11E0200002A11

Instruction Manual
Dust Ignition proof type LED Lighting Fittings

To be conservedLKAB

Thank you very much for purchasing our LED lighting fittings.
Please read this instruction manual to use the product properly.
After installing the product, be sure to hand this manual over to the user of the product.
Prior to use

1) Prior to installing the fitting, check if the product is as per your order.
2) Check for a loose or damaged part due to an accident in transit, etc.

Performance1) The electrical characteristic data is given below (the figure in angle brackets < > in the Installation Type column is a sign placed at the end ofeach model code to represent the type of installation.)
Input
Type ofIP
Input Voltage
PowerModelInstallation Type(Frequency)
Consumption
Current
protection
ratingDirect mount<1>
LKAB07034
Pipe pendant<2>
Bracket<6>
LKAB07035
Stanchion
0.26-0.12A
25.5-26W<1,1H>
Special direct mount<1>
LKAB07031
Horizontal pole mount<4>
LKAB07032
Lamp house replacemen
100-242V AC
SDP-13IP65(50/60Hz)
Direct mount<1>
LKAB07024
Pipe pendant<2>
Bracket<6>
LKAB07025
Stanchion
0.19-0.08A
18-18.5W<1,1H>
Special direct mount<1>
LKAB07021
Horizontal pole mount<4>
LKAB07022
Lamp house replacemen2) Usable in hazardous areas where there may be deflagrative or flammable dust.
Names of the Components and Installation Method- Installation work should be done properly by a qualified electrician in accordance with the related laws and the instruction manual.
- For safety, Installation work should be done by at least two workers.
■ Direct Mount Type, Pipe Pendant Type, Bracket Type (Fig. 1: Example LKAB070341)
Fix the terminal box on a horizontal mounting surface securely with M6
4-φ holes for M6 olts
bolts or equivalent bolts.
NB: For the bracket type, fix it on a vertical mounting surface securely.
Suspension hook hole
Screw the pipe into the lamp house.
Cover gasket
Screw the terminal box cover into the pipe.
Terminal box
Lift the lamp house and hook the suspension hook onto the suspension
Terminal box cover
hook hole of the terminal box.
Suspension hook
After connection of the electric wires (white and black: power wires,
4-Cross recessed
hexagon bolts
green: grounding wire), remove the suspension hook and put it in thePipe
terminal box cover.
Lamp house
Fasten the terminal box and its cover with four cross recessed hexagon
3-Locking screws
bolts.
After adjusting the positions of the lamp house and terminal box,
tighten the three locking screws.
NB1: The pipe, locking screws and cross recessed hexagon blots should betightened securely. Otherwise, the lamp house might fall.
NB2: Caulk the threaded connections.
Fig. 1
NB3: For the bracket type, the lamp house may be installed within anangle range of 0° (down) to 45° (oblique). For the direct mount andPipe pendant type, The lamp house may be installed within an angle
range of 0° (down).
For the direct mount and Pipe pendant type, The lamp house may
be installed within an angle range of 0° (down).
--■ Stanchion Type (Fig. 2: Example LKAB070351)
Retaining screw(w/ rubber piece)

2-Locking screws(w/ rubber piece)

Stand pole

800 mm or more

Top flange

Support(not supplied)

Adapter(thread G3/4)
Lamp house
Short nipple(w/ 2 O rings)
Terminal box

Fig. 2■ Special Direct Mount Type (Fig. 3: Example LKAB070311)
2-φ holes(for M8 bolts)
Mounting bracket
2-Hexagon socket headbolts

