FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

POWER SUPPLY

OUT 4
OUT 3
OUT 2
OUT 1
28V 12A
27V 10A
8A
26V 6A
5A
25V 4A
3A
24V 2AFPS300.245-034-105

IP
65/67

Input AC 100-240V

OUT1 | OUT2

OUT3 | OUT4GENERAL DESCRIPTION

•
•
•
•
•
•
•
•
•
•
•
•
•
•
•

100-240Vac 24V 300W

IP 65/67 Degree of protection
600 Wpeak 5 s
1AC 100-240 V wide-range input
4 switchable outputs
Outputs for actors and sensors separately protected
95.7 % full load and excellent partial load efficiencies
DIN rail mounting possible, option “D”
Output connected to PE (PELV)
Version without connection to PE on request
Large output capacitors
Not potted
Negligible low input inrush current surge
Full power between -25 °C and +55 °C
IO-Link
3 years warranty

SHORT-FORM DATAThe FPS300 is an industrial grade power supply for the
1-phase mains system, it is incorporated into a rugged
wall-mount housing with an IP65/67 degree ofprotection.
It provides two to four stabilized outputs that are
galvanically separated from the input. The negative
potential of the outputs is permanently connected to
PE within the unit.
The most outstanding features of the FPS series are thecompact size, the wide operating temperature range,
the extremely low input inrush current and the very
high efficiencies, which are achieved through various
design technologies. Large output capacitors canabsorb and store regenerative energy from breaking
motors.
Various connector options support the different needsof individual applications. Please contact PULS for
possible options. High immunity to transients andpower surges as well as low electromagnetic emissions
and an international approval package makes the use
in nearly every application possible.

Output voltage
Adjustment range

DC 24 V
24-28 V

NominalFactory setting 24.5 V

Output power

Derate linearly
Number of output
Output currents

Continuous:
Up to:
360 / 300 / 150 W +45 / +55 / +70 °C
Short term up to 5 s
600 / 300 W+55 / +70 °C+55 °C to +70 °C
4
Settable per output; up to 12 A

Input voltage AC
Input voltage DC
Power factor
AC Inrush current

1AC 100-240 V
DC 110-300V*)
0.99 / 0.97
2.6 / 6Apeak-15 / +10%
±20%
At 120 / 230 Vac
At 120 / 230 Vac

Efficiency

94.3 / 95.7 %At 120 / 230 Vac

Losses18.1 / 13.5W

At 120 / 230 Vac

Hold-up time
Temperature range

44 / 44 ms-25 °C to +70 °C

At 120 / 230 Vac

Size (wxhxd)
Weight181x183x59 mm Without connectors
1200 g / 2.7 lb*) For DC supply voltages above 150 Vdc an external fuse isrequired.

MAJOR APPROVALS AND CONFORMITY

ORDER NUMBERS
Description:

Power supply FPS300

Order Number
FPS300.245-034-105*
FPS300.245-047-103
FPS300.245-055-109

Input
M12-S
7/8" 3 pin
7/8" 3 pin

Accessories:
Related Products

Chapter 21
Chapter 22

Output
M12-L
7/8” 4 pin
7/8” 5 pin

For details or a complete approval list, see chapter 21.

IEC 62368-1
IEC 61010-2-201*For DIN rail mounting PSU: (Order Number)De.g. FP300.245-034-105D
All parameters are specified at 24V, 12.5A, 230Vac, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
Feb. 2022 / Rev. 0.1 DS-FPS300-EN

www.pulspower.com

1 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

INDEX
INDEX ..................................................................................2

Approvals and Fulfilled Standards .......................... 31

Intended Use ..............................................................4

Regulatory Compliance ........................................... 31

Installation Instructions .............................................4

Accessories ............................................................... 32

AC-Input .....................................................................5

21.1.
DIN RAIL Mounting KIT: ZM.FPDRA-11 ......... 32
21.2.
Mounting Braket: ZM.FPMBA-11................... 32
21.3.
Connectors ...................................................... 33
Related Products ...................................................... 34

DC-Input .....................................................................6
Input Inrush Current ..................................................6
Output ........................................................................7
Hold-up Time .............................................................9
IO-Link Interface ...................................................... 10
Efficiency and Power Losses .................................... 16
Lifetime Expectancy ................................................. 17
MTBF ......................................................................... 17
Functional Diagram ................................................. 18
Dimensions and Connector Variants ....................... 20
User Interface ........................................................... 23
EMC........................................................................... 26

Application Notes .................................................... 35
23.1.
Repetitive Pulse Loading................................ 35
23.2.
External Input Protection ............................... 35
23.3.
Inductive and Capacitive Loads ..................... 35
23.4.
Back Feeding Loads ........................................ 35
23.5.
Mounting Orientations .................................. 36
IO-Link Data Types and Description ....................... 37
24.1.
24.2.
24.3.

Cyclic Data ...................................................... 37
Acyclic data ..................................................... 39
Events .............................................................. 45

Environment............................................................. 28
Safety and Protection Features ............................... 29
Dielectric Strength ................................................... 30
The information given in this document is correct to the best of our knowledge and experience at the time of publication.
If not expressly agreed otherwise, this information does not represent a warranty in the legal sense of the word. As the stateof our knowledge and experience is constantly changing, the information in this data sheet is subject to revision. We
therefore kindly ask you to always use the latest issue of this document (available under www.pulspower.com).
No part of this document may be reproduced or utilized in any form without our prior permission in writing.
Packaging and packaging aids can and should always be recycled. The product itself may not be disposed of as domestic
refuse.

TERMINOLOGY AND ABREVIATIONSPE andSymbolPE is the abbreviation for Protective Earth and has the same meaning as the symbol.

Earth, Ground

This document uses the term “earth” which is the same as the U.S. term “ground”.

T.b.d.

To be defined, value or description will follow later.

AC 230 V

A figure displayed with the AC or DC before the value represents a nominal voltage withtolerances (usually ±15 %) included.
E.g.: DC 12 V describes a 12 V battery disregarding whether it is full (13.7 V) or flat (10 V)

230VacA figure with the unit (Vac) at the end is a momentary figure without any additional tolerances
included.

50Hz vs. 60Hz

As long as not otherwise stated, AC 100V and AC 230V parameters are valid at 50Hz mains
frequency. AC 120V parameters are valid for 60Hz mains frequency.

may

A key word indicating flexibility of choice with no implied preference.

shall

A key word indicating a mandatory requirement.

shouldA key word indicating flexibility of choice with a strongly preferred implementation.

Us

Sensor output

Ua

Actor output

All parameters are specified at 24V, 12.5A, 230Vac, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
Feb. 2022 / Rev. 0.1 DS-FPS300-EN

www.pulspower.com

2 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

NOMENCLATURE
DetailFPT

Description
380-480 V 3 Phase IP54-67 Power Supply

FPS

100-240 V 1 Phase IP54-67 Power Supply

FPH

200-240 V 1 Phase IP54-67 Power Supply Highline Input Voltage

300

300 W Power Class

500

500 W Power Class

241 / 481

Standard Power Supply with Output Voltage 24-28 V / 48-52 V Setting and LED Bar

242 / 482

Basic Power Supply without Voltage Setting and LED-Bar. This version has a status LED Bar.

245 / 485

Power Supply with up to 4 E-Fuse Channels

246 / 486

Power Supply with up to 4 NEC Class II Channels

247 / 487

Power Supply with NEC Class II and E-Fuse Channel

0xx

Terminal configuration e.g. .002. Input: HanQ4/2 Com: M12-A Output: HanQ4/0

1xx

Consecutively numbered

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

3 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Intended Use
This device is designed for indoor use and is intended for commercial applications, such as in industrial control, processcontrol, monitoring and measurement equipment.
Do not use this device in equipment where malfunction may cause severe personal injury or threaten human life. If thisdevice is used in a manner outside of its specification, the protection provided by the device may be impaired.

Installation Instructions
DANGER

Risk of electrical shock, fire, personal injury or death.

–

Turn power off before working on the device. Protect against inadvertent re-powering.

–

Do not open, modify or repair the device.

–

Do not touch during power-on and immediately after power-off. Hot surfaces may cause burns.

–

Install the device on a large enough flat surface. Sharp edges on the back may cause injury.

–

If damages or malfunctioning occur during installation or operation, immediately turn power off and send unit to thefactory for inspection.

–

The device is designed as “Class of Protection I” equipment according to IEC 61140. Do not use without a proper PE(Protective Earth) connection.
WARNING

Risk of damages on the device–

Keep the following minimum installation clearances: 30 mm on top and bottom, 10 mm on the front and 10 mm left
and right side.

–

The maximum surrounding air temperature is +70 °C (+158 °F). The operational temperature is the same as the ambientor surrounding air temperature and is defined 2 cm below the device.

–

The device is designed to operate in areas between 5 % and 95 % relative humidity.

–

Clean only with a damp cloth.

