قطر دولة   
والتقييس  للمواصفات  القطرية  العامة الھيئة   
QATAR GENERAL ORGANIZATI ON FOR STANDARDIZATION 
 
 
القطرية  القياسية  المواصفة   
QS 2663:2019   
 
 
 
 
 
      والحدود  الطاقة  بطاقات  الدنيامتطلبات   لمكيفات  الطاقة  استھلاك  لكفاءة
الھواء  
 
ENERGY LABELLING AND MINIMUM ENERGY 
PERFORMANCE REQUIREMENTS 
FOR AIR-CONDITIONERS 
 
 
ICS :  : 23.120 
 ﺗـﻘدﻳـم 
 
واﻟﺗﻘﻳﻳس  ﻟﻠﻣواﺻﻔﺎت  اﻟﻘطرﻳﺔ اﻟﻌﺎﻣﺔ اﻟﻬﻳﺋﺔ   ﻣﻬﺎﻣﻬﺎ إﺻدارﻣن  اﻟﻣواﺻﻔﺎت  اﻟﻘﻳﺎﺳﻳﺔ  اﻟﻔﻧﻳﺔ واﻟﻠواﺋﺢ
 ﻗطر، دوﻟﺔ ﻓﻲ واﻟﺧدﻣﺎت  اﻟﻣﻧﺗﺟﺎت  ﺑواﺳطﺔﻟﻣﺧﺗﻠف   ﻟﺟﺎن . ﻣﺗﺧﺻﺻﺔ  ﻓﻧﻳﺔ                                            
 ﻗﺎﻣت ﺑﺎﻟﻬﻳﺋﺔوﻗد  واﻟﻣﻘﺎﻳﻳس  اﻟﻣواﺻﻔﺎت  ادارة   ادارة ﻣﻊ وﺑﺎﻟﺗﻧﺳﻳق  واﻟﺗﻘﻳﻳس  ﻟﻠﻣواﺻﻔﺎت  اﻟﻘطرﻳﺔ اﻟﻌﺎﻣﺔ
اﻟﻘﻳﺎ اﻟﻣواﺻﻔﺔ  ﺑﺈﻋداد واﻟﻣﺎء ﻟﻠﻛﻬرﺑﺎء  اﻟﻘطرﻳﺔ اﻟﻌﺎﻣﺔ ﺑﺎﻟﻣؤﺳﺳﺔ  اﻟطﺎﻗﺔ وﻛﻔﺎءة اﻟﺗرﺷﻳد  رﻗم اﻟﻘطرﻳﺔ ﺳﻳﺔ
QS 2663:2019  "( اﻟدﻧﻳﺎ واﻟﺣدود اﻟطﺎﻗﺔ ﺑطﺎﻗﺎت ﻣﺗطﻠﺑﺎت   ﻟﻣﻛﻳﻔﺎت  اﻟطﺎﻗﺔ اﺳﺗﻬﻼك  ﻟﻛﻔﺎءة
اﻟﻬواء  " .
        )          (     رﻗم واﻟﺑﻳﺋﺔ اﻟﺑﻠدﻳﺔ وزﻳر ﺳﻌﺎدة ﻣن ﺑﻘرار اﻟﻘﻳﺎﺳﻳﺔ اﻟﻣواﺻﻔﺔ  ﻫذﻩ اﻋﺗﻣدت  وﻗد
 ﻟﺳﻧﺔ2019  /     /     ﺑﺗﺎرﻳﺦ ، م1440  اﻟﻣواﻓق ه2019. م          
 
 
Foreword 
One of the main responsibilities of Qatar general Organization  for 
Standardization is to issue different standards and technical regulations on ( 
commodities & services ) in the State of  Qatar, through specialized technical 
committees ( TCs) . 
Standards & Metrology Department with in Qatar General Organization for 
Standardization, in coordination with the Conservation & Energy Efficiency 
Department  of Qatar General Electri city & Water Corporation has been 
preparing Qatari standard No. ( QS 2663:2019)”  ENERGY LABELLING AND 
MINIMUM ENERGY PERFORMANCE REQUIREMENTS FOR AIR-CONDITIONERS. 
             This standard has b een approved as a Qatari  technical regulation by 
the Municipality & Environment Minister held on   /  / 1440 H ,                     /     /  2019 G .  
 
