National  Building  Code  of  the  Philippines      1977  

MALACAÑANG  Manila  PRESIDENTIAL  DECREE  NO.  1096  ADOPTING  A  NATIONAL  BUILDING  CODE  OF  THE  PHILIPPINES  THEREBY  REVISING  REPUBLIC  ACT  NUMBERED  SIXTY-­‐FIVE  HUNDRED  FORTY  ONE    WHEREAS,  the  country’s  accelerating  economic  and  physical  development,  coupled  with  urbanization  and  population  growth,  makes  imperative  the  formulation  and  adoption  of  a  uniform  building  code  which  shall  embody  up-­‐to-­‐date  and  modern  technical  knowledge  on  building  design,  construction,  use,  occupancy  and  maintenance;    WHEREAS,  while  there  is  Republic  Act.  No.  6541,  entitled  “An  Act  to  Ordain  and  Institute  a  National  Building  Code  of  the  Philippines”,  the  same  does  not  conform  with  the  developmental  goals  and  infrastructure  program  of  the  Government  and  does  not  adequately  provide  for  all  the  technological  requirements  of  buildings  and  structures,  in  terms  of  up-­‐to-­‐date  design  and  construction  standards  and  criteria;    WHEREAS,  in  the  formation  of  new  national  building  code,  it  is  the  desire  and  policy  of  the  Government  to  avail  of  and  harness  the  technical  expertise  and  professional  know-­‐how  of  men  not  only  in  the  public  but  in  the  private  sectors  as  well,    NOW,  THEREFORE,  I,  FERDINAND  E.  MARCOS,  President  of  the  Philippines,  by  virtue  of  the  powers  vested  in  me  by  the  Constitution,  do  hereby  order  and  decree  the  revision  of  Republic  Act.  No.  6541  to  read  as  follows:  CHAPTER  1  GENERAL  PROVISIONS    SECTION  101.  Title     This  Decree  shall  be  known  as  the  “National  Building  Code  of  the  Philippines”  and  shall  hereinafter  be  referred  to  as  the  “Code”.  
  SECTION  102.  Declaration  of  Policy  It  is  hereby  declared  to  be  the  policy  of  the  State  to  safeguard  life,  health,  property,  and  public  welfare,  consistent  with  the  principles  of  sound  environmental  management  and  control;  and  to  this  end,  make  it  the  purpose  of  this  Code  to  provide  for  all  buildings  and  structures,  a  framework  of  minimum  standards  and  requirements  to  regulate  and  control  their  location,  site,  design,  quality  of  materials,  construction,  use,  occupancy,  and  maintenance.       SECTION  103.  Scope  and  Application     (a)  The  provisions  of  this  Code  shall  apply  to  the  design,  location,  siting,  construction,  alteration,  repair,  conversion,  use,  occupancy,  maintenance,  moving,  demolition  of,  and  addition  to  public  and  private  buildings  and  structures,  except  traditional  indigenous  family  dwellings  as  defined  herein.     (b)  Buildings  and/or  structures  constructed  before  the  approval  of  this  Code  shall  not  be  affected  thereby  except  when  alterations,  additions,  conversions  or  repairs  are  to  be  made  therein  in  which  case,  this  Code  shall  apply  only  to  portions  to  be  altered,  added,  converted  or  repaired.       SECTION  104.  General  Building  Requirements     (a)  All  buildings  or  structures  as  well  as  accessory  facilities  thereto  shall  conform  in  all  respects  to  the  principles  of  safe  construction  and  must  be  suited  to  the  purpose  for  which  they  are  designed.     

  

1  

(b)  Buildings  or  structures  intended  to  be  used  for  the  manufacture  and/or  production  of  any  kind  of  article  or  product  shall  observe  adequate  environmental  safeguards.     (c)  Buildings  or  structures  and  all  parts  thereof  as  well  as  all  facilities  found  therein  shall  be  maintained  in  safe,  sanitary  and  good  working  condition.       SECTION  105.  Site  Requirements     The  land  or  site  upon  which  will  be  constructed  any  building  or  structure,  or  any  ancillary  or  auxillary  facility  thereto,  shall  be  sanitary,  hygienic  or  safe.  In  the  case  of  sites  or  buildings  intended  for  use  as  human  habitation  or  abode,  the  same  shall  be  at  a  safe  distance,  as  determined  by  competent  authorities,  from  streams  or  bodies  of  water  and/or  sources  of  air  considered  to  be  polluted;  from  a  volcano  or  volcanic  site  and/or  any  other  building  considered  to  be  a  potential  source  of  fire  or  explosion.       SECTION  106.  Definitions     As  used  in  this  Code,  the  words,  terms  and  phrases  enumerated  in  Annex  “A”  hereof  shall  have  the  meaning  or  definition,  correspondingly  provided  therein.       CHAPTER  2  ADMINISTRATION  AND  ENFORCEMENT    SECTION  201.  Responsibility  for  Administration  and  Enforcement     The  administration  and  enforcement  of  the  provisions  of  this  Code  including  the  imposition  of  penalties  for  administrative  violations  thereof  is  hereby  vested  in  the  Secretary  of  Public  Works,  Transportation  and  Communications,  hereinafter  referred  to  as  the  “Secretary”.       SECTION  202.  Technical  Staff     The  Secretary  is  hereby  authorized  to  constitute  and  provide  in  his  Department  a  professional  staff  composed  of  highly  qualified  architects,  engineers  and  technicians  who  possess  diversified  and  professional  experience  in  the  field  of  building  design  and  construction.       SECTION  203.  General  Powers  and  Functions  of  the  Secretary  under  this  Code     For  purposes  of  carrying  out  the  provisions  of  this  Code,  the  Secretary  shall  exercise  the  following  general  powers  and  functions:     (1)  Formulate  policies,  plans,  standards  and  guidelines  on  building  design,  construction,  use,  occupancy  and  maintenance,  in  accordance  with  this  Code.     (2)  Issue  and  promulgate  rules  and  regulations  to  implement  the  provisions  of  this  Code  and  ensure  compliance  with  policies,  plans,  standards  and  guidelines  formulated  under  paragraph  1  of  this  Section.     (3)  Evaluate,  review,  approve  and/or  take  final  action  on  changes  and/or  amendments  to  existing  Referral  Codes  as  well  as  on  the  incorporation  of  other  referral  codes  which  are  not  yet  expressly  made  part  of  this  Code.     (4)  Prescribe  and  fix  the  amount  of  fees  and  other  charges  that  the  Building  Official  shall  collect  in  connection  with  the  performance  of  regulatory  functions.       SECTION  204.  Professional  and  Technical  Assistance     The  Secretary  with  the  assistance  of  his  technical  staff  shall  provide  such  professional,  technical,  scientific  and  other  services  including  testing  laboratories  and  facilities  as  may  be  required  to  carry  out  the  provisions  of  this  Code;  Provided  that  the  Secretary  may  secure  such  services  as  he  may  deem  necessary  from  other  agencies  of  the  National  Government  and  may  make  arrangement  for  the  compensation  of  such  services.  He  may  also  engage  and  compensate  within  appropriations  available  therefore,  the  services  of  such  number  of  consultants,  experts  and  advisers  on  full  or  part-­‐  time  basis,  as  may  be  necessary,  coming  from  the  government  or  private  businesses,  entities  or  associations  to  carry  out  the  provisions  of  this  Code.     
  

  

2  

SECTION  205.  Building  Officials     Except  as  otherwise  provided  herein,  the  Building  Official  shall  be  responsible  for  carrying  out  the  provisions  of  this  Code  in  the  field  as  well  as  the  enforcement  of  orders  and  decisions  made  pursuant  thereto.     Due  to  the  exigencies  of  the  service,  the  Secretary  may  designate  incumbent  Public  Works  District  Engineers,  City  Engineers  and  Municipal  Engineers  to  act  as  Building  Officials  in  their  respective  areas  of  jurisdiction.     The  designation  made  by  the  Secretary  under  this  Section  shall  continue  until  regular  positions  of  Building  Official  are  provided  or  unless  sooner  terminated  for  causes  provided  by  law  or  decree.       SECTION  206.  Qualifications  of  Building  Officials     No  person  shall  be  appointed  as  a  Building  Official  unless  he  possesses  the  following  qualifications:     1.   A  Filipino  citizen  and  of  good  moral  character.  
2.   A  duly  registered  architect  or  civil  engineer.  
3.   A  member  of  good  standing  of  a  duly  accredited  organization  of  his  profession  for  not  less  than  two  years.  
4.   Has  at  least  five  years  of  diversified  and  professional  experience  in  building  design  and  construction.       SECTION  207.  Duties  of  a  Building  Official     In  his  respective  territorial  jurisdiction,  the  Building  Official  shall  be  primarily  responsible  for  the  enforcement  of  the  provisions  of  this  Code  as  well  as  of  the  implementing  rules  and  regulations  issued  therefor.  He  is  the  official  charged  with  the  duties  of  issuing  building  permits.     In  the  performance  of  his  duties,  a  Building  Official  may  enter  any  building  or  its  premises  at  all  reasonable  times  to  inspect  and  determine  compliance  with  the  requirements  of  this  Code,  and  the  terms  and  conditions  provided  for  in  the  building  permit  as  issued.     When  any  building  work  is  found  to  be  contrary  to  the  provisions  of  this  Code,  the  Building  Official  may  order  the  work  stopped  and  prescribe  the  terms  and/or  conditions  when  the  work  will  be  allowed  to  resume.  Likewise,  the  Building  Official  is  authorized  to  order  the  discontinuance  of  the  occupancy  or  use  of  any  building  or  structure  or  portion  thereof  found  to  be  occupied  or  used  contrary  to  the  provisions  of  this  Code.       SECTION  208.  Fees     Every  Building  Official  shall  keep  a  permanent  record  and  accurate  account  of  all  fees  and  other  charges  fixed  and  authorized  by  the  Secretary  to  be  collected  and  received  under  this  Code.     Subject  to  existing  budgetary,  accounting  and  auditing  rules  and  regulations,  the  Building  Official  is  hereby  authorized  to  retain  not  more  than  twenty  percent  of  his  collection  for  the  operating  expenses  of  his  office.     The  remaining  eighty  percent  shall  be  deposited  with  the  city  or  municipal  treasurer  and  shall  accrue  to  the  General  Fund  of  the  province,  city  or  municipality  concerned.       SECTION  209.  Exemption     Public  buildings  and  traditional  indigenous  family  dwellings  shall  be  exempt  from  payment  of  building  permit  fees.     As  used  in  this  Code,  the  term  “traditional  indigenous  family  dwelling”  means  a  dwelling  intended  for  the  use  and  occupancy  by  the  family  of  the  owner  only  and  constructed  of  native  materials  such  as  bamboo,  nipa,  logs,  or  lumber,  the  total  cost  of  which  does  not  exceed  fifteen  thousand  pesos.       SECTION  210.  Use  of  Income  from  Fees     Any  provision  of  law  to  the  contrary  notwithstanding,  the  Secretary  is  hereby  authorized  to  prescribe  the  procedures  for  the  use  of  all  net  income  realized  by  the  office  of  the  Building  Official  from  the  collection  of  fees  and  charges  not  exceeding  twenty  percent  thereof  in  accordance  with  Section  208.     Such  income  may  be  used  to  cover  necessary  operating  expenses  including  the  purchase  of  equipment,  supplies  and  materials,  traveling  expenses,  obligation  expenses  and  sheriff’s  fees  and  payment  of  other  

  

3  

prior  years’  obligations  not  adequately  funded,  subject  to  existing  budgetary  and  auditing  rules  and  regulations.       SECTION  211.  Implementing  Rules  and  Regulations     In  the  implementation  of  the  provisions  of  this  Code,  the  Secretary  shall  formulate  necessary  rules  and  regulations  and  adopt  design  and  construction  standards  and  criteria  for  buildings  and  other  structures.  
Such  standards,  rules  and  regulations  shall  take  effect  after  their  publication  once  a  week  for  three  consecutive  weeks  in  a  newspaper  of  general  circulation.       SECTION  212.  Administrative  Fines     For  the  violation  of  any  of  the  provisions  of  this  Code  or  any  of  the  rules  or  regulations  issued  thereunder,  the  Secretary  is  hereby  empowered  to  prescribe  and  impose  fines  not  exceeding  ten  thousand  pesos.       SECTION  213.  Penal  Provisions     It  shall  be  unlawful  for  any  person,  firm  or  corporation,  to  erect,  construct,  enlarge,  alter,  repair,  move,  improve,  remove,  convert,  demolish,  equip,  use,  occupy,  or  maintain  any  building  or  structure  or  cause  the  same  to  be  done  contrary  to  or  in  violation  of  any  provision  of  this  Code.     Any  person,  firm  or  corporation  who  shall  violate  any  of  the  provisions  of  this  Code  and/or  commit  any  act  hereby  declared  to  be  unlawful  shall  upon  conviction,  be  punished  by  a  fine  of  not  more  than  twenty  thousand  pesos  or  by  imprisonment  of  not  more  than  two  years  or  by  both  such  fine  and  imprisonment:  Provided,  that  in  the  case  of  a  corporation  firm,  partnership  or  association,  the  penalty  shall  be  imposed  upon  its  officials  responsible  for  such  violation  and  in  case  the  guilty  party  is  an  alien,  he  shall  immediately  be  deported  after  payment  of  the  fine  and/or  service  of  his  sentence.       SECTION  214.  Dangerous  and  Ruinous  Buildings  or  Structures     Dangerous  buildings  are  those  which  are  herein  declared  as  such  or  are  structurally  unsafe  or  not  provided  with  safe  egress,  or  which  constitute  a  fire  hazard,  or  are  otherwise  dangerous  to  human  life,  or  which  in  relation  to  existing  use,  constitute  a  hazard  to  safety  or  health  or  public  welfare  because  of  inadequate  maintenance,  dilapidation,  obsolescence,  or  abandonment;  or  which  otherwise  contribute  to  the  pollution  of  the  site  or  the  community  to  an  intolerable  degree.       SECTION  215.  Abatement  of  Dangerous  Buildings     When  any  building  or  structure  is  found  or  declared  to  be  dangerous  or  ruinous,  the  Building  Official  shall  order  its  repair,  vacation  or  demolition  depending  upon  the  degree  of  danger  to  life,  health,  or  safety.  This  is  without  prejudice  to  further  action  that  may  be  taken  under  the  provisions  of  Articles  482  and  694  to  707  of  the  Civil  Code  of  the  Philippines.       SECTION  216.  Other  Remedies     The  rights,  actions  and  remedies  provided  in  this  Code  shall  be  in  addition  to  any  and  all  other  rights  of  action  and  remedies  that  may  be  available  under  existing  laws.       CHAPTER  3  PERMITS  AND  INSPECTION    SECTION  301.  Building  Permits     No  person,  firm  or  corporation,  including  any  agency  or  instrumentality  of  the  government  shall  erect,  construct,  alter,  repair,  move,  convert  or  demolish  any  building  or  structure  or  cause  the  same  to  be  done  without  first  obtaining  a  building  permit  therefor  from  the  Building  Official  assigned  in  the  place  where  the  subject  building  is  located  or  the  building  work  is  to  be  done.       SECTION  302.  Application  for  Permits     

  

4  

In  order  to  obtain  a  building  permit,  the  applicant  shall  file  an  application  therefor  in  writing  and  on  the  prescribed  form  from  the  Office  of  the  Building  Official.  Every  application  shall  provide  at  least  the  following  information:     (1)  A  description  of  the  work  to  be  covered  by  the  permit  applied  for;     (2)  Certified  true  copy  of  the  TCT  covering  the  lot  on  which  the  proposed  work  is  to  be  done.  If  the  applicant  is  not  the  registered  owner,  in  addition  to  the  TCT,  a  copy  of  the  contract  of  lease  shall  be  submitted;     (3)  The  use  or  occupancy  for  which  the  proposal  work  is  intended;  (4)  Estimated  cost  of  the  proposed  work.  
To  be  submitted  together  with  such  application  are  at  least  five  sets  of  corresponding  plans  and  specifications  prepared,  signed  and  sealed  by  a  duly  registered  mechanical  engineer  in  case  of  mechanical  plans,  and  by  a  registered  electrical  engineer  in  case  of  electrical  plans,  except  in  those  cases  exempted  or  not  required  by  the  Building  Official  under  this  Code.       SECTION  303.  Processing  of  Building  Permits     The  processing  of  building  permits  shall  be  under  the  overall  administrative  control  and  supervision  of  the  Building  Official  and  his  technical  staff  of  qualified  professionals.     In  processing  an  application  for  a  building  permit,  the  Building  Official  shall  see  to  it  that  the  applicant  satisfies  and  conforms  with  approved  standard  requirements  on  zoning  and  land  use,  lines  and  grades,  structural  design,  sanitary  and  sewerage,  environmental  health,  electrical  and  mechanical  safety  as  well  as  with  other  rules  and  regulations  promulgated  in  accordance  with  the  provisions  of  this  Code.       SECTION  304.  Issuance  of  Building  Permits     When  satisfied  that  the  work  described  in  an  application  for  building  permit  and  the  plans  and  specifications  submitted  therewith,  conform  to  the  requirements  of  this  Code  and  other  pertinent  rules  and  regulations,  the  Building  Official  shall,  within  fifteen  days  from  payment  of  the  required  fees  by  the  applicant,  issue  the  building  permit  applied  for.     The  Building  Official  may  issue  a  permit  for  the  construction  of  only  a  part  or  portion  of  a  building  or  structure  whenever  the  plans  and  specifications  submitted  together  with  the  application  do  not  cover  the  entire  building  or  structure.     Approved  plans  and  specifications  shall  not  be  changed,  modified  or  altered  without  the  approval  of  the  Building  Official  and  the  work  shall  be  done  strictly  in  accordance  thereto.       SECTION  305.  Validity  of  Building  Permits     The  issuance  of  a  building  permit  shall  not  be  construed  as  an  approval  or  authorization  to  the  permittee  to  disregard  or  violate  any  of  the  provisions  of  this  Code.     Whenever  the  issuance  of  a  permit  is  based  on  approved  plans  and  specifications  which  are  subsequently  found  defective,  the  Building  Official  is  not  precluded  from  requiring  permittee  to  effect  the  necessary  corrections  in  said  plans  and  specifications  or  from  preventing  or  ordering  the  stoppage  of  any  or  all  building  operations  being  carried  on  thereunder  which  are  in  violation  of  this  Code.     A  building  permit  issued  under  the  provisions  of  this  Code  shall  expire  and  become  null  and  void  if  the  building  or  work  authorized  therein  is  not  commenced  within  a  period  of  one  year  from  the  date  of  such  permit,  or  if  the  building  or  work  so  authorized  is  suspended  or  abandoned  at  any  time  after  it  has  been  commenced,  for  a  period  of  120  days.       SECTION  306.  Non-­‐Issuance,  Suspension  or  Revocation  of  Building  Permits     The  Building  Official  may  order  or  cause  the  non-­‐issuance,  suspension  or  revocation  of  building  permits  on  any  or  all  of  the  following  reasons  or  grounds:     (a)     Errors  found  in  the  plans  and  specifications;     (b)     Incorrect  or  inaccurate  data  or  information  supplied;     (c)     Non-­‐compliance  with  the  provisions  of  this  Code  or  of  any  rule  or  regulation.     Notice  of  non-­‐issuance,  suspension  or  revocation  of  building  permits  shall  always  be  made  in  writing,  stating  the  reason  or  grounds  therefor.     
  

  

5  

SECTION  307.  Appeal     Within  fifteen  (15)  days  from  the  date  of  receipt  of  advice  of  the  non-­‐issuance,  suspension  or  revocation  of  permits,  the  applicant/permittee  may  file  an  appeal  with  the  Secretary  who  shall  render  his  decision  within  fifteen  days  from  date  of  receipt  of  notice  of  appeal.  The  decision  of  the  Secretary  shall  be  final  subject  only  to  review  by  the  Office  of  the  President.  
  SECTION  308.  Inspection  and  Supervision  of  Work     The  owner  of  the  Building  who  is  issued  or  granted  a  building  permit  under  this  Code  shall  engage  the  services  of  a  duly  licensed  architect  or  civil  engineer  to  undertake  the  full  time  inspection  and  supervision  of  the  construction  work.     Such  architect  or  civil  engineer  may  or  may  not  be  the  same  architect  or  civil  engineer  who  is  responsible  for  the  design  of  the  building.     It  is  understood  however  that  in  either  case,  the  designing  architect  or  civil  engineer  is  not  precluded  from  conducting  inspection  of  the  construction  work  to  check  and  determine  compliance  with  the  plans  and  specifications  of  the  building  as  submitted.     There  shall  be  kept  at  the  jobsite  at  all  times  a  logbook  wherein  the  actual  progress  of  construction  including  tests  conducted,  weather  conditions  and  other  pertinent  data  are  to  be  recorded.     Upon  completion  of  the  construction,  the  said  licensed  architect  or  civil  engineer  shall  submit  the  logbook,  duly  signed  and  sealed,  to  the  Building  Official.  He  shall  also  prepare  and  submit  a  Certificate  of  Completion  of  the  project  stating  that  the  construction  of  building  conforms  to  the  provisions  of  this  Code  as  well  as  with  the  approved  plans  and  specifications.       SECTION  309.  Certificate  of  Occupancy     No  building  or  structure  shall  be  used  or  occupied  and  no  change  in  the  existing  use  or  occupancy  classification  of  a  building  or  structure  or  portion  thereof  shall  be  made  until  the  Building  Official  has  issued  a  Certificate  of  Occupancy  therefor  as  provided  in  this  Code.     A  Certificate  of  Occupancy  shall  be  issued  by  the  Building  Official  within  thirty  (30)  days  if  after  final  inspection  and  submittal  of  a  Certificate  of  Completion  referred  to  in  the  preceding  Section,  it  is  found  that  the  building  or  structure  complies  with  the  provisions  of  this  Code.     The  Certificate  of  Occupancy  shall  be  posted  or  displayed  in  a  conspicuous  place  on  the  premises  and  shall  not  be  removed  except  upon  order  of  the  Building  Official.     The  non-­‐issuance,  suspension  and  revocation  of  Certificates  of  Occupancy  and  the  procedure  for  appeal  therefrom  shall  be  governed  in  so  far  as  applicable,  by  the  provisions  of  Section  306  and  307  of  this  Code.       CHAPTER  4  TYPES  OF  CONSTRUCTION    SECTION  401.  Types  of  Construction     For  purposes  of  this  Code,  all  buildings  proposed  for  construction  shall  be  classified  or  identified  according  to  the  following  types:     (1)  Type  I  –  Type  I  buildings  shall  be  of  wood  construction.  The  structural  elements  may  be  any  of  the  materials  permitted  by  this  Code.     (2)  Type  II  –  Type  II  buildings  shall  be  of  wood  construction  with  protective  fire-­‐resistant  materials  and  one-­‐hour  fire-­‐resistive  throughout:  Except,  that  permanent  non-­‐bearing  partitions  may  use  fire-­‐retardant  treated  wood  within  the  framing  assembly.     (3)  Type  III  –  Type  III  buildings  shall  be  of  masonry  and  wood  construction.  Structural  elements  may  be  any  of  the  materials  permitted  by  this  Code:  Provided,  that  the  building  shall  be  one-­‐hour  fire-­‐resistive  throughout.  Exterior  walls  shall  be  of  incombustible  fire-­‐resistive  construction.     (4)  Type  IV  –  Type  IV  buildings  shall  be  of  steel,  iron,  concrete,  or  masonry  construction.  Walls,  ceilings,  and  permanent  partitions  shall  be  of  incombustible  fire-­‐resistive  construction:  Except,  that  permanent  non-­‐bearing  partitions  of  one-­‐hour  fire-­‐resistive  construction  may  use  fire-­‐retardant  treated  wood  within  the  framing  assembly.     