Obey the following installation instructions:This device may only be installed and put into operation by qualified personnel. This device does not contain serviceableparts. The tripping of an internal fuse is caused by an internal defect. Install the device onto a flat surface with the terminals
on the bottom of the device. Other mounting orientations require a reduction in output power, chapter 23.6.
For wall mounting use 4 screws. Two on top and 2 on bottom mounting holes. Recommended screw size is M4 (UNC 8-32).
The enclosure of the device provides a degree of protection of IP65/67 when installed with all mating connectors firmly
connected. The device is designed for pollution degree 3 areas in controlled environments.
Assure that during installation no moisture or dirt gets into the connections. Operation in areas where moisture orcondensation can be expected is possible.
The negative potential of the outputs is permanently connected to PE within the unit. Do not connect the negative potentialof any output to PE outside the unit.
For TN,TT mains systems with earthed neutral and IT star mains systems with insulation monitoring the device is designed
for overvoltage category III zones up to 2000 m (6560 ft) and for overvoltage category II zones up to 5000 m (16400 ft).
For TN, TT, IT delta mains systems or IT star mains systems without insulation monitoring the device is intended forovervoltage category II zones up to 2000 m (6560 ft). The device is designed to be safe in case of a single phase loss and does
not require an external protection. Functionality is limited see chapter 23.3.
The device is designed for altitudes up to 5000 m (16400 ft). Above 2000 m (6560 ft) a reduction in output current is required
and the operation is limited according mains systems described above. The device is designed, tested and approved forbranch circuits up to 20 A (UL) and 32 A (IEC) without additional protection device. If an external fuse is utilized, do not use
circuit breakers smaller than 6 A B- or C-characteristic to avoid a nuisance trip. A disconnecting means shall be provided forthe input of the device. This must be suitably located and easily accessible. The disconnecting means must be marked as the
such for the device.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

4 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

AC-Input
The device is suitable to be supplied from TN, TT or IT mains networks. For more details, please review chapter 2.
AC input voltage rated range nom.
AC input operating range

AC 100-240 V
85-264 Vac
264-300 Vac

Continuous operation
For maximal 500ms

Input frequency

Nom.

50–60 Hz

±6 %Turn-on voltage
Shut-down voltage

Typ.
Typ.

80 Vac70 VacSteady-state value, see Fig. 3-1
Steady-state value, see Fig. 3-1

External input protection

See recommendations in chapter 2 .

Input current

typ.

AC 100 V
3.98 AAC 120 V
3.2 A

AC 230 V
1.68 AAt 360 W, symmetrical phase voltages, see Fig. 3-3 PowerPower factor*)

typ.

0.99

0.99

0.97

At 360 W, see Fig. 3-4

Start-up delay
Rise time

typ.
typ.
typ.

2s
22 ms
48 ms

2s
22 ms
46 ms

2s
22 ms
35 ms

At 300 W symmetrical phase voltages, see Fig. 3-2
At 300 W constant current load, 0 mF load, see Fig. 3-2
At 300 W constant current load, 12.5 mF, see Fig. 3-2

Turn-onovershootMax.

200 mV

200 mV

200 mV

See Fig. 3-2

The power factor is the ratio of the true (or real) power to the apparent power in an AC circuit.
POUT

Input
Voltage

max.
500ms

L1

Turn-onShut-down

AC input range

VIN
85V

264V

Rise
Time

Fig. 3-2: Turn-on behavior, definitions

Input Current (A)5
A 100Vac
4
B 120Vac

Power Factor (1)
1,00
0,95
A

C 230Vac
B

2

C

1
0
-40

Start-up
delay

300VacFig. 3-1: Input voltage range

3-5%

OutputVoltage

0,90

A

B
C

0,85

A 100Vac0,80

B 120Vac

0,75
60

Overshoot

*)

160

360
260
Output Power (W)

0,70
-40

C 230Vac

60

160

360
260
Output Power (W)Fig. 3-3:

Fig. 3-4:

Input current vs. output power at 24 V output
voltagePower factor vs. output power at 24 V output
voltage

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

5 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

DC-Input
The device is suitable to be supplied from a DC input voltage.
DC input*)nom.

DC 110-300 V*)

DC input range

min.
max.

88 Vdc180 Vdc

DC input current

typ.
typ.

2.90 A
1.04 A

Turn-on voltage
Shut-down voltage

Typ.
Typ.

80 Vac70 Vac±20 %At 110 Vdc, at 24 V, 300 W
At 150 Vdc, at 24 V, 300 W*)
For DC supply voltage above 150Vdc an external fuse with an appropriate rating is required. Wide range DC
input 110-300V without external fuse on request.
Instructions for DC use:
Battery

Power Supplya)

Use a battery or a similar DC source. A supply from theintermediate DC-bus of a frequency converter is notrecommended and can cause a malfunction or damage the
unit.

b)

Connect +pole to L and –pole to N.

c)Connect the PE terminal to an earth wire or to the machine
ground.

AC

+

L
N

+
Load

PE
-

DC

Fig. 4-1: Wiring for DC Input

Input Inrush Current
An active inrush limitation circuit (NTCs, which are bypassed by a relay contact) limits the input inrush current after turn-onof the input voltage.
The charging current into EMI suppression capacitors is disregarded in the first microseconds after switch-on.

Inrush current

max.

AC 100 V
2.18 Apeak

AC 120 V
2.6 ApeakAC 230 V
6 ApeakInput Current 5A/DIV

Input Voltage

Output Voltage
250ms/DIV

Fig. 5-1: Typical turn-on behavior at nominal load and 25°C ambient temperature
All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

6 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

OutputThe outputs provide a (PELV/ES1) rated voltage, which is galvanically isolated from the input voltage. The negative potentialof the outputs is permanently connected to PE within the unit. Do not connect any output to PE (Ground).
The device is designed to supply any kind of loads, including capacitive and inductive loads. If capacitors with a capacitance>20mF are connected to one output, this output might switch off after turning the unit or the output on or connecting theload.
All outputs are individually current limited. In case of an overload, the individual output switches off and needs to be reset
manually with the reset button on the front of the device or via IO-Link. A cycling of the input power does not reset theoutput. The failure signals are stored until a reset is intentionally initiated.
For protection reasons a delay of at least 5 seconds is mandatory, before an output can be reset after it has been switched
off. Otherwise the green LED will flicker after pushing the button. The unit is shipped with all outputs turned on. The
ON/OFF function has no safety feature included.
The sum of the configured output power of all outputs may exceed the total output power of available power budget, seeFig. 6-2. If this is the case, the output with the highest number will tripped first followed by the next output to ensure thatthe lower channel number will supply continuous power and see no voltage dips.
Outputs start sequentially from 1 to 4 with an interval of 150ms, see Fig. 6-1.
Number of outputs
Output voltage

Nom.

Adjustment range

4
24 V

Factory setting 24.5 V

24-28 V

Adjustable in steps:
24 V, 24.5 V, 25 V, 25.5 V, 26 V, 26.5 V, 27 V and 28 V

Factory setting

Typ.

24.5 V±0.2 %, at nominal load

Line regulation

Max.

25 mV

Between 85 and 300 Vac input voltage change

Load regulation

Typ.

250 mV

Between 0 and 360 W output load, static value

Ripple and noise voltage

Max.

50 mVpp

Bandwidth 20 Hz to 20 MHz, 50 Ohm

Output current

Order number
FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Total output powerNom.

short term up to 5s

Max. current
10 A each output
10 A each output
12 A each output

PictureFig. 6-3
Fig. 6-3
Fig. 6-3

Typ.

360 W

Trip curve

See Fig. 6-3

12 500 µF

Included inside the power supply, common for all four outputs

Parallel Use
Back-feeding loads

Connector
2 x M12-L
2x 7/8” – 4pin
2x 7/8” – 5pin

Up to +45 °C at ambient temperatures, for the sum of all
outputs.
Nom.
300 W
At +55 °C at ambient temperatures, for the sum of all outputs.
Nom.
150 W
At +70 °C at ambient temperatures, for the sum of all outputs.
Nom.
600 W
Up to +55 °C at ambient temperatures, for the sum of all
outputs.
Nom.
300 W
At +70 °C at ambient temperatures, for the sum of all outputs.
Derate linearly between +55 °C and +70 °C

Overload behavior
Output capacitance

Outputs
4
4
4

Do not parallel units for higher output currents
Max.

35 V / 4 J

The unit is resistant and does not show a malfunction when aload feeds back voltage to the power supply. It does notmatter whether the power supply is on or off.
For all four outputs in total

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

7 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Fig. 6-1: Sequential start of the outputs

Fig. 6-2:
Tripping of the channel with the lowest priority when
the power budget is exceeded

Fig. 6-3: Trip curve diagram

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

8 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Hold-up TimeThe hold-up time is the time during which a power supply’s output voltage remains within specification following the lossof input power. The hold-up time is output load dependent. At no load, the hold-up time can be up to several seconds. The
status LED is also on during this time.

Hold-up Time

typ.
min.
typ.
min.

AC 100 V
75 ms
56 ms
44 ms
29 ms

AC 120 V
75 ms
56 ms
44 ms
29 ms

AC 230 V
75 ms
56 ms
44 ms
29 ms

At 150 W output load, see Fig. 7-1
At 150 W output load, see Fig. 7-1
At 300 W output load, see Fig. 7-1
At 300 W output load, see Fig. 7-1

Input
Voltage

L1-5%

OutputVoltage
Hold-up Time

Fig. 7-1: Hold-up time vs. input voltage

Fig. 7-2: Shut-down behavior, definitions

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

9 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

IO-Link Interface
The IO-Link interface used in this power supply is compliant to IO-Link protocol V1.1 and can be connected to any IO-Link
masters compliant to V1.1 of the IO-Link protocol. This allows a transparent data flow to the sensors and actuators andtherefore more transparent and easier way to monitor the current status of the power supply.
In case of no or defective connectivity of the IO-Link, the power supply can also be operated on smoothly. Due to a builtin EEPROM, previously inputted data will be drawn from its storage.
To operate the IO-Link interface it is required to install/upload the IODD-File (IO-Link Device Description) into the connected
IO-Link master. The most recent IODD file can be found on the PULS website (www.pulspower.com) in the download sectionof the individual product page. The device can also be accessed via IO-Link, if the power supply is not connected to ACmains and in a switched off mode.
IO-Link Version
IO-Link master Version
Baud-Rate
Cycle Time
SIO-Mode
Process Data Length

V1.1
V1.1
COM3 (230.4 kBaud)2ms
yes
23 bytes

To get full performance, it is recommended to use IO-Link
Cycle time refers to the reloading speed of certain process data
Class BThe power supply provides three categories of data via IO-Link. They are divided between read only or read- andcustomizable data.

