For the 277/480V Grid for North America
SE80KUS / SE100KUS / SE110KUS / SE120KUS
12-20INVERTER

Three Phase Inverterwith Synergy Technology

YEAR
WARRANTY

Powered by unique pre-commissioning process for rapid system installation
Pre-commissioning feature for automatedvalidation of system components and wiring
during the site installation process and prior togrid connection
Easy 2-person installation with lightweight,
modular design (each inverter consists of 2 or
3 Synergy units and 1 Synergy Manager)
Independent operation of each Synergy unit
enables higher uptime and easy serviceability
Built-in thermal sensors detect faulty wiring,ensuring enhanced protection and safety*Applicable only for DC and AC SPDs

solaredge.com

Built-in arc fault protection and rapid
shutdown
Built-in PID mitigation for maximized system
performance
Monitored* and field-replaceable surge
protection devices, to better withstand surges
caused by lightning or other events
Built-in module-level monitoring with Ethernet
or cellular communication for full system
visibility

Three Phase Inverter with Synergy Technology
For the 277/480V Grid for North America
SE80KUS / SE100KUS / SE110KUS / SE120KUS
MODEL NUMBER

SE80KUSAPPLICABLE TO INVERTERS WITH PART NUMBER

SE100KUS

SE110KUS

SE120KUS

SExxK-USx8Ixxxx

UNITS

OUTPUT
Rated AC Active Output Power

80000

100000110000120000W

Maximum AC Apparent Output Power

80000

100000120000120000VA

AC Output Line Connections

3W + PE, 4W + PE

Supported Grids

WYE: TN-C, TN-S, TN-C-S, TT, IT; Delta: IT

AC Output Voltage Minimum-Nominal-Maximum(1) (L-N)

244 – 277 – 305

Vac

AC Output Voltage Minimum-Nominal-Maximum(1) (L-L)

422.5 – 480 – 529

Vac

AC Frequency Min-Nom-Max(1)59.5 – 60 – 60.5

Maximum Continuous Output Current (per Phase, PF=1)

96.5

Hz120

144.3

GFDI Threshold

1Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds

Yes

Total Harmonic DistortionA≤3Power Factor Range

Aac%±0.85 to 1

INPUT
Maximum DC Power (Module STC) Inverter / Synergy Unit

140000 / 70000

175000 / 58300

Transformer-less, Ungrounded
Maximum Input Voltage DC+ to DC-1000

Operating Voltage Range
Maximum Input Current

2 x 48.25

Vdc

3 x 403 x 48.25

167kΩ sensitivity per Synergy Unit(2)

CEC Weighted Efficiency

98.5<8%< 12ADDITIONAL FEATURES
Smart Energy Management
Inverter Commissioning
Arc Fault Protection
Photovoltaic Rapid Shutdown System
PID Rectifier

2 x RS485, Ethernet, Wi-Fi (optional), Cellular (optional)
Export Limitation
With the SetApp mobile application using built-in Wi-Fi access point for local connection
Built-in, User Configurable (According to UL1699B)
NEC 2014 – 2023, built-in
Nighttime, built-in

RS485 Surge Protection (ports 1+2)

Type II, field replaceable, integrated

AC, DC Surge Protection

Type II, field replaceable, integrated

DC Fuses (Single Pole)

25A, integrated

DC SAFETY SWITCHDC Disconnect

Built-in

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Emissions

Adc

Yes

Ground-Fault Isolation Detection

Supported Communication Interfaces(3)WVdc

850 – 1000

Reverse-Polarity Protection

Nighttime Power Consumption

210000 / 70000
Yes

UL1699B, UL1741, UL1741 SA, UL1741 SB, UL1998, CSA C22.2#107.1,
Canadian AFCI according to T.I.L. M-07
IEEE 1547-2018, Rule 21, Rule 14 (HI)FCC part 15 class A(1) For other regional settings please contact SolarEdge support.
(2) Where permitted by local regulations.
(3) For specifications of the optional communication options, visit the Communication product page or the Knowledge Center to download the relevant product datasheet.

WThree Phase Inverter with Synergy Technology
For the 277/480V Grid for North America
SE80KUS / SE100KUS / SE110KUS / SE120KUS
MODEL NUMBER

SE80KUSSE100KUS

APPLICABLE TO INVERTERS WITH PART NUMBER

SE110KUS

SE120KUS

SExxK-USx8Ixxxx

UNITS

INSTALLATION SPECIFICATIONS
Number of Synergy Units per Inverter

23Ac Max Conduit Size

2 ½‫״‬Max AWG Line / PE

4/0 / 1/0DC Max Conduit Size
DC Input Inverter/Synergy Unit

in1 x 3"; 2 x 2"inMulti-input (SExxK-USxxxxxZ4)

8 / 4 pairs; 6-12 AWG

12 / 4 pairs; 6-12 AWG

Combined input (SExxK-USxxxxxW4)

2 pairs / 1 pair,Max 2 AWG; copperor aluminum

3 pairs / 1 pair,Max 2 AWG; copper or aluminum

Dimensions (H x W x D)
WeightOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting(4) For power de-rating information refer to the Temperature Derating Technical Note for North America.

Synergy Unit: 22 x 12.9 x 10.75 / 558 x 328 x 273
Synergy Manager: 14.17 x 22.4 x 11.6 / 360 x 560 x 295
Synergy Unit: 70.4 / 32
Synergy Manager: 39.6 / 18-40 to +140 / -40 to +60(4)in / mmlb / kg̊ F / ˚C

Fan (user replaceable)< 67
NEMA 3R
Brackets provideddBA

SolarEdge is a global leader in smart energy technology.
By leveraging world-class engineering capabilities and witha relentless focus on innovation, SolarEdge creates smart
energy solutions that power our lives and drive future
progress.
SolarEdge developed an intelligent inverter solution thatchanged the way power is harvested and managed inphotovoltaic (PV) systems. The SolarEdge DC optimized
inverter maximizes power generation while lowering thecost of energy produced by the PV system.
Continuing to advance smart energy, SolarEdge addresses
a broad range of energy market segments through its PV,storage, EV charging, UPS, and grid services solutions.

SolarEdge@SolarEdgePV@SolarEdgePV
SolarEdgePV
SolarEdgewww.solaredge.com/corporate/contact

solaredge.com© SolarEdge Technologies, Ltd. All rights reserved.
SOLAREDGE, the SolarEdge logo, OPTIMIZED BYSOLAREDGE are trademarks or registered trademarksof SolarEdge Technologies, Inc. All other trademarks
mentioned herein are trademarks of their respective
owners. Date: May 8, 2024 DS-000020-NAM
Subject to change without notice.
Cautionary Note Regarding Market Data andIndustry Forecasts: This brochure may containmarket data and industry forecasts fromcertain third-party sources. This information
is based on industry surveys and thepreparer’s expertise in the industry andthere can be no assurance that any suchmarket data is accurate or that any suchindustry forecasts will be achieved.
Although we have not independently
verified the accuracy of such market
data and industry forecasts, webelieve that the market data isreliable and that the industry
forecasts are reasonable.

solaredge.com