 
 QATAR STANDARD QS  2663/2019  
 
2 
 ENERGY LABELLING AND MINIMUM  
ENERGY PERFORMANC E REQUIREMENTS 
FOR AIR-CONDITIONERS 
 
1. SCOPE AND OBJECTIVE  
1.1 Scope 
 This standard specifies the energy labelling requirements and the Minimum 
Energy Performance Standard (MEPS) requirements for single-package (such as window type) and split-system non-duc ted air conditioners using air- and 
water-cooled condensers and heat pumps employing air-cooled condensers and ducted air-conditioners using air-to-air heat pumps for residential, commercial and industrial sector as applicable in accordance with Qatari  standards. 
1.2 Objective 
 The objective of this standard is to: 
a) Provide detailed information on the performance and energy labelling 
requirements which an airconditioning a ppliance has to meet in order to 
carry a valid energy efficiency label; and 
b) Provide detailed information on th e performance requirements which an 
air-conditioning appliance has to meet in order to meet minimum energy performance standard requirements. 
 
2. NORMATIVE REFERENCES 
         Updated editions of the followi ng normative references ar e applied (Including any 
         changes on these normative references). 
 
2.1 QS ISO :5151 “Non-ducted air conditioners and heat Pumps -Testing and rating 
for Performance”. 
2.2 QS ISO :13253 “Ducted air-conditioners and ai r-to-air heat Pumps - Testing 
and rating for Performance” . 
 
3. TERMS AND DEFINITIONS 
 For the purposes of this standard, the terms and definitions given in QS  
mentioned in sub-clauses 2.1 and 2.2 and those below are considered. 
3.1 Ducted airconditioners 
 An airconditioner model configuration wher e the indoor side is situated remote 
to the space to the conditioned.  The cond itioned air is supplied or extracted via 
a duct. 
3.2 Non-ducted airconditioner  
 An airconditioner model configuration wher e the indoor side is situated partly 
or wholly within the space to be cond itioned.  The conditioned air is supplied 
and extracted directly to and from the conditioned space. QATAR STANDARD QS  2663/2019  
 
3 
 3.3 Rated capacity 
 The nominal rated capacity claimed by the manufacturer of an airconditioner 
model determined as follows, as applicable: 
(a) Rated total cooling capacity   As claimed by the manufacturer for 
temperature condition T1 and T3.  (Units: Btu/h). 
(b) Rated heating capacity   As clai med by the manufacturer for temperature 
condition H1.  (Units Btu/h). 
 The rated capacity appears on the energy label as ‘Capacity Output’ (heating 
and/or cooling as applicable.  (Units: Btu/h). 
3.4 Rated power 
 Effective power input of the ai rconditioner model as claimed by the 
manufacturer during the determination of rated cooling capacity and rated 
heating capacity, as applicable.  (Units: W or kW.) 
3.5 Split system 
 An airconditioner with separate i ndoor and outdoor components that are 
connected with refrigerant piping.  Th e indoor unit usually lies within the 
conditioned space and may be installed or portable/mobile. 
3.6 Star rating 
 The number of stars displayed on the ener gy label.  Available stars are between 
a minimum of one and a maximum of six.  It is considered as an indication of the claimed energy efficiency of a mode l at rated conditions.  A higher star 
rating indicates a higher energy efficienc y.  It is derived from the measured 
EER . 
3.7            Estimated annual energy consumption 
                 Rated power expected within 2700 working hour with a full load annually. 
                 Formula to calculate the Estimated Annual Energy Consumption :                  Estimated Annual Energy Consumption = ( Total Input Power in KW at (T1) 
conditions ) x ( 2700 hours/year) .   
 
 
4. REGISTRATION REQUIREMENTS 
4.1       The information about registra tion requirement for energy labelling and 
                   MEPS will be available in Laboratories & Standardization Affairs.  4.2 For registration of an airconditioner fo r energy labelling and MEPS with a test 
report in accordance with recent editi on of QS ISO 5151 or QS ISO 13253, as 
applicable.  An application shall be  provided for each model, in accordance 
with Appendix A, and submitted to the registration body . 
 QATAR STANDARD QS  2663/2019  
 
4 
 4.3 Energy Label Validity (Check Testing) 
 The energy label shall be accepted as valid when a single sample of an 
appliance or unit model, tested for an initial screening test, meets the following criteria for cooling and heating, as applicable: 
              a)      Tested effective power input ………….........……. ≤1.05 x rated power. 
b) Tested cooling and heating capacity ………….….. ≥0.95 x rated capacity. 
c) Tested EER …………………………………….…….. ≥0.95 x rated EER. 
d) Tested COP …………………………………….……. ≥0.95 x rated COP. 
        e)      Tested voltage  .....................240 volt single phase or 415 volt three phase. 
f) Tested frequency …………………………………………………. 50 Hz. 
              g)      Testing conditions ( T1,T3 )...... (refer to the standards mentioned in 
clause 2). 
 