Control Settings

This set of data is customizable. The data in control settings can be adjusted to the user’s preference to ensure an evenbetter operation of the power supply. Typical control settings are e.g. setting tripping points, setting per-alarm levels, etc.

Parameter write
Output Voltage Setpoint

Value range
24.0-28.0 V

Description
Output Voltage Setpoint
Pre-Setting- 24.5 V

Standby0 - unit is operating
1 - unit in standby

PSU can be switched into standby, where all outputs
turn off.
Pre-Setting- 0=unit is operating

Configuration Setting

0 - human-machine interface
only
1 - IO-Link only
2 - both3 - none (button lock)Controls the configurability of the PSU, which can be
restricted to local HMI or IO-Link only.
Configuration can also be blocked completely.
Pre-Setting- 2=both

E-Fuse Channel on/off

0 – off
1 - onUsed to control the state of output channel switches(ON/OFF) or to reconnect a tripped channels.
Bit coded parameter.
Pre-Setting- 1=ON for all channels

E-Fuse trip value
channel 1 to channel 4

1-10/12 A

Defines the output current threshold for each E-Fusechannel, where the electronic fuse is triggered.
Pre-Setting- 10/12 A (depends on type of output
connector)

E-Fuse Pre-alarm level
channel 1 to channel 4

10-100 %Defines the threshold for the event"Output current pre-alarm for each channel".
Pre-Setting- 80 %PSU total output current
Pre-alarm level

1-100 A

Defines the threshold for the event"PSU output current pre-alarm".
To suppress event generation, set this value to max(100 A).
Pre-Setting- 20A

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

10 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Parameter

The parameter values can be accessed to read out additional data (e.g. current output voltage, temperatures etc

Parameter read

read out value range

Description

Output Voltage Setpoint

24.0-28.0 V

Output Voltage Setpoint
Pre-Setting- 24.5 V

Standby0 - unit is operating
1 - unit in standby

PSU can be switched into standby, where all outputs
turn off.
Pre-Setting- 0=unit is operating

Configuration Setting

0 - human-machine interface
only
1 - IO-Link only
2 - both3 - none (button lock)Controls the configurability of the PSU, which can be
restricted to local HMI or IO-Link only.
Configuration can also be blocked completely.
Pre-Setting- 2=both

E-Fuse Channel on/off

0 - off

Used to control the state of output channel switches(ON/OFF) or to reconnect a tripped channels.
Bit coded parameter.
Pre-Setting- 1=ON for all channels

1 - onE-Fuse trip value
channel 1 to channel 4

1-10/12 A

Defines the output current threshold for each E-Fusechannel, where the electronic fuse is triggered.
Pre-Setting- 10/12 A (depends on type of output
connector)

E-Fuse Pre-alarm level
channel 1 to channel 4

10-100 %Defines the threshold for the event"Output current pre-alarm for each channel".
Pre-Setting- 80 %PSU total output current
Pre-alarm level

1-100 A

Defines the threshold for the event"PSU output current pre-alarm".
To suppress event generation, set this value to max(100 A).
Pre-Setting- 20 A

EEPROM Status

0 - OKPSU internal EEPROM status information.
1 - Recoverable error detected If unrecoverable error is detected, the PSU may
2 - Unrecoverable error
operate with pre-setting values.

PSU events

bit 0 - DC-OK
bit 1 - DC-Warning
bit 2 - Bonus Powerbit 3 - Over Temperature CAP
bit 4 - Over Temperature PSU
bit 5 - Over load
bit 6 - High voltage input
bit 7 - Low voltage input
bit 8 - Power supply down
bit 9 - Predictive maintenancepower supply
bit 10 - 2 phase operation
bit 12 - PSU settings changed
via HMI
bit 13 - PSU hardware failure

Collection of active events of the PSU.
Bit-coded parameter, bits 11,14-15 not used.

Temperature secondary inside -40-150 °C

Temperature at secondary DC output area inside PSU

Max. temperature secondary
inside-40-150 °C

Maximum temperature at secondary DC output area
inside PSU

Temperature primary inside-40-150 °C

Temperature at primary AC input area inside PSU

Max. temperature primaryinside-40-150 °C

Maximum temperature at primary AC input area
inside PSU

AC Input Voltage RMS
Actual output voltage

Actual Input Voltage RMS (phase-phase)
0-49 V

Actual average output voltage

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

11 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Parameter read

read out value range

Description

Actual output current

0-68 A

Actual average total output current

E-Fuse current
channel 1 to channel 4

0-15 A

Actual average E-Fuse output current for each E-FusechannelE-Fuse output status

bit 0 - Ch1
bit 1 - Ch2
bit 2 - Ch3
bit 3 - Ch4
0 – off
1 - onActual state of E-Fuse output channels
Bit coded parameter.
0 - channel is off
1 - channel is on

E-Fuse trip statuschannel 1 to channel 4

0 - No trip
1 - Over-load trip
2 - Short circuit trip
3 - Temperature trip
4 - Power budget trip
5 - Installation failure trip
6 - Sensor fault trip
7 - Fatal fault trip

Actual trip state of E-Fuse channel
If the E-Fuse has tripped, this parameter gives
detailed information about the reason. This
information might help for failure analysis in theapplication.

Stress level0 - “<5 %”1 - “>5 %”2 - “>25 %”3 - “>50 %”4 - “>75 %”Stress level based on output power delivery.
This parameter gives an indication about the total
power consumption of the application and theremaining margin.

Remaining Endurance LED
coded

0 - “<10 %”1 - “>10 %”2 - “>25 %”3 - “>50 %”4 - “>75 %”This parameter gives an estimated remaining
endurcance indication.
Overall performance of the PSU might decrease at
low remaining endurance code.

Remaining Endurance

10-99 %

This parameter gives an estimated remaining
endurcance indication in percent.
Overall performance of the PSU might decrease at
low remaining endurance.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

12 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Counter
E-Fuse Number of Startups
channel 1 to channel 40-150000Counts the number of startups on each E-Fusechannel over the whole lifetime.

E-Fuse Number ofOvercurrents channel 1 tochannel 40-150000

Number of Overcurrents on each E-Fuse channel over
the whole lifetime.

0-1000000
0-59

Total operating hours
operating minutes

Operating time
hours
minutes

Transient VDE-0160 Counter 0-150000
overallTransient Counter overall

Transient VDE-0160 Counter 0-65535
last 2 minutes

Transient Counter last 2 minutes

Turn-on Counter

0-150000

Turn-on Counter of the PSU

Uptime since last turn-on
hours
minutes0-1000000
0-59

Uptime since last turn-on – hours
Uptime since last turn-on - minutes

Device Status

0 - Device is operating properly
1 - Maintenance-Required
2 - Out-of-Specification
3 - Functional-Check
4 - Failure

Overall PSU device state

Detailed Device Status
Item [1]Item [2]Item [3]Item [4]Item [5]OctetStrings

Shows up to 5 pending events
3 octets per subindexOctet 1 – EventQualifier
Octet 2,3 - EventCode

Device Status

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

13 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Event Data

This set of data is on read only. Event data reports on parameter errors and warns of device failures of the power supply to
the IO-Link master. It is triggered when certain critical conditions or control settings are exceeded. Typical events are e.g.
ambient temperature too hot, high input voltage, etc.

EventsParameter error --- Check data
sheet and values

Event-type
Error

Description

Device temperature over-run --- Warning
Clear source of heat
Events. DC-Warning

Warning

Output voltage dips more than 10% below adjusted
output voltage

Events. Bonus Power

Notification

Output current is 5% more than maximum for morethan 3s

Events. Over Load

Warning

Load higher than allowed

Events. High Voltage Input

Warning

Input to highEvents. Low Voltage Input

Warning

Input to low

Events. Power Supply down

Warning

No link from IO-Link Transceiver to Power Supply

Events. Predictive Maintenance Warning
Power Supply

The estimated remaining lifetime has reached 10%.
Performance of PSU might be limited due to aging
effects of components.

Events. Two phase AC supply

One leg of the 3-phase system is missing

Warning

Events. PSU setting changed via Warning
HMI

A PSU setting was changed via man-machine

Events. PSU hardware failure

Warning

Critical PSU hardware failure detected. PSU shut down.

Events. PSU output current
Pre-alarm

Warning

Total PSU output current exceeds pre-alarm limit

Events. E-Fuse channel 1 tochannel 4 Tripped

Warning

For each E-Fuse channel when is tripped due toovercurrent

Events. Output current
Pre-alarm channel 1 tochannel 4

Notification

For each E-Fuse channel when Output current exceeds
pre-alarm limit

interface.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

14 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Process Data

This set of data is on read only. Process data reports on the current state and conditions of the power supply to the IO-Link
master. Typical process data are, e.g. actual output voltage of each output channel, internal temperatures, tripping status
reports, etc.

