Weather-proof type LED Lighting Fittings 【LYWA2602101】

Replacement LED Lighting Fixture for Fluorescent 36W-2【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑦Luminaire Flex：5,950Lm②Correlated Color Temperature : 5,000K⑤Body Material : Polycarbonate⑧Energy Efficiency：104.3Lm/W③Power Consumption : 57W⑥Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-2x1pc / LED57W (LYWA2602101)x1pc
Subject

Fluorescent36W-2 x1pc

LED (LYWA2602101) x1pc

Power Consumption (W)LED (LYWA2602101)
x1pc
Fluorescent36W-2
x1pc

57
85
0DistributionCurve

20 40 60 80 100

Lamp Life (H)LED (LYWA2602101)
x1pc
Fluorescent36W-2
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

14.2Lx

87% Up26.6LxPowerConsumption

85W

33% Down

57W

Lamp
Life

12,000h

5 Times

60,000h60,00012,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-2x15pcs / LED57W (LYWA2602101)x8pcs
Subject

Fluorescent36W-2 x15pcs

LED (LYWA2602101) x8pcs

Power Consumption (W)LED (LYWA2602101)
x8pcs
Fluorescent36W-2
x15pcs

456
1,275
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYWA2602101)
x8pcs

Quantity

15pcs

47% Down

8pcs

Average
Illuminance213.1Lx

Equivalent212.8Lx

Power
Consumption

1,275W

64% Down

456W

Lamp
Life

12,000h

5 Times

60,000h8Fluorescent36W-2x15pcs

150510Calculation Condition

Line-up
Ceiling type3.5kg20

Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYWA2602101 has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-2
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LYWA2602101

15Illuminance Level = 87% brighter than Fluorescent 36W-2

Weather-proof type LED Lighting Fittings 【LYWA2601101】

Replacement LED Lighting Fixture for Fluorescent 36W-1【Specifications】①Degree of Protection : IP55
④Lamp Life : 60,000h⑦Luminaire Flex：2,850Lm②Correlated Color Temperature : 5,000K⑤Body Material : Polycarbonate⑧Energy Efficiency：98.2Lm/W③Power Consumption : 29W⑥Voltage ： AC100-242V±6％●Warranty period of LED Lighting Fittings = 5 years●Made in Japan●With anti-glare cover【1 Unit Comparison】 : Fluorescent36W-1x1pc / LED29W (LYWA2601101)x1pc
Subject

Fluorescent36W-1 x1pc

LED (LYWA2601101) x1pc

Power Consumption (W)LED (LYWA2601101)
x1pc
Fluorescent36W-1x1pc

29470DistributionCurve

10 20 30 40 50

Lamp Life (H)LED (LYWA2601101)
x1pc
Fluorescent36W-1
x1pc

Quantity

1pc

Equivalent

1pc

Average
Illuminance

7.2Lx

79% Up12.9LxPowerConsumption

47W

38% Down

29W

Lamp
Life

12,000h

5 Times

60,000h60,00012,0000

20,00040,00060,00080,000

Calculation Condition
Lighting Quantity : 1pc
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%【Comparison for fullfill an illuminance 200Lx】 : Fluorescent36W-1x30pcs / LED29W (LYWA2601101)x16pcs
Subject

Fluorescent36W-1 x30pcs

LED (LYWA2601101) x16pcs

Power Consumption (W)LED (LYWA2601101)
x16pcsFluorescent36W-1
x30pcs

464
1,410
0

Distribution
Curve

500

1,000 1,500

Construction Fee (%)
LED (LYWA2601101)
x16pcsQuantity

30pcs

47% Down

16pcs

Average
Illuminance

216.8Lx

Equivalent

207.1Lx

PowerConsumption

1,410W

67% Down

464W

Lamp
Life

12,000h

5 Times

60,000h16

Fluorescent36W-1
x30pcs30
01020

Calculation Condition

Line-up
Ceiling type

2.5kg

40

Design Illuminance : 200Lx
Area : 10mx10m
Lighting Height : 5m
Reflectance : Ceiling50%,Wall30%,Floor10%

1.LYWA2601101 has higher brightness per 1 unit, therefore less installation
no. gets the same brightness compare to Fluorescent 36W-1
2.Reducing an installation no. contribute in cutdown the TOTAL COST including construction fee.

Model No.LYWA2601101

30

Illuminance Level = 79% brighter than Fluorescent 36W-1