Dust Ignition-proof Mercury Lamp Lighting Fittings (stainless steel)■ SPECIFICATIONS◦Rated voltage : 100V, 200V
(Other voltage can be supplied upon request)◦Materials of main components
Body : pressed sheet stainless steel
Guard : stainless steel bar
Reflector : aluminium sheet
Lamp cover : hard glass
Ballast box : corrosion-proof aluminium alloy
Terminal box : corrosion-proof aluminium alloy
Suspension pipe : stainless steel◦Colour : Mild grey (Munsell 10YR7/1)◦Finish : melamine resin coating◦Entries : G1/2 or 3/4 thread
With integral ballast : t hree ways with two blindplugs
With separate ballast : four ways with three blindplugs◦Photometric data : see P.14

Type of protection : SDP-12◦High reliability in protection against explosion
The HKLB lighting fittings are designed and constructedthoroughly with carefully selected materials to provide
high reliability in protection against explosion. Theirquality is certified by the TIIS.
◦Degree of protection : IP65
The body and ballast have a dust-tight and jet-proof
structure which meets the IP65 requirements of theIEC standards. They, therefore, can be used outdoors.
◦Made of stainless steel-high corrosion and weather
resistanceThe body, guard, suspension pipe and bolts are madeof stainless steel so that they can be used in corrosivelocations.
◦Weatherproof-for outdoor use
The body and ballast are weatherproof so that thy canbe used outdoors.

200W-400W (ceiling)4−φ1070140

10×15Cat. No.

200W

HKLB20941

3368

H2H1

Wattage

300W

400W

4−φ10967050(60)

15.5

̶

20050(60)12.0̶

10050(60)15.5

20050(60)12.010050(60)

16.5

17.0

20050(60)

12.5

17.0

10050(60)18.5

18.020050(60)

13.0

18.0

High P.F.

Constant wattage

Mass(kg)

Mass(kg)

HKLB40941

WattageCat. No.

200W

HKLB20942

336832

140
170

47

H2H1300W

400W

1110050(60)

16.0

̶

20050(60)12.5

̶

10050(60)16.020050(60)12.510050(60)

17.0

17.5

20050(60)

13.0

17.5

10050(60)

19.0

18.5

20050(60)

13.5

18.5

HKLB30942

φ330

BallastH
SupportHigh P.F., 100V
H2=450○High P.F., 200V
H1=278
̶Constant wattage H2=450○

Voltage Freq.
(V)(Hz)HKLB25942

790

250W

Mass(kg)

100

200W-400W (pipe pendant)
10×15

Mass(kg)

HKLB30941

φ330Ballast
HSupport
High P.F., 100V
H2=450○High P.F., 200V
H1=278
̶Constant wattage H2=450○

Constant wattage

HKLB25941

645

250W

Voltage Freq.
(V)
(Hz)

High P.F.

HKLB40942

Dust Ignition-proof Mercury Lamp Lighting Fittings (stainless steel)
200W-400W (bracket)
4−φ10Wattage

Cat. No.

200W

HKLB20946

560

High P.F.

Constant wattage

Mass(kg)

Mass(kg)

10050(60)16.0̶

20050(60)12.5

̶

10050(60)16.020050(60)12.510050(60)

17.0

17.5

20050(60)

13.0

17.5

10050(60)

19.0

18.5

20050(60)

13.5

18.5

High P.F.

Constant wattage

Mass(kg)

Mass(kg)

450450Ｈ2H160°70140

Voltage Freq.
(V)
(Hz)

250W

10×15

HKLB25946

03
φ3300W

BallastHigh P.F., 100VHigh P.F., 200V

H
SupportH2=450○H1=278̶Constant wattage H2=450

400W

HKLB30946

HKLB40946○200W-400W (ﬂoodlight)
WattageCat. No.

200W

HKPA2097

03060250W

4639090 6030φ437

440150

1-10×1560

10050(60)18.0̶

20050(60)15.5

̶

10050(60)18.5

20050(60)15.510050(60)

18.5

19.0

20050(60)

16.0

19.0

10050(60)

20.5

20.5

20050(60)

16.5

20.5

HKPA2597

H300W

Voltage Freq.
(V)
(Hz)

HKPA3097

4-φ10Ballast
High P.F., 100VHigh P.F., 200V
Constant wattage

H465
395
505

400W

12HKPA4097

PHOTOMETRIC DATAHKLB40Coeﬃcient of utilization
70%
50%30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%tance
10%Floor
0.60 .266 .211 .172 .250 .201 .166 .192 .160
0.80 .321 .264 .221 .302 .251 .213 .239 .205
1.00 .371 .314 .270 .349 .299 .260 .284 .250
1.25 .414 .357 .313 .388 .340 .301 .323 .289
1.50 .447 .392 .348 .419 .373 .334 .354 .320
Room 2.00.493 .443 .400 .463 .420 .383 .398 .367
index
2.50 .526 .480 .440 .494 .455 .421 .431 .402
3.00 .549 .506 .469 .516 .480 .448 .455 .428
4.00 .582 .545 .511 .548 .517 .488 .489 .465
5.00 .601 .567 .537 .566 .538 .512 .510 .488
10.00 .654 .633 .613 .619 .601 .584 .571 .556
Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

HKLB40
HF400X
22000m70%

cd/1000lm
0%0%.140.180
.222
.258
.288
.331
.364
.388
.424
.445
.511

180゜150゜150゜120゜120゜90゜90゜50
100

60゜60゜15030゜20030゜2500゜13