Process
Actual Output total Current

Value rangeA

Description

Actual Output Voltage

V

Actual Output Voltage

E-Fuse Current

A

Actual Output Current from each E-Fusechannel 1 to channel 4

ChannelE-Fuse channel states

Actual state of E-Fuse outputs (on/off)

E-Fuse overload trip states

Overload trip state of E-Fuse outputs (ok/tripped)

E-Fuse short circuit states

Short circuit trip state of E-Fuse outputs (ok/tripped)

For a full list of data set, see chapter 24, IO-Link Data Typs and Description.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

15 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Efficiency and Power Losses
Efficiency

typ.

AC 100 V
93.6 %

AC 120 V
94.3 %

AC 230V
95.7 %

Averageefficiency*)typ.

92.9 %

93.5 %

94.6 %

25 % at 80 W, 25 % at 150 W, 25 % at 220 W, 25 % at
300 W

Power losses

typ.
typ.
typ.

2.7 W
10.7 W
20.5 W

2.8 W
10.0 W
18.1 W

2.2 W
8.3 W
13.5 W

At 24 V, 0 W (no load)
At 24 V, 150 W (half load)
At 24 V, 300 W (full load)*)

At 24 V, 300 W

The average efficiency is an assumption for a typical application where the power supply is loaded with 25% of
the nominal load for 25% of the time, 50% of the nominal load for another 25% of the time, 75% of the nominal
load for another 25% of the time and with 100% of the nominal load for the rest of the time.

Efﬁciency (%)
96

A

95

B

94

C

93
A 230Vac92

B 120Vac

91
90

C 100Vac

0

100

200

360
300
Output Power (W)Fig. 9-1: Efficiency vs. output power at 24 V, typ.

Power Losses (W)25
A 100Vac20
B 120VacA

C 230Vac

15

B

C

10
5
-40

60

160

360
260
Output Power (W)Fig. 9-2: Losses vs. output power at 24 V, typ.

Power Losses (W)25,0Efﬁciency (%)
96,0

20,0
94,0
15,0

92,0

50

100

150

300
200
250
Input Voltage (Vac)Fig. 9-3:
Efficiency vs. input voltage at 24 V, 300 W, typ.

10,0

50

100

150

200
250
300
Input Voltage (Vac)Fig. 9-4:
Losses vs. input voltage at 24 V, 300 W, typ.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

16 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Lifetime Expectancy
The Lifetime expectancy shown in the table indicates the minimum operating hours (service life) and is determined by the
lifetime expectancy of the built-in electrolytic capacitors. Lifetime expectancy is specified in operational hours and is
calculated according to the capacitor’s manufacturer specification.
The manufacturer of the electrolytic capacitors only guarantees a maximum life of up to 15 years (131 400 h). Any number
exceeding this value is a calculated theoretical lifetime which can be used to compare devices.

Calculated lifetime expectancy

1AC 100 V
88 600 h
257 900 h
247 300 h
530 100 h

1AC 120 V
121 100 h
319 790 h
352 300 h
610 800 h

1AC 230 V
175 200 h
410 500 h
432 500 h
834 400 h

At 24V, 300 W and 40°C
At 24V, 150 W and 40°C
At 24V, 300 W and 25°C
At 24V, 150 W and 25°C

MTBF
MTBF stands for Mean Time Between Failure, which is calculated according to statistical device failures, and indicatesreliability of a device. It is the statistical representation of the likelihood of a unit to fail and does not necessarily represent
the life of a product.
A MTBF figure of e.g. 1 000 000 h means that statistically one unit will fail every 100 hours if 10 000 units are installed in thefield. However, it can not be determined if the failed unit has been running for 50 000 h or only for 100 h.
For these types of units the MTTF (Mean Time To Failure) value is the same value as the MTBF value.

MTBF SN 29500, IEC61709
MTBF MIL HDBK 217F

1AC 100 V
270 000 h
489 000 h

1AC 120 V
305 000 h
546 000 h

1AC 230 V
384 000 h
679 000 h

At 24 V, 300 W and 40 °C
At 24 V, 300 W and 25 °C

106 000 h
160 000 h
29 000 h
39 000 h

118 000 h
175 000 h
32 000 h
42 000 h

135 000 h
195 000 h
35 000 h
46 000 h

At 24 V, 300 W and 40 °C; Ground Benign GB40
At 24 V, 300 W and 25 °C; Ground Benign GB25
At 24 V, 300 W and 40 °C; Ground Fixed GF40
At 24 V, 300 W and 25 °C; Ground Fixed GF25

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

17 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Functional Diagram

Fig. 12-1: Functional Diagram FPS300.245-034-105

Fig. 12-2: Functional Diagram FPS300.245-047-103

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

18 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Fig. 12-3: Functional Diagram FPS300.245-055-109

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

19 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Dimensions and Connector Variants
FPS300.245-034-105

Width
HeightDepth
Weight181 mm / 7.11''
183 mm / 7.2''
59 mm / 2.32''
1200 g / 2.7lb

Input connector on power supply (X1):
7/8” 3pin Male

Housing body material
Housing cover material
Installation clearances
Mating connectors

Aluminium alloy
Hi-grade polycarbonate
See chapter 2
See chapter 21.3

Pin :Pin 2:Pin 3:

PE connection
LN

Pin 1:Pin 2:Pin 3:
Pin 4:
Pin 5:

24 Vdc supply voltage
not connected
GND Supply voltage
Data IN/OUT
not connected

Output connector on power supply (X3 and X4):
7/8” 5 pin Female
Pin 1:Pin 2:Pin 3:
Pin 4:
Pin 5:

24 Vdc (Out 2 | 4) Us
GND (Out 1 | 3) Ua
GND (Out 2 | 4) Us
24 Vdc (Out 1 | 3) Ua
FE

IO-Link connector on power supply (X2):
M12-A Male

Sensor output
Actor output
Sensor output
Actor output

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

20 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

FPS300.245-047-103

Width
HeightDepth
Weight181 mm / 7.11''
183 mm / 7.2''
59 mm / 2.32''
1200 g / 2.7lb

Input connector on power supply (X1):
7/8” 3pin Male

Housing body material
Housing cover material
Installation clearances
Mating connectors

Aluminium alloy
Hi-grade polycarbonate
See chapter 2
See chapter 21.3

Pin :Pin 2:Pin 3:

PE connection
LN

Pin 1:Pin 2:Pin 3:
Pin 4:
Pin 5:

24 Vdc supply voltage
not connected
GND Supply voltage
Data IN/OUT
not connected

Output connector on power supply (X3 and X4):
7/8” 4 pin Female
Pin 1:Pin 2:Pin 3:
Pin 4:

24 Vdc (Out 2 | 4) Ua
24 Vdc (Out 1 | 3) Us
GND (Out 1 | 3) Us
GND (Out 2 | 4) Ua

3

2

IO-Link connector on power supply (X2):
M12-A Male

Actor output
Sensor output
Sensor output
Actor output

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

21 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

FPS300.245-055-109

Width
HeightDepth
Weight181 mm / 7.11''
183 mm / 7.2''
59 mm / 2.32''
1200 g / 2.7lb

Input connector on power supply (X1):
7/8” 3pin Male

Housing body material
Housing cover material
Installation clearances
Mating connectors

Aluminium alloy
Hi-grade polycarbonate
See chapter 2
See chapter 21.3

Pin :Pin 2:Pin 3:

PE connection
LN

Pin 1:Pin 2:Pin 3:
Pin 4:
Pin 5:

24 Vdc supply voltage
not connected
GND Supply voltage
Data IN/OUT
not connected

Output connector on power supply (X3 and X4):
7/8” 5 pin Female
Pin 1:Pin 2:Pin 3:
Pin 4:
Pin 5:GND (Out 2 | 4) Ua
GND (Out 1 | 3) Us
FE
24 Vdc (Out 1 | 3) Us
24 Vdc (Out 2 | 4) Ua

3

2

IO-Link connector on power supply (X2):
M12-A Male

Actor output
Sensor output
Sensor output
Actor output

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

22 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

User Interface
A
B
C
D
E
F
G

E

Input Connector
Output Connectors
IO-Link Connector
Status LED
LED BarSet Mode and Up and Down Button
Output LEDs ON/OFF & Reset Buttons

D
F

E

G
A

C

B

D
F
G

Overview
LED Bar (E)The LED Bar is a multifunctional displaying tool. The main function is to monitor the sum of all outputs (percentages scale).
It also can display the output voltage (voltage scale) and output current (ampere scale) for the individual outputs. The
integrated Status LED displays different running conditions of the PSU in real-time.
Output Level Controls (F)The Output Level Controls consist of the Set Mode button and the UP/DOWN buttons. The Set Mode is used to change into
tripping current settings. The UP/DOWN are used to adjust different output levels or change into the Output Current Mode.
Output Controls (G)The Output Controls consist of an output LED and an Output ON/OFF button (ON/OFF) for each output. The Output LED
displays different running conditions for output in real-time. The ON/OFF is used to switch the output on/off.