  

6  

(5)  Type  V  –  Type  V  buildings  shall  be  fire-­‐resistive.  The  structural  elements  shall  be  of  steel,  iron,  concrete,  or  masonry  construction.  Walls,  ceilings,  and  permanent  partitions  shall  be  of  incombustible  fire-­‐resistive  construction.       SECTION  402.  Changes  in  Types  No  change  shall  be  made  in  the  type  of  construction  of  any  building  which  would  place  the  building  in  a  different  sub-­‐type  or  type  of  construction  unless  such  building  is  made  to  comply  with  the  requirements  for  such  sub-­‐type  of  construction:  Except,  when  the  changes  is  approved  by  the  Building  Official  upon  showing  that  the  new  or  proposed  construction  is  less  hazardous,  based  on  life  and  fire  risk,  than  the  existing  construction.  
  SECTION  403.  Requirements  on  Type  of  Construction     Subject  to  the  provisions  of  this  Chapter,  the  Secretary  shall  prescribe  standards  for  each  type  of  construction,  and  promulgate  rules  and  regulations  therefor,  relating  to  structural  framework,  exterior  walls  and  openings,  interior  walls  and  enclosures,  floors,  exits  and  stairs  construction,  and  roofs.       CHAPTER  5  REQUIREMENTS  FOR  FIRE  ZONES    SECTION  501.  Fire  Zones  Defined     Fire  zones  are  areas  within  which  only  certain  types  of  buildings  are  permitted  to  be  constructed  based  on  their  use  or  occupancy,  type  of  construction,  and  resistance  to  fire.  
  SECTION  502.  Buildings  located  in  more  than  One  Fire  Zone     A  building  or  structure  which  is  located  partly  in  one  fire  zone  and  partly  in  another  shall  be  considered  to  be  in  the  more  highly  restrictive  fire  zone,  when  more  than  one-­‐third  of  its  total  floor  area  is  located  in  such  zone.       SECTION  503.  Moved  Building     Any  building  or  structure  moved  within  or  into  any  fire  zone  shall  be  made  to  comply  with  all  the  requirements  for  buildings  in  that  fire  zone.       SECTION  504.  Temporary  Buildings     Temporary  buildings  such  as  reviewing  stands  and  other  miscellaneous  structures  conforming  to  the  requirements  of  this  Code,  and  sheds,  canopies  and  fences  used  for  the  protection  of  the  public  around  and  in  conjunction  with  construction  work,  may  be  erected  in  the  fire  zones  by  special  permit  from  the  Building  Official  for  a  limited  period  of  time,  and  such  buildings  or  structures  shall  be-­‐  completely  removed  upon  the  expiration  of  the  time  limit  stated  in  such  permits.       SECTION  505.  Center  Lines  of  Streets     For  the  purpose  of  this  Chapter,  the  center  line  of  an  adjoining  street  or  alley  may  be  considered  an  adjacent  property  line.  Distances  shall  be  measured  at  right  angles  to  the  street  or  alley.       SECTION  506.  Restrictions  on  Existing  Buildings     Existing  buildings  or  structures  in  fire  zones  that  do  not  comply  with  the  requirements  for  a  new  building  erected  therein  shall  not  hereafter  be  enlarged,  altered,  remodeled,  repaired  or  moved  except  as  follows:     (a)  Such  building  is  entirely  demolished;     (b)  Such  building  is  to  be  moved  outside  the  limits  of  the  more  highly  restrictive  Fire  Zone  to  a  zone  where  the  building  meets  the  minimum  standards;     (c)  Changes,  alterations  and  repairs  may  be  made  provided  that  in  any  12-­‐month  period,  the  value  of  the  work  does  not  exceed  twenty  percent  of  the  value  of  the  existing  building,  and  provided  that,  such  changes  do  not  add  additional  combustible  material,  and  do  not,  in  the  opinion  of  the  Building  Official,  increase  the  fire  hazard;     

  

7  

(d)  Additions  thereto  are  separated  from  the  existing  building  by  fire  walls,  as  set  forth  in  Sub-­‐section  604  (b);     (e)  Damage  from  fire  or  earthquake,  typhoons  or  any  fortuitous  event  may  be  repaired,  using  the  same  kind  of  materials  of  which  the  building  or  structure  was  originally  constructed,  provided  that,  the  cost  of  such  repair  shall  not  exceed  twenty  percent  of  the  replacement  cost  of  the  building  or  structure.       SECTION  507.  Designation  of  Fire  Zones     The  Secretary  shall  promulgate  specific  restrictions  for  each  type  of  Fire  Zone.  Cities  and  municipalities  shall  be  divided  into  such  Fire  Zones  in  accordance  with  local,  physical,  and  spatial  framework  plans  submitted  by  city  or  municipal  planning  and/or  development  bodies.       CHAPTER  6  FIRE-­‐RESISTIVE  REQUIREMENTS  IN  CONSTRUCTION    SECTION  601.  Fire-­‐Resistive  Rating  defined     Fire-­‐resistive  rating  means  the  degree  to  which  a  material  can  withstand  fire  as  determined  by  generally  recognized  and  accepted  testing  methods.       SECTION  602.  Fire-­‐Resistive  Time  Period  Rating     Fire-­‐resistive  time  period  rating  is  the  length  of  time  a  material  can  withstand  being  burned  which  may  be  one-­‐hour,  two-­‐hours,  three-­‐hours,  four-­‐hours,  etc.       SECTION  603.  Fire-­‐Resistive  Standards     All  materials  of  construction,  and  assemblies  or  combinations  thereof  shall  be  classified  according  to  their  fire-­‐retardant  or  flame-­‐spread  ratings  as  determined  by  general  accepted  testing  methods  and/or  by  the  Secretary.       SECTION  604.  Fire-­‐Resistive  Regulations     The  Secretary  shall  prescribe  standards  and  promulgate  rules  and  regulations  on  the  testing  of  construction  materials  for  flame-­‐spread  characteristics,  tests  on  fire  damages,  fire  tests  of  building  construction  and  materials,  door  assemblies  and  tinclad  fire  doors  and  window  assemblies,  the  installation  of  fire  doors  and  windows  and  smoke  and  fire  detectors  for  fire  protective  signaling  system,  application  and  use  of  controlled  interior  finish,  fire-­‐resistive  protection  for  structural  members,  fire-­‐resistive  walls  and  partitions,  fire-­‐resistive  floor  or  roof  ceiling,  fire-­‐resistive  assemblies  for  protection  of  openings  and  fire-­‐retardant  roof  coverings.       CHAPTER  7  CLASSIFICATION  AND  GENERAL  REQUIREMENT  OF  ALL  BUILDINGS  BY  USE  OR  OCCUPANCY    SECTION  701.  Occupancy  Classified     (a)  Buildings  proposed  for  construction  shall  be  identified  according  to  their  use  or  the  character  of  its  occupancy  and  shall  be  classified  as  follows:     (1)  Group  A  –  Residential  Dwellings     Group  A  Occupancies  shall  be  dwellings.  
(2)  Group  B  –  Residentials,  Hotels  and  Apartments     Group  B  Occupancies  shall  be  multiple  dwelling  units  including  boarding  or  lodging  houses,  hotels,  apartment  buildings,  row  houses,  convents,  monasteries  and  other  similar  building  each  of  which  accommodates  more  than  10  persons.     (3)  Group  C  –  Education  and  Recreation        Group  C  Occupancies  shall  be  buildings  used  for  school  or  day-­‐care  purposes,  involving  assemblage  for  instruction,  education,  or  recreation,  and  not  classified  in  Group  I  or  in  Division  1  and  2  or  Group  H  Occupancies.     

  

8  

(4)  Group  D  –  Institutional  Group  D  Occupancies  shall  include:     Division  1  –  Mental  hospitals,  mental  sanitaria,  jails,  prisons,  reformatories,  and  buildings  were  personal  liberties  of  inmates  are  similarly  restrained.     Division  2  –  Nurseries  for  full-­‐time  care  of  children  under  kindergarten  age,  hospitals,  sanitaria,  nursing  homes  with  non-­‐ambulatory  patients,  and  similar  buildings  each  accommodating  more  than  five  persons.     Division  3  –  Nursing  homes  for  ambulatory  patients,  homes  for  children  of  kindergarten  age  or  over,  each  accommodating  more  than  five  persons:  Provided,  that  Group  D  Occupancies  shall  not  include  buildings  used  only  for  private  or  family  group  dwelling  purposes.     (5)  Group  E  –  Business  and  Mercantile  Group  E  Occupancies  shall  include:     Division  1  –  Gasoline  filling  and  service  stations,  storage  garages  and  boat  storage  structures  where  no  work  is  done  except  exchange  of  parts  and  maintenance  requiring  no  open  flame,  welding,  or  the  use  of  highly  flammable  liquids.     Division  2  –  Wholesale  and  retail  stores,  office  buildings,  drinking  and  dining  establishments  having  an  occupant  load  of  less  than  one  hundred  persons,  printing  plants,  police  and  fire  stations,  factories  and  workshops  using  not  highly  flammable  or  combustible  materials  and  paint  stores  without  bulk  handlings.     Division  3  –  Aircraft  hangars  and  open  parking  garages  where  no  repair  work  is  done  except  exchange  of  parts  and  maintenance  requiring  no  open  flame,  welding  or  the  use  of  highly  flammable  liquids.  
(6)  Group  F  –  Industrial  Group  F  Occupancies  shall  include:  ice  plants,  power  plants,  pumping  plants,  cold  storage,  and  creameries,  factories  and  workshops  using  incombustible  and  non-­‐explosive  materials,  and  storage  and  sales  rooms  for  incombustible  and  non-­‐explosive  materials.     (7)  Group  G  –  Storage  and  Hazardous  Groups  G  Occupancies  shall  include:     Division  1  –  Storage  and  handling  of  hazardous  and  highly  flammable  material.     Division  2  –  Storage  and  handling  of  flammable  materials,  dry  cleaning  plants  using  flammable  liquids;  paint  stores  with  bulk  handling,  paint  shops  and  spray  painting  rooms.     Division  3  –  Wood  working  establishments,  planning  mills  and  box  factories,  shops,  factories  where  loose  combustible  fibers  or  dust  are  manufactured,  processed  or  generated;  warehouses  where  highly  combustible  materials  is  stored.     Division  4  –  Repair  garages.     Division  5  –  Aircrafts  repair  hangars.  
(8)  Group  H  –  Assembly  Other  Than  Group  I  Group  H  Occupancies  shall  include:     Division  1  –  Any  assembly  building  with  a  stage  and  an  occupant  load  of  less  than  1000  in  the  building.     Division  2  –  Any  assembly  building  without  stage  and  having  an  occupant  load  of  300  or  more  in  the  building.     Division  3  –  Any  assembly  building  without  a  stage  and  having  an  occupant  load  of  less  than  300  in  the  building.     Division  4  –  Stadia,  reviewing  stands,  amusement  park  structures  not  included  within  Group  I  or  in  Division  1,  2,  and  3  of  this  Group.  
(9)  Group  I  –  Assembly  Occupant  Load  1000  or  More  Group  I  Occupancies  shall  be  any  assembly  building  with  a  stage  and  an  occupant  load  of  1000  or  more  in  the  building.     (10)  Group  J  –  Accessory  Group  J  Occupancies  shall  include:     Division  1  –  Private  garage,  carports,  sheds  and  agricultural  buildings.     Division  2  –  Fences  over  1.80  m  high,  tanks  and  towers.  
(b)  Other  subgroupings  or  divisions  within  Groups  A  to  J  may  be  determined  by  the  Secretary.     

  

9  

Any  other  occupancy  not  mentioned  specifically  in  this  Section,  or  about  which  there  is  any  question,  shall  be  included  in  the  Group  which  it  most  nearly  resembles  based  on  the  existing  or  proposed  life  and  fire  hazard.       SECTION  702.  Change  in  Use     No  change  shall  be  made  in  the  character  of  occupancy  or  use  of  any  building  which  would  place  the  building  in  a  different  division  of  the  same  group  of  occupancy  or  in  a  different  group  of  occupancies,  unless  such  building  is  made  to  comply  with  the  requirements  of  this  Code  for  such  division  or  group  of  occupancy.  The  character  of  occupancy  of  existing  buildings  may  be  changed  subject  to  the  approval  of  the  Building  Official  and  the  building  may  be  occupied  for  purposes  set  forth  in  other  Groups:  Provided  the  new  or  proposed  use  is  less  hazardous,  based  on  life  and  fire  risk,  than  the  existing  use.       SECTION  703.  Mixed  Occupancy     (a)  General  Requirements     When  a  building  is  of  mixed  occupancy  or  used  for  more  than  one  occupancy,  the  whole  building  shall  be  subject  to  the  most  restrictive  requirement  pertaining  to  any  of  the  type  of  occupancy  found  therein  except  in  the  following:     (1)  When  a  one-­‐storey  building  houses  more  than  one  occupancy,  each  portion  of  the  building  shall  conform  to  the  requirement  of  the  particular  occupancy  housed  therein  and;     (2)  Where  minor  accessory  uses  do  not  occupy  more  than  ten  percent  of  the  area  of  any  floor  or  a  building,  nor  more  than  ten  percent  of  the  basic  area  permitted  in  the  occupancy  requirements,  in  which  case,  the  major  use  of  the  building  shall  determine  the  occupancy  classification.     (b)  Forms  of  Occupancy  Separation     Occupancy  separations  shall  be  vertical  or  horizontal  or  both,  or  when  necessary,  of  such  other  forms  as  may  be  required  to  afford  a  complete  separation  between  the  various  occupancy  divisions  in  the  building.     (c)  Types  of  Occupancy  Separation     Occupancy  separation  shall  be  classified  as  “One-­‐Hour  Fire-­‐Resistive”,  “Two-­‐Hour  Fire-­‐  Resistive”,  “Three-­‐Hour  Fire-­‐Resistive”  and  “Four-­‐Hour  Fire-­‐Resistive.”     (1)  A  “One-­‐Hour  Fire-­‐Resistive  Occupancy  Separation”  shall  be  of  not  less  than  one-­‐hour  fire-­‐resistive  construction.  All  openings  in  such  separation  shall  be  protected  by  a  fire-­‐  assembly  having  a  one-­‐hour  fire-­‐resistive  rating.     (2)  A  “Two-­‐Hour  Fire-­‐Resistive  Occupancy  Separation”  shall  be  of  not  less  than  two-­‐hour  fire-­‐resistive  construction.  All  openings  in  such  separation  shall  be  protected  by  a  fire  assembly  having  a  two-­‐hour  fire-­‐resistive  rating.     (3)  A  “Three-­‐Hour  Fire-­‐Resistive  Occupancy  Separation”  shall  be  of  not  less  than  three-­‐  hour  fire-­‐resistive  construction.  All  openings  in  walls  forming  such  separation  shall  be  protected  by  a  fire  assembly  having  a  three-­‐hour  fire-­‐resistive  rating.  The  total  width  of  all  openings  in  any  three-­‐hour  fire-­‐resistive  occupancy  separation  wall  in  any  one-­‐storey  shall  not  exceed  25  percent  of  the  length  of  the  wall  in  that  storey  and  no  single  opening  shall  have  an  area  greater  than  10.00  square  m.  All  openings  in  floors  forming  a  “Three-­‐Hour  Fire-­‐  Resistive  Occupancy  Separation”  shall  be  protected  by  vertical  enclosures  extending  above  and  below  such  openings.  The  walls  of  such  vertical  enclosures  shall  be  of  not  less  than  two-­‐  hour  fire-­‐resistive  construction,  and  all  openings  therein  shall  be  protected  by  a  fire  assembly  having  a  three-­‐hour  fire-­‐resistive  rating.     (4)  A  “Four-­‐Hour  Fire-­‐Resistive  Occupancy  Separation”  shall  have  no  openings  therein  and  shall  be  of  not  less  than  four-­‐hour  fire-­‐resistive  construction.     (d)  Fire  Rating  for  Occupancy  Separation     Occupancy  Separations  shall  be  provided  between  groups,  subgroupings,  or  divisions  of  occupancies.  
The  Secretary  shall  promulgate  rules  and  regulations  for  appropriate  occupancy  separations  in  buildings  of  mixed  occupancy;  Provided,  that,  where  any  occupancy  separation  is  required,  the  minimum  shall  be  a  “One-­‐Hour  Fire-­‐Resistive  Occupancy  Separation”;  and  where  the  occupancy  separation  is  horizontal,  structural  members  supporting  the  separation  shall  be  protected  by  an  equivalent  fire-­‐resistive  construction.     
  

  

10  

SECTION  704.  Location  on  Property     (a)  General     No  building  shall  be  constructed  unless  it  adjoins  or  has  direct  access  to  a  public  space,  yard  or  street  on  at  least  one  of  its  sides.     For  the  purpose  of  this  Section,  the  center  line  of  an  adjoining  street  or  alley  shall  be  considered  an  adjacent  property  line.     Eaves  over  required  windows  shall  not  be  less  than  750  mm  from  the  side  and  rear  property  lines.     (b)  Fire  Resistance  of  Walls  Exterior  walls  shall  have  fire  resistance  and  opening  protection  in  accordance  with  the  requirements  set  forth  by  the  Secretary.  Projections  beyond  the  exterior  wall  shall  not  exceed  beyond  a  point  one-­‐third  the  distance  from  an  assumed  vertical  plane  located  where  the  fire-­‐resistive  protection  of  openings  is  first  required  to  the  location  on  property  whichever  is  the  least  restrictive.  Distance  shall  be  measured  at  right  angles  from  the  property  line.  When  openings  in  exterior  walls  are  required  to  be  protected  due  to  distance  from  property  line,  the  sum  of  the  areas  of  such  openings  in  any  storey  shall  not  exceed  50  percent  of  the  total  area  of  the  wall  in  that  storey.     (c)  Buildings  on  Same  Property  and  Buildings  Containing  Courts     For  the  purpose  of  determining  the  required  wall  and  opening  protection,  buildings  on  the  same  property  and  court  walls  shall  be  assumed  to  have  a  property  line  between  them.  When  a  new  building  is  to  be  erected  on  the  same  property  with  an  existing  building,  the  assumed  property  line  from  the  existing  building  shall  be  the  distance  to  the  property  line  for  each  occupancy  as  set  forth  by  the  Secretary:  Provided,  that  two  or  more  buildings  on  the  same  property  may  be  considered  as  one  building  if  the  aggregate  area  of  such  building  is  within  the  limits  of  allowable  floor  areas  for  a  single  building,  and  when  the  buildings  so  considered,  house  different  occupancies  or  are  of  different  types  of  construction,  the  area  shall  be  that  allowed  for  the  most  restrictive  occupancy  or  construction.       SECTION  705.  Allowable  Floor  Areas     The  allowable  floor  areas  for  one-­‐storey  building  and  buildings  over  one-­‐storey  shall  not  exceed  the  limits  prescribed  by  the  Secretary  for  each  occupancy  groups  and/or  types  of  construction.  For  purposes  of  this  Section,  each  portion  of  a  building  separated  by  one  or  more  area  separation  walls  may  be  considered  a  separate  building  provided  the  area  separation  walls  meet  the  requirements  prescribed  therefor  by  the  Secretary.       SECTION  706.  Allowable  Floor  Area  Increases     The  floor  areas  hereinabove  provided  may  be  increased  in  certain  specific  instances  and  under  appropriate  conditions,  based  on  the  existence  of  public  space,  streets  or  yards  extending  along  and  adjoining  two  or  more  sides  of  the  building  or  structure  subject  to  the  approval  of  the  Building  Official.       SECTION  707.  Maximum  Height  of  Buildings     The  maximum  height  and  number  of  storeys  of  every  building  shall  be  dependent  upon  the  character  of  occupancy  and  the  type  of  construction  as  determined  by  the  Secretary  considering  population  density,  building  bulk,  widths  of  streets  and  car  parking  requirements.  The  height  shall  be  measured  from  the  highest  adjoining  sidewalk  or  ground  surface:  Provided,  that  the  height  measured  from  the  lowest  adjoining  surface  shall  not  exceed  such  maximum  height  by  more  than  3.00  m:  Except,  that  towers,  spires,  and  steeples,  erected  as  part  of  a  building  and  not  used  for  habitation  or  storage  are  limited  as  to  height  only  by  structural  design  if  completely  of  incombustible  materials,  or  may  extend  not  to  exceed  6.00  m  above  the  height  limits  for  each  occupancy  group  if  of  combustible  materials.       SECTION  708.  Minimum  Requirements  for  Group  A  Dwellings     (a)  Dwelling  Location  and  Lot  Occupancy     The  dwelling  shall  occupy  not  more  than  ninety  percent  of  a  corner  lot  and  eighty  percent  of  an  inside  lot,  and  subject  to  the  provisions  on  Easements  of  Light  and  View  of  the  Civil  Code  of  Philippines,  shall  be  at  least  2  m  from  the  property  line.     (b)  Light  and  Ventilation  

  

11  

Every  dwelling  shall  be  so  constructed  and  arranged  as  to  provide  adequate  light  and  ventilation  as  provided  under  Section  805  to  Section  811,  of  this  Code.     (c)  Sanitation     Every  dwelling  shall  be  provided  with  at  least  one  sanitary  toilet  and  adequate  washing  and  drainage  facilities.     (d)  Foundation  Footings  shall  be  of  sufficient  size  and  strength  to  support  the  load  of  the  dwelling  and  shall  be  at  least  250  mm  thick  and  600  mm  below  the  surface  of  the  ground.     (e)  Post     The  dimensions  of  wooden  posts  shall  be  those  found  in  Table  708-­‐A:  Dimensions  of  Wooden  Posts  (Annex  B-­‐1).  Each  post  shall  be  anchored  to  such  footing  by  straps  and  bolts  of  adequate  size.     (f)  Floor     The  live  load  of  the  first  floor  shall  be  at  least  200  kilograms  per  square  m  and  for  the  second  floor,  at  least  150  kilograms  per  square  m.     (g)  Roof  The  wind  load  for  roofs  shall  be  at  least  120  kilograms  per  square  m  for  vertical  projection.  
(h)  Stairs     Stairs  shall  be  at  least  750  mm  in  clear  width,  with  a  rise  of  200  mm  and  a  minimum  run  of  200  mm.     (i)  Entrance  and  Exit     There  shall  be  at  least  one  entrance  and  another  one  for  exit.     (j)  Electrical  Requirements     All  electrical  installation  shall  conform  to  the  requirements  of  the  Philippine  Electrical  Code.     (k)  Mechanical  Requirements     Mechanical  systems  and/or  equipment  installation  shall  be  subject  to  the  requirement  of  the  Philippine  Mechanical  Engineering  Code.       SECTION  709.  Requirements  for  Other  Group  Occupancies     Subject  to  the  provisions  of  this  Code,  the  Secretary  shall  promulgate  rules  and  regulations  for  each  of  the  other  Group  Occupancies  covering:  allowable  construction,  height,  and  area;  location  on  property,  exit  facilities,  light,  ventilation,  and  sanitation;  enclosures  of  vertical  openings;  fire  extinguishing  systems;  and  special  hazards.       CHAPTER  8  LIGHT  AND  VENTILATION    SECTION  801.  General  Requirements  of  Light  and  Ventilation     (a)  Subject  to  the  provisions  of  the  Civil  Code  of  the  Philippines  on  Easements  of  Light  and  View,  and  to  the  provisions  of  this  part  of  the  Code,  every  building  shall  be  designed,  constructed,  and  equipped  to  provide  adequate  light  and  ventilation.     (b)  All  buildings  shall  face  a  street  or  public  alley  or  a  private  street  which  has  been  duly  approved.     (c)  No  building  shall  be  altered  nor  arranged  so  as  to  reduce  the  size  of  any  room  or  the  relative  area  of  windows  to  less  than  that  provided  for  buildings  under  this  Code,  or  to  create  an  additional  room,  unless  such  additional  room  conforms  to  the  requirements  of  this  Code.     (d)  No  building  shall  be  enlarged  so  that  the  dimensions  of  the  required  court  or  yard  would  be  less  than  that  prescribed  for  such  building.       SECTION  802.  Measurement  of  Site  Occupancy     (a)  The  measurement  of  site  occupancy  or  lot  occupancy  shall  be  taken  at  the  ground  level  and  shall  be  exclusive  of  courts,  yards,  and  light  wells.     (b)  Courts,  yards,  and  light  wells  shall  be  measured  clear  of  all  projections  from  the  walls  enclosing  such  wells  or  yards  with  the  exception  of  roof  leaders,  wall  copings,  sills,  or  steel  fire  escapes  not  exceeding  1.20  m  in  width.       SECTION  803.  Percentage  of  Site  Occupancy     

