THE  PHILIPPINE  GREEN  BUILDING  CODE  
  

  
  

June  2015  A  Referral  Code  of  the  NATIONAL  BUILDING  CODE  OF  THE  PHILIPPINES  (P.D.  1096)  Message  My  warmest  greetings  to  the  Department  of  Public  Works  and  Highways  on  the  implementation  of  the  Philippine  Green  Building  Code  of  2016.     Today  is  an  historic  moment  as  the  government,  through  the  DPWH,  implements  the  Green  Building  Code,  or  the  “GB  Code.”  This  manual  will  be  one  of  our  enduring  legacies  to  succeeding  generations  and  the  fulfillment  of  our  duty  to  secure  their  rights,  welfare,  and  protection.  I  am  filled  with  pride  that  the  country  is  now  part  of  the  global  movement  towards  ecological  conscientiousness  and  sustainability.     I  am  confident  that  the  ideas  contained  in  this  document  will  help  ensure  that  all  structures  built  from  here  on  will  have  minimal  impact  on  our  environment,  complying  with  various  standards  of  quality  and  efficiency,  and  fulfilling  criteria  that  allow  occupants  to  lead  meaningful  lives.     Indeed,  a  new  era  has  dawned  over  our  nation.  Informed  by  the  lessons  of  the  past,  and  mindful  of  the  needs  of  the  future,  building  better  is  not  just  an  option  but  an  indispensable  part  of  our  efforts  towards  achieving  real,  lasting  progress.  Through  the  observance  of  the  principles  and  guidelines  laid  down  in  the  GB  Code,  we  will  create  a  Philippines  that  we  can  be  proud  to  bequeath  to  the  next  generation.     President  of  the  Philippines           Foreword  In  recent  years,  countries  in  the  Asia-­‐Pacific  region  started  to  adopt  measures  that  promote  resource  management  efficiency  and  site  sustainability  while  minimizing  the  effects  of  buildings  on  human  health  and  environment  by  practicing  Green  Building.     The  time  has  come  for  the  Philippines  to  champion  the  implementation  of  greener  measures  to  address  climate  change.  With  the  Department  of  Public  Works  and  Highways’  partnership  with  International  Finance  Corporation  of  the  World  Bank  group,  the  clamor  for  sustainable  building  regulations  has  been  answered.     The  Philippine  Green  Building  Code,  a  referral  code  to  the  National  Building  Code  of  the  Philippines,  rallies  to  lessen  the  impacts  of  buildings  to  health  and  environment  through  resource  management  efficiency.     A  gamut  of  minimum  standards  aimed  to  reduce  greenhouse  emissions  and  introduce  electricity  and  cost  savings  for  buildings  is  imposed  to  applicable  building  falling  under  certain  gross  floor  area  to  deliver  improved  energy  efficiency,  water  and  wastewater  management,  materials  sustainability,  solid  waste  management,  site  sustainability  and  indoor  environmental  quality.     With  the  implementation  of  this  Code  and  the  promise  of  reducing  greenhouse  gas  emissions  and  energy  and  water  consumption  by  at  least  20%,  DPWH  will  herald  the  achievement  of  the  Philippine  Government’s  commitment  to  reduce  carbon  emissions  by  70%  in  2030.     We  took  the  first  steps  in  engineering  this  Code  with  the  help  of  professional  associations  and  stakeholders  to  answer  the  call  for  a  sustainable  building  regulation.  We  now  call  upon  our  stakeholders,  end-­‐users,  customers  and  other  relevant  parties  to  lend  your  hands  to  us  as,  together,  we  achieve  an  environmentally  sound  Philippines.     Secretary     
  
  

1

TABLE  OF  CONTENTS    Chapter  I.  GENERAL  PROVISIONS  
  
  
  
  
  
  
  
  
  

Section  1.  Title  Section  2.  Policy  Section  3.  Objectives  Section  4.  Principles  Section  5.  Definition  of  Terms  Section  6.  Green  Building  Concept  Section  7.  Approach  Section  8.  Building  Use  /  Occupancy  Coverage  and  Application  Chapter  II.  GREEN  BUILDING  REQUIREMENTS  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  
  

Section  9.  Performance  Standards  Section  10.  Energy  Efficiency    10.1  Building  Envelope      10.1.1  Air  Tightness  and  Moisture  Protection      10.1.2  Glass  Properties      10.1.3  Natural  Ventilation      10.1.4  Building  Envelope  Color      10.1.5  Roof  Insulation    10.2  Mechanical  Systems      10.2.1  Air  Conditioning  System      10.2.2  Water  Heating  System      10.2.3  Variable  Speed  Drives  and  High  Efficiency  Motors      10.2.4  Enthalpy  Recovery  of  Exhaust  Air    10.3  Electrical  Systems      10.3.1  Daylight  Provision      10.3.2  Daylight  Controlled  Lighting  System      10.3.3  Lighting  Power  Density      10.3.4  Occupancy  Sensors  for  Lighting  Control      10.3.5  Elevators  and  Escalators  /  Moving  Ramps  /  Walkways      10.3.6  Transformer      10.3.7  Overhead  or  Elevated  Water  Storage  Section  11.  Water  Efficiency    11.1  Water  Fixtures    11.2  Water  Management      11.2.1  Rainwater  Harvesting      11.2.2  Water  Recycling  Section  12.  Material  Sustainability    12.1  Non-­‐Toxic  Materials  Section  13.  Solid  Waste  Management    13.1  Material  Recovery  Facility  Section  14.  Site  Sustainability    14.1  Site  /  Ground  Preparation  and  Earthworks    14.2  Open  Space  Utilization  Section  15.  Indoor  Environmental  Quality    15.1  Minimum  Fresh  Air  Rates    15.2  Designated  Smoking  Area  Chapter  III.  INSTITUTIONAL  ARRANGEMENTS      Section  16.  Office  of  the  National  Building  Official  Section  17.  Technical  Staff  

2

  
  

Section  18.  Professional  and  Technical  Assistance  Chapter  IV.  CERTIFICATION  PROCESS      Section  19.  Green  Building  Permit  Process  Chapter  V.  FINAL  PROVISIONS    Section  21.  Separability  Clause    Section  22.  Effectivity    Section  23.  Transitory  Provision    Annex  1  Definition  Of  Terms  Annex  2  Glass  Library  Annex  3  Insulating  Values  Of  Common  Building  Materials    Table  1.  Minimum  TGFA  for  Building  Use  /  Occupancy  Table  2.  SHGC  and  VLT  for  different  WWR  Table  3.  Correction  factor  for  each  horizontal  overhang  shading  projection     Table  4.  Correction  factor  for  each  vertical  fin  shading  projection  Table  5.  Solar  Reflectance  Index  Values  Of  Basic  Colored  Coatings  Table  6.  R-­‐Value  of  Common  Roof  Insulation  Table  7.  Electrically  Operated  Unitary  Air  Conditioners  and  Condensing  Units  Table  8.  Water  Chiller  Packages  –  Minimum  Efficiency  Requirements  Table  9.  Minimum  Performance  Requirements  for  Water  Heating  Equipment  Table  10.  Motor  Efficiencies  Table  11.  Maximum  Allowed  LPD  Table  12.  Maximum  Allowed  LPD  Table  13  Water  Fixture  Performance  Requirements  Table  14.  VOC  Limits  Table  15.  MRF  Minimum  Daily  Storage  Space  Requirements  Table  16.  Minimum  Ventilation  Rates  in  Breathing  Zone    Figure  1.  Schematic  representation  of  a  window  and  related  horizontal  overhang  or  vertical  fin  
  
  

3

PHILIPPINE  GREEN  BUILDING  CODE    A  Referral  Code  of  the  NATIONAL  BUILDING  CODE  (P.D.  1096)  CHAPTER  I.  GENERAL  PROVISIONS       Section  1.  Title     This  document  shall  be  known  as  the  “Philippine  Green  Building  Code”  hereinafter  referred  to  as  the  “GB  Code”.       Section  2.  Policy     The  state  shall  protect  and  advance  the  right  of  the  people  to  a  balanced  and  healthful  ecology  in  accord  with  the  rhythm  and  harmony  of  nature  against  harmful  effects  of  climate  change.  It  shall  safeguard  the  environment,  property,  public  health,  in  the  interest  of  the  common  good  and  general  welfare  consistent  with  the  principles  of  sound  environmental  management  and  control;  and  for  this  purpose,  prescribe  acceptable  set  of  standards  and  requirements  for  relevant  buildings  to  regulate  their  location,  site,  planning,  design,  quality  of  material,  construction,  use,  occupancy,  operation  and  maintenance.       Section  3.  Objectives     The  GB  Code  seeks  to  improve  the  efficiency  of  building  performance  through  a  framework  of  acceptable  set  of  standards  that  will  enhance  sound  environmental  and  resource  management  that  will  counter  the  harmful  gases  responsible  for  the  adverse  effects  of  climate  change,  throughout  the  building’s  life-­‐cycle  including  efficient  use  of  resources,  site  selection,  planning,  design,  construction,  use,  occupancy,  operation  and  maintenance,  without  significant  increase  in  cost.  This  GB  Code  is  a  set  of  regulations  setting  minimum  standards  for  compliance  and  not  intended  to  rate  buildings.       Section  4.  Principles       4.1     The  technical  professionals,  developers,  contractors,  property  managers  and  building  owners  involved  in  the  planning,  design,  construction  and  management  of  buildings  have  the  opportunity  and  responsibility  to  help  government  address  the  adverse  effects  of  climate  change  by  ensuring  that  buildings  are  planned,  designed,  constructed,  operated  and  maintained  to  the  required  efficiency  level.       4.2     Resources  must  be  used  efficiently  to  equitably  meet  the  developmental  and  environmental  needs  of  the  present  and  future  generations.       4.3  Occupants  of  green  buildings  will  benefit  from  improved  indoor  environmental  quality,  which  promotes  higher  productivity  and  better  comfort.       Section  5.  Definition  of  Terms     The  words,  terms  and  phrases  as  used  in  this  GB  Code  shall  have  the  meaning  or  definition  as  indicated  in  the  National  Building  Code  (NBC)  and  Annex  1.  
  Section  6.  Green  Building  Concept     Green  building  is  the  practice  of  adopting  measures  that  promote  resource  management  efficiency  and  site  sustainability  while  minimizing  the  negative  impact  of  buildings  on  human  health  and  the  environment.  This  practice  complements  the  conventional  building  design  concerns  of  economy,  durability,  serviceability  and  comfort.       Section  7.  Approach     The  GB  Code  adopts  a  staggered  or  incremental  approach  and  is  subject  to  periodic  review  by  the  Secretary  of  the  Department  of  Public  Works  and  Highways  (DPWH),  through  the  National  Building  Code  4

