CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

POWER SUPPLY













AC 100-240V Wide-range Input
Width only 39mm
Efficiency up to 95.2%
Excellent Partial Load Efficiency
20% Output Power Reserves (PowerBoost)
Safe HiccupPLUS Overload Mode
Easy Fuse Breaking due to High Overload Peak Current
Active Power Factor Correction (PFC)
Minimal Inrush Current Surge
Full Power Between -25°C and +60°C
DC-OK Relay Contact
3 Year Warranty

PRODUCT DESCRIPTIONSHORT-FORM DATAThe DIMENSION CP-Series units are high-end power
supplies in a medium price range without compromisingquality, reliability and performance. The CP-Series ispart of the DIMENSION power supply family. The mostoutstanding features of CP10 series are the highefficiency, advanced inrush current limitation, active PFC
and the wide operational temperature range.

Output voltage
Adjustment range
Output current

The CP-Series includes all the essential basic functions.
The devices also offer PowerBoost: Power reserves of
20%, which may even be used continuously attemperatures up to +45°C. Additionally, the CP10 candeliver three times the nominal output current for atleast 12ms which helps to trip fuses on faulty output
branches.
High immunity to transients and power surges as well as
low electromagnetic emission, a DC-OK relay contact
and a large international approval package for a variety
of applications makes this unit suitable for nearly every
situation.

ORDER NUMBERS

ZM10.WALL
ZM12.SIDE

Input voltage AC
Mains frequency
Input current AC
Power factor
Input voltage DC
Input current DC
Input inrush current
Efficiency
LossesHold-up time
Temperature range
Size (w x h x d)
WeightMAIN APPROVALSPower Supply CP10.241
CP10.241-C1 Conformal coating
CP10.241-S1 Spring-clamp terminals
CP10.241-S2 Push-in terminals
CP10.242
Extended DC-Input range
Accessory

PowerBoost

DC 24V
Nominal24 – 28V
Factory setting 24.1V
10.0-8.6A
Up to +60°C ambient
7.5-6.5A
At +70°C ambient
Derate linearly between +60°C and +70°C
12.0A
Up to +45°C ambient
Linear decrease to nominal power
between +45°C and +60°C
AC 100-240V-15%/ +10%
50-60Hz±6%
2.15 / 1.13A
At 120 / 230Vac
0.99 / 0.97
At 120 / 230Vac
DC 110-150V ±20% For CP10.241 (-xx)
DC 110-300V ±20% CP10.242
2.35A
At 110Vdc
2.35 / 0.84A
At 110 / 300Vdc
6 / 9A pk
At 40°C 120 / 230Vac
93.6 / 95.2%
At 120 / 230Vac
16.4 / 12.1W
At 120 / 230Vac
37 / 37ms
At 120 / 230Vac-25°C to +70°C
39x124x117mm
Without DIN rail
600g

For details and the complete approval list, see chapter 20.

UL 61010-2-201

UL 60950-1

ATEX

IECEx

Class I Div 2

MarineWall/panel mount bracket
Side mount bracket

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

1/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

INDEX
Page
1. Intended Use .......................................................3
2. Installation Instructions ......................................3
3. AC-Input...............................................................5
4. DC-Input...............................................................6
5. Input Inrush Current ...........................................7
6. Output .................................................................8
7. Hold-up Time .......................................................9
8. DC-OK Relay Contact ........................................10
9. Efficiency and Power Losses..............................11
10. Lifetime Expectancy ..........................................12
11. MTBF ..................................................................12
12. Terminals and Wiring ........................................13
13. Functional Diagram...........................................14
14. Front Side and User Elements ...........................15
15. EMC ....................................................................16
16. Environment ......................................................17
17. Protection Features ...........................................18
18. Safety Features ..................................................18
19. Dielectric Strength ............................................19
20. Approved, Fulfilled or Tested Standards .........20
21. Regulatory Product Compliance .......................22Page
22. Physical Dimensions and Weight ..................... 23
23. Accessories ........................................................ 24
23.1. ZM10.WALL - Wall/Panel Mount Bracket 24
23.2. ZM12.SIDE - Side Mounting Bracket ........ 25
23.3. YR20.242 - Redundancy Module .............. 26
23.4. YR20.246 - Redundancy Module with
Automated Load Sharing .................................... 26
24. Application Notes ............................................. 27
24.1. Peak Current Capability ........................... 27
24.2. Back-feeding Loads .................................. 28
24.3. External Input Protection ......................... 28
24.4. Output Circuit Breakers............................ 28
24.5. Series Operation ....................................... 29
24.6. Parallel Use to Increase Output Power .... 29
24.7. Parallel Use for Redundancy .................... 30
24.8. Inductive and Capacitive Loads................ 31
24.9. Charging of Batteries ............................... 31
24.10. Operation on Two Phases ........................ 32
24.11. Use in a Tightly Sealed Enclosure ............ 32
24.12. Mounting Orientations ............................ 33

The information given in this document is correct to the best of our knowledge and experience at the time of
publication. If not expressly agreed otherwise, this information does not represent a warranty in the legal sense of theword. As the state of our knowledge and experience is constantly changing, the information in this data sheet issubject to revision. We therefore kindly ask you to always use the latest issue of this document (available underwww.pulspower.com).
No part of this document may be reproduced or utilized in any form without our prior permission in writing.

TERMINOLOGY AND ABREVIATIONSPE andsymbolPE is the abbreviation for Protective Earth and has the same meaning as the symbol.

Earth, Ground

This document uses the term “earth” which is the same as the U.S. term “ground”.

t.b.d.

To be defined, value or description will follow later.

AC 230V

A figure displayed with the AC or DC before the value represents a nominal voltage withstandard tolerances (usually ±15%) included.
E.g.: DC 12V describes a 12V battery disregarding whether it is full (13.7V) or flat (10V)

230VacA figure with the unit (Vac) at the end is a momentary figure without any additional
tolerances included.

50Hz vs. 60Hz

As long as not otherwise stated, AC 100V and AC 230V parameters are valid at 50Hz mains
frequency. AC 120V parameters are valid for 60Hz mains frequency.

may

A key word indicating flexibility of choice with no implied preference.

shall

A key word indicating a mandatory requirement.

shouldA key word indicating flexibility of choice with a strongly preferred implementation.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

2/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series

24V, 10A, 240W, SINGLE PHASE INPUT

1. INTENDED USEThis device is designed for installation in an enclosure and is intended for commercial use, such as in industrial control,
process control, monitoring and measurement equipment or the like.
Do not use this device in equipment, where malfunctioning may cause severe personal injury or threaten human life
without additional appropriate safety devices, that are suited for the application.
If this device is used in a manner outside of its specification, the protection provided by the device may be impaired.

2. INSTALLATION INSTRUCTIONSWARNING

Risk of electrical shock, fire, personal injury or death.

- Turn power off before working on the device and protect against inadvertent re-powering.
- Do not open, modify or repair the device.
- Use caution to prevent any foreign objects from entering into the housing.
- Do not use in wet locations or in areas where moisture or condensation can be expected.
- Do not touch during power-on, and immediately after power-off. Hot surface may cause burns.
Obey the following installation instructions:This device may only be installed and put into operation by qualified personnel.
This device does not contain serviceable parts. The tripping of an internal fuse is caused by an internal defect.
If damage or malfunction should occur during installation or operation, immediately turn power off and send unit to
the factory for inspection.
Install device in an enclosure providing protection against electrical, mechanical and fire hazards.
Install the device onto a DIN rail according to EN 60715 with the input terminals on the bottom of the device. Other
mounting orientations require a reduction in output current.
Make sure that the wiring is correct by following all local and national codes. Use appropriate copper cables that aredesigned for a minimum operating temperature of 60°C for ambient temperatures up to +45°C, 75°C for ambient
temperatures up to +60°C and 90°C for ambient temperatures up to +70°C.
Ensure that all strands of a stranded wire enter the terminal connection. Use ferrules for wires on the input terminals.
Unused screw terminals should be securely tightened.
The device is designed for pollution degree 2 areas in controlled environments. No condensation or frost is allowed.
The enclosure of the device provides a degree of protection of IP20. The enclosure does not provide protection against
spilled liquids.
The isolation of the device is designed to withstand impulse voltages of overvoltage category III according to IEC
60664-1.
The device is designed as “Class of Protection I” equipment according to IEC 61140. Do not use without a proper PE(Protective Earth) connection.
The device is suitable to be supplied from TN, TT or IT mains networks. The continuous voltage between the input
terminal and the PE potential must not exceed 300Vac.
The input can also be powered from batteries or similar DC sources. The continuous voltage between the supply
voltage and the PE/ground potential must not exceed 375Vdc.
A disconnecting means shall be provided for the input of the device.
The device is designed for convection cooling and does not require an external fan. Do not obstruct airflow and do notcover ventilation grid!