5. MEPS 
The minimum energy performance standard ME PS value for the air conditioner in the 
scope of this standard shall be greater than or equal to the value of Energy Effeicency 
Ratio ( EER ), When calculating the cooling capacity at test conditions ( T1) and test 
condition ( T3) as follows: 
 
 
  
Air Conditioner 
appliance type  
Cooling 
Capacity limit 
(CC) 
(Btu/h) 
At test 
condition (T1)(EER) Value 
(Btu/h)/watt 
To be applied 
mandatory  
 
 First Stage (EER) Value 
(Btu/h)/watt 
To be applied 
mandatory  
 
Second Stage 
T1 T3 T1 T3 
 
 
Window Type 18000  >  CC 8.5 6.12 8.5 6.12 
18000  ≤   CC  
<  24000 8.5 6.12 8.5 6.12 
CC   ≥  24000 8.5 6.12 8.5 6.12 
Split Type and the 
other types All Capacities 9.5 6.84 11.5 8.28 
 
6. NAME PLATE AND INSTRUCTION SHEET OR MANUAL 
 In addition to any information needed to be displayed on the air-conditioner 
unit, the following information shall be marked on the name plate of the air-
conditioner, in Arabic or English or both. The marking shall not be on a detachable part of the unit and shall be indelible, durable and easily legible. 
 Any information related energy performa nce added showed in any part of the 
air-conditioner unit or packaging shall not have any ambiguity or lead to miss 
understand of the performance of the unit. QATAR STANDARD QS  2663/2019  
 
5 
 6.1 The information on the name plate in Arab ic or English or both shall include at 
least: 
– Manufacturer’s name and/or trademark. – Country of origin. – Manufacturer’s model or type reference and serial number of the unit. – Rated voltage or rated voltage range (Volts). – Rated frequency (Hz). – For each of cooling test conditions T1 and T3 according to the standard 
stated in clauses 2.1 and 2.2, as applicable: 
• Rated current in Amperes. 
• Rated power input in watts or kilowatts. 
• Net total room cooling capacity in Btu/h (and any units of kW or 
Kcal/h) when tested according to conditions stated in clauses 2.1 
and 2.2. 
• Energy Efficiency Ratio (EER) in (Btu/hr)/Watt. 
– For heating test conditions according to  the standard stated in clauses 2.1 
and 2.2, as applicable. 
• Current rating (Amperes). 
• Input power rating (watts or kilowatts). 
• Heating capacity in W when tested according to conditions stated 
in clauses 2.1 and 2.2, as applicable. 
• Coefficient of Performance (COP) (watt/watt). 
– Refrigerant used and mass of refrigerant charge in kg. 
6.2 An instruction sheet or manual in both Arabic and English shall be delivered 
with each air-conditioner, including the following information: 
– The information specified in clause 6.1. – Dimensions of the unit and its method of mounting. – Minimum clearances between the va rious parts of the unit and the 
surrounding framework. 
– Instructions necessary for the co rrect operation of the unit and any 
special precautions to be observed to ensure its safe use and maintenance. 
– Instruction for packing and unpacking the unit. – Weight of the unit. – Any other additional information. 
                       –        Annual energy consumption for calcu lating the expected rated power  
                                 within 2700 working hour with full load annually. 
 QATAR STANDARD QS  2663/2019  
 