Development  Office  (NBCDO),  to  modify  or  include  new  aspects  and  emerging  efficient  technologies  and  expand  the  coverage  to  other  building  use  /  occupancy  or  replace  outmoded  measures.       Section  8.  Building  Use  /  Occupancy  Coverage  and  Application       8.1  The  provisions  of  the  GB  Code  shall  apply  to  all  new  construction  and/or  with  alteration  of  buildings  in  the  following  classification  with  the  required  minimum  Total  Gross  Floor  Areas  (TGFA)  as  indicated  in  Table  1  below:       Table  1.  Minimum  TGFA  for  Building  Use  /  Occupancy     USE  /  OCCUPANCY  CLASSIFICATION  of  any  jurisdiction  Residential  Dwelling:  Condominium  Hotel  /  Resort     Educational:  School     Institutional:  Hospital     Business:  Office     Mercantile:  Mall     Mixed  Occupancy  2  TGFA  as  defined  by  NBC  20,000  sqm  10,000  sqm     10,000  sqm     10,000  sqm     10,000  sqm     15,000  sqm     10,000  sqm  Sources:  NBC,  Baseline  Studies,  IFC  Philippine  Green  Building  Code  Project,  May  2013     1  For  Residential  Dwelling:  Condominium,  the  TGFA  is  the  sum  of  the  dwelling  areas,  common  and  accessory  areas  within  the  building.     2  The  areas  for  Mixed  Occupancy  classification  shall  have  a  total  aggregate  area  equal  to  the  TGFA    8.2  GB  Code  does  not  apply  to  existing  buildings  of  the  above  use  /  occupancy  classification  constructed  before  the  effectivity  of  the  GB  Code.       8.3     When  alterations,  additions,  conversions  and  renovations  of  existing  buildings  constructed  after  the  effectivity  of  the  GB  code,  which  reached  the  TGFA  as  indicated  in  Table  1  are  to  be  made,  the  whole  building  shall  be  subject  to  the  applicable  provisions  of  the  GB  Code.       8.4     A  building  of  mixed  occupancy  with  combination  of  classification  as  indicated  in  Table  1,  shall  use  appropriate  measures  applicable  to  each  classification.       CHAPTER  II.  GREEN  BUILDING  REQUIREMENTS       Section  9.  Performance  Standards     The  GB  Code  shall  be  subject  to  the  following  performance  standards:     9.1     Energy  Efficiency     9.2     Water  Efficiency     9.3     Material  Sustainability     9.4     Solid  Waste  Management     9.5     Site  Sustainability     9.6     Indoor  Environmental  Quality       Section  10.  Energy  Efficiency     Energy  efficiency  requires  the  adoption  of  efficient  practices,  designs,  methods  and  technologies  that  reduce  energy  consumption  resulting  in  cost  savings.       10.1  BUILDING  ENVELOPE    10.1.1  Air  Tightness  and  Moisture  Protection     a.  General  As  the  humidity  levels  are  very  high  in  the  Philippines,  the  unwanted  infiltration  and  humidity  ingress  into  the  spaces  can  cause  additional  load  on  the  air  conditioning  system  and  a  detrimental  5impact  on  air  quality.  Buildings  must  be  planned  and  designed  with  specific  details  to  ensure  that  air  tightness  is  maximized.  Details  should  precisely  include  joints,  service  entry  points,  windows  and  doors.  The  implementation  of  these  measures  requires  only  increased  attention  to  the  construction  details  and  it  can  be  implemented  at  practically  no  cost.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  Buildings  shall  be  planned  and  designed  with:     i.  Complete  gaskets,  weather-­‐stripping,  door  bottom  sweeps  and  seals  within  and  around  window  and  door  assemblies     ii.  Moisture  protection  on  the  surface  of  the  external  façade  to  reduce  vapor  or  moisture  migration  from  external  spaces     d.  Exceptions  Buildings  and  spaces  without  provisions  for  air  conditioning  systems  are  exempt.       10.1.2  Glass  Properties     a.  General  Compared  to  wall  assemblies,  glazing  transfers  more  heat  and  hence,  it  is  ideal  to  reduce  the  amount  of  glazing  with  respect  to  the  wall  in  order  to  reduce  internal  heat  gains.     The  requirement  of  Window  to  Wall  Ratio  (WWR)  needs  to  be  balanced  with  the  amount  of  daylight  coming  through  the  glazed  area.     Solar  Heat  Gain  Coefficient  (SHGC)  is  used  to  determine  the  amount  of  solar  heat  admitted  through  the  glass  divided  by  the  total  solar  radiation  incident  on  the  glass.     Visible  light  Transmittance  (VLT)  is  used  to  determine  the  amount  of  light  transmitted  through  the  glass.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     WWR  shall  be  balanced  with  SHGC  to  maintain  flexibility  in  design.  To  further  describe,  the  higher  the  designed  building  WWR,  the  lower  the  required  SHGC  in  glass  windows  shall  be  and  vise-­‐versa.  
This  does  not  however,  remove  the  option  for  building  owners  to  apply  windows  with  low  SHGC  for  building  with  low  WWR.     i.  The  size  of  the  opening  (with  or  without  glass)  shall  be  in  accordance  with  the  NBC.     For  each  WWR  value,  the  SHGC  and  VLT  shall  be  in  accordance  with  Table  2.       Table  2.  SHGC  and  VLT  for  different  WWR     WWR  10     20     30     40     50     60     70     80     90     

  Maximum  SHGC     0.80     0.70     0.60     0.45     0.44     0.37     0.31     0.27     0.24     Minimum  VLT     0.80     0.70     0.70     0.60     0.55     0.50     0.45     0.40     0.35     Source:  Prescribed  Requirements,  IFC  Philippine  Green  Building  Code  Project,  May  2013  The  SHGC  requirement  in  Table  2  can  be  adjusted  if  sun  breakers  are  provided  in  the  windows.  
Sun  breaker  plays  a  very  important  role  in  reducing  solar  heat  gain  as  it  stops  the  solar  radiation  before  it  enters  the  building  and  doing  so  reduces  the  cooling  loads  considerably.  External  shading  has  the  additional  positive  effect  of  improving  the  internal  comfort  cutting  part  of  the  direct  radiation  on  occupants.  This  must  be  applied  only  to  windows  that  are  shaded.     

6

  

  
  
  
  
  
  
  
  
  

SHGC  limits  can  be  adjusted  by  multiplying  it  with  the  correction  factors  summarized  in  the  following  tables,  using  the  formula:     SHGCadj  =  f  x  SHGC     where:     SHGCadj  is  the  adjusted  solar  heat  gain  coefficient  limit  for  windows  with  external  shading     SHGC  f  is  the  solar  heat  gain  coefficient  f  is  the  SHGC  correction  factor  for  the  external  shading     ii.  For  intermediate  values  of  D/H  or  D/W  the  lower  figure  of  correction  factor  should  be  used  as  stated  in  Tables  3  and  4.  
iii.  D  is  the  depth  of  the  shading  device  as  projected  from  the  building  exterior  wall  and  H  or  W  is  the  height  or  distance  of  the  bottom  sill  of  the  window  from  the  bottom  of  the  shading  device  as  shown  in  Figure  1.     iv.  Shading  which  is  not  attached  to  windows  or  placed  on  a  wall  with  no  window  should  not  be  counted.     Figure  1.  Schematic  representation  of  a  window  and  related  horizontal  overhang  or  vertical  fin  Table  3.  Correction  factor  for  each  horizontal  overhang  shading  projection     
D/H  
0.1  
0.5  
1  

  

Table  4.  Correction  factor  for  each  vertical  fin  shading  projection     
D/W  
0.1  
0.5  
1  

  

Correction  Factor  1.03  
1.06  
1.08  

Correction  Factor  1.04  
1.12  
1.17  

Source:  Prescribed  Requirements,  IFC  Philippine  Green  Building  Code  Project,  May  2013     For  glass  products,  see  Annex  2  Glass  Library.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       10.2  NATURAL  VENTILATION     a.  General  This  measure  will  give  building  occupants  the  flexibility  and  opportunity  to  use  natural  ventilation  for  free  cooling  and  fresh  air  in  regularly  occupied  spaces.  This  measure  will  limit  the  tendency  to  create  glass-­‐  sealed  box  type  buildings.  Size  of  each  room  and  space  shall  be  consistent  with  the  occupancy  load  of  the  NBC.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.   Operable  windows  or  balcony  door  shall  be  provided  in  regularly  occupied  spaces.  The  size  of  the  opening  shall  be  equal  to  at  least  ten  percent  (10%)  of  the  floor  area  of  regularly  occupied  spaces.     