  

12  

(a)  Minimum  site  occupancy  shall  be  governed  by  the  use,  type  of  construction,  and  height  of  the  building  and  the  use,  area,  nature,  and  location  of  the  site;  and  subject  to  the  provisions  of  the  local  zoning  requirements  and  in  accordance  with  the  rules  and  regulations  promulgated  by  the  Secretary.       SECTION  804.  Size  and  Dimensions  of  Courts     (a)  Minimum  size  of  courts  and  their  least  dimensions  shall  be  governed  by  the  use,  type  of  construction,  and  height  of  the  building  as  provided  in  the  rules  and  regulations  promulgated  by  the  Secretary,  provided  that  the  minimum  horizontal  dimension  of  court  shall  be  not  less  than  2.00  m.     (b)  All  inner  courts  shall  be  connected  to  a  street  or  yard,  either  by  a  passageway  with  a  minimum  width  of  1.20  m  or  by  a  door  through  a  room  or  rooms.       SECTION  805.  Ceiling  Heights     (a)  Habitable  rooms  provided  with  artificial  ventilation  shall  have  ceiling  heights  not  less  than  2.40  m  measured  from  the  floor  to  the  ceiling;  Provided  that  for  buildings  of  more  than  one-­‐  storey,  the  minimum  ceiling  height  of  the  first  storey  shall  be  2.70  m  and  that  for  the  second  storey  2.40  m  and  succeeding  storeys  shall  have  an  unobstructed  typical  head-­‐room  clearance  of  not  less  than  2.10  m  above  the  finished  floor.  Above  stated  rooms  with  a  natural  ventilation  shall  have  ceiling  heights  not  less  than  2.70  m.     (b)  Mezzanine  floors  shall  have  a  clear  ceiling  height  not  less  than  1.80  m  above  and  below  it.       SECTION  806.  Size  and  Dimension  of  Rooms     Minimum  sizes  of  rooms  and  their  least  horizontal  dimensions  shall  be  as  follows:  1.  Rooms  for  Human  Habitations  –  6.00  square  m  with  a  least  dimension  of  2.00  m;     2.   Kitchens  –  3.0  square  m  with  a  least  dimension  of  1.50  m;     3.   Bath  and  toilet  –  1.20  square  m  with  a  least  dimension  of  0.90  m.       SECTION  807.  Air  Space  Requirements  in  Determining  the  Size  of  Rooms     Minimum  air  space  shall  be  provided  as  follows:     1.   School  Rooms  –  3.00  cubic  m  with  1.00  square  m  of  floor  area  per  person;  2.   Workshops,  Factories,  and  Offices  –  12.00  cubic  m  of  air  space  per  person;  3.   Habitable  rooms  –  14.00  cubic  m  of  air  space  per  person.       SECTION  808.  Window  Openings     Every  room  intended  for  any  use,  not  provided  with  artificial  ventilation  system  as  herein  specified  in  this  Code,  shall  be  provided  with  a  window  or  windows  with  a  total  free  area  of  openings  and  equal  to  at  least  ten  percent  of  the  floor  area  of  room,  and  such  window  shall  open  directly  to  a  court,  yard,  public  street  or  alley,  or  open  water  courses.       SECTION  809.  Vent  Shafts     (a)  Ventilation  or  vent  shafts  shall  have  a  horizontal  cross-­‐sectional  area  of  not  less  than  0.10  square  m  for  every  m  of  height  of  shaft  but  in  no  case  shall  the  area  be  less  than  1.00  square  m.  No  vent  shaft  shall  have  its  least  dimension  less  than  600  mm.     (b)  Skylights  –  Unless  open  to  the  outer  air  at  the  top  for  its  full  area,  vent  shaft  shall  be  covered  by  a  skylight  having  a  net  free  area  or  fixed  louver  openings  equal  to  the  maximum  required  shaft  area.     (c)  Air  ducts  shall  open  to  a  street  or  court  by  a  horizontal  duct  or  intake  at  a  point  below  the  lowest  window  opening.  Such  duct  or  intake  shall  have  a  minimum  unobstructed  cross-­‐sectional  area  of  not  less  than  0.30  square  m  with  a  minimum  dimension  of  300  mm.  The  openings  to  the  duct  or  intake  shall  be  not  less  than  300  mm  above  the  bottom  of  the  shaft  and  the  street  surface  or  level  of  court,  at  the  respective  ends  of  the  duct  or  intake.       SECTION  810.  Ventilation  Skylights     Skylights  shall  have  a  glass  area  not  less  than  that  required  for  the  windows  that  are  replaced.  They  shall  be  equipped  with  movable  sashes  or  louvers  with  an  aggregate  net  free  area  not  less  than  that  required  

  

13  

for  openable  parts  in  the  window  that  are  replaced  or  provided  with  approved  artificial  ventilation  of  equivalent  effectiveness.       SECTION  811.  Artificial  Ventilation     (a)  Rooms  or  spaces  housing  industrial  or  heating  equipment  shall  be  provided  with  artificial  means  of  ventilation  to  prevent  excessive  accumulation  of  hot  and/or  polluted  air.     (b)  Whenever  artificial  ventilation  is  required,  the  equipment  shall  be  designed  and  constructed  to  meet  the  following  minimum  requirements  in  air  changes:     1.      For  rooms  entirely  above  grade  and  used  for  office,  clerical,  or  administrative  purposes,  or  as  stores,  sales  rooms,  restaurants,  markets,  factories,  workshops,  or  machinery  rooms,  not  less  than  three  changes  of  air  per  hour  shall  be  provided.  
2.   For  rooms  entirely  above  grade  and  used  as  bakeries,  hotel  or  restaurant  kitchens,  laundries  other  than  accessory  to  dwellings,  and  boiler  rooms  –  not  less  than  ten  changes  of  air  per  hour  shall  be  provided.     3.   For  auditorium  and  other  rooms  used  for  assembly  purposes,  with  seats  or  other  accommodations  –  not  less  than  0.30  cubic  m  of  air  per  minute  shall  be  supplied  for  each  person.     4.   For  wards  and  dormitories  of  institutional  buildings  –  not  less  than  0.45  cubic  m  of  air  per  minute  shall  be  supplied  for  each  person  accommodated.     5.   For  other  rooms  or  spaces  not  specifically  covered  under  this  Section  of  the  Code,  applicable  provisions  of  the  Philippine  Mechanical  Engineering  Code,  shall  be  followed.       CHAPTER  9  SANITATION    SECTION  901.  General  Requirements     Subject  to  the  provisions  of  Book  II  of  the  Civil  Code  of  the  Philippines  on  Property,  Ownership,  and  its  Modification,  all  buildings  hereafter  erected,  altered,  remodeled,  relocated  or  repaired  for  human  habitation  shall  be  provided  with  adequate  and  potable  water  supply,  plumbing  installation,  and  suitable  wastewater  treatment  or  disposal  system,  storm  water  drainage,  pest  and  vermin  control,  noise  abatement  device,  and  such  other  measures  required  for  the  protection  and  promotion  of  health  of  persons  occupying  the  premises  and  others  living  nearby.       SECTION  902.  Water  Supply  System     (a)  Whenever  available,  the  potable  water  requirements  for  a  building  used  for  human  habitation  shall  be  supplied  from  existing  municipal  or  city  waterworks  system.     (b)  The  quality  of  drinking  water  from  meteoric,  surface  or  underground  sources  shall  conform  to  the  criteria  set  in  the  latest  approved  National  Standards  for  Drinking  Water.     (c)  The  design,  construction  and  operation  of  deep  wells  for  the  abstraction  of  groundwater  shall  be  subject  to  the  provisions  of  the  Water  Code  of  the  Philippines.     (d)  The  design,  construction  and  operation  of  independent  waterworks  systems  private  housing  subdivisions  or  industrial  estates  shall  be  governed  by  existing  laws  relating  to  local  waterworks  system.     (e)  The  water  piping  installations  inside  buildings  and  premises  shall  conform  to  the  provisions  of  the  National  Plumbing  Code  of  the  Philippines.       SECTION  903.  Wastewater  Disposal  System     (a)  Sanitary  sewage  from  buildings  and  neutralized  or  pre-­‐treated  industrial  wastewater  shall  be  discharged  directly  into  the  nearest  street  sanitary  sewer  main  of  existing  municipal  or  city  sanitary  sewerage  system  in  accordance  with  the  criteria  set  by  the  Code  on  Sanitation  and  the  National  Pollution  Control  Commission.     (b)  All  buildings  located  in  areas  where  there  are  no  available  sanitary  sewerage  system  shall  dispose  their  sewage  “Imhoff”  or  septic  tank  and  subsurface  absorption  field.     (c)  Sanitary  and  industrial  plumbing  installations  inside  buildings  and  premises  shall  conform  to  the  provisions  of  the  National  Plumbing  Code.     

  

14  

  
SECTION  904.  Storm  Drainage  System     (a)  Rainwater  drainage  shall  not  discharge  to  the  sanitary  sewer  system.  
(b)  Adequate  provisions  shall  be  made  to  drain  low  areas  in  buildings  and  their  premises.       SECTION  905.  Pest  and  Vermin  Control     (a)  All  buildings  with  hollow  and/or  wood  construction  shall  be  provided  with  rat  proofing.     (b)  Garbage  bins  and  receptacles  shall  be  provided  with  ready  means  for  cleaning  and  with  positive  protection  against  entry  of  pest  and  vermins.  
(c)  Dining  rooms  for  public  use  without  artificial  ventilation  shall  be  properly  screened.       SECTION  906.  Noise  Pollution  Control     Industrial  establishments  shall  be  provided  with  positive  noise  abatement  devices  to  tone  down  the  noise  level  of  equipment  and  machineries  to  acceptable  limits  set  down  by  the  Department  of  Labor  and  the  National  Pollution  Control  Commission.       SECTION  907.  Pipe  Materials     All  pipe  materials  to  be  used  in  buildings  shall  conform  to  the  Standard  Specifications  of  the  Philippine  Standard  Council.       CHAPTER  10  BUILDING  PROJECTION  OVER  PUBLIC  STREETS    SECTION  1001.  General  Requirements     (a)  No  part  of  any  building  or  structure  or  any  of  its  appendages  shall  project  beyond  the  property  line  of  the  building  site,  except  as  provided  in  this  Code.     (b)  The  projection  of  any  structure  or  appendage  over  a  public  property  shall  be  the  distance  measured  horizontally  from  the  property  line  to  the  uttermost  point  of  the  projection.       SECTION  1002.  Projection  into  Alleys  or  Streets     (a)  No  part  of  any  structure  or  its  appendage  shall  project  into  any  alley  or  street,  national  road  or  public  highway  except  as  provided  in  this  Code.     (b)  Footings  located  at  least  2.40  m  below  grade  along  national  roads  or  public  highway  may  project  not  more  than  300  mm  beyond  the  property  line.     (c)  Foundations  may  be  permitted  to  encroach  into  public  sidewalk  areas  to  a  width  not  exceeding  500  mm;  provided,  that  the  top  of  the  said  foundations  is  not  less  than  600  mm  below  the  established  grade;  and  provided  further,  that  said  projection  does  not  obstruct  any  existing  utility  such  as  power,  communication,  gas,  water,  or  sewer  lines,  unless  the  owner  concerned  shall  pay  the  corresponding  entities  for  the  rerouting  of  the  parts  of  the  affected  utilities.       SECTION  1003.  Projection  of  Balconies  and  Appendages  Over  Streets     (a)  The  extent  of  any  projection  over  an  alley  or  street  shall  be  uniform  within  a  block  and  shall  conform  to  the  limitations  set  forth  in  Table  1003-­‐A;  Projection  of  Balconies  and  Appendages  (Annex  B-­‐2).     (b)  The  clearance  between  the  established  grade  of  the  street  and/or  sidewalk  and  the  lowest  under  surface  of  any  part  of  the  balcony  shall  not  be  less  than  3.00  m.       SECTION  1004.  Arcades     (a)  Whenever  required  by  existing  building  and  zoning  regulations,  arcades  shall  be  constructed  on  sidewalks  of  streets.  The  width  of  the  arcade  and  its  height  shall  be  uniform  throughout  the  street  provided,  that  in  no  case,  shall  an  arcade  be  less  than  3.00  m  above  the  established  sidewalk  grade.       SECTION  1005.  Canopies  (Marquees)     

  

15  

(a)  Definition:  A  canopy  or  marquee  is  a  permanent  roofed  structure  above  a  door  attached  to  and  supported  by  the  building  and  projecting  over  a  wall  or  sidewalk.  This  includes  any  object  or  decoration  attached  thereto.     (b)  Projection  and  Clearance.  The  horizontal  clearance  between  the  outermost  edge  of  the  marquee  and  the  curb  line  shall  be  not  less  than  300  mm.  The  vertical  clearance  between  the  pavement  or  ground  line  and  the  undersurface  of  any  part  the  marquee  shall  not  be  less  than  3.00  m.     (c)  Construction.  A  marquee  shall  be  constructed  of  incombustible  material  or  materials  of  not  less  than  two-­‐hours  fire-­‐resistive  construction.  It  shall  be  provided  with  necessary  drainage  facility.     (d)  Location.  Every  marquee  shall  be  so  located  as  not  to  interfere  with  the  operation  of  any  exterior  standpipe  connection  or  to  obstruct  the  clear  passage  from  stairway  exits  from  the  building  or  the  installation  or  maintenance  of  electroliers.       SECTION  1006.  Movable  Awnings  or  Hoods     (a)  Definition.  An  awning  is  a  movable  shelter  supported  entirely  from  an  exterior  wall  of  a  building  and  of  a  type  which  can  be  retracted,  folded,  or  collapsed  against  the  face  of  a  supporting  building.     (b)  Clearance.  The  horizontal  clearance  between  the  awning  and  the  curb  line  shall  not  be  less  than  300  mm.  The  vertical  clearance  between  the  undermost  surface  of  the  awning  and  the  pavement  or  ground  line  shall  be  not  less  than  2.40  m.  Collapsible  awnings  shall  be  so  designated  that  they  shall  not  block  a  required  exit  when  collapsed  or  folded.       SECTION  1007.  Doors,  Windows,  and  the  like     Doors,  windows,  and  the  like  less  than  2.40  m  above  the  pavement  or  ground  line  shall  not,  when  fully  opened  or  upon  opening,  project  beyond  the  property  line  except  fire  exit  doors.       SECTION  1008.  Corner  Buildings  with  Chaflans     (a)  Every  corner  building  or  solid  fence  on  a  public  street  or  alley  less  than  3.60  m  in  width  shall  be  truncated  at  the  corner.  The  face  of  the  triangle  so  formed  shall  be  at  right  angles  to  the  bisector  of  the  angle  of  the  intersection  of  the  street  lines;  provided,  that  in  no  case,  the  Secretary  shall  determine  the  size  and  form  of  the  chaflan.     (b)  If  the  building  is  arcaded,  no  chaflan  is  required  notwithstanding  the  width  of  the  public  street  or  alley,  less  than  12.00  m.       CHAPTER  11  PROTECTION  OF  PEDESTRIANS  DURING  CONSTRUCTION  OR  DEMOLITION    SECTION  1101.  General  Requirements     (a)  No  person  shall  use  or  occupy  a  street,  alley  or  public  sidewalk  for  the  performance  of  work  covered  by  a  building  permit  except  in  accordance  with  the  provisions  of  this  Chapter.     (b)  No  person  shall  perform  any  work  on  any  building  or  structure  adjacent  to  a  public  way  in  general  use  for  pedestrian  travel,  unless  the  pedestrians  are  protected  as  specified  in  this  Chapter.     (c)  Any  material  or  structure  temporarily  occupying  public  property,  including  fence,  canopies,  and  walkways,  shall  be  adequately  lighted,  between  sunset  and  sunrise.       SECTION  1102.  Storage  in  Public  Property     Materials  and  equipment  necessary  for  work  to  be  done  under  a  permit  when  placed  or  stored  on  public  property  shall  not  obstruct  free  and  convenient  approach  to  and  use  of  any  fire  hydrant,  fire  or  police  alarm  box,  utility  box,  catch  basin,  or  manhole  and  shall  not  interfere  with  any  drainage  of  any  street  or  alley  gutter.       SECTION  1103.  Mixing  Mortar  on  Public  Property     The  mixing  of  mortar,  concrete,  or  similar  materials  on  public  streets  shall  not  be  allowed.       SECTION  1104.  Protection  of  Utilities     

  

16  

All  public  or  private  utilities  above  or  below  the  ground  shall  be  protected  from  any  damage  by  any  work  being  done  under  the  permit.  The  protection  shall  be  maintained  while  such  work  is  being  done  and  shall  not  obstruct  the  normal  functioning  of  any  such  utility.       SECTION  1105.  Walkway     (a)  When  the  Building  Official  authorizes  a  sidewalk  to  be  fenced  or  closed,  or  in  case  there  is  no  sidewalk  in  front  of  the  building  site  during  construction  or  demolition,  a  temporary  walkway  of  not  less  than  1.20  m  wide  shall  be  provided.     (b)  The  walkway  shall  be  capable  of  supporting  a  uniform  live  load  of  650  kilograms  per  square  m.  A  durable  wearing  surface  shall  be  provided  throughout  the  construction  period.       SECTION  1106.  Pedestrian  Protection     (a)  Protection  Required.  Pedestrian  traffic  shall  be  protected  by  a  railing  on  the  street  side  when  the  walkway  extends  into  the  roadway,  by  a  railing  when  adjacent  to  excavations,  and  by  such  as  set  forth  in  Table  1106-­‐A:  Type  of  Protection  Required  for  Pedestrians  (Annex  B-­‐2).     (b)  Railings.  Adequate  railings  when  required  shall  be  built  substantially  strong  and  should  be  at  least  1.00  m  in  height.     (c)  Fences.  Fences  shall  be  built  of  an  approved  material,  not  less  than  2.40  m  in  height  above  grade,  and  be  placed  on  the  side  of  the  walkway  nearest  to  the  building  site.  Fences  shall  enclose  entirely  the  building  site.  Openings  in  such  fences  shall  be  provided  with  doors  which  shall  be  kept  closed  at  all  times.     (d)  Canopies.  The  protective  canopy  shall  have  a  clear  height  of  2.40  m  above  the  railway,  and  shall  be  structurally  safe.  Every  canopy  shall  have  a  solid  fence  built  along  its  entire  length  on  the  construction  side.  If  materials  are  stored  or  work  is  done  on  top  of  the  canopy,  the  edge  along  the  street  shall  be  protected  by  a  tight  curb  board  not  less  than  300  mm  high  and  a  railing  not  less  than  1.00  m  high  shall  be  provided.  The  entire  structure  shall  be  designed  to  carry  the  loads  imposed  upon  it:  Provided,  that  the  live  load  shall  be  not  less  than  600  kilograms  per  square  m.       SECTION  1107.  Maintenance  and  Removal  of  Protective  Devices     (a)  Maintenance.  All  protective  devices  shall  be  properly  maintained  in  place  and  kept  in  good  order  for  the  entire  length  of  time  pedestrians  may  be  endangered.     (b)  Removal.  Every  protective  fence  or  canopy  shall  be  removed  within  30  days  after  such  protection  is  no  longer  required  as  determined  by  the  Building  Official.       SECTION  1108.  Demolition     (a)  The  work  of  demolishing  any  building  shall  not  be  commenced  until  all  the  necessary  pedestrian  protective  structures  are  in  place.     (b)  The  Building  Official  may  require  the  permittee  to  submit  plans,  specifications  and  complete  schedule  of  demolition.  When  so  required,  no  work  shall  be  done  until  such  plans,  specifications  and  schedule  are  approved  by  the  Building  Official.       CHAPTER  12  GENERAL  DESIGN  AND  CONSTRUCTION  REQUIREMENTS    SECTION  1201.  General  Requirements     Buildings  proposed  for  construction  shall  comply  with  all  the  regulations  and  specifications  herein  set  forth  governing  quality,  characteristics  and  properties  of  materials,  methods  of  design  and  construction,  type  of  occupancy  and  classification.     All  other  matters  relative  to  the  structural  design  of  all  buildings  and  other  structures  not  provided  for  in  this  Chapter  shall  conform  with  the  provisions  of  the  National  Structural  Code  of  Buildings,  as  adopted  and  promulgated  by  the  Board  of  Civil  Engineering  pursuant  to  Republic  Act  Number  544,  as  amended,  otherwise  known  as  the  “Civil  Engineering  Law”.       SECTION  1202.  Excavation,  Foundation,  and  Retaining  Walls     

  

