PULS does it again:
practical, versatile and reliable likethe SilverLine – yet small likeno other.

Data Sheet

MiniLine ML95.100
with DC 24-28V / 95W• Adjustable output voltage
up to DC 24-28V• Mounted and connected
in record time, no tools required• PULS Overload Design™
(high output overload capability)• World-wide approvals (UL, EN, CSA) for
industry and office/home• 115/230V Auto Select Input• Tiny: WxHxD = 73 x 75 x 103mm• Limited Power Source, NEC class 2 andHazardous Location Class I Div. 2

PULS GmbH, Elektrastr.6, 81925 Munich
Tel. +49(0)899278-0, Fax: +49(0)899278-299
sales@pulspower.com, http://www.pulspower.com

Mini is more.
ML95e100/210408

Technical Data ML95.100

Sprilamng Cps

X Output

X Input
Input voltage

AC 100-120/220-240V (Auto Select), 47...63 Hz(AC 85...132V / AC 184...264V,
DC 220...375V N= + and L= - )Input current<2.0 A (@ AC 100Vin, 95 W Pout)<0.95 A (@ AC 220Vin, 95 W Pout)

External fusing

not required, unit provides internal fuse
(T3A15H, not accessible)

Transient immunity

Transient resistance acc. to VDE 0160 / W2
(750V/ 1.3 ms), over entire load range

Hold-up time(see diagram below)>40 ms @ AC 230V, 24.5V / 3.9 A>20 ms @ AC 196V, 24.5V / 3.9 A>20 ms @ AC 100V, 24.5V / 3.9 A

Output voltage• preset

DC 24-28V (adj. by front panel potentiometer)
24.5V ± 0.5% @ 3.9 A

Voltage regulation

stat. <1% Voutdyn. ±1.5% Vout over all

Ripple/Noise<50mVPP (20 MHz bandw., 50 Ω measurem.)

Overvoltage prot. (OVP) <36V
Output noisesuppression

EMI values below EN 61000-6-3, even when using
long (>2m), unscreened output cables

Rated continuousloading

up to 3.9 A @ 24.5 V / 3.2 A @ 28 V (convectioncooling), depending on built-in orientation,Vin and Tamb
For details see derating diagram below

Overload behaviour

PULS Overload Design™: No switch-off at
overload/short-circuit, instead: up to 1.4 ⋅ Irated.
So you need no oversizing to start awkward
loads.

appr. 500.000 h acc. to Siemensnorm SN 29500(24.5 V / 4.2 A, AC 230 V, Tamb = +40 °C)

ProtectionUnit is protected against (also permanent) shortcircuit, overload and open-circuit.

Prior to shipment, every unit undergoes the following tests in order toisolate any defective units which might suffer an early failure:• Run-in / burn-in (Full load, Tamb = +60°C, on/off cycle)• Functional test (100 %)Derating

depending on built-in orientation;
see diagram below

Parallel operation

possible, no active load sharing

Power back immunity

35V

X Construction, Mechanics, Installation

Operating indicator

Green LED

X Efficiency, Reliability
Efficiency

typ. 90%(AC 230 V, 24.5 V / 3.9 A)(see also diagram below)
typ. 10.5 W (AC 230V, 24.5 V / 3.9 A)

LossesMTBF (Reliability)

Robust plastic housing (US Patent No. D442, 923S), fine ventilation gridon three housing sides to keep out small parts (e.g. screws), IP20

X Environmental Data, EMC, Safety
Ambient temperature range (measured 25 mm below unit)• storage/transport-25°C ... +85°C• operation-10°C ... +70°C (for derating see diagram below)

Dimensions and weight• WxHxD
73 mm x 75 mm x 103 mm + DIN rail
(2.87in x 2.95in x 4.06in + DIN rail)
Depth incl. terminals: 98 mm (3,85in) + DIN rail
• Weight360 g
Mounting orientationor,(cf. ’Output’)

Ventilation/Cooling
Normal convection, no fan required• Free space f. cooling recom'd.: 25 mm (1in) on sides with ventilation
grid
Easy snap-on mounting onto the DIN-rail (TS35/7,5 or TS35/15).
Unit sits safely and firmly on the rail; no tools required even to remove
Connection

by Spring Clamp terminals; uniformly firm hold,vibration-resistant and maintenance-free:2 terminals per output

Connector size range• flexible cable• solid cable• Wire strip length

Humiditymax. 95% (without condensation)

Electromagneticemissions (EME)

EN 61000-6-3 (includes EN 61000-6-4)
Class B (EN 55011, EN 55032) incl. output
noise suppression
EN 61000-3-2 (PFC)Electromagnetic
immunity (EMI)EN 61000-6-2 (includes EN 61000-6-1)

Safety:Prot. class/degree:

SELV (IEC/UL 60950-1), PELV (EN 50178)
Class I (EC/UL 60950-1) / IP20 (EN 60529)

The PSU complies with all major safety approvals forEU (EN IEC 61010-2-201), USA (UL 60950-1: E137006,UL508 LISTED: E198865), Canada (CAN/CSA-C22.2 No 60950-1 [CUR],
CAN/CSA-C22.2 No. 14 [CUL]), CB Scheme (IEC 60950-1, IEC 61010-2-201),
Hazardous Location Class I Div 2, NEC Class

0.3-2.5mm2 (28-12 AWG)
0.3-4mm2 (28-12 AWG)
Ferrules admissible
6mm (0.24in) recommended

Design details – for your advantage:• All terminals are easy to reach as mounted on the front panel.
• Input and output are strictly apart from each other (input below, output above) and so cannot be mixed up.
• Mounting and connection do not require any screwdriver→ Easy, quick, durable and reliable installation.

X Diagrams

100913025

10Pout [W]

Efficiency [%]Output voltage Vout [V]15888786115 V ACin
230 V ACin

85584083A

12070b60
50

Mounting

4085-132 V ACin A-a A-b A-b185-264 V ACin A-a A-b A-b220-375 V DCin A-a A-b A-b

30
20123

Output current Iout [A]

45611,4

1,8 2,2 2,633,4
Output current Iout [A]3,84,20-10100
80
60402010095W, typ.
Pout=100W,typ.
95W, min.
Pout=100W,min.
Pout=50W, typ.
Pout=50W, min.

140a808920160909024-28V

Hold-up time with ACin
(at Vout = 24.5V, typ. + min.)Deratingof output power

Efficiency(@ Vout = 24.5V, typ.)Hold-up time [ms]Output characteristic Vout/Iout

00102030

4050

Tamb [°C]

60

7080

120
160
200
240
Input voltage VACin [V]280

Product information (ML95.100), Rev.: 08.04.2021 Unless otherwise stated, specifications are valid for AC 230V input voltage, +25°C ambient temperature, and 5 min. run-in time. They
are subject to change without prior notice.
PULS GmbH, Elektrastr.6 15, D-81925 München X Tel: +49 (0)89 9278-0 Fax: +49 (0)89 9278-299, E-Mail: sales@pulspower.com X www.pulspower.com