルスカウントユニット出力端子 X0 の出力状態。

パルスカウントユニット X1

パルスカウントユニット出力端子 X1 の出力状態。

パルスカウントユニット X2

パルスカウントユニット出力端子 X2 の出力状態。

メーカ設定用メーカ設定用領域となります。

【注意事項】
パルスカウント機能を使用している場合、本アドレスは不定となりますので使用しないでください。
Ver1.10 以降にてパルスカウントと DI を混在して使用する場合、システム領域の DI 情報をご使用ください。
システム領域の DI 情報に関しては『６．４．４ パルスカウント子局入力レジスタ一覧』参照

例）パルスカウント子局 2 台目、3 台目のレジスタ一覧
パルスカウント子局 2 台目、3 台目の場合、前ページで示した nn、m は以下の値となり、下表に示すようなレジスタマップとなります。
2 台目 ： nn = 02、m = 2
3 台目 ： nn = 03、m = 3
レジスタアドレス
オフセット値※
6510H(25872 )6511H(25873 )
6512H(25874 )
6513H ～651FH(25875 ～ 25887)
6520H(25888 )6521H(25889 )6522H(25890 )6523H ～ 652FH(25891 ～ 25903)

データ名称

データ内容

パルスカウントユニット 2 台目
X0
パルスカウントユニット 2 台目
X1
パルスカウントユニット 2 台目
X2

パルスカウントユニット 2 台目
出力端子 X0 の出力状態。
パルスカウントユニット 2 台目
出力端子 X1 の出力状態。
パルスカウントユニット 2 台目
出力端子 X2 の出力状態。

メーカ設定用メーカ設定用領域となります。

パルスカウントユニット 3 台目
X0
パルスカウントユニット 3 台目
X1
パルスカウントユニット 3 台目
X2

パルスカウントユニット 3 台目
出力端子 X0 の出力状態。
パルスカウントユニット 3 台目
出力端子 X1 の出力状態。
パルスカウントユニット 3 台目
出力端子 X2 の出力状態。

メーカ設定用メーカ設定用領域となります。

6-11

6.4.

保持レジスタ一覧(4X)

６．４．１ 親局保持レジスタ一覧
レジスタアドレス
オフセット値
0000H(0)0001H(1)0002H(2)0003H(3)0004H(4)～000FH(15)親局パルスカウント 1Ch 下位
親局パルスカウント 1Ch 上位
親局パルスカウント 2Ch 下位
親局パルスカウント 2Ch 上位
メーカ設定用

0010H(16)

温湿度センサ子局 1 台目 温度

0011H(17)

温湿度センサ子局 1 台目 湿度

0012H(18)予備
温湿度センサ子局 1 台目
システムデータ
温湿度センサ子局 2 台目データ
温湿度センサ子局 3 台目データ

0013H(19)0014H(20)～0017H(23)0018H(24)～001BH(27)

データ名称

データ内容

001CH(28) ～ 00F7H(247)（温湿度センサ子局 4 台目～
58 台目データ）

00F8H(248)～00FBH(251)00FCH(252)～00FFH(255)

温湿度センサ子局 59 台目データ
温湿度センサ子局 60 台目データ

親局にてカウントしているパルスカウント値
メーカ設定用領域となります。
温湿度センサ子局 1 台目の温度データ
小数点 1 桁を含むデータが格納されます。
例) 235 ⇒ 23.5℃
温湿度センサ子局 1 台目の湿度データ
小数点 1 桁を含むデータが格納されます。
例) 485 ⇒ 48.5%
温湿度センサ子局 1 台目の電池残量や通信エラー。
(6.4.2 センサユニットシステムデータ詳細参照)

温湿度センサ子局の温度、湿度、システムデータが格納されます。
データの並びは温湿度センサ子局 1 台目と同様の並びとなります。
例）0034H には温湿度センサ子局 10 の温度データが0035H には温湿度センサ子局 10 の湿度データが格納されます。

注意）温湿度センサ子局は親局に「温湿度センサ子局」(SWL90-TH1(E))と設定されたものから順に前詰で台数が認識されます。
R例）子局 1～4 に SWL90-R4MD(MODBUS○タイプ)を、子局 5 に SWL90-TH1（温湿度センサ子局）を設定した場合
子局 5 の温湿度センサ子局はセンサ 1 台目となります。
温湿度データやシステムデータはセンサ 1 台目のアドレスに格納され、子局 5 のアドレスには格納されません
のでご注意ください。