17  

(a)  Subject  to  the  provisions  of  Articles  684  to  686  of  the  Civil  Code  of  the  Philippines  on  lateral  and  subjacent  support,  the  design  and  quality  of  materials  used  structurally  in  excavation,  footings,  and  in  foundations  shall  conform  to  accepted  engineering  practice.     (b)  Excavation  and  Fills  (1)  Excavation  or  fills  for  buildings  or  structures  shall  be  so  constructed  or  protected  that  they  do  not  endanger  life  or  property.  
(2)  Whenever  the  depth  of  excavation  for  any  construction  is  such  that  the  lateral  and  subjacent  support  of  the  adjoining  property  or  existing  structure  thereon  would  be  affected  in  a  manner  that  the  stability  or  safety  of  the  same  is  endangered,  the  person  undertaking  or  causing  the  excavation  to  be  undertaken  shall  be  responsible  for  the  expense  of  underpinning  or  extending  the  foundation  or  footings  of  the  aforementioned  property  or  structure.     (3)  Excavation  and  other  similar  disturbances  made  on  public  property  shall,  unless  otherwise  excluded  by  the  Building  Official,  be  restored  immediately  to  its  former  condition  within  48  hours  from  the  start  of  such  excavation  and  disturbances  by  whosoever  caused  such  excavation  or  disturbance.     (c)  Footings,  Foundations,  and  Retaining  Walls     (1)  Footings  and  foundations  shall  be  of  the  appropriate  type,  of  adequate  size,  and  capacity  in  order  to  safely  sustain  the  superimposed  loads  under  seismic  or  any  condition  of  external  forces  that  may  affect  the  safety  or  stability  of  the  structure.  It  shall  be  the  responsibility  of  the  architect  and/or  engineer  to  adopt  the  type  and  design  of  the  same  in  accordance  with  the  standards  set  forth  by  the  Secretary.     (2)  Whenever  or  wherever  there  exist  in  the  site  of  the  construction  an  abrupt  change  in  the  ground  levels  or  level  of  the  foundation  such  that  instability  of  the  soil  could  result,  retaining  walls  shall  be  provided  and  such  shall  be  of  adequate  design  and  type  of  construction  as  prescribed  by  the  Secretary.       SECTION  1203.  Veneer     (a)  Definition.  Veneer  is  a  nonstructural  facing  of  brick,  concrete,  tile,  metal,  plastic,  glass,  or  other  similar  approved  materials  attached  to  a  backing  or  structural  components  of  the  building  for  the  purpose  of  ornamentation,  protection,  or  enclosure  that  may  be  adhered,  integrated,  or  anchored  either  on  the  interior  or  exterior  of  the  building  or  structure.     (b)  Design  Requirements.  The  design  of  all  veneer  shall  comply  with  the  following:  (1)  Veneer  shall  support  no  load  other  than  its  own  weight  and  the  vertical  dead  load  of  veneer  immediately  above.     (2)  Surfaces  to  which  veneer  is  attached  shall  be  designed  to  support  the  additional  vertical  and  lateral  loads  imposed  by  the  veneer.     (3)  Consideration  shall  be  given  to  differential  movements  of  the  supports  including  those  caused  by  temperature  changes,  shrinkage,  creep,  and  deflection.     (4)  Adhered  veneer  and  its  backing  shall  be  designed  to  have  a  bond  to  the  supporting  elements  sufficient  to  withstand  shearing  stresses  due  to  their  weights  including  seismic  effects  on  the  total  assemblage.     (5)  Anchored  veneer  and  its  attachment  shall  be  designed  to  resist  horizontal  forces  equal  to  twice  the  weight  of  the  veneer.     (6)  Anchors  supports  and  ties  shall  be  non-­‐combustible  and  corrosion-­‐resistant.       SECTION  1204.  Enclosure  of  Vertical  Openings     (a)  General.  Vertical  openings  shall  be  enclosed  depending  upon  the  fire-­‐resistive  requirements  of  a  particular  type  of  construction  as  set  forth  in  this  Code.     (b)  Elevator  Enclosures.  Walls  and  partitions  enclosing  elevators  and  escalators  shall  be  of  not  less  than  the  fire-­‐resistive  construction  required  under  the  Types  of  Construction.  Enclosing  walls  of  elevator  shafts  may  consist  of  wire  glass  set  in  metal  frames  on  the  entrance  side  only.  Elevator  shafts  extending  through  more  than  two  storeys  shall  be  equipped  with  an  approved  means  of  adequate  ventilations  to  and  through  the  main  roof  of  the  building:  Provided,  that  in  those  buildings  housing  Groups  F  and  G  Occupancies  equipped  with  automatic  fire-­‐extinguishing  systems  throughout,  

  

18  

enclosures  shall  not  be  required  for  escalators:  Provided,  further  that  the  top  of  the  escalator  opening  at  each  storey  shall  be  provided  with  a  draft  curtain.  Such  draft  curtain  shall  enclose  the  perim  of  the  unenclosed  opening  and  shall  extend  from  the  ceiling  downward  at  least  300  mm  on  all  sides.  Automatic  sprinklers  shall  be  provided  around  the  perim  of  the  opening  and  within  a  600  mm  of  the  draft  curtain.  The  distance  between  the  sprinkles  shall  not  exceed  1.80  m  center-­‐to-­‐center.     (c)  Other  Vertical  Openings.  All  shafts,  ducts,  chutes,  and  other  vertical  openings  not  covered  in  paragraph  (b)  above  shall  have  enclosing  walls  conforming  to  the  requirements  specified  under  the  type  of  construction  of  the  building  in  which  they  are  located.  In  other  than  Group  A  Occupancies  rubbish  and  linen  chutes  shall  terminate  in  rooms  separated  from  the  remainder  of  the  building  by  a  One-­‐Hour  Fire-­‐Resistive  Occupancy  Separation.  Openings  into  the  chutes  shall  not  be  located  in  required  exit  corridors  or  stairways.     (d)  Air  Ducts.  Air  ducts  passing  through  a  floor  shall  be  enclosed  in  a  shaft.  The  shaft  shall  be  as  required  in  this  Code  for  vertical  openings.  Dampers  shall  be  installed  where  ducts  pierce  the  shaft  enclosure  walls.  Air  ducts  in  Group  A  Occupancies  need  not  be  enclosed  in  a  shaft  if  conforming  to  the  mechanical  provisions  of  this  Code.       SECTION  1205.  Floor  Construction     (a)  Floors  shall  be  of  such  materials  and  construction  as  specified  under  Chapter  5  Fire  Zones  and  Fire-­‐Resistive  Standards  and  under  Chapter  6  –  Types  of  Construction.     (b)  All  floors  shall  be  so  framed  and  secured  into  the  framework  and  supporting  walls  as  to  form  an  integral  part  of  the  whole  building.     (c)  The  types  of  floor  construction  used  shall  provide  means  to  keep  the  beam  and  girders  from  lateral  buckling.       SECTION  1206.  Roof  Construction  and  Covering     (a)  Roof  Covering.  Roof  covering  for  all  buildings  shall  be  either  fire-­‐retardant  or  ordinary  depending  upon  the  fire-­‐resistive  requirements  of  the  particular  type  of  construction.  The  use  of  combustible  roof  insulation  shall  be  permitted  in  all  types  of  construction  provided  it  is  covered  with  approved  roof  covering  applied  directly  thereto.     (b)  Roof  Trusses.  All  roofs  shall  be  so  framed  and  tied  into  the  framework  and  supporting  walls  so  as  to  form  an  integral  part  of  the  whole  building.  Roof  trusses  shall  have  all  joints  well  fitted  and  shall  have  all  tension  members  well  tightened  before  any  load  is  placed  in  the  truss.  Diagonal  and  sway  bracing  shall  be  used  to  brace  all  roof  trusses.  The  allowable  working  stresses  of  materials  in  trusses  shall  conform  to  this  Code.  Camber  shall  be  provided  to  prevent  sagging.     (c)  Attics.     (1)  Access.  An  attic  access  opening  shall  be  provided  in  the  ceiling  of  the  top  floor  of  buildings  with  a  combustible  ceiling  or  roof  construction.  The  opening  shall  be  located  in  a  corridor  or  hallway  of  buildings  of  three  or  more  storeys  in  height,  and  readily  accessible  in  buildings  of  any  height.  An  opening  shall  not  be  less  than  600  mm  square  or  600  mm  in  diam.  The  minimum  clear  headroom  of  800  mm  shall  be  provided  above  the  access  opening.  For  ladder  requirements,  refer  to  the  Philippine  Mechanical  Engineering  code.     (2)  Area  Separation.  Enclosed  attic  spaces  of  combustible  construction  shall  be  divided  into  horizontal  areas  not  exceeding  250  square  m  by  fire-­‐resistive  partitions  extending  from  the  ceiling  to  the  roof.  Except,  that  where  the  entire  attic  is  equipped  with  approved  automatic  fire-­‐extinguishing  system,  the  attic  space  may  be  divided  into  areas  not  to  exceed  750  square  m.  
Openings  in  the  partitions  shall  be  protected  by  self-­‐closing  doors.     (3)  Draft  Stops.  Regardless  of  the  type  of  construction,  draft  stops  shall  be  installed  in  trusses  roofs,  between  roof  and  bottom  chords  or  trusses,  in  all  buildings  exceeding  2000  square  m.  Draft  stops  shall  be  constructed  as  for  attic  area  separations.     (4)  Ventilation.  Enclosed  attics  including  rafter  spaces  formed  where  ceilings  are  applied  direct  to  the  underside  or  roof  rafters,  shall  be  provided  with  adequate  ventilation  protected  against  the  entrance  of  rain.     (d)  Roof  Drainage  System     

  

19  

(1)  Roof  Drains.  Roof  drains  shall  be  installed  at  low  points  of  the  roof  and  shall  be  adequate  in  size  to  discharge  all  tributary  waters.     (2)  Overflow  Drains  and  Scuppers.  Where  roof  drains  are  required,  adequate  overflow  drains  shall  be  provided.     (3)  Concealed  Piping.  Roof  drains  and  overflow  drains,  when  concealed  within  the  construction  of  the  building,  shall  be  installed  in  accordance  with  the  provisions  of  the  National  Plumbing  Code.     (4)  Over  Public  Property.  Roof  drainage  water  from  a  building  shall  not  be  permitted  to  flow  over  public  property,  except  for  Group  A  and  J  Occupancies.     (e)  Flashing.  Flashing  and  counterflashing  shall  be  provided  at  the  juncture  of  the  roof  and  vertical  surfaces.       SECTION  1207.  Stairs,  Exits,  and  Occupant  Loads     (a)  General.  The  construction  of  stairs  and  exits  shall  conform  to  the  occupant  load  requirements  of  buildings,  reviewing  stands,  bleachers,  and  grandstands.     (1)  Determination  of  Occupant  Loads.  The  occupant  load  permitted  in  any  building  or  portion  thereof  shall  be  determined  by  dividing  the  floor  area  assigned  to  that  use  by  the  unit  area  allowed  per  occupant  as  determined  by  the  Secretary.     (2)  Exit  Requirements.  Exist  requirements  of  a  building  or  portion  thereof  used  for  different  purposes  shall  be  determined  by  the  occupant  load  which  gives  the  largest  number  of  persons.  No  obstruction  shall  be  placed  in  the  required  width  of  an  exit  except  projections  permitted  by  this  Code.     (3)  Posting  of  Room  Capacity.  Any  room  having  an  occupant  load  of  more  than  50  where  fixed  seats  are  not  installed,  and  which  is  used  for  classroom,  assembly,  or  similar  purpose  shall  have  the  capacity  of  the  room  posted  in  a  conspicuous  place  near  the  main  exit  from  the  room.     (4)  Changes  in  Elevation.  Except  in  Group  A  Occupancies,  changes  in  floor  elevations  of  less  than  300  mm  along  any  exit  serving  a  tributary  occupant  load  of  10  or  more  shall  be  by  means  of  ramps:     (b)  Exits     (1)  Number  of  Exits.  Every  building  or  usable  portion  thereof  shall  have  at  lease  one  exit.  In  all  occupancies,  floors  above  the  first  storey  having  an  occupant  load  of  more  than  10  shall  not  have  less  than  two  exits.  Each  mezzanine  floor  used  for  other  than  storage  purposes,  if  greater  in  area  than  185  square  m  or  more  than  18.00  m  in  any  dimension,  shall  have  at  least  two  stairways  to  an  adjacent  floor.  Every  storey  or  portion  thereof,  having  an  occupant  load  of  500  to  999  shall  have  at  least  three  exits.  Every  storey  or  portion  thereof  having  an  occupant  load  of  1000  or  more  shall  have  at  least  four  (4)  exits.  The  number  of  exits  required  from  any  storey  of  a  building  shall  be  determined  by  using  the  occupant  loads  of  floors  which  exit  through  the  level  under  consideration  as  follows:  50  percent  of  the  occupant  load  in  the  first  adjacent  storey  above  (and  the  first  adjacent  storey  below,  when  a  storey  below  exits  through  the  level  under  consideration)  and  25  percent  of  the  occupant  load  in  the  storey  immediately  beyond  the  first  adjacent  storey.  The  maximum  number  of  exits  required  for  any  storey  shall  be  maintained  until  egress  is  provided  from  the  structures.  For  purposes  of  this  Section  basement  or  cellars  and  occupied  roofs  shall  be  provided  with  exits  as  required  for  storeys.  Floors  above  the  second  storey,  basements  and  cellars  used  for  other  than  service  of  the  building  shall  have  not  less  than  two  exits.     (2)  Width.  The  total  width  of  exits  in  m  shall  not  be  less  than  the  total  occupant  load  served  divided  by  165.  Such  width  of  exits  shall  be  divided  approximately  equally  among  the  separate  exits.  The  total  exit  width  required  from  any  storey  of  a  building  shall  be  determined  by  using  the  occupant  load  of  that  storey  plus  the  percentage  of  the  occupant  loads  of  floors  which  exits  through  the  level  under  consideration  as  follows:  fifty  (50)  percent  of  the  occupant  load  in  the  first  adjacent  storey  above  (and  the  first  adjacent  storey  below  when  a  storey  below  exits  through  the  level  under  consideration)  and  twenty  five  percent  of  the  occupant  load  in  the  storey  immediately  beyond  the  first  adjacent  storey.  The  maximum  exit  width  from  any  storey  of  a  building  shall  be  maintained.     (3)  Arrangement  of  Exits.  If  only  two  exits  are  required  they  shall  be  placed  a  distance  apart  to  not  less  than  one-­‐fifth  of  the  perim  of  the  area  served  measured  in  a  straight  line  between  exits.  

  

20  

Where  three  or  more  exits  are  required  they  shall  be  arranged  a  reasonable  distance  apart  so  that  if  one  becomes  blocked,  the  others  will  be  available.     (4)  Distance  to  Exists.  No  point  in  a  building  without  a  sprinkler  system  shall  be  more  than  45.00  m  from  an  exterior  exit  door,  a  horizontal  exit,  exit  passageway,  or  an  enclosed  stairway,  measured  along  the  line  of  travel.  In  a  building  equipped  with  a  complete  automatic  fire  extinguishing  system  the  distance  from  exits  may  be  increased  to  60.00  m.     (c)  Doors.  The  provisions  herein  shall  apply  to  every  exit  door  serving  an  area  having  an  occupant  load  of  more  than  10,  or  serving  hazardous  rooms  or  areas.     (1)  Swing.  Exit  door  shall  swing  in  the  direction  of  exit  travel  when  serving  any  hazardous  areas  or  when  serving  an  occupant  load  of  50  or  more.  Double  acting  doors  shall  not  be  used  as  exits  serving  a  tributary  occupant  load  of  more  than  100;  nor  shall  they  be  used  as  a  part  of  fire  assembly,  nor  equipped  with  panic  hardware.  A  double  acting  door  shall  be  provided  with  a  view  panel  of  not  less  than  1,300  square  cm.     (2)  Type  of  Lock  or  Latch.  Exit  door  shall  be  openable  from  the  inside  without  the  use  of  a  key  or  any  special  knowledge  or  effort:  Except,  that  this  requirement  shall  not  apply  to  exterior  exit  doors  in  a  group  E  or  F  Occupancy  if  there  is  a  conspicuous,  readily  visible  and  durable  sign  on  or  adjacent  to  the  door,  stating  that  the  door  is  to  remain  unlocked  during  business  hours.  The  locking  device  must  be  of  a  type  that  will  readily  be  distinguishable  as  locked.  Flush  bolts  or  surface  bolts  are  prohibited.     (3)  Width  and  Height.  Every  required  exit  doorway  shall  be  of  a  size  as  to  permit  the  installation  of  a  door  not  less  than  900  mm  in  width  and  not  less  than  2.00  m  in  height.  When  installed  in  exit  doorways,  exit  doors  shall  be  capable  of  opening  at  least  90  degrees  and  shall  be  so  mounted  that  the  clear  width  of  the  exitway  is  not  less  than  700  mm.  In  computing  the  required  exit  width  the  net  dimension  of  the  exitway  shall  be  used.     (4)  Door  Leaf  Width.  No  leaf  of  an  exit  door  shall  exceed  1.20  m  in  width.     (5)  Special  Doors.  Revolving,  sliding,  and  overhead  doors  shall  not  be  used  as  required  exits.     (6)  Egress  from  Door.  Every  required  exit  door  shall  give  immediate  access  to  an  approved  means  of  egress  from  the  building.     (7)  Change  in  Floor  Level  at  Doors.  Regardless  of  the  occupant  load  there  shall  be  a  floor  or  landing  on  each  side  of  an  exit  door.  The  floor  or  landing  shall  be  leveled  with,  or  not  more  than  50  mm  lower  than  the  threshold  of  the  doorway:  Except,  that  in  Group  A  and  B  Occupancies,  a  door  may  open  on  the  top  step  of  a  flight  of  stairs  or  an  exterior  landing  provided  the  door  does  not  swing  over  the  top  step  or  exterior  landing  and  the  landing  is  not  more  than  200  mm  below  the  floor  level.     (8)  Door  Identification.  Glass  doors  shall  conform  to  the  requirements  in  Section  1805.  Other  exit  doors  shall  be  so  marked  that  they  are  readily  distinguishable  from  the  adjacent  construction.     (9)  Additional  Doors.  When  additional  doors  are  provided  for  egress  purposes,  they  shall  conform  to  all  provisions  in  the  following  cases:  Approved  revolving  doors  having  leaves  which  will  collapse  under  opposing  pressures  may  be  used  in  exit  situations;  provided;  that  such  doors  have  a  minimum  width  of  2.00  m  or  they  are  not  used  in  occupancies  where  exits  are  required  to  be  equipped  with  panic  hardware  or  at  least  one  conforming  exit  door  is  located  adjacent  to  each  revolving  doors  installed  in  a  building  and  the  revolving  door  shall  not  be  considered  to  provide  nay  exit  width.     (d)  Corridors  and  Exterior  Exit  Balconies.  The  provisions  herein  shall  apply  to  every  corridor  and  exterior  exit  balcony  serving  as  a  required  exit  for  an  occupant  load  of  more  than  ten.     (1)  Width.  Every  corridor  or  exit  balcony  shall  not  be  less  than  1.10  m  in  width.     (2)  Projections.  The  required  width  of  corridors  and  exterior  exit  balconies  shall  be  unobstructed.  
Except,  that  trim  handrails,  and  doors  when  fully  opened  shall  not  reduce  the  required  width  by  more  than  200  mm.  Doors  in  any  position  shall  not  reduce  the  required  width  of  the  corridor  by  more  than  one-­‐half.     (3)  Access  to  Exits.  When  more  than  one  exit  is  required,  they  shall  be  so  arranged  to  allow  going  to  either  direction  from  any  point  in  the  corridor  or  exterior  exit  balcony  to  a  separate  exit,  except  for  dead  ends  permitted  by  this  Code.     

  

21  

(4)  Dead  Ends.  Corridors  and  exterior  exit  balconies  with  dead  ends  are  permitted  when  the  dead  end  does  not  exceed  6.00  m  in  length.     (5)  Construction.  Walls  and  ceilings  of  corridors  shall  not  be  less  than  one-­‐hour  fire-­‐  resistive  construction.  Provided,  that  this  requirement  shall  not  apply  to  exterior  exit  balconies,  railings,  and  corridors  of  one-­‐storey  building  housing  a  Group  E  and  F  Occupancy  occupied  by  one  tenant  only  and  which  serves  an  occupant  load  of  30  or  less,  nor  to  corridors,  formed  by  temporary  partitions.  Exterior  exit  balconies  shall  not  project  into  an  area  where  protected  openings  are  required.     (6)  Openings.  Where  corridor  wall  are  required  to  be  one-­‐hour  fire-­‐resistive  construction,  every  interior  door  opening  shall  be  protected  as  set  forth  in  generally  recognized  and  accepted  requirements  for  dual  purpose  fire  exit  doors.  Other  interior  openings  except  ventilation  louvers  equipped  with  approved  automatic  fire  shutters  shall  be  7  mm  thick  fixed  wire  glass  set  in  steel  frames.  The  total  area  of  all  openings  other  than  doors,  in  any  portion  of  an  interior  corridor  wall  shall  not  exceed  twenty-­‐five  percent  of  the  area  of  the  corridor  wall  of  the  room  being  separated  from  the  corridor.     (e)  Stairways.  Except  stairs  or  ladders  used  only  to  access  equipment,  every  stairway  serving  any  building  or  portion  thereof  shall  conform  to  the  following  requirements:     (1)  Width.  Stairways  serving  an  occupant  load  of  more  than  50  shall  not  be  less  than  1.10  m.  
Stairways  serving  an  occupant  load  of  50  or  less  may  be  900  mm  wide.  Private  stairways  serving  an  occupant  load  of  less  than  10  may  be  750  mm.  Trim  and  handrails  shall  not  reduce  the  required  width  by  more  than  100  mm.     (2)  Rise  and  Run.  The  rise  of  every  step  in  a  stairway  shall  not  exceed  200  mm  and  the  run  shall  not  be  less  than  250  mm.  The  maximum  variations  in  the  height  of  risers  and  the  width  of  treads  in  any  one  flight  shall  be  5  mm:  Except,  in  case  of  private  stairways  serving  an  occupant  load  of  less  than  10,  the  rise  may  be  200  mm  and  the  run  may  be  250  mm,  except  as  provided  in  sub-­‐
paragraph  (3)  below.     (3)  Winding  Stairways.  In  Group  A  Occupancy  and  in  private  stairways  in  Group  B  Occupancies,  winders  may  be  used  if  the  required  width  of  run  is  provided  at  a  point  not  more  than  300  mm  from  the  side  of  the  stairway  where  the  treads  are  narrower  but  in  no  case  shall  any  width  of  run  be  less  than  150  mm  at  any  point.     (4)  Circular  Stairways.  Circular  stairs  may  be  used  as  an  exit  provided  the  minimum  width  of  run  is  not  less  than  250  mm.  All  treads  in  any  one  flight  between  landings  shall  have  identical  dimensions  within  a  5  mm  tolerance.     (5)  Landings.  Every  landing  shall  have  a  dimension  measured  in  the  direction  of  travel  equal  to  the  width  of  the  stairway.  Such  dimension  need  not  exceed  1.20  m  when  the  stairs  has  a  straight  run.  
Landings  when  provided  shall  not  be  reduced  in  width  by  more  than  100  mm  by  a  door  when  fully  open.     (6)  Basement  Stairways.  Where  a  basement  stairway  and  a  stairway  to  an  upper  storey  terminate  in  the  same  exit  enclosure,  an  approved  barrier  shall  be  provided  to  prevent  persons  from  continuing  on  to  the  basements.  Directional  exit  signs  shall  be  provided  as  specified  in  this  Code.     (7)  Distance  Between  Landings.  There  shall  be  not  more  than  3.60  m  vertical  distance  between  landings.     (8)  Handrails.  Stairways  shall  have  handrails  on  each  side  and  every  stairway  required  to  be  more  than  3.00  m  in  width  shall  be  provided  with  not  less  than  one  intermediate  handrail  for  each  3.00  m  of  required  width.  Intermediate  handrails  shall  be  spaced  approximately  equal  within  the  entire  width  of  the  stairway.  Handrails  shall  be  placed  not  less  than  800  mm  nor  more  than  900  mm  above  the  nosing  of  treads,  and  ends  of  handrails  shall  be  returned  or  shall  terminate  in  newel  posts  or  safety  terminals:  Except,  in  the  following  cases:  Stairways  1.10  m  or  less  in  width  and  stairways  serving  one  individual  dwelling  unit  in  Group  A  or  B  Occupancies  may  have  one  handrail,  except  that  such  stairway,  open  on  one  or  both,  sides  shall  have  handrails  provided  on  the  open  side  or  sides:  or  stairways  having  less  than  four  risers  need  not  have  handrails.     (9)  Exterior  Stairway  Protection.  All  openings  in  the  exterior  wall  below  or  within  3.00  m,  measured  horizontally,  of  an  exterior  exit  stairway  serving  a  building  over  two  storeys  in  height  shall  be  protected  by  a  self-­‐closing  fire  assembly  having  a  three-­‐fourths  hour  fire-­‐  resistive  rating:  Except,  

