smartLink HW-DP

Industry 4.0 connectivity for new and existing PROFIBUS DP networks▪ PLC Independent access to PROFIBUS DP networks▪ Integration without interference with the operation of existing installations▪ Compatible with products of leading device manufacturers
Plant Asset Management

Monitoring& Optimization
HART-IPdataFEED SIS= NOA DiodeOPC UA (NOA)

smartLink HW-DP
PLC
PROFIBUS DP
Remote I/O  
stationField Devices

HART
Field Device

Field Device

Configuration, Parameterization and Plant AssetManagement Using Standard Industry Tools

Key Component for Transition to State-of-the-ArtTechnology▪ Independent of configuration tools▪ Re-use of existing PROFIBUS segments
without requiring modification▪ Centralized and time-saving parameterizationof PROFIBUS and HART field devices directlyfrom the control room using HART IP andHART over PROFIBUS▪ Access to Plant Asset Management applications
for field devices configuration based on FDT / DTM
and EDDL standards (acyclic master)
Direct Connectivity to PROFIBUS Segments▪ Single access point to PROFIBUS DP segmentfrom Industrial Ethernet networks▪ Acts as PROFIBUS DP master class 2▪ Support of one PROFIBUS DP segment▪ Access to cyclic and acyclic data via HART-IPand OPC UAsmartLink HW-DP
Technical Data
Hardware
Interfaces andConnectors
PhysicalProperties

Processor

Altera Cyclone V SoC with dual-core ARM Cortex-A9Status LEDs (Gateway)

PWR, RUN, ERR, BUS

Ethernet

IEEE802.3 10BASE-T/100BASE-TX/1000BASE-T
RESTful API interface for device configuration

PROFIBUS DP-V0 / V1

1 Segment with RS485 Physical Layer, Connector: 9-pin Sub-D socket

Dimensions (H x W x D)

120 mm x 28 mm x 110 mm

WeightApprox. 430g

Power Supply

18 VDC ... 32 VDC; SELV/PELV power supply mandatory
Typical input current: 200 mA, maximum input current: 1 A (allowing for in-rush current at switch-on)

Typical Power Loss

5W

Operating Temperature-40 °C ... +65 °C (see detailed mounting description in user manual)-40 °C ... +85 °C

Storage Temperature
Relative Humidity
Cooling
Mounting
Conformity /Standards

10 % ... 95 %, non-condensing
Convection, no fan
DIN rail 35 mm

Protection Class

IP20

CE

Electromagnetic compatibility (EMC) and Restriction of Hazardous Substances (RoHS)
EN 61000-6-2 Generic standards - Immunity standard for industrial environments
EN 61000-6-4 Generic standards - Emission standard for industrial environments
EN 55032 Electromagnetic compatibility of multimedia equipment - Emission Requirements Class A
EN 55011 Industrial, scientific and medical equipment - Radio-frequency disturbance characteristics –Limits and methods of measurement Class A
EN 50581:2012/EN IEC 63000:2018 RoHS, Assessment to the restriction of hazardous substances

FCC

FCC 47 CFR Part 15B Section 15.109 (Class A)

VCCI

VCCI Voluntary Control Council for Interferences by Information Technology Equipment, April 2015

Scope of Delivery
HardwaresmartLink HW-DP

Documentation

On Website

Order NumbersGEA-YN-026000

smartLink HW-DP, Access to PROFIBUS networks via Ethernet. Supports 1 PROFIBUS DP segment (RS485).

Additional Products and Services
LRL-DY-134501

dataFEED OPC Suite, Version 4.01 and higher, including all supported PLC protocols, support for OPC UA, accessfor any number of dataFEED OPC Tunnel Clients, for simultaneous access to a total of up to 100 OPC UA Servers,
OPC Servers and OPC Tunnel Servers, and many more Functionalities such as Database and File Access, Data
Exchange, Optimizer, Concentrator and Bridge

LRL-DY-14000

dataFEED Secure Integration Server, Version 1.01, single user license for up to 10 OPC UA connections,
including care and support contract for 1 year

LRA-NN-027001

smartPlus PB, Licensing access to one PROFIBUS device for smartLink/smartGate

LRA-MM-027002

smartPlus HT, Licensing access to one HART device for smartLink/smartGate

Your local Softing contact:

Technical changes reserved © Softing Industrial Automation GmbH, smartLink_HW-DP_D_EN_200907_105, September 2020

http://industrial.softing.com