６．４．２ 温湿度センサ子局システムデータ詳細
温湿度センサ子局の「システムデータ」の詳細を以下に記載します。
レジスタアドレス
オフセット値b0(0 ビット目)

b1(1 ビット目)

b2(2 ビット目)～
b3(3 ビット目)～
b7(7 ビット目)
b8(8 ビット目)
b9(9 ビット目)～
bF(F ビット目)

データ名称

データ内容
電池駆動の場合、電池残量が格納されます。
内容により、電池レベルが分ります。
0 ビット目 ON、1 ビット目 ON ：電池残量あり0 ビット目 ON、1 ビット目 OFF：
電池残量低下※ 電池交換をお願いいたします。
中継局設定で運用されていることを示します。
（温湿度センサ子局本体のディップスイッチで設定）

電池残量

中継局設定
メーカ設定用メーカ設定用領域となります。

通信異常

通信タイムアウト時、本ビットが ON します。

メーカ設定用メーカ設定用領域となります。

6-12

６．４．３ 子局入力レジスタ一覧※：nn は子局番号(16 進数)、m は子局番号(10 進数)を示しています。
レジスタアドレス
オフセット値※
nn00H(256×m)
nn01H((256×m) +1)
nn02H((256×m) +2)
nn03H((256×m) +3)
nn04H((256×m) +4)～
nn0FH((256×m) +15)
nn10H((256×m) +16)
nｎ11H((256×m）+17)
nｎ12H((256×m）+18)
nｎ13H((256×m）+19)

データ名称

データ内容

子局パルスカウント 1Ch 下位
子局パルスカウント 1Ch 上位
子局パルスカウント 2Ch 下位
子局パルスカウント 2Ch 上位

子局にてカウントしているパルスカウント値

メーカ設定用メーカ設定用領域となります。

アナログ増設 1 台目
入力 Ch1
アナログ増設 1 台目
入力 Ch2
アナログ増設 1 台目
入力 Ch3
アナログ増設 1 台目
入力 Ch4

子局 m に接続されているアナログ増設ユニット
1 台目の各入力端子の入力状態

nｎ14H((256×m）+20)～
nｎ2FH((256×m）+47)

アナログ増設 2～8 台目
入力 Ch1～4

nｎ30H((256×n）+48)～nｎFFH((256×n）+255）

未使用

子局 m に接続されているアナログ増設ユニット
2～8 台目の各入力端子の入力状態
データの順番はアナログ増設 1 台目と同様に増設番号の小さい増設ユニットのデータから順に並びます。
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

6-13

例）子局２７のレジスタ一覧
子局２７の場合、前ページで示した nn=１B、m=27 となり、以下に示すようなレジスタマップとなります。
レジスタアドレス
オフセット値※
1B00H(6912)
1B01H(6913)
1B02H(6914)
1B03H(6915)
1B04H(6916)～
1B0FH(6927)
1B10H(6928)
1B11H(6929)
1B12H(6930)
1B13H(6931)
1B14H(6932)～
1B17H(6935)
1B18H(6936)～
1B1BH(6939)
1B1CH(6940)～
1B1FH(6943)
1B20H(6944)～
1B23H(6947)
1B24H(6948)～
1B27H(6951)
1B28H(6952)～
1B2BH(6955)
1B2CH(6956)～
1B2FH(6959)
1B30H(6960)～1BFFH(7176）

データ名称

データ内容

子局パルスカウント 1Ch 下位
子局パルスカウント 1Ch 上位
子局パルスカウント 2Ch 下位
子局パルスカウント 2Ch 上位

子局にてカウントしているパルスカウント値

メーカ設定用メーカ設定用領域となります。

アナログ増設 1 台目
入力 Ch1
アナログ増設 1 台目
入力 Ch2
アナログ増設 1 台目
入力 Ch3
アナログ増設 1 台目
入力 Ch4アナログ増設 2 台目
入力 Ch1～4
アナログ増設 3 台目
入力 Ch1～4
アナログ増設 4 台目
入力 Ch1～4
アナログ増設 5 台目
入力 Ch1～4
アナログ増設 6 台目
入力 Ch1～4
アナログ増設 7 台目
入力 Ch1～4
アナログ増設 8 台目
入力 Ch1～4

