ULS type Pump installation, disassembly, and reassembly● This instruction manual describes how to disassemble and reassemble the ULS type pump.
For details about other operations, see main part of the instruction manual.
● Be sure to deliver this instruction manual with main part of the instruction manual to operators
who actually operate the pump.
● Be sure to store this instruction manual and main part of the instruction manual in a safe place
where all concerned personnel can refer to it immediately.

Pump installation●Install the electric motor above the pump or next to the pump horizontally.
*
Never install the electric motor hanging downward.
CAUTION
If the electric motor is installed hanging downward, slight water leak may enter the electric motor,
causing an accident.

（Example of pump installation）

SuctionDischarge*Never install the electricmotor hanging downward.

Discharge

Discharge
SuctionDischarge

SuctionSuctionPump disassembly* This pump can be disassembled without disconnecting it from the piping. However, when necessary,remove the suction flange and discharge flange to detach the casing from the piping.

３３０① Close the gate valves on the suction and discharge sides and remove the draindischarge plug (510) to discharge the fluid from the inside of the pump.
② Disconnect the small piping (external pipe, etc.) around the pump.
(For mechanical sealing pump, disconnect the SF pipe (330).)

５１０

０４４
③ Remove the bolts that secure the casing (001), casing cover (011), and motor base (044).
Remove the casing cover (011) together with the motor from the casing (001).
(It is convenient to use the motor eye bolts for this work.)
In this status, you can inspect the inside of the pump. So, inspect for wear or fault.

④ Remove the impeller nut (460) and whirl-stop (461), pull out the impeller (020),
and remove the impeller key (470).
(A groove is provided at the shaft end on the rear of the motor shaft. So, use a slottedscrewdriver, etc.)

０１１
００１

３４００１１
４７００２０* 1. For mechanical sealing pump

● For detailed drawing of the mechanical seal, see "Replacing the mechanical seal" on page 12.
Remove the mechanical cover (340) from the casing cover (011).

－１－４６１
４６０

HC3-595-1

⑤ Remove the casing cover (011) from the motor base (044), and pull out the sleeve (031), sleeve packing (032),
mechanical cover (340), and deflector (250) from the motor shaft (681).

２５００４４３４０

０３２０３１

６８１０１１* For mechanical sealing pump, loosen the set screw and pull out the mechanical seal rotating ring (310) fromthe sleeve (031).

０３１
３１０
Set screw
セットスクリューRotating ring
回転環

⑥ Remove the motor base (044) from the motor.

０４４* 2. For gland packing pump

Remove the packing retainer (090) from the casing cover (011), and take out the gland packing (300) and watersealing ring (082) from the inside of the pump.

０９０
３００

０１１

０８２

Pump reassembly
Reassembly of the pump is possible by the reverse order of disassembly.
However, pay special attention to the following points.
（1） Replace each packing with a new one.
（2） If any part is worn out or damaged, replace it with a new one.
（3） If the inside of each part is clogged with contaminant, clean it before use.
●For mechanical sealing pump, be sure to bleed the air through the air vent valve(500)
before starting the operation.
If the air is not bled, the mechanical seal may be broken.
●When changing the gland packing to the mechanical sealing, be sure to install
the air vent valve (500) and SF pipe (330).
CAUTION
Otherwise, the mechanical seal may be broken.
●Do not stretch the SF pipe (330) excessively or give any damage to it.
Additionally, do not operate the pump under operating conditions other than those shown below.
* Operating pressure
12 kg/㎠ orless* Fluid temperature
80 ℃ orless
Otherwise, the pipe may be broken, leading to scattering of fluid inside the pump.

－２－

HC3-595-2