§DETECTOR §STATIC

AC/DC DETECTORCOMMON SPECIFICATION■ USE
Small sized and multi-function electronic detector forcontrolling to cope with automation of electric power
facility, labor and energy saving.
S-63 series is used for protection in various fields
such as heavy current circuit measuring, reverse
power of generator in shipping industry and frequency
control and overload detection of motor.
Countermeasure against damage by input line surge
and false operation is implemented.

■ TYPE NAME CONSTRUCTURE(1) (2) − (3) − (4) (5) − (6)(1) Series(3) Setting(5) About period

Mark

Series name

Mark

Mark

S

Still detector

H

Upper limit(2) Input

L

Lower limit

HL

Upper/Lower limit

DWith definite period

Mark

Input

HH

Upper limit 2 steps

I

With inverse periodA

AC current

LL

Lower limit 2 stepsV

AC voltage

F

FrequencyW

AC powerRW

AC reverse powerD

DC current/voltage

Mark
63

: input position /state )W/ or w/o period
No period

None(immediate operation)(6) Circuit(4) Outer case

■ CONTACT CONSTRUCTION(

Setting

DimensionMark

Circuit3φ3-phase 3-wire(depth×width× high)120×110×112mm■ FEATURE► High quality, high reliability andnoise resistance design.
► Voltage or current detector has
strong structure against distorted
waveform.
► Detection operation can be
confirmed with operation display.
► Definite time and inverse time
can be integrated.
► Multi type with multi functioned
to cope with various needs.

Products List

1§DETECTOR §STATIC■ COMMON STANDARD SPECIFICATION
Item
Setting stability
Error of operating
value setting
Operating time
setting error
Temperature
influenceControl power
voltage influence
Frequency
influence
Waveform
influence
Operating time(detector w/ time
limit is excluded).
Reset time
Contact system
Contact capacity
Relay type
Overvoltage
strength
Overcurrent
strength
Control power
voltage strength
Insulation
resistanceWithstand voltage
Impulse withstandvoltagevibration (false
operation)
Shock
External color
Mass
Operatingtemperature/humidity range
Storagetemperature range
Altitude

Products List

Specification
Operation value: % against max. input value. Frequency is Hz.
Operation time: % against max. setting value.
% against setting range when setting range is 1/3 of max. input or more:±5%% against max. input value when setting range is below 1/3 of max. input: ±1.5%(However frequency is according to individual specification.)% against max. setting time.
Error at 23±20℃ change（％）.
(Permissible limit is same as setting stability counterpart)
AC: Error at ±15% change of rating voltage
DC: Error at ±20% change of rating voltage(Permissible limit is same as setting stability counterpart)
Error at 45-65Hz change.
Error against waveform including 3rd harmonics 15%
0.3 sec. or lessH type: 90→110% of operating time.
L type: 110→90% of operating time.

H type: 110→90% of operating time.
L type: 90→110% of operating time.
1C contact for each
AC200V, 5A (resistance load) DC30V, 5A (resistance load)
NTI relay (manufactured by Panasonic Electric Works Co., Ltd.)AC 2 times (10 sec.), 1.2 times (continuation) of rating voltage.
DC According to individual specification.
AC 40 times (1 sec.), 1.2 times (continuation) of rating current.
DC According to individual specification.
AC 2 times (10 sec.), 1.2 times (continuation) of rating voltage.
DC 1.3 times (continuation) of rating voltage.
DC500V 50MΩ or more between electric circuit and outer case.
DC500V 20MΩ or more between input, control power supply and contact
AC2, 000V (50/60Hz) 1 min. between electric circuit and outer case.
AC1, 500V (standard) or AC2, 000V (50/60Hz) 1 min. between input, control power
supply and contact.
4.5kV 1.2×50μs between electric circuit and outer case,

