SB® 350 Connectors
Up to 500 Amps

The SB® 350 is the largest connector in the series withpower capabilities up to 500 amps with a 350 mcm wire.
Wires ranging from 1/0 to 350 mcm (53.5 to 185 mm²)
fit into the one piece housing available in standard PC ora chemical resistant PBT/PC blend. Silver plated wire orbusbar contacts minimize electrical resistance while
offering supreme durability and reliability.
• Up to 350 mcm (185 mm²) Wires
Allows UL rated currents up to 500 amps

• Chemical Resistant Housing Option
Extends temperature range down to -40°C, while offering enhanced UV andchemical resistance• Same Housings Used for Wire and Busbar Contacts
Enables color-coded mechanically keyed wire to busbar connectionsSB® 350 ORDERING INFORMATION
SB® 350 Standard Housings

The largest SB® housings work with wire contacts up to 350 mcm (150 mm²) as well as busbar contacts.
Genderless design mates with itself. Mechanical keys are color-coded. NOTE: SB® 350 Black and Blue
Housings have the same keying features and can be intermated.			
Description		
Part Numbers
Minimum Quantity
5025
Yellow		 914-BK914
Orange		 932-BK
932
Bottom View
Red		 913-BK
913[ 69.9 ]Gray		 906-BK
906
P = Chemical Resistant
2.75
Blue		 912-BK
912
Green		 931-BK
931
Black		2-7250G8			[ 28.6 ] [ 34.9 ]
1.38
1.13

[ 6.6 ]
Ø 0.26(2) PLC’S

MATERIAL ID[ 182.6 ]7.19

SB® 350 Chemical Resistant HousingsSame features as the Standard SB® 350 but molded in achemical resistant PBT/ PC blend. Suitable for use to -40°C.		
Description		
Part Numbers
Minimum Quantity
5025
Red		
P913-BK
P913
Gray		P906-BKP906[ 107.9 ]4.25

Mated Length[ 33.3 ]1.31

SB® 350 Silver Plated Wire Contacts

Silver plated contacts offer superior electrical performance and durability up to 10,000
mating cycles. See reducing bushings in accessory section for smaller wires.													Mating-AAWGmm²Force
Loose Piece Part Numbers
inches mm
Minimum Quantity 		
200
150
50350 mcm 185
High		 -		910-BK
910 *
0.75
19.05
300 mcm 152
High		 -		910-BK
910 *
0.75
19.05
4/0107.2
High		 908-BK 908 *
0.64
16.26
3/085
High		 916-BK 916 *
0.58
14.73
2/067.4
High		 907-BK 907 *
0.49
12.45
1/053.5
High		 917-BK 917 *
0.44
11.18Dimensions- B -		inches mm-Cinches mm

0.87
0.87
0.75
0.70
0.64
0.51

3.04
3.04
3.03
3.00
2.96
2.91

22.10
22.10
19.05
17.78
16.26
12.95

[ 32.8 ]1.29 MIN

77.2
77.2
77.0
76.2
75.2
73.9

[ C ± 2.0 ]C ± 0.08

A
B[ 20.6 ]0.81* Sold as pairs. 2 parts shipped for every 1 part ordered.

SB® 350 Silver Plated Busbar Contacts

Use 2 busbar contacts per housing to provide a quick disconnect input or output busbar
connection. Busbar contacts are for mating with wire contacts only. Part number 350BBSincludes lock nuts. Locknuts must be ordered separately for B01998P1.
TypeThread
Minimum QuantityBusbar
3/8-16Lock Nut 3/8-16

MatingForceHigh-[ 131.7 ]5.19

Loose Piece Part Numbers
5010B01998P1350BBS
H1216P9110G73[ 17.0 ]0.67

NOTE: Has not been tested by UL.

See Busbar contact drawing on
website for further detail.

# 3/8 - 16 THD
B[ 2.5 ]
0.10

SB® 350 CONNECTOR TEMPERATURE CHARTS - Temperature rise charts are based on a 25°C

ambient temperature.

