PULS does it again:
practical, versatile and reliable likethe SilverLine – yet small like no other.

Data Sheet

MiniLine ML30.100
with DC 24-28V / 30W• Mounted and connected
in record time, no tools required• World-wide approvals (UL, EN, CSA,CB Scheme) for industry and office/home• Tiny: WxHxD = 45 x 75 x 91mm

• Output voltage adjustable to DC 28V• 100-240V Wide Range Input(AC 85...264V permitted)• PULS Overload Design™
(no switch off at overload butup to 1.5 times nominal current)• NEC Class 2 Power Supply andHazardous Location Class I Div. 2(UL 1604)

PULS GmbH, Arabellastrasse 15, D-81925 Munich
Tel. +49.(0)89.9278-244, Fax: +49.(0)89.9278-299
sales@puls-power.com, http://www.puls-power.com

Mini is more.
ML30e100/040629

Technical Data ML30.100

SX Input

Clamgnprips

X Output

Input voltage

AC100-240V (Wide Range), 47...63Hz
Admiss. limits: AC 85...264V (DC 85...375V)

Output voltage• preset

DC 24-28V, adj. by front panel potentiometer
24.5V ±0.5%

Input current<0.6A (@ AC 100V, 30W Pout)<0.35A (@ AC 196V, 30W Pout)

Voltage regulation

stat. 0.5% Vout, dyn. ±2% Vout overall

Ripple/Noise<50mVPP (20MHz bandw., 50 Ω−measurem.)

External Fusing

Not required, unit provides internal fuse
(T3AH, not accessible)

Transient immunity

Transient resistance acc. to VDE 0160 / W2
(750V / 1.3ms), over entire load range

Hold-up time(see diagram below)>190ms bei AC 230V, 24V / 1.3A
>107ms @ AC 196V, 24V / 1.3A
>19ms @ AC 100V, 24V / 1.3A

Overvoltage prot. (OVP) <40V
Output noisesuppression

EMI values below EN 61000-6-3, even when using long (>2m), unscreened output cables

Rated continuous
loading

up to 1.3A (convection cooling)depending on built-in orientation, Vin and Tamb;for details see derating diagram below

Overload behaviour

PULS Overload Design™: No switch-off at
overload/short-circuit, instead: up to 1.5 ⋅ Irated.
So you need no oversizing to start awkward
loads.

Protection

Unit is protected against (also permanent)
short-circuit, overload and open-circuit

Derating

depending on built-in orientation;
see diagram below

Parallel operationYes

X Efficiency, Reliability
Efficiency

typ. 87.5% (AC 230V, 24V / 1.3A)(see also diagram below)
typ. 4.5W (AC 230V, 24V / 1.3A)

LossesMTBF (Reliability)ca. 650.000h acc. to Siemensnorm SN 29500(24V/1.3A, AC 230V, Tamb = +40°C)

Prior to shipment, every unit undergoes the following tests in order toisolate any defective units which might suffer an early failure:• Run-in / burn-in (Full load, Tamb = +60°C, on/off cycle)• Functional test (100%)

Power back immunity35V

Operation indicator

Green LED (DC ON)

X Construction, Mechanics, Installation

X Environmental Data, EMC, Safety

Robust plastic housing (US Patent No. D442, 923S), fine ventilation grid on
three housing sides to keep out small parts (e.g. screws), IP20

Ambient temperature range (measured 25mm below unit)• storage, transport-25°C ... +85°C• operation-10°C ... +70°C (for derating see diagram below)

Dimensions and weight• BxHxT
45mm x 75mm x 91mm (+ DIN Rail)
Depth incl. terminals: 98mm (+ DIN Rail)230g• Weight

Humiditymax. 95% (without condensation)

Electromagneticemissions (EME)

EN 61000-6-3 (includes EN 61000-6-4)
Class B (EN 55011, EN 55022) incl. output noise
suppression

Ventilation/Cooling
Normal convection, no fan required• Free space f. cooling recom’d.: 25mm on sides with ventilation gridElectromagnetic
immunity (EMI)EN 61000-6-2 (includes EN 61000-6-1)

Easy snap-on mounting onto the DIN-Rail (TS35/7,5 or TS35/15).
Unit sits safely and firmly on the rail; no tools required even to remove

Safe low voltage:
Prot. class/degree:

SELV (EN60950, VDE0100/T.410), PELV (EN50178)
Class I (EN60950) / IP20 (EN60529)

Connection

The PSU complies with all major safety approvals for EU (EN 60 950,EN 60204-1, EN 50178), USA (UL 60950, E137006, UL508 LISTED, E198865),
Canada (CAN/CSA-C22.2 No 60950 [CUR], CAN/CSA-C22.2 No. 14 [CUL]),CB Scheme (IEC 60950). NEC Class 2 Power Supply and Hazardous Location Class I Div. 2 (UL 1604)

Mounting orientation,or(cf. ’Output’)by Spring Clamp terminals; uniformly firm hold,vibration-resistant and maintenance-free:
2 terminals per output

Connector size range• flexible cable• solid cable• Wire strip length

0.3-2.5mm2 (28-12 AWG)
0.3-4mm2 (28-12 AWG)
Ferrules admissible
6mm (0.24in) recommended

Design details – for your advantage:• All terminals are easy to reach as mounted on the front panel.
• Input and output are strictly apart from each other (input below, output above) and so cannot be mixed up• Mounting and connection do not require any screwdriver→ Easy, quick, durable and reliable installation

X Diagrams902530230V ACin100-120V ACin

10582

Output power [W]8415100 V ACin
120 V ACin
230 V ACin80787620Mounting
100,51,01,52,0Ausgangsstrom Iout [A]2,5b85-264 V ACin A-a A-a A-b85-370 V DCin B-a B-a B-b0,30,50,70,91,1

Output current Iout [A]

1,380
60
40

Pout=30W, typ.
Pout=30W, min.
Pout=15W, typ.
Pout=15W, min.

200720,0aB

740100A86201204088Vout range

Efficiency [%]Ausgangsspannung Vout [V]30

Hold-up time with ACin(@ Vout = 24V, typ. + min.)Deratingof output power

Efficiency(@ Vout = 24V, typ.)Hold-up time [ms]Output characteristic Vout/Iout(min.)

0-1001020304050

Ambient Temperature [°C]607090,0125,0160,0195,0Input voltage V ACin [V]Product information (ML30e100 / 040629), Rev.: 29. June 2004
Unless otherwise stated, specifications are valid for AC 230V input voltage, +25°C ambient temperature, and 5 min. run-in time. They are subject to change without prior notice..
PULS GmbH, Arabellastr. 15, D-81925 München X Tel: +49.(0)89.9278-244, Fax: +49.(0)89.9278-299, E-Mail: sales@puls-power.com X www.puls-power.com

230,0