Safe Handling of

Sodium Hypochlorite

Japan Soda Industry Association

Contents
Introduction ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 1
I

Information on Sodium Hypochlorite ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 2
1. Commercial Sodium Hypochlorite ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 2
2. General Characteristics of Sodium Hypochlorite ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 2
3. Effects of Sodium Hypochlorite on the Human Body⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 3

II

Containers for Sodium Hypochlorite ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 4
1. Types of Containers ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 4
2. Displays on the Containers ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 4

III Handling of Containers ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 4
1. Transportation⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 4
2. Precautions for Storage ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 5IV

Tank Trucks, Rail Tanks, and Tankers ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 5
1. Structure ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 5
2. Unloading from Tank Trucks, Rail Tanks, and Tankers ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 6

V

Use of Sodium Hypochlorite⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 7
1. General Precautions ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 7
2. Treatment of Empty Containers and Waste ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 8
3. Accident Prevention Measures ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 8
4. Prevention Measures for Hygiene ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 9

VI

Actions to be Taken in Case of a Leakage⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 10

VII Maintenance of Facilities (Cleaning and Repairing) ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 11
VIII Safety Facilities⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 12
IX

Emergency Measures ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 13

X

Reference Tables ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 14
1. Relationship between the Specific Gravity of Sodium Hypochlorite and the
Effective Chlorine Concentration ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 14
2. Relationship between the Concentration of Sodium Hypochlorite and the Specific
Heat ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 14
3. Change in the Available Chlorine ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 15

XI

Related Laws and Regulations ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 16

XII Cases of Disasters ⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯⋯ 17

Introduction

Sodium hypochlorite is not designated as a
toxic or deleterious substance under the
Poisonous and Deleterious Substances Control
Law, or as a hazardous material under the Fire
Defense Law; however, if it is accidentally mixed
with an acid during handling, an accident may
occur, such as the generation of chlorine gas.
Therefore, persons who handle sodium
hypochlorite should learn about its properties,
precautions on handling, and the related laws
and regulations (such as the Food Hygiene Law),and should observe them to ensure safety.
This leaflet compiles the information that dealers, transporters, and consumers handling sodium hypochlorite need to know as a guideline forthe routine prevention of accidents.

―1―

I. Information on Sodium Hypochlorite
1. Commercial Sodium Hypochlorite
Commercial sodium hypochlorite is normally a transparent light greenish yellow
liquid containing not less than 12% of available chlorine and having a pH of 12 ormore. To inhibit the decomposition of the sodium hypochlorite, the product contains free (excess) sodium hydroxide. Specifically, the product called sodium
hypochlorite is an aqueous solution containing sodium hypochlorite, sodium
chloride (normally about 12%, but some grades contain 4 to 6%, or about 1%), anda small quantity of sodium hydroxide. In addition to this, sodium hypochlorite
for use in waterworks (JWWA K 120-2005), or sodium hypochlorite for food additives (available chlorine: 4 to 6%) is also available.
The quality standards for sodium hypochlorite for waterworks are as follows:
Quality standards of sodium hypochlorite for waterworks (JWWA K 120-2005)
Appearance
Available chlorine (%)
Free alkali (%)

Transparent light yellow liquid
＞
―5
＞
―2

Sodium hypochlorite for use in waterworks shall comply with the above
quality, as well as the ministerial ordinance for facility criteria.

2. General Characteristics of Sodium Hypochlorite
・Unstable compound even at normal temperatures, which gradually decomposes naturally.
・Decomposition is accelerated by sunlight, especially ultraviolet rays.
・The decomposition rate rises with elevation of the temperature.
・ Decomposition is significantly accelerated if a heavy metal, such as cobalt,
nickel, copper, and iron, or its salt is present.
・Decomposition is accelerated if the pH is lowered.
―2―

・If an acid is added and the pH lowers to 7 or less, a decomposition reaction
takes place rapidly, and chlorine gas is generated.
・Since commercial aqueous solutions are diluted with a large quantity of water,
there is no danger of ignition or explosion.
・Most metals and fibers are corroded by sodium hypochlorite due to its oxidizing properties. Excellent corrosion resistant materials are titanium, glass, andceramics. Other corrosion resistant materials are rigid polyvinyl chloride,
polyvinylidene chloride, polyethylene, fluororesin, flexible polyvinyl chloride,and ebonite. Rubbers are less resistant to corrosion by sodium hypochlorite.

