Frequency inverters M-MaxTM, H-MaxTM
Frequency inverters permit the continuously variable speed control of three-phaseasynchronous motors, by converting a one- or three-phase alternating current of specificfrequency and voltage amplitudes into a three-phase alternating current with variable
voltage amplitude.
The M-MaxTM and H-MaxTM device series find universal application:
Device series M-MaxTM is preferred in machinery construction; device series H-MaxTM
is primarily used in heating, ventilation and air conditioning (HVAC).
Frequency inverters M-MaxTM
Output voltage with sinusoidal evaluated Pulse-Width Modulation (PWM) for voltage/frequency
control (U/f control) and voltage-steered vector control
MMX…-N…: Compact construction type in three sizes, protection type IP20
MMX…-F…: Compact construction type in three sizes, protection type IP20, with internal radio
interference suppression filter (EMC)
MMX12…, MMX32…: Nominal current 1.7 – 9.6 A with 230 V single phase mains connection,
assigned motor power 0.25 – 2.2 kW (230 V) ￫ Page 10/5
MMX34…: Nominal current 1.3 – 14 A with 400 V three-phase mains connection, assigned
motor power 0.37 – 7.5 kW (400 V) ￫ Page 10/7

Eaton After Sales Service
Extended warranty for
authorized commissioning￫ Chapter 22

Frequency inverters H-MaxTM
Output voltage with sinusoidal evaluated Pulse-Width Modulation (PWM) for voltage /frequency control (U/f control) and sensorless flow vector control
HMX…1-B: Compact construction type in five sizes, protection type IP21, with internal radio
interference suppression filter (EMC) and intermediate circuit choke
HMX…2-B: Compact construction type in six sizes, protection type IP54, with internal radio
interference suppression filter (EMC) and intermediate circuit choke
HMX32…: Nominal current 3.7 – 310A with 230 V three-phase mains connection , assigned
motor power 0.75 – 90 kW (230 V) ￫ Page 10/10
HMX34…: Nominal current 3.4 – 310 A with 400 V three-phase mains connection, assigned
motor power 1.1 – 60 kW (400 V) ￫ Page 10/12

2010 CA08103002Z-EN   www.eaton.com

Frequency inverters

System overview
Frequency inverter M-Max™

10/2

Description
Frequency inverter M-Max™

10/3

Frequency inverters M-Max™ in overview

10/4

Ordering
Frequency inverter M-Max™

10/5

System overview
Frequency inverter H-Max™

10/8

Description
Frequency inverter H-Max™

10/9

Ordering
Frequency inverter H-Max™

10/10

Description
Braking resistances

10/13Interface cards

10/14

Mains chokes, motor chokes

10/16

Ordering
Accessories for M-Max™, H-Max™
Braking resistances

10/17Interface cards

10/18

Radio interference suppression filters

10/19

Enclosure accessories

10/19

Mains chokes

10/20

Motor chokes

10/21

Engineering
F

Q

R

K

T

BACK
RESET
OK

R

3~

LOC
REM

I

R

3

3

10/22

Components of the Power Drives System (PDS)

10/23

Connecting example for M-Max™

10/26

Assigned switching and protective elements for
M-Max™

10/28

Assigned switching and protective elements
for H-Max™

10/30

M
3~

Technical dataaa1oFrequency inverter M-Max™

10/32

Mains chokes, motor chokes

10/36

Dimensions
b1bM

M-Max™, H-Max™ key to part numbersFrequency inverter M-Max™

10/38

Frequency inverter H-Max™

10/39

Braking resistances

10/41

Radio interference suppression filters

10/42

Mains chokes, motor chokes

10/43

10/2

Frequency inverters
M-Max™

System overview
M-Max™

1

2

4
6

3

5

Basic device

System accessories

Frequency inverters

1

MMX12…
Mains: single-phase, 230/240 V
Assigned motor ratingfrom 0.25 up to 2.2 kW (230 V)￫ Page 10/5
MMX32…
Mains: 3-phase, 230/240 V
Assigned motor ratingfrom 0.25 up to 2.2 kW (230 V)￫ Page 10/6
MMX34…
Mains: 3-phase, 400/480 V
Assigned motor ratingfrom 0.37 up to 7.5 kW (400 V)￫ Page 10/7

2010 CA08103002Z-EN

www.eaton.com

Communication module

Accessories
3

Versions• CANopen fieldbus connection• PROFIBUS DP fieldbus connection• DeviceNet fieldbus connection￫ Page 10/18

PC interface card

For fieldbus connection￫ Page 10/18

4￫ Page 10/20

Motor chokes

4￫ Page 10/21
6

Braking resistor￫ Page 10/17

MMX-COM-PC communication
module￫ Page 10/18

Mounting frame

Mains chokes

25Frequency inverters

10/3

M-Max™

Description
M-Max™

Application

Features

Functions

Documentation

The frequency inverters of the
M-Max™ series allow a continuously
variable speed control of three-phaseasynchronous motors. They are
specially suited for applications inwhich ease of handling and costeffectiveness have a high priority.
The characteristics-controlled voltage/frequency (U/f) control alreadyallows a wide range of applications
even with the default settings: from
simple pump and fan drives, standard
packaging applications to theoperation of multiple motors inhorizontal transportation andconveying.
With sensorless vector control, an
individual drive can also be used indemanding applications, in which ahigh torque and concentricity in thelower speed range are vital, such as in
the plastics and metal industries, thetextile, paper and printing industries orin crane and elevator systems.
Rated operational currents from 1.4 to
21 A allow the operation of standard
four-pole asynchronous motors in an
assigned rating range of:• Compact design through state-ofthe-art IGBT modules• Integrated radio interference
suppression filter (EMC)• Keypad with backlit LCD display• 6 digital inputs (24 V DC) for sinkand source-type control• 2 relays (1 changeover contact,
1 normally open contact, 230 V)• 1 transistor output (N/O or N/C,
48 V DC)• 2 analog inputs (0 to +10 V, 4 to
20 mA), selectable and scaleable• 1 analog output (0 to +10 V),
scaleable• 1 serial interface (RS485, Modbus
RTU)• Built-in braking transistor with size
MMX34…
• Optional fieldbus connection(CANopen, PROFIBUS-DP,
DeviceNet)• User-friendly commissioning
through fast configuration andapplication menu
• Compliance with global standards to
CE, UL, c-UL and c-Tick

A comprehensive range of protection
functions allow safe operation and theprotection of frequency inverter, motor
and application. They offer protection
against:An instructional leaflet and a CD are
included with each frequency inverterof the M-Max™ series.
The instructional leaflet is a quick
guide with illustrations and notes in
23 languages about the correct
handling, mounting and electricalconnection of the device. The CDcontains the instructional leaflet aswell as the Hardware and Engineering
manual in several languages.
The current documentation is alsoavailable for download fromwww.moeller.net/support• 0.25 to 2.2 kW at 230 V(single-phase mains connection),• 0.25 to 2.2 kW at 230 V(three-phase mains connection),• 0.37 to 7.5 kW at 400 V(three-phase mains connection).

• Overcurrent, ground fault• Overload (electronic motor
protection)• Overtemperature• Overvoltage, undervoltage
Further functions are:
• Restart inhibit• U/f control or sensorless vector
control• Double starting current and1.5 times overcurrent• PID controller• Sequence control• Braking control (DC braking)• 8 fixed frequencies• Electronic motor potentiometer• Logic function (AND, OR, XOR)
• Upper and lower frequency andcurrent limits• Frequency hopping (frequency
masking)• DC braking before start and up to
motor standstill• 2 parameter sets

2010 CA08103002Z-EN

www.eaton.com

10/4

Frequency inverters
M-Max™ frequency inverter
MMX...

M-Max™ frequency inverter

MMX12…
230 V

MMX32…
230 V

MMX34…
400 V●
50/60 Hz ±10 %1.7 - 9.6 A1)
100 % Ie, continuous current at
max. +50 °C
200 % Ie for 2 s every 20 s
150 % Ie for 60 s every 600 s
0.25 - 2.2 kW1)●
50/60 Hz ±10 %1.7 - 11 A1)
100 % Ie, continuous current at
max. +50 °C
200 % Ie for 2 s every 20 s
150 % Ie for 60 s every 600 s
0.25 - 2.2 kW1)●
50/60 Hz ±10 %1.3 - 14 A1)
100 % Ie, continuous current at
max. +50 °C
200 % Ie for 2 s every 20 s
150 % Ie for 60 s every 600 s
0.37 - 7.5 kW1)

-10 - +50 °C
U/f control, sensorless vector control
1 - 16 kHz (default settings: 6 kHz)
0 - ULN V
0 - 50 Hz (default settings: 50 Hz)-10 - +50 °C
U/f control, sensorless vector control
1 - 16 kHz (default settings: 6 kHz)
0 - ULN V
0 - 50 Hz (default settings: 50 Hz)-10 - +50 °C
U/f control, sensorless vector control
1 - 16 kHz (default settings: 6 kHz)
0 - ULN V
0 - 50 Hz (default settings: 50 Hz)● (for MMX…F…)● (for MMX…N…)-● (for MMX…F…)● (for MMX…N…)-● (for MMX…F…)● (for MMX…N…)-●● (optional)●
LCD, 7 segment●● (optional)●
LCD, 7 segment●● (optional)●
LCD, 7 segment

RS485, Modbus RTU,
system interface
CANopen or PROFIBUS-DP

RS485, Modbus RTU,
system interface
CANopen or PROFIBUS-DP

RS485, Modbus RTU,
system interface
CANopen or PROFIBUS-DPPID controller
Internal brake chopper

6 (max. +30 V DC, Ri > 12 kΩ)
1 (max. 48 V DC, max. 50 mA)
2 (0 - +10 V, 4 - 20 mA)
1 (0 - +10 V, max. 10 mA)
2 (1 normally open contact, 1 changeover contact, 250 V, max.°2 A)●-

6 (max. +30 V DC, Ri > 12 kΩ)
1 (max. 48 V DC, max. 50 mA)
2 (0 - +10 V, 4 - 20 mA)
1 (0 - + 10 V, max. 10 mA)
2 (1 normally open contact, 1 changeover contact, 250 V, max.°2 A)●-

Production quality
Product standard, regulation
Approval, Certification

RoHS, ISO 9001
IEC61800-3, UL508C
CE, UL, cUL, c-Tick

RoHS, ISO 9001
IEC61800-3, UL508C
CE, UL, cUL, c-Tick

6 (max. +30 V DC, Ri > 12 kΩ)
1 (max. 48 V DC, max. 50 mA)
2 (0 - +10 V, 4 - 20 mA)
1 (0 - + 10 V, max. 10 mA)
2 (1 normally open contact, 1 changeover contact, 250 V, max.°2 A)●● (from 3.3 A rated operational
current Ie)
RoHS, ISO 9001
IEC61800-3, UL508C
CE, UL, cUL, c-Tick

Notes

1) The principle here is that the range is not covered by a single device but by the entire device group.

Rated operational voltage Ue
System configuration
1 AC 208 V - 15 % … 240 V + 10 %3 AC 208 V - 15 % … 240 V + 10 %3 AC 380 V - 15 % … 480 V + 10 %Mains frequency
Rated operational current Ie
Rated operational current
Starting current
Overload current
Assigned motor rating at rated
operational voltage ULN
Operating temperature
Operating mode
Pulse frequency (sinusoidal PWM)
Output voltage
Output frequency
Radio interference suppression filter(EMC)
Internal
Optional
DC link choke
Protection type
IP20
IP21/NEMA1
IP54
KeypadDisplay
Communication interface
Internal
Optional
Control signal terminals
Digital input
Digital output
Analog input
Analog output
RelaysFor specific data of the individual performance values ￫ Ordering

2010 CA08103002Z-EN

www.eaton.com

Frequency inverters

10/5

M-Max™ frequency inverter
MMX...

HPL10005EN

Ordering
M-Max™ frequency inverter

Rated operational current
frequency
inverter1)

Assigned
motor rating(50/60 Hz)2)

Rated
operational
current motor

Ie

P

Ie

A

kW

A

1.7

0.25

1.4

2.4

0.37

2

2.8

0.55

2.7

3.7

0.75

3.2

4.8

1.1

4.6

7

1.5

6.3

9.6

2.2

8.7

With internal radio
interference suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Without internal
radio interference
suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Rated operational voltage 1 AC 230 V

OK

MMX12AA1D7F0-0
121363
MMX12AA2D4F0-0
121364
MMX12AA2D8F0-0
121365

1 off

MMX12AA1D7N0-0
122660
MMX12AA2D4N0-0
122661
MMX12AA2D8N0-0
122662

1 off

I

MMX12AA3D7F0-0
121366
MMX12AA4D8F0-0
121367
MMX12AA7D0F0-0
121368

MMX12AA3D7N0-0
122663
MMX12AA4D8N0-0
122664
MMX12AA7D0N0-0
122665

MMX12AA9D6F0-0
121369

MMX12AA9D6N0-0
122666

OK

I

OK

I

Notes

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +50 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors with 1500 rpm (at 50 Hz)

or 1800 rpm (at 60 Hz)
Information relevant for export to North America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
E134360
NMMS, NMMS7
UL report applies to both US and Canada
3211-06
UL Listed, certified by UL for use in Canada
Branch circuits
1~ 240 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP20; optionally UL/CSA NEMA 1

2010 CA08103002Z-EN

www.eaton.com

10/6

Frequency inverters
M-Max™ frequency inverter
HPL10006EN

Rated operational current
frequency
inverter1)

Assigned
motor rating(50/60 Hz)2)

Rated
operational
current motor

Ie

P

Ie

A

kW

A

1.7

0.25

1.4

2.4

0.37

2

2.8

0.55

2.7

3.7

0.75

3.2

4.8

1.1

4.6

7

1.5

6.3

9.6

2.2

8.7

With internal radio
interference suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Without internal
radio interference
suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Rated operational voltage 3 AC 230 V

OK

MMX32AA1D7F0-0
121390
MMX32AA2D4F0-0
121391
MMX32AA2D8F0-0
121392

1 off

MMX32AA1D7N0-0
122667
MMX32AA2D4N0-0
122668
MMX32AA2D8N0-0
1226691 off

I

MMX32AA3D7F0-0
121393
MMX32AA4D8F0-0
121394
MMX32AA7D0F0-0
121395

MMX32AA3D7N0-0
122670
MMX32AA4D8N0-0
122671
MMX32AA7D0N0-0122672

MMX32AA011F0-0
121396

MMX32AA011N0-0
122673

OK

I

OK

I

Notes

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +50 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors with 1500 rpm (at 50 Hz)

or 1800 rpm (at 60 Hz)
Information relevant for export to North America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
E134360
NMMS, NMMS7
UL report applies to both US and Canada
3211-06
UL Listed, certified by UL for use in Canada
Branch circuits
1~ 240 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP20; optionally UL/CSA NEMA 1

Frequency inverters

10/7

M-Max™ frequency inverter
HPL10007EN

Rated operational current
frequency
inverter1)

Assigned
motor rating(50/60 Hz)2)

Rated
operational
current motor

Ie

P

Ie

A

kW

A

1.3

0.37

1.1

1.9

0.55

1.5

2.4

0.75

1.9

3.3

1.1

2.6

4.3

1.5

3.6

5.6

2.2

5

7.6

3

6.6

9

4

8.5

12

5.5

11.3

14

7.5

15.2

With internal radio
interference suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Without internal
radio interference
suppression filter
Part no.
Article no.