7ii.   All  operable  windows  shall  be  provided  with  safety  features  for  protection  against  strong  winds,  water  penetration  and  protection  for  building  occupants  including  child  safety  and  security.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       10.3  BUILDING  ENVELOPE  COLOR     a.  General  Light-­‐colored  building  envelope,  especially  the  roof  areas  which  are  the  most  vulnerable,  can  reduce  heat  transfer  from  the  outside  to  the  inside  of  the  building  by  having  surfaces  with  high  Solar  Reflectance  Index  (SRI).     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     Building  metal  roof  surfaces  shall  either  be  colored  white  or  have  a  minimum  SRI  of  70.  See  Table  5.       Table  5.  Solar  Reflectance  Index  Values  Of  Basic  Colored  Coatings     METAL  SURFACE  Reflective  white  Basic  white  Beige  /  Tan  Dark  brown  Light  to  medium  brown  Light  to  medium  grey  Dark  grey  Blue  
Light  to  medium  blue  Red  Terracotta  red  Green  Light  to  medium  green  

  

SRI  
86  to  92  80  to  88  74  to  80  0  to  33  45  to  56  39  to  63  0  to  41  23  to  30  35  to  38  28  to  36  38  to  40  25  to  32  30  to  48  d.  Exceptions.  
      There  are  no  exceptions  to  this  provision.       10.4  ROOF  INSULATION  a.  General  Insulation  can  help  reduce  heat  gain  in  a  building  thus  improving  thermal  comfort,  acoustic  quality  and  reducing  the  load  on  the  air  conditioning  system.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  Buildings  shall  be  provided  with  roof  insulation  so  that  the  average  thermal  resistance  value  (R-­‐
Value)  of  the  roof  is  at  least  R-­‐8.  See  Annex  4  (Insulation  R-­‐Value).     For  Insulating  Values  of  Common  Building  Materials  see  Annex  3       Table  6.  R-­‐Value  of  Common  Roof  Insulation     Insulation  Polyisocyanurate     Polyurethane     Closed  cell  spray  foam     Phenolic  foam     Urea  formaldehyde  foam     Plastic  fiber     Mineral  fiber     

R-­‐Value  /  inch  (25.4  mm)     5.6  to  8.0     5.6  to  6.5     5.5  to  6.0     4.8     4.6     4.3     4.2  to  4.5     

8Cementitious  foam     Polystyrene     Fiberglass     Rockwool     Rigid  foam     Cellulose     Open  cell  spray  foam     Sheep’s  wool     Hemp     Cotton     Loose  cellulose     Mineral  wool     Straw     Vermiculite  /  Perlite     Reflective  bubble  foil       3.9     3.8  to  5.0     3.7     3.7     3.6  to  6.7     3.6  to  3.8     3.6     3.5     3.5     3.4     3.0  to  3.7     2.8  to  3.7     2.4  to  3.0     2.4     1to1.1     Source:  US  Department  of  Energy  –  insulation  materials  d.  Exceptions.     There  are  no  exceptions  to  this  provision.       10.5  MECHANICAL  SYSTEMS       10.5.1  Air  Conditioning  System     a.  General  Air  conditioning  typically  accounts  for  more  than  fifty  percent  (50%)  of  total  electricity  costs  in  a  centrally  air-­‐conditioned  building.  Hence,  the  efficiency  of  an  air  conditioning  system  is  of  prime  importance.  The  heart  of  the  air  conditioning  system  is  the  cooling  system,  typically  chillers  in  large  buildings  and  is  important  to  procure  an  efficient  cooling  system.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  The  cooling  equipment  shall  meet  or  exceed  the  minimum  efficiency  requirements  as  indicated  in  Tables  7  and  8.       Table  7.  Electrically  Operated  Unitary  Air  Conditioners  and  Condensing  Units     Equipment  Type  
Air  conditioners,  air-­‐cooled  Size  Category  (in  Btu/h)  <65,000  Through-­‐the-­‐  wall,  air-­‐cooled  Small-­‐duct  high  velocity,  air-­‐cooled  Air  conditioners,  air-­‐cooled  <30,000       <31,655  Split  systems  Single  packaged  <65,000     <68,585  Split  systems  ≥65,  000  &     <135,000     ≥135,  000  &  <240,000  ≥240,  000  &  <760,000  ≥760,  000  ≥68,  585  &  <142,447  ≥142,  447  <253,238  ≥253,  238  &  <801,922  ≥801,  922  Split  systems  and  single  packaged  (in  kJ/h)     <68,585  Sub-­‐Category  or  Rating  Conditions  Split  systems  Single  packaged  9Minimum  Efficiency  14.0  SEER  12.0  EER  14.0  SEER  11.6  EER  12.0  SEER     12.0  SEER  Test  Procedure  AHRI  210/240;  PNS  ISO  5151:2014;  PNS  ISO  
16358-­‐1  AHRI  210/240;  PNS  ISO  5151:2014;  PNS  ISO  
16358-­‐1     10.0  SEER      AHRI  210/240;  PNS  ISO  5151:2014;  PNS  ISO  
16358-­‐1  11.5  EER  AHRI  340/360;  PNS  ISO  5151:2014;  PNS  ISO  11.3  EER  16358-­‐1  11.5  EER  11.3  EER  10.0  EER  9.8  EER  9.7  EER  Air  
conditioners,  water  and  evaporative  cooled    <65,000  <68,585  ≥65,  000  &  135,000  ≥135,  000  &  240,000  ≥  240,000     ≥68,  585  &  142,447  ≥142,447  &  253,238  ≥  253,238  Split  systems  and  single  packaged  9.5  EER  14.0  EER  14.0  EER  13.8  EER  AHRI  210/240;  PNS  ISO  5151:2014;  PNS  ISO  
16358-­‐1  AHRI  340/360;  PNS  ISO  5151:2014;  PNS  ISO  
16358-­‐1  

13.8  EER  14.0  EER  13.8  EER  Source:  2010  PSVARE  Standards     Table  8.  Water  Chiller  Packages  –  Minimum  Efficiency  Requirements     Equipment  Type  Air-­‐cooled  chillers  with,   <  150  tons     condenser,  electrically  ≥150  tons     operated     Air-­‐cooled  chillers  without  condenser,  All  capacities     electrically  operated     Water-­‐cooled,  electrically  operated,  positive     EER  Minimum  Efficiency  Full  Load  10     

EER  10     

Size  category  All  capacities     <  75  tons     Water-­‐cooled,  ≥  75  tons  and  <  150  tons     Electrically  operated,  positive  displacement      ≥  150  tons  and  <  300  tons     ≥  300  tons     <  150  tons     Water-­‐cooled  ≥  150  tons  and  <  300  tons     electrically  operated,  ≥  300  tons  and  <  600  tons     centrifugal     ≥  600  tons     Air-­‐cooled  absorption  All  capacities     single  effect     Water-­‐cooled  All  capacities     absorption  single  effect     Absorption  double  All  capacities     effect  indirect-­‐fired    All  capacities     Test  Procedures  AHRI  550/590     Kw/ton  Kw/ton  Kw/ton  Kw/ton  Kw/ton  Kw/ton  Kw/ton  Kw/ton  Condenserless  units  shall  be  rated  with  matched  AHRI  550/590     condensers     Reciprocating  units  required  to  comply  with  water-­‐cooled  AHRI  550/590     positive  displacement  requirements     0.78     0.775     AHRI  550/590     0.68     0.62     0.634     0.634     AHRI  550/590     0.576     0.57     COP  0.6     COP  0.6     

COP  

1  

COP  

1  

EER  

Kw/ton  Source:  2010  PSVARE  Standards     d.  Exceptions  Buildings  with  no  air-­‐conditioning  systems  are  exempt.     AHRI  560       10.5.2  Water  Heating  System     a.  General  The  use  of  energy-­‐efficient  water  heating  systems  in  buildings,  by  observing  minimum  power  performance  requirements,  will  help  reduce  energy  consumption  due  to  heating  of  water.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements.     Applicable  buildings  shall  comply  with  the  minimum  performance  requirements  for  water  heating  in  the  2010  PSVARE  Standards,  as  shown  in  Table  9.     d.  Exceptions  

10

  

Buildings  with  no  water  heating  systems  and  buildings  with  using  solar  water  heating  and/or  heat  pump  for  water  heating  are  exempt.     Table  9.  Minimum  Performance  Requirements  for  Water  Heating  Equipment     Equipment  Type  

Size  Category  (Input)  I-­‐P  

Electric  Water  12  kW  Heaters  >  12  kW  All  sizes     ≤  75,000  Gas  Storage   Btu/h     Water  >  75,000  Heaters  Btu/h     SI  12  kW  >  12  kW  All  sizes     ≤  22  kW     >  22  kW     Subcategory  or  Rating  Condition  I-­‐P  >  75,000  Btu/h     Resistance  ≥   >  75,000  20  gal  Btu/h     Resistance  ≥   >  75,000  20  gal  Btu/h     >  75,000  Heat  Pump     Btu/h     >  75,000  ≥  20  gal     Btu/h     Performance  Required     
I-­‐P  SI  Test  Procedure     

EF≥0.97-­‐  EF≥0.97-­‐   DOE  10  CFR  0.00132V  0.00132V   Part  430  SL≤20+  35√V,     ANSI  Z21.10.3  Btu/h  DOE  10  CFR  EF≥2.0     EF≥2.0     Part  430     DOE  10  CFR  EF  ≥  0.67     EF  ≥  0.67     Part  430     E  ≥  80%  and  <  4,000  <  0.31  kw/L     SL  ≤  (Q/800  +     ANSI  Z21.10.3  (Btu/h)/gal     
110√V),  Btu/h     >  50,000  ≥  4,000  Btu/h  and  <   >  15  kW  and  ≥  0.31  kw/L  DOE  10  CFR  (Btu/h)/gal  EF  ≥  0.82     EF  ≥  0.82     200,000  <  58kW     and  7.57  L     Part  430     and  <  2  gal     Btu/h    Gas  Instantaneous  ≥  4,000  ≤  200,000  ≥  0.31  kw/L  Water  
≤  58  kW      (Btu/h)/gal  E  ≥  80%     E  ≥  80%     Btu/h     and  37.85  L     Heaters     and  <  10  gal     ANSI  Z21.10.3     4000  
E  ≥  80%  and  ≥  200,000  0.31  kw/L  ≥  58  kW      (Btu/h)/gal  SL  ≤  (Q/800  +     Btu/h     and≥  37.85  L     and  ≥  10  gal     
110√V),  Btu/h     ≤  105,000  EF≥0.59-­‐  EF≥0.59-­‐   DOE  10  CFR  ≤  31  kW      ≥  20  gal     ≥  76  L     Btu/h    0.0019V    0.0019V      Part  430     Oil  Storage  Water  E  ≥  78%  and  >  105,000  <  4,000  Heaters     >31  kW     <  0.31  kw/L     SL  ≤  (Q/800  +     Btu/h     (Btu/h)/gal     
110√V),  Btu/h     DOE  10  CFR  Part  430     ≥  4,000  ≤  210,000  ≥  0.31  kw/L   EF≥0.59-­‐  EF≥0.59-­‐  ≤  62  kW      (Btu/h)/gal  Btu/h     and  <7.87  L     0.0019V     0.0019V     and  <  2  gal     Oil  ≥  4,000  Instantaneous  >  210,000  ≥  0.31  kw/L  >  62  kW      (Btu/h)/gal  E  ≥  80%     E  ≥  80%     Water  Btu/h     and  <37.85  L     and  <  10  gal     Heaters     ANSI  Z21.10.3     ≥  4,000  E  ≥  78%  and  >  210,000  ≥  0.31  kw/L  >  62  kW      (Btu/h)/gal  SL  ≤  (Q/800  +     Btu/h     and  ≥37.85  L     and  ≥10  gal     
110√V),  Btu/h     Hot-­‐water  300,000  ≥  4,000  supply  Btu/h  and  <   88  kW  and  <  ≥  0.31  kw/L  (Btu/h)/gal  E  ≥  80%     E  ≥  80%     boilers,  gas   12,500,000   3664  kW     and  <37.85  L     and  <  10  gal     and  oil     Btu/h     Hot-­‐water  ≥  4,000  E  ≥  80%  and  ≥  0.31  kw/L  ANSI  Z21.10.3         supply  (Btu/h)/gal  SL  ≤  (Q/800  +     and  ≥37.85  L     boilers,  gas     and  ≥10  gal     
110√V),  Btu/h     Hot-­‐water  ≥  4,000  E  ≥  78%  and  ≥  0.31  kw/L      supply  (Btu/h)/gal  SL  ≤  (Q/800  +     and  ≥37.85  L     boilers,  oil     and  ≥10  gal     
110√V),  Btu/h     Pool  heaters  All  sizes  oil  and  gas  All  sizes  

