Explosion-proof type LED Floodlight 【LZIP795A】

Replacement LED Floodlight for Mercury 400W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 77.5W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED77.5W (LZIP795A)x1pc
Subject

Mercury400W x1pc

LED (LZIP795A) x1pc

Power Consumption (W)LED (LZIP795A) x1pc

77.5

Mercury400W x1pc

425
0 100 200 300 400 500

Lamp Life (H)LED (LZIP795A) x1pc

60,000Mercury400W x1pc

12,0000Distribution
Curve

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°

Quantity

1pc

Equivalent

1pc

Average
Illuminance

3.4Lx

2.3 Times

7.9LxPowerConsumption

425W

82% Down

77.5W

Lamp
Life

12,000h

5 Times

60,000hLine-upModel No.LZIP795A

Floodlight type

9.6Kg

Illuminance Level = 2.3 times brighter than Mercury 400W

Explosion-proof type LED Floodlight 【LZIP605A】

Replacement LED Floodlight for Mercury 400W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 59W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED59W (LZIP605A)x1pc
Subject

Mercury400W x1pc

LED (LZIP605A) x1pc

Power Consumption (W)LED (LZIP605A) x1pc

59

Mercury400W x1pc

425
0 100 200 300 400 500

Lamp Life (H)LED (LZIP605A) x1pc

60,000Mercury400W x1pc

12,0000Distribution
Curve

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°

Quantity

1pc

Equivalent

1pc

Average
Illuminance

3.4Lx

1.7 Times

5.9Lx

PowerConsumption

425W

86% Down

59W

Lamp
Life

12,000h

5 Times

60,000hLine-upModel No.LZIP605A

Floodlight type

9.6Kg

Illuminance Level = 1.7 times brighter than Mercury 400W

Explosion-proof type LED Floodlight 【LZIP375A】

Replacement LED Floodlight for Mercury 400W
【Specifications】①Type of Protection : ExebmbⅡCT5Gb (Zone1), ExtbⅢCT85℃Db (Zone21)②Degree of Protection : IP65
③Correlated Color Temperature : 5,000K④Power Consumption : 36.5W⑤Lamp Life : 60,000h⑥Body Material : Aluminum die-cast⑦Optional Parts : Guard⑧Voltage : AC100-242V±6％⑨Ambient Temperature : -20℃～+50℃ with high temperature protection⑩Surge protection : 15kV
⑪Salt resistant paint (Urethane resin coating)●Warranty period of LED Lighting Fittings = 5 years●Made in Japan【1 Unit Comparison】 : Mercury400Wx1pc / LED36.5W (LZIP375A)x1pc
Subject

Mercury400W x1pc

LED (LZIP375A) x1pc

Power Consumption (W)LED (LZIP375A) x1pc

36.5

Mercury400W x1pc

425
0 100 200 300 400 500

Lamp Life (H)LED (LZIP375A) x1pc

60,000Mercury400W x1pc

12,0000Distribution
Curve

Calculation Condition
Lighting Quantity : 1pc
Area : 20mx40m
Lighting Height : 10m
Fitting Angle : 70°

Quantity

1pc

Equivalent

1pc

Average
Illuminance

3.4Lx

Equivalent

3.5Lx

PowerConsumption

425W

91% Down

36.5W

Lamp
Life

12,000h

5 Times

60,000hLine-upModel No.LZIP375A

Floodlight type

9.6Kg

Illuminance Level = Equivalent to Mercury 400W

20,00040,00060,00080,000