3. Effects of Sodium Hypochlorite on the Human Body
・The level of corrosive action is comparable to sodium hydroxide. If an acidic
solution is added, hypochlorous acid is isolated and irritates the human skinand mucous membranes, but there is hardly any systemic poisoning due toabsorption.
・ Exposure to the eyes causes severe pain, and the cornea can be damaged
unless the eyes are washed immediately.
・Exposure of the skin to sodium hypochlorite for extensive periods may cause
skin inflammation or a rash due to irritation.
・ Inhalation of the mist from an aqueous solution of sodium hypochlorite irritates the mucous membrane of the respiratory tract and causes a hoarse voice,burning sensation and pain in the throat, severe coughing, and pulmonary
edema. Oral intake may cause a burning sensation and pain in the mouth,esophagus, and stomach; and may rarely cause perforation of the esophagus
or stomach.

―3―

II. Containers for Sodium Hypochlorite
1. Types of Containers
For bulk supply, sodium hypochlorite is frequently transported by tank trucks,
and for small quantities, containers with capacities of 500 milliliters to 20 liters
are usually used.

2. Displays on the Containers
When sodium hypochlorite is used for food additives, mandatory information
specified by laws and regulations must be displayed on the containers.

III. Handling of Containers
1. Transportation(1)

General precautions
・ Since sodium hypochlorite is highly corrosive, use corrosion resistant shipping containers and liquid transfer facilities (pipes, valves, pumps, etc.).
・ Since sodium hypochlorite is easily decomposed, avoid long-distance transportation as far as possible. Transportation under direct sunlight is unfavorable since decomposition is accelerated with a rise in temperature.
・ Since sodium hypochlorite is decomposed to release chlorine gas when it
comes in contact with an acid, avoid the consolidated transport of sodium
hypochlorite in small containers along with acids.
・ Do not use the containers for sodium hypochlorite as containers for othermaterials.
・When small containers containing sodium hypochlorite are transported, loadthem with the caps facing up.

―4―

(2)

Transportation of sodium hypochlorite by ship
・ When sodium hypochlorite is transported by ship, refer to the “Ship Safety
Law”.

2. Precautions for Storage
・Store sodium hypochlorite in a cool dark place, away from direct sunlight.
・Since heavy metals (such as cobalt, nickel, copper, and iron) act as a catalyst
and accelerate the decomposition of sodium hypochlorite, care must be taken
so that they are not mixed in the storage containers.
・Use a concrete or steel tank whose inner surface is lined or coated with a corrosion resistant material, or a tank fabricated using a corrosion resistant material. The tank should be of a structure that makes it easy to flush precipitates(such as silt).
・ Since sodium hypochlorite is highly corrosive, and generates chlorine gas if
erroneously mixed with an acidic solution, it is desirable to appoint a person in
charge of the indication, acceptance and inspection of the tank, and ensure that
this person witnesses the acceptance.

IV. Tank Trucks, Rail Tanks, and Tankers
・The capacity of a tank truck is normally 8 m3.
・The capacity of a rail tank is 10 to 35 m3.
・The capacity of some tankers is 160 m3.

1. Structure
When sodium hypochlorite is transported, shipped, or received using a tanktruck, rail tank, or tanker, it is important to have an accurate knowledge of thestructure and materials of the valves and pipes, as well as the interior and exteri―5―

or of the storage tanks related to transport, receiving, and shipping operations on
the basis of correct and accurate drawings; and to keep everyone informed about
these.