6 
  
7. ENERGY RATING CLASSIFICATION 
7.1 The energy efficiency class rating is used  for the comparative label used with 
window type and split type air-cooled air-conditioner with cooling capacity 
less than and including 70000 Btu/h (20000 W).  
7.2 The energy efficiency class is then  determined in accordance with the 
following table, where the EER (energy efficiency ratio) is determined in accordance with the test procedures of the harmonized standards referred to in 
Article 2 at condition 
T1 & T 3. 
 7.3           Stars No. on Label For 1st & 2ed Stages: 
  a) 1st Stage: 
EER limits 
(Btu/h)/w at T 1 EER limits 
(Btu/h)/w at T 3 Star Rating Status 
EER   ≥  12.5 EER   ≥   9.00 8 Applied 
12.5    >  EER   ≥  11.5 9.00   >  EER   ≥   8.28 7 Applied 
11.5    >  EER   ≥  10.0 8.28   >  EER   ≥   7.20 6 Applied 
10.0    >  EER   ≥   9.5 7.20   >  EER   ≥   6.84 5 Applied 
9.5      >  EER   ≥   9.0 6.84   >  EER   ≥   6.48 4 Applied 
9.0      >  EER   ≥   8.5 6.48   >  EER   ≥   6.12 3 Applied for 
 Window Type only 
 
EER   ˂  8.5  
EER  ˂  6.12  
Not Applicable 
 
  
           QATAR STANDARD QS  2663/2019  
 
7 
 b) 2ed Stage for split type: 
EER limits 
(Btu/h)/w at T 1 EER limits 
(Btu/h)/w at T 3 Star 
Rating Status 
EER   ≥  14.5 EER   ≥   10.44 9  
   
Applied for 
split Type only 14.5    >  EER   ≥  
13.5 10.44   >  EER   ≥  
9.72 8 
13.5    >  EER   ≥  
12.5 9.72   >  EER   ≥   
9.00 7 
12.5    >  EER   ≥   
11.5 9.   >  EER       ≥   
8.28 6 
EER ˂  11.5 EER ˂  8.28  Not Applicable 
 
C) 2ed Stage for window type:  
EER limits 
(Btu/h)/w at T1 EER limits 
(Btu/h)/w at T3 Star Rating 
Status 
11    >  EER   ≥   10 7.92   >  EER   ≥   7.20 5 
Applied for 
Window Type only 10      >  EER   ≥   9.0 7.20  >  EER   ≥   6.48 4 
9.0      >  EER   ≥   8.5 6.48  >  EER   ≥   6.12 3 
 
EER   ˂  8.5  
EER  ˂  6.12   
Not Applicable 
8.  ENERGY LABELLING REQUIREMENTS 
8.1 Information and Values Contained in the Energy Labels   
The font should be written “AXt ALMANAL  Bold” for Arabic and “Arial”  for 
English as well as the Sticker Color Palle te are as illustrated in the Figure7&8  
entitled (Colors , Fonts & Dimensions of the Stickers) Figure 7&8 .  
 Note :  The cooling capacity and power input values shown on the energy label are based on the 
tested  cooling capacity and the tested power, as decl ared by the manufacturer as well as shown 
in the nameplate for condition T1 for cooli ng capacity in accordance with the standard 
mentioned in clause 2.1 and 2.2. 
8.2 Sample Labels 
 Example of printed energy label for air-conditioning appliances are shown in 
Figures 2, 3, 4, & 5. 
                  Qatar General Organizati on for Standardization has right  to modify the form of 
the label.  QATAR STANDARD QS  2663/2019  
 
8 
 8.3 Dimensions of Labels 
 Figure 8&9 shows the dimensions of labelFor the split & window type. 
8.4 Placement of Energy Labels 
 The label shall be adhered, or attached as a swing tag, on the front of the unit.  
Additional label may be attached to the exterior of the packaging.  The label 
shall be existed on the unit when the un it is removed from its packaging for 
display purposes. 
8.5 Material and Shape of Energy Labels 
 The label shall be of durable cardboard, if it is to be attached as a swing tag, or 
be self-adhesive, and shall be cut to th e outline shown in Figure 8&9. A trim or 
die cut margin of up to 5 mm around the label is acceptable.  
 