  

22  

that  openings  may  be  unprotected  when  two  separated  exterior  stairways  serve  an  exterior  exit  balcony.     (10a)  Stairways  Construction  -­‐  Interior.  Interior  stairways  shall  be  constructed  as  specified  in  this  Code.  Where  there  is  enclosed  usable  space  under  the  stairs  the  walls  and  soffits  of  the  enclosed  space  shall  be  protected  on  the  enclosed  side  as  required  for  one-­‐hour  fire  resistive  construction.     (10b)  Stairway  Construction  -­‐  Exterior.  Exterior  stairways  shall  be  of  incombustible  material:  Except,  that  on  Type  III  buildings  which  do  not  exceed  two  storeys  in  height,  which  are  located  in  less  fire-­‐restrictive  Fire  Zones,  as  well  as  on  Type  I  buildings  which  may  be  of  wood  not  less  than  50  mm  in  nominal  thickness.  Exterior  stairs  shall  be  protected  as  required  for  exterior  walls  due  to  location  on  property  as  specified  in  this  Code.  Exterior  stairways  shall  not  project  into  an  area  where  openings  are  required  to  be  protected.  Where  there  is  enclosed  usable  space  under  stairs,  the  walls  and  soffits  of  the  enclosed  space  shall  be  protected  on  the  enclosed  side  as  required  for  one-­‐hour  fire-­‐resistive  construction.     (11)  Stairway  to  Roof.  In  every  building  four  or  more  storeys  in  height,  one  stairway  shall  extend  to  the  roof  unless  the  roof  has  C  slope  greater  than  1  in  3.     (12)  Headroom.  Every  required  stairway  shall  have  a  headroom  clearance  of  not  less  than  2.00  m.  
Such  clearance  shall  be  established  by  measuring  vertically  from  a  plane  parallel  and  tangent  to  the  stairway  tread  nosing  to  the  soffit  above  all  points.     (f)  Ramps.  A  ramp  conforming  to  the  provisions  of  this  Code  may  be  used  as  an  exit.  The  width  of  ramps  shall  be  as  required  for  corridors.     (g)  Horizontal  Exit.  If  conforming  to  the  provisions  of  this  Code,  a  horizontal  exit  may  be  considered  as  the  required  exit.  All  openings  in  a  separation  wall  shall  be  protected  by  a  fire  assembly  having  a  fire-­‐resistive  rating  of  not  less  than  one  hour.  A  horizontal  exit  shall  not  lead  into  a  floor  area  having  a  capacity  for  an  occupant  load  not  less  than  the  occupant  load  served  by  such  exit.  The  capacity  shall  be  determined  by  allowing  0.30  square  m  of  net  floor  area  per  ambulatory  occupant  and  1.90  square  m  per  non-­‐ambulatory  occupant.  The  dispersal  area  into  which  the  horizontal  exit  leads  shall  be  provided  with  exits  as  required  by  this  Code.     (h)  Exit  Enclosure.  Every  interior  stairway,  ramp,  or  escalator  shall  be  enclosed  as  specified  in  this  Code:  Except,  that  in  other  than  Group  D  Occupancies,  an  enclosure  will  not  be  required  for  stairway,  ramp,  or  escalator  serving  only  one  adjacent  floor  and  not  connected  with  corridors  or  stairways  serving  other  floors.  Stairs  in  Group  A  Occupancies  need  not  be  enclosed.     (1)  Enclosure  walls  shall  not  be  less  than  two-­‐hour  fire-­‐resistive  construction.  There  shall  be  no  openings  into  exit  enclosures  except  exit  doorways  and  openings  in  exterior  walls.  All  exit  doors  in  an  exit  enclosure  shall  be  appropriately  protected.     (2)  Stairway  and  ramp  enclosures  shall  include  landings  and  parts  of  floors  connecting  stairway  flights  and  shall  include  a  corridor  on  the  ground  floor  leading  from  the  stairway  to  the  exterior  of  the  building.  Enclosed  corridors  or  passageways  are  not  required  for  unenclosed  stairways.     (3)  A  stairway  in  an  exit  enclosure  shall  not  continue  below  the  grade  level  exit  unless  an  approved  barrier  is  provided  at  the  ground  floor  level  to  prevent  persons  from  accidentally  continuing  into  the  basement.     (4)  There  shall  be  no  enclosed  usable  space  under  stairways  in  an  exit  enclosure,  nor  shall  the  open  space  under  such  stairways  be  used  for  any  purpose.     (i)  Smokeproof  Enclosures     A  smokeproof  enclosure  shall  consist  of  a  vestibule  and  a  continuous  stairway  enclosed  from  the  highest  point  to  the  lowest  point  by  walls  of  two-­‐hour  fire-­‐resistive  construction.  In  buildings  five  storeys  or  more  in  height,  one  of  the  required  exits  shall  be  a  smokeproof  enclosure.     (1)  Stairs  in  smokeproof  enclosures  shall  be  of  incombustible  construction.     (2)  There  shall  be  no  openings  in  smokeproof  enclosures,  except  exit  doorways  and  openings  in  exterior  walls.  There  shall  be  no  openings  directly  into  the  interior  of  the  building.  Access  shall  be  through  a  vestibule  with  one  wall  at  least  fifty  percent  open  to  the  exterior  and  having  an  exit  door  from  the  interior  of  the  building  and  an  exit  door  leading  to  the  smokeproof  enclosure.  In  lieu  of  a  vestibule,  access  may  be  by  way  of  an  open  exterior  balcony  of  incombustible  materials.     (3)  The  opening  from  the  building  to  the  vestibule  or  balcony  shall  be  protected  with  a  self-­‐closing  fire  assembly  having  one-­‐hour  fire-­‐resistive  rating.  The  opening  from  the  vestibule  or  balcony  to  

  

23  

the  stair  tower  shall  be  protected  by  a  self-­‐closing  fire  assembly  having  a  one-­‐hour  fire-­‐resistive  rating.     (4)  A  smokeproof  enclosure  shall  exit  into  a  public  way  or  into  an  exit  passageway  leading  to  a  public  way.  The  exit  passageway  shall  be  without  other  openings  and  shall  have  walls,  floors,  and  ceilings  of  two-­‐hour  fire-­‐resistance.     (5)  A  stairway  in  a  smokeproof  enclosure  shall  not  continue  below  the  grade  level  exit  unless  an  approved  barrier  is  provided  at  a  ground  floor  level  to  prevent  persons  from  accidentally  walking  into  the  basement.     (j)  Exit  Outlets,  Courts,  and  Passageways     Every  exit  shall  discharge  into  a  public  way,  exit  court,  or  exit  passageway.  Every  exit  court  shall  discharge  into  a  public  way  or  an  exit  passageway.  Passageways  shall  be  without  openings  other  than  required  exits  and  shall  have  walls,  floors,  and  ceilings  of  the  same  period  of  fire-­‐resistance  as  the  walls,  floors  and  ceilings  of  the  building  but  shall  not  be  less  than  one-­‐hour  fire-­‐resistive  construction.     (1)  Width.  Every  exit  court  and  exit  passageways  shall  be  at  least  as  wide  as  the  required  total  width  of  the  tributary  exits,  such  required  width  being  based  on  the  occupant  load  served.  The  required  width  of  exit  courts  or  exit  passageways  shall  be  unobstructed  except  as  permitted  in  corridors.  At  any  point  where  the  width  of  an  exit  court  is  reduced  from  any  cause,  the  reduction  in  width  shall  be  affected  gradually  by  a  guardrail  at  least  900  mm  in  height.  The  guardrail  shall  make  an  angle  of  not  more  than  30  degrees  with  the  axis  of  the  exit  court.     (2)  Slope.  The  slope  of  exit  courts  shall  not  exceed  1  in  10.  The  slope  of  exit  passageway  shall  not  exceed  1  in  8.     (3)  Number  of  Exits.  Every  exit  court  shall  be  provided  with  exits  as  required  in  this  Code.     (4)  Openings.  All  openings  into  an  exit  court  less  than  3.00  m  wide  shall  be  protected  by  fire  assemblies  having  not  less  than  three-­‐fourth  hour  fire-­‐resistive  rating.  Except,  that  openings  more  than  3.00  m  above  the  floor  of  the  exit  court  may  be  unprotected.     (k)  Exit  Signs  and  Illuminations     Exits  shall  be  illuminated  at  any  time  the  building  is  occupied  with  lights  having  an  intensity  of  not  less  than  10.7  lux  at  floor  level:  Except,  that  for  Group  A  Occupancies,  the  exit  illumination  shall  be  provided  with  separate  circuits  or  separated  sources  of  power  (but  not  necessarily  separate  from  exit  signs  when  these  are  required  for  exit  sign  illumination)     (l)  Aisles     Every  portion  or  every  building  in  which  are  installed  seats,  tables,  merchandise,  equipment,  or  similar  materials  shall  be  provided  with  aisles  leading  to  an  exit.     (1)  Width.  Every  aisle  shall  be  not  less  than  800  mm  wide  if  serving  only  one  side,  and  not  less  than  1  m  wide  if  serving  both  sides.  Such  minimum  width  shall  be  measured  at  the  point  farthest  from  an  exit,  cross  aisle,  or  foyer  and  shall  be  increased  by  30  mm  for  every  m  in  length  towards  the  exit,  cross  aisle  or  foyer.  
Side  aisles  shall  not  be  less  than  1.10  m  in  width.     (2)  Exit  Distance.  In  areas  occupied  by  seats  and  in  Groups  H  and  I  Occupancies  without  seats,  the  line  of  travel  to  an  exit  door  by  an  aisle  shall  be  not  more  than  45.00  m.  With  standard  spacing,  as  specified  in  this  Code,  aisles  shall  be  so  located  that  there  will  be  not  more  than  seven  seats  between  the  wall  and  an  aisle  and  not  more  than  fourteen  seats  between  aisles.  The  number  of  seats  between  aisles  may  be  increased  to  30  where  exits  doors  are  provided  along  each  side  aisle  of  the  row  of  seats  at  the  rate  of  one  pair  of  exit  doors  for  every  five  rows  of  seats,  provided  further  that  the  distance  between  seats  back  to  back  is  at  least  one  much  exit  doors  shall  provide  a  minimum  clear  width  of  1.70  m.     (3)  Cross  aisles.  Aisles  shall  terminate  in  a  cross  aisle,  foyer,  or  exit.  The  width  of  the  cross  aisle  shall  be  not  less  than  the  sum  of  the  required  width  of  the  widest  aisle  plus  fifty  percent  of  the  total  required  width  of  the  remaining  aisle  leading  thereto.  In  Groups  C,  H  and  E  Occupancies,  aisles  shall  not  be  provided  a  dead  end  greater  than  6.00  m  in  length.     (4)  Vomitories.  Vomitories  connecting  the  foyer  or  main  exit  with  the  cross  aisles  shall  have  a  total  width  not  less  than  the  sum  of  the  required  width  of  the  widest  aisles  leading  thereto  plus  fifty  percent  of  the  total  required  width  of  the  remaining  aisles  leading  thereto.     

  

24  

(5)  Slope.  The  slope  portion  of  aisles  shall  not  exceed  a  fall  of  1  in  8.     (m)  Seats  (1)  Seat  Spacing.  With  standard  seating,  the  spacing  of  rows  of  seats  from  back-­‐to-­‐back  shall  be  not  less  than  840  mm.  With  continental  seating,  the  spacing  of  rows  of  unoccupied  seats  shall  provide  a  clear  width  measured  horizontally,  as  follows:  450  mm  clear  for  rows  of  18  seats  or  less;  500  mm  clear  for  rows  of  35  seats  or  less;  525  mm  clear  for  rows  of  45  seats  or  less;  and  550  mm  clear  for  rows  of  46  seats  or  more.     (2)  Width.  The  width  of  any  seat  shall  be  not  less  than  450  mm.     (n)  Reviewing  Stands,  Grandstands,  and  Bleachers  (1)  Height  of  Stands.  Stands  made  of  combustible  framing  shall  be  limited  to  11  rows  or  2.70  m  in  height.  
(2)  Design  Requirements.  The  minimum  unit  live  load  for  reviewing  stands,  grandstands,  and  bleachers  shall  be  500  kilograms  per  square  m  of  horizontal  projection  for  the  structure  as  a  whole.  Seat  and  footboards  shall  be  180  kilograms  per  linear  m.  The  sway  force,  applied  to  seats,  shall  be  35  kilograms  per  linear  m  parallel  to  the  seats  and  15  kilograms  per  linear  m  perpendicular  to  the  seats.  Sway  forces  need  not  be  applied  simultaneously  with  other  lateral  forces.     (3)  Spacing  of  Seats  (3.1)  Row  Spacing.  The  minimum  spacing  of  rows  of  seats  measured  from  back-­‐to-­‐back  shall  be:  600  mm  for  seats  without  backrests  in  open  air  stands;  750  mm  for  seats  with  backrests;  and  850  mm  for  chair  seating.  There  shall  be  a  space  of  not  less  than  300  mm  between  the  back  of  each  seat  and  the  front  of  the  seat  immediately  behind  it.     (3.2)  Rise  Between  Rows.  The  maximum  rise  from  one  row  of  seats  to  the  next  shall  not  exceed  400  mm.     (3.3)  Seating  Capacity.  For  determining  the  seating  capacity  of  a  stand,  the  width  of  any  seat  shall  not  be  less  than  450  mm  nor  more  than  480  mm.     (3.4)  Number  of  Seats  Between  Aisles.  The  number  of  seats  between  any  seat  and  an  aisle  shall  not  be  greater  than  15  for  open  air  stands  with  seats  without  backrests,  a  far  open  air  stands  with  seats  having  backrests  and  seats  without  backrests  within  buildings  and  6  for  seats  with  backrests  in  buildings.     (4)  Aisles  (4.1)  Aisles  Required.  Aisles  shall  be  provided  in  all  stands;  Except,  that  aisles  may  be  omitted  when  all  the  following  conditions  exist:  Seats  are  without  backrests;  the  rise  from  row  to  row  does  not  exceed  300  mm  per  row;  the  number  of  rows  does  not  exceed  11  in  height;  the  top  seating  board  is  not  over  3.00  m  above  grade;  and  the  first  seating  board  is  not  more  than  500  mm  above  grade.     (4.2)  Obstructions.  No  obstruction  shall  be  placed  in  the  required  width  of  any  aisle  or  exitway.     (4.3)  Stairs  Required.  When  an  aisle  is  elevated  more  than  200  mm  above  grade,  the  aisle  shall  be  provided  with  a  stairway  or  ramp  whose  width  is  not  less  than  the  width  of  the  aisle.     (4.4)  Dead  End.  No  vertical  aisle  shall  have  a  dead  end  more  than  16  rows  in  depth  regardless  of  the  number  of  exits  required.     (4.5)  Width.  Aisles  shall  have  a  minimum  width  of  1.10  m.     (5)  Stairs  and  Ramps     The  requirements  in  this  Code  shall  apply  to  all  stairs  and  ramps  except  for  portions  that  pass  through  the  seating  area.     (5.1)  Stair  Rise  and  Run.  The  maximum  rise  of  treads  shall  not  exceed  200  mm  and  the  minimum  width  of  the  run  shall  be  280  mm.  The  maximum  variation  in  the  width  of  treads  in  any  one  flight  shall  not  be  more  than  5  mm  and  the  maximum  variation  in  one  height  of  two  adjacent  rises  shall  not  exceed  5  mm.     (5.2)  Ramp  Slope.  The  slope  of  a  ramp  shall  not  exceed  1  in  8.  Ramps  shall  be  roughened  or  shall  be  of  approved  nonslip  material.     (5.3)  Handrails.  A  ramp  with  a  slope  exceeding  1  in  10  shall  have  handrails.  Stairs  for  stands  shall  have  handrails.  Handrails  shall  conform  to  the  requirements  of  this  Code.     (6)  Guardrails  

  

25  

(6.1)  Guardrails  shall  be  required  in  all  locations  where  the  top  of  a  seat  plank  is  more  than  1.20  m  above  the  grade  and  at  the  front  of  stands  elevated  more  than  600  mm  above  grade.  Where  only  sections  of  stands  are  used,  guardrails  shall  be  provided  as  required  in  this  Code.     (6.2)  Railings  shall  be  1.10  m  above  the  rear  of  a  seat  plank  or  1.10  m  above  the  rear  of  the  steps  in  an  aisle  when  the  guardrail  is  parallel  and  adjacent  to  the  aisle:  Except,  that  the  height  may  be  reduced  to  900  mm  for  guardrails  located  in  front  of  the  grandstand.     (6.3)  A  midrail  shall  be  placed  adjacent  to  any  seat  to  limit  the  open  distance  above  the  top  of  any  part  of  a  seat  to  250  mm  where  the  seat  is  at  the  extreme  end  or  at  the  extreme  rear  of  the  bleachers  or  grandstand.  The  intervening  space  shall  have  one  additional  rail  midway  in  the  opening:  Except,  that  railings  may  be  omitted  when  stands  are  placed  directly  against  a  wall  or  fence  giving  equivalent  protection;  stairs  and  ramps  shall  be  provided  with  guardrails.  
Handrails  at  the  front  of  stands  and  adjacent  to  an  aisle  shall  be  designed  to  resist  a  load  of  75  kilograms  per  linear  m  applied  at  the  top  rail.  Other  handrails  shall  be  designed  to  resist  a  load  of  40  kilograms  per  linear  m.     (7)  Foot  Boards  Footboards  shall  be  provided  for  all  rows  of  seats  above  the  third  row  or  beginning  at  such  point  where  the  seating  plank  is  more  than  600  mm  above  grade.     (8)  Exits     (8.1)  Distance  to  Exit.  The  line  of  travel  to  an  exit  shall  not  be  more  than  45.00  m.  For  stands  with  seats  without  backseats  this  distance  may  be  measured  by  direct  line  from  a  seat  to  the  exit  from  the  stand.     (8.2)  Aisle  Used  as  Exit.  An  aisle  may  be  considered  as  only  one  exit  unless  it  is  continuous  at  both  ends  to  a  legal  building  exit  or  to  a  safe  dispersal  area.     (8.3)  Two  Exits  Required.  A  stand  with  the  first  seating  board  not  more  than  500  mm  above  grade  of  floor  may  be  considered  to  have  two  exits  when  the  bottom  of  the  stand  is  open  at  both  ends.  Every  stand  or  section  of  a  stand  within  a  building  shall  have  at  least  two  means  of  egress  when  the  stand  accommodates  more  than  50  persons.  Every  open  air  stand  having  seats  without  backrests  shall  have  at  least  two  means  of  egress  when  the  stand  accommodates  more  than  300  persons.     (8.4)  Three  Exits  Required.  Three  exits  shall  be  required  for  stands  within  a  building  when  there  are  more  than  300  occupants  within  a  stand  and  for  open  air  stands  with  seats  without  backrests  where  a  stand  or  section  of  a  stand  accommodates  more  than  1000  occupants.     (8.5)  Four  Exits  Required.  Four  exits  shall  be  required  when  a  stand  or  section  of  a  stand  accommodates  more  than  1000  occupants:  Except,  that  for  an  open  air  stand  with  seats  without  backrest  four  exits  need  not  be  provided  unless  there  are  accommodations  for  more  than  3000  occupants.     (8.6)  Width.  The  total  width  of  exits  in  m  shall  not  be  less  than  the  total  occupant  load  served  divided  by  165:  Except,  that  for  open  air  stands  with  seats  without  backrest  the  total  width  of  exits  in  m  shall  be  not  less  than  the  total  occupant  load  served  divided  by  500  when  exiting  by  stairs,  and  divided  by  650  when  exiting  by  ramps  or  horizontally.  When  both  horizontal  and  stair  exits  are  used,  the  total  width  of  exits  shall  be  determined  by  using  both  figures  as  applicable.  No  exit  shall  be  less  than  1.10  m  in  width.  Exits  shall  be  located  at  a  reasonable  distance  apart.  When  only  two  exits  are  provided,  they  shall  be  spaced  not  less  than  one-­‐fifth  of  the  perim  apart.     (9)  Securing  of  Chairs  Chairs  and  benches  used  on  raised  stands  shall  be  secured  to  the  platforms  upon  which  they  are  placed:  Except,  that  when  less  than  25  chairs  are  used  upon  a  single  raised  platform  the  fastening  of  seats  to  the  platform  may  be  omitted.  When  more  than  500  loose  chairs  are  used  in  connection  with  athletic  events,  chairs  shall  be  fastened  together  in  groups  of  not  less  than  three,  and  shall  be  tied  or  staked  to  the  ground.     (10)  Safe  Dispersal  Area  Each  safe  dispersal  area  shall  have  at  least  two  exits.  If  more  than  6000  persons  are  to  be  accommodated  within  such  an  area,  there  shall  be  a  minimum  of  three  exits,  and  for  more  than  9000  persons  there  shall  be  a  minimum  of  four  exits.  The  aggregate  clear  width  of  exits  from  a  

  

26  

safe  dispersal  area  shall  be  determined  on  the  basis  of  not  less  than  one  exit  unit  of  600  mm  for  each  500  persons  to  be  accommodated  and  no  exit  shall  be  less  than  1.10  m  in  width,  a  reasonable  distance  apart  but  shall  be  spaced  not  less  than  one-­‐fifth  of  the  perim  of  the  area  apart  from  each  other.  
(o)  Special  Hazards  (1)  Boiler  Rooms.  Except  in  Group  A  Occupancies,  every  boiler  room  and  every  room  containing  an  incinerator  or  liquefied  petroleum  gas  or  liquid  fuel-­‐fired  equipment  shall  be  provided  with  at  least  two  means  of  egress,  one  of  which  may  be  a  ladder.  All  interior  openings  shall  be  protected  as  provided  for  in  this  Code.  
(2)  Cellulose  Nitrate  Handling.  Film  laboratories,  projection  rooms,  and  nitro-­‐cellulose  processing  rooms  shall  have  not  less  than  two  exits.  
  SECTION  1208.  Skylights  (a)  All  skylights  shall  be  constructed  with  metal  frames  except  those  for  Groups  A  and  J  Occupancies.  
Frames  of  skylights  shall  be  designed  to  carry  loads  required  for  roofs.  All  skylights,  the  glass  of  which  is  set  at  an  angle  of  less  than  45  degrees  from  the  horizontal,  if  located  above  the  first  storey,  shall  be  set  at  least  100  mm  above  the  roof.  Curbs  on  which  the  skylights  rest  shall  be  constructed  of  incombustible  materials  except  for  Types  I  or  II  Construction.  
(b)  Spacing  between  supports  in  one  direction  for  flat  wired  glass  in  skylights  shall  not  exceed  625  mm.  
Corrugated  wired  glass  may  have  supports  1.50  m  apart  in  the  direction  of  the  corrugation.  All  glass  in  skylights  shall  be  wired  glass:  Except,  that  skylights  over  vertical  shafts  extending  through  two  or  more  storeys  shall  be  glazed  with  plain  glass  as  specified  in  this  Code:  Provided,  that  wired  glass  may  be  used  in  ventilation  equal  to  not  less  than  one-­‐eight  the  cross-­‐sectional  area  of  the  shaft  but  never  less  than  1.20  m  provided  at  the  top  of  such  shaft.  Any  glass  not  wired  glass  shall  be  protected  above  and  below  with  a  screen  constructed  of  wire  not  smaller  than  2.5  mm  in  diam  with  a  mesh  not  larger  than  25  mm.  The  screen  shall  be  substantially  supported  below  the  glass.  
(c)  Skylights  installed  for  the  use  of  photographers  may  be  constructed  of  metal  frames  and  plate  glass  without  wire  netting.  
(d)  Ordinary  glass  may  be  used  in  the  roof  and  skylights  for  greenhouses,  Provided,  that  height  of  the  greenhouses  at  the  ridge  does  not  exceed  6.00  m  above  the  grade.  The  use  of  wood  in  the  frames  of  skylights  will  be  permitted  in  greenhouses  outside  of  highly  restrictive  Fire  Zones  if  the  height  of  the  skylight  does  not  exceed  6.00  m  above  the  grade,  but  in  other  cases  metal  frames  and  metal  sash  bars  shall  be  used.     (e)  Glass  used  for  the  transmission  of  light,  if  placed  in  floors  or  sidewalks,  shall  be  supported  by  metal  or  reinforced  concrete  frames,  and  such  glass  shall  not  be  less  than  12.5  mm  in  thickness.  Any  such  glass  over  100  square  cm  in  area  shall  have  wire  mesh  embedded  in  the  same  or  shall  be  provided  with  a  wire  screen  underneath  as  specified  for  skylights  in  this  Code.  All  portions  of  the  floor  lights  or  sidewalk  lights  shall  be  of  the  same  strength  as  required  for  floor  or  sidewalk  construction,  except  in  cases  where  the  floor  is  surrounded  by  a  railing  not  less  1.10  m  in  height,  in  which  case  the  construction  shall  be  calculated  for  not  less  than  roof  loads.       SECTION  1209.  Bays,  Porches,  and  Balconies     (a)  Walls  and  floors  in  bay  and  oriel  windows  shall  conform  to  the  construction  allowed  for  exterior  walls  and  floors  of  the  type  of  construction  of  the  building  to  which  they  are  attached.  The  roof  covering  of  a  bay  or  oriel  window  shall  conform  to  the  requirements  of  the  roofing  of  the  main  roof.  
Exterior  balconies  attached  to  or  supported  by  wall  required  to  be  of  masonry,  shall  have  brackets  or  beams  constructed  of  incombustible  materials.  Railings  shall  be  provided  for  balconies,  landings,  or  porches  which  are  more  than  750  mm  above  grade.       SECTION  1210.  Penthouses  and  Roof  Structures     (a)  Height     No  penthouse  or  other  projection  above  the  roof  in  structures  of  other  than  Type  V  construction  shall  exceed  8.40  m  above  the  roof  when  used  as  an  enclosure  for  tanks  or  for  elevators  which  run  to  the  roof  and  in  all  other  cases  shall  not  extend  more  than  3.60  m  in  height  with  the  roof.     