  

  

11

E  ≥  78%  E  ≥  78%  ASHRAE  146  Heat  pump  All  sizes  pool  heaters  Unfired  All  sizes  storage  tanks  All  sizes      ≥  4.0  COP  ≥  4.0  COP   ASHRAE  146  All  sizes      ≥  R-­‐12.5  ≥  R-­‐12.5  None  

Source:  2010  PSVARE  Standards       10.5.3.  Variable  Speed  Drives  and  High  Efficiency  Motors     a.  General  Variable  Speed  Drive  (VSD)  describes  the  equipment  used  to  control  the  speed  of  machinery  by  changing  the  frequency  of  the  motor  that  is  being  operated.  Where  process  conditions  demand  adjustment  of  flow  from  a  pump  or  fan,  varying  the  speed  of  the  drive  may  save  energy  compared  with  other  techniques  for  flow  control.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.   All  motors  for  mechanical  equipment  over  five  (5)  kW  shall  be  provided  with  variable  speed  drive  and  high  efficiency  motors  in  accordance  with  Table  10.     ii.   All  motors  of  cooling  towers  shall  be  provided  with  variable  speed  drive  and  high  efficiency  motors.     iii.   All  motors  for  domestic  pumps  shall  have  high  efficiency  motors  as  indicated  in  Table  10.     d.  Exceptions  Kitchen  ventilation  fans  are  exempt  from  this  requirement.  Non-­‐  centralized  air-­‐conditioning  systems  in  buildings  are  not  required  to  employ  variable  speed  controllers.       Table  10.  Motor  Efficiencies     Number  of  Poles  
  
  
  
  
  
  
  
  
  
  
  
Source:  2010  PSVARE  Standards       10.5.4.  Enthalpy  Recovery  of  Exhaust  Air     a.  General  When  buildings  have  outside  air  or  fresh  air  supply  and  extract  system  through  mechanical  means,  using  heat  exchangers  can  use  the  air  extracted  from  the  building  areas  to  pre-­‐condition  the  incoming  outdoor  air.  This  process  exploits  the  fact  that  the  extract  air  is  usually  already  conditioned  and  therefore  colder  and  drier.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements.  
All  buildings  with  centralized  air  supply  system  shall  use  enthalpy  recovery  wheels  with  efficiency  of  at  least  sixty  percent  (60%)  of  ninety  percent  (90%)  exhaust  air.     d.  Exceptions.  
Buildings  without  centralized  cooling  systems  are  exempt.       10.6  ELECTRICAL  SYSTEMS  10.6.1  Daylight  Provision       10.6.1  Daylight  Provision  a.  General  Building  should  be  planned  and  designed  to  maximize  the  use  of  natural  light  so  to  reduce  the  use  of  artificial  illumination.     b.  Applicability.  
This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.  For  residential  condominiums,  it  does  not  apply  to  individual  dwelling  units.     c.  Requirements.  

12All  regularly  occupied  spaces  inside  the  building  shall  have  a  view  of  any  combination  of  the  following  features  that  can  allow  daylight  into  the  room  space:     i.   Window     ii.   Light  shelf     iii.   Clerestory     iv.   Skylight     v.   Light  monitor  /  light  scoop     vi.   Other  devices  that  can  allow  daylight  inside     d.  Exceptions  Spaces  where  daylight  access  hinders  its  intended  function  are  exempt  from  this  provision  with  justification  for  exemption.       10.6.2  Daylight  Controlled  Lighting  System     a.  General  Building  interior  perimeter  zones  exposed  to  daylight  generally  do  not  require  artificial  lighting  during  the  day.  However,  sub-­‐optimal  design  and  operation  of  the  building  results  in  use  of  artificial  lighting  when  not  required.     Photoelectric  sensors  connected  to  luminaires  help  in  dimming  or  switching  off  lamps  that  do  not  require  to  be  operated  due  to  presence  of  adequate  daylight.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  stated  in  Table  1.  For  residential  condominiums,  this  applies  only  to  common  indoor  areas  with  access  to  daylight.     c.  Requirements  Applicable  buildings  shall  comply  with  the  following:     i.   Lighting  fixtures  within  the  daylight  zone  shall  be  controlled  with  photoelectric  sensors  with  an  auto  on-­‐off  basis  or  continual  dimming.  The  photoelectric  sensor  shall  be  located  approximately  at  half  (1⁄2)  the  depth  of  daylight  zone.     ii.   If  occupancy  sensors  are  installed  in  the  daylight  zone,  the  occupancy  sensor  shall  override  the  photoelectric  sensor  during  non-­‐occupancy  period.     d.  Exceptions  Installed  lighting  fixtures  within  the  day-­‐lit  zones  are  exempt  from  using  photoelectric  sensor  if  this  hinders  its  intended  function,  with  justification  for  exemption.       10.6.3  Lighting  Power  Density  (LPD)     a.  General     Limitation  of  LPD  will  help  to  design  the  lighting  system  in  the  most  efficient  way  and  reduce  the  lighting  and  cooling  in  the  building.  The  maximum  allowed  LPD  for  each  space  type  is  specified  in  Table  11.  
b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  All  applicable  building  types  shall  comply  with  the  LPD  limits  in  the  2010  PSVARE  Standards,  as  shown  in  Table  11.       Table  11  Maximum  Allowed  LPD  *4  Source  2010  PSVARE  Standards     *4  Above  requirement  excludes  parking  and  exterior  lighting  (see  Table  12)       Table  12.  Maximum  Allowed  LPD     Source  :  ASHRAE  -­‐  IESNA  90.1       d.  Exceptions     There  are  no  exceptions  to  this  provision.  
  13

10.6.4  Occupancy  Sensors  for  Lighting  Control     a.  General  Occupancy  sensors  linked  to  lighting  shall  be  installed  in  areas  with  variable  occupancy.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1,  except  for  hospitals  and  malls.     c.  Requirements  Applicable  buildings  shall  comply  with  the  following:     i.  In  order  to  limit  the  use  of  electricity  in  unoccupied  areas  of  buildings,  occupancy  sensors  linked  to  lighting  (except  for  emergency  and  security  lighting)  shall  be  installed  in  the  following  areas  with  variable  occupancy:     -­‐     corridors     -­‐     private  offices     -­‐     storage  rooms     -­‐     common  toilets     -­‐     meeting  rooms     -­‐     stairways     -­‐     other  similar  areas     ii.  For  covered  car  parks:  minimum  of  sixty  per  cent  (60%)  of  the  lighting  must  be  controlled  by  the  occupancy  sensors.     d.  Exceptions  Provisions  for  emergency  and  security  lighting  are  exempted  from  this  requirement.       10.6.5  Elevators  and  Escalators  /  Moving  Ramps  /  Walkways     a.  General  Escalators  /  Moving  Ramp  /  Walkway  must  be  fitted  with  controls  to  automatically  reduce  speed  or  stop  when  no  traffic  is  detected.  Elevators  must  be  fitted  with  mechanisms  to  reduce  energy  demand.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     Applicable  buildings  shall  comply  with  the  following:     i.  Escalators  /  Moving  Ramps  /  Walkways     •  Escalators  /  Moving  Ramps  /  Walkways  shall  be  fitted  with  automated  controls  to  reduce  to  a  slower  speed  when  no  activity  has  been  detected  for  a  maximum  period  of  one  and  a  half  (1-­‐1/2)  minutes  and  duration  may  be  adjusted  depending  on  the  demand.     •  The  escalator  /  moving  ramp  /  walkway  shall  automatically  be  put  on  a  standby  mode  when  no  activity  has  been  detected  for  a  maximum  period  of  five  (5)  minutes  and  duration  may  be  adjusted  depending  on  the  demand.     •  These  escalators  /  moving  ramps  /  walkways  shall  be  designed  with  energy  efficient  soft  start  technology.  Activation  of  reduced  speed,  power  off  and  power  on  modes  shall  be  done  through  sensors  installed  in  the  top  or  bottom  landing  areas.     ii.  Elevators     •  Elevators  shall  be  provided  with  controls  to  reduce  the  energy  demand.  To  meet  this  requirement,  the  following  features  must  be  incorporated:     -­‐     Use  of  Alternating  Current  (AC)  Variable  Voltage  and  Variable  Frequency  (VVVF)  drives  on  non-­‐hydraulic  elevators     -­‐     Use  of  energy  efficient  lighting  and  display  lighting  in  the  elevator  car  shall  have  an  average  lamp  efficacy,  across  all  fittings  in  the  car,  of  more  than  55  lumens  /  watt     -­‐     Lighting  shall  switch  off  after  the  elevator  has  been  inactive  for  a  maximum  period  of  five  (5)  minutes     -­‐     The  elevators  shall  operate  in  a  stand-­‐by  condition  during  off-­‐peak  periods     d.  Exceptions           There  are  no  exceptions  to  this  provision.     