Price
See
price list

Std. pack

Rated operational voltage 3 AC 400 V

OK

MMX34AA1D3F0-0
121397
MMX34AA1D9F0-0
121398
MMX34AA2D4F0-0
1213991 off

MMX34AA1D3N0-0
122674
MMX34AA1D9N0-0
122675
MMX34AA2D4N0-0
122676

1 off

I

MMX34AA3D3F0-0
121400MMX34AA4D3F0-0
121401
MMX34AA5D6F0-0
121402

MMX34AA3D3N0-0
122677
MMX34AA4D3N0-0
122678
MMX34AA5D6N0-0
122679

MMX34AA7D6F0-0
121403
MMX34AA9D0F0-0
121404
MMX34AA012F0-0
121405
MMX34AA014F0-0
122684

MMX34AA7D6N0-0
122680MMX34AA9D0N0-0122681
MMX34AA012N0-0
122682
MMX34AA014N0-0
122683

OK

I

OK

I

Notes

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +50 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors with 1500 rpm (at 50 Hz)

or 1800 rpm (at 60 Hz)
Information relevant for export to North America

Product Standards
UL File No.
UL CCNCSA File No.
CSA Class No.
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
E134360
NMMS, NMMS7
UL report applies to both US and Canada
3211-06
UL Listed, certified by UL for use in Canada
Branch circuits
1~ 240 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP20; optionally UL/CSA NEMA 1

2010 CA08103002Z-EN

www.eaton.com

10/8

Frequency inverters
H-Max™

System overview
H-Max™

1

4

2

3

Basic device

System accessories

Frequency inverters

1

HMX32…
Mains: 3-phase, 230/240 V
Assigned motor ratingfrom 0.75 to 90 kW (230 V)￫ Page 10/10
HMX34…
Mains: 3-phase, 400/480 V
Assigned motor ratingfrom 1.1 to 160 kW (400 V)￫ Page 10/12

2010 CA08103002Z-EN

www.eaton.com

Communication module
Versions• CANopen fieldbus connection• PROFIBUS DP fieldbus connection• DeviceNet fieldbus connection￫ Page 10/18

Accessories
4

Motor chokes

2￫ Page 10/21

Braking resistor￫ Page 10/17

3

Frequency inverters

10/9

H-Max™

Description
H-Max™

Application

Features

Functions

Documentation

H-Max™ frequency inverters are
specially suitable for continuously
variable speed control of three-phaseasynchronous motors in heating,ventilation and air conditioning (HVAC)
applications. A comprehensive rangeof control and function modules allow
an automatic changeover in applications with severalmotors, cascade andbypass controllers and direct control
of non-stabilized motors.
The devices of the H-Max™ series
support energy-optimized applications
with fluid flow machines (pumps, fans).
They allow the PID controllers tomaintain a constant conveying
pressure in booster stations regardless of throughput. A fire control ensures reliable operation of pumps insprinkler systems.
The network protocols relevant for
HVAC applications – BACNet andModbus – are included onboard as
standard in two versions (RS485,
Ethernet).
With this comprehensive range ofsetting options, ease of handling isimportant. The frequency inverters arepreset for the assigned motor rating
and can be taken into operation
without any parameterization
required. A clear, comprehensivegraphic display shows all relevant
drive parameters. Two enclosure
versions with IP21 and IP54 protection
types are available for individual
installation.
For the operation of standard threephase asynchronous motors thedevices supply rated operational
currents of 3.4 to 310 A for assigned
shaft ratings of:• Compact design through state-ofthe-art IGBT modules• Integrated radio interference
suppression filter (EMC)• Integrated DC link choke• Plug-in keypad with backlit graphic
LCD display• 6 digital inputs (24 V DC) for sinkand source-type control• 3 relays (2 changeover contacts,
1 N/O, 230 V) on a plug-in card, canbe replaced with other relay
configurations or additional digital
and analog inputs and outputs• 2 analog inputs (0 to +10 V, 4 to
20 mA), selectable and scaleable• 1 analog output (0 to +10 V),
scaleable• 1 serial interface (RS485, Modbus
RTU)• Internal braking transistor• 2 slots for optional fieldbus connection (CANopen, PROFIBUS-DP,
DeviceNet, LonWorks)• User-friendly commissioning
through fast configuration andapplication menu
• Compliance with global standards to
CE, UL, c-UL and c-Tick

A comprehensive range of protection
functions allow safe operation and theprotection of frequency inverter, motor
and application. They offer protection
against:An instructional leaflet and a CD are
included with each frequency inverterof the H-Max™ series.
The instructional leaflet is a quick
guide with illustrations and notes in
23 languages about the correct
handling, mounting and electricalconnection of the device. The CDcontains the instructional leaflet aswell as the Hardware and Engineering
manual in several languages.
The current documentation is alsoavailable for download fromwww.moeller.net/support• Overcurrent, ground fault• Overload (electronic motor protection), underload, dry running• Overtemperature• Overvoltage, undervoltage
Further functions are:
• Flying restart circuit• Thermistor protection• Restart interlock, automatic restart• Actual/reference value monitoring• U/f control or sensorless vector
control• Double starting current and1.1 times overcurrent• 2 PID controllers• Sequencing, multi-motor andbypass control, cascading• Fire control• Automatic sleep and wake-up
function• Timer function (day/time control)• Braking control• DC braking before start and up to
motor standstill• 8 fixed frequencies• Electronic motor potentiometer• Logic function (AND, OR, XOR)
• Upper and lower frequency andcurrent limits• Frequency hopping (frequency
masking)• 2 parameter sets

• 0.75 to 90 kW at 230 V(three-phase mains connection),• 1.1 to 160 kW at 400 V(three-phase mains connection).

2010 CA08103002Z-EN

www.eaton.com

10/10Frequency inverters
H-Max™ Frequency inverter
HMX32...

HPL10010EN

Ordering
H-Max™ Frequency inverter

With internal radio
interference
suppression filter,
protection type IP21
Rated operational currentof frequency
inverter1)

Assigned
motor rating(50/60 Hz)2)

Rated
operational
current motor

Ie

P

Ie

A

kW

A

Part no.
Article no.

With internal radio
interference
suppression filter,
protection type IP54
Price
See price
list

Std. packPart no.
Article no.

Price
See pricelist

HMX32AG3D721-B
127151
HMX32AG4D821-B
127152
HMX32AG6D621-B
127153
HMX32AG8D021-B
127154
HMX32AG01121-B
127155
HMX32AG01221-B
127156

1 off

HMX32AG3D722-B
127170
HMX32AG4D822-B
127171
HMX32AG6D622-B
127172
HMX32AG8D022-B
127173
HMX32AG01122-B
127174
HMX32AG01222-B
127175

1 off

HMX32AG01821-B
127157
HMX32AG02421-B
127158
HMX32AG03121-B
1271591 off

HMX32AG01822-B
127176
HMX32AG02422-B
127177
HMX32AG03122-B
127178

1 off

HMX32AG04821-B
127160
HMX32AG06221-B
127161

1 off

HMX32AG04822-B
127179
HMX32AG06222-B
127180

1 off

Std. pack

Rated operational voltage 3 AC 230 V

BACK
RESET

LOC
REM

OK

I

BACK
RESET

OK

LOC
REM

3.7

0.55

2.7

4.8

0.75

3.2

6.6

1.1

4.6

8

1.5

6.3

11

2.2

8.7

12.5

3

11.5

18

4

14.8

24.2

5.5

19.6

31

7.5

26.4

48

11

38

62

15

51

I

BACK
RESET

OK

LOC
REM

I

Notes

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +40 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors with 1500 rpm(at 50 Hz) or 1800 rpm (at 60 Hz)
Information relevant for export to North America

Product Standards
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
Request filed for UL and CSA
Branch circuits
3~ 240 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP21; UL/CSA NEMA 1

Frequency inverters

10/11

H-Max™ Frequency inverter
HMX32...HMX34...

HPL10011EN
With internal radio
interference
suppression filter,
protection type IP21
Rated operational currentof frequency
inverter1)

Assigned
motor rating(50/60 Hz)2)

Rated
operational
current motor

Ie

P

Ie

A

kW

A

Part no.
Article no.

With internal radio
interference
suppression filter,
protection type IP54
Price
See price
list

Std. packPart no.
Article no.

1 off

HMX32AG07722-B
127181
HMX32AG08822-B
127182
HMX32AG10622-B
127183
HMX32AG14322-B
127184
HMX32AG17022-B
127185
HMX32AG20822-B
127186
HMX32AG26122-B
127187
HMX32AG31022-B
127188Price
See price
list

Std. pack

Rated operational voltage 3 AC 230 V

Notes

77

18.5

63

88

22

71

106

30

96

143

45

117

170

45

141

208

55

173

261

75

233

310

90

279

HMX32AG07721-B
127162
HMX32AG08821-B
127163
HMX32AG10621-B
127164
HMX32AG14321-B
127165
HMX32AG17021-B
127166
HMX32AG20821-B
127167
HMX32AG26121-B
127168
HMX32AG31021-B
1271691 off

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +40 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors with 1500 rpm(at 50 Hz) or 1800 rpm (at 60 Hz)
Information relevant for export to North America

Product Standards
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
Request filed for UL and CSA
Branch circuits
3~ 240 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP21; UL/CSA NEMA 1

2010 CA08103002Z-EN

www.eaton.com

10/12Frequency inverters
H-Max™ Frequency inverter
HMX34...

HPL10012EN

H-Max™ Frequency inverter

Rated operational current of
frequency
inverter1)

Assigned motor
rating(50/60 Hz)2)

Rated operational current
Motor

Ie

P

Ie

A

kWh

A

3.4

1.1

2.1

4.8

1.5

3.6

5.6

2.2

5

8

3

6.6

9.6

4

8.5

12

5.5

11.3

16

7.5

15.2

23

11

21.7

31

15

29.3

38

18.5

36

46

22

41

61

30

55

72

37

68

87

45

81

105

55

99

140

75

134

170

90

161

205

110

196

261

132

231

310

160

279

With integrated radio interference
suppression filter
Protection type IP21
Part no.
Price
Article no.
See pricelistWith integrated radio interference
suppression filter
Protection type IP54
Part no.
Price
Article no.
See pricelist

HMX34AG3D421-B
126928
HMX34AG4D821-B
126929
HMX34AG5D621-B
126940
HMX34AG8D021-B
126941
HMX34AG9D621-B
126942
HMX34AG01221-B
126943
HMX34AG01621-B
126944
HMX34AG02321-B
126945
HMX34AG03121-B
126946

HMX34AG3D422-B
126958
HMX34AG4D822-B
126959
HMX34AG5D622-B
126960
HMX34AG8D022-B
126961
HMX34AG9D622-B
126962
HMX34AG01222-B
126963
HMX34AG01622-B
126964
HMX34AG02322-B
126965
HMX34AG03122-B
126966

HMX34AG03821-B
126947
HMX34AG04621-B
126948
HMX34AG06121-B
126949

HMX34AG03822-B
126967
HMX34AG04622-B
126968
HMX34AG06122-B
126969

HMX34AG07221-B
126950
HMX34AG08721-B
126951
HMX34AG10521-B
126952
HMX34AG14021-B
126953
HMX34AG17021-B
126954
HMX34AG20521-B
126955
HMX34AG26121-B
126956
HMX34AG31021-B
126957

HMX34AG07222-B
126970
HMX34AG08722-B
126971
HMX34AG10522-B
126972
HMX34AG14022-B
126973
HMX34AG17022-B
126974
HMX34AG20522-B
126975
HMX34AG26122-B
126976
HMX34AG31022-B
126977

Std. pack

Rated operational voltage 3 AC 400 V

BACK
RESET

LOC
REM

OK

I

BACK
RESET

OK

LOC
REM

I

BACK
RESET

OK

1 off

LOC
REM

I

Notes

1) Rated operational current at an operating frequency of 6 kHz and an ambient temperature of +40 °C
2) Assigned motor rating for normal internally and externally ventilated four-pole, three-phase asynchronous motors

with 1500 rpm (at 50 Hz) or 1800 rpm (at 60 Hz)
Information relevant for export to North America
Product Standards
NA Certification
Suitable forMax. Voltage Rating
Degree of Protection2010 CA08103002Z-EN

www.eaton.com

UL 508C; CSA-C22.2 No. 14; IEC/EN61800-3; IEC/EN61800-5; CE marking
Request filed for UL and CSA
Branch circuits
3~ 480 V AC IEC: TN-S UL/CSA: "Y" (Solidly Grounded Wey)
IEC: IP21; UL/CSA NEMA 1

Frequency inverters

10/13

Braking resistors
BR...

