RAPPLICATION & ASSEMBLY INSTRUCTION
powerCON | Locking 3 pole Power Connector
NAC3FXXA-W-* & NAC3FXXB-W-*®

A

APPLICATION & SAFETY INSTRUCTIONAPPLICATION:· The powerCON system is certified as a connector with breaking capacity according

IEC / EN / UL / CSA-C22.2 No. 60320-1.
· It is intended for use as an appliance coupler and interconnection coupler.
· It serves to supply power to an appliance and from an appliance to other equipment.
· To be installed by qualified person only.

Connector Combination & Keyways:
With the two non-interchangeable types of connectors (A type and B type) it is impossible to produce a short circuit.
Mating connectors (combination) are identified by mechanical keyways and by color.
APPLIANCE INLETAPPLIANCE OUTLET

A type (color coding blue)
Power IN

B type (color coding gray)Power OUT

NAC3FXXA-W-*

NAC3FXXB-W-*

Approval based:

IEC/EN 60320-1

UL 60320-1
CAN/CSA-C22.2 No. 60320-1

Rating:250 V ac / 16 A

127 V ac / 20 A

Wire size:

1.5 - 2.5 mm2

16 - 12 AWG*-S:

6.0 - 12.0 mm (0.24 - 0.47")

6.0 - 12.0 mm (0.24 - 0.47")*-L:

10.0 - 16.0 mm (0.39 - 0.63")

10.0 - 16.0 mm (0.39 - 0.63")

Cable O.D.:

CABLE LIST
Cable: IEC/EN 60320-1
H07RN-F
H05RN-F
H05VV-F

3 x 1.5 mm2

3 x 2.5 mm2-S-S-S-L-S

Cable: UL 60320-1, CAN/CSA-C22.2 No. 60320-1
SOOW
SJOOW
SJTOOW

16/3 AWG

14/3 AWG

12/3 AWG-S-S-S-L-S-S-L-L-Sð
BDA 639

Page 1ASSEMBLY INSTRUCTION I Locking 3 pole powerCONBASSEMBLY INFORMATIONA

2.

Place the bushing (1) and chuck (2) over the cable.
Important: Chuck and Bushing cannot be placed
over the cable after the assembly of the insert.

1.

(3) For easier assembly please use a cablelubricant.

3.

B

Prepare cable as shown.
IEC/EN 60320-1

UL60320-1
CAN/CSA-C22.2 No. 60320-1

Cable O.D.:
S: 6.0 - 12.0 mm (0.24 - 0.47")
L: 10.0 - 16.0 mm (0.39 - 0.63")

24 mm[0.94”]

9 mm[0.35"]

Cable O.D.:
S: 6.0 - 12.0 mm (0.24 - 0.47")
L: 10.0 - 16.0 mm (0.39 - 0.63")

PE 27 mm [1.06”]

CL

Torque Value 0.7 Nm(6.2 inch pound / 0.52 lb.ft)

TypicalWiring

IEC/EN60230-1

L ÞN Þbrown
bluegreen / yellowÞLN

9 mm[0.35"]

PE 27 mm [1.06”]

Torx size
T8

UL60320-1
CAN/CSA-C22.2 No. 60320-1[0.94”]

Slide the cable into the contacts and clamp with thescrew with Torx size T8.

IEC/EN 60230-1

N24 mm

UL60320-1
CAN/CSA-C22.2
No. 60320-1
blackwhitegreen

32.

D
Important:
Push and turnsimultaneously.

41.

Position chuck (1) on insert (2).
Slide insert (2) with chuck (1) together intohousing (3).
Important: Align the chuck by positioning the noseinto keyway.
Slide bushing (4) over chuck (1).

BDA 639ðPage 2ASSEMBLY INSTRUCTION I Locking 3 pole powerCON

E27 mm 1 1/8 inch
Hex bit7
NeutrikHTLACA

5
Torque Value 2.5 Nm(22 inch pound / 1.8 lb-ft)

4
6

Hold the connector with the NEUTRIK tool (5) andtighten bushing with the NEUTRIK tool (6) asshown.
For an exact mounting position use a torquewrench with 27 mm (1 1/8 inch) hex bit (7) andtighten it with 2.5 Nm (22 inch pound / 1.8 lb-ft).
Neutrik
HTLACBNEUTRIK tool Information:

C(5)HTLACA(6)

HTLACB

DISASSEMBLY INFORMATIONFOR DISASSEMBLY!
1.
2.

Use the Neutrik tool HTLACB.
Position the tool on the surfaces and open theclamping sleeve.

HTLACBð
BDA 639

Page 3

ASSEMBLY INSTRUCTION I Locking 3 pole powerCON

DSAFETY INFORMATIONCAUTIONTo ensure protection category, do not expose the connection tobending forces (e.g. do not attach loads to the cable, no freedangling cable windings etc.).

LIECHTENSTEIN

FORCESAFETY WARNING
For safety and certification reasons the connector must bereplaced in case of any broken parts or excessive wear and tear.

E

More Information on the www.neutrik.com

https://www.neutrik.com/products/audio/powercon

Neutrik AG
Neutrik USA Inc.
Neutrik (UK) Ltd.
Neutrik Vertriebs GmbHLIUSAUK
DE / NL / AT/DK

T: +423 / 237 24 24
T: +1 704 / 972 3050
T: +44 1983 / 811 441
T: +49 8131 / 280 890

F: +423 / 232 53 93
F: +1 704 / 438 9202
F: +44 1983 / 811 439
F: +49 8131 / 280 830

Neutrik France
Neutrik Tokyo Ltd.
Neutrik Hong Kong Ltd.

FRJPHK

T: +33 1 / 4131 6750
T: +81 3 / 3663 4733
T: +852 / 2687 6055

F: +33 1 / 4131 0511
F: +81 3 / 3663 4796
F: +852 / 2687 6052

Draft. Nr.: BDA 639 V1 I Update: 2022-11-16 I Data subject to change without prior notice. © 2022 NEUTRIK®. NEUTRIK® are registered trademark of Neutrik AG. ALL RIGHTS RESERVED.
R

www.neutrik.com

Page 4