Retainer

Mounting angle(up to 70° left/right)
Lamphouse

Flexible fitting
Terminal box

Fig.3

Pass the electric wires (white and black: power wires, green:grounding wire) through the stand pole.
Fit the top flange attached to the lamp house into the standpole (in the arrow direction).
Tighten the retaining screw and two locking screws suppliedwith the top flange and confirm that the lamp house does notturn.
NB: Don't remove the waterproof rubber pieces from theretaining screw and locking screws.
Attach the short nipple and terminal box, referring to theshort nipple installation manual. For installation of theterminal box, see Fig. 1.
Completely fix the stand pole with the support (not supplied)and prescribed terminal box mounting screws.
Bring the electric wires to the terminal box and connect thewires in the terminal box.
NB: The lamp house should be installed within an angle range
from 0° (down) to 15°.
Fix the mounting bracket on a horizontal mounting surface
securely with M6 bolts or equivalent bolts.
Pass the electric wires (white and black: power wires, green:grounding wire) through the flexible fitting and attach theflexible fitting to the retainer (lamp house).
Pass the electric wires through the terminal box and attach
the terminal box to the flexible fitting.
Connect the electric wires in the terminal box.
Adjust the angle of the lamp house using the mounting
bracket.
NB: The product is mounted on a ceiling. The lamp house isinstalled within an angle range from 0 to 70 degrees in theleft and right directions. For angle adjustment, loosen thetwo hexagon socket head bolts on the retainer. After
adjustment, be sure to tighten the hexagon socket headbolts.

■ Horizontal Pole Mount Type (Figs. 4 and 5: Example LKAB070314)
2-Hexagon bolts

Pole (handrail)(not supplied)

2-Hexagon bolts

Mounting band

2-Hexagon nuts
SupportRetainer

Mounting bracket

2-Hexagon nuts
Lamphouse

Flexible fitting
Terminal box

Fig.4
Pole (handrail)(not supplied)
SupportMounting band

Fig.5--As shown in Fig. 5, put the mounting band onto the supportand insert the horizontal pole (handrail).
Keeping the support horizontal, fix the mounting band and the
support securely with the pole between them using the two
hexagon bolts and two hexagon nuts on the mounting band.
Lift the lamp house and fix the lamp house mounting bracket
to the support securely with the two hexagon bolts and two
hexagon nuts on the mounting bracket.
Pass the electric wires (white and black: power wires, green:
grounding wire) through the flexible fitting and attach theflexible fitting to the retainer (lamp house).
Pass the electric wires through the terminal box and attach
the terminal box to the flexible fitting.
Connect the electric wires in the terminal box.
Adjust the angle of the lamp house using the mounting bracket.
NB: The lamp house is installed within an angle range from 0 to
70 degrees in the left and right directions. For angle
adjustment, loosen the two hexagon socket head bolts on
the retainer. After adjustment, be sure to tighten thehexagon socket head bolts.

■ Lamp House Replacement Type (Fig. 6: Example LKAB037032)
Pass the electric wires (white and red: power wires, black: grounding
Existing junction boxwire) through the pipe (existing or supplied pipe) and the existing
Existing pipejunction box.
Attach the lamp house to the existing pipe.
Connect the electric wires in the existing junction box.
NB1: Before attaching the lamp house, check the existing piping (includingPower cable
the pipe and junction box) for corrosion.
NB2: If the product is used in a place subject to water splashes,
waterproof the connection between the lamp house and theLamp house
existing pipe.

Fig.6■ Attachment of Cable Gland (Fig. 7: Example ZCGS-22B)
Separate the cable gland into parts as shown in Fig. 7 and pass
the cable through the cable gland in the following order:
2-Cable fixing screws
cover, connecting member, cable fixing member, washer,
2-Washersrubber sleeve, washer, body, and lock nut.
Cable retaining plate
NB1: The cable should be a round cable applicable to the rubber
O ringsleeve. For information on cables applicable to the cable
Connecting member
gland, see the catalog.
NB2: Be sure to remove the locking screw on the cable gland
O ringbody before separating the cable gland into parts.
Rubber sleeve
Locking screw
Cable fixing member
Screw in the lock nut on the body until it touches the body flange.
CoverFasten the gland onto the entry of the terminal box (or theBody
device to which the gland is to be attached) until the bodystops.
Cable gland (ZCGS)
Tighten the lock nut toward the terminal box (or the device towhich the gland is to be attached).
Cable (round)
NB: Waterproof the threaded connection.
Push the washer, rubber sleeve, and washer into the body andpull out the cable to a sufficient length for cable connection.
Screw the cable fixing member into the body.
Fig.7
Fasten the cable retaining plate on the cable fixing member.
NB: Confirm that the cable does not move.
Tighten the locking screw on the body to prevent the cablefixing member from loosening.
Attach the protective tube to the connecting member, thenscrew the cover into the body securely.
NB1: Confirm that the cover is invisible from the O ring. If visible,
the waterproofness is not ensured.
NB2: The cable gland should be a product as specified by SEIWA.
Lock nutTerminal box

How to Use

The LED lamp is turned on by applying the rated voltage to the power cable of the product.