Description
Braking resistors

BACK
RESET
OK

LOC
REM

I

BR2
BACK
RESET
OK

LOC
REM

I

MMX
R+

RBR…-T-SAF braking resistor in subassembly frame

Type overview

Type overview

BR1...-T-PF, BR3...-T-PF
Braking resistors

BR2..., BR2...-T-SAF
Braking resistors

Application

Function

Features

An external braking resistor isrequired for braking larger moments ofinertia or for prolonged regenerative
operation. This converts the motor’smechanical braking energy into heat.

The frequency inverter’s built-in
braking transistor automaticallyswitches in the connected braking
resistor as soon as the internal DC link
voltage exceeds the switching threshold. This prevents excessive voltages
on the internal DC link, which would
otherwise cause an overvoltage fault
message and the frequency inverter’spulse inhibitor to be set. The drive thencoasts to a halt uncontrolled.

BR2… is a short-circuit proof,
intrinsically safe braking resistor inan anodized aluminum enclosure withprotection type IP65 and without athermostat.

Features
These resistors are built into a perforated metal sheet enclosure andequipped with a thermostatic circuitbreaker (230 V, 1 A, AC-1). The enclosures are made of galvanized sheet
metal and are open at the bottom. Theyfulfil protection type IP65 only in theirfitted state.
With a combination of several seriesand parallel-connected resistors,
a higher braking power can beachieved. The braking resistors canbe connected directly to the brake
choppers of MMX34… frequency
inverters.

T1

2

1

i

PE

T2

RB

Note: When used according to UL
directives, the rating data forcontinuous braking and the maximum
pulse performance must be reduced
by 25%.
Caution: The surface temperature canexceed 100 °C!

• BR2...-T-SAF is a combination ofseveral braking resistors BR2…
braking resistors with a thermostat.
They are built into a subassembly
frame for the
M-Max™ frequency inverters.
• BR1...-T-PF is a braking resistor ora combination of several braking
resistors with a thermostat. It is
installed in an encapsulated
enclosure with protection type IP54
and protected against accidental
contact.
• BR3...-T-PF is a braking resistor
in a steel mesh design with athermostat. It is installed in an
encapsulated enclosure withprotection type IP54 and protectedagainst accidental contact.
• ...-T = with a thermostat• ...-SAF = subassembly frame• ...-PF = protection frame (protects
against accidental contact)

Documentation
The documentation can also be
obtained on the Internet from:www.moeller.net/support

2010 CA08103002Z-EN

www.eaton.com

10/14Frequency inverters
Interface cards
MMX-COM-PC, XMX-NET-DN-AInterface cards

Type overview

Type overview

MMX-COM-PC
PC connection for the frequency
inverters of M-Max™ series

XMX-NET-DN-A
DeviceNet fieldbus connection for
the frequency inverters of the
M-Max™ and H-Max™ series

Application
MMX-COM-PC allows communicationand data transfer between a frequency inverter and a PC.
The parameters can also be coplied
directly between frequency invertersof the same device series without a PC
connection. If a battery (9 V block) is
fitted, mains power supply is also not
required for this.

Application
XMX-NET-DN-A allows the connection as slave of the M-Max™ and
H-Max™ frequency inverters to thestandard DeviceNet field bus.
The fieldbus connection is implemented via pluggable 5-pole screw
terminals with the XMX-NET-PS-A anda 9-pole SUB-D connector with the
XMX-NET-PD-A.

Features
The MMX-COM-PC communication
module is plugged in at the front of
M-Max™ frequency inverters.
The connection cable included as
standard (length: 3.2 m) with anisolated interface converter allows
connection to a PC with a USB port.
This communication module can help
increase data security and cut
commissioning and maintenancetimes:• Online parameterization andmonitoring display (oscilloscope)on a PC; on a connected printerparameter lists and monitor displays
can also be printed out• Upload and download of allparameters• Parameter backup and comparison• Parameter copy function (e.g. forseries machines or for device
replacement)

Documentation
Instructional leaflet AWA8240-2428(included as standard with each card)
Documentation available for downloadat www.moeller.net/support

2010 CA08103002Z-EN

www.eaton.com

FeaturesOn the H-Max™ frequency inverters,interface card XMX-NET-DN-A isslotted into the housing.
On M-Max™ frequency inverters,
mounting frame MMX-NET-XA is
required. Here the interface card isconnected via a plug-in connector on
the right side of the frequency inverter.
Technical data:• Communication protocol: CAN• Data transfer:
ODVA 2.0 compliant• Transfer rate (adjustable):
125, 250 and 500 Kbit/s• Maximum cable length, dependingon transfer rate: 125 Kbits/s → 500 m,
250 Kbits/s → 250 m, 500 Kbit/s→ 100 m• Network supply: 11 to 25 V DC, 28 mA(typical), peak inrush current 125 mA• Addressing (adjustable): to 64 (nodes)• Status indication via LEDs

Documentation
Documentation available for downloadat www.moeller.net/support

Frequency inverters

10/15

Interface cards
XMX-NET-CO-A, XMX-PD-A, XMX-PS-A
Interface cards

Type overview

Type overview

XMX-NET-CO-A
CANopen connection for thefrequency inverters of the
M-Max™ and H-Max™ series

XMX-NET-PD-A, XMX-NET-PS-A
PROFIBUS-DP connection for thefrequency inverters of the
M-Max™ and H-Max™ series

Application

Application

XMX-NET-CO-A allows the connection
as slave of the M-Max™ and H-Max™
frequency inverters to the standard
CANopen field bus. They are connected to the field bus through 5-polescrew terminals.

XMX-NET-DP-... allows the connection as slave of the M-Max™ and
H-Max™ frequency inverters to thestandard PROFIBUS-DP field bus.
The XMX-NET-PS-A is connected to
the field bus through 5-pole plug-in
screw terminals and XMX-NET-PD-A
through a 9-pin Sub-D connector.

FeaturesOn the H-Max™ frequency inverters,
the XMX-NET-CO-A interface card isslotted into the housing.
On M-Max™ frequency inverters,
mounting frame MMX-NET-XA is
required. Here the interface card isconnected via a plug-in connector on
the right side of the frequency inverter.
Technical data:• Communications protocol:
CiA DS-301,• CiA-DSP-402• Data transfer: CAN (ISO 11898)• Transfer rate (adjustable): 10 Kbits/s
up to 1 Mbit/s• Maximum cable length, dependingon transfer rate (without amplifier):• 30 m up to 2.5 km• Addressing (adjustable): 1 - 127• Status indication via LEDs

Documentation
Instructional leaflet AWA8240-2426(included as standard with each card)
Manual AWB8240-1632
Documentation available for downloadat www.moeller.net/support

FeaturesOn the H-Max™ frequency inverters,
the XMX-NET-DP-... interface card isslotted into the housing.
On M-Max™ frequency inverters,
mounting frame MMX-NET-XA is
required. Here the interface card isconnected via a plug-in connector on
the right side of the frequency inverter.
Technical data:• Communication protocol: Profidrive(PROFIBUS profile for variablespeed drives)• Data transfer: RS485, half-duplex• PPO type: 1, 2, 3, 4, 5
• Transfer rate (adjustable): 9.6 Kbits/s
up to 12 Mbit/s• Maximum cable length, dependingon transfer rate (without amplifier):
100 m up to 1.2 km• Addressing (adjustable): 2 - 126• Status indication via LEDs

Documentation
Instructional leaflet AWA8240-2427(included as standard with each card)
Documentation available for downloadat www.moeller.net/support

2010 CA08103002Z-EN

www.eaton.com

10/16Frequency inverters
Mains chokes, motor chokes
DEX-LN…, DEX-LM3…

Mains chokes, motor chokesType overview

Type overview

DEX-LN1…
Mains chokes, single-phase

DEX-LM3…
Motor chokes, three-phase

DEX-LN3…
Mains chokes, three-phase

Application

FunctionsApplication

Functions

Mains chokes (also called mains
chokes) are connected in series on themains side of electronic devices, suchas frequency inverters.

Mains chokes attenuate any current
harmonics and peaks and limit thestarting current (internal DC link
capacitors). Through the reduction ofcurrent harmonics, the r.m.s. value ofthe absorbed current can be reduced
by up to 30 percent. In addition, mains
chokes permit a short-circuit voltage
to the mains (uk value) of about four
percent, which is often required.
Mains chokes also extend the lifespanof components (rectifier diodes, DC
link capacitors) in devices with an
input-side internal DC link (frequency
inverters, USPs).

Motor chokes are connected in series
to the output of frequency inverters.

Motor chokes reduce the edge
gradient of the output voltage(du/dt < 500 V/ms) of a frequency
inverter. They also reduce the motor’snoise emission and heat generation.
Through the use of motor chokes thepermissible motor cable length can beincreased to up to 200 meters. When
operating several motors in parallel atthe output of a single frequency
inverter, the use of motor chokes isrecommended, as they attenuate thehigh capacitive reactive currents.

Features
The DEX-LN… line reactors arevacuum-impregnated. Their air gaps
are therefore bridged with a lowfatigue, metallically and magneticallyneutral connection, which reduces
noise emission.
Note: Because of the flux distribution
caused by their physical design, motor
chokes should be installed at a
distance of at least 50 mm from metalparts and adjacent subassemblies.

Documentation
Every line reactor is supplied with an
instructional leaflet (AWA 8240-1711).
The documentation is also available
for download fromwww.moeller.net/support

2010 CA08103002Z-EN

www.eaton.com

Features
The DEX-LM3… motor chokes arevacuum-impregnated. Their air gaps
are therefore bridged with a lowfatigue, metallically and magneticallyneutral connection, which reduces
noise emission.
Motor chokes have larger dimensions
than comparable mains chokes withthe same rated operational current.
Note: Because of the flux distribution
caused by their physical design, motor
chokes should be installed at a
distance of at least 50 mm from metalparts and adjacent subassemblies.

Documentation
Every motor choke is supplied with an
instructional leaflet (AWA 8240-1711).
The documentation is also available
for download fromwww.moeller.net/support

Frequency inverters

10/17

Accessories for M-Max™
BR...

HPL10017EN
Accessories for M-Max™

Braking resistanceContinuous braking
power

R

PDB

Ω

W

For use withPart no.
Article no.

Price
See price list

Std. pack

Braking resistors
Protection type IP65
Short-circuit proof, intrinsically safe braking resistor in anodized aluminum enclosure, with thermostat
47

240

MMX34…

60

200

MMX34…

Short-circuit proof, intrinsically safe braking resistor with thermostat,with mounting frame for base (footprint) mounting
36
400

MMX34…

47

240

MMX34…

60

200

MMX34…

65

400

MMX34…

75

480

MMX34…

36

2450

MMX34…

36

2800

MMX34…

36

3600

MMX34…

36

500

MMX34…

36

1000

MMX34…

56

300

MMX34…

56

800

MMX34…

56

1000

MMX34…

BR2047240
140434
BR2060200
140433

1 off

BR2036400-T-SAF
140437
BR2047240-T-SAF
140436
BR2060200-T-SAF
140435
BR2065400-T-SAF
140438BR2075480-T-SAF
1404391 off

BR30362K4-T-PF141325
BR30362K8-T-PF141326
BR30363K6-T-PF141327

1 off

BR1036500-T-PF141323
BR10361K0-T-PF141324
BR1056300-T-PF141320BR1056800-T-PF141321
BR10561K0-T-PF141322

1 off

1 off

Protection type IP54

Protection type IP54

2010 CA08103002Z-EN

www.eaton.com

10/18Frequency inverters
Accessories for M-Max™ and H-Max™
Interface cards

HPL10018EN

Accessories for M-Max™ and H-Max™

Part no.
Article no.

Price
See price
list

Std. pack

Notes

Interface cards
For use with MMX…
PC connection (USB/RJ45) for the frequency inverters of M-Max series• With 3.2 m connection cable and interface converter• Data transfer with PC software and copy function (retentive memory)
between MMX... frequency inverters

MaxConnect

BACK
RESET
OK

USB

MMX-COM-PC
121406

1 off

MMX-NET-XA
134510

1 off

Mounting frame for sideconnection to M-Max™
frequency inverters

Std. pack

Notes

1 off

Mounting frame MMX-NET-XA
required for M-Max™

1 off

–

LOC
REM

COMM
ERROR
AC DRIVE

RJ 45

Mounting frame for XMX-NET... fieldbus interface cards
On M-Max™ frequency inverters

Accessories for H-Max™

Description

Part no.
Article no.

CANopen

Connection through plug-in screw terminals
The interface card is slotted into the device.

XMX-NET-CO-A
134511PROFIBUS-DP(Screw terminal)

Connection through plug-in screw terminals
The interface card is slotted into the device.

XMX-NET-PS-A136556

PROFIBUS-DP(Sub D)

Connection through Sub-D plug
The interface card is slotted into the device.

XMX-NET-PD-A136557

PROFINETThe interface card is slotted into the device.

DeviceNet

The interface card is slotted into the device.

XMX-NET-PN-A138237XMX-NET-DN-A
136558LON

The interface card is slotted into the device.

XMX-NET-LO-A138238

Digital I/O card

6 digital input (24 V DC)
6 digital outputs(transistor, 24 - 48 V DC)
24 V supply
1 relay (changeover contact, N/O/NC, 250 V, 2A)
1 relay (normally open contact, N/O, 250 V, 2 A)
1 thermistor input
1 analog input (0 -+ 10 V, 4 - 20 mA)
2 analog outputs (0 -+ 10 V, 4 - 20 mA)
3 relays (normally open contact, N/O, 250 V, 2 A)

XMX-IO-B1-A
138239For use with MMX... und HMX...

Price
See price
list

Fieldbus connection

Plug-in modules
For use with HMX...