  

27  

(b)  Area     The  aggregate  area  of  all  penthouses  and  other  roof  structures  shall  not  exceed  one  third  of  the  area  of  the  supporting  roof.     (c)  Prohibited  Uses     No  penthouse,  bulkhead,  or  any  other  similar  projection  above  the  roof  shall  be  used  for  purposes  other  than  shelter  of  mechanical  equipment  or  shelter  of  vertical  shaft  openings  in  the  roof.  A  penthouse  or  bulkhead  used  for  purposes  other  than  that  allowed  by  this  Section  shall  conform  to  the  requirements  of  this  Code  for  an  additional  storey.     (d)  Construction     Roof  structures  shall  be  constructed  with  walls,  floors,  and  roof  as  required  for  the  main  portion  of  the  building  except  in  the  following  cases:     (1)  On  Types  III  and  IV  constructions,  the  exterior  walls  and  roofs  of  penthouses  which  are  1.50  m  or  more  from  an  adjacent  property  line  may  be  of  one-­‐hour  fire-­‐resistive  incombustible  construction.     (2)  Walls  not  less  than  1.50  m  from  an  exterior  wall  of  a  Type  IV  construction  may  be  of  one-­‐hour  fire-­‐resistive  incombustible  construction.  
The  above  restrictions  shall  not  prohibit  the  placing  of  wood  flagpoles  or  similar  structures  on  the  roof  of  any  building.     (e)  Towers  and  Spires     Towers  and  spires  when  enclosed  shall  have  exterior  walls  as  required  for  the  building  to  which  they  are  attached.  Towers  not  enclosed  and  which  extend  more  than  20.00  m  above  the  grade  shall  have  their  framework  constructed  of  iron,  steel,  or  reinforced  concrete.  No  tower  or  spire  shall  occupy  more  than  one-­‐fourth  of  the  street  frontage  of  any  building  to  which  it  is  attached  and  in  no  case  shall  the  base  area  exceed  150  square  m  unless  it  conforms  entirely  to  the  type  of  construction  requirements  of  the  building  to  which  it  is  attached  and  is  limited  in  height  as  a  main  part  of  the  building.  If  the  area  of  the  tower  and  spire  exceeds  10.00  square  m  on  any  horizontal  cross  section,  its  supporting  frames  shall  extend  directly  to  the  ground.  The  roof  covering  of  the  spires  shall  be  as  required  for  the  main  room  of  the  rest  of  the  structure.  Skeleton  towers  used  as  radio  masts,  neon  signs,  or  advertisement  frames  and  placed  on  the  roof  of  any  building  shall  be  constructed  entirely  of  incombustible  materials  when  more  than  7.50  m  in  height,  and  shall  be  directly  supported  on  an  incombustible  framework  to  the  ground.  No  such  skeleton  towers  shall  be  supported  on  roofs  of  combustible  framings.  They  shall  be  designed  to  withstand  a  wind  load  from  any  direction  in  addition  to  any  other  loads.       SECTION  1211.  Chimneys,  Fireplaces,  and  Barbecues     (a)  Chimneys  (1)  Structural  Design.  Chimneys  shall  be  designed,  anchored,  supported,  reinforced,  constructed,  and  installed  in  accordance  with  generally  accepted  principles  of  engineering.  Every  chimney  shall  be  capable  of  producing  a  draft  at  the  appliance  not  less  than  that  required  for  the  safe  operation  of  the  appliance  connected  thereto.  No  chimney  shall  support  any  structural  load  other  than  its  own  weight  unless  it  is  designed  to  act  as  a  supporting  member.  Chimneys  in  a  wood-­‐framed  building  shall  be  anchored  laterally  at  the  ceiling  line  and  at  each  floor  line  which  is  more  than  1.80  m  above  grade,  except  when  entirely  within  the  framework  or  when  designed  to  be  free  standing.     (2)  Walls.  Every  masonry  chimney  shall  have  walls  of  masonry  units,  bricks,  stones,  listed  masonry  chimney  units,  reinforced  concrete  or  equivalent  solid  thickness  of  hollow  masonry  and  lined  with  suitable  liners  in  accordance  with  the  following  requirements:     (2.1)  Masonry  Chimneys  for  Residential  Type  Appliances.  Masonry  chimneys  shall  be  constructed  of  masonry  units  or  reinforced  concrete  with  walls  not  less  than  100  mm  thick;  or  of  rubble  stone  masonry  not  less  than  300  mm  thick.  The  chimney  liner  shall  be  in  accordance  with  this  Code.     (2.2)  Masonry  Chimneys  for  Low  Heat  Appliances.  Masonry  chimneys  shall  be  constructed  of  masonry  units  or  reinforced  concrete  with  walls  not  less  than  200  mm  thick:  Except,  that  rubble  stone  masonry  shall  be  not  less  than  300  mm  thick.  The  chimney  liner  shall  be  in  accordance  with  this  Code.     

  

28  

(2.3)  Masonry  Chimneys  for  Medium-­‐Heat  Appliances.  Masonry  chimneys  for  medium-­‐heat  appliances  shall  be  constructed  of  solid  masonry  units  of  reinforced  concrete  not  less  than  200  mm  thick,  Except,  that  stone  masonry  shall  be  not  less  than  300  mm  thick  and,  in  addition  shall  be  lined  with  not  less  than  100  mm  of  firebrick  laid  in  a  solid  bed  of  fire  clay  mortar  with  solidly  filled  head,  bed,  and  wall  joints,  starting  not  less  than  600  mm  below  the  chimney  connector  entrance.  Chimneys  extending  7.50  m  or  less  above  the  chimney  connector  shall  be  lined  to  the  top.     (2.4)  Masonry  Chimneys  for  High-­‐Heat  Appliances.  Masonry  chimneys  for  high-­‐  heat  appliances  shall  be  constructed  with  double  walls  of  solid  masonry  units  or  reinforced  concrete  not  less  than  200  mm  in  thickness,  with  an  air  space  of  not  less  than  50  mm  between  walls.  The  inside  of  the  interior  walls  shall  be  of  firebrick  not  less  than  100  mm  in  thickness  laid  in  a  solid  bed  of  fire  clay  mortar  with  solidly  filled  head,  bed,  and  wall  joints.     (2.5)  Masonry  Chimneys  for  incinerators  installed  in  Multi-­‐Storey  Buildings  (Apartment-­‐Type  Incinerators).  Chimneys  for  incinerators  installed  in  multi-­‐storey  buildings  using  the  chimney  passageway  as  a  refuse  chute  where  the  horizontal  grate  area  of  combustion  chamber  does  not  exceed  0.80  square  m  hall  have  walls  of  solid  masonry  or  reinforced  concrete,  not  less  than  100  mm  thick  with  a  chimney  lining  as  specified  in  this  Code.  If  the  grate  area  of  such  an  incinerator  exceeds  0.80  square,  m,  the  walls  shall  not  be  less  than  100  mm  of  firebrick  except  that  higher  than  9.00  m  above  the  roof  of  the  combustion  chamber,  common  brick  alone  200  mm  in  thickness  may  be  used.     (2.6)  Masonry  Chimneys  for  Commercial  and  Industrial  Type  Incinerators.  Masonry  chimneys  for  commercial  and  industrial  type  incinerators  of  a  size  designed  for  not  more  than  110  kilograms  of  refuse  per  hour  and  having  a  horizontal  grate  area  not  exceeding  0.50  square  m  hall  have  walls  of  solid  masonry  or  reinforced  concrete  not  less  than  100  mm  thick  with  lining  of  not  less  than  100  mm  of  firebrick,  which  lining  shall  extend  for  not  less  than  12.00  m  above  the  roof  of  the  combustion  chamber.  If  the  design  capacity  of  grate  area  of  such  an  incinerator  exceeds  110  kilograms  per  hour  and  0.80  square  m  respectively,  walls  shall  not  be  less  than  200  mm  thick,  lined  with  not  less  than  100  mm  of  firebrick  extending  the  full  height  of  the  chimney.     (3)  Linings.  Fire  clay  chimney  lining  shall  not  be  less  than  15  mm  thick.  The  lining  shall  extend  from  200  mm  below  the  lowest  inlet  or,  in  the  case  of  fireplace,  from  the  throat  of  the  fireplace  to  a  point  above  enclosing  masonry  walls.  Fire  clay  chimney  linings  shall  be  installed  ahead  of  the  construction  of  the  chimney  as  it  is  carried  up,  carefully  bedded  one  on  the  other  in  fire  clay  mortar,  with  close-­‐fitting  joints  left  smooth  on  the  inside.  Firebrick  not  less  than  500  mm  thick  may  be  used  in  place  of  fire  clay  chimney.     (4)  Area.  No  chimney  passageway  shall  be  smaller  in  area  than  the  vent  connection  of  the  appliance  attached  thereto.     (5)  Height.  Every  masonry  chimney  shall  extend  at  least  600  mm  above  the  part  of  the  roof  through  which  it  passes  and  at  least  600  mm  above  the  highest  elevation  of  any  part  of  a  building  within  3.00  m  to  the  chimney.     (6)  Corbeling.  No  masonry  chimney  shall  be  corbeled  from  a  wall  more  than  150  mm  nor  shall  a  masonry  chimney  be  corbelled  from  a  wall  which  is  less  than  300  mm  in  thickness  unless  it  projects  equally  on  each  side  of  the  wall.  In  the  second  storey  of  a  two-­‐storey  building  of  Group  A  Occupancy,  corbeling  of  masonry  chimneys  on  the  exterior  of  the  enclosing  walls  may  equal  the  wall  thickness.  In  every  case  the  corbeling  shall  not  exceed  25  mm  projection  for  each  course  of  brick.     (7)  Change  in  size  or  Shape.  No  change  in  the  size  or  shape  of  a  masonry  chimney  shall  be  made  within  a  distance  of  150  mm  above  or  below  the  roof  joints  or  rafters  where  the  chimney  passes  through  the  roof.     (8)  Separation.  When  more  than  one  passageway  is  contained  in  the  same  chimney,  masonry  separation  at  least  100  mm  thick  bonded  into  the  masonry  wall  of  the  chimney  shall  be  provided  to  separate  passageways.     (9)  Inlets.  Every  inlet  to  any  masonry  chimney  shall  enter  the  side  thereof  and  shall  be  of  not  less  than  3  mm  thick  metal  or  16  mm  refractory  material.     

  

29  

(10)  Clearance.  Combustible  materials  shall  not  be  placed  within  50  mm  of  smoke  chamber  or  masonry  chimney  walls  when  built  within  a  structure,  or  within  25  mm  when  the  chimney  is  built  entirely  outside  the  structure.     (11)  Termination.  An  incinerator  chimney  shall  terminate  in  a  substantially  constructed  spark  arrester  having  a  mesh  not  exceeding  20  mm.     (12)  Cleanouts.  Cleanout  openings  shall  be  provided  at  the  base  of  every  masonry  chimney.     (b)  Fireplaces  and  Barbecues     Fireplaces,  barbecues,  smoke  chambers,  and  fireplace  chimneys  shall  be  of  solid  masonry  or  reinforced  concrete  and  shall  conform  to  the  minimum  requirements  specified  in  this  Code.     (1)  Fireplace  Walls.  Walls  of  fireplaces  shall  not  be  less  than  200  mm  in  thickness.  Walls  of  fireboxes  shall  not  be  less  than  250  mm  in  thickness:  Except,  that  where  a  lining  of  firebrick  is  used,  such  walls  shall  not  be  less  than  200  mm  in  thickness.  The  firebox  shall  not  be  less  than  500  mm  in  depth.  The  maximum  thickness  of  joints  in  firebrick  shall  be  10  mm.     (2)  Hoods.  Metal  hoods  used  as  part  of  a  fireplace  or  barbecue  shall  be  not  less  than  No.  18  gauge  copper,  galvanized  iron,  or  other  equivalent  corrosion-­‐resistant  ferrous  metal  with  all  seams  and  connections  of  smokeproof  unsoldered  construction.  The  hoods  shall  be  sloped  at  an  angle  of  45  degrees  or  les  from  the  vertical  and  shall  extend  horizontally  at  least  150  mm  beyond  the  limits  of  the  firebox.  Metal  hoods  shall  be  kept  a  minimum  of  400  mm  from  combustible  materials.     (3)  Circulators.  Approved  metal  heat  circulators  may  be  installed  in  fireplaces.     (4)  Smoke  Chamber.  Front  and  side  walls  shall  not  be  less  than  200  mm  in  thickness.  Smoke  chamber  back  walls  shall  not  be  less  than  150  mm  in  thickness.     (5)  Fireplace  Chimneys.  Walls  of  chimneys  without  flue  lining  shall  not  be  less  than  200  mm  in  thickness.  Walls  of  chimneys  with  flue  lining  shall  not  be  less  than  100  mm  in  thickness  and  shall  be  constructed  in  accordance  with  the  requirements  of  this  Code.     (6)  Clearance  to  Combustible  Materials.  Combustible  materials  shall  not  be  placed  within  50  mm  of  fireplace,  smoke  chamber,  or  chimney  walls  when  built  entirely  within  a  structure,  or  within  25  mm  when  the  chimney  is  built  entirely  outside  the  structure.  Combustible  materials  shall  not  be  placed  within  150  mm  of  the  fireplace  opening.  No  such  combustible  material  within  300  mm  of  the  fireplace  opening  shall  project  more  than  3  mm  for  each  25  mm  clearance  from  such  opening.  
No  part  of  metal  hoods  used  as  part  of  a  fireplace,  barbecue  or  heating  stoves  shall  be  less  than  400  mm  from  combustible  material.  This  clearance  may  be  reduced  to  the  minimum  requirements  set  forth  in  this  Code.     (7)  Area  of  Flues,  Throats,  and  Dampers.  The  net  cross-­‐sectional  area  of  the  flue  and  of  the  throat  between  the  firebox  and  the  smoke  chamber  of  a  fireplace  shall  not  be  less  than  the  requirements  to  be  set  forth  by  the  Secretary.  Where  dampers  are  used,  they  shall  be  of  not  less  than  No.  12  gauge  metal.  When  fully  opened,  damper  opening  shall  be  not  less  than  ninety  percent  of  the  required  flue  area.  When  fully  open,  damper  blades  shall  not  extend  beyond  the  line  of  the  inner  face  of  the  flue.     (8)  Lintel  –  Masonry  over  the  fireplace  opening  shall  be  supported  by  a  non-­‐combustible  lintel.     (9)  Hearth  –  Every  fireplace  shall  be  provided  with  a  brick,  concrete,  stone,  or  other  approved  non-­‐combustible  hearth  slab  at  least  300  mm  wider  on  each  side  then  the  fireplace  opening  and  projecting  at  least  450  mm  therefrom.  This  slab  shall  not  be  less  than  100  mm  thick  and  shall  be  supported  by  a  noncombustible  material  or  reinforced  to  carry  its  own  weight  and  all  imposed  loads.       SECTION  1212.  Fire-­‐Extinguishing  Systems     (a)  Fire-­‐Extinguishing  Systems  –  Where  required,  standard  automatic  fire-­‐extinguishing  systems  shall  be  installed  in  the  following  places,  and  in  the  manner  provided  in  this  Code.     (1)  In  every  storey,  basement  or  cellar  with  an  area  of  200  square  m  or  more  which  is  used  for  habitation,  recreation,  dining,  study,  or  work,  and  which  has  an  occupant  load  of  more  than  20.     (2)  In  all  dressing  rooms,  rehearsal  rooms,  workshops  or  factories,  and  other  rooms  with  an  occupant  load  of  more  than  10  or  assembly  halls  under  Group  H  and  I  occupancies  with  occupant  load  of  more  than  500,  and  if  the  next  doors  of  said  rooms  are  more  than  30.00  m  from  the  nearest  safe  fire  dispersal  area  of  the  building  or  opening  to  an  exit  court  or  street.     

  

30  

(3)  In  all  rooms  used  for  storage  or  handling  of  photographic  x-­‐ray  nitrocellulose  films  and  other  inflammable  articles.     (b)  Dry  Standpipes  –  Every  building  four  or  more  storeys  in  height  shall  be  equipped  with  one  or  more  dry  standpipes.     (1)  Construction  and  Tests  –  Dry  standpipes  shall  be  of  wrought  iron  or  galvanized  steel  and  together  with  fittings  and  connections  shall  be  of  sufficient  strength  to  withstand  20  kilograms  per  square  centim  of  water  pressure  when  ready  for  service,  without  leaking  at  the  joints,  valves,  or  fittings.  
Tests  shall  be  conducted  by  the  owner  or  the  building  contractor  in  the  presence  of  a  representative  of  the  Building  Official  whenever  deemed  necessary  for  the  purpose  of  certification  of  its  proper  function.     (2)  Size  –  Dry  standpipes  shall  be  of  such  size  as  to  be  capable  of  delivering  900  liters  or  water  per  minute  from  each  of  any  three  outlets  simultaneously  under  the  pressure  created  by  one  fire  engine  or  pumper  based  on  the  standard  equipment  available.     (3)  Number  Required  –  Every  building  four  or  more  storeys  in  height  where  the  area  of  any  floor  above  the  third  floor  is  950  square  m  or  less,  shall  be  equipped  with  at  least  one  dry  standpipe  and  an  additional  standpipe  shall  be  installed  for  each  additional  950  square  m  or  fraction  thereof.     (4)  Location  –  Standpipes  shall  be  located  within  enclosed  stairway  landings  or  near  such  stairways  as  possible  or  immediately  inside  of  an  exterior  wall  and  within  300  mm  of  an  opening  in  a  stairway  enclosure  of  the  balcony  or  vestibule  of  a  smokeproof  tower  or  an  outside  exit  stairway.     (5)  Siamese  Connections  –  Subject  to  the  provisions  of  subparagraph  (2)  all  100  mm  dry  standpipes  shall  be  equipped  with  a  two-­‐way  Siamese  fire  department  connection.  All  125  mm  dry  standpipes  shall  be  equipped  with  a  three-­‐way  Siamese  fire  department  connection  and  150  mm  dry  standpipes  shall  be  equipped  with  a  four-­‐  way  Siamese  fire  department  connections.  All  Siamese  inlet  connections  shall  be  located  on  a  street-­‐front  of  the  building  and  not  less  than  300  mm  nor  more  than  1.20  m  above  the  grade  and  shall  be  equipped  with  a  clapper-­‐checks  and  substantial  plugs.  All  Siamese  inlet  connections  shall  be  recessed  in  the  wall  or  otherwise  substantially  protected.     (6)  Outlets  –  All  dry  standpipes  shall  extend  from  the  ground  floor  to  and  over  the  roof  and  shall  be  equipped  with  a  63  mm  outlet  nor  more  than  1.20  m  above  the  floor  level  at  each  storey.  All  dry  standpipes  shall  be  equipped  with  a  two-­‐way  63  mm  outlet  above  the  roof.  All  outlets  shall  be  equipped  with  gate  valves.     (7)  Signs  –  An  iron  or  bronze  sign  with  raised  letters  at  least  25  mm  high  shall  be  rigidly  attached  to  the  building  adjacent  to  all  Siamese  connections  and  such  signs  shall  read:  “CONNECTION  TO  DRY  STANDPIPE”.     (c)  Wet  Standpipes  –  Every  Group  H  and  I  Occupancy  of  any  height,  and  every  Group  C  Occupancy  of  two  more  storeys  in  height,  and  every  Group  B,  D,  E,  F  and  G  Occupancy  of  three  or  more  storeys  in  height  and  every  Group  G  and  E  Occupancy  over  1800  square  m  in  area  shall  be  equipped  with  one  or  more  interior  wet  standpipes  extending  from  the  cellar  or  basement  into  the  topmost  storey:  Provided,  that  Group  H  buildings  having  no  stage  and  having  a  seating  capacity  of  less  than  500  need  not  be  equipped  with  interior  wet  standpipes.     (1)  Construction  –  Interior  wet  standpipes  shall  be  constructed  of  the  same  materials  as  those  required  for  dry  standpipes.     (2)  Size  (2.1)  Interior  wet  standpipes  shall  have  an  internal  diamufficient  to  deliver  190  liters  of  water  per  minute  under  2.0  kilograms  per  square  centim  pressure  at  the  hose  connections.  Buildings  of  Group  H  and  I  Occupancy  shall  have  wet  standpipes  systems  capable  of  delivering  the  required  quantity  and  pressure  from  any  two  outlets  simultaneously;  for  all  other  occupancies  only  one  outlet  need  be  figured  to  be  opened  at  one  time.  In  no  case  shall  the  internal  diam  of  a  wet  standpipe  be  less  than  50  mm,  except  when  the  standpipe  is  attached  to  an  automatic  fire-­‐extinguishing  system.     (2.2)  Any  approved  formula  which  determine  pipe  sizes  on  a  pressure  drop  basis  may  be  used  to  determine  pipe  size  for  wet  standpipe  systems.  The  Building  Official  may  require  discharge  capacity  and  pressure  tests  on  completed  wet  standpipe  systems.     