14  10.6.6  Transformer     a.  General  The  transformer  shall  be  tested  in  accordance  with  relevant  Philippine  National  Standards  (PNS)  at  test  conditions  of  full  load,  free  of  harmonics  and  at  unity  power  factor.     b.  Applicability  This  measure  applies  to  all  building  occupancies,  with  own  transformer,  as  indicated  in  Table  1.     c.  Requirements  Transformers  that  are  part  of  the  building  electrical  system  shall  have  efficiencies  not  lower  than  98%  as  prescribed  in  the  DOE  Guidelines  on  Energy  Conserving  Design  of  Buildings.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       10.6.7  Overhead  or  Elevated  Water  Storage     a.  General  To  reduce  dependence  on  motorized  systems  to  supply  and  distribute  potable  or  non-­‐potable  water  within  the  building,  thus  help  reduce  energy  consumption,  overhead  or  elevated  water  storage  systems  are  used,  provided  there’s  a  twenty  percent  (20%)  fire  reserve  over  and  above  the  average  daily  demand  supply.  The  system  relies  mostly  on  elevation  and  gravity  to  distribute  water  within  the  building.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  Applicable  buildings  shall  include  in  the  water  distribution  system  the  integration  of  overhead  or  elevated  water  tanks  that  will  facilitate  the  distribution  of  potable  and  /  or  non-­‐potable  water  into  the  building  spaces,  without  compromising  the  required  water  volume  and  pressure  based  on  demand  and  the  Plumbing  Code  of  the  Philippines.     d.  Exceptions  Buildings  below  ten  (10)  storeys  high  are  exempt  from  this  provision.       Section  11.  WATER  EFFICIENCY     Water  efficiency  requires  the  adoption  of  efficient  practices,  plan,  design,  materials,  fixtures,  equipment     and  methods  that  reduce  water  consumption  resulting  in  cost  savings.       11.1  WATER  FIXTURES     a.  General  Efficient  water  fixtures  include  faucets,  showerheads  and  water  closets  that  use  less  water  in  order  to  perform  the  same  function  of  cleaning  as  effectively  as  standard  models.  Water  efficiency  is  an  important  aspect,  especially  as  fresh  water  resources  start  getting  depleted  at  a  rate  faster  than  they  are  replenished.  Use  of  efficient  plumbing  fixtures,  sensors,  auto  control  valves,  aerators,  flow  control  and  pressure-­‐reducing  devices,  wherever  possible,  can  result  in  significant  reduction  in  water  consumption.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  Applicable  buildings  shall  comply  with  the  requirements  as  shown  in  Table  13.     d.  Exceptions.  
There  are  no  exceptions  to  this  provision.       Table  13  Water  Fixture  Performance  Requirements     Source:  Prescribed  Requirements,  IFC  Philippine  Green  Building  Code  Project,  May  2013       11.2  WATER  MANAGEMENT  11.2.1  Rainwater  Harvesting       

1511.2.1  Rainwater  Harvesting  a.  General  Rainwater  is  one  of  the  purest  sources  of  water  available.  Rainwater  from  roofs  and  hardscape  must  be  collected  and  reused  for  non-­‐  potable  purposes.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.  Minimum  storage  tanks  size  (in  cu.m)  shall  be  calculated  by  dividing  the  building  footprint  area  by  75.     ii.  Collected  water  shall  be  used  for  non-­‐potable  purposes  such  as  toilet  flushing,  irrigation  and  cooling  towers.     d.  Exceptions.  
There  are  no  exceptions  to  this  provision.       11.2.2  Water  Recycling     a.  General  Recycled  water  from  Sewage  Treatment  Plants  (STP)  shall  be  reused  for  non-­‐potable  purposes.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  The  recycled  water  produced  on  site  shall  be  reused  for  non-­‐potable  purposes  such  as  toilet  flushing,  irrigation  and  cooling  towers,  through  a  distinct  and  separate  piping  system  from  the  potable  water  supply  system.     d.  Exceptions  Buildings  with  no  dedicated  STP  are  exempted  from  this  requirement.       Section  12.  MATERIAL  SUSTAINABILITY     Material  Sustainability  governs  all  matters  related  to  resource  efficiency  and  material  selection  and  use  with  the  least  impact  on  the  environment.       12.1  Non-­‐Toxic  Materials     a.  General  Non-­‐Toxic  building  materials  refer  to  building  materials  without  hazardous     or  toxic  chemicals  that  could  cause  Sick  Building  Syndrome  (SBS)  and  eventually  lead  to  Building  Related  Illness  (BRI).     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.   Paints,  coatings,  adhesives  and  sealants  used  indoors  or  non-­‐  ventilated  areas  shall  not  contain  Volatile  Organic  Compounds  (VOC)  or  should  be  within  levels  tolerable  to  humans  as  specified  in  Table  14.     ii.   Composite  wood  shall  not  have  urea  formaldehyde  content.     iii.   All  other  materials  containing  chemicals  used  in  construction  shall  not  compromise  and  be  deleterious  to  the  health  and  safety  of  the  workers  and  occupants  of  the  building.     iv.   Specifications  shall  comply  with  the  allowable  VOC  limits  as  stated  in  Table  14  with  Material  Safety  Data  Sheet  (MSDS)  from  supplier  and  other  certification  to  justify  the  compliance  of  the  material.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       Table  14.  VOC  Limits     VOC  levels  are  measured  in  grams  of  VOC  per  liter  of  material  Source:  USGBC  LEED  Addenda  #  100000419,  14  April  2010       16Section  13.  SOLID  WASTE  MANAGEMENT     Efficient  waste  management  requires  the  adoption  of  efficient  waste  management  practices  and  use  of  eco-­‐friendly  materials.       13.1  Material  Recovery  Facility  (MRF)     a.  General  MRF  shall  be  provided  for  the  collection  and  segregation  of  solid  waste  materials     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.   Buildings  shall  be  provided  with  a  minimum  area  for  MRF  as  specified  in  Table  15.     ii.   MRF  shall  be  fully  enclosed  and  easily  accessible  from  within  the  building  and  from  the  outside  for  easy  collection  of  waste.     iii.   Solid  waste  containers  shall  be  provided  for  at  least  four  (4)  types  of  wastes:     -­‐     compostable  (biodegradable)     -­‐     non-­‐recyclable  (to  be  disposed  off  in  the  landfill)     -­‐     recyclable  (paper,  cardboard,  plastic,  metal,  wood,  etc.)     -­‐     special  waste     iv.   For  hospitals,  isolated  bins  for  hazardous  wastes  shall  be  provided  to  avoid  contamination.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       Table  15.  MRF  Minimum  Daily  Storage  Space  Requirements     Source:  DENR  (EMB  Report  on  Solid  Waste  Generation)  and  NBC       Section  14.  SITE  SUSTAINABILITY     Site  sustainability  requires  the  adoption  of  planning,  design,  construction  and  operation  practices  that  minimize  the  adverse  impact  of  buildings  on  ecosystems  and  water  resources.       14.1  Site  /  Ground  Preparation  and  Earthworks     a.  General  Site  clearing,  grading  and  excavation  shall  be  planned  at  the  start  of  construction  to  mitigate  pollution  caused  by  erosion  and  sedimentation  taking  into  consideration  existing  endemic  foliage  as  regulated  by  the  DENR.     All  existing  utilities  and  water  bodies  and  waterways,  shall  be  protected  and  shall  not  be  disturbed.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  Measures  for  site  protection  shall  be  in  place  before  the  start  of  construction.     i.   Building  site  erosion  and  sedimentation  control  plan  that  outlines  measures  to  be  applied  to  prevent  soil  that  can  run-­‐off  at  the  natural  bodies  of  water,  causing  water  pollution.     ii.   Additional  measures  to  mitigate  the  effect  of  pollution  and  safety  on  construction  conforming  to  Rule  XI  of  the  NBC     iii.   Storm  water  collection  management  plan     iv.   Structures  or  facilities  for  storm  water  collection     d.  Exceptions  There  are  no  exceptions  to  this  provision.       14.2  Open  Space  Utilization     a.  General  The  inclusion  of  green  areas  or  landscaped  areas  for  indigenous  or  adaptable  species  of  grass,  shrubs  and  trees  will  help  in  providing  more  permeable  surface  for  the  building  development’s  open  space  and  thus  allow  the  re-­‐charging  of  natural  ground  water  reservoir,  control  storm  water  surface  run-­‐17

off,  cool  the  building  surroundings,  and  provide  indoor  to  outdoor  connectivity  for  the  building  occupants.     b.  Applicability  This  measure  applies  to  all  building  occupancies  as  indicated  in  Table  1.     c.  Requirements  A  minimum  of  fifty  percent  (50%)  of  the  required  Unpaved  Surface  Area  (USA),  as  required  in  Rule  VII  and  VIII  of  the  NBC,  shall  be  vegetated  with  indigenous  and  adaptable  species.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       Section  15.  INDOOR  ENVIRONMENTAL  QUALITY     Indoor  Environmental  Quality  requires  the  adoption  of  efficient  design  and  operation  practices  that  take  into  consideration  the  building  environment  to  improve  occupant  health,  productivity  and  safety.       15.1  Minimum  Fresh  Air  Rates     a.  General  The  building  indoor  environment  can  contain  more  contaminants  many  times  over  than  the  outside.  
Various  studies  have  shown  that  indoor  air  contaminants  can  cause  health  disorders,  through  symptoms  of  SBS  and  BRI.  The  introduction  and  application  of  minimum  fresh  air  rates  will  maintain  acceptable  indoor  air  quality  thru  the  constant  replacement  of  indoor  air  in  buildings.     b.  Applicability  This  measure  applies  to  all  buildings  occupancies  as  indicated  in  Table  1.     c.  Requirements  Compliance  to  the  minimum  fresh  air  rates  provided  in  the  latest  Philippine  Society  of  Ventilating,  Air-­‐Conditioning  and  Refrigerating  Engineers  (PSVARE)  Standards.  See  Table  16.     d.  Exceptions  There  are  no  exceptions  to  this  provision.       Table  16      Minimum  Ventilation  Rates  in  Breathing  Zone     Source:  2010  PSVARE  Standards       15.2  Designated  Smoking  Area     a.  General  Environmental  Tobacco  Smoke  (ETS)  is  one  of  the  leading  causes  of  respiratory  illnesses  in  building  occupants.  RA  9211,  the  Tobacco  Regulations  Act,  restricts  tobacco  smoking  in  public  spaces  and  the  prescription  of  designated  smoking  areas  inside  buildings.     b.  Applicability  This  measure  applies  to  all  buildings  occupancies  as  indicated  in  Table  1.     c.  Requirements     i.  If  smoking  is  banned  within  the  building  and  property  premises,  “NO  SMOKING”  signs  in  compliance  with  the  RA  9514  (Fire  Code  of  the  Philippines  2008),  shall  be  posted  in  conspicuous  areas  of  the  building  and  property  premises  to  remind  building  occupants  of  the  policy.     ii.If  smoking  is  only  allowed  outdoors,  designated  smoking  areas  shall  be  naturally  ventilated,  outside  of  the  building  shell  and  away  from  building  entrances,  windows  and  outside  supply  air  (OSA)  intakes  by  at  least  ten  (10)  meters.     iii.If  smoking  is  allowed  indoors,  designated  smoking  areas  shall  be  provided,  partitioned  from  the  rest  of  the  indoor  areas.  Partitions  shall  be  from  floor  to  soffit  of  the  next  floor  or  roof  structure.  
Enclosed  smoking  areas  shall  be  equipped  with  adequate  exhaust  system  with  exhaust  rate  in  accordance  with  the  latest  PSVARE  Standards.  Exhaust  shall  directly  vent  out  to  the  outside  of  the  building  and  away  from  any  building  openings  or  air  intakes.     iv.Doors  and  windows  of  enclosed  smoking  area  shall  always  be  closed  and  well  sealed.  Negative  pressure  within  is  recommended  to  prevent  smoke  infiltration  to  adjacent  spaces.     d.  Exceptions  18