Maintenance■ Inspection

1) In cleaning the fitting, gently wipe with water or mild detergent. Don’t use thinner, benzene or alkaline detergent. Suchchemicals might cause discoloration or deterioration in quality and strength, resulting in a damage.
2) Prior to maintenance, be sure to turn off the power.
3) Carry out maintenance properly in accordance with the related law and regulations.
4) If a repair is needed, consult us.

Disassembly and Disposal
1) In the period when the product is in use, never disassemble it.
2) For disposal of the product, follow the regulations and rules of your local government.

--

Reordering

Nameplate

When reordering, please let us know:
・Drawing or drawing No. for the delivered product・Manufacturing lot number on the nameplate
If the above information is unavailable, give us any material showing the appearance of theproduct or details of the product specification (dimensions, mounting interval, lamp type, etc.).

Fig.8

CAUTIONS
1. The product must be installed so that the angle of the lamp house is within a prescribed range from its downward oriented position (0°).
If the angle is out of the range, an insulation failure or electric shock might result.
2. Prior to maintenance or inspection, be sure to turn off the power.
3. Confirm that the screws and bolts are fastened properly and tightly.
4. In the case of the stanchion type, be sure to provide a support at least 800 mm above the bottom of the pole.
5. For outdoor use, waterproof the screwed portion of the conduit, the cable entry fittings and the joint with the stand pole to prevent
rainwater infiltration.
6. When installing the fitting, be sure to connect external wires inside a specified part of the fitting. Don't open any other part of the fitting
unless necessary.
7. The product must be used in a location where it can be used safely according to its explosion protection type (indicated on the body).
8. The supply voltage variation should be within ±6% of the rating.
9. Close unused entries of the terminal box with plugs.
10. The ambient temperature should be within the range of -20°Cto +40°C. The use of the product out of this range may shorten the servicelife.
11. In grounding work, be sure to follow the technical standards for electrical equipment and explosion-protected equipment of your country.
Inadequate grounding might cause an explosion, fire or electric shock.
12. Prior to maintenance or inspection, be sure to turn off the power.
13. To prevent shortening of the service life, avoid turning on the fitting in direct sunlight.
14. To avoid noise or malfunctioning, don't use a radio, television or wireless infrared remote control near the fitting.
15. For white LED lamps, the luminescent color and brightness may vary with individual LEDs because of their nature. Also note that the rateof attenuation with time varies with individual LED lamps.
16. The product must be mounted on a sturdy wall surface or structure which is vibration-free and less susceptible to damage. Otherwise, it
might fall or be damaged.
17. For use in an unfavorable location (a very hot, cold or humid place or a place in which there is strong wind or vibration, a salt damage
environment or a dusty or corrosive gas atmosphere), a special countermeasure should be taken.
18. Do ’t ope the produ t. Otherwise, a e plosio , fire, or ele tri sho k ight result.
19. The cable gland must be a product specified by SEIWA.
20. The LED lamp and the power supply unit cannot be replaced.
21. Do ’t look straight at the LED la p. It a da age our e es.

--

11E0000712D11

Safety Precautions-To be conserved

Prior to use, please read the safety precautions and instruction manual thoroughly to use the product properly.
After installing the product, be sure to hand the safety precautions and instruction manual over to the user of the product.
Please keep the manual in a handy place for later reference.
● The various marks have the following meanings:

WARNING: Improper handling may lead to a human death or serious bodily injury.
CAUTION:

Improper handling may lead to a bodily injury or property damage.

Be sure tofollow theinstructions.

Be sure to turnoff the power.

Disassembly &conversion
prohibited.

Don’t use neara water source.

Be sure toground.

Prohibited.

Don’t touch.

CautionBe careful ofignition.