2. Unloading from Tank Trucks, Rail Tanks, and Tankers
・On receiving, make sure that the person in charge of the establishment continually observes the checking of pipes, opening and closing of valves, checkingof the commencement and termination of receiving, and the checking of thequantities received.
・ When loading or unloading using a tank truck, make sure that the manualbrakes and the vehicle lock are applied so that the truck does not move during
these operations. Under no circumstances should the truck be left unobserved.
・When unloading from a tank truck, rail tank, or tanker, use a pump or compressed air. If a gas other than air (nitrogen or carbon dioxide gas) is used,
immediately inform the loading operator or indicate this fact on the tank. If
the operator needs to enter the tank, replace the contents with water, measure
the oxygen concentration, and wear protective clothing so that there is no fearof suffocation.
・The supervisor of the unloading should make sure that the operators have sufficient knowledge of the properties of sodium hypochlorite, the joints and thepipelines; and allow them to operate these only after checking the contents ofthe tank and testing the vents and the safety valves.
・When unloading using a pump (or siphon), remove the vent flange of the tankin the tank truck, rail tank, or tanker to allow the entry of air. Remove theblanking plate of the delivery pipe, connect the pipeline of the storage tank tothe flange of the delivery pipe, and activate the pump (or siphon) to start delivery. When the tank has been emptied, stop the pump (or siphon), remove thepipeline from the delivery pipe, and close the vent and the flange of the tank.
During this operation, care should be taken so as not to spill the solution.
However, if it is spilt, flush it away with a large quantity of water.
・When sodium hypochlorite is delivered by air injection, make sure in advancethat there are no defects in the lid of the tank, the flange connected to the―6―pipeline, the valves and so on. Open the block valve slowly and properly adjust
the flow rate to the tank. Although the internal pressure of the tank is rapidly
lowers after deliver y has been completed, continue air injection until the
pipeline has been emptied before closing the valve.
・ The facility for pressure-pumping a sodium hypochlorite solution through aflexible pipe, such as a rubber hose must be equipped with a pressure gauge,
and an anticorrosive and pressure-resistant hose must be used. Before pressure-pumping, inspect the hose, pressure gauge, and the connection of thehose; and take sufficient care as to the limit of the working pressure of the
hose.

V. Use of Sodium Hypochlorite
1. General Precautions
・Since sodium hypochlorite is highly corrosive, iron cannot be used as a material for the facilities. Titanium or plastics, such as rigid polyvinyl chloride, aresuitable. Since some rubbers expand over a long period of time, care should
be taken.
・ Before handling sodium hypochlorite, the operators should maintain close
contact with each other, and check for any abnormalities in the opening andclosing of the valves and the connection of the hose.
・Before delivery, check the facilities so that decomposition or leakage does notoccur. Provide indications on the container to warn outsiders not to touch thevalves or cocks of the container.
・ Since oxygen or chlorine is released if the temperature rises, the pH is lowered, or foreign matter, such as a heavy metal, is mixed in during handling
operations, care should be taken.
・After use, make sure that the valve or cock has been closed. Install safety covers on valves and cocks so that outsiders cannot touch them.

―7―

・ When the sodium hypochlorite solution is being transferred between thetanker and the land, if the solution leaks into the water, fish and shellfish may
be harmed. In particular, if the delivery hose becomes immersed in the water,
care should be taken since any leakage may not be apparent.
・When the solution is being divided into smaller portions, make sure that thecontainers used for this have been thoroughly cleaned so that no acidic solution and no other materials remains in the container.

2. Treatment of Empty Containers and Waste
・Inspect the containers thoroughly after use, and to prevent leakage or deterioration in the quality, check for deformation of the containers, cracking andpeeling of the inner lining and coating, or the presence of residual matter, thenwash the containers with water and drain them.
・During inspections or repairs, ensure a proper airflow and good ventilation. If
ventilation cannot be assured, wear a gas mask.
・ If any waste solution or silt is disposed of without treatment, rivers may becontaminated. In addition, farm or fishery products maybe damaged. Thus,
such waste materials must always be disposed of after treatment.
・If the sodium hypochlorite is to be decomposed using an acid, this produces
chlorine gas, which negatively affects air quality ; thus, it should be disposed ofonly after decomposition has been per formed using a sealed container
equipped with a safety apparatus for the absorption of chlorine gas.