Buildings  with  a  general  policy  of  “no  smoking”  within  building  premises  may  be  exempted  from  having  designated  smoking  areas.       CHAPTER  III.  INSTITUTIONAL  ARRANGEMENTS       Section  16.  OFFICE  OF  THE  NATIONAL  BUILDING  OFFICIAL     The  Secretary  of  the  Department  of  Public  Works  and  Highways  (DPWH),  as  the  concurrent  National  Building  Official,  pursuant  to  Section  203  of  the  NBC,  through  the  NBCDO,  shall  regularly  review  the  GB  Code  not  to  exceed  three  (3)  years  from  the  date  of  effectivity  and  every  three  (3)  years  thereafter.     For  this  purpose,  the  NBCDO  shall  convene  the  Technical  Working  Group  (TWG)  to  review  and  update  the  GB  Code  implementation  vis-­‐à-­‐vis  current  and  emerging  trends  in  the  industry  and  make  recommendations  for  reform.     The  NBCDO  shall  serve  as  the  center  for  the  development  and  promotion  of  green  buildings  in  the  Philippines.  As  such,  it  shall  be  the  repository  of  resource  materials  relating  to  green  buildings.  It  shall  also  be  responsible  for  developing  modules  and  providing  green  building  training.       Section  17.  TECHNICAL  STAFF     The  Secretary  is  hereby  authorized  to  constitute  and  provide  in  his  department  a  professional  staff  composed  of  highly  qualified  architects,  engineers  and  technicians  who  possess  diversified  and  professional  experience  in  the  field  of  green  building  planning,  design  and  construction.  
  Section  18.  PROFESSIONAL  AND  TECHNICAL  ASSISTANCE     The  Executive  Director  of  NBCDO  shall  chair  the  Technical  Working  Group  (TWG)  and  may  make  arrangements  with  the  Secretary  for  compensation  of  the  services  of  the  TWG.  He  may  also  engage  and  compensate  within  appropriations  available  thereof,  the  services  of  such  number  of  consultants,  experts  and  advisers  on  full  or  part-­‐time  basis  as  may  be  necessary  coming  from  any  concerned  government  agency  or  private  business,  Accredited  Professional  Organizations  (APO)  and  other  associations  to  carry  out  the  provisions  of  the  GB  Code.  The  members  are  the  duly  authorized  representatives  from  the  following:     18.1     CCC  (Climate  Change  Commission)     18.2     DENR  (Department  of  Environment  and  Natural  Resources)     18.3     DILG  (Department  of  Interior  and  Local  Government)     18.4     DOE  (Department  of  Energy)     18.5     DOST  (Department  of  Science  and  Technology)     18.6     DTI  (Department  of  Trade  and  Industry)     18.7     GEP  (Geodetic  Engineers  of  the  Philippines)     18.8     IECEP  (Institute  of  Electronics  Engineers  of  the  Philippines)     18.9     IIEE  (Institute  of  Integrated  Electrical  Engineers)     18.10     PALA  (Philippine  Association  of  Landscape  Architects)     18.11     PICE  (Philippine  Institute  of  Civil  Engineers)     18.12     PIEP  (Philippine  Institute  of  Environmental  Planners)     18.13     PIID  (Philippine  Institute  of  Interior  Designers)     18.14     PSME  (Philippine  Society  of  Mechanical  Engineers)     18.15     PSSE  (Philippine  Society  of  Sanitary  Engineers)     18.16     UAP  (United  Architects  of  the  Philippines)     18.17     BOMAP  (Building  Owners  and  Managers  Association  of  the  Philippines)     18.18     PABA  (Philippine  Association  of  Building  Administrators)     18.19     PABO  (Philippine  Association  of  the  Building  Officials)       CHAPTER  IV.  CERTIFICATION  PROCESS       Section  19.  GREEN  BUILDING  PERMIT  PROCESS     

19

  

The  Office  of  the  Building  Official  shall  review  the  building  permit  application  for  Green  Buildings  as  prepared  by  the  design  professionals  in  compliance  with  the  requirements  of  the  GB  Code  and  the  various  referral  codes  in  accordance  with  Rule  3  of  the  NBC.     CHAPTER  V.  FINAL  PROVISIONS       Section  20.  SEPARABILITY  CLAUSE     Should  any  part  or  provision  of  the  GB  Code  be  held  unconstitutional  or  invalid  by  a  competent  court,  the  other  parts  or  provisions  hereof  which  are  not  affected  thereby  shall  continue  to  be  in  full  force  and  effect.       Section  21.  EFFECTIVITY     This  GB  Code  shall  take  effect  fifteen  (15)  days  after  its  publication  once  a  week  for  three  (3)  consecutive  weeks  in  a  newspaper  of  general  circulation.       Section  22.  TRANSITORY  PROVISION     Those  projects  with  building  designs  and  plans  that  have  already  been  prepared  and  signed  by  all  duly  licensed  design  professionals  shall  be  exempt  from  the  coverage,  provided  that  the  request  for  exemption  shall  be  filed  with  the  Office  of  the  Building  Official  within  30  days  after  the  effectivity  of  this  Code.     
  ANNEX  1  DEFINITION  OF  TERMS    Accredited  Professional  Organizations  (APO)  -­‐  professional  organizations  accredited  by  the  Professional  Regulatory  Commission  (PRC)     Addition  -­‐  any  new  construction  which  increases  the  height  and  /  or  floor  area  of  existing  buildings  /  structures     Air  Conditioning  -­‐  the  process  of  treating  air  so  as  to  control  simultaneously  its  temperature,  humidity,  cleanliness,  and  distribution  to  meet  the  requirements  of  conditioned  space     Air-­‐Conditioning,  Heating,  and  Refrigeration  Institute  (AHRI)  -­‐  trade  association  representing  manufacturers  of  HVACR  and  water  heating  equipment  within  the  global  industry7     Alteration  -­‐  works  in  buildings  /  structures  involving  changes  in  the  materials  used,  partitioning,  location  /  size  of  openings,  structural  parts,  existing  utilities  and  equipment  but  does  not  increase  the  building  height  and/or  floor  area     American  Society  of  Heating,  Refrigerating  and  Air-­‐Conditioning  Engineers  (ASHRAE)  -­‐  global  society  founded  in  1894,  advancing  human  well-­‐being  through  sustainable  technology  for  the  built  environment  with  focus  on  building  systems,  energy  efficiency,  indoor  air  quality,  refrigeration  and  sustainability  within  the  industry     Applicable  Provision  –  any  requirement  that  relates  to  a  given  condition     Building  Owners  and  Managers  Association  of  the  Philippines  (BOMAP)  -­‐  helps  members  ensure  tenants’  satisfaction,  maximize  profits,  and  enhance  asset  values  for  building  owners  and  investors  through  market  intelligence,  education,  networking,  and  government  advocacy     British  thermal  unit  (Btu)  -­‐  amount  of  heat  energy  needed  to  raise  the  temperature  of  one  pound  of  water  by  one  degree  Fahrenheit     Building  Official  (BO)  -­‐  the  Executive  Officer  of  the  Office  of  the  Building  Official  (OBO)  appointed  by  the  Secretary     Building  Permit  -­‐  document  issued  by  the  Building  Official  (BO)  to  an  owner  /  applicant  to  proceed  with  the  construction,  installation,  addition,  alteration,  renovation,  conversion,  repair,  moving,  demolition  or  other  work  activity  of  a  specific  project/building/structure  or  portions  thereof  after  the  accompanying  principal  plans,  specifications  and  other  pertinent  documents  with  the  duly  notarized  application  are  found  satisfactory  and  substantially  conforming  with  the  NBC  and  its  Implementing  Rules  and  Regulations  (IRR).     Building  Related  Illness  (BRI)  -­‐  diagnosable  illness  whose  cause  and  symptoms  can  be  directly  attributed  to  a  specific  pollutant  source  within  a  building     

