PULS MiniLine:
practical, versatile and reliable likethe Silverline – yet small likeno other.

Data Sheet

MiniLine ML30.101
with 5 V DC / 25 W
• Mounted and connected in record time,no tools required• Adjustable output voltage
up to DC 5.5V

• World-wide approvals (UL, EN, CSA,CB Scheme) for industry and office/home• 100-240V Wide Range Input• Tiny: WxHxD = 45 x 75 x 91mm

PULS GmbH, Arabellastrasse 15, 81925 Munich
Tel. +49.(0)89.9278-244, Fax: +49.(0)89.9278-299
sales@puls-power.com, http://www.puls-power.com• NEC Class 2 Power Supply andHazardous Location Class I Div. 2(UL 1604)

Mini is more.
ML30e101/040629

Technical Data ML30.101

Spri

X InputsamplCng

X Output

Input voltage

AC 100-240V (Wide Range), 47...63Hz
Admiss. limits: AC 85...264V (DC 85...370V)

Output voltage• preset

DC 5-5.5V; adj. by front panel potentiometer
5.1V ±0.5% @ 5A

Input current<0.6A (@ AC 100V, 25W Pout)<0.35A (@ AC 196V, 25W Pout)

Voltage regulation

stat. <2% Voutdyn. ±5% Vout over allExternal fusing

not required, unit provides internal fuse
(T3A15H, not accessible)

Ripple/Noise<50mVPP (20MHz bandw., 50Ω measurement)

Overvoltage prot. (OVP) <6.5V

Transient immunity

Transient resistance acc. to VDE 0160 / W2
(750V / 1.3ms), over entire load range

Rated continuousloading

Iout = 5A @ Vout = 5.1V (convection cooling);
details see derating diagram below

Hold-up time(see diagram below)>19ms @ AC 100V, 5.1V / 5A
>107ms @ AC 196V, 5.1V / 5A
>170ms @ AC 230V, 5.1V / 5A

• power reserve

20%-35% (depending on Vin); for details see
diagram 'output characteristic' below

Overload behaviour

Straight V/I characteristic (depending on Vin);details see diagr. 'output characteristic' below

Protection

Unit is protected against (also permanent)
short-circuit, overload and open-circuit.

Derating

depending on built-in orientation;
details see diagram below

Power back immunity

10V

Operating indicator

Green LED

X Efficiency, Reliability
Efficiency>80%(AC 230V, 5.1V / 5A)(see also diagram below)
typ. 6W(AC 230V, 5.1V / 5A)

LossesMTBF (Reliability)

600.000h acc. to Siemensnorm SN 29500(5.1V / 5A, AC 230V, Tamb = +40°C)

Prior to shipment, every unit undergoes the following tests in order toisolate any defective units which might suffer an early failure:• Run-in / burn-in (Full load, Tamb = +60°C, on/off cycle)• Functional test (100 %)X Environmental Data, EMC, Safety
Ambient temperature range (measured 25mm below unit)• storage/transport-25°C ... +85°C• operation-10°C ... +70°C (for derating see diagram below)

X Construction, Mechanics, Installation
Robust plastic housing (US Patent No. D442, 923S), fine ventilation gridon three housing sides to keep out small parts (e.g. screws), IP20
Dimensions and weight• WxHxD
45mm x 75mm x 91mm (+ DIN Rail)
Depth incl. terminals: 98 mm (+ DIN Rail)240g• Weight
Mounting orientation,or(cf. ’Output’)

Ventilation/Cooling
Normal convection, no fan required• Free space f. cooling recom’d.: 25mm on sides with ventilation gridby Spring Clamp terminals; uniformly firm hold,vibration-resistant and maintenance-free:
2 terminals per output

Connector size range• flexible cable• solid cable• Wire strip length

max. 95% (without condensation)

Electromagneticemissions (EME)

EN 61000-6-3 (includes EN 61000-6-4)
Class B (EN 55011, EN 55022)

Electromagneticimmunity (EMI)EN 61000-6-2 (includes EN 61000-6-1)

Safe low voltage.:Prot. class/degree:

SELV (EN60950, VDE0100/T.410), PELV (EN50178)
Class I (EN60950) / IP20 (EN60529)

The PSU complies with all major safety approvals for EU (EN 60 950,EN 60204-1, EN 50178), USA (UL 60950, E137006, UL508 LISTED, E198865),
Canada (CAN/CSA-C22.2 No 60950 [CUR],CAN/CSA-C22.2 No. 14 [CUL]),CB Scheme (IEC 60950). NEC Class 2 Power Supply and Hazardous Location Class I Div. 2 (UL 1604)

Easy snap-on mounting onto the DIN-rail (TS35/7,5 or TS35/15).
Unit sits safely and firmly on the rail; no tools required even to remove
Connection

Humidity

Design details – for your advantage:• All terminals are easy to reach as mounted on the front panel.
• Input and output are strictly apart from each other (input below, output above) and so cannot be mixed up• Mounting and connection do not require any screwdriver→ Easy, quick, durable and reliable installation

0.3-2.5mm2 (28-12 AWG)
0.3-4mm2 (28-12 AWG)
Ferrules admissible
6mm (0.24in) recommended

X Diagrams
Deratingof output power
30

85

5,554,5480

25100-120V ACin

2,52
1,51Output power [W]75

3,5370120 V ACin
230 V ACin6560230V ACin0,50012345Output current Iout [A]7500,511,5 2 2,5 3 3,5 4
Output current Iout [A]4,55120A

15
100-10100

B20555

6

Hold-up time with ACin(@ Vout = 5.1V, typ. + min.)abMounting
85-150 V ACin150-264 V ACin100-370 V DCin
85-100 V DCin

A-a
A-a
A-a
B-b

A-a
A-a
A-a
B-b

A-b
A-a
A-b
B-cc

Hold-up time [ms]Efficiency(@ Vout = 5.1V, typ.)

Efficiency [%]Output voltage Vout [V]Output characteristic Vout/Iout(@ Vout = 5.1V, typ.)8060
Pout=25W, typ.
Pout=25W, min.
Pout=15W, typ.
Pout=15W, min.

40200010 20 30 40 50
Ambient temperature [°C]607090125160195
Input voltage V ACin [V]230

Product information (ML30e101), Stand: 29. June 2004. Alle Angaben gelten, sofern nicht anders angegeben, für AC 230V, +25°C Umgebungstemp. und 5 min. Einlaufzeit. Sie dienen ausschließlich der Produktbeschreibung und sind nicht als zugesicherte Eigenschaften im Rechtssinne aufzufassen. Änderungen vorbehalten.
PULS GmbH, Arabellastraße 15, D-81925 Munich X Tel: +49.(0)89.9278-244, Fax: +49.(0)89.9278-299, E-Mail: sales@puls-power.com X www.puls-power.com