  

31  

(3)  Number  required  –  The  number  of  wet  standpipes  when  required  in  this  Code  shall  be  so  determined  that  all  portions  of  the  building  are  within  6.00  m  of  a  nozzle  attached  to  a  hose  23.00  m  in  length.     (4)  Location  –  In  Group  H  and  I  Occupancies,  outlets  shall  be  located  as  follows:  one  on  each  side  of  the  stage,  one  at  the  rear  of  the  auditorium,  and  one  at  the  rear  of  the  balcony.  Where  occupant  loads  are  less  than  500  the  above  requirements  may  be  waived:  Provided,  that  portable  fire-­‐extinguishers  of  appropriate  capacity  and  type  are  installed  within  easy  access  from  the  said  locations.  In  Group  B,  C,  D,  E,  F  and  G  Occupancies,  the  location  of  all  interior  wet  standpipes  shall  be  in  accordance  with  the  requirement  for  dry  standpipes:  Provided,  that  at  least  one  standpipe  is  installed  to  cover  not  more  than  650  square  m.     (5)  Outlets.  All  interior  wet  standpipes  shall  be  equipped  with  a  38  mm  valve  in  each  storey,  including  the  basement  or  cellar  of  the  building,  and  located  not  less  than  300  mm  nor  more  than  1.20  m  above  the  floor.     (6)  Threads.  All  those  threads  used  in  connection  with  the  installation  of  such  standpipes,  including  valves  and  reducing  fittings  shall  be  uniform  with  that  prescribed  by  the  Secretary.     (7)  Water  Supply.  All  interior  wet  standpipes  shall  be  connected  to  a  street  main  not  less  than  100  mm  in  diam,  or  when  the  water  pressure  is  insufficient,  to  a  water  tank  of  sufficient  size  as  provided  in  subparagraph  (8).  When  more  than  one  interior  wet  standpipe  is  required  in  the  building,  such  standpipe  shall  be  connected  at  their  bases  or  at  their  tops  by  pipes  of  equal  size.     (8)  Pressure  and  Gravity  Tanks  –  Tanks  shall  have  a  capacity  sufficient  to  furnish  at  least  1,500  liters  per  minute  for  a  period  of  not  less  than  10  minutes.  Such  tanks  shall  be  located  so  as  to  provide  not  less  than  2  kilograms  per  square  centim  pressure  at  the  topmost  base  outlet  for  its  entire  supply.  Discharge  pipes  from  pressure  tanks  shall  extend  50  mm  into  and  above  the  bottom  of  such  tanks.  All  tanks  shall  be  tested  in  place  after  installation  and  proved  tight  at  a  hydrostatic  pressure  fifty  percent  in  excess  of  the  working  pressure  required.  Where  such  tanks  are  used  for  domestic  purposes  the  supply  pipe  for  such  purposes  shall  be  located  at  or  above  the  center  line  of  such  tanks.  Incombustible  supports  shall  be  provided  for  all  such  supply  tanks  and  not  less  than  a  900  mm  clearance  shall  be  maintained  over  the  top  and  under  the  bottom  of  all  pressure  tanks.     (9)  Fire  pumps.  Fire  pumps  shall  have  a  capacity  of  not  less  than  1,000  liters  per  minute  with  a  pressure  not  less  than  2  kilograms  per  square  centim  at  the  topmost  hose  outlet.  The  source  of  supply  for  such  pump  shall  be  a  street  water  main  of  not  less  than  100  mm  diam  or  a  well  or  cistern  containing  a  one-­‐hour  supply.  Such  pumps  shall  be  supplied  with  an  adequate  source  of  power  and  shall  be  automatic  in  operation.     (10)  Hose  and  Hose  Reels  –  Each  hose  outlet  of  all  interior  wet  standpipes  shall  be  supplied  with  a  hose  not  less  than  38  mm  in  diamuch  hose  shall  be  equipped  with  a  suitable  brass  or  bronze  nozzle  and  shall  be  not  over  23.00  m  in  length.  An  approved  standard  form  of  wall  hose  reel  or  rack  shall  be  provided  for  the  hose  and  shall  be  located  so  as  to  make  the  hose  readily  accessible  at  all  times  and  shall  be  recessed  in  the  walls  or  protected  by  suitable  cabinets.     (d)  Basement  Pipe  Inlets  –  Basement  pipe  inlets  shall  be  installed  in  the  first  floor  of  every  store,  warehouse,  or  factory  where  there  are  cellars  or  basements  under  same:  Except,  where  in  such  cellars  or  basements  there  is  installed  a  fire-­‐extinguishing  system  as  specified  in  this  Code  or  where  such  cellars  or  basements  are  used  for  banking  purposes,  safe  deposit  vaults,  or  similar  uses.     (1)  Material  –  All  basement  pipe  inlets  shall  be  of  cast  iron,  steel,  brass,  or  bronze  with  lids  of  cast  brass  or  bronze  and  shall  consist  of  a  sleeve  not  less  than  200  mm  in  diam  through  the  floor  extending  to  and  flush  with  the  ceiling  below  and  with  a  top  flange,  recessed  with  an  inside  shoulder,  to  receive  the  lid  and  flush  with  the  finished  floor  surface.  The  lid  shall  be  a  solid  casting  and  shall  have  a  ring  lift  recessed  on  the  top  thereof,  so  as  to  be  flushed.  The  lid  shall  have  the  words  “FOR  FIRE  DEPARTMENT  ONLY,  DO  NOT  COVER  UP”  cast  on  the  top  thereof.  The  lid  shall  be  installed  in  such  a  manner  as  to  permit  its  removal  readily  from  the  inlet.     (2)  Location.  Basement  pipe  inlets  shall  be  strategically  located  and  kept  readily  accessible  at  all  times  to  the  Fire  Department.     (e)  Approval  –  All  fire-­‐extinguishing  systems,  including  automatic  sprinklers,  wet  and  dry  standpipes,  automatic  chemical  extinguishers,  basement  pipe  inlets,  and  the  appurtenances  thereto  shall  meet  

  

32  

the  approval  of  the  Fire  Department  as  to  installation  and  location  and  shall  be  subject  to  such  periodic  tests  as  it  may  require.       SECTION  1213.  Stages  and  Platform     (a)  Stage  Ventilators  –  There  shall  be  one  or  more  ventilators  constructed  of  metal  or  other  incombustible  material  near  the  center  and  above  the  highest  part  of  any  working  stage  raised  above  the  stage  roof  and  having  a  total  ventilation  area  equal  to  at  least  five  percent  of  the  floor  area  within  the  stage  walls.  The  entire  equipment  shall  conform  to  the  following  requirements:     (1)  Opening  Action  –  Ventilators  shall  open  by  spring  action  or  force  of  gravity  sufficient  to  overcome  the  effects  of  neglect,  rust,  dirt,  or  expansion  by  heat  or  warping  of  the  framework.     (2)  Glass  –  Glass,  if  used  in  ventilators,  must  be  protected  against  falling  on  the  stage.  A  wire  screen,  if  used  under  the  glass,  must  be  so  placed  that  if  clogged  it  cannot  reduce  the  required  ventilating  area  or  interfere  with  the  operating  mechanism  or  obstruct  the  distribution  of  water  from  the  automatic  fire  extinguishing  systems.     (3)  Design  –  Ventilators,  penthouses,  and  supporting  framework  shall  be  designed  in  accordance  with  this  Code.     (4)  Spring  Actuation  –  Springs,  when  employed  to  actuate  ventilator  doors,  shall  be  capable  of  maintaining  full  required  tension  indefinitely.  Springs  shall  not  be  stressed  more  than  fifty  percent  of  their  rated  capacity  and  shall  not  be  located  directly  in  the  air  stream,  nor  exposed  to  elements.     (5)  Location  of  Fusible  Links  –  A  fusible  link  shall  be  placed  in  the  cable  control  system  on  the  underside  of  the  ventilator  at  or  above  the  roof  line  or  as  approved  by  the  Building  Official,  and  shall  be  so  located  as  not  to  be  affected  by  the  operation  of  fire-­‐extinguishing  systems.     (6)  Control  –  Remote,  manual  or  electrical  control  shall  provide  for  both  opening  and  closing  of  the  ventilator  doors  for  periodic  testing  and  shall  be  located  at  a  point  on  the  stage  designated  by  the  Building  Official.  When  remote  control  of  ventilator  is  electrical,  power  failure  shall  not  affect  its  instant  operation  in  the  event  of  fire.  Hand  winches  may  be  employed  to  facilitate  operation  of  manually  controlled  ventilators.     (b)  Gridirons  –     (1)  Gridirons  fly  galleries,  and  pin-­‐rails  shall  be  constructed  of  incombustible  materials  and  fire  protection  of  steel  and  iron  may  be  omitted.  Gridirons  and  fly  galleries  shall  be  designed  to  support  a  live  load  of  not  less  than  367  kilograms  per  square  m.  Each  loft  block  well  shall  be  designed  to  support  373  kilograms  per  linear  m  and  the  head  block  well  shall  be  designed  to  support  the  aggregate  weight  of  all  the  loft  block  wells  served.  The  head  block  well  must  be  provided  with  an  adequate  strong  back  or  lateral  brace  to  offset  torque.     (2)  The  main  counterweight  sheave  beam  shall  be  designed  to  support  a  horizontal  and  vertical  uniformly  distributed  live  load  sufficient  to  accommodate  the  weight  imposed  by  the  total  number  of  loft  blocks  in  the  gridiron.  The  sheave  blocks  shall  be  designed  to  accommodate  the  maximum  load  for  the  loft  or  head  blocks  served  with  a  safety  factor  of  five.     (c)  Rooms  Accessory  to  Stage  –  In  a  building  having  a  stage,  the  dressing  room  sections,  workshops,  and  storerooms  shall  be  located  on  the  stage  side  of  the  proscenium  wall  and  shall  be  separated  from  each  other  and  from  the  stage  by  not  less  than  a  One-­‐Hour  Fire-­‐Resistive  Occupancy  Separation.     (d)  Proscenium  Walls  –  A  stage  shall  be  completely  separated  from  the  auditorium  by  a  proscenium  wall  of  not  less  than  two-­‐hour  incombustible  construction.  The  proscenium  wall  shall  extend  not  less  than  1.20  m  above  the  roof  over  the  auditorium.  Proscenium  walls  may  have,  in  addition  to  the  main  proscenium  openings,  one  opening  at  the  orchestra  pit  level  and  not  more  than  two  openings  at  the  stage  floor  level,  each  of  which  shall  be  not  more  than  2.00  square  m  in  area.  All  openings  in  the  proscenium  wall  of  stage  shall  be  protected  by  a  fire  assembly  having  a  one  and  one-­‐half-­‐hour  fire-­‐resistive  rating.  The  proscenium  opening,  which  shall  be  the  main  opening  for  viewing  performances,  shall  be  provided  with  a  self  closing  fire-­‐resistive  curtain  as  specified  in  this  Code.     (e)  Stage  Floor  –  The  type  of  construction  for  stage  floors  shall  depend  upon  the  requirements  based  on  the  type  of  Occupancy  and  the  corresponding  fire-­‐resistive  requirements.  All  parts  of  the  stage  floor  shall  be  designed  to  support  not  less  than  620  kilograms  per  square  m.  Openings  through  stage  floors  shall  be  equipped  with  tight-­‐fitting  trap  doors  of  wood  of  not  less  than  50  mm  nominal  thickness.     

  

33  

(f)  Platforms  –  The  type  of  construction  for  platforms  shall  depend  upon  the  requirements  based  on  the  Type  of  Occupancy  and  corresponding  fire-­‐resistive  requirements.  Enclosed  platforms  shall  be  provided  with  one  or  more  ventilators  conforming  to  the  requirements  of  stage  ventilators:  Except,  that  the  total  area  shall  be  equal  to  five  percent  of  the  area  of  the  platform.  When  more  than  one  ventilator  is  provided,  they  shall  be  so  spaced  as  to  provide  proper  exhaust  ventilation.  Ventilators  shall  not  be  required  for  enclosed  platforms  having  a  floor  area  of  45.00  square  m  or  less.     (g)  Stage  Exits  –  At  least  one  exit  not  less  than  900  mm  wide  shall  be  provided  from  each  side  of  the  stage  opening  directly  or  by  means  of  a  passageway  not  less  than  900  mm  in  width  to  a  street  or  exit  court.  An  exit  stair  not  less  than  750  mm  wide  shall  be  provided  for  egress  from  each  fly  gallery.  Each  tier  of  dressing  rooms  shall  be  provided  with  at  least  two  means  of  egress  each  not  less  than  750  mm  wide  and  all  such  stairs  shall  be  constructed  in  accordance  with  the  requirement  specified  in  this  Code.  The  stairs  required  in  this  Sub-­‐section  need  not  be  enclosed.       SECTION  1214.  Motion  Picture  Projection  Rooms     (a)  General  Requirements  –  The  provisions  of  this  Section  shall  apply  only  where  ribbon  type  motion  picture  films  in  excess  of  22-­‐mm  width  and  electric  projection  equipment  are  used.  Every  motion  picture  machine  using  ribbon  type  film  in  excess  of  22  mm  width  and  electric  arc  projections  equipment,  together  with  all  electrical  devices,  rheostats,  machines,  and  all  such  films  present  in  any  Group  C,  I,  or  H  Occupancy,  shall  be  enclosed  in  a  projection  room  large  enough  to  permit  the  operator  to  walk  freely  on  either  side  and  back  of  the  machine.  
(b)  Construction  –  Every  projection  room  shall  be  of  not  less  than  one-­‐hour  fire-­‐resistive  construction  throughout  and  the  walls  and  ceiling  shall  be  finished  with  incombustible  materials.  The  ceiling  shall  be  not  less  than  2.40  m  from  the  finished  floor.  The  room  shall  have  a  floor  area  of  not  less  than  7.00  square  m  and  3.50  square  m  for  each  additional  machine.     (c)  Exit  –  Every  projection  room  shall  have  at  least  two  doorways  separated  by  not  less  than  one-­‐third  the  perim  of  the  room,  each  at  least  750  mm  wide  and  2.00  m  high.  All  entrances  to  a  projection  room  shall  be  protected  by  a  self-­‐closing  fire  assembly  having  a  three-­‐  fourths  hour  fire-­‐resistive  rating.  Such  doors  shall  open  outward  and  lead  to  proper  exits  as  required  in  this  Code  and  shall  not  be  equipped  with  any  latch.  The  maximum  width  of  such  door  shall  be  750  mm.     (d)  Ports  and  Openings  –  Ports  in  projection  room  walls  shall  be  of  three  kinds:  projection  ports;  observation  ports;  and  combination  ports  used  for  both  observation  and  for  stereopticon,  spot  or  floodlight  machines.     (1)  Ports  Required  –  There  shall  be  provided  for  each  motion  picture  projector  not  more  than  one  projection  port,  which  shall  be  limited  in  area  to  750  square  cm,  and  not  more  than  one  observation  port,  which  shall  be  limited  in  area  to  1,300  square  cm.  There  shall  be  not  more  than  three  combination  ports,  each  of  which  shall  not  exceed  750  mm  by  600  mm.  Each  port  opening  shall  be  completely  covered  with  a  pane  of  glass:  Except,  that  when  acetate  safety  film  is  used,  projection  ports  may  be  increased  in  size  to  an  area  not  to  exceed  4,500  square  cm.     (2)  Shutters  –  Each  port  and  every  other  opening  in  projection  room  walls,  including,  any  fresh-­‐air  inlets  but  excluding  exit  doors  and  exhaust  ducts,  shall  be  provided  with  a  shutter  of  not  less  than  2.4  mm  thick  sheet  metal  or  its  equivalent  large  enough  to  overlap  at  least  25  mm  on  all  sides  of  such  openings.  Shutters  shall  be  arranged  to  slide  without  binding  in  guides  constructed  of  material  equal  to  the  shutters  in  strength  and  fire-­‐resistance.  Each  shutter  shall  be  equipped  with  a  74°  fusible  link,  which  when  fused  by  heat  will  cause  closure  of  the  shutter  by  gravity.  Shutters  of  a  size  greater  than  1,300  square  cm  shall  be  equipped  with  a  counter-­‐balance.  There  shall  also  be  a  fusible  link  located  over  the  upper  magazine  of  each  projector,  which  upon  operating,  will  close  all  the  shutters.  In  addition,  there  shall  be  provided  suitable  means  for  manually  closing  all  shutters  simultaneously  from  any  projector  head  and  from  a  point  within  the  projection  room  near  each  exit  door.  Shutters  on  openings  not  in  use  shall  be  kept  closed:  Except,  that  shutters  may  be  omitted  when  only  acetate  safety  film  is  used.     (e)  Ventilation  –  (1)  Inlet  –  A  fresh-­‐air  inlet  from  the  exterior  of  the  building  not  less  than  900  square  cm  and  protected  with  wire  netting,  shall  be  installed  within  50  mm  of  the  floor  in  every  projection  room,  the  source  of  which  shall  be  remote  from  other  outside  vents  or  flues.     

  

34  

(2)  Outlets  –  Ventilation  shall  be  provided  by  one  or  more  mechanical  exhaust  systems  which  shall  draw  air  from  each  arc  lamp  housing  to  out-­‐doors  either  directly  or  through  an  incombustible  flue  used  for  no  other  purpose.  Exhaust  capacity  shall  not  be  less  than  0.50  cubic  m  nor  more  than  1.40  cubic  m  per  minute  for  each  arc  lamp  plus  5.60  cubic  m  for  the  room  itself.  Systems  shall  be  controlled  from  within  the  enclosure  and  shall  have  pilot  lights  to  indicate  operation.  The  exhaust  systems  serving  the  projection  room  may  be  extended  to  cover  rooms  associated  therewith  such  as  rewind  rooms.  No  dampers  shall  be  installed  in  such  exhaust  systems.  Ventilation  of  these  rooms  shall  not  be  connected  in  any  way  with  ventilating  or  air-­‐conditioning  systems  serving  other  portions  of  the  building.  Exhaust  ducts  shall  be  of  incombustible  material  and  shall  either  be  kept  25  mm  from  combustible  material  or  covered  with  10  mm  of  incombustible  heat-­‐insulating  material.     (f)  Regulation  of  Equipment  –  All  shelves,  fixtures,  and  fixed  equipment  in  a  projection  room  shall  be  constructed  of  incombustible  materials.  All  films  not  in  actual  use  shall  be  stored  in  metal  cabinets  having  individual  compartments  for  reels  or  shall  be  in  generally  accepted  shipping  containers.  No  solder  shall  be  used  in  the  construction  of  such  cabinets.       SECTION  1215.  Lathing,  Plastering,  and  Installation  of  Wall  Boards     The  installation  of  lath,  plaster  and  gypsum  wall  board  shall  conform  to  the  fire-­‐resistive  rating  requirements  and  the  type  of  construction  of  building.       CHAPTER  13  ELECTRICAL  AND  MECHANICAL  REGULATIONS    SECTION  1301.  Electrical  Regulations     All  electrical  systems,  equipment  and  installation  mentioned  in  this  Code  shall  conform  to  the  provisions  of  the  Philippine  Electrical  Code,  as  adopted  by  the  Board  of  Electrical  Engineering  pursuant  to  Republic  Act  No.  184  otherwise  known  as  the  Electrical  Engineering  Law.       SECTION  1302.  Mechanical  Regulations     All  mechanical  systems,  equipment  and  installations  mentioned  in  this  Code  shall  conform  to  the  provisions  of  the  Philippine  Mechanical  Engineering  code,  as  adopted  by  the  Board  of  Mechanical  Engineering  pursuant  to  Commonwealth  Act  No.  294  as  amended,  otherwise  known  as  the  Mechanical  Engineering  Law.       CHAPTER  14  PHOTOGRAPHIC  AND  X-­‐RAY  FILMS    SECTION  1401.  Storage  and  Handling     (a)  Storage  rooms  of  unexposed  photographic  and  x-­‐ray  films  shall  be  provided  with  automatic  fire  extinguishing  systems  in  the  following  cases:     (1)  When  unexposed  films  in  generally  accepted  safety  shipping  containers  exceed  the  aggregate  of  14.00  cubic  m.     (2)  Where  shelving  used  for  storage  of  individual  packages  not  in  said  shipping  containers  exceeds  1.40  cubic  m  in  capacity;  and     (3)  Storage  is  not  in  generally  accepted  safety  shipping  containers  in  any  section  not  exceeding  14.00  cubic  m.     (b)  Film  negatives  in  storage  or  in  process  of  handling  shall  be  kept  in  heavy  Manila  envelopes,  not  exceeding  12  films  to  an  envelope.  Expanding  envelopes  shall  not  be  used.     (c)  Film  negatives  shall  be  kept  in  properly  insulated  vented  cabinets,  vented  storage  vaults  or  outside  storage  houses.  Not  more  than  110  kilograms  shall  be  stored  in  any  single  cabinet.  Where  the  film  stored  exceeds  450  kilograms,  it  shall  be  in  vented  storage  vaults  or  in  a  detached  structure  or  roof  vault.  Door  openings  in  vaults  shall  be  of  four-­‐hour  fire-­‐resistive  construction  and  shall  be  kept  closed  except  when  in  use.     