Operation Settings
Monitor Output Power Mode
The Output Power Mode displays the actual total output power after startup. It is the default mode of the LED Bar. The
output Power is Displayed in percentages of 300 W. E.g. If the LED Bar is powered up till 50 %, 150 W is expended. If the
LED Bar rises above 100% and therefore exceeds 300 W the 125 %-LED flashes orange. Refer to the percentage scale on theleft sidebar.
Monitor Output Current Mode
The Output Current Mode is to check the output current of the individual outputs.
To inspect these output currents:

Press the UP or DOWN button. OUT1 in the LED bar lights up in orange. The output current is displayed in real-timein the LED Bar below. Refer to the ampere scale on the right sidebar.
In the LED Bar switch between the OUT1 - OUT4 using the UP/DOWN buttons to check the different output current
values.

Return to the Output Power Mode/default mode by pushing beyond the highest (OUT4) or lowest (OUT1) output
number.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

23 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Set Tripping Current
To set a new tripping current:Press Set Mode for 3 s. After all LEDs light up once, the LED now displays the set voltage.

Press Set Mode to select the right output to change the tripping current. The orange LED will indicate which output
is selected.
Push UP/DOWN to increase or decrease the set point. Refer to the current scale on the right sidebar. (e.g. 20 %-LED
indicates 3 A).

New point is set.

After 15 s of non-action, the PSU will automatically switch to Output Power Mode.
Set Output Voltage
To set a new output voltage:
Press Set Mode for 3 s. After all LEDs light up once, the LED now displays the set voltage.

Push UP/DOWN to increase or decrease the set point. Refer to the current scale on the right sidebar. (e.g. 20 %-LED
indicates 24.5 V).

New point is set.

After 15 s of non-action, the PSU will automatically switch to Output Power Mode.
Set Button LockTo activate/deactivate the button lock:
Press the UP and DOWN buttons simultaneously for 3 s. The LED bar will flash for 5 s to indicate the changed button
lock status.
Reset Output
In a failure mode where the output did/didn’t switched OFF:
Push and hold ON/OFF for more than 1s.

LED Signaling
Status LED (D)The Status LED displays different running conditions of the PSU in real-time.
Green: On
DC voltage is above 90 % of set point voltage. All outputs areoperating according to their settings.
OFF
DC voltage is below 90 % of set point voltage or an output channel
has tripped or PSU is not powered.
Red: AC input failure
AC input drops below the specified levels and outputs turned off.
Flashes orange: HiccupPlus mode!
Output is OFF during these 18s.
Flashes red: Overtemperature
The PSU turns OFF to prevent overheating. Normal operating range
continues
after the Status LED turns to solid green again.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

24 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Channel LED Signaling Overview
Below is an overview of the output LED signaling.
OFF
Output is switched OFF by ON/OFF or PSU is not powered (s. Status LED).
Green: Default
Output is switched on by ON/OFF.

Fig. 14-1: Location of outputs LEDs

Flashes green: Power budget tripped (slow rate: 250 ms ON / 250 ms OFF)Low priority outputs are tripped. Sum of output currents are above
PSU powerbudget.
Flashes green: Buttons Locked (fast rate: 125 ms ON / 125 ms OFF)No action is carried out. Button lock feature activated. Unlock buttons
by following Operation Settings > Set Button Lock. Other reason:
MOSFET protection MOSFET is >90 °C or Interval between Charge
Up/ Turn On cycles <5 s.
Orange: Pre-Alarm!
Output is still running. Current is above pre-alarm level and close to overload.
Flashes orange: Overload! (slow rate: 500 ms ON / 500 ms OFF)
Output is tripped. Output current is overloaded. Restart by pushing
the ON/OFF.
Flashes orange: Faulty Installation (medium rate: 250 ms ON / 250 ms OFF)
Output is turned OFF automatically. Cable or connected hardware on
the outputs are not installed correctly. Switch OFF the output manuallyby pushing the specific output ON/OFF button.
 PSU with NEC Class II outputs: Difference between positive andnegative/Input-Output current of the output are >1 A for 6-6.5 s
 PSU without NEC Class II outputs: Connector negative wireovercurrent according to negative trip curve, or output wascontributing to negative overcurrent of another output (Ipos --- Ineg
> threshold), or High PE current (>12 A) was detected based on
overall output current sum.
Flashes orange: Short Circuit (fast rate: 125 ms ON / 125 ms OFF)
Output is tripped. The Output's output current exceeded approx. 48A.
Short circuit reasons may be electrical short, loads beyond specification,
plugging-in a large capacitance during operation, etc. After pushing ofspecific output ON/OFF button, e-fuse output tries to turn ON.
Flashes Orange/Green: Overtemperature! (slow rate, 250 ms orange /250 ms)
Output will automatically turned OFF when MOSFET overtemperature(125 °C) is reached. When MOSFET temperature falls below 90 °C theoutput will turn on automatically.
Red: Fatal MOSFET Malfunction!
PSU turns OFF. Power switch on specific output is damaged.
Replacement of PSU might be required.
Possible malfunction:
 Positive current output in OFF state exceeds >2 A for more than >0.5sFlashes red: Hardware Specs Out of Range! (slow rate, 500 ms ON /500 ms OFF)
Affected output channel turns OFF. Measurement Circuit Hardware isout of specified range. Replacement of PSU might be required.
Possible malfunction:
 Deviations of internal output current sensors exceed acceptable
limits.
 Temperature sensor measurement out of range (-40 °C or +150 °C)
for more than 5 s

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

25 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

EMC
The EMC behavior of the device is designed for applications in industrial environment as well as in residential, commercial
and light industry environments.
The device is investigated according to EN 61000-6-1, EN 61000-6-2, EN 61000-6-3, EN 61000-6-4, EN 61000-3-2 andEN 61000-3-3.

EMC immunity
Electrostatic discharge
Air discharge

EN 61000-4-2

Contact discharge
Air discharge

8 kV
15 kV

Criterion A
Criterion A

Electromagnetic RF field

EN 61000-4-3

80 MHz - 2.7 GHz
2.7 GHz – 6 GHz

20 V/m
10 V/mCriterion A
Criterion A

Magnetic field

EN 61000-4-8

50 Hz/60 Hz

30 A/mCriterion A

Fast transients (Burst)

EN 61000-4-4

AC Input lines
DC Output lines
IO-Link

4 kV
4 kV
4 kV

Criterion A
Criterion A
Criterion A

Surge voltage on AC input

EN 61000-4-5

L to N
L to PE, N to PE

2 kV
4 kV

Criterion A
Criterion A

Surge voltage on DC output EN 61000-4-5+ to +/- to PE

1 kV
2 kV

Criterion A
Criterion A

Surge voltage on IO-Link

EN 61000-4-5

IO-Link to PE

1 kV

Criterion A

Conducted immunity

EN 61000-4-6

0.15 – 80 MHz

20 V

Criterion A

Voltage dips

EN 61000-4-11

0 % of 100 Vac
40 % of 100 Vac
70 % of 100 Vac
0 % of 200 Vac
40 % of 200 Vac
70 % of 200 Vac

0 Vac, 20 ms
40 Vac, 200 ms
70 Vac, 500 ms
0 Vac, 20 ms
80 Vac, 200 ms
140 Vac, 500 ms

Criterion A
Criterion C
Criterion C
Criterion A
Criterion A
Criterion A

Voltage interruptions

EN 61000-4-11

0V

5000 ms

Criterion C

Voltage sags

SEMI F47

Dips on the input voltage according to SEMI F47 standard
80 % of 120 Vac (96 Vac) 1000 ms
Criterion A
70 % of 120 Vac (84 Vac) 500 ms
Criterion A
50 % of 120 Vac (60 Vac) 200 ms
Criterion A

Powerful transients

VDE 0160

Over entire load range

750 V, 0.3 ms

Criterion A

Performance criterions:
A: The device shows normal operation behavior within the defined limits.
C: Temporary loss of function is possible. The device may shut-down and restarts by itself. No damage or hazards
for the device will occur.
*) For IO Link certification immunity test levels according EN 61326-1:2013-01 have been tested

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

26 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

EMC Emission
Conducted emission AC input lines

EN 55011, EN 55015, EN 55032,
FCC Part 15, CISPR 11, CISPR 32
IEC/CISPR 16-1-2, IEC/CISPR 16-2-1

Class B

Radiated emission

EN 55032 / EN 55011

Class B

Harmonics

EN 61000-3-2Class A fulfilled between 0A and 12A load

Voltage fluctuations, flicker

EN 61000-3-3

Pass tested with constant current loads, non
pulsing

Conducted emission DC output lines
Conducted emission IO-Link output

This device complies with FCC Part 15 rules.
Operation is subjected to following two conditions: (1) this device may not cause harmful interference, and (2) thisdevice must accept any interference received, including interference that may cause undesired operation.

Switching Frequencies
PFC converter
Main converter
Auxiliary converter
Microcontroller clocks

20 kHz to 135 kHz
60 kHz to 140 kHz
54 kHz to 66 kHz
48 Mhz and 32 MHz

Input voltage and output load dependent
Output load dependent
Output load dependent
Fixed frequency

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

27 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Environment
Operational temperature-25 °C to +70 °C (-13 °F to 158 °F)

Operational temperature is the same as theambient or surrounding temperature and isdefined as the air temperature 2cm below theunit.

Storage temperature-40 °C to +85 °C (-40 °F to 185 °F)

For storage and transportation

Output derating

6 W/°C
10 W/°C
20 W/1000 m or 5°C/1000 m

Humidity

5 to 95 % r.h.