3. Accident Prevention Measures(1)

Measures to prevent erroneous operation
・Keep the containers and tanks containing sodium hypochlorite separate fromother materials, and display an indication of the contents, such as the words“SODIUM HYPOCHLORITE.” Store containers containing sodium hypochlorite in a yard exclusively used for this purpose as far as possible, or keep themseparated from other chemicals (especially acids). Do not use the containers―8―for other purposes. When a tank is being used, it must be separated fromother tanks, especially from tanks containing acids. In all cases, display theindication of the contents as “SODIUM HYPOCHLORITE.”
・ Separate the receiving piping from other piping. Display a white band of awidth of 5 cm or more around the receiving port for sodium hypochlorite, anddisplay the product name in a place where it can be easily seen. The productname and flow direction should also be properly displayed on piping used forother chemicals. These are the first steps for preventing erroneous operation.
Periodically check these displays to make sure that they have not been erased
or removed.
(2)

Education and training
・ Ensure that operators handling sodium hypochlorite observe the operating
standard for safe operations. For this, it is necessary to provide education andtraining concerning:
The location of protectors, showers, eye washers, cleaning hoses, andfirst aid facilities○ Proper method for the use of protectors and first aid facilities○ First aid measures to be taken in case of an emergency○ Properties, hazards, and proper handling of sodium hypochlorite○ For operators filling tanks, measures for preventing a lack of oxygen
deficiency
It is also important to train supervisors concerning the following, and regularly
carry out training drills for dealing with disasters:○ Proper usage of the first aid facilities○ Measures to be taken in case of chemical injury○

4. Prevention Measures for Hygiene・ During handling operations, keep the working area well ventilated, and as
required, use proper protective wear (such as a face mask, rubber gloves, rubber boots, rubber clothing, and protective goggles).

―9―VI. Actions to be Taken in Case of a Leakage
・If sodium hypochlorite is accidentally mixed with an acid, immediately neutralize it with an alkali, such as sodium hydroxide (caustic soda) or calcium
hydroxide (hydrated lime). Should a large quantity of chlorine gas be formed,
and there is the possibility that the chlorine gas will become diffused into theambient air, inform the relevant authorities, such as the fire station and thepolice, so as not to cause harm to others; at the same time take action to evacuate people or guide them upwind.
・If chlorine gas is inhaled, take the following action:○ If the patient is simply coughing, take him/her to a place that is well ventilated with fresh air, and get him/her to rest comfortably.
○ If the patient is coughing very hard and feeling that is hard to breathe, gethim/her to inhale the vapor of a 1:1 alcohol-ether mixture, or give him/herbuttery coffee, candies or sweet syrup to make him/her comfortable.
○ If the eyes are injured by chlorine gas, immediately wash the eyes with flowing tap water for at least 15 minutes. Depending on the symptoms, consult adoctor.
○ In case of severe symptoms, immediately call a doctor and follow the instructions given, and then take the following action.
a) Gently move the patient to a chlorine-free place, and if possible, lay thepatient on the back in a room at about 20℃ with the head and back held
higher, and keep the him/her warm with a blanket.
b) If the patient has difficulty in breathing, perform oxygen inhalation. Give
oxygen for 2 minutes, and then stop for 2 minutes. and repeat the treatment for 30 minutes. (If possible, use an oxygen cylinder for medical
use.)c) If breathing stops, perform mouth-to-mouth resuscitation. However, do
not perform this more than 18 times per minute.
・ If sodium hypochlorite comes into contact with the human skin or clothing,
immediately wash it off with a large quantity of flowing water.
・ If sodium hypochlorite gets into the eyes, immediately rinse it with a large
quantity of flowing water for at least 15 minutes, and consult a doctor.

― 10 ―

VII. Maintenance of Facilities(Cleaning and Repairing)
The cleaning or repair of a facility after the use of sodium hypochlorite solution
must be directed by an experienced supervisor who knows the dangers well. In
addition to general precautions, take care of the following:・Make sure that the solution is completely blocked off at the inlet port of thetank.
・When an operator enters the tank or the facility, remove the contents by pumping or flowing out as much as possible, and thoroughly clean it with water.
・Remove all the pipes connected to the tank or the facility. If possible, remove
them by sorting them into groups.
・Supply fresh air with a small air blower. Do not use compressed air since thisis dangerous.
・Display a warning sign when an operator is inside the tank or the facilities.
・ When the piping is being repaired, remove any solution in the pipe beforehand, and clean the pipe sufficiently with water.

