For North America
SE30KUS / SE40KUS
12-20YEARWARRANTY

INVERTERS

Three Phase Inverters
for the 277/480V Grid

The best choice for SolarEdge enabled systems
Specifically designed to work with power
optimizers
Quick and easy inverter commissioning directlyfrom a smartphone using SolarEdge SetApp
Fixed voltage inverter for superior efficiency(98.5%) and longer strings
Built-in type 2 DC and AC Surge Protection, tobetter withstand lightning events
Small, lightest in its class, and easy to installoutdoors or indoors on provided bracket

solaredge.com

Integrated arc fault protection and rapid
shutdown for NEC 2014 – 2023, per articles
690.11 and 690.12
Built-in module level monitoring with Ethernet,
wireless, or cellular communication for full system
visibility
Integrated safety switch
UL1741 SA and SB certified, for CPUC Rule 21 gridcomplianceThree Phase Inverters for the 277/480V Grid(1)for North America
SE30KUS / SE40KUS
MODEL NUMBER

SE30KUSAPPLICABLE TO INVERTERS WITH PART NUMBER

SE40KUSSEXXK-USX8IXXXXUNITSOUTPUT
Rated AC Power Output

30000

40000

W

Maximum Apparent AC Output Power

30000

40000

VA

AC Output Line Connections

3W + PE, 4W + PE

AC Output Voltage Minimum-Nominal-Maximum(2) (L-N)

244 – 277 – 305

Vac

AC Output Voltage Minimum-Nominal-Maximum(2) (L-L)

422.5 – 480 – 529

Vac

AC Frequency Min-Nom-Max(2)59.3 – 60 – 60.5

Maximum Continuous Output Current (per Phase)

36.25

GFDI Threshold

1

Utility Monitoring, Islanding Protection, Country Configurable Set Points

Yes

Total Harmonic Distortion

Hz
48.25

A

≤3

Power Factor Range

Aac%+/- 0.85 to 1

INPUT
Maximum DC Power (Module STC)

52500

Transformer-less, Ungrounded

70000

W

Yes

Maximum Input Voltage DC+ to DC-1000

Operating Voltage Range

Vdc

840 – 1000

Maximum Input Current

36.25

Maximum Input Short Circuit Current

55

Reverse-Polarity Protection

Yes

Ground-Fault Isolation Detection

Vdc
48.25

Adc
Adc

167kΩ Sensitivity(3)CEC Weighted Efficiency

98.5

%

Night-time Power Consumption<4W

ADDITIONAL FEATURES
Supported Communication Interfaces
Inverter Commissioning

2 x RS485, Ethernet, Cellular (optional)
With the SetApp mobile application using built-in access point for local connection

Arc Fault Protection
Rapid Shutdown

Integrated, User Configurable (According to UL1699B)
NEC 2014 – 2023, built-in

RS485 Surge Protection Plug-in

Supplied with the inverter, built-in

DC Surge Protection

Type II, field replaceable, built-in

AC Surge Protection

Type II, field replaceable, built-in

DC Fuses (Single Pole)
Smart Energy Management

25A, built-in
Export Limitation

DC SAFETY SWITCHDC Disconnect

Integrated

STANDARD COMPLIANCE
SafetyGrid Connection Standards
Emissions

UL 1741, UL 1741 SA, UL 1741 SB, UL 1699B, CSA C22.2,
Canadian AFCI according to T.I.L. M-07
IEEE 1547-2018, Rule 21, Rule 14 (HI)FCC Part 15 Class A

INSTALLATION SPECIFICATIONSAC Output Conduit Size / AWG Range¾” or 1” / 6 – 10 AWG

DC Input Conduit Size / AWG Range¾” or 1” / 6 – 12 AWG

Number of DC Inputs Pairs
Dimensions with Safety Switch (H x W x D)
Weight with Safety Switch
Cooling
Noise
Operating Temperature Range
Protection Rating
Mounting

431.8 x 12.5 x 11.8 / 808 x 317 x 300

in / mm

78.2 / 35.5lb / kg

Fans (user replaceable)< 62dBA-40 to +140 / -40 to +60(4)˚F / ˚C

NEMA 3R
Bracket provided(1) For 120/208V inverters refer to the Three Phase Inverters for the 120/208V Grid for North America datasheet.
(2) For other regional settings please contact SolarEdge support.
(3) Where permitted by local regulations.
(4) For power derating information refer to the Temperature Derating technical note for North America.

© SolarEdge Technologies, Ltd. All rights reserved. SOLAREDGE, the SolarEdge logo, OPTIMIZED BY SOLAREDGE are trademarks or registered trademarks of SolarEdge Technologies, Inc.
All other trademarks mentioned herein are trademarks of their respective owners. Date: May 16, 2024 DS-000070-NAM. Subject to change without notice.