According to IEC 60068-2-30

Atmospheric pressure

54-110k Pa

see Fig. 16-2: Output power vs. for details

Altitude

Up to 5000 m (16 400 ft)

see Fig. 16-2: Output power vs. for details

Over-voltage categoryIII

According to IEC 60664-1
For TN, TT mains systems with earthed neutral
and IT star mains systems with insulation
monitoring for altitudes up to 2000 m
According to IEC 60664-1
For TN, TT mains systems with earthed neutral
and IT star mains systems with insulation
monitoring for altitudes between 2000 m and5000 m
According to IEC 60664-1
For TN, TT, IT Delta mains systems or IT starmains systems without insulation monitoring
for altitudes up to 2000 m

Between +45 °C and +55 °C (113 °F to 131 °F)
Between +55 °C and +70 °C (131 °F to 140 °F)
For altitudes >2000 m (6560 ft), see Fig. 16 2:
Output power vs. altitude
The derating is not hardware controlled. The user has to take care to stay below thederated current limits in order not to overload the unit.

II

Degree of pollution

3

Vibration sinusoidal

2-17.8 Hz: ±1.6 mm; 17.8-500 Hz: 2 g According to IEC 60068-2-6
2 hours / axis
30 g 6 ms, 20 g 11 ms
According to IEC 60068-2-27
3 bumps / direction, 18 bumps in
total
Shock and vibration is tested in combination with DIN-Rails according to EN 60715 witha height of 15 mm and a thickness of 1.3 mm and standard orientation.

Shock

According to IEC 62477-1, not conductive

LABS compatibility

Yes

Audible noise

Some audible noise may be emitted from the power supply during no load, overload
or short circuit.

Allowed Output Power (W)
600

A

450
B

360
300
150
0
-25

A short term (max. 5s)
B continuous

0+45 +55+70
Ambient Temperature (°C)

Fig. 16-1: Output power vs. ambient temp.

Fig. 16-2: Output power vs. altitude

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

28 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Safety and Protection Features
Isolation resistancemin.

500 MOhm

At delivered condition between input and output,
measured with 500 Vdc
At delivered condition between input and PE, measured
with 500 Vdc

min.

500 MOhm

PE resistance
Input/Output separation

max.

0.1 Ohm
PELV

Output over-voltage protection

typ.
31.8 Vdc
max.
32.5 Vdc
In case of an internal defect, a redundant circuit limits the maximum output voltage.
The output shuts down and automatically attempts to restart

Resistance between PE terminal and the housing
IEC/EN/UL 61010-2-201, IEC/EN 62368-1, IEC/EN 60950-1

Class of protection

According to IEC 61140
A PE (Protective Earth) connection is required

Ingress protection

IP 65/67

According to EN/IEC 60529

Over-temperature protection

Included

Output shut down with automatic restart. Temperature
sensors are installed on critical components inside theunit and turns the unit off in safety critical situations,which can happen e.g. when ambient temperature is too
high, ventilation is obstructed or the de-rating
requirements are not followed. There is no correlation
between the operating temperature and turn-off
temperature since this is dependent on input voltage,load and installation methods.

Input transient protection

MOV (Metal
Oxide Varistor)
Included

For protection values, see chapter 26, EMC.

0.51 mArms

At 264Vac, 60Hz

Internal input fuse
Touch current (leakage current)max.

Not user replaceable slow-blow high-breaking capacity
fuse

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

29 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Dielectric Strength
The negative terminal of the outputs is permanently connected to PE within the unit. The output is insulated from the input
by a double or reinforced insulation.
Type and routine tests are conducted by the manufacturer. Field tests may be conducted in the field using the appropriate
test equipment which applies the voltage with a slow ramp (2s up and 2s down). Connect all input-terminals before
conducting the test. When testing, set the cut-off current settings to the value in the table below.

Earth, PE

L1

Output(s)
+
-

N

D

Input

A

D

Type test

60 s

2500 Vac

500 Vac

Routine test

5s

2500 Vac

500 VacField test

5s

2000 Vac

500 VacCut-off current setting
for field test

>10 mA>10 mAIO-LinkFig. 18-1: Dielectric strength

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

30 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Approvals and Fulfilled Standards
IEC 62368

CB Report
IEC 61010

IEC 60950

CB Scheme Certificate
IEC 62368-1 - Audio/video, information and communication
technology equipment - Safety requirements
Output safety level: ES1
CB Scheme Certificate
IEC 61010-2-201 - Electrical Equipment for Measurement, Control andLaboratory Use - Particular requirements for control equipment

CB Report

Manufacturers Declaration
IEC 60950-1 - General safety requirements for Information Technology
Equipment (ITE)UL 61010

UL Certificate
Listed equipment for category NMTR - UL 61010-2-201 - Electricalequipment for measurement, control and laboratory use - Particularrequirements for control equipment
Applicable for US and Canada
E-File: E198865

Semi F47

Test Report
Voltage Sag Immunity for Semiconductor Processing Equipment Tested
for AC 208V L-L or L-N mains voltages, nominal output voltage andnominal output load

VDMA 24364

Paint Wetting Impairment Substances Test (or LABS-Test)
Tested for Zone 2 and test class C1 according to VDMA 24364-C1-L/W for
solvents and water-based paints

Regulatory Compliance
EU Declaration ofConformity

Trade conformity assessment for Europe
The CE mark indicates conformance with the European–
EMC directive–
Low-voltage directive (LVD)–
RoHS directive

WEEE Directive

Manufacturer's Statement
EU-Directive on Waste Electrical and Electronic Equipment (WEEE)
registered in Germany as business to business (B2B) products.
WEEE-Reg.-Nr. DE 55837529

REACH Regulation(EU)

Manufacturer's Statement
EU regulation regarding the Registration, Evaluation, Authorization andRestriction of Chemicals (REACH) fulfilled.

China RoHS

Manufacturer's Statement
The device meets the Measures for Restriction of the Use of Hazardous
Substances in Electrical & Electronic Products according the China-RoHS
requirements.
The device is marked with EFUP symbol 25 years (Environmentally
Friendly Use Period)

IEC/EN 61558-2-16(Annex BB)

Safety Isolating
Transformer

Safety Isolating Transformers corresponding to Part 2-6 of the IEC/EN
61558

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

31 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Accessories
21.1. DIN RAIL Mounting KIT: ZM.FPDRA-11
In addition to screw mounting FIEPOS can easily be attached to a DIN rail using the ZM.FPDRA-11 DIN rail mounting kit.

•

DIN-Rail not included•

DIN-Fixture pre-assembled

21.2. Mounting Braket: ZM.FPMBA-11
In addition to screw mounting FIEPOS can easily be attached to a mounting bracket the ZM.FPMBA-11.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

32 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

21.3. Connectors
FIEPOS features a large number of different connectors. Mating connectors can be ordered at PULS from stock in order tosupply customers quickly during the design-in phase.
For a higher demand or other connector options go to HARTING-PULS-cabling.

Connector Name

PULS order code

Harting order code

Connector Description

Harting HANQ4/2

ZCF.hanq42

6104401263700

Q4/2 Set AS female 2.5-6mm² 7-13mm

Harting HANQ4/2

ZCF.hanq42-1

6104401263800

Q4/2 Set AS female 2.5-6mm² 14-17mm

Harting HANQ2/0

ZCM.hanq20

6104401263900

Q2/0 Set screw male 2.5-6mm² 6-12mm

Harting HANQ4/0

ZCM.hanq40

6104401265100

Q4/0 Set crimp 2,5mm2 IP67

Harting HANQ5/0

ZCF.hanq50

6104401265000

Q5/0 Set QuickLock female 0.5-2.5mm² 6-12mm

Harting M12-A

ZCF.m12a5p

21032722505

M12-A 5pin cut clamp female 0.34-0.5mm² / 6-8mm

Harting M12-A

ZCM.m12a5p

21032721505

M12-A 5pin cut clamp male 0.34-0.5mm² / 6-8mm

Harting M12-S

ZCF.m12s4p

6102201020400

M12-S 4pin screw female 2.5mm² / 6-8mm

Harting M12-L

ZCM.m12l5p

21032961505

M12-L 5pin cut clamp male 0.75-1.5mm² / 5.8-13.5mm

Harting M12-T

ZCM.m12t4p

6102201021000

M12-T 4pin screw male 1.5mm² / 8-10mm

Harting 7/8”

ZCM.78inch4p

6102201021100

7/8” 4pin screw male 1.5mm² / 6-8mm

Harting 7/8”

ZCF.78inch3p

6102201021200

7/8” 3pin screw female 1.5mm² / 6-8mm

Harting 7/8”

ZCM.78inch5p

21041162505

7/8” 5pin screw male 0.75-1.5mm² / 6.8-12.5mm

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

33 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Related Products
The FIEPOS product family includes various devices with different technical parameters and features. The following page
provides a general overview of the available solutions. Please also get in touch with your PULS contact person, for moredetailed application advice and technical information.
FPS300.245-049-102:
Power Supply with three fused channels (2–10A) and Output-OK contact.

SHORT-FORM DATA
Input voltage

1AC 100-240 V-15 / +10%

Output voltage
Adjustment range

DC 24V
24-28Vdc

NominalFactory setting 24.5V

Output power

Continuous:
360W
Up to +45°C ambient
300W
At +55°C ambient
150W
At +70°C ambient
Short-term, up to 5s:
600W
Below +55°C ambient
300W
At +70°C ambient
Derate linearly between +55 °C to +70 °C

Number of outputs

3

Output current

Settable per output; up to 10A

Input connector
Output connector

7/8” 3pin
7/8” 4pin

FPT500.246-049-102:
Power Supply with three NEC CLASS II channels and IO-Link.