0.3 sec. or lesspositive/negative polarity。

Frequency: 16.7Hz, peak to peak: 1mm,
10 min. each for X, Y and Z directions.
False operation: 98m/s2, endurance: 294m/s2,
2 times each for X, Y and Z directions.
Black (Munsell N 1.5)
1kg or less-10-50℃, 40-85% RH-30〜60℃
1000m or less2§DETECTOR §STATIC■ CONNECTION DIAGRAM●AC Current detector●AC Power/Reverse power detector

AC control power

DC control power

AC100/110V: No.1-2
AC200/220V: No.1-3

DC24V: (R) with built-in multiplier
DC48V: (R) with built-in multiplier
DC110V: (R) with built-in multiplier

AC control power

DC control power

DC24V: (R) with built-in multiplier DC110V: (R) with built-in multiplier
DC48V: (R) with built-in multiplier●AC Voltage/Frequency detector●DC Voltage/Current detector

AC control power

DC control power

AC control power

DC control power

AC100/110V: No.1-2
AC200/220V: No.1-3

DC24V: (R) with built-in multiplier
DC48V: (R) with built-in multiplier
DC110V: (R) with built-in multiplier

AC100/110V: No.1-2

AC200/220V: No.1-3■ DIMENTIOAN
Multiplier for DC110V (RWH60G)*SVPR-63 is unequipped

Products List

3

§DETECTOR §STATIC

AC/DC DETECTOR

63 SERIES

SA-H-63(120×110×112mm/0.7kg)■ SPECIFICATION
Setting method
Product

Type nameSA-AC
current

SA-

- 63

H

L

HL

HH

LL

○

○

○

○

○

current

5A

- 63D

○

(w/definite time)SA-

Rating○○○○(consumptionSetting range
example (VROperating
Frequencychangeable)changeable)

0.5-5A

-

2.5-5A

0.5-5sec.

0.25-2.5A
1.5-4A

50/60Hz

VA:1VA)- 63I(w/inverse time)

0.5-10sec.
0.5-50sec.
1-5sec.

2-5A○time (VR5-13sec.
10-50sec.

Control power

AC110/220V

Operation
display
Specify(50/60Hz)
2.5VA or less
DC24V (3W)

(10W)

*When control
power is DC

with

110V,
multiplier is

DC48V (5W)
*DC110V

Notes

externallywithequipped.

・Operating time at 40ms or less is also manufacturable by designation.
SV-

- 63

○

○

○

○

○

150V

-

Specifyor 300V
AC current(consu
SV-

- 63D

○

(w/definite time)

○

○

○

○

50/60Hz*1

mption0.5-5sec.
0.5-10sec.

VA:1VA)

0.5-50sec.
46-50Hz

SF-

- 63

○

○

○

○

○

Frequency(consumpti
SF-

on

- 63D

○

(w/inverse time)

○

○

○

○

VA:1VA)-

42-50Hz

220V
50Hz or 60Hz

60-64Hz52-60Hz60-68Hzwith

DC48V (5W)

*2 Whencontrol power

2.5VA or lessis DC 110V,
Specify*2 DC110V

50-58Hz56-60Hz(50/60Hz)
DC24V (3W)

50-54Hz

110V or

AC110/220V

multiplier isexternallyequipped.

(10W)
0.5-5sec.
0.5-10sec.

with

0.5-50sec.

・Operating time at 40ms or less is also manufacturable by designation for voltage detector.
・3-phase detector type is also manufacturable for voltage detector.
*1 Setting range example
100-140V
80-120V
60-100V
150V

120-140V
110-130V
100-120V
90-110V
80-100V

Products List

200-180V
160-240V
120-200V
300V

240-280V
330-260V
200-240V
180-220V
160-200V

4§DETECTOR §STATIC

Setting
Product3-phasepower

Type nameSW-- 63– 3φ

H

L

power

○

○

voltage

SRW – H – 63 – 3φ3-phasepower
3-phasereversepower

current

frequency

SW-- 63D– 3φ○(w/definite time)
SRW – H – 63D – 3φ○

SRW – H – 63I – 3φchangeable)

5A

1kW

220V

(consuOperationor(consumption2kWmption

VA

VA

1VA)

(50/60Hz)

50-90%

AC220V

50/60

5-50%

(2.5VA)

Hz

2-20%

1VA)

0.5-5sec.