20Car,  elevator  –  the  load-­‐carrying  unit  including  its  platform,  enclosure  and  door  or  gate  Clerestory  -­‐  high  windows  above  eye  level     Climate  Change  -­‐  refers  to  any  significant  change  in  measures  of  climate,  such  as  temperature,  precipitation,  or  wind,  lasting  for  an  extended  period     Climate  Change  Commission  (CCC)  -­‐  the  lead  policy-­‐making  body  of  the  government  tasked  to  coordinate,  monitor  and  evaluate  programs  and  action  plans  on  climate  change     Coefficient  of  Performance  (COP)  -­‐  ratio  of  heating  or  cooling  provided  to  electrical  energy  consumed  where  higher  COPs  equate  to  lower  operating  costs     Common  Area  -­‐  part  of  the  building  premises  is  used  by  the  occupants,  owners,  tenants  or  other  building  users  of  which  the  landlord  retains  control  and  is  responsible  to  maintain  in  a  reasonably  safe  condition  that  includes  spaces  such  as  lobby,  corridor,  hallway,  toilet,  elevator  or  stairway     Compostable  waste  -­‐  mixture  of  various  organic  substances  that  can  be  placed  into  a  composition  of  decaying  biodegradable  materials  which  eventually  turns  into  a  nutrient-­‐  rich  material,  used  for  fertilizing  soil     Construction  -­‐  all  on-­‐site  work  done  in  the  site  preparation,  excavation,  foundation,  assembly  of  all  the  components  and  installation  of  utilities,  machineries  and  equipment  of  buildings  /  structures     Conversion  -­‐  change  in  the  use  or  occupancy  of  buildings  /  structures  or  any  portion/s  thereof,  which  has  different  requirements     Daylight  -­‐  the  natural  light  of  day,  which  is  a  combination  of  all  direct  and  indirect  sunlight  during  the  daytime     Daylight  Zone  -­‐  area  substantially  illuminated  by  daylight  consistently  receiving  significant  quantities  of  daylight  during  the  day  (ASHRAE/IES  90.1-­‐2010  energy  standard)     Demolition  -­‐  systematic  dismantling  or  destruction  of  a  building/structure,  in  whole  or  in  part     Department  -­‐  the  Department  of  Public  Works  and  Highways     Department  of  Energy  (DOE)  -­‐  the  executive  department  of  the  Philippine  Government  responsible  for  preparing,  integrating,  coordinating,  supervising  and  controlling  all  plans,  programs,  projects  and  activities  of  the  Government  relative  to  energy  exploration,  development,  utilization,  distribution  and  conservation     Department  of  Environment  and  Natural  Resources  (DENR)  -­‐  the  executive  department  of  the  Philippine  Government  responsible  for  supervising  and  managing  the  different  programs  and  implementing  rules  governing  the  use  and  development  of  the  country's  natural  resources     Department  of  Interior  and  Local  Government  (DILG)  -­‐  the  executive  department  of  the  Philippine  Government  responsible  for  promoting  peace  and  order,  ensuring  public  safety  and  strengthening  local  government  capability  aimed  towards  the  effective  delivery  of  basic  services  to  the  citizenry     Department  of  Public  Works  and  Highways  (DPWH)  -­‐  executive  department  of  the  Philippine  Government  that  functions  as  the  engineering  and  construction  arm  of  the  Government  tasked  to  continuously  develop  its  technology  for  the  purpose  of  ensuring  the  safety  of  all  infrastructure  facilities  and  securing  for  all  public  works  and  highways  the  highest  efficiency  and  quality  in  construction     Department  of  Science  and  Technology  (DOST)  -­‐  the  executive  department  of  the  Philippine  Government  responsible  for  the  coordination  of  science  and  technology-­‐  related  projects  in  the  Philippines  and  to  formulate  policies  and  projects  in  the  fields  of  science  and  technology  in  support  of  national  development     Department  of  Trade  and  Industry  (DTI)  -­‐  the  executive  department  of  the  Philippine  Government  tasked  to  expand  Philippine  trade,  industries  and  investments  as  the  means  to  generate  jobs  and  raise  incomes  for  Filipinos     Door  assembly  -­‐  unit  composed  of  a  group  of  parts  or  components  which  make  up  a  closure  for  an  opening  to  control  passageway  through  a  wall  which  consists  of  the  following  parts:  door;  hinges;  locking  device  or  devices;  operation  contacts  (such  as  handles,  knobs,  push  plates);  miscellaneous  hardware  and  closures;  the  frame,  including  the  head,  threshold  and  jambs  plus  the  anchorage  devices     Elevator  -­‐  a  hoisting  and  lowering  mechanism  other  than  a  dumbwaiter  or  freight  elevator  which  is  designed  to  carry  passanger  or  authorized  personnel,  in  a  protected  enclosure  (elevator  car)  which  moves  along  fixed  guides  in  a  vertical  direction  serving  two  or  more  fixed  landings/  floors  on  a  hoistway.     

21Energy  Efficiency  Ratio  (EER)  -­‐  energy  efficiency  rating  for  room  air  conditioners  that  lists  how  many  Btu  per  hour  are  used  for  each  watt  of  power  it  draws     Enthalpy  Recovery  Wheel  –  an  energy  recovery  device  that  transfers  outgoing  temperature  and  humidity  to  the  incoming  outdoor  air     Environmental  Tobacco  Smoke  (ETS)  -­‐  secondhand  smoke  consisting  of  airborne  particles  emitted  from  the  burning  end  of  cigarettes,  pipes,  and  cigars,  exhaled  by  smokers  containing  about  4,000  compounds,  up  to  50  of  which  are  known  to  cause  cancer     Environmental  Management  Bureau  (EMB)  -­‐  national  authority  in  the  Philippines  that  sets  air  and  water  quality  standards  and  monitors  ambient  and  point  source  pollutants     Escalator  –  a  power  driven,  inclined,  continuous  stairway  for  raising  or  lowering  passengers     Executive  Director  -­‐  the  executive  officer  or  head  of  the  NBCDO     Geodetic  Engineers  of  the  Philippines  (GEP)  -­‐  accredited  professional  organization  of  Geodetic  Engineers  composed  of  technically  competent  engineers  with  a  high  degree  of  integrity,  moral  standards  and  professionalism  and  at  pace  with  modern  geodetic  engineering  technologies     Government  Agency  -­‐  refers  to  any  of  the  various  units  of  the  government  including  a  department,  bureau,  office,  instrumentality,  or  government  owned  or  controlled  corporation     Harmonics  -­‐  increased  heating  in  equipment  and  conductors,  the  reduction  of  which  is  desirable     Hazardous  –  anything  that  involves  risk  or  danger  to  the  safety  and  welfare  of  the  public     Heat  Island  Effect  (HIE)  -­‐  describes  built  up  areas  that  are  hotter  than  nearby  rural  areas     Heating,  Ventilating  and  Air  Conditioning  (HVAC)  -­‐  system  that  helps  maintain  good  indoor  air  quality  through  adequate  ventilation  with  filtration  and  provide  thermal  comfort     Illuminating  Engineering  Society  of  North  America  (IESNA)  –  a  non-­‐profit  learned  society  whose  mission  is  to  improve  the  lighted  environment  by  bringing  together  those  with  lighting  knowledge  and  translating  that  knowledge  into  actions  that  would  benefit  the  public     Implementing  Rules  and  Regulations  (IRR)  -­‐  rules  and  regulations  necessary  in  the  implementation  of  the  provisions  of  GB  Code     Indoor  Environmental  Quality  (IEQ)  -­‐  conditions  inside  the  building  that  includes  air  quality,  access  to  daylight  and  views,  pleasant  acoustic  conditions,  and  occupant  control  over  lighting  and  thermal  comfort     Institute  of  Electronics  Engineers  of  the  Philippines  (IECEP)  -­‐  the  integrated  accredited  professional  organization  of  professional  electronics  engineers,  electronics  engineers  and  electronics  technicians,  whose  objective  is  to  promote,  through  scientific  inquiry  and  study  the  advancement  of  electronics  in  theory  and  practice,  and  its  application  to  allied  fields  of  engineering  and  to  human  needs     Institute  of  Integrated  Electrical  Engineers  of  the  Philippines  (IIEE)  -­‐  the  accredited  organization  of  Electrical  Engineers  that  aims  to  instill  excellence  to  Electrical  Engineers  and  to  give  contribution  to  the  development  of  the  Philippines     Joint  -­‐  a  space  between  the  adjacent  surfaces  of  two  bodies  joined  and  held  together  Light  Monitor  -­‐  raised  structure  running  along  the  ridge  of  a  double-­‐pitched  roof,  with     its  own  roof  running  parallel  with  the  main  roof     Light  Scoop  -­‐  south-­‐facing  skylight,  that  uses  tilted  panels  of  transparent  glass  to  strategically  bring  daylight  into  an  interior  space.     Light  Shelf  -­‐  a  horizontal  surface  that  reflects  daylight  deep  into  a  building,  placed  above  eye-­‐level  with  high-­‐reflectance  upper  surfaces,  which  reflect  daylight  onto  the  ceiling  and  deeper  into  the  space     Lighting  Power  Density  (LPD)  -­‐  amount  of  electric  lighting,  usually  measured  in  watts  per  square  foot,  being  used  to  illuminate  a  given  space     Material  Recovery  Facility  (MRF)  -­‐  a  facility  designed  to  receive,  sort,  process,  and  store  compostable  and  recyclable  materials  efficiently  and  in  an  environmentally  sound  manner     Material  Safety  Data  Sheet  (MSDS)  -­‐  data  providing  procedures  for  handling  or  working  with  a  material  or  product  in  a  safe  manner,  which  includes  information  such  as  physical  data,  toxicity,  health  effects,  first  aid,  reactivity,  storage,  disposal,  protective  equipment  and  spill  handling  procedures     Mixed  Occupancy  -­‐  enclosed  structure  with  two  or  more  primary  usages  and  where  at  least  two  of  these  primary  usages  fall  into  different  classification  of  use     Moving  Ramp  /  Walkway  –  a  type  of  horizontal  passenger-­‐carrying  device  on  which  passengers  stand  or  walk,  with  its  surface  remaining  parallel  to  its  direction  of  motion  is  uninterrupted     