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

3/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series

24V, 10A, 240W, SINGLE PHASE INPUT

The device is designed for altitudes up to 5000m. Above 2000m a reduction in output current and over voltage
category is required.
Keep the following minimum installation clearances: 40mm on top, 20mm on the bottom, 5mm left and right side.
Increase the 5mm to 15mm in case the adjacent device is a heat source. When the device is permanently loaded withless than 50%, the 5mm can be reduced to zero.
The device is designed, tested and approved for branch circuits up to 32A (IEC) and 30A (UL) without additional
protection device. If an external fuse is utilized, do not use circuit breakers smaller than 6A B- or C-Characteristic toavoid a nuisance tripping of the circuit breaker.
The maximum surrounding air temperature is +70°C. The operational temperature is the same as the ambient or
surrounding air temperature and is defined 2cm below the device.
The device is designed to operate in areas between 5% and 95% relative humidity.
Installation Instructions for Hazardous Location Areas
The device is suitable for use in Class I Division 2 Groups A, B, C, D locations and for use in Group II Category 3 (Zone 2)
environments.
Classification: ATEX: EPS 15 ATEX 1 101 X, II 3G Ex ec nC IIC T4 Gc / IECEx EPS 15.0079X
WARNING EXPLOSION HAZARDS!
Use only in standard vertical mounting orientation with the input terminals on bottom of the unit. Substitution ofcomponents may impair suitability for this environment.
Do not disconnect the device or operate the voltage adjustment unless power has been switched off or the area isknown to be non-hazardous.
A suitable enclosure must be provided for the end product, which has a minimum protection of IP54 and fulfils therequirements of the EN 60079-0.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

4/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

3. AC-INPUT
AC input
AC input range

Nom.

External input protection

AC 100-240V
Suitable for TN-, TT- and IT mains networks
85-264Vac
264-300Vac
For maximal 500ms
Max.
300VacContinuous, according to IEC 62477-1
Nom.
50–60Hz
±6%
Typ.
80Vac
Steady-state value, see Fig. 3-1
Typ.
70Vac
Steady-state value, see Fig. 3-1
Typ.
55Vac
Dynamic value for maximal 250ms
See recommendations in chapter 24.3.

Input current
Power factor*)
Crest factor**)Start-up delay
Rise time

Typ.
Typ.
Typ.
Typ.
Typ.

AC 100V
2.60A
0.99
1.5
300ms
30ms

AC 120V
2.15A
0.99
1.5
290ms
30ms

AC 230V
1.13A
0.97
1.65
240ms
30ms

Typ.

75ms

75ms

75ms

Allowed voltage L or N to earth
Input frequency
Turn-on voltage
Shut-down voltage

Turn-on overshootExternal input protection

Max.
200mV
200mV
200mV
See recommendations in chapter 24.3.

At 24V, 10A, see Fig. 3-3
At 24V, 10A, see Fig. 3-4
At 24V, 10A
See Fig. 3-2
At 24V, 10A const. current load,
0mF load capacitance, see Fig. 3-2
at 24V, 10A const. current load,
10mF load capacitance,, see Fig. 3-2
See Fig. 3-2*) The power factor is the ratio of the true (or real) power to the apparent power in an AC circuit.
**) The crest factor is the mathematical ratio of the peak value to RMS value of the input current waveform.

Rated
input range

max.
500ms

Turn-onShut-down

POUT

Fig. 3-2 Turn-on behavior, definitions

Input
Voltage

OutputVoltage

VIN
85V

- 5%
Start-up
delay

Rise
Time

OvershootFig. 3-1 Input voltage range

264V 300Vac

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

5/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

Fig. 3-3 Input current vs. output current at
24V output voltage

Fig. 3-4 Power factor vs. output current at
24V output voltage

Input Current, typ.

Power Factor, typ.

3A

a

2.5

b

1.0

2.0
1.5

0.85

1.0

1

2

3

4

5

6

7

8

(a) 100Vac,(b) 120Vac,(c) 230Vac

(c)

0.8

Output Current

0

(b)

0.9

c

0.5

(a)

0.95

a) 100Vacb) 120Vacc) 230Vac

0.75

9 10 11 12A

Output Current

1

2

3

4

5

6

7

8

9 10 11 12A

4. DC-INPUT
DC inputNom.

DC 110-150V

Nom.

DC 110-300V

DC input range

88-180Vdc

DC input current
Allowed Voltage L/N to Earth
Turn-on voltage
Shut-down voltage

Typ.
Typ.
Max.
Typ.
Typ.
Typ.

88-360Vdc
2.35A
0.84A
375Vdc
80Vdc
70Vdc
55Vdc

Fig. 4-1 Wiring for DC Input

Battery+

Power Supply
AC
L
N
PE

-

+
-

Load

±20%
For CP10.241, CP10.241-C1, CP10.241-S1, CP10.241S2±20%
For CP10.242
For CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2
For CP10.242
At 110Vdc, at 24V, 10A
At 300Vdc, at 24V, 10A
Continuous, according to IEC 62477-1
Steady state value
Steady state value
Dynamic value for maximal 250ms

Instructions for DC use:a) Use a battery or a similar DC source. A supply from theintermediate DC-bus of a frequency converter is notrecommended and can cause a malfunction or damage
the unit.
b) Connect +pole to L and –pole to N.
c) Connect the PE terminal to an earth wire or to themachine ground.

DC

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

6/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

5. INPUT INRUSH CURRENT
An active inrush limitation circuit (NTCs, which are bypassed by a relay contact) limits the input inrush current afterturn-on of the input voltage.
The charging current into EMI suppression capacitors is disregarded in the first microseconds after switch-on.

Inrush current

Inrush energy

Max.
Typ.
Typ.
Max.

Fig. 5-1 Typical turn-on behaviour at nominal
load, 120Vac input and 25°C ambient

AC 100V
11Apeak
9Apeak9Apeak
0.1A²sAC 120V
7Apeak
6Apeak
6Apeak
0.1A²s

AC 230V
11Apeak
6Apeak9Apeak
0.4A²sAt 40°C, cold start
At 25°C, cold start
At 40°C, cold start
At 40°C, cold startFig. 5-2 Typical turn-on behaviour at nominal
load, 230Vac input and 25°C ambientJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

7/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

6. OUTPUT
Output voltage
Adjustment range

Nom.

