Explosion-Proof Type Mercury Lamp Lighting Fittings
Products conforming to the international standard (IEC Standard 60079)
Zone. 1 and 2 Areas◦Type of protection :Lighting fitting : ExdeⅡB+H2T3X (200-400W)
Lighting fitting : ExdeⅡB+H2T4X (100W)
Ballast : ExseⅡT4X
The HZAB lighting fittings are qualified for use in hazardous areas of Zone. 1 and 2 by the TIIS. The lighting
fitting consists of a flameproof lamp house and an increased-safety terminal compartment. The ballast consists ofa flameproof ballast box and an increased-safety terminal box. They are designed and constructed thoroughly withcarefully selected materials to provide high reliability in protection against explosion.
◦Degree of protection : IP65
They have a dust- and jet-proof structure which meets the IP65 requirements of the IEC standards, ensuring
trouble-free operation in outdoor use.
◦High corrosion resistanceThe body is made of corrosion-proof aluminium alloy, and the bolts are made of stainless steel.
◦Easy lamp replacement
The lamp can be replaced simply by loosening the four bolts on the lamp cover holder.
◦Easy installation and wiring
Installation is easy since the body is suspended by a union coupling at the terminal box. The terminal box has power
cable entries and a removable cover to permit wiring work after installation of the lighting fitting.
■SPECIFICATIONS◦Rated voltage : 100V, 200V (Other voltages can be supplied upon request.)◦Materials of main components
Body :
corrosion-proof aluminium alloy casting
Ballast box :corrosion-proof aluminium alloy
Terminal box :corrosion-proof aluminium die casting
Lamp cover :hard glass
Reflector :aluminium sheet
Suspension pipe : carbon steel◦Colour : Mild grey (Munsell 10YR7/1)◦Finish : melamine resin coating◦Entries : four ways (G1/2 or 3/4 thread) with three blind plugs◦Guard (Cat. No. G) and external reflector (Cat. No. R)
can be optionally supplied.
◦Photometric data : see p.12
◦External reflector (stainless steel)◦External reflector (Cat. No. R)◦External reflector (Cat. No. R)◦Guard (Cat. No. G)

100W (ceiling)
4-φ10holes

70

140

2-10×15holes
60

H2High P.F.
Cat. No.

H1Voltage
(V)

Freq.
(Hz)

Mass (kg)10050(60)13.020050(60)12.0

Support40

HZAB10941

567

Type of protection
body : ExdeIIB+H2T4X
ballast : ExseIIT4X

BallastHigh P.F., 100VHigh P.F., 200V

φ200

1H
H2=420H1=327

Support○–Explosion-Proof Type Mercury Lamp Lighting Fittings
Type of protection
body : ExdeIIB+H2T4X
ballast : ExseIIT4X

100W (pipe pendant)High P.F.

4-φ10holes

70Cat. No.

60

140

2-10×15holes

H1Freq.
(Hz)

Mass (kg)10050(60)13.5

20050(60)

12.5

HZAB10942
40

H2Voltage(V)717

Support

φ200

BallastHSupport

High P.F., 100VHigh P.F., 200V

H2=420H1=327○–100W (bracket)

2-10×15holes

60High P.F.

Support140

380

4-φ10holes

Voltage(V)

Freq.
(Hz)

Mass (kg)10050(60)13.5

20050(60)

12.5

HZAB10946

70

H2H1Cat. No.

40560

00
φ230

BallastHigh P.F., 100VHigh P.F., 200V

2H
H2=420H1=327

Support○–Explosion-Proof Type Mercury Lamp Lighting Fittings
Zone. 1 and 2 Areas

Type of protection
body : ExdeIIB+H2T3X
ballast : ExseIIT4X

200W-400W (ceilling)

Wattage60140

2-10×15holes

H2High P.F.

4-φ10holes

70Cat. No.

Voltage
(V)

Freq.
(Hz)

10050(60)20.0–20050(60)18.0–10050(60)20.5

20050(60)18.010050(60)

21.0

22.5

20050(60)

18.0

22.5

10050(60)

22.0

24.0

20050(60)

18.0

24.0

200W HZAB20941

H140250W HZAB25941

702

SupportConstant
wattage

300W HZAB30941

400W HZAB40941

Mass (kg)

φ298
BallastHigh P.F., 200W-300W,100V

H
H2=420High P.F., 200V
High P.F., 400W, 100V

H1=327–

H2=500○Constant wattage 100V, 200V

Support○200W-400W (pipe pendant)High P.F.

4-φ10holes702-10×15holes
60140

WattageCat. No.