Relay/thermistor
card

Analog I/O card
Relay card
PT100 card
Digital input/relay
card
Output card2010 CA08103002Z-EN

www.eaton.com

3 PT 100 thermistor inputs
24 V supply
1 relay (normally open contact, N/O, 250 V, 2 A)
5 digital inputs (42 - 240 V AC)
1 relay (normally open contact, N/O, 250 V, 2 A)
1 digital output (transistor, 24 - 48 V DC)
1 analog output (0 -+ 10 V, 4 - 20 mA)

XMX-IO-B2-A
138240–XMX-IO-B4-A
138241XMX-IO-B5-A
138242XMX-IO-B8-A
138243XMX-IO-B9-A
138244
XMX-IO-BF-A138245–––––

Frequency inverters accessories for M-Max™

10/19

Radio interference suppression filters, enclosure accessories
HPL10019EN
Radio interference suppression filters, enclosure accessories

Input current

For use withPart no.
Article no.

Price
See price
list

Std.
pack

Notes

MMX-LZ1-009
138231

1 off

For mounting next to or underneath the MMX...
for size FS1

MMX-LZ1-015
138232
MMX-LZ1-017
138233

1 off

For mounting next to or underneath the MMX...
for size FS2
For mounting next to or underneath the MMX...
for size FS3

MMX-LZ3-006
138234

1 off

For mounting next to or underneath the MMX...
for size FS1

MMX-LZ3-009
138235

1 off

For mounting next to or underneath the MMX...
for size FS2

MMX-LZ3-020
138236

1 off

For mounting next to or underneath the MMX...
for size FS3

ILN
ARadio interference suppression filters, single-phase
Maximum mains voltage ULN: 240 + 10 % V (50/60 Hz)
9

15
17

MMX12AA1D7…
MMX12AA2D4…
MMX12AA2D8…
MMX12AA3D7…
MMX12AA4D8…
MMX12AA7D0…
MMX12AA9D6…

1 off

Radio interference suppression filters, three-phase
Maximum mains voltage ULN: 480 + 10 % V (50/60 Hz)
6
MMX32AA1D7…
MMX32AA2D4…
MMX32AA2D8…
MMX32AA3D7…
MMX34AA1D3…
MMX34AA1D9…
MMX34AA2D4…
MMX34AA3D3…
9
MMX32AA4D8…
MMX32AA7D0…
MMX34AA4D3…
MMX34AA5D6…
22
MMX32AA9D6…
MMX34AA7D6…
MMX34AA9D0…
MMX34AA012…
MMX34AA014…
Enclosure accessories

For use withPart no.
Article no.

Price
See price list

Std. packEnclosure accessories
Increased protection type IP21/NEMA 1, two-part enclosure cover with cable retention clip for EMC-conformant
connection
For size FS1

For size FS2

For size FS3

MMX12AA1D7…
MMX12AA2D4…
MMX12AA2D8…
MMX32AA1D7…
MMX32AA2D4…
MMX32AA2D8…
MMX34AA1D3…
MMX34AA1D9…
MMX34AA2D4…
MMX12AA3D7…
MMX12AA4D8…
MMX12AA7D0…
MMX32AA3D7…
MMX32AA4D8…
MMX32AA7D0…
MMX34AA3D3…
MMX34AA4D3…
MMX34AA5D6…
MMX12AA9D6…
MMX32AA9D6…
MMX34AA7D6…
MMX34AA9D0…
MMX34AA012…
MMX34AA014…

MMX-IP21-FS1
121407

1 off

MMX-IP21-FS2
121408

1 off

MMX-IP21-FS3
1214091 off2010 CA08103002Z-EN

www.eaton.com

10/20Frequency inverters
Mains chokes
DEX-LN...

Mains chokes

HPL10020EN
Rated operational
current
Ie

InductanceLMax.
heat dissipation
Pv

A

mH

W

5.8

5.05

9

8.6

3.41

11

13

2.25

12

18

1.63

17

24

1.22

20

3.9

7.51

17

6

4.9

19

10

2.94

33

16

1.84

44

25

1.18

57

40

0.64

59

50

0.37

58

60

0.31

60

80

0.23

86

100

0.18

101

120

0.15

100

160

0.11

140

200

0.09

154

250

0.07

155

300

0.06

169

Part no.
Article no.

Price
See price list

Std. pack

Mains chokes, single-phaseMax. permissible mains voltage: 260 V +0 % (50/60 Hz)
DEX-LN1-006
269490
DEX-LN1-009
269495
DEX-LN1-013
269496
DEX-LN1-018
269497
DEX-LN1-024
269498

1 off

DEX-LN3-004
269500
DEX-LN3-006
269501
DEX-LN3-010
269502
DEX-LN3-016
269503
DEX-LN3-025
269504
DEX-LN3-040
269505
DEX-LN3-050
269506
DEX-LN3-060
269507
DEX-LN3-080
269508
DEX-LN3-100
269509
DEX-LN3-120
269510
DEX-LN3-160
269511
DEX-LN3-200
269512
DEX-LN3-250
269513
DEX-LN3-300
269514

1 off

Mains chokes, three-phaseMax. permissible mains voltage: 550 V +0 % (50/60 Hz)

2010 CA08103002Z-EN

www.eaton.com

Frequency inverters
HPL10021EN
Motor chokes

10/21

Motor chokes
DEX-LM3
Rated operational
current

Inductance

Ie

L

Max.
heat dissipation
at 12 kHz
Pv

A

mH

W

5

2

24

8

4.1

54

11

3

71

16

1.5

78

35

1

116

50

0.6

168

63

0.5

193

80

0.5

206

100

0.45

294

150

0.35

424

180

0.3

498

220

0.2

517

260

0.15

520

Part no.
Article no.

Price
See price list

Std. pack

Motor chokes, three-phaseMax. permissible mains voltage: 750 V +0 % (50/60 Hz)
DEX-LM3-005
269538
DEX-LM3-008
269539
DEX-LM3-011
269541
DEX-LM3-016
269542
DEX-LM3-035
269543
DEX-LM3-050
269544
DEX-LM3-063
269545
DEX-LM3-080
269546
DEX-LM3-100
269547
DEX-LM3-150
269548
DEX-LM3-180269549
DEX-LM3-220
269560
DEX-LM3-260
269561

2010 CA08103002Z-EN

1 off

www.eaton.com

10/22Frequency inverters
Key to part numbers

Key to part numbers

Series MMX
MMX32AA1D7F0-0 (example)
MMX
MMX

3
1
3

2
2
4

A
A

A
A

1D7
Variable code

F
F
N

0
0

-

0
0

MMX = Product family M-Max™
Number of phases
1 = Single-phase mains supply
3 = Three-phase mains supply
Voltage class2 = 200 V (208 V -15 % to 240 V +10 %)4 = 400 V (380 V -15 % to 480 V +10 %)VersionA = Software version
Display unit
A = Display unit built-in
Rated operational current (in amperes)
xDy = x,y A(digital; e.g. 1D7 = 1.7 A)
0xy = xy A
Radio interference suppression filters
F = with integrated radio interference suppression filter (C2)
N = without radio interference suppression filter
Protection type
0 = IP20 = NEMA 0
Optional module0 = no module built in
Series HMX
HMX34AG3D421-B (example)
HMX
HMX

3
3

4
2
4

A
A

G
G

3D4
Variable
code

2
2

1
1
2

-

B
B

HMX = Product family H-Max™
Number of phases
3 = Three-phase mains supply
Voltage class2 = 200 V (208 V -15 % to 240 V +10 %)4 = 400 V (380 V -15 % to 480 V +10 %)VersionA = Software version
Display unit
G = Graphics
Rated operational current (in amperes)
xDy = x,y A(digital; e.g. 3D4 = 3.4 A)
xyz = xyz A
Radio interference suppression filter (built-in)
2 = C2
Protection type
1 = IP21 = NEMA 1
2 = IP54 = NEMA 2
Brake chopper
B = Built-in brake chopper
2010 CA08103002Z-EN

www.eaton.com

Frequency inverters

10/23

General information about engineering information
Components of a Power Drives System (PDS)Engineering
General information about engineering information

Frequency inverters can be connected without limitation to AC supply systems
with a grounded star point (TN and TT networks).

Fuses (circuit-breakers) allow the protection of lines and electricalapparatus.
For personnel protection AC/DC-sensitive residual current devices(RCD Type B) are required in addition.

F

Contactors are used to switch mains voltage on and off.

Q

Mains chokes attenuate any current harmonics and peaks and limit the inrush
current (internal DC link capacitors).

R

Radio interference suppression filters attenuate high-frequency electromagnetic emissions from devices. They ensure that the EMC limit values for
conducted interference specified in the applicable product standards aremaintained (frequency inverters).

K

Frequency inverters allow a continuously variable speed control of three-phasemotors.

T

BACK
RESET
OK

3~

R

A braking resistor convert the frequency inverter’s regenerative braking
energy into heat.

LOC
REM

The frequency inverter must be equipped with a brake chopper, which connects
the braking resistor parallel to the internal DC link.

I

Motor chokes• Compensate the capacitive reactive currents,• Reduce current ripple and the motor’s current change noise,• Attenuate the retroaction on parallel connection of several motors.
Sine-wave filters• Smoothen the output voltage sinusoidally,• Reduce motor noise through du/dt reduction, and thereby increase themotor insulation’s lifespan,• Reduce the leakage currents to allow better motor performance at
improved EMC values.

R

3

3

Shielded motor cables attenuate emitted and conducted high-frequency
emissions within the limit values specified in the applicable product standard(EMC).

Three-phase asynchronous motor (standard motor)

M

M
3~

Item designations
F = fuses and circuit-breakers
Q = controlled switching within energy flow (contactors, circuit-breakers)
R = limitation (reactors, chokes, resistors)
K = radio interference suppression filters
T = frequency inverters
M = motors

2010 CA08103002Z-EN

www.eaton.com

10/24Frequency inverters
General information about engineering information

Electrical mains connection
General information about engineering information

M-Max™ and H-Max™ frequency
inverters can be connected andoperated on star-point-grounded
AC mains (according to IEC 60364)
without limitation.
L1
L2
L3
N
PE

L1
L2
L3
PEN

Connection and operation on
asymmetrically grounded networks,
such as phase-grounded delta (USA)or non-grounded or high-resistancegrounded (> 30 Ω) IT systems ispermitted with limitations. In these
networks only frequency inverters
Supply voltage ULN of theutility company
120 V
240 V
480 V
600 V

without integrated radio interference
suppression filters (EMC) must be
used. On devices with integrated radio
interference suppression filter the
filer’s ground connection must be
disconnected.
The standardized rated operational
voltages of the utility companies fulfil
the following conditions at the point oftransfer to the consumer:• Maximum deviation from the rated
voltage (ULN): ±10 %• Maximum deviation in the voltage
symmetry: ±3 %• Maximum deviation from the rated
frequency: ±4 %Regarding the lower voltage value(ULN -10 %) of the mains voltage, afurther voltage drop of 4 percent in the
consumer networks is permissible.
The power supply voltage at theconsumer must have a value of
ULN -14 %.
In ring-operated mesh networks(such as in the EU) the standardized
consumer voltages (230/400/690 V) are
identical with the utility company’s
supply voltages. In star networks (forexample in North America/USA), thestated consumer voltages take thevoltage drop from the utility company’s
infeed point to the last consumer into
account.

Motor voltage according
to UL 508 C
110 - 120 V
220 - 240 V
440 - 480 V
550 - 600 V

The wide tolerance band of thefrequency inverters of the M-Max™
and H-Max™ series takes all known
deviations from the standardized rated
operational voltages worldwide into
account (IEC 60038):
230 V: 208 V -15 % - 240 V +10 %400 V: 380 V -15 % - 480 V +10 %The permissible frequency range is
50 Hz -10 % – 60 Hz +10 %.

Consumer voltage, rated
value for the motors
115 V
230 V
460 V
575 V

Public medium-voltage supply grid

Measuringpoint

Publiclow-voltage supply grid

Category C1/C2
1st enviroment

The mains-side components are
assigned according to the frequency
inverter’s input-side rated operational
current ILN and utilization category
AC-1.
Fuses, circuit-breakers and conductor
cross-sections must meet the nationaland regional requirements and therequired approvals at the point ofoperation.
For fire prevention and the protectionof persons and domestic animals fromexcessive contact voltages residualcurrent devices (RCD) must be used.
In combination with a frequency
inverter only AC/DC sensitive RCDs
(Type B) must be used.

Identification on the residualcurrent circuit-breakers
AC/DC sensitive (RCD, type B)

Frequency inverters work with fastelectronic switches (IGBT) in the
inverter. This can cause radio interference in a PDS, which, in turn, canadversely affect nearby electronicequipment. To provide protection fromthis high-frequency interference,these should be spatially separated
and shielded from frequencycontrolled PDS.
In Europe, adherence to the EMC
Directive is mandatory. The EMC
product standard for power drive
systems (PDS) is IEC/EN 61800-3. This
standard covers the complete drive
system, from mains infeed to themotor.
Both versions of the frequency
inverters of the M-Max™ and H-Max™
series (with built-in and external radio
interference suppression filter) fulfil
the requirements of the EMC productstandard for residential areas (firstenvironment), and therefore also forthe higher limit values in industrial
areas (second environment).

With frequency-controlled power
drive systems (PDS), leakage currents
to ground occur. The main causes are
external capacitances between thephases of the motor cable, the motor
cable shielding, Y capacitors in the2010 CA08103002Z-EN

www.eaton.com

Category C3/C4

Category C3/C4

2nd enviroment

Frequency inverters• control terminals (I/O) with analog
and digital (binary) inputs,• a keypad with function keys anddisplay,• serial interfaces (bus) with RS485(Modbus RTU) and optional field bus
connections (CANopen,
PROFIBUS-DP, etc.) and an optional
PC connection.
Internal open and closed-loop control
circuits monitor all variable values in
the frequency inverter and automatically switch the process off if aquantity value reaches a dangerous
level.
The power section of a static andcompact frequency generally consistsof three subgroups:• Rectifier (A),• Internal DC link (B),
• Inverter module (C).
The devices of the H-Max™ series
contain a brake chopper as standard.
Depending on their rating, somedevices of the M-Max™ series also
contain a brake chopper.

