PBpro ETH

Remote PROFIBUS Interfaces for Use as Master or Slave▪▪Proven solution for device parameterization, controller programming anddata acquisition via Ethernet▪▪Individual protocol settings for each channel▪▪Easy configuration and integration
Measuring
SystemPlant
Supervision

Intelligent
DeviceRemoteDevice
Configuration

Asset
Management

ETHERNET

INDUSTRIALETHERNETPROFIBUS DPSensor

Wide range of applications▪▪ De-facto standard for device parameterization via FDT/DTM▪▪ PROFIBUS connection for PC-based measuringand monitoring systems▪▪ External PROFIBUS interface for PC-based field devices
and embedded computer systems

Remote access to one, two, three or four PROFIBUS
segments via Ethernet▪▪ Access to process data and parameters in connected

devices as PROFIBUS DP Master or Master Class 2(also simultaneously with existing control systems)▪▪ Data exchange with controllers as PROFIBUS DP Slave▪▪ Integration into PROFIBUS FMS systems, or into proprietary
applications via PROFIBUS FDL▪▪ Each channel acting as an individual PROFIBUS PC interface

Input /Output

Drive

Production
Cell

PLC

Practical administration and efficient integration▪▪ Assignment of IP address and configuration withaccompanying “Search and Configure” tool andintegrated web interface▪▪ Commented sample programs for easy use of the PROFIBUS
application programming interface (API)▪▪ Free-of-charge communication DTM for PBpro ETH

supporting parameterization of PROFIBUS devices by FDTtools

PBpro ETH
Technical Data
PBpro ETH
Single Channel

PBpro ETH
Dual Channel

PBpro ETH
Triple Channel

PBpro ETH
Quad Channel

1234



All Channels
All Channels
All Channels
All Channels
Channel 2

All Channels
All Channels
All Channels
All Channels
Channels 2, 3

All Channels
All Channels
All Channels
All Channels
Channels 2, 3, 4

Number of Channels
PROFIBUS Protocol
DP-V0 Master
DP-V1 Master: Acyclic C2 Services
FMS
FDL
DP-V0 SlaveConnector

9-pin D-Sub female, EIA-485 (RS-485), galvanically isolated

Transfer Rates

9.6; 19.2; 45.45; 93.75; 187.5; 500; 1500; 3000; 6000; 12000 Kbit/s

Host Interface
100BASE-TX/10BASE-T, 100 Mbit/s and 10 Mbit/s with automatic detection, RJ45 connector
For device status and configuration
Windows DLL for host computer
Easily portable source code and programming samples for non-Windows computers

EthernetWeb Server
Remote API
TCP/IP Socket Library
MiscellaneousMounting

35 mm DIN Rail

Dimensions (W x H x D in mm)

47 x 131 x 111

110 x 131 x 111

110 x 131 x 111

110 x 131 x  111

Power Supply

24 VDC (±20 %),typically 0.2 A

24 VDC (±20 %),typically 0.3 A

24 VDC (±20 %),typically 0.4 A

24 VDC (±20 %),typically 0.5 A

Temperature Range

0 °C … +55 °C (Operation); -20 °C … +70 °C (Storage); fanless convection cooling

Relative Humidity< 90 %, non-condensing

Protection Class

IP20

Available Drivers

Windows 2000, Windows XP, Windows Vista, Windows 7, Windows 8,
Windows Server 2003 R2, Windows Server 2008

Conformity

FCC

Scope of Delivery
Hardware

PROFIBUS Remote Interface

Software

Windows Drivers, Sample Programs, PROFIdtm

Documentation

User Guide

Order Numbers
PBpro ETH
Single Channel

PBpro ETH
Dual Channel

PBpro ETH
Triple Channel

PBpro ETH
Quad Channel

DEL-NN-012311

DEL-NN-012312

DEL-NN-012313

DEL-NN-012314

Your local Softing contact:

Technical changes reserved © Softing Industrial Automation GmbH, TH_LINK_PB_D_DE_190724_301, July 2019http://industrial.softing.com