DIESEL ENGINE DRIVEN GENERATOR〈SOUNDGENERATO SOUND PROOF
GENERATO〈SOUNDPROOFTYPE〉
TYPETYPE〉

DCA-45LSK2

Quality and Endurance for commercial use
This high quality generator for commercial uses stronger windings, compared to other products. Due to the low noise level it qualifies
especially for loads from inverters or electric devices like computers etc. Excellent starting performance due to the low transient reactanceand the unique excitation system.

Dual Voltage System
For companies that operate internationally or have motors that require power at different voltages, a different generator
is usually required for each voltage setting. However, the DCA-45LSK2 is equipped with a dual voltage system,
so one generator can be used to power motors with different voltage settings. An extremely convenient feature.

Equipped With Clean Engine
We work on improving environmental performance and has assembled a line of environmentally friendly engine-drivengenerators. Compliant with the Japanese exhaust gas regulations (StageⅢ ).

Quiet Operation
Exceptionally quiet operation accomplished through the use of state-of-the-art
soundproofing technology. DCA-45LSK2 is designed “Low noise constructionequipment” by the MLIT Japan.

DIESEL ENGINE DRIVEN GENERATOR<SOUND PROOF TYPE>
Control Panel with Outstanding User-Friendliness
Denyo’s generators feature a functional panel layout thatcan be easily operated even by first-timers.
(1)(9) (7) (2) (5)(4) (3)(17)(6)

DCA-45LSK2
Provision of Various Protective
Devices and Warning Lamps-A circuit breaker is provided to protect the generator fromshorting of the load circuit or an overload.
-An emergency stop device is provided to automaticallydetect an engine malfunction and shut down the unit aswell as a warning lamp.

(14)
(15)
(16)

OperationDisplay
ItemLow Oil Pressure
High water temperatureOver Current
Earth leakage
Insufficient charging
Low fuel level
Air Element Blinding
Over-speed

(18)

(13)

(10) (11) (12)(8)( 1 ) Indicator(10) Speed Changeover Switch( 2 ) AC Ammeter(11) Preheat Lamp/Warning Lamp

( 3 ) Voltmeter(12) Starter Switch( 4 ) Pilot Lamp

(13) Frequency Changeover Switch( 5 ) Panel Light(14) Indicator(Oil Pressure)( 6 ) Circuit Breaker(15) Indicator(Water Temperature)( 7 ) Panel Light Switch(16) Fuel Level Indicator( 8 ) Voltage Regulator(17) Earth Leakage Relay( 9 ) Frequency Meter(18) Hour MeterMarkEngine
Shut down

Circuit breaker
will trip

Alarm Lamp–––––––––––––: Operates Mark – :Does not operate

Earth Leakage Relay
DCA-45LSK2 is equipped with Earth Leakage
Relay to prevent electric shock.

Output Terminal
Emergency Stop Button

SPECIFICATION TABLE

DCA-45LSK2MODELUNIT

A LT E R N AT O RFrequency
Output RatingkVA
No. of Phases
Rated Voltage
Power Factor
Voltage Regulation
Excitation
Insulation

HzContinuousStandbyV%50373760
45453-Phase,4-Wire
190-240V
190-220V
380-480V
380-440V
0.8(Lagging)Within ±0.5
Brushless , rotating exciter(With A.V.R)
Class H

Dimensions

LengthWidthHeight

Dry Weightmmmmmm
kg

1850
880
1250
935

SOUND LEVEL
7m dB(A) *25760*1 Fuel consumption is based on operation at 75% load.
*2 Sound level reflects high-speed no-load operation and is calculated byaveraging the measurements at four points, each 7 meters from the source.

ENGINE
Maker & Model
TypePs/rpm
kW/min -1No.of Cylinders-Bore ×Stroke mm
Piston Displacement
FuelL/h*1
Fuel Consumption
L
Lube Oil Sump Capacity
LCoolant Capacity
Battery×Quantity
Fuel Tank Capacity
LEngine Emissions

Output Rating

Kubota V3600-T-K3A
Inlined, Swirl Chambered
51.3/1800
45.0/1500
37.7/1800
33.1/1500
4-98×120
3.620
ASTM No. 2 Diesel Fuel or Equivalent
8.9
7.1
13.2
10.9
115D31R×1100
StageⅢ (Japanese)
The specifications given herein are subject to change without notice.

May.2023