The frequency inverter is an electronic
apparatus for controlling variablespeed drives with three-phase motors.
It is intended for installation in amachine or for assembly with othercomponents to a machine or plant. The
main components of a modern
compact frequency inverter are a
power section and a control section.
Example: M-Max™ series
The frequency inverter’s control
section contains a centrally controlling microprocessor, through which all
variable values that occur in thefrequency inverter are influenced.
These values and all control functions
are represented as parameters.
The functional control of the frequency
inverter and the output values in the
power section (such as frequency,
voltage and current) can be adjusted
through:① Power section with:
A = Rectifier
B = Internal DC link
C = Inverter module② Control section with:

a
BACK
RESET
OK

I/O = analog and binary inputs andoutputs
KEYPAD = keypad with display
BUS = serial interfaces(RS485, field bus, PC interface)

b

LOC
REM

I

Safety and switching

Industry
grid 2Category C1

frequency inverter and radio interference suppression filters andgrounding measures at the motor’ssite of operation. These leakage
currents can exceed 3.5 mA andrequire increased grounding of the
PDS according to EN 50178 (ground
conductor cross-section ≥ 10 mm2).

EMC measures

Industry
grid 1I/O
CPU

KEYPAD
BUS

M
3h
A

B

C

ULN = phase voltage from UDC = DC link voltage
Output voltage =supplying AC mains
UDC = 1.41 × ULN
switched DC link voltage(single-phase phase voltage)
with sinusoidal pulseUDC = 1.35 × ULN
width modulation(three-phase phase voltage)(PWM)
Block diagram with main components of a frequency inverter

Frequency inverters

10/25

General information about engineering information
Modulation

In sensorless vector control themagnetic fields of the stator and rotor
windings are aligned so as to oppose
each other. With asynchronous
motors the magnetic flux in the rotor
must be described in an electronicmodel of the motor. This requires thephysical parameters on the motor’s
rating plate to be entered.
In vector operation the frequency
inverter can control only one motor.
A parallel operation of several motors
is not possible here. The exact
calculation of the phase voltages at
the frequency inverter’s output,
however, improves the motor’soperational behavior. The motor alsoheats up less in the lower speed range.
The field-oriented vector control
results in a significant improvementin the drive dynamics as well as
optimizing performance; it also
increases the range of possible
applications.

General information about engineering information

The IGBTs in the inverter of the
M-Max™ and H-Max™ frequency
inverters are controlled withsinusoidal pulse-width modulation(PWM). Two control methods are
possible:• Voltage/frequency (U/f) control,• Sensorless vector control (speed
control).
Voltage/frequency control is thebest-known and most commonly usedmethod. A simple characteristic curve(linear or square) defines the motor’srotating field frequency and thecorresponding three-phase line-toline voltage of the motor is selected
so that the motor is neither overmagnetized nor under magnetized.
The main fields of application of U/fcontrol are:

The main applications of sensorless
vector control are:

• Heavy starting duty (extruders,agitators, mixers),• Horizontal conveying equipment(cranes, elevators).

• Material processing machines,• compressors,
X1

R1

i1

iw

im

u1

R'2
s

X'2

a

Xh

b

c

① Stator winding② Air gap
③ Transformed rotor winding

Simplified equivalent circuit diagram with associated current vectors
Explanation:
EMC = electromagnetic
compatibility
IGBT = insulated-gate bipolartransistor
PDS = power drive system
RCD = residual-current device• Pump and fan drives,• Horizontal conveying and transportation systems,• Drives with several motors (parallel
operation of several motors at theoutput of a frequency inverter).

Technical information about the braking resistors:
The stated ratings PDB of the braking resistors apply to continuous operation.
In short-time operation these values can be increased through multiplication with thetype-specific power factor according to the following formula:
Pmax ≤ (PDB × 100 %) ÷ DF [%]Pmax = max. pulse rating
PDB = continuous rating at a duty factor of 100 %DF = duty factor
tc = cycle time (max. 120 seconds)
The duty factor is given in percent (%) and is calculated with the following formula:
DF [%] = (DF × 100 %) ÷ tc

PDB

t [s]

ED
tC (F 120 s)

Pmax
20
10

6

3.4

PDB
ED

1.1

1.25

1.4

1.7

1
100

90

80

70

60

2

50

2.6

40

30

20

10

5
ED [%]

2010 CA08103002Z-EN

www.eaton.com

10/26Frequency inverters
Connection example for M-Max™

Connection example for M-Max™

Connecting example for a 0.75 kW
motor with the rating plateillustrated here
By default, the M-Max™ frequency
inverters are configured so that they
can be operated immediately without
configuration when connected to theassigned motor rating.

To ensure an optimum operational
behavior, the data on the motor’s
rating label should be entered in thefrequency inverter (electrical image).

P7.1

P7.5

The following example shows theparameters for quick configuration
with the selected drive-specificparameters for four standard
applications.

230/400 V
4.0/2.3 A
cos v 0.67
0,75 KW
1410 min-1
50 Hz

P7.4
P7.3

P7.6

Parameters

Basic(Standard drive)

Pump drive

Fan drive

Feed unit(high load)

Designation

P1.1

1 = Only quickconfiguration parameters
1 = Pump drive

1 = Only quickconfiguration parameters
2 = Fan drive

P 1.3

0 = EU

0 = EU

0 = EU

1 = Only quickconfiguration parameters
3 = Feed unit
(High load)
0 = EUParameter range

P1.2

1 = Only quickconfiguration parameters
0 = Basic

P6.1

P6.3

1 = Control signal
terminals (I/O)(Input/Output)
3 = AI1(analog setpoint value 1)
0.00 Hz

1 = Control signal
terminals (I/O)(Input/Output)
3 = AI1(analog setpoint value 1)
20.00 Hz

1 = Control signal
terminals (I/O)(Input/Output)
3 = AI1(analog setpoint value 1)
20.00 Hz

1 = Control signal
terminals (I/O)(Input/Output)
3 = AI1(analog setpoint value 1)
0.00 Hz

P6.4

50.00 Hz50.00 Hz50.00 Hz50.00 Hz

Maximum frequency

P6.5

3.0 s

5.0 s

20.0 s1.0 sAcceleration time (acc1)

P6.6

3.0 s

5.0 s

20.0 s1.0 sDeceleration time (dec1)

P 6.7

0 = Ramp(Acceleration)
0 = Free coasting

0 = Ramp(Acceleration)
0 = Free coasting

P7.1

Ie

0 = Ramp(Acceleration)
1 = Ramp(deceleration)
Ie

Start function

P6.8

0 = Ramp(Acceleration)
0 = Free coasting

Ie

Ie

P7.3

1440 rpm

1440 rpm

1440 rpm

1440 rpm

P7.4

0.85

0.85

0.85

0.85

P7.5

230/400 V1)

230/400 V1)

230/400 V1)

230/400 V1)

P7.6

50.00 Hz50.00 Hz50.00 Hz50.00 Hz

Motor, rated operational
current2)
Motor, rated speed(rpm)2)
Power factor of the
motor (cos ϕ)2)
Motor, rated operational
voltage
Motor, rated frequency

P11.7

0 = Deactivated

0 = Deactivated

0 = Deactivated

1 = Enabled

Torque increase

M1.1

0.00 Hz0.00 Hz0.00 Hz0.00 Hz

Output frequency

Notes1) 230 V = MMX12…, MMX32…; 400 V = MMX34…

P6.22) Depending on output

2010 CA08103002Z-EN

www.eaton.com

Application
Default settings
country-specific (EU/USA)
Control level

Setpoint input(0 - 10 V) terminal 2
Minimum frequency

Stop function

Frequency inverters

10/27

Connection example for M-Max™
Connection example for M-Max™

FWD

REV

FF1

FF2

Reset

PI-Off

7

8

9

10

14

15

16

DI_COM

DI1

DI2

DI3

DI4

DI5

DI6

24 V
6
+24 V Out< 50 mA

3 AC

PE

L1 L2/N L3

120 O
X1
S4
A

EMC

S1
B

R+
200 kO

R-

AI1

GND

AI2

AO
< 10 mA

DO< 50 mA

DO+

24

26

3

1

2

5

4

18

13

20

e

M
3~

Ready

+10 V Out< 10 mA25

f-Out
0...+10 V

GND

23

f-Soll0...+10 V

R24

22

Error

R22

PE

200 O

R21

W

S3

R14

V

Run

U

S2

R13
PE

200 O

200 kOPI-Ist0 (4)...20 mA

a

+

e

3 AC

Block diagram MMX32 and MMX34
Terminals R+ and R- for external braking resistor (optional), only with MMX34…4D3…, MMX34…5D6…, MMX34…7D6…, MMX34…9D0, MMX34…012… andMMX34…014…
The control signal terminals have thefollowing default assignment2:

AI1: f-Soll = frequency referencevalue(0 - +10 V)

4:

AI2: PI-Ist = PID controller actual
value(Process variable, 4 - 20 mA)
DI1: FWD = enable forward(clockwise rotating field)
DI2: REV = enable reverse(counterclockwise rotating field)

8:9:

10: DI3: FF1 = Fixed frequency 1

13: DO-: Ready = Ready for operation(transistor output with voltage ofterminal 20)
14: DI4: FF2 = Fixed frequency 2
15: DI5: Reset = Error message
acknowledge
16: DI6: PI-Off = PID controller disabled
18: AO: f-Out = output frequency to
motor (0 – +10 V)
20: DO+: input voltage for transistor
output22/23:

R13/R14: RUN = run signal (relay)
24/25/26: R21/R22/R24: Error = error message(relay)The function of the digital inputs and outputs,
and the scaling of the analog inputs andoutputs are defined with parameters. These
are described in manual AWB8230-1603.

2010 CA08103002Z-EN

www.eaton.com

10/28Frequency inverters

Frequency inverters

Assigned switching and protective elements
M-Max™

10/29

Assigned switching and protective elements
M-Max™

Assigned switching and protective elements

Part no.

Motor

Frequency inverters

Mains supply

Assigned
motor rating(ULN, 50/60 Hz)

Motor current1)

Rated operational
current
Frequency inverters

Mains current
Without mains
choke

P
kW

Ie
A

Ie
A

ILN
A

MMX12… frequency inverters
Single-phase mains connection (1 AC 230 V/240 V)
MMX12AA1D7F0-0
MMX12AA1D7N0-0
0.25
MMX12AA2D4F0-0
MMX12AA2D4N0-0
0.37
MMX12AA2D8F0-0
MMX12AA2D8N0-0
0.55
MMX12AA3D7F0-0
MMX12AA3D7N0-0
0.75
MMX12AA4D8F0-0
MMX12AA4D8N0-0
1.1
MMX12AA7D0F0-0
MMX12AA7D0N0-0
1.5
MMX12AA9D6F0-0
MMX12AA9D6N0-0
2.2

1.4
2
2.7
3.2
4.6
6.3
8.7

1.7
2.4
2.8
3.7
4.8
7
9.6

MMX32… frequency inverters
Three-phase mains connection (3 AC 230 V/240 V)
MMX32AA1D7F0-0
MMX32AA1D7N0-0
0.25
MMX32AA2D4F0-0
MMX32AA2D4N0-0
0.37
MMX32AA2D8F0-0
MMX32AA2D8N0-0
0.55
MMX32AA3D7F0-0
MMX32AA3D7N0-0
0.75
MMX32AA4D8F0-0
MMX32AA4D8N0-0
1.1
MMX32AA7D0F0-0
MMX32AA7D0N0-0
1.5
MMX32AA011F0-0
MMX32AA011N0-0
2.2

1.4
2
2.7
3.2
4.6
6.3
8.7

MMX34… frequency inverters
Three-phase mains connection (3 AC 400 V/480 V)
MMX34AA1D3F0-0
MMX34AA1D3N0-0
0.37
MMX34AA1D9F0-0
MMX34AA1D9N0-0
0.55
MMX34AA2D4F0-0
MMX34AA2D4N0-0
0.75
MMX34AA3D3F0-0
MMX34AA3D3N0-0
1.1
MMX34AA4D3F0-0
MMX34AA4D3N0-0
1.5
MMX34AA5D6F0-0
MMX34AA5D6N0-0
2.2
MMX34AA7D6F0-0
MMX34AA7D6N0-0
3
MMX34AA9D0F0-0
MMX34AA9D0N0-0
4
MMX34AA012F0-0
MMX34AA012N0-0
5.5
MMX34AA014F0-0
MMX34AA014N0-0
7.54)

1.1
1.5
1.9
2.6
3.6
5
6.6
8.5
11.3
15.24)

With internal
radio interference
suppression filter

Notes

Without internal
radio interference
suppression filter

Motor connection

Short-circuit andcable protection(fuse)2)

Short-circuit andcable protection(fuse)

Mains contactor

Mains contactor withparallel connector(main current-

Mains choke

Radio interference
suppression filters(only for part nos.
MMX…N…)

Motor chokes

Sine-wave filters

4.2
5.7
6.6
8.3
11.2
14.1
15.8

FAZ-B10/1N
FAZ-B10/1N
FAZ-B10/1N
FAZ-B10/1N
FAZ-B20/1N
FAZ-B20/1N
FAZ-B32/1N

–
–
–
–
–
–
–

DILM7
DILM7
DILM7
DILM7
DILM7
DILM7
DILM7

DILEM+P1DILEM
DILEM+P1DILEM
DILEM+P1DILEM
DILEM+P1DILEM–––

DEX-LN1-006
DEX-LN1-006
DEX-LN1-009
DEX-LN1-009
DEX-LN1-013
DEX-LN1-018
DEX-LN1-018

MMX-LZ1-009
MMX-LZ1-009
MMX-LZ1-009
MMX-LZ1-009
MMX-LZ1-015
MMX-LZ1-015
MMX-LZ1-017

DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-008
DEX-LM3-011

SFB400/4
SFB400/4
SFB400/4
SFB400/4
SFB400/10
SFB400/10
SFB400/10

1.7
2.4
2.8
3.7
4.8
7
11

2.7
3.5
3.8
4.3
6.8
8.4
13.4

FAZ-B6/3
FAZ-B6/3
FAZ-B6/3
FAZ-B6/3
FAZ-B10/3
FAZ-B10/3
FAZ-B20/3

PKM0-6,3
PKM0-6,3
PKM0-6,3
PKM0-6,3
PKM0-10
PKM0-10
PKM0-20

DILEM
DILEM
DILEM
DILEM
DILEM
DILEM
DILM7

–
–
–
–
–
–
–

DEX-LN3-004
DEX-LN3-004
DEX-LN3-004
DEX-LN3-006
DEX-LN3-010
DEX-LN3-010
DEX-LN3-016

MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-009
MMX-LZ3-009
MMX-LZ3-020

DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-008
DEX-LM3-011

SFB400/4
SFB400/4
SFB400/4
SFB400/4
SFB400/10
SFB400/10
SFB400/10

1.3
1.9
2.4
3.3
4.3
5.6
7.6
9
12
144)

2.2
2.8
3.2
4
5.6
7.3
9.6
11.5
14.9
18.7

FAZ-B6/3
FAZ-B6/3
FAZ-B6/3
FAZ-B6/3
FAZ-B10/3
FAZ-B10/3
FAZ-B20/3
FAZ-B20/3
FAZ-B20/3
FAZ-B25/3

PKM0-6,3
PKM0-6,3
PKM0-6,3
PKM0-6,3
PKM0-10
PKM0-10
PKM0-20
PKM0-20
PKM0-20
PKM0-25

DILEM
DILEM
DILEM
DILEM
DILEM
DILEM
DILEM
DILM7
DILM7
DILM7

–
–
–
–
–
–
–
–
–
–

DEX-LN3-004
DEX-LN3-004
DEX-LN3-004
DEX-LN3-006
DEX-LN3-006
DEX-LN3-010
DEX-LN3-010
DEX-LN3-016
DEX-LN3-016
DEX-LN3-016

MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-006
MMX-LZ3-009
MMX-LZ3-009
MMX-LZ3-020
MMX-LZ3-020
MMX-LZ3-020
MMX-LZ3-020

DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-005
DEX-LM3-008
DEX-LM3-008
DEX-LM3-011
DEX-LM3-016
DEX-LM3-016

SFB400/4
SFB400/4
SFB400/4
SFB400/4
SFB400/4
SFB400/10
SFB400/10
SFB400/10
SFB400/16.5
SFB400/16.5

paths)3)

All data apply at an ambient air temperature of up to +50 °C.
1) The rated motor currents apply to normal internally and surface-cooled three-phase motors with 1500 rpm at 50 Hz or 1800 rpm at 60 Hz.
2) If a frequency inverter is operated without mains chokes, current peaks can occur when mains power is applied. This can cause the FAZ-B…
to trip prematurely.
Remedy: fit a mains choke upstream or use an FAZ-C...
3) Instead of PKM0, PKZM0 can also be used.
4) Reduced rated operational data: Ambient air temperature up to +40 °C, operating frequency up to 4 kHz, mounting distance at sides (left andright) > 10 mm
cable protection FAZ, PKM, PKZM ￫ chapter 7, 19
DIL mains contactor ￫ chapter 5
Mains chokes DEX-LN… ￫ Page 10/20
Radio interference suppression filters MMX-LZ… ￫ Page 10/19
DEX-LM3-… motor chokes ￫ Page 10/21
Sinusoidal filters SFB400/... please enquire2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

10/30Frequency inverters

Frequency inverters

Assigned switching and protective elements
H-Max™

10/31

Assigned switching and protective elements
H-Max™

Engineering
Assigned switching and protective elements

Part no.

Motor

Frequency inverters

Mains supply

Assigned motor rating(ULN, 50/60 Hz)

Motor current1)

Rated operational current
Frequency inverters

Mains current(DC link choke)

P
kW

Ie
A

Ie
A

ILN
A

HMX32… frequency inverters
Three-phase mains connection (3 AC 230 V/240 V)
HMX32AG3D721-B
HMX32AG3D722-B
HMX32AG4D821-B
HMX32AG4D822-B
HMX32AG6D621-B
HMX32AG6D622-B
HMX32AG8D021-B
HMX32AG8D022-B
HMX32AG01121-B
HMX32AG01122-B
HMX32AG01221-B
HMX32AG01222-B
HMX32AG01821-B
HMX32AG01822-B
HMX32AG02421-B
HMX32AG02422-B
HMX32AG03121-B
HMX32AG03122-B
HMX32AG04821-B
HMX32AG04822-B
HMX32AG06221-B
HMX32AG06222-B
HMX32AG07721-B
HMX32AG07722-B
HMX32AG08821-B
HMX32AG08822-B
HMX32AG10621-B
HMX32AG10622-B
HMX32AG14321-B
HMX32AG14322-B
HMX32AG17021-B
HMX32AG17022-B
HMX32AG20521-B
HMX32AG20522-B
HMX32AG26121-B
HMX32AG26122-B
HMX32AG31021-B
HMX32AG31022-B

0.75
1.1
1.5
1.5
2.2
3
4
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90

3.2
4.6
6.3
6.3
8.7
11.5
14.8
19.6
26.4
38
51
63
71
96
117
141
173
233
279

HMX34… frequency inverters
Three-phase mains connection (3 AC 400 V/480 V)
HMX34AG3D421-B
HMX34AG3D422-B
HMX34AG4D821-B
HMX34AG4D822-B
HMX34AG5D621-B
HMX34AG5D622-B
HMX34AG8D021-B
HMX34AG8D022-B
HMX34AG9D621-B
HMX34AG9D622-B
HMX34AG01221-B
HMX34AG01222-B
HMX34AG01621-B
HMX34AG01622-B
HMX34AG02321-B
HMX34AG02322-B
HMX34AG03121-B
HMX34AG03122-B
HMX34AG03821-B
HMX34AG03822-B
HMX34AG04621-B
HMX34AG04622-B
HMX34AG06121-B
HMX34AG06122-B
HMX34AG07221-B
HMX34AG07222-B
HMX34AG08721-B
HMX34AG08722-B
HMX34AG10521-B
HMX34AG10522-B
HMX34AG14021-B
HMX34AG14022-B
HMX34AG17021-B
HMX34AG17022-B
HMX34AG20521-B
HMX34AG20522-B
HMX34AG26121-B
HMX34AG26122-B
HMX34AG31021-B
HMX34AG31022-B

1.1
1.5
2.2
3
4
5.5
7.5
11
15
18.5
22
30
37
45
55
75
90
110
132
160

2.6
3.6
5
6.6
8.5
11.3
15.2
21.7
29.3
36
41
55
68
81
99
134
161
196
231
279

Protection type IP21

Notes

Protection type IP54

Motor connection

Short-circuit and line
protection (fuse)2)

Mains contactor

Motor chokes

Sine-wave filters

3.7
4.8
6.6
8
11
12.5
18
24.2
31
48
62
77
88
106
143
170
208
261
310

PKM0-6,3
PKM0-6,3
PKM0-10
PKM0-10
PKM0-16
PKM0-16
PKM0-25
PKM0-32
PKM4-40
PKM4-50
PKM4-63
NZM...1-A80
NZM...1-A100
NZM...1-A125
NZM...1-A160
NZM...2-A200
NZM...2-A250
NZM...3-AE400
NZM...3-AE400

DILEM
DILEM
DILEM
DILEM
DILM7
DILM7
DILM7
DILM17
DILM17
DILM40
DILM50
DILM65
DILM80
DILM95
DILM150
DILM170
DILM185
DILM185
DILM250

DEX-LM3-005
DEX-LM3-005
DEX-LM3-008
DEX-LM3-008
DEX-LM3-011
DEX-LM3-016
DEX-LM3-035
DEX-LM3-035
DEX-LM3-035
DEX-LM3-050
DEX-LM3-063
DEX-LM3-080
DEX-LM3-100
DEX-LM3-1002)
DEX-LM3-150
DEX-LM3-180
DEX-LM3-220
DEX-LM3-260
Please enquire

SFB400/4
SFB400/4
SFB400/10
SFB400/10
SFB400/16.5
SFB400/16.5
SFB400/32
SFB400/32
SFB400/32
SFB400/48
SFB400/115
SFB400/115
SFB400/115
SFB400/115
SFB400/150
SFB400/180
SFB400/250
SFB400/440
SFB400/440

3.4
4.8
5.6
8
9.6
12
16
23
31
38
46
61
72
87
105
140
170
205
261
310

PKM0-6,3
PKM0-6,3
PKM0-6,3
PKM0-10
PKM0-10
PKM0-16
PKM0-16
PKM0-25
PKM0-32
PKM4-40
PKM4-50
PKM4-63
NZM...1-A80
NZM...1-A100
NZM...1-A125
NZM...1-A160
NZM...2-A200
NZM...2-A250
NZM...3-AE400
NZM...3-AE400

DILEM
DILEM
DILEM
DILEM
DILEM
DILM7
DILM7
DILM7
DILM17
DILM17
DILM40
DILM50
DILM65
DILM80
DILM95
DILM150
DILM170
DILM185
DILM185
DILM250

DEX-LM3-005
DEX-LM3-005
DEX-LM3-008
DEX-LM3-008
DEX-LM3-011
DEX-LM3-016
DEX-LM3-016
DEX-LM3-035
DEX-LM3-035
DEX-LM3-050
DEX-LM3-050
DEX-LM3-063
DEX-LM3-080
DEX-LM3-100
DEX-LM3-1002)
DEX-LM3-150
DEX-LM3-180
DEX-LM3-220
DEX-LM3-260
Please enquire

SFB400/4
SFB400/4
SFB400/10
SFB400/10
SFB400/10
SFB400/16.5
SFB400/16.5
SFB400/23.5
SFB400/32
SFB400/37
SFB400/48
SFB400/115
SFB400/115
SFB400/115
SFB400/115
SFB400/150
SFB400/180
SFB400/250
SFB400/440
SFB400/440

All data apply at an ambient air temperature of up to +40 °C.
1) The rated motor currents apply to normal internally and surface-cooled three-phase motors with 1500 rpm at 50 Hz or 1800 rpm at 60 Hz.
2) At motor currents above 100 A use frame size DEX-LM3-150.
DIL mains contactor ￫ chapter 5
DEX-LM3-… motor chokes ￫ Page 10/21
SFB400/... sine-wave filters please enquire2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

10/32Frequency inverters

Frequency inverters

MMX12... ,MMX32...

10/33

MMX12... ,MMX32...

Technical data
MMX12... ,MMX32...

MMX12...

Power side (primary side)
Number of phases
Mains connection voltage
IEC (50/60Hz)
UL/CSA (45 - 66 Hz ±0 %)Rated operational voltage
Rated operational current
Input current
Overload current for 60 s every 600 s at 50 °C
Starting current for 2 s every 20 s at 50 °C
Maximum leakage current to ground (PE) without motor
Apparent power at rated operation 230 V
Apparent power at rated operation 240 V
Assigned motor rating (230 V)
Assigned motor rating (230 V)
Braking torqueStandard
DC braking
Pulse frequency
Heat dissipation at rated operational current Ie
Efficiency
Fan (built into device, temperature-controlled)
Frame size
Weight

MMX...1D7...

MMX...2D4...

MMX...2D8...

MMX...3D7...

MMX...4D8...

MMX...7D0...

MMX...9D6...

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

1 (L and N) or
2 (e.g. L1 and L2)

208 -15 % - 240 +10 %177 - 264 ±0 %
230
1.7
4.2
2.6
3.4
15.4
0.68
0.71
0.25
1/31)

208 -15 % - 240 +10 %177 - 264 ±0 %
230
2.4
5.7
3.6
4.8
15.4
0.96
0.99
0.37
1/2

208 -15 % - 240 +10 %177 - 264 ±0 %
230
2.8
6.6
4.2
5.6
15.4
1.12
1.16
0.55
1/2

208 -15 % - 240 +10 %177 - 264 ±0 %
230
3.7
8.3
5.6
7.4
11.8
1.47
1.54
0.75
3/4

208 -15 % - 240 +10 %177 - 264 ±0 %
230
4.8
11.2
7.2
9.6
11.8
1.91
1.99
1.1
1.0

208 -15 % - 240 +10 %177 - 264 ±0 %
230
7
14.1
10.4
14
11.8
2.79
2.91
1.5
2.0

208 -15 % - 240 +10 %177 - 264 ±0 %
230
9.6
15.8
14.4
19.2
24.4
3.82
3.99
2.2
3.0

Max. 30 % MN
Max. 30 % MN
Max. 100 % of rated operational current Ie, adjustable
6 (adjustable 1 – 16)
6 (adjustable 1 – 16)
29.2
40.2
0.95
0.95
•
•
FS1
FS2
0.55
0.70

Max. 30 % MN

Max. 30 % MN

Max. 30 % MN

6 (adjustable 1 – 16)
49.6
0.95
•
FS2
0.70

6 (adjustable 1 – 16)
66.8
0.96
•
FS2
0.70

6 (adjustable 1 – 16)
78.1
0.96
•
FS3
0.99

ULN

Ue
Ie
ILN

IPE

P
P

V
V
V
A
A
A
A
mA
kVA
kVA
kWh
HP

fPWM
PV
η

kHz
W

m

kg

Max. 30 % MN
Max. 30 % MN
Max. 100 % of rated operational current Ie, adjustable
6 (adjustable 1 – 16)
6 (adjustable 1 – 16)
17.9
24.6
0.93
0.93
•
•
FS1
FS1
0.55
0.55
1) Not a standardized output

Notes

MMX32...