Guaranteed value
This is the maximum output voltage which can occur
at the clockwise end position of the potentiometer
due to tolerances. It is not a guaranteed value which
can be achieved.
Typ.
24.1V
±0.2%, at full load and cold unit
Max.
10mV
Between 85 and 300Vac
Max.
50mV
Between 0 and 12A, static value, see Fig. 6-1
Max.
50mVpp
Bandwidth 20Hz to 20MHz, 50Ohm
At 24V and up to +60°C ambient temperature, see
Nom.
10A
Fig. 6-1
Nom.
7.5A
At 24V and +70°C ambient temperature, see Fig. 16-1
Nom.
8.6A
At 28V up to +60°C ambient temperature, see Fig. 6-1
Nom.
6.45A
At 28V and +70°C ambient temperature, see Fig. 16-1
Derate linearly between +60°C and +70°C, see chapter 16
At 24V and up to +45°C ambient temperature, see
Nom.
12A
Fig. 16-1
At 28V and up to +45°C ambient temperature, see
Nom.
10.3A
Fig. 16-1
PowerBoost decreases linearly to nominal power between +45°C and +60°C, seechapter 16
For minimal 12ms once every five seconds, see Fig. 6-2.
Typ.
30A
The output voltage stays above 20V. See chapter 24.1
for more peak current measurements. For AC 100V
mains, the pulse length is shorter than 12ms.
Continuous current Output voltage above 13Vdc, see Fig. 6-1
HiccupPLUS mode2)
Output voltage below 13Vdc, see Fig. 6-1
Min.
12.5A3)
Load impedance <45mOhm, see Fig. 6-3
Max.
15.5A3)
Load impedance <45mOhm, see Fig. 6-3
Average (R.M.S.) current, load impedance 50mOhm, seeMax.
5A
Fig. 6-3
Min.
28A
Up to 12ms, load impedance <45mOhm, see Fig. 6-2
Typ.
30.5A
Up to 12ms, load impedance <45mOhm, see Fig. 6-2
Typ.
4 400µF
Included inside the power supply
Max.

Factory settings
Line regulation
Load regulation
Ripple and noise voltage
Output current

PowerBoost1)

Fuse breaking current

Overload behaviour
Short-circuit current

Output capacitance

24V
24-28V
30.0V

1) PowerBoost
This power/ current is continuously allowed up to an ambient temperature of +45°C.
Above +45°C, do not use this power or current longer than a duty cycle of 10% and/or not longer than 1 minute every 10 minutes.
2) HiccupPLUS ModeAt heavy overloads (when output voltage falls below 13V), the power supply delivers continuous output current for 2s. After this, theoutput is switched off for approx. 18s before a new start attempt is automatically performed. This cycle is repeated as long as the overload
exists. If the overload has been cleared, the device will operate normally. See Fig. 6-3
3) Discharge current of output capacitors is not included.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

8/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

Fig. 6-1 Output voltage vs. output current,
typ.

Output Voltage

28V

Continuous
current

24
Factory
setting

16

Output Voltage (dynamic behavior, < 12ms)

Adjustment
Range

28V
20

Fig. 6-2 Dynamic output current capability,
typ.

24
Adjustment
Range

20
16

12

12

8

8

HiccupPLUS
mode

4
0

4
0

Output Current

2.5

0

5

7.5 10 12.5 15 17.5 20A

Output Current

0

5 10 15 20 25 30 35 40 45 50A

Fig. 6-3 Short-circuit on output, HiccupPLUS mode, typ.
OutputCurrent

Normaloperation

Normaloperation

Short -circuit

14A

t

0
2s

2s

18s

2s

18s

18s

7. HOLD-UP TIME
Hold-up TimeAC 100V
73ms
55ms
37ms
28ms

Typ.
Min.
Typ.
Min.

Fig. 7-1 Hold-up time vs. input voltage

Hold-up Time

80ms
70
60
50
40
30
20
10
0

a) 24V 5A typ.
b) 24V 5A min.

AC 120V
73ms
55ms
37ms
28ms

c) 24V 10A typ.
d) 24V 10A min.

acdZero Transition
Input
Voltage

155

190

- 5%

OutputVoltage
Hold-up Time

Input Voltage

120

At 24V, 5A, see Fig. 7-1
At 24V, 5A, see Fig. 7-1
At 24V, 10A, see Fig. 7-1
At 24V, 10A, see Fig. 7-1

Fig. 7-2 Shut-down ehaviour, definitionsb90

AC 230V
73ms
55ms
37ms
28ms

230VacJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

9/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

8. DC-OK RELAY CONTACT
This feature monitors the output voltage on the output terminals of a running power supply.
Contact closes
Contact opens

As soon as the output voltage reaches typ. 90% of the adjusted output voltage level.
As soon as the output voltage dips more than 10% below the adjusted output voltage.
Short dips will be extended to a signal length of 100ms. Dips shorter than 1ms will be ignored.
1V
Maximal 60Vdc 0.3A, 30Vdc 1A, 30Vac 0.5A, resistive load
Minimal permissible load: 1mA at 5Vdc
See dielectric strength table in chapter 18.

Switching hysteresis
Contact ratings
Isolation voltage

Fig. 8-1 DC-OK relay contact behavior

VOUT = VADJ
10%

<
1ms

open

closed>1ms

0.9* VADJ

100ms

open

closedJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

10/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

9. EFFICIENCY AND POWER LOSSES
Efficiency
Average efficiency*)
Power losses

*)

Typ.
Typ.
Typ.

AC 100V
92.9%
92.5%
92.5%

AC 120V
93.6%
93.4%
93.0%

AC 230V
95.2%
95.1%
94.3%

Typ.
Typ.
Typ.
Typ.

2.5W
9.8W
18.3W
23.4W

2.1W
8.9W
16.4W
21.7W

1.8W
7.1W
12.1W
14.8W

At 24V, 10A
At 24V, 12A (PowerBoost)
25% at 2.5A, 25% at 5A,
25% at 7.5A. 25% at 10A
At 24V, 0A
At 24V, 5A
At 24V, 10A
At 24V, 12A (PowerBoost)

The average efficiency is an assumption for a typical application where the power supply is loaded with 25% of the nominal load for 25%of the time, 50% of the nominal load for another 25% of the time, 75% of the nominal load for another 25% of the time and with 100%of the nominal load for the rest of the time.

Fig. 9-1 Efficiency vs. output current at 24V,
typ.

Fig. 9-2 Losses vs. output current at 24V, typ.

Efficiency

Power Losses

96%

30W
(c)

95
94

(b)

93
(a) 100Vac(b) 120Vac(c) 230Vac

92
91

(a)

Output Current

90
2

3

4

5

6

7

8

(a) 100Vac(b) 120Vac(c) 230Vac

25

(a)
(b)

20
15

(c)

10
5

Output Current0

0 1 2 3 4 5 6 7 8 9 10 11 12A

9 10 11 12A

Fig. 9-3 Efficiency vs. input voltage at 24V,
10A, typ.

Fig. 9-4 Losses vs. input voltage at 24V, 10A,
typ.

Efficiency

Power Losses

96%

22W

95

20

94

18

93

16

92

14

91

12

Input Voltage

90
100 120

180

Input Voltage

10

230

264Vac100 120180

230

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

264Vac11/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

10. LIFETIME EXPECTANCYThe Lifetime expectancy shown in the table indicates the minimum operating hours (service life) and is determined by
the lifetime expectancy of the built-in electrolytic capacitors. Lifetime expectancy is specified in operational hours andis calculated according to the capacitor’s manufacturer specification. The manufacturer of the electrolytic capacitors
only guarantees a maximum life of up to 15 years (131 400h). Any number exceeding this value is a calculated
theoretical lifetime which can be used to compare devices.

Lifetime expectancy

AC 100V
128 000h
61 000h47 000h
363 000h
173 000h
132 000h

AC 120V
141 000h
75 000h59 000h
399 000h
211 000h
166 000h

AC 230V
176 000h
120 000h
101 000h
499 000h
338 000h
286 000h

At 24V, 5A and 40°C
At 24V, 10A and 40°C
At 24V, 12A and 40°C
At 24V, 5A and 25°C
At 24V, 10A and 25°C
At 24V, 12A and 25°C

11. MTBF
MTBF stands for Mean Time Between Failure, which is calculated according to statistical device failures, and indicatesreliability of a device. It is the statistical representation of the likelihood of a unit to fail and does not necessarily
represent the life of a product.
The MTBF figure is a statistical representation of the likelihood of a device to fail. A MTBF figure of e.g. 1 000 000h
means that statistically one unit will fail every 100 hours if 10 000 units are installed in the field. However, it can not
be determined if the failed unit has been running for 50 000h or only for 100h.
For these types of units the MTTF (Mean Time To Failure) value is the same value as the MTBF value.