 
   QATAR STANDARD QS  2663/2019  
 
9 
  
FIGURE1: Example of Label For Wi ndow type& Cooling Unit – 3 stars 
    
QATAR STANDARD QS  2663/2019  
 
10 
  
FIGURE 2: Example of Label For Wi ndow type & Cooling Unit – 4 stars 
  
QATAR STANDARD QS  2663/2019  
 
11 
  
FIGURE 3: Example of Label For Wi ndow type & Cooling Unit – 5 stars 
 
QATAR STANDARD QS  2663/2019  
 
12 
  
FIGURE 4: Example of Label for sp lit type& Cooling Unit – 6 stars 
 
QATAR STANDARD QS  2663/2019  
 
13 
  
FIGURE 5: Example of Label for sp lit type & Coolin g Unit – 7stars 
 
QATAR STANDARD QS  2663/2019  
 
14 
  
FIGURE 6: Example of Label for sp lit type & Cooling Unit – 8 stars 
    
QATAR STANDARD QS  2663/2019  
 
15 
  
FIGURE 7: Example of Label for sp lit type & Cooling Unit – 9 stars 
      
 
QATAR STANDARD QS  2663/2019  
 
16 
  
 
FIGURE 8:Colors, Fonts & Dimensio ns of Sticker for split type 
 
 
QATAR STANDARD QS  2663/2019  
 
17 
  
FIGURE 9:Colors, Fonts & Dimensio ns of Sticker for window type 
 
QATAR STANDARD QS  2663/2019  
 
18 
  
 
                      
QATAR STANDARD QS  2663/2019  
 
19 
 APPENDIX A 
APPLICATION FOR REGISTRATION OF  
AIR-CONDITIONERS FOR ENER GY LABELLING AND MEPS 
(please type or print) 
  
This Appendix sets out the required format for submitting an application for registration. 
Application for registration of an air-conditioner for energy efficiency.  
 
I hereby apply for registration of  an electrical appliance/s for the purpose of energy labelling. 
 
In the Country of ............................................................................................................. ............................  
(specify the country in whic h this application is made ) 
 
 
  
   PART 1   APPLICANT INFORMATION 
 
   Applicant Name : ………………………………........................................................................... 
   Company Name : ………………………...........................................................................………    Company Address : …………...........................................................................………………....    P.O.Box                : …………………………....   Post Code: .......................................................    Contact Person : (Name and Adrees  and workplace in each sales country) 
   Jop Title : ……………………………………    Phone : ……………………       Fax : ………………….       Electronic Mail  : .......................... 
 
     Supplier or Vendor in Qatar : 
               No.    Supplier or 
Vendor Name Contact Address 
(Mail Address, Phone, Fax, Electronic Mail) License Number or 
Commercial Licenses (related to import and sale of goods in Qatar.  
    
    QATAR STANDARD QS  2663/2019  
 
20 
 Part 2  DESCRIPTION OF THE APPLIANCE 
Model Name (if available)   
Model Number or Family Number:  
Model Number: 
(on indoor unit for split systems)  
Model Number on Outdoor Unit:  (split systems only)  
Other Model Numbers to be included under this 
registration:  
Country of Manufacture:  
Year in which model first available in Qatar :  
Model Number(s) to appear on the Energy Label: 
  
Date of manufacture traceability (of package unit or indoor 
unit if split system): Is the date of manufacture permanently marked on the 
rating plate in a non-encrypted format? 
If yes, provide an example of the date format. 
If no, provide details on how to determine (from the 
serial number or other permanent markings for this model)  
 Yes 
Date format: No Provide details: 
'Date of manufacture traceability  (of outdoor unit if split 
system): 
Is the date of manufacture permanently marked on the 
rating plate in a non-encrypted format? 
If yes, provide an example of the date format. 
If no, provide details on how to be determined (from the 
serial number or other permanent markings for this model)  Yes 
Date format: No                 Provide details: 
Does this model or family replace or supplement another 
model or family with identical energy consumption and 
energy efficiency rating? 
(indicate correct answer)  Yes No 
If yes, indicate relevant details: 
 
  Model 
name 
 Model 
number Registration number 
Informtion about the components used in the 
manfucturing: 
There must be complemantry documents for the 
materials used in the Manufacturing including 1- Compressor 
Country of origin:…………………………….. 
Name of Manufacturer or his trading mark: …… Compressor model number: …………………… Compressor type: …………………….…………. QATAR STANDARD QS  2663/2019  
 
21 
 drawings and figures and technical specifications 
and product model accreditation (if any) for each of the components mentioned here.
  
2- Fan 
Country of origin:……….. Name of Manufacturer or his trading mark: ……. Fan Model number: ……….. Fan type: …………………….  3- Heat Exchanger Volume and description of the heat exchanger:….
 