Power side (primary side):
Number of phases
Mains connection voltage
IEC (50/60Hz)
UL/CSA (45 - 66 Hz ±0 %)Rated operational voltage
Rated operational current
Input current
Overload current for 60 s every 600 s at 50 °C
Starting current for 2 s every 20 s at 50 °C
Maximum leakage current to ground (PE) without motor
Apparent power at rated operation 230 V
Apparent power at rated operation 240 V
Assigned motor rating (230 V)
Assigned motor rating (230 V)
Braking torqueStandard
DC braking
Pulse frequency
Heat dissipation at rated operational current Ie
Efficiency
Fan (built into device, temperature-controlled)
Frame size
WeightUe
Ie
ILN

MMX...2D8...

MMX...3D7...

MMX...4D8...

MMX...7D0...

MMX... 011...

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

208 -15 % - 240 +10 %177 - 264 ±0 %
230
1.7
2.7
2.6
3.4
8.6
0.68
0.71
0.25
1/31)

208 -15 % - 240 +10 %177 - 264 ±0 %
230
2.4
3.5
3.6
4.8
8.6
0.96
0.99
0.37
1/2

208 -15 % - 240 +10 %177 - 264 ±0 %
230
2.8
3.8
4.2
5.6
8.6
1.12
1.16
0.55
1/2

208 -15 % - 240 +10 %177 - 264 ±0 %
230
3.7
4.3
5.6
7.4
16.1
1.47
1.54
0.75
3/4

208 -15 % - 240 +10 %177 - 264 ±0 %
230
4.8
6.8
7.2
9.6
16.1
1.91
1.99
1.1
1.0

208 -15 % - 240 +10 %177 - 264 ±0 %
230
7
8.4
10.4
14
16.1
2.79
2.91
1.5
2.0

208 -15 % - 240 +10 %177 - 264 ±0 %
230
11
13.4
14.4
19.2
8.6
3.82
3.99
2.2
3.0

Max. 30 % MN

Max. 30 % MN
Max. 30 % MN
Max. 100 % of rated operational current Ie, adjustable
6 (adjustable 1 – 16)
6 (adjustable 1 – 16)
37.9
48.4
0.95
0.96
•
•
FS2
FS2
0.70
0.70

Max. 30 % MN

Max. 30 % MN

6 (adjustable 1 – 16)
63.8
0.96
•
FS2
0.70

6 (adjustable 1 – 16)
84.0
0.96
•
FS3
0.99

ULN

Ue
Ie
ILN

IPE

P
P

η

MMX...2D4...

fPWM
PV
η

m

Max. 30 % MN
Max. 30 % MN
Max. 100 % of rated operational current Ie, adjustable
6 (adjustable 1 – 16)
6 (adjustable 1 – 16)
17.4
23.7
0.93
0.94
•
•
FS1
FS1
0.55
0.55

6 (adjustable 1 – 16)
28.3
0.95
•
FS1
0.55

1) Guide value, not a standardized output

Notes

2010 CA08103002Z-EN

ULN

MMX...1D7...

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

10/34Frequency inverters

Frequency inverters

MMX34...

10/35

MMX34...

MMX34...

Power side (primary side):
Number of phases
Mains connection voltage
IEC (50/60Hz)

MMX...1D3...

MMX...1D9...

MMX...2D4...

MMX...3D3...

MMX...4D3...

MMX...5D6...

MMX...7D6...

MMX...9D0...

MMX...012...

MMX...014...

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

3 (L1, L2, L3)

V
V
A
A
A

380 -15 % 480 +10 %323 - 528 ±0 %
400
1.3
2.2
2.0

380 -15 % 480 +10 %323 - 528 ±0 %
400
1.9
2.8
2.9

380 -15 % 480 +10 %323 - 528 ±0 %
400
2.4
3.2
3.6

380 -15 % 480 +10 %323 - 528 ±0 %
400
3.3
4.0
5.0

380 -15 % 480 +10 %323 - 528 ±0 %
400
4.3
5.6
6.5

380 -15 % 480 +10 %323 - 528 ±0 %
400
5.6
7.3
8.4

380 -15 % 480 +10 %323 - 528 ±0 %
400
7.6
9.6
11.4

380 -15 % 480 +10 %323 - 528 ±0 %
400
9.0
11.5
13.5

380 -15 % 480 +10 %323 - 528 ±0 %
400
12.0
14.9
18.0

380 -15 % 480 +10 %323 - 528 ±0 %
400
21.0
18.7
21.0

A
mA
kVA
kVA
kWh
HP

2.6
45.1
0.9
1.08
0.37
1/2

3.8
45.1
1.32
1.56
0.55
3/4

4.8
45.1
1.66
2.00
0.75
1

6.6
25.1
2.29
2.74
1.10
1-1/2

8.6
25.1
2.98
3.57
1.50
2

11.2
25.1
3.88
4.66
2.20
3

15.2
24.9
5.27
6.32
3.00
43)

18.0
24.9
6.24
7.48
4.00
5

24.0
24.9
8.32
9.98
5.50
7-1/2

28.0
24.9
9.70
11.64
7.502)
10

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 30 % MN
Max. 100 % of rated
operational current
Ie, adjustable

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

Max. 100 % of rated
operational current
Ie with external
braking resistor

55
765
6 (adjustable 1 – 16)
66.4

55
765
6 (adjustable 1 – 16)
88.3

35
765
6 (adjustable 1 – 16)
116.9

35
765
6 (adjustable 1 – 16)
136.2

35
765
6 (adjustable 1 – 16)
185.1

35
765
1 - 4, adjustable
223.7

ULN
V

UL/CSA (45 - 66 Hz ±0 %)Rated operational voltage
Rated operational current
Input current
Overload current for 60 s every 600 s at 50 °C

Ue
Ie
ILN

Starting current for 2 s every 20 s at 50 °C
Maximum leakage current to ground (PE) without motor
Apparent power at rated operation 400 V
Apparent power at rated operation 480 V
Assigned motor (400 V)
Assigned motor rating (460 V)
Braking torqueStandard
DC braking

IPE

P
P

Brake chopper with external braking resistor

Minimum braking resistance
Closing ripple for braking transistor
Pulse frequency
Heat dissipation at rated operational current Ie

RB
UDC
fPWM
PV

Efficiency
Fan (built into device, temperature-controlled)η

Frame size
Weight

m

Ω
V DC
kHz
W

kg

6 (adjustable 1 – 16)
21.7

6 (adjustable 1 – 16)
29.7

6 (adjustable 1 – 16)
31.7

55
765
6 (adjustable 1 – 16)
51.5

0.94
•

0.95
•

0.95
•

0.95
•

0.96
•

0.96
•

0.96
•

0.97
•

0.97
•

0.97
•

FS1
0.55

FS1
0.55

FS1
0.55

FS2
0.70

FS2
0.70

FS2
0.70

FS3
0.99

FS3
0.99

FS3
0.99

FS3
0.99

1) The rated operational data of the MMX34AA014… is limited to 4 kHz at a maximum ambient air temperatureNotes

of +40 °C.
2) Assigned motor rating with reduced load torque (about -10 %)3) Guide value, not a standardized output

2010 CA08103002Z-EN

www.eaton.com

2010 CA08103002Z-EN

www.eaton.com

10/36Frequency inverters
Mains chokes, motor chokes
DEX-LN..., DEX-LM3...

Technical data
Mains chokes, motor chokes

Mains chokes DEX-LN1-…

Mains chokes DEX-LN3-…

DEX-LM3-… motor chokes

IEC/EN 61558-2-20-2000, VDE 0570
Part 2-20/04-2001,
UL, CSA
-25 – +40, up to 70 with current
reduction (see note)-25 - +85

IEC/EN 61558-2-20-2000, VDE 0570
Part 2-20/04-2001,
UL, CSA
-25 – +40, up to 70 with current
reduction (see note)-25 - +85

IEC/EN 61558-2-20-2000, VDE 0570
Part 2-20/04-2001,
UL, CSA
-25 – +40, up to 70 with current
reduction (see note)-25 - +85

11 ms2/15 g, 3 impacts

11 ms2/15 g, 3 impacts

11 ms2/15 g, 3 impacts

GeneralStandards

Operating temperatureϑ

°C

Storage temperatureϑ°C

Mechanical shock resistance

1 (0 - 150 Hz)

1 (0 - 150 Hz)

1 (0 - 150 Hz)

Vibration

Resistance to vibrationg

0.35 mm at 10 - 55 Hz

0.35 mm at 10 - 55 Hz

0.35 mm at 10 - 55 Hz

Pollution degree

1 (VDE 0160)

1 (VDE 0160)

1 (VDE 0160)

0 – 1000 above seal level, up to 5000
with current reduction (see note)0 – 1000 above seal level, up to 5000
with current reduction (see note)0 – 1000 above seal level, up to 5000
with current reduction (see note)

Free surrounding areas

Standing vertically,suspended horizontally< 50

Standing vertically,suspended horizontally< 50

Standing vertically,suspended horizontally< 50

Degree of protection (terminals)

IP20
100

IP20 to 40 A
IP00 from 50 A
100

IP20 up to 50 A
IP00 from 63 A
100

1.5 x Ie for 60 s every 600 s

1.5 x Ie for 60 s every 600 s

Installation altitude

Hm

Mounting position

Rated duty factor% DF

Overload cycle
Weightmkg

0.7 - 2

1.5 - 20.6

1.5 x Ie for 60 s every 600 s (< 24 A)
1.2 x Ie for 60 s every 600 s (> 24 A)
1.5 - 45

Electrical data
Rated operational voltage

Ue

V AC

230/240

400/480

230/400/460/575

Max. supply voltage

UL

V AC

260 +0 %550 +0 %750 +0 %Operating frequency

f

Hz

50/60

50/60

0 - 200

B

B

B (100 A) F (150 A)

Insulation classElectrical connection
Terminations●● (≦ 40 A)● (≦ 40 A)

Connection lugs–

● (≧ 50 A)● (≧ 63 A)

PE stud

●

●

●

Notes

All rated operational data is based on an ambient air temperature of +40 °C. An ambient air temperatureof +50 °C results in a derating of 4 percent.
The derating due to altitude relates to the rated operational current.e
I
Ie

1.0
0.9
0.8
0.7
0.6
0.5
0

1000

2000

3000

4000

5000
h [m]

2010 CA08103002Z-EN

www.eaton.com

Frequency inverters

10/37

Mains chokes, motor chokes
DEX-LN..., DEX-LM3...
Mains chokes, motor chokes

Part no.

Rated
operatingcurrent
Ie

InductanceL

Maximumheat
dissipation
Pv

A

mH

W

Cu factor1)

Voltage drop

Connection
Terminal/connection lug

Bore hole

Pick-up

%

mm2

AWG

mm

Nm

uk

Mains chokes, single-phase, rated operational voltage 1 AC 230 V, 50 Hz
DEX-LN1-006

5.8

5.05

9

0.09

4

4

20 - 10–0.8

DEX-LN1-009

8.6

3.41

11

0.11

4

4

20 - 10–0.8

DEX-LN1-013

13

2.25

12

0.18

4

4

20 - 10–0.8

DEX-LN1-018

18

1.63

17

0.27

4

4

20 - 10–0.8

DEX-LN1-024

24

1.22

20

0.33

4

4

20 - 10–0.8

Mains chokes, three-phase, rated operational voltage 3 AC 400 V, 50 Hz
DEX-LN3-004

3.9

7.51

17

0.25

4

4

20 - 10–0.8

DEX-LN3-006

6

4.9

19

0.34

4

4

20 - 10–0.8

DEX-LN3-010

10

2.94

33

0.45

4

4

20 - 10–0.8

DEX-LN3-016

16

1.84

44

0.53

4

4

20 - 10–0.8

DEX-LN3-025

25

1.18

57

0.90

4

4

20 - 10–0.8

DEX-LN3-040

40

0.64

59

0.91

2.5

10

20 - 6–

1.5

DEX-LN3-050

50

0.37

58

1.08

2.5

Cu 15 x 2

7

3

DEX-LN3-060

60

0.31

60

1.51

2.5

Cu 15 x 2

7

3

DEX-LN3-080

80

0.23

86

1.67

2.5

Cu 20 x 3

96

DEX-LN3-100

100

0.18

101

1.68

2.5

Cu 20 x 3

96

DEX-LN3-120

120

0.15

100

2.26

2.5

Cu 25 x 5

11

10

DEX-LN3-160

160

0.11

140

2.35

2.5

Cu 25 x 5

11

10

DEX-LN3-200

200

0.09

154

3.81

2.5

Cu 25 x 5

11

10

DEX-LN3-250

250

0.07

155

4.26

0

Cu 40 x 5

14

15.5

DEX-LN3-300

300

0.06

169

4.28

2.5

Cu 40 x 5

14

15.5

Part no.

Rated
operatingcurrent

Inductance

Maximumheat
dissipation

Max. heat dissipation(pulse frequency)

Ie

L

Pv

Pv

Pv

Pv

(3 kHz)(5 kHz)(12 kHz)

A

mH

W

W

W

W

Cu factor1)

Connection

Bore hole

Pick-up

Terminal/connection lug

mm2

AWG

mm

Nm

Motor chokes, three-phase, rated operational voltage 3 AC 400 V, max. 200 Hz
DEX-LM3-005

5

2

24

12

14

24

0.29

4

20 - 10–0.8

DEX-LM3-008

8

4.1

54

32

46

54

1.09

4

20 - 10–0.8

DEX-LM3-011

11

3

71

45

66

71

1.23

4

20 - 10–0.8

DEX-LM3-016

16

1.5

78

50

75

78

0.88

4

20 - 10–0.8

DEX-LM3-035

35

1

116

75

114

116

2.30

4

20 - 10–0.8

DEX-LM3-050

50

0.6

168

110

157

168

3.60

10

20 - 6–

1.5

DEX-LM3-063

63

0.5

193

130

190

193

3.01

Cu 15 x 2

7

3

DEX-LM3-080

80

0.5

206

132

206

206

5.88

Cu 20 x 3

96

DEX-LM3-100

100

0.45

294

177

279

294

10.10

Cu 20 x 3

96

DEX-LM3-150

150

0.35

424

293

418

424

8.22

Cu 25 x 5

11

10

DEX-LM3-180

180

0.3

498

418

439

498

14.75

Cu 25 x 5

11

10

DEX-LM3-220

220

0.2

517

344

512

517

11.37

Cu 40 x 5

14

15.5

DEX-LM3-260

260

0.15

520

358

526

520

11.10

Cu 40 x 5

14

15.5

Notes

1) For material price surcharge ￫ Chapter General information2010 CA08103002Z-EN

www.eaton.com

10/38Frequency inverters
MMX...