SB® 350
Temperature Rise at Constant Current

5040302010100755025050 100 150 200 250 300 350 400 450 500
Amperes Applied
350 MCM
300 MCM
3/0 AWG
2/0 AWG

0 50 100 150 200 250 300 350 400 450 500 550

4/0 AWG
1/0 AWG

350 MCM
3/0 AWG

Amperes Applied
300 MCM
2/0 AWG

4/0 AWG
1/0 AWG

SB®350 InRush Current Curve
Baesd on 40°C Rise

3000
2500
Amperes0SB® 350
Derating vs. Ambient Temperature

125

Ambient Temperature (°C)

60

Temperature Rise
Above Ambient (°C)

Current - Temperature Derating per IEC 60512-5-2 Test 5B

2000
1500
1000
5000020406080

100120 140

Time (Seconds)
1/0 AWG
3/0 AWG
4/0 AWG
300 MCM
2/0 AWG[ 22.3 ]0.88

SB® 350 CONNECTOR SPECIFICATIONSELECTRICALMECHANICAL

Current Rating Amperes

1

Wire-to-Wire (350 mcm)

UL 1977

CSA

500

325

Voltage Rating AC/DCUL 1977

Wire Size Range

AWG

mm²

Wire Contacts with Bushings

1/0 to 350 mcm

53.5 to 185

Max. Wire Insulation Diameter

in.

mm

1.100

27.900600

Dielectric Withstanding Voltage

Operating Temperature ²°F°C

Volts ACStandard-4° to 221°-20° to 105°

Chemical Resistant-40 to 221°-40° to 105°

Mating Cycles No Load by Plating

Silver (Ag)Hot Plug Current Rating Amperes - Wire & Busbar

Wire and Busbar Contacts

10,000250 cycles at 120V DCAvg. Mating / Unmating Force

Lbf.

N2 Pole30133

Min. Contact / Spring Retention Force

Lbf.

N150

667

2,200

Avg. Mated Contact Resistance Milliohms 12 1/2” of 300 mcm Wire

0.050
100A

MATERIALS
HousingStandard Plastic Resin

Polycarbonate

Chemical Resistant Resin

Polycarbonate / PBT blend

Contact Retention Spring

Stainless Steel

Housing Flammability Rating
UL94

V-0Glow Wire

960°C (GWFI) / 800°C GWIT)

Wire & Busbar Contacts

4Base

Copper Alloy

Plating

SilverContact Termination Methods
Crimp ³

Wire Contacts

Hand Solder

Wire Contacts

Wrench / Socket

Busbar Contacts

NOTE 1: See IEC 60664-1 for working voltage.
1 - Based on: 105°C rated or better cable of the largest size. Properly calibrated
Anderson Power™ recommended tooling, and a 25°C ambient temperature.
UL rating not to exceed the maximum operating temperature. CSA rating
below a 30°C temperature rise.
2 - Limited by the thermal properties of the connector plastic housing.
3 - Use Anderson Power™ recommended tooling only. Alternate tools may
adversely affect the performance of our connectors along with UL and CSA
recognition.
4 - Has not been tested by UL.

IEC INFORMATION
Connector
SeriesSB® 350

Creepage /Configurations Clearance per
IEC 60950-1
Unmated5.66 mmMated

5.66 mmPROTECTION
Touch Safety with Wire Contacts
IEC 60529

IP10 unmatedMaterialGroupIIIa

ATTRIBUTESSB® 350

AMP Rating AC/DC

350

Voltage Rating AC/DC (Steady State)

500 V AC/DC (Operational)

Breaking Capacity - AMP Rating / Cycles

100 Amp / 10 cycles

Voltage Rating (Breaking Capacity)

125 VDC

Finger Safety - Mated Only

IEC 60529 - IP20

Wire Size Tested

120 mm²Contact Series Tested

908

Climatic Testing (Cold, Heat & MFG)