  

35  

(d)  Only  incandescent  electric  light  shall  be  permitted;  protected  with  substantial  wire  guards  or  vapor  proof  globes  or  both.  Portable  lights  on  extension  cords  are  prohibited.  Conspicuous  “NO  SMOKING”  signs  shall  be  posted.     (e)  No  films  shall  be  stored  within  600  mm  of  steam  pipes,  chimneys,  or  other  sources  of  heat.     (f)  There  shall  be  first  aid  provisions  of  types  using  water  or  water  solutions.  Discarded  films  shall  be  stored  and  handled  in  the  same  manner  as  other  films  until  removed  from  the  premises.       SECTION  1402.  Classes  of  Film  Exempted     (a)  The  provisions  of  this  Section  do  not  apply  to  the  following:  film  for  amateur  photographic  use  in  original  packages  of  “roll”  and  “film  pack”  films  in  quantities  of  less  than  1.40  cubic  m;  safety  film;  dental  X-­‐ray  film;  establishments  manufacturing  photographic  films  and  their  storage  incidental  thereto  and  films  stored  or  being  used  in  standard  motion  picture  booths.     (b)  Safety  photographic  X-­‐ray  film  may  be  identified  by  the  marking  on  the  edge  of  the  film.       SECTION  1403.  Fire  Extinguishing  System     Unless  otherwise  provided  in  this  Code,  all  fire  extinguishing  systems  when  so  required  shall  be  of  a  type,  specifications,  and  methods  of  installation  as  prescribed  in  accordance  with  the  requirements  of  the  Secretary.       CHAPTER  15  PRE-­‐FABRICATED  CONSTRUCTION    SECTION  1501.  Prefabricated  Assembly     (a)  Prefabricated  assembly  is  a  structural  unit,  the  integral  parts  of  which  have  been  built  up  or  assembled  prior  to  incorporation  in  the  building.     (b)  The  Secretary  shall  prescribe  special  tests  to  determine  the  structural  adequacy,  durability,  soundness,  weather  and  fire  resistance  of  prefabricated  assemblies.     (c)  Every  device  or  system  to  connect  prefabricated  assemblies  shall  be  capable  of  developing  the  strength  of  the  different  members  as  an  integral  structure.  Except,  in  the  case  of  members  forming  part  of  a  structural  frame  as  specified  in  this  Code.  Anchorages  and  connections  between  members  and  the  supporting  elements  of  the  structure  or  walls  shall  be  capable  of  withstanding  all  probable  external  and  internal  forces  or  other  conditions  for  a  structurally  adequate  construction.  In  structural  design,  proper  allowances  shall  be  made  for  any  material  to  be  displaced  or  removed  for  the  installation  of  pipes,  conduits,  or  other  equipment.     (d)  Placement  of  prefabricated  assemblies  shall  be  inspected  to  determine  compliance  with  this  Code.       CHAPTER  16  PLASTICS    SECTION  1601.  Approved  Plastics     Approved  plastic  materials  shall  be  those  which  have  a  flame-­‐spread  rating  of  225  or  less  and  a  smoke  density  not  greater  than  that  obtained  from  the  burning  of  untreated  wood  under  similar  conditions  when  tested  in  accordance  with  generally  accepted  engineering  practices.  The  products  of  combustion  shall  be  no  more  toxic  than  the  burning  of  untreated  wood  under  similar  conditions.       SECTION  1602.  Installation     (a)  Structural  Requirements  –  All  plastic  materials  shall  be  of  adequate  strength  and  durability  to  withstand  the  prescribed  design  loads.  Sufficient  and  substantial  technical  data  shall  be  submitted  to  establish  stresses,  maximum  unsupported  spans,  and  such  other  information  as  may  be  deemed  necessary  for  the  various  thicknesses  and  forms  used.     (b)  Fastenings  –  Fastenings  shall  be  adequate  to  withstand  design  loads  and  internal  and  external  stresses  required  of  the  assembly.  Proper  allowances  of  plastic  materials  in  conjunction  with  other  materials  with  which  it  is  assembled  or  integrated  shall  be  provided.     
  

  

36  

SECTION  1603.  Glazing  of  Openings     (a)  Doors,  sashes  and  framed  openings  in  exterior  walls  of  all  buildings  except  Types  IV  and  V  Constructions  may  be  glazed  or  equipped  with  approved  plastics:  Provided,  that:     (1)  The  wall  in  which  such  glazing  is  installed  is  so  located  that  openings  are  not  required  to  be  fire-­‐protected.     (2)  Except  for  Type  I  Construction,  the  location,  size,  and  spacing  of  such  glazed  openings  do  not  exceed  the  values  set  forth  by  the  Secretary.     (3)  Plastics  used  in  glazed  openings  for  Type  II  Construction  shall  be  materials  appropriate  for  use  according  to  flame-­‐spread  characteristics  and  the  location,  size,  and  spacing  of  the  openings  do  not  exceed  the  values  set  forth  by  the  Secretary.       SECTION  1604.  Skylights     (a)  General  –  Approved  plastics  may  be  used  in  skylights  installed  on  roofs  of  Types  I,  II  or  III  constructions  and  all  buildings  in  these  categories  shall  be  equipped  with  an  approved  automatic  fire-­‐  extinguishing  system  in  Groups  A,  B,  C,  E,  F,  J,  H-­‐3  and  H-­‐4  Occupancies:  Except,  that:     (1)  Approved  plastics  may  be  used  in  any  type  of  construction  or  occupancy  as  a  fire  venting  system  when  approved  by  the  Building  Official.     (2)  Plastics  may  be  used  in  approved  skylights  in  Type  II  one-­‐hour  fire-­‐resistive  construction  which  are  located  300  mm  or  more  above  the  lower  flange  of  the  ceiling.  The  walls  of  the  skylight  well  shall  be  no  less  fire-­‐resistive  than  the  adjacent  ceiling.     (3)  Where  a  fire-­‐resistive  ceiling  is  not  required  in  one-­‐storey  buildings,  approved  plastics  may  be  used  in  skylights.     (b)  Installation  Requirements  (1)  Except  in  Group  A  Occupancies,  no  skylight  shall  be  installed  within  3.00  m  of  a  property  line.  
(2)  The  edges  of  dome-­‐type  skylights  shall  be  properly  flashed.  
(3)  Plastic  skylights  shall  be  separated  from  each  other  by  at  least  2.50  m  laterally  and  3.00  m  along  the  slope  of  the  roof.     (c)  Allowable  areas  –  The  area  of  individual  plastic  skylights  shall  not  exceed  10.00  square  m.  The  total  aggregate  area  of  plastics  used  in  skylights,  monitors,  and  sawtooth  glazing  shall  not  exceed  twenty  percent  of  the  floor  area  of  the  room  or  occupancy  sheltered.     (d)  Curb  Requirements  –  Plastic  skylights  in  roofs  having  a  slope  of  less  than  1  in  3  shall  have  a  100  mm  high  curb.  The  curb  may  be  omitted  where  a  wire  screen  not  smaller  than  No.  12  U.S.  gauge  with  a  mesh  not  larger  than  25-­‐mm  is  provided  immediately  below  the  skylight.  The  screen  shall  be  substantially  mounted  below  the  skylight.       SECTION  1605.  Light-­‐Transmitting  Panels  in  Monitors  and  Sawtooth  Roofs     (a)  General  –  Where  a  fire-­‐resistive  rating  is  not  required  for  the  roof  structure,  and  in  all  buildings  provided  with  an  approved  automatic  fire-­‐extinguishing  system,  approved  plastics  may  be  used  with  or  without  sash  as  the  light-­‐transmitting  medium  in  monitors  and  sawtooth;  Except,  that  plastics  used  in  monitors  or  sawtooth  roofs  of  Type  II  Construction  shall  be  of  materials  appropriate  to  be  used  according  to  flame-­‐spread  characteristics.     (b)  Allowable  Areas  –  The  area  of  individual  plastic  glazing  used  in  monitors  and  sawtooth  glazing  shall  not  exceed  15.00  square  m.  The  total  aggregate  area  of  plastics  used  in  skylights,  monitors,  and  sawtooth  glazing  shall  not  exceed  twenty  percent  of  the  floor  area  of  the  room  or  occupancy  sheltered.     (c)  Area  Separation  –  The  area  of  such  plastic  panels  shall  be  separated  from  each  other  by  a  section  of  incombustible  material  or  by  a  section  of  the  roofing  material  of  the  structure  not  less  than  1.50  m  in  length.  The  lower  edge  of  the  plastic  material  shall  be  at  least  150  mm  above  the  surface  of  the  adjoining  roof  surface.       SECTION  1606.  Plastic  Light  Diffusers  in  Ceilings     (a)  General  –  Ceiling  light  diffusers  having  an  area  greater  than  ten  percent  of  any  10.00  square  m  of  room  area  shall  be  of  approved  plastics  conforming  to  the  requirements  specified  in  this  Code.     

  

37  

(b)  Installation  –  Plastic  light  diffusers  shall  be  installed  in  such  a  manner  that  they  will  not  readily  become  detached  when  subjected  to  room  temperature  of  80°C  for  15  minutes,  Except,  for  plastic  light  diffusers  which  are  installed  in  the  first  floor  area  of  Group  C  Occupancies  having  egress  directly  to  the  exterior  of  the  building;  and  plastic  light  diffusers  which  are  located  between  an  approved  automatic  Fire-­‐extinguishing  system  and  the  area  to  be  protected  other  than  public  corridors  for  Group  A,  B,  C,  D,  E,  G,  H,  and  I  Occupancies  if  tests  required  by  the  Secretary  have  established  that  such  installation  will  not  interfere  with  the  efficient  operation  of  such  automatic  fire-­‐extinguishing  systems.       SECTION  1607.  Partitions     Where  partitions  are  not  required  to  be  of  fire-­‐resistive  or  incombustible  construction,  approved  plastics  conforming  to  the  requirements  specified  in  this  Code  may  be  used.       SECTION  1608.  Exterior  Veneer     (a)  General     Exterior  veneer  may  be  of  approved  plastic  materials,  and  shall  conform  to  the  provisions  of  this  Section.     (b)  Height     Plastic  veneer  shall  not  be  attached  to  any  exterior  wall  above  the  first  storey:  Provided,  that  plastic  veneer  may  be  attached  to  exterior  walls  above  the  first  storey  of  buildings  located  outside  of  highly  restrictive  Fire  Zones:  Provided,  further  that  the  height  of  veneer  is  not  in  excess  of  10.00  m  above  the  adjacent  grade  of  elevation.     (c)  Area     Sections  of  plastic  veneer  shall  not  exceed  15.00  square  m  in  area,  Except,  that  in  less  restrictive  Fire  Zones,  the  area  may  be  increased  by  fifty  percent.     (d)  Separation     Sections  of  plastic  veneer  shall  be  separated  by  a  minimum  of  1.20  m  vertically  and  600  mm  horizontally.       SECTION  1609.  Awnings  and  Canopies     (a)  Plastic  materials  appropriate  for  use  according  to  Flame  Spread  characteristics  may  be  utilized  in  awnings  and  canopies,  provided  such  awnings  and  canopies  are  constructed  in  accordance  with  provisions  governing  projections  and  appendages  as  specified  in  this  Code.     (b)  Approved  plastics  may  be  used  in  awnings  where  untreated  canvass  is  permitted.     (c)  Approved  plastics  may  be  used  in  lieu  of  plain  glass  in  green-­‐houses  in  less  restrictive  Fire  Zones.       CHAPTER  17  SHEET  METAL  PAINT  SPRAY  BOOTHS    SECTION  1701.  Sheet  Metal  Paint  Spray  Booths     (a)  General     Paint  spray  booths  shall  be  constructed  of  steel  of  not  less  than  No.  18  U.S.  gauge  in  thickness  and  shall  be  designed  in  accordance  with  this  Code.     (b)  Area     The  area  of  a  paint  spray  booth  shall  not  exceed  150  square  m  nor  ten  percent  of  the  basic  area  permitted  for  the  major  use  of  the  building  according  to  its  Occupancy  Group.     (c)  Floor  Construction  The  floor  shall  be  constructed  of  incombustible  material.     (d)  Interior  Surface     Paint  spray  booths  shall  be  designed  to  permit  the  free  passage  of  exhaust  air  from  all  parts  of  the  interior  and  all  interior  surfaces  shall  be  smooth  and  continuous  without  outstanding  edges.       SECTION  1702.  Fire  Protection     

  

38  

Every  spray  booth  having  an  open  front  elevation  larger  than  1.00  square  m  and  which  is  not  equipped  with  doors,  shall  have  a  fire  curtain  or  metal  deflector  not  less  than  100  mm  deep  installed  at  the  upper  outer  edge  of  the  booth  opening.       SECTION  1703.  Light     Paint  spray  booths  shall  be  illuminated  through  hammered  wire  or  heat-­‐treated  glass  panels.  The  glass  panels  shall  be  located  in  such  a  manner  as  to  reduce  the  hazard  of  ignition  caused  by  paint  spray  deposit.       SECTION  1704.  Ventilation     (a)  General     Mechanical  ventilation  shall  be  provided  direct  to  the  exterior  of  the  building.  The  mechanical  exhaust  system  shall  be  designed  to  move  the  air  through  any  portion  of  the  paint  spray  area  at  the  rate  of  not  less  than  30.00  lineal  m  per  minute.  The  blades  of  exhaust  fans  shall  be  constructed  of  non-­‐ferrous  material  and  shall  be  mounted  in  such  a  manner  as  to  prevent  contact  with  the  exhaust  duct.  The  motor  shall  not  be  mounted  in  the  spray  booth  or  the  duct  system  and  belts  shall  be  enclosed  where  they  enter  the  booth  or  duct  system.     (b)  Exhaust  Ducts     Exhaust  ducts  shall  be  constructed  of  steel  having  a  thickness  not  less  than  the  values  set  by  the  Secretary.  The  discharge  point  for  ducts  in  a  paint  spray  booth  shall  be  not  less  than  2.00  m  from  adjoining  combustible  construction  nor  less  than  8.00  m  from  adjoining  exterior  wall  openings:  Except,  that  the  discharge  point  for  exhaust  ducts  is  not  regulated  in  a  waterwash  spray  booth.       CHAPTER  18  GLASS  AND  GLAZING    SECTION  1801.  General  Requirements     (a)  This  Chapter  shall  apply  to  exterior  glass  and  glazing  in  all  Occupancies  except  Groups  A,  B,  and  J  Occupancies  not  over  three  storeys  in  height,  and  to  interior  and  exterior  glass  and  glazing  in  all  occupancies  subject  to  human  impact  as  specified  in  this  Code.     (b)  Standards  for  materials  shall  conform  to  the  provisions  set  by  the  Secretary  on  glass  dimensional  tolerances,  breaking  stress  levels,  and  design  safety  factors.     (c)  Each  light  shall  bear  the  manufacturer’s  label  designating  the  type  and  thickness  of  glass.  Each  light  with  special  performance  characteristics  such  as  laminated,  heat  strengthened,  fully  tempered  or  insulated,  shall  bear  the  manufacturer’s  identification  showing  the  special  characteristics  and  thickness  by  etching  or  other  permanent  identification  that  shall  be  visible  after  the  glass  is  glazed.       SECTION  1802.  Area  Limitation     Exterior  glass  and  glazing  shall  be  capable  of  safely  withstanding  the  load  due  to  wind  pressures  for  various  height  zones  above  ground  acting  inward  or  outward.  The  area  of  individual  lights  shall  not  be  more  than  the  maximum  allowable  area  of  glass  according  to  the  wind  load  multiplied  by  the  appropriate  adjustment  factor.       SECTION  1803.  Glazing     Glass  firmly  supported  on  all  four  edges  shall  be  glazed  with  minimum  laps  and  edge  clearances  in  accordance  with  Section  1801  paragraph  (b),  Provided,  that  glass  edge  clearance  in  fixed  openings  shall  be  not  less  than  what  is  required  for  wind  and  earthquake  drift.  For  glass  not  firmly  supported  on  all  four  edges  and  design  shall  be  submitted  for  approval  of  the  Building  Official.  Glass  supports  shall  be  considered  firm  when  deflection  of  the  support  at  design  load  does  not  exceed  1/175  of  the  span.       SECTION  1804.  Louvered  Windows     Regular  plate,  sheet,  or  patterned  glass  in  jalousies  and  louvered  windows  shall  not  be  thinner  than  5.6  mm  minimal  and  not  longer  than  1.20  m.  Exposed  glass  edges  shall  be  smooth.     
  

  

39  

SECTION  1805.  Impact     Frameless  glass  doors,  glass  in  doors,  fixed  glass  panels,  and  similar  glazed  openings  which  may  be  subject  to  accidental  human  impact  shall  conform  with  the  requirements  set  forth  by  the  Secretary  on  impact  loads  of  glass:  Except  in  the  following  cases:     (1)  Bathtub  and  shower  enclosures  shall  be  constructed  from  approved  shatter-­‐resistant  materials,  such  as:  wire-­‐reinforced  glass  not  less  than  5.6  mm  thick;  fully  tempered  glass  not  less  than  4.8  mm  thick;  or  laminated  safety  glass  not  less  than  6.4  mm  thick.     (2)  Glass  lights  located  not  less  than  450  mm  above  the  adjacent  finished  floor  or  walking  surface.     (3)  Glass  lights  when  the  least  dimension  is  not  greater  than  450  mm.  (4)  Glass  lights  1.50  square  m  or  less  in  area.       CHAPTER  19  THE  USE  OF  COMPUTERS    SECTION  1901.  General  Rule     The  use  of  computers  for  all  or  any  part  of  the  design  of  buildings  under  this  Code  is  permitted  provided  that  all  programs  to  be  used  are  documented.       SECTION  1902.  Program  Documentation     Documenting  a  program  under  this  Code  consists  of  filing  with  the  Building  Official  a  reference  to  a  publication  or  publications  accessible  to  him  where  the  detailed  description  of  the  program  or  a  brief  statement  of  the  theoretical  background  of  the  program  including  a  description  of  the  algorithms  used  are  found.       SECTION  1903.  Submission  of  Computer-­‐Generated  Computations     A  copy  of  the  output  sheets  for  computer-­‐generated  computations  shall  be  submitted  as  a  part  of  the  design  computations.  The  out  sheets  shall  be  accompanied  by  a  certification  of  a  designer  and/or  consultant  that  the  output  sheets  are  the  results  obtained  through  the  use  of  documented  programs.  
The  certification  should  include  the  identification  of  the  specific  program  used  for  each  portion  of  the  computer-­‐generated  computations  being  submitted.       CHAPTER  20  SIGNS    SECTION  2001.  General  Requirements     (a)  No  sign  or  signboard  shall  be  erected  in  such  a  manner  as  to  confuse  or  obstruct  the  view  or  interpretation  of  any  official  traffic  sign,  signal,  or  device.     (b)  No  sign  or  signboard  shall  be  constructed  as  to  unduly  obstruct  the  natural  view  of  the  landscape,  distract  or  obstruct  the  view  of  the  public  as  to  constitute  a  traffic  hazard,  or  otherwise  defile,  debase  or  offend  aesthetic  and  cultural  values  and  traditions.       SECTION  2002.  Maintenance     All  signs,  together  with  all  of  their  supports,  braces,  guys,  and  anchors,  shall  be  kept  in  repair  and  in  proper  state  of  preservation.  The  display  of  all  signs  shall  be  kept  neatly  painted  and  secured  at  all  times.       SECTION  2003.  Design  and  Construction     Sign  structures  shall  be  designed  and  constructed  to  resist  all  forces  in  accordance  with  the  National  Structural  Code  for  Buildings.  For  signs  on  buildings,  the  dead  lateral  loads  shall  be  transmitted  through  the  structural  frame  of  the  building  to  the  ground  in  such  a  manner  as  not  to  overstress  any  of  the  elements  of  the  building.  The  weight  of  earth  superimposed  over  footings  may  be  used  in  determining  the  dead  load  resisting  moment.  Such  earth  shall  be  carefully  placed  and  thoroughly  compacted.       SECTION  2004.  Supports  and  Anchorages     

  

40  

(a)  General.  The  supports  and  anchorages  of  all  signs  or  sign  structures  shall  be  placed  in  or  upon  private  property  and  shall  be  constructed  conformity  with  the  requirements  of  this  Code.     (b)  Materials.  Materials  for  construction  of  signs  or  sign  structures  shall  be  of  the  quality  and  grade  as  specified  in  this  Code.     (c)  Restrictions  on  Combustible  Materials  –  All  signs  or  sign  structures  erected  in  highly  restrictive  Fire  Zones  shall  have  structural  members  of  incombustible  materials.  Ground  signs  may  be  constructed  of  any  material  meeting  the  requirements  of  this  Code.  Combination  signs,  roof  signs,  wall  signs,  projecting  signs,  and  signs  on  marquees  shall  be  constructed  of  incombustible  materials.  No  combustible  material  other  than  approved  plastics  shall  be  used  in  the  construction  of  electric  signs.  
(d)  Non-­‐structural  Trim  –  Non-­‐structural  trim  and  portable  display  surfaces  may  be  of  wood,  metal,  approved  plastics,  or  any  combination  thereof.     (e)  Display  Surfaces  –  Display  surfaces  in  all  types  of  signs  may  be  made  of  metal,  glass,  or  approved  plastics.       SECTION  2005.  Projections  and  Clearances     (a)  Clearances  from  High  Voltage  Power  Lines  –  Clearances  of  signs  from  high  voltage  power  lines  shall  be  in  accordance  with  the  Philippine  Electrical  Code.     (b)  Clearances  from  Fire  Escapes,  Exits,  or  Standpipes  –  No  signs  or  sign  structures  shall  be  erected  in  such  a  manner  than  any  portion  of  its  surface  or  supports  will  interfere  in  any  way  with  the  free  use  of  any  fire  escape,  exit,  or  standpipe.     (c)  Obstruction  of  Openings.  No  sign  shall  obstruct  any  opening  to  such  an  extent  that  light  or  ventilation  is  reduced  to  a  point  below  that  required  by  this  Code.  Signs  erected  within  1.50  m  of  an  exterior  wall  in  which  there  are  openings  within  the  area  of  the  sign  shall  be  constructed  of  incombustible  material  or  approved  plastics.     (d)  Projection  over  Alleys.  No  sign  or  sign  structure  shall  project  into  any  public  alley  below  a  height  of  3.00  m  above  established  sidewalk  grade,  nor  project  more  than  300  mm  where  the  sign  structure  is  located  3.00  m  to  4.5  m  above  established  sidewalk  grade.  The  sign  or  sign  structure  must  not  project  more  than  1.00  m  into  the  public  alley  where  the  sign  or  sign  structure  is  located  more  than  4.50  m  above  established  sidewalk  grade.       SECTION  2006.  Lighting     Signs  shall  be  illuminated  only  by  electrical  means  in  accordance  with  the  Philippine  Electrical  Code.       CHAPTER  21  TRANSITORY  AND  FINAL  PROVISIONS    SECTION  2101.  Existing  Building  and  Structures     All  buildings  or  structures  constructed  under  R.A.  6541  or  existing  city  or  municipal  building  codes  or  ordinances,  if  legally  done  in  accordance  therewith,  shall  be  respected  subject  to  such  limitations  established  in  this  Code.     However,  alterations,  additions,  conversions  and/or  repairs  to  be  made  in  such  buildings  or  structures  shall  be  subject  to  the  provisions  of  this  Code.       SECTION  2102.  Interim  Rules  and  Regulations     Interim  rules  and  regulations  on  buildings  promulgated  by  the  Secretary  before  the  adoption  of  this  Code  pursuant  to  existing  laws  or  decrees  shall  continue  to  have  binding  force  and  effect,  when  not  in  conflict  with  the  provisions  of  this  Code.       SECTION  2103.  Separability  Clause     If  any  provision  of  this  Decree  or  the  application  thereof  is  to  any  person  or  circumstance  declared  unconstitutional  or  invalid  for  any  reason,  the  same  shall  not  affect  the  validity  of  the  other  provisions.       SECTION  2104.  Repealing  Clause     

  

41  

All  laws,  decrees,  provisions  of  charters,  executive  orders,  ordinances,  rules  and  regulations  or  parts  thereof  contrary  to  or  inconsistent  with  the  provisions  of  this  Decree  are  hereby  repealed,  amended,  or  modified  accordingly.       SECTION  2105.  Effectivity     This  Decree  shall  take  effect  upon  its  promulgation.  
Done  in  the  city  of  Manilla,  this  19th  day  of  February,  in  the  year  of  our  Lord,  nineteen  hundred  and  seventy  seven.  
  (SGD.)     FERDINAND  E.  MARCOS     President  Republic  of  the  Philippines       By  the  President:       (SGD.)     SGD.  JUAN  C.  TUVERA     Presidential  Assistant       CERTIFIED  COPY:     (SGD.)     MELQUIADES  T.  DELA  CRUZ,  CESO  II     Presidential  Staff  Director  Malacañang  Records  Section     
  

  

42