(50/60Hz)

0.5-10sec.

DC24V (3W)

0.5-50sec.

DC48V (5W)

Notes

display

Specify*When control
power is DC
110V, multiplier iswithexternallyequipped.

*DC110V
0.5-10sec.

1-20%

○

(w/inverse time)

Control power(2.5VA)-

10-100%or○(w/definite time)(VR changeable)

AC110V○power

Operating time

example (VR110V

3-phasereverseSetting range

Rating current

method

(10W)

with

0.5-20sec.

・3-phase balance type 1-wattmeter method.
Setting method
Product

Type name

SD-

- 63

H

○

L

○

HL

○

HH

○

LL

○

DC
voltageorDCcurrent

SD-

- 63D

(w/definite time)

○

○

○

○

○

Setting range

Continuous

example (VRwithstandchangeable)

over input

Input
resistanceDC4-20mA

10Ω

0.2-1A

60mV

1-5A

60mV

Operatingtime (VRControl powerchangeable)-

AC110/220V

DC5-10mA

±10V

100kΩ

(50/60Hz)

10-60mA

±10V

100kΩ

2.5VA

20-100mA

±10V

100kΩ

(50/60Hz)

DC0.2-1V

±250V

500kΩ

1-5V

±250V

500kΩ

0.5-5sec.

DC24V (3W)

5-15V

±250V

500kΩ

0.5-10sec.

DC48V (3W)

10-30V

±250V

500kΩ

0.5-50sec.

DC110V (5W)

30-70V

±250V

500kΩ

50-150V

±250V

500kΩ

Operation
displayspecify

DC12V (3W)
with・Setting range and operation time of each product is changeable by specification.

Products List

5§DETECTOR §STATICAC TACHOGENERATOR REVOLUTION SPEED DETECTORCOMMON SPECIFICATION■ USEThis product receives output voltage signal or
output frequency signal of AC tachogenerator anddetects starting operation signal, control signal, overspeed stop signal and outputs contact signal. As thisproduct is all electronized, detection with highsensitivity, high speed is possible. No influence ofvarious factors such as external noise.

■ FEATURES► High quality, high reliability and noise
resistance design.
► 3-step detection level equipped.
► Easy setting adjust from exterior byscrewdriver adjustor.

■ COMMON STANDARD SPECIFICATION
Item
Setting stability
Error of operating
value setting
Temperature
influence
Waveform
influenceContact system
Contact capacity
Relay type
Overvoltage
strength

Specification
Operation value: % against max. input value.
% against max. input value
at 23±20℃(Permissible limit is same as setting stability counterpart)
Error against waveform including 3rd harmonics 15% (except SFTG)
1a contact for each
AC220V, 0.5A, DC100V 0.5A, resistance load
NTI relay (manufactured by Panasonic Electric Works Co., Ltd.)
2 times (10 sec.), 1.2 times (continuation) of rating voltage.
STG

Control power
voltage strength
Influence of noise
Operation time
Insulation
resistanceWithstand voltage

1.3 times (continuation) of rating voltage.
DC: 1.3 times (continuation) of rating voltage.
SFTG AC single phase full wave rectifier waveform: 1.1 times (continuation) of
rating voltage.
Error when noise is applied (800ms, 1000V), % against max. input value (normal
mode noise/common mode noise)
0.3sec. or less against setting value 90→110% input.
DC500V 50MΩ or more between electric circuit and outer case.
DC500V 20MΩ or more between input, power supply and contact
AC2, 000V (50/60Hz) 1 min. between electric circuit and outer case.
AC1, 500V (50/60Hz) 1 min. between input, power supply and contact.