MTBF SN 29500, IEC 61709
MTBF MIL HDBK 217F

AC 100V
550 000h
1 003 000h
188 000h

AC 120V
560 000h
1 017 000h
188 000h

AC 230V
661 000h
1 176 000h
213 000h

252 000h

252 000h

290 000h

40 000h40 000h47 000h51 000h51 000h61 000h

At 24V, 10A and 40°C
At 24V, 10A and 25°C
At 24V, 10A and 40°C;
Ground Benign GB40
At 24V, 10A and 25°C;
Ground Benign GB25
At 24V, 10A and 40°C;
Ground Fixed GF40
At 24V, 10A and 25°C;
Ground Fixed GF25

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

12/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

12. TERMINALS AND WIRING
The terminals are IP20 Finger safe constructed and suitable for field- and factory wiring.
CP10.241, CP10.241-C1, CP10.242
Type
Solid wire
Stranded wire
American Wire Gauge
Max. wire diameter (including ferrules)
Recommended tightening torque
Wire stripping length
Screwdriver

Input
Screw terminal
Max. 6mm2Max. 4mm2
AWG 20-10
2.8mm
Max. 1Nm
7mm
3.5mm slotted or crosshead No 2

OutputScrew terminal
Max. 6mm2Max. 4mm2
AWG 20-10
2.8mm
Max. 1Nm
7mm
3.5mm slotted or crosshead No 2

DC-OK-Signal
Push-in terminal
Max. 1.5mm2Max. 1.5mm2
AWG 24-16
1.6mm
7mm
3mm slotted to open
the spring

CP10.241-S1
Type

Input
Quick-connect springclamp terminal
Max. 6mm2Max. 4mm2
AWG 20-10
2.8mm
10mm
-

OutputQuick-connect springclamp terminal
Max. 6mm2Max. 4mm2
AWG 20-10
2.8mm
10mm
-

DC-OK-Signal
Push-in terminal

Input
Push-in terminal
Max. 2.5mm2Max. 2.5mm2Max. 1.5mm2
AWG 24-12
2.3mm
10mm
3.0mm slotted to open
the spring

OutputPush-in terminal
Max. 2.5mm2Max. 2.5mm2Max. 1.5mm2
AWG 24-12
2.3mm
10mm
3.0mm slotted to open
the spring

DC-OK-Signal
Push-in terminal
Max. 1.5mm2Max. 1.5mm2Max. 1.5mm2
AWG 24-16
1.6mm
7mm
3mm slotted to open
the spring

Solid wire
Stranded wire
American Wire Gauge
Max. wire diameter (including ferrules)
Wire stripping length
Screwdriver

CP10.241-S2
Type
Solid wire
Stranded wire
Stranded wire with ferrules
American Wire Gauge
Max. wire diameter (including ferrules)
Wire stripping length
ScrewdriverMax. 1.5mm2Max. 1.5mm2
AWG 24-16
1.6mm
7mm
3mm slotted to open
the spring

Instructions for wiring:a) Use appropriate copper cables that are designed for minimum operating temperatures of:
60°C for ambient up to 45°C and
75°C for ambient up to 60°C and
90°C for ambient up to 70°C minimum.
b) Follow national installation codes and installation regulations!
c) Ensure that all strands of a stranded wire enter the terminal connection!
d) Unused terminal compartments should be securely tightened.
e) Ferrules are allowed.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

13/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

Daisy chaining:
Daisy chaining is allowed for CP10.241, CP10.241-C1, CP10.241-S1 and CP10.242.
Daisy chaining is not allowed for CP10.241-S2
Daisy chaining (jumping from one power supply output to the next) is allowed as long as the average output current
through one terminal pin does not exceed 25A. If the current is higher, use a separate distribution terminal block asshown in Fig. 12-2.

Fig. 12-1 Daisy chaining of outputs

Power
SupplyPower
Supply

+ + -

+ + -

-

Output-OutputFig. 12-2 Using distribution terminals

Load
+

-

Power
SupplyPower
Supply

+ + -

+ + -

-

Distribution
Terminals
Load-

OutputOutput+-max 25A!
continuous

13. FUNCTIONAL DIAGRAM
Fig. 13-1 Functional diagram

L
N

Input Fuse
Input Filter
Input Rectifier
Inrush Current Limiter

PFC
ConverterPower
Converter

OutputFilterOutputVoltage
Regulator
Temperature
Shutdown

OutputPower
Manager

OutputOverVoltage
Protection

OutputVoltage
Monitor

+
+
VOUT
DC-ok
LED

DC-ok
Relay

DC-ok
Contact

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

14/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

14. FRONT SIDE AND USER ELEMENTS
Fig. 14-1
Front side CP10.241

A

Fig. 14-2
Front side CP10.241-C1

Fig. 14-3
Front side CP10.241-S1

Fig. 14-4
Front side CP10.241-S2

Fig. 14-5
Front side CP10.242

Input Terminals
CP10.241, CP10.241-C1, CP10.242: Screw terminals
CP10.241-S1: Spring-clamp terminals
CP10.241-S2: Push-in terminals
N, LLine input

PE (Protective Earth) input
Output Terminals(two identical + poles and three identical - poles)
CP10.241, CP10.241-C1, CP10.242: Screw terminals
CP10.241-S1: Spring-clamp terminals
CP10.241-S2: Push-in terminals+
Positive output–
Negative (return) output
C Output voltage potentiometer
Open the flap to adjust the output voltage. Factory set: 24.1V
D DC-OK LED (green)
On, when the output voltage is in range and the DC-OK contact is closed.
B

E

DC-OK Relay Contact (push-in terminals)
Monitors the output voltage of the running power supply. See chapter 8 for details.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

15/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series

24V, 10A, 240W, SINGLE PHASE INPUT

15. EMCThe power supply is suitable for applications in industrial environment as well as in residential, commercial and lightindustry environments.
EMC Immunity
Electrostatic discharge
Electromagnetic RF field
Fast transients (Burst)

Surge voltage on input
Surge voltage on output
Surge voltage on Signals
Conducted disturbance
Mains voltage dips

Voltage interruptions
Voltage sags

Powerful transients

According to generic standards: EN 61000-6-1 and EN 61000-6-2
Contact discharge
8kV
Criterion A
EN 61000-4-2
Air discharge
15kV
Criterion A
EN 61000-4-3
80MHz-2.7GHz
20V/m
Criterion A
Input lines
4kV
Criterion A
EN 61000-4-4
Output lines
2kV
Criterion A
DC-OK signal (coupling clamp)
2kV
Criterion A
LN
2kV
Criterion A
EN 61000-4-5
L  PE, N  PE
4kV
Criterion A+1kV
Criterion A
EN 61000-4-5+ / -  PE
2kV
Criterion A
EN 61000-4-5
DC-OK signal  PE
1kV
Criterion A
EN 61000-4-6
0.15-80MHz
20V
Criterion A
0% of 100Vac
0Vac, 20ms
Criterion A
EN 61000-4-11
40% of 100Vac
40Vac, 200ms
Criterion C
70% of 100Vac
70Vac, 500ms
Criterion C
0% of 200Vac
0Vac, 20ms
Criterion A
40% of 200Vac
80Vac, 200ms
Criterion A
70% of 200Vac
140Vac, 500ms
Criterion A
EN 61000-4-11
0% of 200Vac (=0V)
5000msCriterion C
SEMI F47
Dips on the input voltage according to SEMI F47 standard
80% of 120Vac (96Vac)
1000msCriterion A
70% of 120Vac (84Vac)
500ms
Criterion A
50% of 120Vac (60Vac)
200ms
Criterion A
VDE 0160
Over entire load range
750V, 0.3ms
Criterion A

Criterions:
A: Power supply shows normal operation behavior within the defined limits.
C: Temporary loss of function is possible. Power supply may shut-down and restarts by itself. No damage or hazards for the power supply will
occur.