WARNING
If you use a product in a hazardous location where there is a gaseous, steamy or dusty atmosphere, it should be of theflameproof type suitable for the location. Use of an unsuitable type apparatus might cause an explosion or fire.
The ambient temperature should be within the operating temperature range specified in the instruction manual. If theproduct should be used at a temperature higher than specified, an early lighting failure or malfunction might occur or anexplosion or fire might result.
If a product must be oriented in a specific manner for use, install it properly according to the marking on its body or theinstruction manual. Otherwise, an explosion, fire or electric shock might result.
For electrical connections, use crimp-type terminals, etc. to secure the connections and conduct insulation treatment. An
inadequate connection or inadequate insulation might cause an imperfect contact, leading to an explosion, fire or electricshock.
In grounding work, be sure to follow the technical standards for electrical equipment and explosion-protected equipment of
your country. Inadequate grounding might cause an explosion, fire or electric shock.
Do ’t o ert the produ t.
Conversion might cause the product to fall or result in a fire or electric shock.
Do ’t o er the produ t ith a i fla
a le aterial su h as loth or paper or put a ythi g i the produ t.
Such a material or thing might cause an explosion or fire.
When leading the power cable into the product, be sure to follow the technical standards for electrical equipment andexplosion-protected equipment of your country. Inadequate cable connection or waterproofing might cause an explosion,
fire or electric shock.
Do ’t e d, t ist or pull the po er a le y for e.
Inadequate handling of the cable might damage it and result in a fire or electric shock.
The parts once removed for cleaning should be replaced properly according to the instruction manual.
An improperly placed part might cause the product to explode or fall, resultng in an injury or property damage.
When leading the power cable into the product through a conduit or the like, waterproof the connection and joint
adequately to prevent water infiltration. Inadequate waterproofing might cause a fire or electric shock.
Do ’t ope LED la p prote ti e o ers su h as the fro t glass a d glass glo e.
Do ’t tou h a LED la p, other ise a alfu tio or lighti g failure ight o ur.
L照- 1/2 -6

WARNING
Before cleaning, be sure to turn off the power.
Otherwise, a fire or electric shock might result.
If you continue to use the product in an abnormal condition (smoke, odor, etc.), an explosion, a fire or electric shock might
result. If you detect an abnormality, immediately turn off the power switch. Confirm that the abnormal condition has been
eliminated and make a repair call.
Don’t use the product in a strong corrosive gas atmosphere which contains hydrochloric acid or chlorine gases or the like.
Use in a corrosive gas atmosphere might cause the product to corrode and fall, resulting in an injury.
The product should be mounted on a surface robust enough to support its weight, properly according to the instruction
manual. Improper installation might cause the product to fall or result in an electric shock or injury.

CAUTIONAny product not marked as a product for outdoor use should not be used outdoors or in a humid place or near a water
source. Its use in such a place might cause a fire or electric shock.
Do ’t use the produ t at a oltage other tha the rated oltage i di ated o the a eplate.
Otherwise, breakage, fire or electric shock might result.
For a product marked with a frequency, don’t use the product at a frequency other than 50 or 60 Hz (local power supply
frequency). Use at a wrong frequency might cause a fire.
Installation of the product should be carried out by a qualified person.
Installation by an unqualified person is legally prohibited.
Never touch LED light sources and their surroundings.
The light sources and their surroundings are very hot, so an accidental touch might cause a burn.
To ensure brightness and safety, carry out periodical cleaning and inspection.
If you find a problem, discontinue the use of the product and have it repaired by a specialist.
A lighting fitting has a service life. A product which has been used for eight to ten years may have degraded internal partseven if it looks normal. For safety and energy saving, we recommend you check and replace it. The LED module design life is
6,0000 hours (different from the lighting fitting life) when used at an ambient temperature of 30°C, 10 hours per day, 3,000
hours per year. If used at a higher temperature or more hours per year, the life would be shortened. Have a specialist
inspect the product every three years. If used for an extended period without inspection, a smoke, fire, or electric shockmight result.

Resycling
Ni-Cd
Ni-MHJBRC

Please bring used Secondary batteries to the recycling station for effective use of precious
resources and global environment conservation.

Japan Portable Rechargeable Battery Recycling Center

Phone +81 3 6403 5763

CONTACT DETAILSFor further information on the product, contact any of our offices listed below (if you like to make an inquiry, let us know the model nameindicated on the product nameplate).

SEIWA ELECTRIC MFG.CO., LTD.
Head Office

36 Shinike, Terada, Joyo, Kyoto Pref. 610-0192 JapanTokyo Branch

2-19-6 Yanagibashi, Taito-ku, Tokyo 111-0052 Japan

Phone
Fax
Phone
Fax+81 774 55 8181
+81 774 58 2034
+81 3 5833 8946
+81 3 5833 8971

Please note that the above addresses and phone numbers may be changed.
L照- 2/2 -6