Vibration
Frequency: 16.7Hz, peak to peak: 1mm, 10 min. each for X, Y and Z directions.
(false operation)
Shock
False operation: 98m/s2, endurance: 294m/s2, 2 times each for X, Y and Z directions.
External color
Black (Munsell N 1.5)
Operating temperature/humidity range-10〜+50℃, 40〜85% RH
Storage temperature range-30〜+60℃

Products List

6§DETECTOR §STATIC■ CONTROL OUTPUT CONDITION■ CONNECTION DIAGRAM■ DIMENSIONS (Unit: mm)

Products List

7

§DETECTOR §STATICAC TACHOGENERATOR REVOLUTION SPEED (FREQUENCY) DETECTOR
SFTG-HHH-63

SFTG-HHH-63(120×110×112mm/0.7kg)■ STANDARD SPECIFICATION
Item
Type name
Setting
methodInput
voltageMax. input
frequency
Control
supplySetting
range

SFTG-

Description- 63

H, HH, HHH
Refer to kinds of input voltage →Refer to setting range example.→
Refer to kinds of control power.→
H1
H2
H3

Hz 〜
Hz 〜
Hz 〜

Hz
Hz
Hz

(Refer tosetting range
example)●Kinds of input voltage
Input voltage
AC50V
AC75V
AC100V
AC150V
AC200V
AC300V●Kinds of control supply power
Control power
voltage
DC24V■ FUNCTION
Item
Setting stability
Error of operating value setting
Dead band
Waveform influence
Temperature influence
Control power voltage influence
Noise influenceMasscharacteristics±1%±5%
3% or less
±1%
±1%
±1%
±2%
0.7kg

Input impedanceApprox. 60kΩApprox. 80kΩApprox. 100kΩ
Approx. 150kΩ
Approx. 200kΩ
Approx. 300kΩ

DC100V

Fluctuation range
DC24V±20% 3.5W
Single phase full wave rectifier waveform of
AC24V±15% 5VA
DC80V-140V 5W
Single phase full wave rectifier waveform ofAC100/110V (85V-121V) 7VA●Setting range example
H1 (LOW)
30-150Hz
20-100Hz
15-75HzH2 (RATED)
240-330Hz
160-220Hz
120-170Hz

H3 (OVER)
330-430Hz
220-290Hz
160-220Hz

Max. input
430Hz
290Hz
220Hz

■ BLOCK DIAGRAM

Products List

8§DETECTOR §STATICAC TACHOGENERATOR REVOLUTION SPEED (VOLTAGE) DETECTOR
STG-HHH-63

STG-HHH-63(120×110×112mm/0.7kg)■ STANDARD SPECIFICATION■ FUNCTION

Item
Type name
Setting method
Input voltage

Item
Setting stability
Error of operating value setting
Dead band

Control supply
Setting range

Description
STG- 63
H, HH, HHH
Refer to kinds of input voltage
DC24V/48V/100V 5W or lessSpecify, please.
V 〜 V
H1(Refer to setting
H2
V 〜 V
range example)
H3
V 〜 V

characteristics±1%±5%
2% or lessTemperature influence±1%

Control power voltage influence
Frequency influence
Noise influence
Mass

±1%
±1%
±2%
0.7kg

●Setting range example
Max.input voltage
AC50V
AC75V
AC100V
AC150V
AC200V
AC300V

Setting range example
10-20V, 20-30V, 20-40V, 30-50V
10-60V, 20-40V, 30-50V, 55-75V
10-30V, 50-70V, 40-90V, 75-95V
35-55V, 60-80V, 80-100V, 100-150V
40-60V, 95-115V, 70-120V, 150-200V
80-130V, 120-170V, 200-250V, 250-300V

Input impedanceApprox.50kΩ
Approx.100kΩ
Approx.100kΩ
Approx.160kΩ
Approx.160kΩ
Approx.210kΩ

■ BLOCK DIAGRAM

Items for specifying
1, type name4, control supply power

Products List

2, rating5, quantity

3, setting range
6, others

9§DETECTOR §STATICPOWER FLOW DETECTOR
SDA-HL-83-33■ USE
This product is detector to detect power flow
and control/protect AC equipment.
SDA-HL-83-33(120×110×130mm/1.0kg)■ FEATURES► High quality, high reliability and noise resistance design.
► Conformed to IEC standard.
► Response time is 60mS or less.
► Incoming/outgoing current can be detected by 2% of rated value.
► Use relay of Au-plated cross bar twin contact, arc-barrier for switching of low power circuit.