EMC Emission
Conducted emission
input lines
Conducted emission
output lines 2)
Radiated emission
Harmonic input current

According to generic standards: EN 61000-6-3 and EN 61000-6-4
EN 55011, EN 55015, EN 55032, FCC PartClass B
15, CISPR 11, CISPR 32
Limits for DC power port according EN
IEC/CISPR 16-1-2, IEC/CISPR 16-2-1
61000-6-3 fulfilled
EN 55011, EN 55032
Class BClass A fulfilled between 0A and 12A load
EN 61000-3-2Class C fulfilled between 6A and 12A load
Voltage fluctuations, flicker
EN 61000-3-3
Fulfilled 1)
This device complies with FCC Part 15 rules.
Operation is subjected to following two conditions: (1) this device may not cause harmful interference, and (2) thisdevice must accept any interference received, including interference that may cause undesired operation.
1) Tested with constant current loads, non pulsing2) For information only, not mandatory for EN 61000-6-3

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

16/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

Switching Frequencies
PFC converter
Main converter
Auxiliary converter

110kHz84kHz to 140kHz
60kHz

Fixed frequency
Output load dependent
Fixed frequency

16. ENVIRONMENT
Operational temperature 1)
Storage temperature
Output derating
Humidity-25°C to +70°C-40°C to +85°C
6W/K
5 to 95% r.h.

Vibration sinusoidal 2)

2-17.8Hz: ±1.6mm; 17.8-500Hz: 2g
2 hours / axis
30g 6ms, 20g 11ms
3 bumps / direction, 18 bumps in total
0 to 2000m
2000 to 6000m

Shock 2)
Altitude

Reduce output power according to Fig. 16-1
For storage and transportation
Between +60°C and +70°C
According to IEC 60068-2-30
Do not energize while condensation is present.
According to IEC 60068-2-6
According to IEC 60068-2-27

Without any restrictions
Reduce output power or ambient
temperature, see Fig. 16-2.
15W/1000m or 5K/1000m
For altitudes >2000m, see Fig. 16-2
According to IEC 62477-1 for altitudes up to
III
2000m
According to IEC 62477-1 for altitudes fromII
2000m to 6000m
2
According to IEC 62477-1, not conductive
Some audible noise may be emitted from the power supply during no load, overload or
short circuit.

Altitude derating
Over-voltage category

Degree of pollution
Audible noise

1) Operational temperature is the same as the ambient or surrounding temperature and is defined as the air temperature 2cm below the unit.
2) Tested in combination with DIN rails according to EN 60715 with a height of 15mm and a thickness of 1.3mm and standard orientation.
Fig. 16-1 Output current vs. ambient temp.
(Inom 10A; Iout with PowerBoost = 12A)

Fig. 16-2 Output current vs. altitude

Allowed Output Current at 24V

Allowed Output Current at 24V

12A

B
A

10A

12A
10A

8A

8A

6A

6A

4A

4A

2A
0
-25

A... 85 to 264Vac, continuous
B... short term

0

20

40

D
C
B
A
A... Tamb < 60°C
B... Tamb < 50°C
C... Tamb < 40°C
D... Short term

2A

60 70°C

Ambient Temperature

0

0

2000m

4000m

6000m
AltitudeJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

17/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

17. PROTECTION FEATURES
Output protection
Output over-voltage protection

Degree of protection
Penetration protection
Over-temperature protection

Input transient protection
Internal input fuse

Electronically protected against overload, no-load and short-circuits. In case of aprotection event, audible noise may occur.
Typ. 30.5Vdc
In case of an internal power supply defect, a redundantMax. 32Vdc
circuit limits the maximum output voltage. The output
shuts down and automatically attempts to restart.
IP 20
EN/IEC 60529> 4mm
E.g. screws, small parts
Output shut-down with automatic restart.
Yes
The temperature sensor is installed on criticalcomponents inside the unit and turns the unit off insafety critical situations, which can happen e.g. whenderating requirements are not observed, ambient
temperature is too high, ventilation is obstructed or
the derating requirements for different mounting
orientation is not followed. There is no correlation
between the operating temperature and turn-off
temperature since this is dependent on input voltage,load and installation methods.
MOV
For protection values see chapter 15 (EMC).
(Metal Oxide Varistor)
Not user replaceable slow-blow high-braking capacity
Includedfuse

18. SAFETY FEATURES
Input / output separation

Class of protection
Isolation resistancePE resistance
Touch current (leakage current)

Double or reinforced galvanic isolation
SELV
IEC/EN 60950-1
PELV
IEC/EN 60204-1, EN 62477-1, IEC 60364-4-41
I
PE (Protective Earth) connection required
At delivered condition between input and output,> 500MOhm
measured with 500Vdc
At delivered condition between input and PE,> 500MOhm
measured with 500Vdc
At delivered condition between output and PE,> 500MOhm
measured with 500Vdc
At delivered condition between output and DC-OK> 500MOhm
contacts, measured with 500Vdc
Resistance between PE terminal and the housing in the< 0.1Ohm
area of the DIN rail mounting bracket.
Typ. 0.14mA / 0.36mA
At 100Vac, 50Hz, TN-,TT-mains / IT-mains
Typ. 0.20mA / 0.50mA
At 120Vac, 60Hz, TN-,TT-mains / IT-mains
Typ. 0.33mA / 0.86mA
At 230Vac, 50Hz, TN-,TT-mains / IT-mains
Max. 0.18mA / 0.43mA
At 110Vac, 50Hz, TN-,TT-mains / IT-mains
Max. 0.26mA / 0.61mA
At 132Vac, 60Hz, TN-,TT-mains / IT-mains
Max. 0.44mA / 1.05mA
At 264Vac, 50Hz, TN-,TT-mains / IT-mains

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

18/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

19. DIELECTRIC STRENGTH
The output voltage is floating and has no ohmic connection to the ground. Type and factory tests are conducted by
the manufacturer. Field tests may be conducted in the field using the appropriate test equipment which applies thevoltage with a slow ramp (2s up and 2s down). Connect all input-terminals together as well as all output poles before
conducting the test. When testing, set the cut-off current settings to the value in the table below.
Type test

60s

A
2500Vac

B
4000Vac

C
1000Vac

D
500Vac

500Vac

500VacFig. 19-1 Dielectric strength

Input
L
N

B

B

A

Factory test

5s

2500Vac

2500Vac13

Field test

5s

2000Vac

2000Vac

500Vac

500Vac14

Cut-off current setting> 10mA> 10mA> 20mA

> 1mA

DC-ok
*)

D
OutputEarth, PEC+-

To fulfil the PELV requirements according to EN60204-1 § 6.4.1, werecommend that either the + pole, the – pole or any other part ofthe output circuit shall be connected to the protective earthsystem. This helps to avoid situations in which a load starts
unexpectedly or can not be switched off when unnoticed earth
faults occur.