IEC 60512 Test -11j, 11i & 11g

Cycle Life

IEC 60512 Test 9a - 5,000 Cycles

Mechanical Strength Impact

IEC 60512-5 @ 29.5 Inches Dropped 8 Times

Temperature Range-20 °C to 105 °C-4 °F to 221 °F

SB® 350 ACCESSORIES
Cable Clamps *			Durable metal cable clamps securely hold cables to prevent accidental strain or pulls
from dislodging wire or contacts from the housing. Cable clamps are recommended
for solder terminated wires.
Cable Size
Min / Max
Min / Max
Description
Inches O.D.
mm O.D.
Part Number
Minimum Quantity 			
10Bolt on for Discrete Conductor
1.00 to 0.35
25.4 to 8.8996G1996G1* Torque value 50 (in - lbs) / 5.6 (Nm)

[ 60.5 ]2.38

NOTE: For assembly of clamp to housing only
The given wire O.D. information is an estimate.
Cable clamps should be evaluated for
performance with the actual wire to be used.

[ 65 ]
2.56[ 76.1 ]3.00[ 10.8 ]0.43[ 1.5 ]
0.06
[ 11.9 ]0.47[ 2.1 ]
0.08

[ 61.9 ]2.44

Handles *Handles are made out of durable PC plastic.
Hardware to attach to connector body included in kits.		
DescriptionPart Numbers
Minimum Quantity
10025
Gray Handle Kit
995G2
Red Handle Kit
995G4
Handle Only, Gray
3-5074P1
Handle Only, Red
3-5074P3
Handle Only, Black
3-5074P5
Hardware Bag
106G7* Torque value 50 (in - lbs) / 5.6 (Nm)NOTE: For assembly of clamp to housing only

Dust Cover

Prevents dust and dirt from entering the mating interfaceof the connector when unmated. NOTE: Not a Hermetic Seal.
Description
Minimum Quantity
Dust Cover with Lanyard Strap, RedPart Numbers
50050113890P3134G3

Slide cover overmating end.

SB® 350 Lockout		
Works with standard lockout - tagout equipment to prevent access tothe mating interface of the connector. Made from durable PC plastic.
Description
Minimum Quantity
Red Lockout - Tagout Kit

Part Number
25
SB350-LOCKOUT

SB® 350 Connector
not included.

Manual Release Bracket - Mounting Side *Works with the Locking Side to ease mating and unmating connectors.
Description

Part Numbers

Minimum Quantity
Bracket and Hardware Kit
Bracket OnlyHardware Bag

66
B00229P1-25106G6

10922G1
Mounting Plate* Torque value 50 (in - lbs) / 5.6 (Nm)NOTE: For assembly of brackets to housing only

HardwareManual Release Bracket - Locking Side with Cable Clamp *Works with the Mounting Side to ease mating and unmating connectors.

Cable Size		
Min / Max
Min / Max
Description

Inches O.D.

Minimum Quantity 		Bracket and Hardware Kit w/ Clamp Kit
0.94 to 0.61mm O.D.

Part Number

23.7 to 15.5

10919

* Torque value 50 (in - lbs) / 5.6 (Nm)NOTE: For assembly of bracket to housing only
The given wire O.D. information is an estimate. Cable clamps shouldbe evaluated for performance with the actual wire to be used.

Manual Release Bracket - Locking Side no Cable Clamp *Works with the Battery side to ease mating and unmating connectors.
Description

Part Number

Minimum Quantity
Bracket and Hardware Kit No Clamp Kit

10919G1* Torque value 50 (in lbs) / 5.6 (N - M)

NOTE: For assembly of bracket to housing only

Silver Plated Reducing Bushings: for use with Contact Part Number 907
Use with contact part number 907-BK to allow a smaller wire to be usedwith the connector. Electrical capability is derated with smaller wire.
Contact Barrel Size

Wire Size

AWG mmAWG

Minimum Quantity
2/0
67.4

1/0mm²

Part Numbers

53.5500
5918-BK

1005918[ 28.4 ]1.12[ 11.1 ]0.44

Wire EntranceDouble Stacked Manual Assist Brackets
The robust frames ensure connector alignment and provide the ability to mount the truck/charger bracket assembly. The brackets include anergonomic handle that reduces the operator effort required for mating and unmating the connectors. This ensures complete engagement ofmated pairs reducing the possibility of shorts or disconnects.
Part Numbers