■ STANDARD SPECIFICATION
Item
Type name
Conversion method
Max. input
Input voltage
Input current
Input frequency
Control supply
Neutral zone setting range
Dead band
Setting stability
Neutral zone setting error
Response speed
Contact output
Contact capacity
Insulation resistanceWithstand voltage
Impulse withstand voltage
Operating temperature/humidity range
Storage temperature range
External color
MassStandard specification
SDA-HL-83-33
I cosφconversion
I cosφ; ±5A (or ±1A)
line voltage 110V±15% 1VA
S-phase current: 5A (or 1A) 1VA *1
50/60Hz
AC100V/200V or DC110V (90-140V) 5W
2-10% (setting VR changeable)
1% or less (% against max. input value.)±1% (% against max. input value.)±1% (% against max. input value.)
60ms or less (0-200% of setting value.)
H; 1a L;1a
DC110V L/R=7ms, 90mA *2
DC500V 50MΩ or more between electric circuit and outer case.
DC500V 20MΩ or more between input, power supply and contact terminal.
AC2, 000V 1min. (50/60Hz) between electric circuit and outer case.
AC2, 000V 1min. (50/60Hz) between input, power supply and contact terminal.
5kV, 1.2/50μs (positive/negative) 10 times each between electric circuit andouter case.
-10〜+50℃;
40-85% RH-30〜+60℃
Black (Munsell N 1.5)
Approx. 1kg.

*1: T-phase or R-phase can be measured when doing wire-connecting change though S-phase measurement on thestandard issue. (Measure it as an example of T-phase.)*2: It is possible to produce from being in a large contact capacity relay by designation (MY-2Z-2, DC100V, 0.2A
L/R=7ms) though MY-4Z-4 and CBG are used for the relay on the standard specification.

Products List

10§DETECTOR §STATIC■CONNECTION DIAGRAM
2nd phase (S-phase) current measuring (standard)

3rd phase (T-phase) current measuring connection■DIMENSION (Unit: mm)■ OPERATION

Items for specifying
1, type name2, rating3, setting range
4, input 5, control supply power
6, quantity and others

Products List

11§DETECTOR §STATICGROUND RESISTANCE DETECTOR
SGR-L- 63
SDGR-L-63■ USE
This product detects grounding resistance of isolated
neutral system DC power circuit and outputs contact
signal. As DC bus voltage of measuring circuit is used
as it is and grounding resistance is sought in bridge
detection circuit, influence such as stray capacity
generated upon wiring circuit such as ship can beremoved. As circuit composition has no influence ofpower voltage fluctuation, stable performance can berealized with possible high sensitivity setting.

SGR-L-63(120×110×112mm/1.0kg)■ FEATURES► Influence of measuring circuit power voltage fluctuation can be compensated.
►Stray capacitance between lines upon measuring circuit can be removed.

■ STANDARD SPECIFICATION
Item
Product
Type name
Input
Measuring circuit voltage
Control supply
Contact output
Contact capacity
Starting delay (S/D)
Setting range
External color
Operating temperature/humidity range
Storage temperature
range
Mass
Setting stability
Operating value setting
error
Dead band
Temperature influence
Measuring circuit voltage
influence

Products List

Standard specification
AC earth resistance detector
DC earth resistance detector
SGR-L-63
SDGR-L-63
Identical to setting range.
AC110/220/440V
DC24V+30%, -20%
AC100/110V±15%, 5VA or

AC400/440V±15%

identical to measuring circuit voltage

AC200/220V±15%,5VA(50/60Hz)(power consumption 3W)

L;1C
AC200V 5A, DC24V 5A resistance load/DC125V 80mA L/R=30mS
Fixed: 0.5 sec.
Refer to setting range example.
Black (Munsell N 1.5)
-10〜+50℃;
40-85% RH-30〜+60℃
1kg±5%Approx. 500g(% against setting value.)±10%(% against setting value.)