SHORT-FORM DATA
Input voltage

1AC 100-240 V-15 / +10%

Output voltage
Adjustment range

DC 24V
24-28Vdc

NominalFactory setting 24.5V

Output power

Continuous:
360W
Up to +45°C ambient
300W
At +55°C ambient
150W
At +70°C ambient
Short-term, up to 5s:
600W
Below +55°C ambient
300W
At +70°C ambient
Derate linearly between +55 °C to +70 °C

Number of outputs

3

Output current

NEC Class II

Input connector
Output connector

7/8” 3pin
7/8” 4pin

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

34 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

Application Notes
23.1. Repetitive Pulse Loading
Typically, a load current is not constant and varies over time. This power supply is designed to support loads with a higher
short-term power demand (BonusPower). The short-term duration is hardware controlled by an output power manager andis available on a repeated basis. If the average load is higher than the sum of all output power, the output voltage will dip.
To avoid this, the following rules must be followed:a)

The power demand of the pulse must be below 200 of the nominal output power.

b)

The duration of the pulse power must be shorter than the allowed BonusPower time, see chapter 6c)

The average power should be lower than the nominal output power.

The R.M.S. output current must be below the specified continuous output current. If the R.M.S. current is higher, the unit
may respond with a thermal shut-down after a period of time.

23.2. External Input Protection
The device is designed, tested and approved for branch circuits up to 20 A (UL) and 32 A (IEC) without additional protection
device. If an external fuse is utilized, do not use circuit breakers smaller than 6 A B- or C-Characteristic to avoid a nuisancetrip.

23.3. Inductive and Capacitive Loads
The unit is designed to supply any kind of loads, including capacitive and inductive loads. If extreme large capacitors, suchas EDLCs (electric double layer capacitors or “UltraCaps”) with a capacitance larger than 20mF are connected to the output,
the unit might charge the capacitor or the output might trip, chapter 6.

23.4. Back Feeding Loads
Loads such as decelerating motors and inductors can feed voltage back to the power supply. This feature is also called return
voltage immunity or resistance against Back- E.M.F. (Electro Magnetic Force).
This power supply is resistant and does not show malfunctioning when a load feeds back voltage to the power supply. It
does not matter whether the power supply is on or off.

All parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

35 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS300.245-055-109

23.5. Mounting Orientations
The device can be mounted in various mounting orientations. The listed lifetime and MTBF values from this datasheet apply
only for the standard mounting orientation. The following curves give an indication for allowed output power in different
mounting orientations for altitudes up to 2000 m (6560 ft).
A

Output Power (W)Standard Orientation

360
300
Power
Supply150
Input

Output0+45 +55+70
Ambient Temperature (°C)

Output Input

B
Power
SupplyUpside down

Output Power (W)
300

Power
SupplyD
Over-head andTable-top mounting

Power
SupplyOutput Input

Horizontal
cw and ccw

PowerSupplyC

Output Input

150

0

+55
+70
Ambient Temperature (°C)

Power
SupplyAll parameters are specified at 24 V, 12.5 A, 230 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

36 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

IO-Link Data Types and Description
24.1. Cyclic Data
The first dataset is called process data and refers to data that is periodically sent to the IO-Link master. The data is updated and communicated every 2ms. All other data in the
power supply itself is generated every 50ms and stored in the IO-Link registers. The higher cycle frequency enables operation with IO-Link masters and attached PLCs without
configuration.
Process

Sub-index

Bit offset

Data type

Bit length

Data Format

Resolution

Actual Output total Current

1

104

uint16_t

16Q8.8

2-8 A/bit

Allowed values

Actual Output Voltage

2

88

uint16_t

16Q8.8

2-8 A/bit

E-Fuse Current CH1
E-Fuse Current CH2

3
4

72
56

uint16_t
uint16_t

16
16

Q8.8
Q8.8

2-8 A/bit
2-8 A/bit

E-Fuse Current CH3

5

40

uint16_t

16Q8.8

2-8 A/bit

E-Fuse Current CH4

6

24

uint16_t

16Q8.8

2-8 A/bit

E-Fuse CH1 state
E-Fuse CH2 state
E-Fuse CH3 state
E-Fuse CH4 state

10
11
12
13

16
17
18
19

bool
bool
bool
bool

1
1
1
1

-

-

true = On
false = Off

E-Fuse CH1 overload trip state
E-Fuse CH2 overload trip state
E-Fuse CH3 overload trip state
E-Fuse CH4 overload trip state

14
15
16
17

8
9
10
11

bool
bool
bool
bool

1
1
1
1

-

-

true = tripped
false = Ok

E-Fuse CH1 short circuit state
E-Fuse CH2 short circuit state
E-Fuse CH3 short circuit state
E-Fuse CH4 short circuit state

18
19
20
21

0
1
2
3

bool
bool
bool
bool

1
1
1
1

-

-

true = tripped
false = Ok

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

37 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109
Octet
Subindex
Bit offset

01
119-1121
1
111-1042
2
103-96

3
2
95-88

4
3
87-80

5
3
79-72

6
4
71-64

7
4
63-56

Subindex
Bit offset

23

22

21

Octet 12
20

13
19

12
18

11
17

10
16

Subindex
Bit offset

15

14

13

Octet13
12

17
11

16
10

15
9

14
8

Subindex
Bit offset

7

6

5

4

21
3

20
2

19
1

18
0

8
5
55-48

9
5
47-40

10
6
39-32

11
6
31-24

Octet14

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

38 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

24.2. Acyclic data
The parameter values can be accessed to read out additional data (e.g. current output voltage, temperatures etc.), but in addition some of these values can also be written by theuser to configure the power supply (e.g. output voltage and remote on/off).
Parameter
Output Voltage Setpoint

Para.
Index
105

Subindex
0

Data
type
uint16

Standby

101

0

bool

Configuration Setting

103

0

uint8

E-Fuse Channel on/off
Chanel 1
Chanel 2
Chanel 3
Chanel 4

0
106

Bit
offset15-0

DataResolution
FormatQ8.8
2-8 V/bit

7-00bool array1
8-bit Record
2
3Default
values6272(24.5V)

Read [R] Allowed values
Write [W]R/W
6144…7168

Description

0R/W

0 = PSU normal operation (default
value)
1 = PSU standby

Dynamic, excluded from data storage2

R/W

0 = human-machine interface only
1 = IO-Link only
2 = both (default value)
3 = none (button lock)Dynamic

1

R/W

0 = off
1 = onR
R
R
R
R

256…2560 at 10A | 256…3072 at 12A
256…2560 at 10A | 256…3072 at 12A
Dynamic
256…2560 at 10A | 256…3072 at 12A
Default is max. current available
256…2560 at 10A | 256…3072 at 12A
256…2560 at 10A | 256…3072 at 12A

Output Voltage Setpoint
Minimum value is 24.0V
Maximum value is 28.0V

Dynamic
Bit 4…7 not used
Access via subindex 0 only

108

0
1
2
3
4

uint16 array 63-0
uint16
63-48
uint1647-32
uint1631-16
uint16
15-0

Q8.8
Q8.8
Q8.8
Q8.8
Q8.8

2-8 A/bit
2-8 A/bit
2-8 A/bit
2-8 A/bit
Q8.8

max
max
max
max
max

E-Fuse Pre-alarm level all CHs
E-Fuse Pre-alarm level CH1
E-Fuse Pre-alarm level CH2
109
E-Fuse Pre-alarm level CH3
E-Fuse Pre-alarm level CH4

0
1
2
3
4

uint8 array
uint8
uint8
uint8
uint8

31-0
31-24
23-16
15-8
7-0

Q9.7
Q9.7
Q9.7
Q9.7
Q9.7

2-7 /bit
2-7 /bit
2-7 /bit
2-7 /bit
2-7 /bit103 (80%) R/W
103 (80%) R/W
103 (80%) R/W
103 (80%) R/W
103 (80%) R/W

13…192 (10% -150%)
13…192 (10% -150%)
13…192 (10% -150%)
13…192 (10% -150%)
13…192 (10% -150%)

Dynamic

PSU total output current
Pre-alarm level

1040

uint16

15-0

Q8.8

2-8 A/bit

5120 (20A) R/W

256…25600 (1A-100A)

Dynamic

EEPROM Status

64

0

uint8

7-0

0 = ok1 = recoverable error detected
2 = unrecoverable error

Dynamic

E-Fuse trip value all CH
E-Fuse trip value CH1
E-Fuse trip value CH2
E-Fuse trip value CH3
E-Fuse trip value CH4R

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

39 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109
Parameter

Para.
Index
65

Subindex

Bit
offsetData
typeuint16

Output-OK

1

0

bool

R

bit 0…Output Voltage >90% of adjusted output voltage

DC-Warning

2

1

bool

R

bit 1… Output voltage dips more than 10% below adjusted output voltage

Bonus Power

3

2

bool

R

bit 2… Output current is 5% more than maximum for more than 3s

Over Temperature CAP
Over Temperature PSU

4

3

bool

R

bit 3…Temperature Capacitor is higher than 95°C

5

4

bool

R

bit 4… Temperature of PSU is higher than 95°C

Over Load

6

5

bool

R

bit 5… Load higher than allowedHigh Voltage Input

7

6

bool

R

bit 6… Input to high

Low Voltage Input

8

7

bool

R

bit 7… Input to low

Power Supply down

9

8

bool

R

bit 8… No link from IO-Link Transceiver to Power Supply

Predictive Maintenance Power Supply

10

9

bool

R

bit 9… Operating hours exceed estimated lifetime

PSU hardware failure

14

13

bool

R

bit 13…PSU hardware failure

PSU events

Subindex
Bit offset

15
-

14
-

13
14

Octet 012-

Subindex
Bit offset

7
8

6
7

5
6

4
5

Bit
length16

Read [R]
Description
Write [W]R
dynamic

11
-

11

9
10

8
9

3
4

2
3

1
2

0
1

Octet1

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

40 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109
ParameterPara. Sub- Data
Index index type
69
0
int16