Freq.
(Hz)

10050(60)20.5–

20050(60)18.0–10050(60)21.020050(60)18.010050(60)

21.0

22.5

20050(60)

18.5

22.5

10050(60)

22.0

24.0

20050(60)

18.5

24.0

200W HZAB20942

H2H140250W HZAB25942

Support852

300W HZAB30942

400W HZAB40942

φ298

3

Constant
wattage

Voltage(V)

BallastHigh P.F., 200W-300W, 100VHigh P.F., 200V
High P.F., 400W, 100V
Constant wattage 100V, 200V

Mass (kg)H
H2=420H1=327

Support○–

H2=500○Explosion-Proof Type Mercury Lamp Lighting Fittings
Type of protection
body : ExdeIIB+H2T3X
ballast : ExseIIT4X

200W-400W (bracket)
60

70

H2Support

H12-10×15holes

14060
゜

40500

4-φ10holes

650

BallastHigh P.F., 200W-300W, 100V

H
H2=420Support○High P.F., 200V
High P.F., 400W, 100V

H1=327–

H2=500○Constant wattage 100V, 200V

4WattageCat. No.

200W

HZAB20946

250W

HZAB25946

300W

HZAB30946

400W

HZAB40946

89φ2High P.F.

Constantwattage

Voltage(V)

Freq.
(Hz)

Weight (kg)Mass (kg)10050(60)

20.5–20050(60)18.0–10050(60)21.020050(60)18.010050(60)

21.0

22.5

20050(60)

18.5

22.5

10050(60)22.0

24.020050(60)

18.5

24.0

Explosion-Proof Type Mercury Lamp Lighting Fittings
Products conforming to the international standard (IEC Standard 60079)
Type of protection : ExdeIIB+H2T4X

Zone. 1 and 2 Areas

100W (ceilling)
85 4-φ9holes

Mass (kg)

HZAB10041

6.0

Cat. No.

Mass (kg)

HZAB10042

6.5

Cat. No.

Mass (kg)

HZAB10046

6.5476

2585

Cat. No.

φ200100W (pipe pendant)
85 4-φ9holes

626

2585
φ200

100W (bracket)

852547038085

4-φ9holes

00φ230゜5Explosion-Proof Type Mercury Lamp Lighting Fittings
Type of protection : ExdeIIB+H2T3X

200W-400W (ceilling)
85 4-φ9holes

611

2585

WattageCat. No.

Mass(kg)

200W

HZAB20041

11.5

250W

HZAB25041

11.5

300W

HZAB30041

11.5

400W

HZAB40041

11.5

WattageCat. No.

Mass(kg)

200W

HZAB20042

12.0

250W

HZAB25042

12.0

300W

HZAB30042

12.0

400W

HZAB40042

12.0

WattageCat. No.

Mass(kg)

200W

HZAB20046

12.0

250W

HZAB25046

12.0300W

HZAB30046

12.0

400W

HZAB40046

12.0

φ298

200W-400W (pipe pendant)
85 4-φ9holes

761

2585
φ298

200W-400W (bracket)

85557

60
゜

500

85

4-φ9holes

2589φ26

Explosion-Proof Type Mercury Lamp Lighting Fittings (stanchion)
Products conforming to the international standard (IEC Standard 60079)
Zone. 1 and 2 Areas

100W

200W-400W

Type of protection
body : ExdeIIB+H2T4X

Type of protection
body : ExdeIIB+H2T3X

400

400

φ48.6

φ48.6

HZAB10051

200W

HZAB20051

250W

HZAB25051

300W

HZAB30051

400W

HZAB40051

800 or more

800 or more

100W

200W-400W

Type of protection
body : ExdeIIB+H2T4X
ballast : ExseIIT4X

Type of protection
body : ExdeIIB+H2T3X
ballast : ExseIIT4X
400

400

φ48.6

φ48.6

40BallastHigh P.F., 100VHigh P.F., 200V

H
H=397
H=327

2600
2025

800 or more

75 H

75 H

140

70

4-φ10holes

140

70

φ298

2160

800 or more

2600

φ200

4-φ10holes

100W

2025

2160

φ298

Cat. No.

Stand pole : rust-proof

2600

2600

φ200

Wattage

40BallastHigh P.F., 200W-300W, 100VHigh P.F., 200V
High P.F., 400W, 100V
Constant wattage 100V, 200V

7H
H=397H=327
H=477

WattageCat. No.

100W

HZAB10951

200W

HZAB20951

250W

HZAB25951

300W

HZAB30951

400W

HZAB40951

Stand pole : rust-proof

Explosion-Proof Type Mercury Lamp Lighting Fittings (pole)
Products conforming to the international standard (IEC Standard 60079)
Zone. 1 and 2 Areas
body : ExdeIIB+H2T3X
ballast : ExseIIT4X

Type of protection

Type-B

Type-R

Type-C
400
1405

1000

φ48.6
34
φ

φ48.6

φ89.1

7000

ballast

φ89.1

7000

gasketφ165.2

15゜

7000

φ89.1

cover
φ165.2400
2-50×100Cable entry slot

250
350

2-50×100Cable entry slot

1200

2-50×100Cable entry slot

4-φ30holes

1200

400

400
1200

1-φ150holes

φ165.2

φ165.2250
350

Bolted base type

WattageCat. No.

