For the 277/480V Grid for North America(Ground Mount Installation)
SE110KUS / SE120KUS
12-20

INVERTER

Three Phase Inverterwith Synergy TechnologyYEAR
WARRANTY

Powered by unique pre-commissioning process for rapid system installation
Pre-commissioning feature for automatedvalidation of system components and wiring
during the site installation process and prior togrid connection

Built-in arc fault protection

Easy 2-person installation with lightweight,
modular design (each inverter consists of3 Synergy units and 1 Synergy Manager)

Monitored* and field-replaceable surge
protection devices, to better withstand surges
caused by lightning or other events

Independent operation of each Synergy unit
enables higher uptime and easy serviceability

Built-in module-level monitoring with Ethernet
or cellular communication for full system
visibility

Built-in thermal sensors detect faulty wiring
ensuring enhanced protection and safety

solaredge.com

Built-in PID mitigation for maximized system
performanceThree Phase Inverter with Synergy Technology
For the 277/480V Grid for North America (Ground Mount Installation)
SE110KUS / SE120KUS
MODEL NUMBER

SE110K

SE120KUNITS

Rated AC Active Output Power

110000120000W

Maximum AC Apparent Output Power120000

120000VA

OUTPUT

AC Output Line Connections
Supported Grids

3W + PE, 4W + PE
WYE: TN-C, TN-S, TN-C-S, TT, IT; Delta: IT

AC Output Voltage Minimum-Nominal-Maximum(1) (L-N)

244 – 277 – 305

Vac

AC Output Voltage Minimum-Nominal-Maximum(1) (L-L)

422.5 – 480 – 529

Vac

AC Frequency Min-Nom-Max(1)59.5 – 60 – 60.5

Hz

144.3

Aac

1

AMaximum Continuous Output Current (per Phase, PF=1)
GFDI Threshold
Utility Monitoring, Islanding Protection, Configurable Power Factor,
Country Configurable Thresholds

YesTotal Harmonic Distortion≤3Power Factor Range%+/-0.2 to 1

INPUT
Maximum DC Power (Module STC) Inverter / Synergy Unit
Transformer-less, Ungrounded
Maximum Input Voltage DC+ to DC-

210000 / 70000

WYes
1000

Vdc

Operating Voltage Range

840 – 1000

Vdc

Maximum Input Current

3 x 48.25

Adc

Reverse-Polarity Protection
Ground-Fault Isolation Detection

Yes
167kΩ sensitivity per Synergy Unit(2)

CEC Weighted Efficiency

98.5%

Nighttime Power Consumption< 12W

ADDITIONAL FEATURES
Supported Communication Interfaces(3)Smart Energy Management
Inverter Commissioning
Arc Fault Protection
PID Rectifier

2 x RS485, Ethernet, Wi-Fi (optional), Cellular (optional)
Export Limitation
With the SetApp mobile application using built-in Wi-Fi access point for local connection
Built-in, User Configurable (According to UL1699B)
Nighttime, built-in

RS485 Surge Protection (ports 1+2)

Type II, field replaceable, integrated

AC, DC Surge Protection

Type II, field replaceable, integrated

DC SAFETY SWITCHDC Disconnect

Built-in

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Emissions

UL1699B, UL1741, UL1741 SA, UL1741 SB, UL1998, CSA C22.2#107.1,Canadian AFCI according to T.I.L. M-07
IEEE 1547-2018, Rule 21, Rule 14 (HI)FCC part 15 class A(1) For other regional settings please contact SolarEdge support.
(2) Where permitted by local regulations.
(3) For specifications of the optional communication options, visit the Communication product page or the Resource Library to download the relevant product datasheet.

Three Phase Inverter with Synergy Technology
For the 277/480V Grid for North America (Ground Mount Installation)
SE110KUS / SE120KUS
MODEL NUMBER

SE110K

SE120KUNITS

INSTALLATION SPECIFICATIONS
Number of Synergy Units per Inverter

3AC Max Conduit Size

2 ½‫״‬Max AC AWG Line / PE

4/0 / 1/0

DC Max Conduit Size

1 x 3"; 2 x 2"

inin

12 / 4 pairs; 6 – 12 AWG
DC Inputs Inverter / Synergy Unit
Dimensions (H x W x D)
WeightOperating Temperature Range
Cooling
Noise
Protection Rating
Mounting(4) For power de-rating information refer to the Temperature De-rating - Technical Note (North America).

3 pairs / 1 pair,Max 2 AWG; copper or aluminum
Synergy Unit: 22 x 12.9 x 10.75 / 558 x 328 x 273
Synergy Manager: 14.17 x 22.4 x 11.6 / 360 x 560 x 295
Synergy Unit: 70.4 / 32
Synergy Manager: 39.6 / 18

in / mm-40 to +140 / -40 to +60(4)̊ F / ˚Clb / kg

Fan (user replaceable)< 67
NEMA 3R
Brackets provideddBA

SolarEdge is a global leader in smart energy technology.
By leveraging world-class engineering capabilities and witha relentless focus on innovation, SolarEdge creates smart
energy solutions that power our lives and drive future
progress.
SolarEdge developed an intelligent inverter solution thatchanged the way power is harvested and managed inphotovoltaic (PV) systems. The SolarEdge DC optimized
inverter maximizes power generation while lowering thecost of energy produced by the PV system.
Continuing to advance smart energy, SolarEdge addresses
a broad range of energy market segments through its PV,
storage, EV charging, UPS, and grid services solutions.

SolarEdge@SolarEdgePV@SolarEdgePV
SolarEdgePV
SolarEdgewww.solaredge.com/corporate/contact

solaredge.com© SolarEdge Technologies, Ltd. All rights reserved.
SOLAREDGE, the SolarEdge logo, OPTIMIZED BYSOLAREDGE are trademarks or registered trademarksof SolarEdge Technologies, Inc. All other trademarks
mentioned herein are trademarks of their respective
owners. Date: November 27, 2022 DS-000021-NAM
Subject to change without notice.
Cautionary Note Regarding Market Data andIndustry Forecasts: This brochure may containmarket data and industry forecasts fromcertain third-party sources. This information
is based on industry surveys and thepreparer’s expertise in the industry andthere can be no assurance that any suchmarket data is accurate or that any suchindustry forecasts will be achieved.
Although we have not independently
verified the accuracy of such market
data and industry forecasts, webelieve that the market data isreliable and that the industry
forecasts are reasonable.

solaredge.com