Bit
offset15-0

DataResolution
FormatQ9.7
2-7 °C/bit

Max. temperature secondary
inside

70

0

int16

15-0

Q9.7

2-7 °C/bit

R-5120…32640

Maximum temperature secondary inside PSU -40 ..
150°C

Temperature primary inside

71

0

int16

15-0

Q9.7

2-7 °C/bit

R-5120…32640

Temperature primary inside -40 .. 150°C

Max. temperature primaryinside

72

0

int16

15-0

Q9.7

2-7 °C/bit

R-5120…32640

Maximum temperature primary inside -40 .. 150°C

AC Input Voltage RMS

78

0

uint16

15-0

Q12.4

2-4 V/bit

R

0…24000 (0-1500V)

Actual Input Voltage RMS (phase-phase)

Temperature secondary inside-8

Default
valuesRead [R] Allowed values
Write [W]R
-5120…32640

Description
Temperature secondary inside PSU -40 .. 150°C

Actual output voltage

790

uint1615-0

Q8.8

2 V/bitR

0…12544 (0-49V)

Actual average output voltage

Actual output current

81

0

uint16

15-0

Q8.8

2-8 V/bit

R

0…12800 (0-50V)

Actual average output current

R

0…12800 (0-50A)
0…12800 (0-50A)
0…12800 (0-50A)
0…12800 (0-50A)
0…12800 (0-50A)

Actual average E-Fuse current all CH
Actual average E-Fuse current CH1
Actual average E-Fuse current CH2
Actual average E-Fuse current CH3
Actual average E-Fuse current CH4

R

0…off
1…on

Dynamic
Bit 4…7 not used
Access via subindex 0 onlyR

0 = No trip
1 = Over-load trip
2 = Short circuit trip
3 = Temperature trip
Dynamic
4 = Power budget trip
Access via subindex 0 only
5 = Installation failure trip
6 = Sensor fault trip
7 = Fatal fault tripR

0 … “<=5%”
1 … “>5%”
2 … “>=25%”
3 … “>=50%”
4 … “>=75%”

E-Fuse current all CHs
E-Fuse current CH1
E-Fuse current CH2
E-Fuse current CH3
E-Fuse current CH4
E-Fuse output status
Channel 1
Channel 2
Channel 3
Channel 4

E-Fuse trip status CH1
E-Fuse trip status CH2
E-Fuse trip status CH3
E-Fuse trip status CH4

Stress level

84

0
1
2
3
4
0

85

86

66

0

0

Unit16 arrayuint16
uint16
uint16
uint16

63-0
63-48
47-32
31-16
15-0

0
Array of bool
1
8-bit Record
23

4-bit enum
array

uint8

3-0
7-4
11-8
15-12

7-0

Q8.8
Q8.8
Q8.8
Q8.8
Q8.8

-8

2 A/bit
2-8 A/bit
2-8 A/bit
2-8 A/bit
2-8 A/bit

current load

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

41 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

ParameterPara. Sub- Data
Index index type

Bit
offsetRemaining Endurance LED
coded

67

0

uint8

7-0

Remaining Endurance

68

0

uint8

7-0

Data
Resolution
Format%Default
values99

Read [R] Allowed values
Write [W]R

0 … “<=10%”
1 … “>10%”
2 … “>=25%”
3 … “>=50%”
4 … “>=75%”

R

10…99

Description

Dynamic

Remaining Endurance in percent
Value range 10 to 99 %All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

42 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

CounterParameter
E-Fuse Number of Startups all CHs
E-Fuse Number of Startups CH1
E-Fuse Number of Startups CH2
E-Fuse Number of Startups CH3
E-Fuse Number of Startups CH4

Para.
Index

87

E-Fuse Number of Overcurrents all CHs
E-Fuse Number of Overcurrents CH1
E-Fuse Number of Overcurrents CH2
E-Fuse Number of Overcurrents CH3
E-Fuse Number of Overcurrents CH4

88

Operating time
hours
minutes

73

Transient VDE-0160 Counter overall

74

Transient VDE-0160 Counter
last 2 minutes

Subindex
012
34

Data type

0
1
2
3
4

uint16 array 63-0
uint16
63-48
uint1647-32
uint1631-16
uint1615-0

0

Bit
offsetuint32 array 127-0
uint32
127-96
uint32
95-64
uint32
63-32
uint3231-0

Data
Resolution
FormatDefault Read [R] Allowed values
value
Write [W]0…150000
0…150000
0R
0…150000
0…150000
0…1500000

Number of Startups all Channels
Number of Startups Channel 1
Number of Startups Channel 2
Number of Startups Channel 3
Number of Startups Channel 4

R

Number of Overcurrents all Channels
Number of Overcurrents Channel 1
Number of Overcurrents Channel 2
Number of Overcurrents Channel 3
Number of Overcurrents Channel 4

R

0...59

Access via subindex 0 only
Operating hours
Operating minutes

uint32
uint8

39-8
7-0

0

uint3231-0

0R0…150000

Transient Counter overall

75

0

uint3231-0

0R0…150000

Transient Counter last 2 minutes

Turn-on Counter82

0

uint3231-0

R0…150000

Turn-on Counter of the PSU

Uptime since last turn-on
hours
minutes83

uint32
uint8

39-8
7-0

0...59

Access via subindex 0 only
Uptime since last turn-on - hours
Uptime since last turn-on - minutes

0

h
min

Description

h
min

R

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

43 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

Device Status
Parameter

Para.
Index

Sub- Data type
index

Bit
offsetDevice Status

36

0

uint8

7-0

Detailed Device Status
Item [1]Item [2]Item [3]Item [4]Item [5]

37

0
1
2
3
4
5

3-OctetString array[5]3-OctetString
119-963-OctetString
95-72
3-OctetString
71-48
3-OctetString
47-24
3-OctetString
23-0

Read [R]Write [W]R

Allowed values

Description

0…Device is operating properly
1…Maintenance-Required
2…Out-of-Specification
3…Functional-Check
4…Failure

0…Device is operating properly
1…Maintenance-Required
2…Out-of-Specification
3…Functional-Check
4…FailureR

Shows up to 5 pending events (3 octets per
subindex)
Octet 1…EventQualifier
Octet 2, 3…EventCode

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

44 / 45

FPS300.245-034-105
FPS300.245-047-103
FPS500.245-055-109

24.3. Events
This information is triggered by certain situations and will result in an event notification to the IO-Link master. Typical events are notification in case of ideal (e.g. DC-OK) and nonideal situations (e.g. ambient temperature too hot, high input voltage etc.).

EventsParameter error – Check data sheet and values

Event-code
0x6320

Event-type
Error

Description

Device temperature over-run – Clear source of heat

0x4210Warning

Events. DC-Warning

0x1800Warning

Output voltage dips more than 10% below adjusted output voltage

Events. Bonus Power0x1801

Notification

Output current is 5% more than maximum for more than 3s

Events. Over Load

0x1802

Warning

Load higher than allowed

Events. High Voltage Input

0x1803Warning

Input to highEvents. Low Voltage Input

0x1804

Warning

Input to low

Events. Power Supply down

0x1805Warning

No link from IO-Link Transceiver to Power Supply

Events. Predictive Maintenance Power Supply

0x1806

Warning

The estimated remaining lifetime has reached 10%. Performance of PSU might belimited due to aging effects of components.

Events. PSU setting changed via HMI

0x1809Notification

A PSU setting was changed via man-machine interface.

Events. PSU hardware failure

0x1825Warning

Critical PSU hardware failure detected. PSU shut down.

Events. PSU output current pre-alarm

0x1830Warning

Total PSU output current exceeds pre-alarm limit

Events. E-Fuse CH1 Tripped

0x1840Warning

E-Fuse Ch1 tripped due to overcurrent

Events. E-Fuse CH2 Tripped

0x1841

Warning

E-Fuse Ch2 tripped due to overcurrent

Events. E-Fuse CH3 Tripped

0x1842

Warning

E-Fuse Ch3 tripped due to overcurrent

Events. E-Fuse CH4 Tripped

0x1843Warning

E-Fuse Ch4 tripped due to overcurrent

Events. Output current pre-alarm CH1

0x1850

Notification

Output current on E-Fuse Ch1 exceeds pre-alarm limit

Events. Output current pre-alarm CH20x1851

Notification

Output current on E-Fuse Ch2 exceeds pre-alarm limit

Events. Output current pre-alarm CH30x1852

Notification

Output current on E-Fuse Ch3 exceeds pre-alarm limit

Events. Output current pre-alarm CH40x1853

Notification

Output current on E-Fuse Ch4 exceeds pre-alarm limit

All parameters are specified at 24 V, 20 A, 400 Vac, 25 °C ambient and after a 5 minutes run-in time unless otherwise noted.
Apr. 2022 / Rev. 0.2 FPS300.245-EN

www.pulspower.com

45 / 45