B*) When testing input to DC-OK ensure that the max. voltage between DC-OK and the output is not exceeded (column D). We recommend
connecting DC-OK pins and the output pins together when performing the test.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

19/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series

24V, 10A, 240W, SINGLE PHASE INPUT

20. APPROVED, FULFILLED OR TESTED STANDARDSUL 508(only CP10.241, CP10.241-C1,
CP10.241-S1, CP10.242)

UL 61010-2-201(only CP10.241-S2)

IEC 61010-2-201(only CP10.241, CP10.241-C1,
CP10.241-S1, CP10.242)
IEC 61010-2-201(only CP10.241-S2)
IEC 62368-1(only CP10.241-S2)

IEC 60950-1

UL 60950-1(only CP10.241, CP10.241-C1,
CP10.241-S1, CP10.242)

ATEX

IECEx

Class 1 Div 2UL Certificate
Listed equipment for category NMTR - Industrial Control
Equipment
Applicable for US and Canada
E-File: E198865
UL Certificate
Listed equipment for category NMTR - Electrical Equipment for
Measurement, Control and Laboratory Use - Particularrequirements for control equipment
Applicable for US and Canada
E-File: E198865
Manufacturer's Declaration
Electrical Equipment for Measurement, Control and Laboratory
Use - Particular requirements for control equipment
CB Scheme Certificate
Electrical Equipment for Measurement, Control and Laboratory
Use - Particular requirements for control equipment
CB Scheme Certificate
IEC 62368-1 Audio/video, information and communication
technology equipment - Safety requirements
Output safety level: ES
CB Scheme Certificate
General safety requirements for Information Technology
Equipment (ITE)UL Certificate
Recognized component for category QQGQ - Information
Technology Equipment (ITE)
Applicable for US and Canada
E-File: E137006
Agency Certificate (Bureau Veritas)
EN 60079-0 Explosive atmospheres - General requirements
EN 60079-7, EN 60079-15 Equipment protection by type ofprotection "e" and "n"Certificate: EPS 15 ATEX 1 101 X
Temperature Code: T4
Type of Protection: ec nC
IECEx Certificate
IEC 60079-0 Explosive atmospheres - General requirements
IEC 60079-7, IEC 60079-15 Equipment protection by type ofprotection "e" and "n"Certificate: IECEx EPS 15.0079X
Temperature Code: T4
Type of Protection: ec nC
UL Certificate
Listed equipment for category NRAD - Listed equipment
Industrial Control Equipment for Use in Hazardous Locations
Applicable for US and Canada
E-File: E327416
Temperature Code: T4
Groups: A, B, C and D

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

20/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series
Marine (DNV)(only CP10.241, CP10.241-C1,
CP10.241-S1, CP10.242)

Marine (ABS)(only CP10.241, CP10.241-S1,
CP10.242)
IEC 61558-2-16(only CP10.241)

SEMI 47

IEC 60068-2-60

ISA-71.04 G3

Labs

24V, 10A, 240W, SINGLE PHASE INPUTDNV Certificate
DNV Type approved product
Certificate: TAA00002YX
Temperature: Class D
Humidity: Class B
Vibration: Class C
EMC: Class A
Enclosure: Class A
ABS Design Assessment Certificate
ABS (American Bureau of Shipment) assessed product
Certificate: 17-HG1599236-PDA
Test Certificate
IEC 61558-2-16 - Safety of transformers, reactors, power supply
units and similar products for supply voltages up to 1100 V
Particular requirements and tests for switch mode power
supply units and transformers for switch mode power supply
units
Test Report
Voltage Sag Immunity for Semiconductor Processing
Equipment
Tested for AC 208V L-L or L-N mains voltages, nominal output
voltage and nominal output load
Manufacturer's Declaration (Online Document)
Environmental Tests, Flowing Mixed Gas Corrosion Test
IEC 60068-2-60 Method 4
Test Ke - Method 4
H2S: 10ppb
NO2: 200ppb
Cl2: 10ppb
SO2: 200ppb
Test Duration: 3 weeks, this simulates a service life of 10 years.
Manufacturer's Declaration (Online Document)
Airborne Contaminants Corrosion Test
ISA-71.04 G3
Severity Level: G3 Harsh
H2S: 100ppb
NOx: 1250ppb
Cl2: 20ppb
SO2: 300ppb
Test Duration: 3 weeks, this simulates a service life of 10 years.
Paint Wetting Impairment Substances Test (or LABS-Test)
Tested for Zone 2 and test class C1 according to VDMA 24364C1-L/W for solvents and water-based paints

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

21/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

21. REGULATORY PRODUCT COMPLIANCE
EU Declaration ofConformity

REACH Regulation (EU)

WEEE Regulation

KC

UKCA

CCC

The CE mark indicates conformance with the- EMC directive- ATEX directive- RoHS directive
Manufacturer's Declaration
EU regulation regarding the Registration, Evaluation,
Authorisation and Restriction of Chemicals (REACH) fulfilled.
EU Regulation (EC) 1907/2006.
Manufacturer's Declaration
EU Regulation on Waste Electrical and Electronic Equipment
Registered as business to business (B2B) products.
EU Regulation 2012/19/EU
KC Korean Certification
Korean - Registration of Broadcasting and Communication
Equipment
Registered under Clause3, Article 58-2 of Radio Waves Act.
Registration No. R-R-PUG-CP10_241.
UKCA Declaration of Conformity
Trade conformity assessment for England, Scotland and WalesThe UKCA mark indicates conformity with the UK Statutory
Instruments
2016 No.1101,
2016 No.1091,
2012 No.3032
CCC Certificate
China Compulsory Certification (CNCA-C23-01:2019)
Certificate for devices made in Suzhou/China (PULSElectronics): 2021122303114443
Certificate for devices made in Chomutov/Czech Republic(PULS investiční): 2021122303114444
CCC-ExJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

22/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

22. PHYSICAL DIMENSIONS AND WEIGHT
Width
HeightDepth

WeightDIN rail
Housing material
Installation clearances

39mm
124mm
117mm
The DIN rail depth must be added to the unit depth to calculate the total required
installation depth.
600g
Use 35mm DIN rails according to EN 60715 or EN 50022 with a height of 7.5 or 15mm.
Body: Aluminium alloy
Cover: Zinc-plated steel
See chapter 2

Fig. 22-1
Front view
CP10.241, CP10.241C1, CP10.242

Fig. 22-2
Front view
CP10.241-S1

Fig. 22-3
Front view
CP10.241-S2

Fig. 22-4
Side viewAll dimensions in mm

All dimensions in mm

All dimensions in mm

All dimensions in mm

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

23/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

23. ACCESSORIES
23.1. ZM10.WALL - WALL/PANEL MOUNT BRACKETThis bracket is used to mount the devices on a wall/panel without utilizing the DIN rail. The bracket can be mounted
without detaching the DIN rail brackets from the power supply. PSU for illustration purpose only.
Fig. 23-1 Isometric viewFig. 23-4 Wall/panel mounting,front viewFig. 23-2 Isometric viewFig. 23-5 Hole pattern for wall
mounting

Fig. 23-3 Isometric viewFig. 23-6 Wall/panel mounting, side viewJan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

24/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

23.2. ZM12.SIDE - SIDE MOUNTING BRACKETThis bracket is used to mount the power supply sideways with or without utilizing a DIN rail.
The two aluminum brackets and the black plastic slider of the unit have to be detached, so that thesteel brackets can be mounted.
For sideway DIN rail mounting, the removed aluminum brackets and the black plastic slider need to be
mounted on the steel bracket.

Fig. 23-4
Side mounting without DIN
rail brackets

Fig. 23-5
Side mounting with DIN rail
brackets

Fig. 23-6
Mounting Dimensions
Side mounting bracket

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

25/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

23.3. YR20.242 - REDUNDANCY MODULEThe YR20.242 is equipped with two input channels, which are individually
decoupled by utilizing MOSFET technology. Using MOSFETSs instead of diodes
reduces the heat generation and the voltage drop between input and output. The
YR20.242 does not require an additional auxiliary voltage and is self-powered
even in case of a short circuit across the output.
Due to the low power losses, the unit is very slender and only requires 32mm
width on the DIN rail.
The YR20.242 can be used for n+1 and 1+1 redundancy systems.
Further information and wiring configurations can be found in chapter 24.7.