10% or less5%(% against setting value.)(% against setting value.) (23℃±20℃)

5%(% against setting value.) (24V±30%, -20%)

12§DETECTOR §STATIC■ CONTROL OUTPUT CONDITION●Setting range eg.(SGR-L-63)

L

Setting range
0.01-1MΩ
0.05-5MΩ
0.1-10MΩ

Internal impedance
100kΩ
500kΩ
1MΩ

●Setting range eg.(SDGR-L-63)

L

Setting range
1k- 5k- 25kΩ
2k- 10k- 50kΩ
4k- 20k- 100kΩ

■ CONNECTION DIAGRAM■ DIMENSION

Products List

13§DETECTOR §STATICHIGH ACCURACY FREQUENCY DETECTOR
SFD-HL- 74

SFD-HL-74(120×165×130mm/0.7kg)■ USE

This product receives frequency signal, detects excess or deficiency and outputs contact
signal. As this product is all electron, setting with high sensitivity is possible. Stableperformance because of no influence by various factors such as vibration/external noise.

■ FEATURES► High quality, high reliability and noise resistance design.
► High accuracy (0.01Hz) can be realized with frequency detection by CPU.
► Accurate setting is possible by digital switch.

■ STANDARD SPECIFICATION
Item
Type name
Input

Standard specification
SFD-HL-74

Rating frequency

50Hz or 60Hz (specify)

Rating voltage

AC100/110V or AC200/220V (specify)

Control supply

AC100V±15% (3VA or less) *Contact output

H: 1C

Contact capacity

AC220V 5A, DC24V 5A resistance load

L:1C

50Hz setting range example

L: 49.0-49.9Hz

External color

Black (Munsell N 1.5)

H: 50.0-50.9Hz

Operating temperature/humidity range-10〜+50℃, 40-85% RH

Storage temperature range-30〜+60℃

Mass

0.7kg

* DC110V, DC24V, AC200V are manufacturabile by specify.

■ BLOCK DIAGRAM

Products List

14§DETECTOR §STATIC■ FUNCTION
Item

Condition

Permissible limit

Setting stability

Operating value against setting value.

±0.01Hz

operating value against setting value (23℃±20deg).

±0.01Hz

operating value against setting value (±15％ of rating value).

±0.01Hz

Overvoltage strength

2 times (10 sec.) of rating voltage.

no abnormality

Control

AC: 2 times (10 sec.), 1.2 times (continuation) of rating voltage.

Temperature
influenceControl

power

voltage influence
power

voltage strength
Insulation resistanceWithstand voltage
ImpulsewithstandDC: 1.2 times (continuation) of rating voltage.
DC500V between electric circuit and outer case.
DC500V between input, control power supply and contact
AC2, 000V (50/60Hz) 1 min. between electric circuit and outer case.
AC2, 000V (50/60Hz) 1 min. between input, power supply and contact.
5kV 1.2/50μs between electric circuit and outer case,no abnormality
50MΩ or more
no abnormality
no abnormality

voltagepositive/negative polarity。

Vibration

Frequency: 16.7Hz, peak to peak: 1mm,

(false operation)

10 min. each for X, Y and Z directions.

Sock

294m/S2 2 times for X, Y and Z directions

no abnormality

Response time

Time for relay to operate after input changes.

0.5sec. or lessno abnormality■ DIMENSION

Mark
①
②
③

Products List

Name
box
Terminal board
Terminal block

Material
SPCC
SPCC
PM-GE

15

§DETECTOR §STATIC■ CONTROL OUTPUT CONDITION*HH type and LL type are also manufacturable by specifying.

■ CONNECTION DIAGRAM

Items for specifying
1, type name4, control supply power

Products List

2, rating5, quantity

3, setting range

16