― 11 ―

VIII. Safety Facilities
In order to prevent leaked sodium hypochlorite from flowing out of the area ofthe storage facilities, it is preferable to install facilities for the safe storage of sodium hypochlorite or facilities for recovering and preventing it from causing harm.
The examples of such facilities are as follows:・Spare tanks that can receive sodium hypochlorite in a short time in an
emergency

Tank

Spare tank・Liquid bank around the tank or group of tanks
a Earth fill

Protected by asphalt,
concreteor lawns

b Concrete

・Pit-like structure, pond and depression, etc.
Pit or water
channelTank
Pit or water
channelPit or water
channel

Tank

Discharging
pump

The leaked sodium hypochlorite is recovered or disposed of. For disposal, flash
it away with a large quantity of water.
― 12 ―

IX. Emergency Measures
・ If sodium hypochlorite comes into contact with the human skin or clothing,
immediately wash it off with a large quantity of flowing water.
・If sodium hypochlorite gets in the eyes, immediately rinse it with a large quantity of flowing water for at least 15 minutes, and consult a doctor. In this case,if clean lukewarm water is easily available, it is more effective in reducing thepain than cold water.
・ Should sodium hypochlorite be swallowed, immediately wash the mouth out
with water, and give the patient a large quantity of water, milk or raw egg. (Ifthe patient is unconscious, give nothing through the mouth.) Do not force thepatient to vomit, and consult a doctor promptly.
・If chlorine gas is inhaled, take the following action:○ If the patient is simply coughing, take him/her to a place that is well ventilated with fresh air, and get him/her to rest comfortably.
○ If the patient is coughing ver y hard and feeling hard to breathe, gethim/her to inhale the vapor of a 1:1 alcohol-ether mixture, or givehim/her buttery coffee, candies, or sweet syrup to make him/her comfortable.
○ If the eyes are injured by chlorine gas, immediately wash the eyes withflowing tap water for at least 15 minutes. Depending on the symptoms,
consult a doctor.
○ In case of severe symptoms, immediately call a doctor and follow the
instructions given, and then take the following action.
a) Gently move the patient to a chlorine-free place, and if possible, lay thepatient on the back in a room at about 20 ℃ with the head and backheld higher, and keep him/her warm with a blanket.
b) If the patient has difficulty in breathing, perform oxygen inhalation.
Give oxygen for 2 minutes, and then stop for 2 minutes. and repeat thetreatment for 30 minutes. (If possible, use an oxygen cylinder for medical use.)c) If the breathing stops, per form mouth-to-mouth resuscitation.
However, do not perform this more than 18 times per minute.

― 13 ―

X. Reference Tables
1. Relationship between the Specific Gravity of Sodium Hypochlorite and the
Effective Chlorine Concentration
Specific Effective chloSodiumrine concen- hypochlorite
gravity(20 ℃) tration (g/r)(wt %)

Specific Effective chloSodiumrine concen- hypochlorite
gravity(20℃) tration (g/r)(wt %)

1.05

030.0

3.00

1.16

110.0

10.05

1.07

040.0

3.94

1.17

120.0

10.76

1.08

050.0

4.87

1.18

130.0

11.53

1.09

060.0

5.76

1.20

140.0

12.28

1.11

070.0

6.64

1.21

150.0

13.03

1.12

080.0

7.50

1.22

160.0

13.75

1.13

090.0

8.34

1.24

170.0

14.45

1.15

100.0

9.16

1.24

178.0

15.00

The specific gravity of commercial sodium hypochlorite solution is about 1.20.

2. Relationship between the Concentration of Sodium Hypochlorite and theSpecific Heat
（20℃）
NaClO（g/r）

Specific heat(cal/g・℃)

NaClO（g/r）

Specific heat(cal/g・℃)

140.48

0.918

56.26

0.969

092.58

0.949

28.22

0.987

― 14 ―

Decrease in
the available chlorine (%)

13
15℃
12
30℃

11
10

1

2

3

4

5

6

7

1.0
0.8
0.6

30℃

0.4
15℃

0.2
0

12 13 14 15 16 17 18 19(Days)

Concentration of sodium
hypochlorite in the solution (%)

Figure 1 Change in the available
chlorine over time at a solution
temperature of 15℃ and 30℃(available chlorine: 12%, shieldedfrom light)

Figure 2 Decrease in the available
chlorine per day according to
the concentration of sodium
hypochlorite in the solution at asolution temperature of 15℃ and
30℃ (shielded from light)

Decrease in the available chlorine (%)

Available chlorine (%)

3. Change in the Available Chlorine

2.5
2.0
1.5
1.0
0.5
1

2

3

4

5

6

7

8

9 10 11 12(Months)
Figure 3 Decrease in the available chlorine by month(available chlorine: 12%, shielded from light, after
standing for 10 days)― 15 ―

XI. Related Laws and Regulations(1)

Food Sanitation Law
Sodium hypochlorite is specified as a chemically-synthesized compound when it
is intended for use as a food additive, and is subject to restrictions when it is marketed, displayed, manufactured, and processed.