23.4. YR20.246 - REDUNDANCY MODULE WITH AUTOMATED LOAD SHARINGThe YR20.246 is equipped with two input channels, which are individually
decoupled by utilizing MOSFET technology. Using MOSFETSs instead of diodes
reduces the heat generation and the voltage drop between input and output. The
YR20.246 does not require an additional auxiliary voltage and is self-powered
even in case of a short circuit across the output.
Due to the low power losses, the unit is very slender and only requires 32mm
width on the DIN rail.
The YR20.246 is optimized for 1+1 redundancy systems.
Compared to the YR20.242, the YR20.246 is featured with an automated load
sharing between the connected power supplies. The YR20.246 monitors thefunction of the redundancy circuitry and provides a signal in case of too high ofoutput current, which could prevent redundancy, if one power supply fails.
Further information and wiring configurations can be found in 24.7.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

26/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

24. APPLICATION NOTES
24.1. PEAK CURRENT CAPABILITY
The unit can deliver peak currents (up to several milliseconds) which are higher than the specified short term currents.
This helps to start current demanding loads. Solenoids, contactors and pneumatic modules often have a steady state
coil and a pick-up coil. The inrush current demand of the pick-up coil is several times higher than the steady-state
current and usually exceeds the nominal output current (including the PowerBoost). The same situation applies whenstarting a capacitive load.
The peak current capability also ensures the safe operation of subsequent circuit breakers of load circuits. The loadbranches are often individually protected with circuit breakers or fuses. In case of a short or an overload in one branch
circuit, the fuse or circuit breaker need a certain amount of over-current to open in a timely manner. This avoids
voltage loss in adjacent circuits.
The extra current (peak current) is supplied by the power converter and the built-in large sized output capacitors of
the power supply. The capacitors get discharged during such an event, which causes a voltage dip on the output. The
following two examples show typical voltage dips for resistive loads:
Fig. 24-1 20A peak current for 50ms , typ.
(2x the nominal current)

Fig. 24-2 50A peak current for 5ms , typ.
(5x the nominal current)

Fig. 24-3 30A peak current for 12ms , typ.
(3x the nominal current)

Please note: The DC-OK relay triggers when the voltage
dips more than 10% for longer than 1ms.

Peak current voltage dips

Typically from 24V to 17V
Typically from 24V to 19V
Typically from 24V to 15.5V

At 20A for 50ms, resistive load
At 50A for 2ms, resistive load
At 50A for 5ms, resistive load

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

27/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

24.2. BACK-FEEDING LOADS
Loads such as decelerating motors and inductors can feed voltage back to the power supply. This feature is also called
return voltage immunity or resistance against Back- E.M.F. (Electro Magnetic Force).
This power supply is resistant and does not show malfunctioning when a load feeds back voltage to the power supply.
It does not matter whether the power supply is on or off.
The maximum allowed feed-back-voltage is 35Vdc. The maximum allowed feed-back peak current is 40A. Higher
currents can temporarily shut-down the output voltage. The absorbing energy can be calculated according to thebuilt-in large sized output capacitor which is specified in chapter 6.

24.3. EXTERNAL INPUT PROTECTION
The unit is tested and approved for branch circuits up to 30A (UL) and 32A (IEC). An external protection is only
required if the supplying branch has an ampacity greater than this. Check also local codes and local requirements. In
some countries local regulations might apply.
If an external fuse is necessary or utilized, minimum requirements need to be considered to avoid nuisance tripping of
the circuit breaker. A minimum value of 6A B- or C-Characteristic breaker should be used.

24.4. OUTPUT CIRCUIT BREAKERS
Standard miniature circuit breakers (MCB’s or UL 1077 circuit breakers) are commonly used for AC-supply systems andmay also be used on 24V branches.
MCB’s are designed to protect wires and circuits. If the ampere value and the characteristics of the MCB are adapted to
the wire size that is used, the wiring is considered as thermally safe regardless of whether the MCB opens or not.
To avoid voltage dips and under-voltage situations in adjacent 24V branches which are supplied by the same source, afast (magnetic) tripping of the MCB is desired. A quick shutdown within 10ms is necessary corresponding roughly tothe ride-through time of PLC's. This requires power supplies with high current reserves and large output capacitors.
Furthermore, the impedance of the faulty branch must be sufficiently small in order for the current to actually flow.
The best current reserve in the power supply does not help if Ohm’s law does not permit current flow. The following
table has typical test results showing which B- and C-Characteristic MCBs magnetically trip depending on the wire crosschapter and wire length.
Fig. 24-4 Test circuit

Power Supply

AC

MCB

+

+
Wire length

DC S1... Fault simulation switch

*)

Load

S1

-

Maximal wire length*) for a fast (magnetic) tripping:
0.75mm²
1.0mm²1.5mm²2.5mm²
30 m
37 m
54 m
84 m
C-2A
25 m
30 m
46 m
69 m
C-3A
9m
15 m
25 m
34 m
C-4A
3m
3m
4m
7m
C-6A
C-8A
B-6A
B-10A
B-13A

12 m
3m
2m

15 m
3m
2m

21 m
4m
3m

34 m
9m
6m

Don’t forget to consider twice the distance to the load (or cable length) when calculating the total wire length (+ and – wire).

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

28/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
CP-Series

24V, 10A, 240W, SINGLE PHASE INPUT

24.5. SERIES OPERATION

Unit AACPower supplies of the same type can be connected in series for higher
output voltages. It is possible to connect as many units in series as needed,
providing the sum of the output voltage does not exceed 150Vdc. Voltages
with a potential above 60Vdc are not SELV any more and can be dangerous.
Such voltages must be installed with a protection against touching.

DC

+
+

Unit B

Load

AC

Earthing of the output is required when the sum of the output voltage isabove 60Vdc.

DC

Avoid return voltage (e.g. from a decelerating motor or battery) which isapplied to the output terminals.

-

+
-

Earth
(see notes)

Restrictions:
Keep an installation clearance of 15mm (left / right) between two power supplies and avoid installing the power
supplies on top of each other.
Do not use power supplies in series in mounting orientations other than the standard mounting orientation (terminals
on bottom of the unit).
Pay attention that leakage current, EMI, inrush current, harmonics will increase when using multiple power supplies.

24.6. PARALLEL USE TO INCREASE OUTPUT POWER
CP10.241 power supplies can be paralleled to increase the output power. The
output voltage of all power supplies shall be adjusted to the same value(±100mV) with the same load conditions on all units, or the units can be left
with the factory settings. There is no feature included which balances the load
current between the power supplies. Usually the power supply with the higher
adjusted output voltage draws current until it goes into current limitation. Thismeans no harm to this power supply as long as the ambient temperature stays
below 40°C.
If more than three units are connected in parallel, a fuse or circuit breakerwith a rating of 15A or 16A is required on each output. Alternatively, a diodeor redundancy module can also be utilized.

Unit AAC
DC++

Unit B

AC
DC

Load

+
-

-

Energize all units at the same time to avoid the overload HiccupPLUS mode. It also might be necessary to cycle the input
power (turn-off for at least five seconds), if the output was in HiccupPLUS mode due to overload or short circuits and therequired output current is higher than the current of one unit.
Restrictions:
Keep an installation clearance of 15mm (left / right) between two power supplies and avoid installing the power
supplies on top of each other.
Do not use power supplies in parallel in mounting orientations other than the standard mounting orientation(terminals on bottom of the unit) or in any other condition where a derating of the output current is required (e.g.
altitude, …).
Pay attention that leakage current, EMI, inrush current, harmonics will increase when using multiple power supplies.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