子局 27 に接続されているアナログ増設ユニット
1 台目の各入力端子の入力状態

子局 27 に接続されているアナログ増設ユニット
2 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
3 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
4 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
5 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
6 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
7 台目の各入力端子の入力状態
子局 27 に接続されているアナログ増設ユニット
8 台目の各入力端子の入力状態
未使用領域となります。
このレジスタを読み出すとデータ値エラー(エラーコード：03)が応答されます。

未使用

6-14

６．４．４ パルスカウント子局入力レジスタ一覧
レジスタアドレス
オフセット値※
6500H + (nn-1)0H(25856+ 16 × (m-1) )6500H + (nn-1)1H(25857+ 16 × (m-1) )6500H + (nn-1)2H(25858+ 16 × (m-1) )6500H + (nn-1)3H(25859+ 16 × (m-1) )6500H + (nn-1)4H(25860+ 16 × (m-1) )6500H + (nn-1)5H(25861+ 16 × (m-1) )6500H + (nn-1)6H ～6500H + (nn-1)FH(25862 + 16 × (m-1) ～25870 + 16 × (m-2))
6500H + (nn-1)FH(25871+ 16 × (m-1) )

データ名称

データ内容

パルスカウント子局
パルスカウント 1Ch 下位
パルスカウント子局
パルスカウント 1Ch 上位
パルスカウント子局
パルスカウント 2Ch 下位
パルスカウント子局
パルスカウント 2Ch 上位
パルスカウント子局
パルスカウント 3Ch 下位
パルスカウント子局
パルスカウント 3Ch 上位

子局にてカウントしているパルスカウント値

メーカ設定用メーカ設定用領域となります。

システムデータ

温湿度センサ子局 1 台目の電池残量や通信エラー。
(下表 パルスカウント子局システムデータ詳細参照)

注意）パルスカウント子局はパルスカウント子局と設定されたものから順に前詰で台数が認識されます。
R例）子局 1～4 に SWL90-R4MD(MODBUS○タイプ)を、子局 5 に SWL90-PL3（パルスカウント子局）を設定した場合、子局 5 がパルスカウント子局の 1 台目となります。
データはパルスカウント子局 1 台目のアドレスに格納され、子局 5 のアドレスには格納されませんのでご注意ください。

【注意事項】① パルスカウント子局の入力レジスタは先頭(パルスカウント 1Ch 下位)から読み出してください。
途中からの読み出しはできません。
② パルスカウント未使用チャンネル領域に不定値が入る可能性があります。
③ パルスカウント値に 8 桁(99999999)を超える値を書込んだ場合、異常な値が表示されます。
8 桁を超える値をパルスカウントのデバイスに書き込まないでください。
8 桁を超える値が書き込まれた状態でパルスを受けるとカウントが 0 になります。

6-15

パルスカウント子局のシステムデータのアドレス割付けとデータ内容を下記に記載します。
パルスカウント子局のシステム領域内訳
レジスタアドレス
オフセット値

データ名称
Ver1.02 以前
Ver1.10 以降

電池残量や AC アダプタ動作等、電源の状態が格納されます。
状態に関しては下表をご参照ください。

b0(0 ビット目)

電源状態
b2
1

b1(1 ビット目)

電源状態

変更なし

通信異常

メーカ設定用ユニット X0
ユニット X1
ユニット X2
メーカ設定用
変更なし

メーカ設定用

変更なし

メーカ設定用

電池残量
b1
b0
― ※
1

1

0

1

0

0

0

0

b2(2 ビット目)

b3(3 ビット目)
b4(4 ビット目)
b5(5 ビット目)
b6(6 ビット目)
b7(7 ビット目)
b8(8 ビット目)
b9(9 ビット目)～
bF(F ビット目)

データ内容

内容
外部電源供給で動作しています。
電池供給で動作しています。
電池残量あり(10～100%)
電池残量低下(10%未満)※ 電池交換の準備をお願いいたします。
通信未接続/通信異常時※外部電源供給での運用中は電池供給は行われていない為
電池残量は確認できません。
電源のバックアップ(停電時等)として電池を使用される際に電池残量を確認したい場合は定期的に外部電源供給を切り離し、電池残量ビットの状態を確認してください。
(b2 が「0」の状態での b1,b0 の状態を確認してください。)
メーカ設定用領域となります。
Ver1.02 以前：メーカ設定用領域となります。
Ver1.10 以降：入力端子の ON/OFF 情報
メーカ設定用領域となります。
通信タイムアウト時、本ビットが ON します。
メーカ設定用領域となります。