 
 
Part 3  TESTING AND TEST REPORT   
Test Laboratory Type: 
(put (√) inside the appropriate box) 
   Own 'in-house' laboratory: 
 Independent laboratory: 
Test Laboratory Name:  
Test Laboratory Address:  
Test Laboratory Location: 
 
  Qatar  
 Other— (please specify):  
Test Laboratory Accreditation: 
   Accredited from a body member in (ILAC)  
 
Test Standard Used: 
 
  QS ISO 5151 (the standard mentioned in 2.1) 
 QS ISO 13253 (the standard mentioned in 2.2) 
Other— (please specify) 
 
Does this airconditioner have separate indoor 
and outdoor units  Yes 
 No 
Serial number of test units/s and date tested: SERIAL NUMBER 
Unitary unit or 
indoor unit if split 
system SERIAL 
NUMBER 
Outdoor unit if 
split system Test date 
Rated voltage and frequency of tested unit Package unit Unitary unit or 
indoor unit if 
split system Outdoor unit if split 
system 
Rated voltage or  Rated voltage range 
(V)   
Rated frequency 
(Hz)   
Tested voltage and frequency of tested unit  Unitary unit or indoor unit if split system Outdoor unit if split 
system 
Tested voltage (V)   
Test frequency (Hz)   QATAR STANDARD QS  2663/2019  
 
22 
  
 
 
 
  Part 4  SPECIFIC APPLICANCE DETAILS
Air-conditioner dimensions (Advisory 
only): (for split systems note only dimensions of the 
internal unit)  Width (mm): 
 Height (mm): 
 Depth (mm): 
 
Air-conditioner type:   Cooling only  
 Reverse cycle  
 Heating only 
 Other (please specify) 
 
Power supply: 
  Single-phase 
 Three-phase 
Rated Voltage  (V):  
Rated Frequencu (Hz):  
Refrigerant Number : 
  R22,  
 Other (please specify)  
 
A/C Configuration 1—Air Distribution 
 
  Ducted 
 Non ducted 
A/C Configuration 2—Type  
   Window/Wall,  
 Spot cooler,  
 Portable cooler, 
 Single split system 
 Double/triple split system,  
 Multiple split system,  
 Packaged 
 
Does this air-conditioner use a variable speed drive (inverter) or a multi-speed compressor?   Yes 
 No 
 QATAR STANDARD QS  2663/2019  
 
23 
  
Part 5  TEST RESULTS  
 
TEST RESULTS—COOLING—CONDITION T1 
 
COOLING POWER 
 Rated Effective Power 
Input (kW)* 
  
Tested Cooling Power 
Input  (kW)** 
  
COOLING CAPACITY 
 Rated Total Cooling 
Capacity (Btu)* 
  
Tested Total Cooling 
Capacity   (Btu)** 
  
EER (Btu/h)/W 
 Rated EER **  
Tested EER **  
The class rating number  accord ing to  clause 7 of QS 
2663/201 5 (This standard) 
  Yes 
 No 
 
 
*     to 2 decimal places 
**   to 3 decimal places  QATAR STANDARD QS  2663/2019  
 
24 
  
TEST RESULTS—COOLING—CONDITION T3 
 
COOLING POWER 
 Rated Effective Power 
Input (kW)* 
  
Tested Cooling Power 
Input  (kW)** 
  
COOLING CAPACITY 
 Rated Total Cooling 
Capacity (kW)* 
  
Tested Total Cooling 
Capacity   (kW)** 
  
EER (Btu/h)/W 
 Rated EER **  
Tested EER **  
The class rating number according to clause 7 of of QS 
2663/2019 (This standard)  Yes 
 No 
 
*    to 2 decimal places 
**  to 3 decimal places 
 
 
  
 
  
 
 QATAR STANDARD QS  2663/2019  
 
25 
 TEST RESULTS—HEATING— 
Does this model incorporate el ectric resistance heating?   Yes 
 No 
HEATING POWER 
 Rated Effective Power 
Input (kW)*  
Tested Heating Power 
Input  (kW)**   
HEATING CAPACITY 
 Rated Total Heating 
Capacity  (kW)*  
Tested Heating Capacity   
(kW)**   
COP (w/w) 
 Rated COP **    
Tested COP ** 
* to 2 decimal places 
** to 3 decimal places 
 
 
DECLARATION 
 
I declare that the details st ated above are correct.  
Signature of Applicant: .............................................       Date: ................................... 
Office use only 
 Date received: .............................             Registration number: ..................................