Safety Agency Ratings

993G5 – SBE®320 & SBX®350 Double Stack Battery Bracket*SBE®320 & SBX®350 – UL 700 amps / CSA 450 amps

994G5 – SBE®320 & SBX®350 Double Stack Truck Charger Bracket*SBE®320 & SBX®350 – UL 700 amps / CSA 450 amps

* Ratings with four connectors assembled using Double Stack Brackets and 4/0 wire
994G5 						993G5[ 6.6 ]
R168

[ 0.27 ]Ø 6.8 (4)

[ 0.62 ]15.8 (2)[ 1.13 ]28.6 (2)[ 9.6 ]
243 MAX (OPEN POSITION)[ 12.2 ]309 MAX (OPEN POSITION)[ 6.6 ]
R 168

[ 7.0 ]
177

[ 9.6 ]
[ 12.2 ]243 MAX (OPEN POSITION)
309 MAX (OPEN POSITION)[ 0.16 ]4.0 MAX PANEL THICKNESSFOR THRU HOLE MOUNTING

SB® Tooling Information
Wire Size

Loose Piece Part
NumberAWG

mm²

Silver Plating

350 mcm

185

910

300 mcm

152910

4/0

107.2

908

3/085

916

2/0

67.4

907

1/0

53.5

917

Loose Piece Contact Crimp Tools
Hand Tool

OR

PneumaticTool+Die+Locator

Number ofCrimpsSB® 350
N/A
1368 Series

Double1387G21303G121304G31

NOTE: See website for the most current information.
All Data Subject to Change Without Notice2024-0103

DS-SB350

REV 8Your Best Connection™

Anderson™ will use reasonable efforts to include accurate and up-to-date content in the data sheet. All product information contained in the data sheet including ordering information,
illustrations, specifications, and dimensions, are believed to be reliable as of the date of publishing, but is subject to change without notice. Anderson™ makes no warranty or representation
as to its accuracy. Content in the data sheet may contain technical inaccuracies, typographical errors and may be changed or updated without notice. Anderson™ may also make
improvements and/or changes to the products and/or to the programs described in the content at any time without notice. Current sales drawings and specifications are available uponrequest.
©2024 Anderson Power Products, Inc. All rights reserved. A®, Anderson Power Products®, SB®, are registered trademarks of Anderson Power Products, Inc. Anderson™, Anderson
Power™, Anderson Power™ logo and Your Best Connection™ are trademarks of Anderson Power Products, Inc.
HEADQUARTERS: Anderson Power Products®, 13 Pratts Junction Road, Sterling, MA 01564-2305 USA T: +1 978-422-3800 F: +1 978-422-0128 • EUROPE: Anderson
Power Products® Ltd., Unit 3, Europa Court, Europa Boulevard, Westbrook, Warrington, Cheshire, WA5 7TN United Kingdom T: +44 (0) 1925 428390 F: +44 (0) 1925520203 • GERMANY: IDEAL® Industries Germany GmbH, Esslinger Strasse 7, D – 70771 Leinfelden-Echterdingen, T: +49 (0) 711 – 997606666 • ASIA / PACIFIC:IDEAL® Anderson Asia Pacific Ltd., Unit 922-928 Topsail Plaza, 11 On Sum Street, Shatin N.T., Hong Kong T: +(852) 2636 0836 F: +(852) 2635 9036 • INDIA: IDEAL®
INDUSTRIES India Private Limited, 229-230, SPAZEDGE, Tower B, Sector 47, Sohna Road, Gurgaon – 122018, Haryana, India T: +(91) 956-0075905 T: +(91) 124-4495101• CHINA: IDEAL® Anderson Technologies (Shenzhen) Ltd., Block A8 Tantou Western Industrial Park, Songgang Baoan District, Shenzhen, PR. China 518105 T: +(86) 7552768 2118 F: +(86) 755 2768 2218 • www.ideal-Industries.in • www.andersonpower.com