【注意事項】① 親局パラメータのクリア/ホールド設定をクリア又はビットホールド/ワードクリア(P110 = 0 又は 3)に設定した場合、本システム領域の値もクリアされます。
② エラー発生時はユニット X0～X2 の値は不定となりますので、エラー発生時に停止する必要がある場合、8 ビット目の通信異常と合わせてご使用ください。

6-16例）パルスカウント子局 2 台目、3 台目のレジスタ一覧
パルスカウント子局 2 台目、3 台目の場合、前ページで示した nn、m は以下の値となり、下表に示すようなレジスタマップとなります。
2 台目 ： nn = 02、m = 2
3 台目 ： nn = 03、m = 3
レジスタアドレス
オフセット値※
6510H(25872 )6511H(25873 )
6512H(25874 )
6513H(25875 )6514H(25876 )
6515H(25877 )6513H ～651EH(25875 ～ 25886)
651FH (25887)
6520H(25888 )6521H(25889 )6522H(25890 )6523H(25891 )6524H(25892 )6525H(25893 )

データ名称

データ内容

パルスカウントユニット 2 台目
パルスカウント Ch1 下位
パルスカウントユニット 2 台目
パルスカウント Ch1 上位
パルスカウントユニット 2 台目
パルスカウント Ch2 下位
パルスカウントユニット 2 台目
パルスカウント Ch3 上位
パルスカウントユニット 2 台目
パルスカウント Ch3 下位
パルスカウントユニット 2 台目
パルスカウント Ch3 上位

パルスカウントユニット 2 台目
パルスカウント値 Ch1 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch1 上位
パルスカウントユニット 2 台目
パルスカウント値 Ch2 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch2 上位
パルスカウントユニット 2 台目
パルスカウント値 Ch3 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch3 上位

メーカ設定用メーカ設定用領域となります。

パルスカウントユニット 3 台目
システムデータ
パルスカウントユニット 3 台目
パルスカウント Ch1 下位
パルスカウントユニット 3 台目
パルスカウント Ch1 上位
パルスカウントユニット 3 台目
パルスカウント Ch2 下位
パルスカウントユニット 3 台目
パルスカウント Ch3 上位
パルスカウントユニット 3 台目
パルスカウント Ch3 下位
パルスカウントユニット 3 台目
パルスカウント Ch3 上位

パルスカウントユニット 2 台目のシステムデータ
パルスカウントユニット 2 台目
パルスカウント値 Ch1 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch1 上位
パルスカウントユニット 2 台目
パルスカウント値 Ch2 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch2 上位
パルスカウントユニット 2 台目
パルスカウント値 Ch3 下位。
パルスカウントユニット 2 台目
パルスカウント値 Ch3 上位

6523H ～652EH(25894 ～ 25902)

メーカ設定用メーカ設定用領域となります。

652FH (25903)

パルスカウントユニット 3 台目
システムデータ

パルスカウントユニット 2 台目のシステムデータ

6-17

製品仕様の変更
カタログ,仕様書,技術資料などに記載されている仕様は,お断りなしに変更することがあります。

製品の適用について■使用条件
当社製品をご使用される場合は,万一,故障,不具合などが発生した場合でも重大な事故にいたらない用途であること,バックアップなどの対策が実施されていることをご使用の条件とさせていただきます。
■適用の除外など(1)当社製品は,一般工業などへの用途を対象として設計・製造されています。原子力発電所およびその他発電所,鉄道
や航空などの公共交通機関といった公共への影響が大きい用途や車両設備医用機械,娯楽機械,安全装置,焼却設
備,および行政機関や個別業界の規制に従う設備への使 s 用で,特別品質保証体制をご要求になる用途には,適用を除外させていただきます。
(2)人命や財産に大きな影響が予測され,安全面や制御システムにとくに高信頼性が要求される用途には適用を除外させていただきます。
(3)ただし,上記の用途であっても,用途を限定して特別な品質をご要求にならないことをお客様にご承認いただいた場合には,適用可能とさせていただきます。

その他
上記の記載内容は,日本国内での取引および使用を前提としております。

◆ 製品のお問い合わせ
各製品に関するお問い合わせ先は、当社ホームページにてご確認ください。
www.melsc.co.jp/business/introduction/inquiry.htmlⓇ

MODBUS は Schneider Electric SA の登録商標です。

・お断りなしに内容を変更することがありますのでご了承ください。
・許可なく、本ユーザーズマニュアルの無断転載をしないでください。
X903140905H

２０２３年５月作成

6-18