Dimensions
MMX...

MMX12AA1D7...
MMX12AA2D4...
MMX12AA2D8...
MMX32AA1D7...
MMX32AA2D4...
MMX32AA2D8...
MMX34AA1D3...
MMX34AA1D9...
MMX34AA2D4...

MMX12AA3D7...
MMX12AA4D8...
MMX12AA7D0...
MMX32AA3D7...
MMX32AA4D8...
MMX32AA7D0...
MMX34AA3D3...
MMX34AA4D3...
MMX34AA5D6...

MMX12AA7D0...
MMX32AA011...
MMX34AA7D6...
MMX34AA9D0...
MMX34AA012...
MMX34AA014...

FS1

FS2

FS3

a
a1

a
a1

a
a1

o

o

b1
b

b1
b

b1
b

o

b2

7 mm
(0.275”)c
1 mm = 0.0394 inches
1 inch (1”) = 25.4 mm

Part no.

a1
mm
38
38
38
62.5
62.5
62.5
75

b
mm
160
160
160
195
195
195
253

b1
mm
147
147
147
182
182
182
242

b2
mm
32
32
32
32
32
32
34

c
mm
102
102
102
105
105
105
112

⌀
mm
4.5
4.5
4.5
5.5
5.5
5.5
5.5

Weight
kg
0.55
0.55
0.55
0.7
0.7
0.7
0.99

Frame size

MMX12AA1D7…
MMX12AA2D4…
MMX12AA2D8…
MMX12AA3D7…
MMX12AA4D8…
MMX12AA7D0…
MMX12AA9D6…

a
mm
66
66
66
90
90
90
100

MMX32AA1D7…
MMX32AA2D4…
MMX32AA2D8…
MMX32AA3D7…
MMX32AA4D8…
MMX32AA7D0…
MMX32AA011…

66
66
66
90
90
90
100

38
38
38
62.5
62.5
62.5
75

160
160
160
195
195
195
253

147
147
147
182
182
182
242

32
32
32
32
32
32
34

102
102
102
105
105
105
112

4.5
4.5
4.5
5.5
5.5
5.5
5.5

0.55
0.55
0.55
0.7
0.7
0.7
0.99

FS1
FS1
FS1
FS2
FS2
FS2
FS3

MMX34AA1D3…
MMX34AA1D9…
MMX34AA2D4…
MMX34AA3D3…
MMX34AA4D3…
MMX34AA5D6…
MMX34AA7D6…
MMX34AA9D0…
MMX34AA012…
MMX34AA014…

66
66
66
90
90
90
100
100
100
100

38
38
38
62.5
62.5
62.5
75
75
75
75

160
160
160
195
195
195
253
253
253
253

147
147
147
182
182
182
242
242
242
242

32
32
32
32
32
32
34
34
34
34

102
102
102
105
105
105
112
112
112
112

4.5
4.5
4.5
5.5
5.5
5.5
5.5
5.5
5.5
5.5

0.55
0.55
0.55
0.7
0.7
0.7
0.99
0.99
0.99
0.99

FS1
FS1
FS1
FS2
FS2
FS2
FS3
FS3
FS3
FS3

FS = frame size2010 CA08103002Z-EN

www.eaton.com

FS1
FS1
FS1
FS2
FS2
FS2
FS3

Frequency inverters

10/39

HMX...

Dimensions
HMX...

Frequency inverters
HMX34AG3D421-B
HMX34AG4D821-B
HMX34AG5D621-B
HMX34AG8D021-B
HMX34AG9D621-B
HMX34AG01221-B
HMX34AG3D422-B
HMX34AG4D822-B
HMX34AG5D622-B
HMX34AG8D022-B
HMX34AG9D622-B
HMX34AG01222-B

197

o

I

313
328

HMX32AG3D721-B
HMX32AG4D821-B
HMX32AG6D621-B
HMX32AG8D021-B
HMX32AG01121-B
HMX32AG01221-B
HMX32AG3D722-B
HMX32AG4D822-B
HMX32AG6D622-B
HMX32AG8D022-B
HMX32AG01122-B
HMX32AG01222-B

128
100

e

o
HMX32AG01821-B
HMX32AG02421-B
HMX32AG03121-B
HMX32AG01822-B
HMX32AG02422-B
HMX32AG03122-B

HMX34AG01621-B
HMX34AG02321-B
HMX34AG03121-B
HMX34AG01622-B
HMX34AG02322-B
HMX34AG03122-B

144
115

222

o

406
419

I

e

o
HMX34AG03821-B
HMX34AG04621-B
HMX34AG06121-B
HMX34AG03822-B
HMX34AG04622-B
HMX34AG06122-B

195
148

o

236

I

541
557

HMX32AG04821-B
HMX32AG06221-B
HMX32AG04822-B
HMX32AG06222-Beo2010 CA08103002Z-EN

www.eaton.com

10/40Frequency inverters
HMX...

Part no.
HMX32AG011…
HMX32AG012…
HMX32AG018…
HMX32AG024…
HMX32AG031…
HMX32AG048…
HMX32AG062…
HMX32AG077…
HMX32AG088…
HMX32AG106…
HMX32AG143…
HMX32AG170…
HMX32AG208…
HMX32AG261…
HMX32AG310…
HMX32AG3D7…
HMX32AG4D8…
HMX32AG6D6…
HMX32AG8D0…

a
mm
128
128
144
144
144
195
195
234
234
234
290
290
290
480
480
128
128
128
128

HMX34AG012…
HMX34AG016…
HMX34AG023…
HMX34AG031…
HMX34AG038…
HMX34AG046…
HMX34AG061…
HMX34AG077…
HMX34AG088…
HMX34AG106…
HMX34AG140…
HMX34AG170…
HMX34AG205…
HMX34AG261…
HMX34AG310…
HMX34AG3D4…
HMX34AG4D8…
HMX34AG5D6…
HMX34AG8D0…
HMX34AG9D6…

128
144
144
144
195
195
195
234
234
234
290
290
290
480
480
128
128
128
128
128

a1
mm
100
100
115
115
115
148
148

100
100
100
100
100
115
115
115
148
148
148

100
100
100
100
100

FS = frame size2010 CA08103002Z-EN

www.eaton.com

b
mm
328
328
419
419
419
557
557
660
660
660
966
966
966
1150
1150
328
328
328
328
328
419
419
419
557
557
557
660
660
660
966
966
966
1150
1150
328
328
328
328
328

b1
mm
313
313
406
406
406
541
541

313
313
313
313
313
406
406
406
541
541
541

313
313
313
313
313

c
mm
197
197
222
222
222
236
236
266
266
266
350
350
350
372
372
197
197
197
197
197
222
222
222
236
236
236
266
266
266
350
350
350
372
372
197
197
197
197
197

⌀
mm
7
7
7
7
7
9
9

7
7
7
7
7
7
7
7
9
9
9

7
7
7
7
7

Weight
kg
6
6
10
10
10
20
20
37.5
37.5
37.5
70
70
70
108
108
6
6
6
6

Frame size
FS
FS4
FS4
FS5
FS5
FS5
FS6
FS6
FS7
FS7
FS7
FS8
FS8
FS8
FS9
FS9
FS4
FS4
FS4
FS4

6
10
10
10
20
20
20
37.5
37.5
37.5
70
70
70
108
108
6
6
6
6
6

FS4
FS5
FS5
FS5
FS6
FS6
FS6
FS7
FS7
FS7
FS8
FS8
FS8
FS9
FS9
FS4
FS4
FS4
FS4
FS4

Frequency inverters

10/41

Braking resistors, PC connection
BR2...-T-SAF, BR1...-T-PF, BR3...-T-PF; MMX-COM-PC
Braking resistors, PC connection

Braking resistors
BR2036400-T-SAF
BR2047240-T-SAF
BR2060200-T-SAF
BR2065400-T-SAF
BR2075480-T-SAF
272

273

315

90

70

100

80

100

336

320

320

Braking resistors
BR10361K0-T-PF
BR10561K0-T-PF
BR1036500-T-PF
BR1056300-T-PF
BR1056800-T-PF
BR30362K4-T-PF
BR30362K8-T-PF
BR30363K6-T-PF
Part no.
c

BR10361K0-T-PF
BR10561K0-T-PF
BR1036500-T-PF

a1

b1

BR1056300-T-PFab

BR1056800-T-PF
BR30362K4-T-PF
BR30362K8-T-PF

d

a1
mm
428
428
428
328
378
380
380
380

b
mm
140
140
95
95
140
326
326
326

b1
mm
120
120
70
70
120
300
300
300

c
d
mm mm
120 6 x 12
120 6 x 12
95 6 x 12
95 6 x 12
120 6 x 12
301
9
301
9
301
9

b1

BR30363K6-T-PF

a
mm
445
445
445
335
395
485
485
485

a1

PC interfacing

ADAPTERCOMM

66

MMX-COM-PC

ERROR
AC DRIVE

63

32
50

2010 CA08103002Z-EN

www.eaton.com

10/42Frequency inverters
Radio interference suppression filters
MMX-LZ1..., MMX-LZ3...

Radio interference suppression filters

MMX-LZ1-009

MMX-LZ1-015

MMX-LZ1-017

100

66
90

50

60

303

293

253

245

235

195

207

197

157

70

4.5
30
4.5
45

5.5
45

MMX-LZ3-006

MMX-LZ3-009

MMX-LZ3-020

66
90

100

70

60

4.5
30
5.5
45
5.5
45

2010 CA08103002Z-EN

www.eaton.com

303

293

253

245

235

195

207

197

157

50

Frequency inverters

10/43

Mains chokes, motor chokes
DEX-LN..., DEX-LM3...
Mains chokes, motor chokes

Mains chokes
DEX-LN1-...
Part no.

a
mm
66
66
84
84
84

c±5

1 2

c1 ± 5PE

da1

DEX-LN1-006
DEX-LN1-009
DEX-LN1-013
DEX-LN1-018
DEX-LN1-024

a1
mm
50
50
64
64
64

b
mm
71
71
67
90
67

b1
mm
44
44
47
70
47

b2
mm
55
55
60
83
60

c
mm
80
80
90
90
90

c1
mm
61
61
75
75
75

⌀d
mm
4.5 x 84.5 x 84.8 x 84.8 x 84.8 x 8Weight
kg
0.7
0.7
1.5
1.5
2

b1
b2

a

b 5

Mains chokes/motor chokes
DEX-LN3-..., DEX-LM3-...
Part no.
DEX-LN3-004
DEX-LN3-006
DEX-LN3-010
DEX-LN3-016
DEX-LN3-025
DEX-LN3-040

a
mm
115
115
140
140
195
195

a1
mm
100
100
125
125
175
175

b
mm
66
66
61
71
104
104

b1
mm
50
50
50
50
50
50

b2
mm
66
66
61
71
76.5
76.5

c
mm
118
118
138
138
175
188

c1
mm
84
84
105
105
134
134

⌀d
mm
5 x 105 x 105 x 105 x 108 x 138 x 13Weight
kg
1.5
1.5
2.2
2.9
4.8
4.8

DEX-LM3-005
DEX-LM3-008
DEX-LM3-011
DEX-LM3-016
DEX-LM3-035
DEX-LM3-050

115
195
195
195
220
270

100
175
175
175
200
250

66
104
104
104
132
106

50
50
50
50
75
75

66
76.5
76.5
76.5
101.5
96

118
175
175
175
195
228

84
134
134
134
160
198

5 x 108 x 138 x 138 x 138 x 138 x 13

1.5
4.8
4.8
4.8
7.3
12.3

⌀d
mm
8 x 138 x 138 x 138 x 138 x 138 x 138 x 1310 x 18
10 x 18

Weight
kg
5.9
5.9
7.3
10.2
10.2
12.3
14.9
20.6
20.6

U1 U2 V1 V2 W1W2

c1± 5

c ±5

PE

d

a1

b1

a

b2
b±5

Mains chokes/motor chokes
DEX-LN3-..., DEX-LM3-...
PE

1)

a1
a

c

PE

od

1)

b1
b2

DEX-LN3-050
DEX-LN3-060
DEX-LN3-080
DEX-LN3-100
DEX-LN3-120
DEX-LN3-160
DEX-LN3-200
DEX-LN3-250
DEX-LN3-300

a
mm
195
195
220
220
220
270
270
270
270

a1
mm
175
175
200
200
200
250
250
250
250

b
mm
105
105
110
130
130
125
155
155
155

b1
mm
75
75
50
75
75
75
100
100
100

b2
mm
91.5
91.5
81.5
101.5
101.5
96
120
125
125

c2)
mm
132 ±5132 ±5160 ±5160 ±5160 ±5200 ±5202 ±5210 ±5210 ±5

DEX-LM3-063
DEX-LM3-080

270
270

250
250

155
155

100
100

120
125

202 ±10 8 x 13
210 ±10 10 x 18

14.9
20.6

DEX-LM3-100
DEX-LM3-150
DEX-LM3-180
DEX-LM3-220
DEX-LM3-260

384
384
384
384
384

350
350
350
350
350

215
260
260
260
260

100
150
150
150
150

130
180
180
180
180

258 ±30258 ±30258 ±30258 ±30258 ±30

31
45
45
45
45

Part no.

b ± 1012 x 20
12 x 20
12 x 20
12 x 20
12 x 20

1) The position of connection lugs U2-V2-W2 depends on the coil material and can deviate from the position illustrated here.
2) Tolerance depending on air gap

2010 CA08103002Z-EN

www.eaton.com