29/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

24.7. PARALLEL USE FOR REDUNDANCY
1+1 Redundancy:
Power supplies can be paralleled for redundancy to gain higher system availability. Redundant systems require acertain amount of extra power to support the load in case one power supply unit fails. The simplest way is to put two
power supplies in parallel. This is called a 1+1 redundancy. In case one power supply unit fails, the other one is
automatically able to support the load current without any interruption. It is essential to use a redundancy module todecouple power supplies from each other. This prevents that the defective unit becomes a load for the other power
supplies and the output voltage cannot be maintained any more.
Optionally to the use of external redundancy modules, power supplies with built-in redundancy CP10.241-R1 (springclamp terminals), the CP10.241-R2 (plug connectors for hot swap) or the CP10.241-R3 (screw terminals) can be used.
Recommendations for building redundant power systems:- Use separate input fuses for each power supply.
- Monitor the individual power supply units. Therefore, use the DC-OK relay contact of the power supply.
- It is desirable to set the output voltages of all units to the same value (± 100mV) or leave it at the factory setting.
Pay attention that leakage current, EMI, inrush current, harmonics will increase when using multiple power supplies.
Wiring examples for 1+1 redundancy:
Fig. 24-5 Wiring for 1+1 redundancy with the redundancy module
YR20.242

Fig. 24-6 Wiring for 1+1 redundancy with the redundancy module
YR20.246

FailureMonitor-

Output
24V,10A
DCOK

Power
Supplyoo+ - + -

YR20.242
Redundancy
Module- +optional

I

L

-

+ + -

-

+ + -

-

DCOK

o
o

DCOK

o
o

DCOK

o
o

Output
24V, 10A

Output
24V, 10A

Power
SupplyOutputInput

L N PE+ + -Output
24V,10A

Input Input
2
1

Power
SupplyInput

L N PE

I

+

N

-

PE

PE

Redudnadcy
OK

o
o
o
o

OutputInput

L N PE

I

Load ShareOK

YR20.246
Redundancy
Module

Input

I

2
Input

Power
SupplyL N PE

Max.
10A
Load

- - + +

1
Input

- +

Load
Share
Warning

FailureMonitor

Max.
10A
Load

optional+ + -N+1 Redundancy:
Redundant systems for a higher power demand are usually built in a N+1 method. E.g. four power supplies, each rated
for 10A are paralleled to build a 30A redundant system.
Pay attention that leakage current, EMI, inrush current, harmonics will increase when using multiple power supplies.
Keep an installation clearance of 15mm (left / right) between two power supplies and avoid installing the power
supplies on top of each other.
Do not use power supplies in parallel in mounting orientations other than the standard mounting orientation or in
any other condition, where a derating of the output current is required.

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

30/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series
Wiring examples for 1+1 redundancy:

Fig. 24-7 Wiring for N+1 redundancy with four power supplies and two redundancy modules
YR20.242
FailureMonitor+ + --Output
24V,10A
DCOK

Power
Supplyoo+ - + -

YR20.242
Redundancy
Module+ + --+ - + -

Output
24V,10A

o
o

DCOK

DCOK

o
o

Input

Input

L N PEL N PE

+ + -

-

DCOK

o
o

Output
24V,10A

Input Input
2
1

YR20.242
Redundancy
ModulePower
SupplyPower
Supply- +optional-

Output
24V,10A

OutputInput

L N PEI+ + -Input Input
2
1

Power
SupplyOutputInput- +L N PE
30A
Load

I

I

I

L
N
PE

24.8. INDUCTIVE AND CAPACITIVE LOADSThe unit is designed to supply any kind of loads, including capacitive and inductive loads. If extreme large capacitors,
such as EDLCs (electric double layer capacitors or “UltraCaps”) with a capacitance larger than 1.5F are connected to the
output, the unit might charge the capacitor in the HiccupPLUS mode (see chapter 6).

24.9. CHARGING OF BATTERIESThe power supply can be used to charge lead-acid or maintenance free batteries (SLA or VRLA batteries). Two 12V
batteries are needed in series.
Instructions for charging batteries:a)Ensure that the ambient temperature of the power supply stays below 40°C for mains voltage of AC 120V or
higher and 35°C for a mains voltage of AC 100V.

b)

Set output voltage (measured at no load and at the battery end of the cable) very precisely to the end-of-charge
voltage.
End-of-charge voltage

27.8V

27.5V

27.15V

26.8V

Battery temperature

10°C

20°C

30°C

40°C

c)

Use a 15A or 16A circuit breaker (or blocking diode) between the power supply and the battery.

d)Ensure that the output current of the power supply is below the allowed charging current of the battery.

e)

Use only matched batteries when putting 12V types in series.

f)

The return current to the power supply (battery discharge current is typ. 3.5mA when the power supply isswitched off (except in case a blocking diode is utilized).

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

31/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

24.10. OPERATION ON TWO PHASESPower Supply

L3

CenterTap

240V +10% max.

L1

The power supply can also be used on two-phases of a three-phasesystem. Such a phase-to-phase connection is allowed as long as the
supplying voltage is below 240V+10%.

AC
L
N
PE
DC

L2

24.11. USE IN A TIGHTLY SEALED ENCLOSURE
When the power supply is installed in a tightly sealed enclosure, the temperature inside the enclosure will be higher
than outside. In such situations, the inside temperature defines the ambient temperature for the power supply.
The following measurement results can be used as a reference to estimate the temperature rise inside the enclosure.
The power supply is placed in the middle of the box, no other heat producing items are inside the box
The temperature sensor inside the box is placed in the middle of the right side of the power supply with a distance of
1cm.

Enclosure size

Input voltage
Load
Temperature inside the box
Temperature outside the box
Temperature rise

Case A
110x180x165mm
Rittal Typ IP66 Box
PK 9516 100,plastic
230Vac
24V, 8A; (=80%)
48.6°C
26.3°C
22.3K

Case B
110x180x165mm
Rittal Typ IP66 Box
PK 9516 100,plastic
230Vac
24V, 10A; (=100%)
53.8°C
26.6°C
27.3K

Case C
180x180x165mm
Rittal Typ IP66 Box
PK 9519 100,plastic
230Vac
24V, 8A; (=80%)
42.0°C
25.8°C
16.2K

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

Case D
180x180x165mm
Rittal Typ IP66 Box
PK 9519 100,plastic
230Vac
24V, 10A; (=100%)
48.1°C
26.2°C
21.9K

32/33

CP10.241, CP10.241-C1, CP10.241-S1,
CP10.241-S2, CP10.242
24V, 10A, 240W, SINGLE PHASE INPUT

CP-Series

24.12. MOUNTING ORIENTATIONSMounting orientations other than all terminals on the bottom require a reduction in continuous output power or alimitation in the maximum allowed ambient temperature. The amount of reduction influences the lifetime expectancyof the power supply. Therefore, two different derating curves for continuous operation can be found below:
Curve A1
Curve A2

Recommended output current.
Max allowed output current (results in approximately half the lifetime expectancy of A1).

Fig. 24-8
Mounting
Orientation A(Standardorientation)

Output Current

12A

OUTPUT

A1

9
Power
Supply6
3
Ambient Temperature

0

INPUT

10
Fig. 24-9
Mounting
Orientation B(Upside down)

20

30

40

50

60°C

Output Current

12A
A1

INPUT

9

A2

Power
Supply6
3
Ambient Temperature

0

OUTPUT

10
Fig. 24-10
Mounting
Orientation C(Table-top
mounting)

20

30

40

50

60°C

Output Current

12A
A1

9

A2

6
3
Ambient Temperature

0
10

40

50

60°C

12A
OUTPUT

Power
Supply

9

A1

6

A2

3
Ambient Temperature

0
10

20

30

40

A1

A2

50

60°C

Output Current

9
INPUT

Power
Supply12A
OUTPUT

Fig. 24-12
Mounting
Orientation E(Horizontal ccw)

30

Output Current

INPUT

Fig. 24-11
Mounting
Orientation D(Horizontal cw)

20

6
3

Ambient Temperature

0
10

20

30

40

50

60°C

Jan. 2023 / Rev. 1.7 DS-CP10.241-EN
All values are typical at 24V, 10A, 230Vac, 50Hz, 25°C ambient and after a 5 minutes run-in time unless otherwise noted.
www.pulspower.com Phone +49 89 9278 0Germany

33/33