MiniLineDataSheet

MiniLine ML100.105

with DC 48-56V / 100W

• Mounted and connected
within seconds, no tools required• Adjustable output voltage
up to DC 56V• World-wide approvals (UL, EN, CSA,CBScheme) for industry and office/home• 115/230V Auto Select Input• Tiny: WxHxD = 73 x 75 x 103mm• PULS Overload Design(high output overload capability)• Selectable single/parallel operation
(jumper)

PULS GmbH, Elektrastr. 6, 81925 MunichTel. +49.(0)89.9278-0, info@pulspower.com,
http://www.pulspower.com
ML100e105/240202Technical Data ML100.105
X Input

X Output

Input voltage

AC 100-120/220-240V (Auto Select), 50...60 Hz
(AC 85...132V / AC 184...264V,
DC 220...375V, N= + and L= - )Input current<2.1A (@ AC 100Vin, 100W Pout)<1A (@ AC 220Vin, 100W Pout)

External fusing

not required, unit provides internal fuse
(T3A15H, not accessible)

Overvoltage prot. (OVP) <60V

Transient immunity

Transient resistance acc. to VDE 0160 / W2
(750V/ 1.3 ms), over entire load range

Rated continuousloading

Hold-up time(see diagram below)>40 ms @ AC 230V, 48V / 2.1A
>20 ms @ AC 196V, 48V / 2.1A
>20 ms @ AC 100V, 48V / 2.1A

up to 2.1A @ 48V / 1.8A @ 56V (convection cooling), depending on built-in orientation,
Vin and Tamb
For details see derating diagram below

Overload behaviour

typ. 91%(AC 230V, 48V / 2.1A)(see also diagram below)
typ. 10W(AC 230V, 48V / 2.1A)

PULS Overload Design: No switch-off at
overload/short-circuit, instead: up to 1.9 ⋅ Irated.
So you need no oversizing to start awkward
loads.

Protection

Unit is protected against (also permanent) shortcircuit, overload and open-circuit.

appr. 500.000 h acc. to Siemensnorm SN 29500
48V / 2.1A, AC 230V, Tamb = +40 °C)

Derating

depending on built-in orientation;
see diagram below

Parallel operation

yes (selectable by front panel jumper)

Power back immunity

63V

Operating indicator

Green LED

Output voltage• preset

DC 48-56V (adj. by front panel potentiometer)
48V ± 0.5% @ 2.1A

Voltage regulation

stat. <1% Vout (Jumper in pos. 'Single Use')stat. <3% Vout (Jumper in pos. 'Parallel Use'),dyn. ±1.5% Vout over all

Ripple/Noise<50mVPP (20 MHz bandw., 50 Ω measurem.)

X Efficiency, Reliability
Efficiency
LossesMTBF (Reliability)

Prior to shipment, every unit undergoes the following tests in order toisolate any defective units which might suffer an early failure:• Run-in / burn-in (Full load, Tamb = +60°C, on/off cycle)• Functional test (100 %)X Construction, Mechanics, Installation

X Environmental Data, EMC, Safety

Robust plastic housing (US Patent No. D442, 923S), fine ventilation gridon three housing sides to keep out small parts (e.g. screws), IP20

Ambient temperature range (measured 25 mm below unit)• storage/transport -25°C ... +85°C• operation-10°C ... +70°C (for derating see diagram below)

Dimensions and weight• WxHxD
73 mm x 75 mm x 103 mm (+ DIN rail)
Depth incl. terminals: 98 mm (+ DIN rail)• Weight
360 g
Mounting orientationor,(cf. ’Output’)Easy snap-on mounting onto the DIN-rail (TS35/7,5 or TS35/15).
Unit sits safely and firmly on the rail; no tools required even to removeby Spring Clamp terminals; uniformly firm hold,vibration-resistant and maintenance-free:
2 terminals per output

Connector size range• flexible cable• solid cable• Wire strip length

max. 95% (without condensation)

Safe low voltage:
Prot. class/degree:

SELV (IEC/UL 60950-1, VDE0100/T.410), PELV (EN 50178)
Class 1 (IEC/UL 60950-1) / IP20 (EN 60529)

This unit fulfills all major safety approvals
UL 508 LISTED: E198865,
IEC 61010-2-201 Manufacturer´s Declaration,
IEC 60950-1 CB Scheme,
UL 60950-1: E137006 US and Canada,
Marine DNV: TAA00002JT

Ventilation/Cooling
Normal convection, no fan required• Free space f. cooling recom’d.: 25mm on sides with ventilation gridConnection

Humidity

CE: EU Declaration of Conformity (EU DoC): 2014/35/EU (LVD), 2014/30/EU (EMC), 2011/65/EU (RoHS),
WEEE Directive (2012/19/EU), WEEE-Reg.-Nr. DE 55837529

0.3-2.5mm2 (28-12 AWG)
0.3-4mm2 (28-12 AWG)
Ferrules admissible
6mm recommended

Design details – for your advantage:• All terminals are easy to reach as mounted on the front panel.
• Input and output are strictly apart from each other (input below, output above) and so cannot be mixed up.
• Mounting and connection do not require any screwdriver→ Easy, quick, durable and reliable installation.

X Diagrams

93

56

92

120
100

91

48

24

889
88

230 VACin

87

115 VACin86

Vin = AC 115/230V'Single Use'Vin = AC 115/230V'Parallel Use'

16

Output power [W]

32

85

12
3
Output current Iout [A]a60bMounting4085-132 V ACin A-a A-b A-b185-264 V ACin A-a A-b A-b220-375 V DCin A-a A-b A-b

2083080

8404

5Pout=100W, typ.
Pout=100W, min.
Pout=50W, typ.
Pout=50W, min.

1401209040160

A0,50,75

11,25 1,5 1,75
Output current Iout [A]22,10-10

Hold-up time [ms]64

Hold-up time with ACin
(at Vout = 48V, typ. + min.)Deratingof output power

Efficiency(@ Vout = 48V, typ.)

Efficiency [%]Output voltage Vout [V]Output characteristic Vout/Iout(min.)

10080604020001020304050
Ambient temperature [°C]607080120160200240
Input voltage VACin [V]Product information (ML100e105), Rev.: 2. Feb. 2024. Unless otherwise stated, specifications are valid for AC 230V input voltage, +25°C ambient temperature, and 5 min. run-in time.
They are subject to change without prior notice.
PULS GmbH, Elektrastr. 6, D-81925 München X Tel: +49 (0)89 9278-0, E-Mail: info@pulspower.com X www.pulspower.com

280