(2)

Ship Safety Law
Sodium hypochlorite (excluding solutions containing 5% or less of available chlorine by weight) is specified as a hazardous material (corrosive material) in theregulations for shipping and storing hazardous materials under this Law, and theshipper must observe the preparation of hazardous material specifications, therules for packaging, the notification of hazardous materials when shipping by
motor vehicle ferry, etc.

(3)

Water Pollution Control Law
Since sodium hypochlorite affects the hydrogen ion concentration specified byregulations and standards related to water discharged from establishments, careshould be taken.

(4)

Waste Disposal and Public Cleaning Law
Waste alkali is specified as industrial waste, and its collection, transfer, and disposal must be carried out by enterprises themselves in accordance with specified
standards, or entrusted to industrial waste disposal services approved by theGovernor that exercises jurisdiction over the district.

― 16 ―

XII. Cases of Disasters(1)

Accidents during handling and transportation(a) When an operator was checking the rotating conditions of a pump for loading
sodium hypochlorite solution into a tank truck, the rubber hose for loading
broke, the solution sprayed out, and the droplets entered the operator's left
eye causing a mild case of conjunctival congestion.
(b) Since a tank truck was overloaded during a shipping operation for sodium
hypochlorite solution, the solution was returned to the shipping tank. Whenthe hose was removed from the inlet pipe of the shipping tank, the droplets
entered both eyes of the operator causing a mild case of conjunctival congestion.
(c) Since an operator accidentally connected a wrong receiving pipe to a tanktruck, and sulfuric acid was fed into a sodium hypochlorite tank, chlorine gas
was emitted. Twenty-one operators and 115 nearby residents were affected by
the gas, and five of them had to take time off from work.
(d) A truck for transporting chemicals rolled onto its side, the base of the steeltank cracked, and sodium hypochlorite solution used as a fixing agent in dyeing leaked out, causing the traffic to be blocked.
(e) Since an operator accidentally connected the wrong pipe in a chemical
receiving station for a wastewater treatment facility, and sodium hypochlorite
solution was fed into an aluminum sulfate tank, chlorine gas was emitted. A
dozen nearby residents were affected by the gas.

(2)

Accident in a manufacturing plant(a) When an operator closed a cock for the maintenance of the manometer formeasuring the circulation in a sodium hypochlorite manufacturing facility, a
glass U-tube was accidentally broken, some solution was ejected, and droplets
entered both eyes of the operator, causing superficial keratitis in both eyes,
which required 7 days for recovery.

(3)

Accidents during use(a) In a building that used a 12% sodium hypochlorite solution for the disinfection of the toilets and hydrochloric acid for cleaning, when a female cleaner
mixed the two chemicals so as to try to finish both jobs at the same time, chlorine gas was generated, and she inhaled the gas and died.
― 17 ―

(b) When sulfuric acid was poured into a plastic bucket from a tank to feed thesulfuric acid into a drain treatment facility, sodium hypochlorite had been left
in the bucket and reacted with the sulfuric acid to generate chlorine gas, andone person was intoxicated.
(c) When an operator fed dilute sulfuric acid into plating drain for chromium
treatment without knowing that an excess of sodium hypochlorite had been
added to the plating drain, chlorine gas was generated, and the person was
intoxicated.
(d) When sodium hypochlorite was fed after dilute sulfuric acid was extracted
from a dilute sulfuric acid tank and the tank was cleaned for changing it to contain sodium hypochlorite, since the cleaning was insufficient, the sodium
hypochlorite reacted with the remaining dilute sulfuric acid to emit chlorine
gas, and 20 operators and other persons were affected by the gas.

― 18 ―

Safe Handling of Sodium Hypochlorite
First edition :Revised edition :Edited by :Published by :July 15, 1982
November 20, 2006
Permanent Committee on
Technology and Safety
Japan Soda Industry Association
Japan Soda Industry Association