22National  Building  Code  (NBC)  –  P.D.  1096  is  a  uniform  building  code  in  the  Philippines  which  embodies  up-­‐to-­‐date  and  modern  technical  knowledge  on  building  design,  construction,  use,  occupancy  and  maintenance     National  Building  Code  Development  Office  (NBCDO)  -­‐  created  through  DPWH  Department  Order,  assist  the  Secretary  in  the  administration  and  enforcement  of  the  provisions  of  the  GB  Code  and  its  IRR     Non-­‐recyclable  Waste  -­‐  not  able  to  be  processed  or  treated  for  reuse  in  some  form     Office  of  the  Building  Official  (OBO)  -­‐  the  office  authorized  to  enforce  the  provisions  of  NBC  and  its  IRR  in  the  field  as  well  as  the  enforcement  of  orders  and  decisions  made  pursuant  thereto     Operable  Window  -­‐  a  window  unit  with  one  or  more  sections  that  can  be  opened  for  ventilation     Overall  Thermal  Transfer  Value  -­‐  (OTTV)  measure  of  the  energy  consumption  of  a  building  envelope     Outside  Supply  Air  (OSA)  -­‐  air  containing  at  least  the  minimum  volume  of  outside  air  filtered  and  conditioned  to  the  required  temperature  and  humidity     Parking,  Covered  -­‐  parking  under  roof  that  does  not  contribute  to  the  heat  island  effect     Parking,  Open  -­‐  parking  structure  with  wall  openings  open  to  the  atmosphere,  distributed  over  40  percent  of  the  building  perimeter  or  uniformly  over  two  opposing  sides  to  provide  ventilation     Philippine  Association  of  Building  Administrators  (PABA)  –  a  non-­‐profit  organization  for  Building  Administrators  and  Property  Managers     Philippine  Association  of  Building  Officials  (PABO)  –  association  of  Building  Officials  in  the  Philippines     Philippine  Association  of  Landscape  Architects  (PALA)  -­‐  the  integrated  and  accredited  organization  of  landscape  architecture  professionals  responsible  for  the  advancement  of  the  profession  as  an  instrument  of  service  in  improving  the  quality  of  life  within  a  better  natural  and  built  environment     Philippine  Institute  of  Civil  Engineers  (PICE)  -­‐  a  professional  organization  for  civil  engineers  in  the  Philippines  formed  by  merging  two  separate  organizations  of  civil  engineers:  one  group  working  from  government  sector  and  the  second  group  working  in  the  private  sector     Philippine  Institute  of  Environmental  Planners  (PIEP)  -­‐  a  national  organization  of  professionally  trained  planners  who  will  make  an  advancement  in  the  studies  of  environmental  planning  in  the  best  interest  of  the  nation     Philippine  Institute  of  Interior  Designers  (PIID)  –  the  accredited  professional  organization  of  Interior  Designers  creating  platforms  for  learning  and  sustainable  creativity,  adhering  to  international  standards  while  preserving  the  Filipino  heritage     Philippine  National  Standards  (PNS)  -­‐  documents  established  by  consensus  through  technical  committees  and  approved  by  the  Department  of  Trade  and  Industry  Bureau  of  Product  Standards  that  ensures  desirable  characteristics  of  products  and  services  such  as  quality,  environmental  friendliness,  safety,  reliability,  efficiency  and  interchangeability     Philippine  Society  of  Mechanical  Engineers  (PSME)  –  the  organization  of  Mechanical  Engineers  in  the  Philippines  uniting  and  enjoining  the  mechanical  engineers  in  the  pursuit  of  further  professional  growth  and  to  uplift  the  profession     Philippine  Society  of  Sanitary  Engineers  (PSSE)  -­‐  the  only  professional  organization  of  Sanitary  Engineers  in  the  Philippines  accredited  by  PRC  and  soon  to  be  renamed  to  Philippine  Society  of  Environmental  and  Sanitary  Engineers,  Inc.  (PSEnSE)     Philippine  Society  of  Ventilating  Air-­‐Conditioning  and  Refrigerating  Engineers  (PSVARE)  -­‐  is  a  duly  registered  non-­‐stock,  non-­‐profit  organization,  the  members  of  which  are  consultants,  contractors,  manufacturers,  suppliers  who  are  all  involved  in  the  practice  of  air  conditioning,  ventilation,  and  refrigeration  systems     Professional  Regulatory  Commission  (PRC)  -­‐  the  instrument  of  the  Filipino  people  in  securing  for  the  nation  a  reliable,  trustworthy  and  progressive  system  of  determining  the  competence  of  professionals  by  credible  and  valid  licensure  examinations  and  standards  of  professional  practice  that  are  globally  recognized     Photoelectric  Sensor  -­‐  a  device  used  to  detect  the  distance,  absence,  or  presence  of  an  object  by  using  a  light  transmitter,  often  infrared  and  a  photoelectric  receiver     
R-­‐Value  -­‐  resistance  value  or  the  capacity  to  resist  heat  loss  or  its  thermal  resistance  Recyclable  Waste  -­‐  an  item  or  material  capable  of  being  used  again     Referral  Codes  –  the  applicable  provisions  of  the  various  agency  and  technical  professional  codes  supplementary  to  the  NBC  and  GB  Code     

23Regularly  Occupied  Space  -­‐  areas  where  one  or  more  individuals  normally  spend  time  (more  than  one  hour  per  person  per  day  on  average)  seated  or  standing  as  they  work,  study,  or  perform  other  focused  activities  inside  a  building     Renovation  -­‐  any  physical  change  made  on  buildings/structures  to  increase  the  value,  quality,  and/or  to  improve  the  aesthetic     Repair  -­‐  remedial  work  done  on  any  damaged  or  deteriorated  portion/s  of  building  /  structure  to  restore  to  its  original  condition     Seasonal  Energy  Efficiency  Ratio  (SEER)  -­‐  energy  efficiency  rating  for  central  air  conditioners     Secretary  -­‐  head  or  chief  executive  officer  of  the  DPWH     Sewage  Treatment  Plant  (STP)  -­‐  an  industrial  structure  designed  to  remove  biological  or  chemical  waste  products  from  water,  thereby  permitting  the  treated  water  to  be  used  for  other  purposes     Sick  Building  Syndrome  (SBS)  -­‐  Building  whose  occupants  experience  acute  health  and/or  comfort  effects  that  appear  to  be  linked  to  time  spent  therein,  but  where  no  specific  illness  or  cause  can  be  identified     Smoking  Area  -­‐  a  designated  area  in  which  smoking  is  permitted  Solar  Heat  Gain  Coefficient  (SHGC)  -­‐  fraction  of  solar  gain  admitted  through  a     window,  expressed  as  a  number  between  0  and  1     Solar  Reflectance  Index  (SRI)  -­‐  a  measure  of  a  material’s  ability  to  reflect  heat  with  white  or  light  colors  having  high  reflectance  and  dark  or  black  surfaces  with  low  or  little  reflectance  thereby  having  higher  temperatures     Special  Waste  -­‐  a  class  of  waste  that  has  unique  regulatory  requirements  with  potential  environmental  impacts  that  needs  to  be  managed  to  minimize  the  risk  of  harm  to  the  environment  and  human  health     Staff  -­‐  personnel  of  the  NBCDO     Storey  –  portion  of  a  building/structure  included  between  the  uppermost  surface  (or  finish  level)  of  any  floor  and  the  uppermost  surface  (or  finish  level)  of  the  next  floor  above  or  below  it.  If  the  uppermost  surface  (or  finish  level)  of  a  floor/level  above  the  uppermost  surface  (or  finish  level)  of  a  basement,  cellar  or  unused  under-­‐floor  space  is  more  than  3.60  meters  above  established  grade  as  defined  herein  at  any  point,  such  basement,  cellar  or  unused  under-­‐floor  space  shall  be  considered  a  storey.     Sun  breaker  -­‐  feature  of  a  building  commonly  used  as  external  shading  devices,  which  reduces  heat  gain  within  that  building  by  deflecting  solar  rays  to  reduce  energy  cooling  loads     Total  Gross  Floor  Area  (TGFA)  -­‐  the  total  floor  space  within  the  main  auxiliary  buildings  primarily  consisting  of  the  GFA  and  all  other  enclosed  support  areas  together  with  all  other  usable  horizontal  areas/surfaces  above  and  below  established  grade  level  that  are  all  physically  attached  to  the  building/s  which  shall  consists  of  the  following:  Covered  areas  used  for  parking  and  driveways,  services  and  utilities.     Toxic  Materials  -­‐  substances  that  may  cause  harm  to  an  individual  if  it  enters  the  body  through  inhalation,  skin  contactor  ingestion     
U-­‐Value  -­‐  describes  how  well  a  building  element  conducts  heat,  measuring  the  rate  of  heat  transfer  through  a  building  element  over  a  given  area,  under  standardized  conditions     United  Architects  of  the  Philippines  (UAP)  -­‐  the  Integrated  and  Accredited  Professional  Organization  of  Architects  in  the  Philippines  responsible  in  the  improvement  and  sustainability  of  the  quality  of  built  environment     Unity  Power  Factor  -­‐  power  factor  of  1.0  obtained  when  current  and  voltage  are  in  phase,  as  in  a  circuit  containing  only  resistance  or  in  a  reactive  circuit  at  resonance.     Unpaved  Surface  Area  (USA)  -­‐  the  portion  of  the  lot  that  shall  remain  unpaved  and  reserved  for  softscaping  /  planting;  expressed  as  a  percentage  (%)  of  the  Total  Lot  Area  or  TLA  and  may  be  combined  with  the  Impervious  Surface  Area  (ISA)  to  satisfy  the  Total  Open  Space  within  Lot  (TOSL),  i.e.,  the  total  open  space  requirement  for  each  type  of  use  or  occupancy     Urea  formaldehyde  -­‐  combination  of  urea  and  formaldehyde  used  in  some  glues  and  adhesives,  particularly  in  composite  wood  products,  emitting  formaldehyde  at  room  temperature,  which  is  a  toxic  and  possibly  carcinogenic  gas     Variable  Speed  Drive  (VSD)  -­‐  a  piece  of  equipment  that  regulates  the  speed  and  rotational  force,  or  torque  output,  of  an  electric  motor.     

24Variable-­‐Voltage  and  Variable-­‐Frequency  (VVVF)  -­‐  employs  frequency  inverter  technology  which  regulates  input  voltage  and  frequency  throughout  the  journey,  drawing  much  less  current  during  acceleration  and  deceleration     Ventilation  –  process  of  supplying  or  removing  air  by  natural  or  mechanical  means  to  or  from  any  space.     Visible  Transmittance  (Tvis)  -­‐  the  ratio  of  total  transmitted  light  to  total  incident  light  with  the  higher  value  allowing  more  incident  light  to  pass  through  the  glazing     Volatile  Organic  Compound  (VOC)  -­‐  organic  chemicals  with  have  a  high  vapor  pressure  at  ordinary  room  temperature  that  are  dangerous  to  human  health  or  cause  harm  to  the  environment     Weather-­‐Stripping  -­‐  narrow  piece  of  material,  such  as  plastic,  rubber,  felt,  or  metal,  installed  around  doors  and  windows  to  protect  an  interior  from  external  extremes  in  temperature.     Window  assembly  -­‐  a  unit,  which  includes  a  window  and  the  anchorage  between  the  window  and  the  wall     Window  to  Wall  Ratio  (WWR)  -­‐  ratio  of  the  total  area  of  a  building  facade,  which  is  occupied  by  windows  (glass  area  and  frame)         ANNEX  2  GLASS  LIBRARY     
  
  
  

Source:  US  Department  of  Energy     ANNEX  3  Insulating  Values  of  Common  Building  Materials     
  
  
  

Source:  2013  ASHRAE  Handbook  of  Fundamentals  /  1958  ASHAE  Guide  /  www.inspectApedia.com     ANNEX  4  Philippine  Green  Building  Code  Activities       25