PlantedWattage

HZAB20961

200W(Bolted base type)

HZAB20962

TY
P
E
|B

250W

(Bolted base type)

HZAB25962(Planted)

HZAB30961

300W(Bolted base type)

HZAB30962(Planted)

200W(Bolted base type)

HZAB40962(Planted)

Wattage

200W

HZAB20966

TY 250W
P
E| 300WC

HZAB25965(Bolted base type)

HZAB25966(Planted)

HZAB30965(Bolted base type)

HZAB30966(Planted)(Bolted base type)

HZAB40966(Planted)(Bolted base type)

HZAB20968(Planted)

TYPE|RHZAB25967

250W(Bolted base type)

HZAB25968(Planted)

HZAB30967

300W(Bolted base type)

HZAB30968(Planted)

HZAB40965

400W

Cat. No.

HZAB20967(Bolted base type)(Planted)

HZAB40961

400W

Cat. No.

HZAB20965(Planted)

HZAB25961

PlantedPlantedHZAB40967

400W(Bolted base type)

HZAB40968(Planted)

Pole : rust-proof

8

PHOTOMETRIC DATAHZAB10

HZAB40Coeﬃcient of utilization
70%
50%30%
Ceiling
Reﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%
tance
10%
Floor
0.60 .234 .167 .120 .212 .153 .110 .139 .100
0.80 .293 .221 .168 .264 .202 .155 .183 .141
1.00 .349 .276 .221 .316 .253 .205 .231 .189
1.25 .398 .326 .270 .361 .300 .250 .274 .231
1.50 .436 .366 .310 .396 .337 .287 .308 .265
Room 2.00.492 .426 .371 .448 .392 .344 .359 .319
index
2.50 .532 .472 .419 .486 .435 .390 .399 .361
3.00 .561 .504 .454 .513 .465 .422 .427 .391
4.00 .602 .552 .507 .552 .510 .472 .470 .438
5.00 .626 .581 .539 .575 .537 .502 .495 .466
10.00 .697 .668 .640 .645 .621 .597 .575 .556
Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

cd/1000lm
0%0%.072
.107
.150
.187
.218
.266
.306
.334
.377
.403
.489

Coeﬃcient of utilization
70%
50%
30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%
tance
10%
Floor
0.60 .220 .160 .117 .197 .145 .107 .130 .096
0.80 .275 .211 .163 .247 .191 .149 .172 .135
1.00 .326 .261 .212 .293 .237 .194 .215 .177
1.25 .371 .306 .256 .334 .279 .235 .252 .215
1.50 .405 .343 .292 .365 .312 .268 .283 .245
Room 2.00.455 .397 .347 .411 .362 .319 .328 .292
index
2.50 .492 .437 .391 .445 .399 .360 .363 .329
3.00 .517 .467 .422 .469 .426 .389 .388 .356
4.00 .554 .509 .469 .504 .466 .433 .425 .397
5.00 .576 .535 .498 .524 .490 .459 .447 .421
10.00 .639 .613 .588 .586 .564 .544 .518 .501

180゜
150゜150゜
120゜120゜90゜90゜
255060゜60゜75
30゜

HZAB10
HF100X
4200m80%

10030゜Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

1250゜

HZAB25
Coeﬃcient of utilization
70%
50%30%CeilingReﬂec Wall 50% 30% 10% 50% 30% 10% 30% 10%tance
10%Floor
0.60 .212 .152 .110 .194 .141 .103 .131 .096
0.80 .267 .203 .156 .245 .189 .146 .175 .137
1.00 .319 .254 .205 .293 .237 .193 .220 .182
1.25 .363 .300 .250 .334 .279 .235 .260 .2211.50 .398 .336 .286 .367 .313 .270 .291 .253
Room 2.00.448 .390 .341 .413 .364 .322 .339 .302
index
2.50 .484 .431 .385 .448 .402 .363 .375 .341
3.00 .510 .460 .416 .472 .430 .392 .401 .369
4.00 .547 .503 .464 .508 .471 .437 .440 .411
5.00 .568 .529 .492 .528 .495 .464 .463 .436
10.00 .631 .605 .581 .590 .569 .549 .534 .517
Lighting Fittings
Lamp
Lamp Lumens
Lamp Output Ratio

HZAB25
HF250X
12700m71%

cd/1000lm
0%0%.073.109.150.186.216.261.298.324.364.388.466

180゜150゜

150゜120゜120゜90゜90゜
255060゜60゜75
30゜10030゜1250゜

12HZAB40
HF400X
22000m73%

cd/1000lm
0%
0%

.069
.101
.139
.171
.198
.240
.274
.298
.335
.358
.433

180゜
150゜150゜120゜120゜90゜90゜
255060゜60゜75
30゜

100
125
0゜30゜