# Firestop

A firestop or fire-stopping is a form of passive fire protection that is used to seal around openings and between joints in a fire-resistance-rated wall or floor assembly. Firestops are designed to maintain the fire-resistance rating of a wall or floor assembly intended to impede the spread of fire and smoke.

## Description

Firestops prevent unprotected horizontal and vertical penetrations in a fire-resistance-rated wall or floor assembly from creating a route by which fire and smoke can spread that would otherwise have been fire resisting construction, e.g. where a pipe passes through a firewall.
Fire stopping is also to seal around gaps between fire resisting constructions, e.g. the linear gap between a wall and the floor above, in order for construction to form a complete barrier to fire and smoke spread.

### Opening types

Firestops are used in:
* Electrical, mechanical, and structural penetrations
* Unpenetrated openings (such as openings for future use)
* Re-entries of existing firestops
* Control or sway joints in fire-resistance-rated wall or floor assemblies
* Junctions between fire-resistance-rated wall or floor assemblies
* Head-of-wall (HOW) joints, where non-load-bearing wall assemblies meet floor assemblies
Numeric characters are used to identify what penetrant, if any, can be found within the present system and help identify what UL-tested system was used.
Classification for penetrations and the barriers they penetrate, are categorized by a standardized letter-number system that has been adopted by all firestop products manufacturers. A typical system would consist of several letters, followed by a series of numbers indicating the type of penetrant that is passing through the particular barrier ex: (FB-5533.)

### Materials

Components include intumescents, cementitious mortars, silicone, firestop pillows, mineral fibers, and rubber compounds.
* Fire test of mortar-based firestop
* Pipe with metallic piping penetrations in a 2-hour fire-resistance rated concrete floor slab
* Inadequate firestop with rockwool
* Construction drawing of a firestop
* Firestop mortar seal of a cable tray

## Maintenance

Firestops should be maintained in accordance with the certification listing. Construction documentation sometimes includes an inventory of all firestops in a building, with drawings indicating their location and certification listings. Using this, a building owner can meet the fire code relating to fire barriers. Improper repairs may otherwise result, which would violate the fire code and could allow a fire to travel between areas intended by code to be separated during a fire.

## Ratings

Firestop materials are not rated per se. They receive a fire rating by combining materials in an arrangement specific to the item (a pipe or cable, for example) penetrating the fire-rated wall or floor and the construction arrangement of the fire-rated wall or floor. A two-hour-rated pipe-penetration firestop may consist of a layer of caulking over packed mineral wool. The arrangement, not the caulking, provides the two-hour rating. The individual firestop materials and the overall firestop assembly are listed.

## Brattberg Multi-Cable Transit system

Brattberg Multi-Cable Transit is a firestop system invented by John A. Birmingham and Rogers A. Moore, the patent expired in 2011. It is used onboard of large steal vessels (Offshore Platforms, ships) when penetration bulkheads, high rise buildings, laboratories, explosions areas and EMI risk.
It uses fix sizes frames, fix sizes insert blocks (U, Spare, Standard insert, Add block), Stayplate, Endpacking and Presswedge. Insert blocks are made out of Lycron.
Frames Size:
* 120x100mm
* 120x160mm
* 120x220mm
* 120x280mm
Sleeves Sizes, round holds with approx inner diameter in milimeter:
* 50
* 70
* 100
* 125
* 150
* 200
* 300
Insert Blocks is designed to accommodate cables ranging from 4 to 100mm in diameter.
AddBlocks is a more flexible version for Insert Blocks, giving 5mm of adjustable diameters.
The U-Block is used to convert the external dimensions of Insert Blocks, AddBlocks and Spare Blocks to the next modular size.
Solid spare blocks are used to fill any vacant areas within the frame.

## Testing and certification

Certification listings include those available from:
* Underwriters Laboratories
* Underwriters Laboratories of Canada
* Deutsches Intitut für Bautechnik (Germany)
FIRAS scheme- Warrington Fire (UK)
* Efectis (Netherlands, France, and Norway)
* FM Global

## Regulations and compliance

When the installed configuration does not comply with the appropriate certification listing, the fire-resistance rating may be lower than expected. Each opening in a fire-resistance-rated wall or floor in a building must have a certification listing. There are thousands of listings from various certification and testing laboratories. The Canadian and United States Underwriters Laboratories publish books listing firestop manufacturers who have contracted with them for testing and certification.

## Inadequate firestopping
### No firestopping

Older buildings often lack firestops. A thorough inspection can identify all vertical and horizontal fire barriers and their fire ratings, and all breaches in these barriers (which can be sealed with approved methods).
* Unsealed pipe penetration in two-hour fire-resistance rated concrete block wall
* Improper breach of fire-resistance rated drywall assembly

### Non-listed attempts

Firestops created by contractors or building maintenance personnel which are not listed are not credited with an adequate fire resistance rating for building-code compliance purposes. They are usually short-term, cost-cutting measures at the expense of fire safety and code compliance. One common error is citing a listing for a product which may be for another use. An insulation with an active listing of a certain flame-spread rating is unacceptable for firestopping purposes.
* Common concrete, with no testing intended for certification listing
* Stuffed fiberglass insulation would rapidly melt and fall out in a fire.
* Spray fireproofing improperly used to cover penetrations
* Polyurethane foam used to fill a cable tray penetration; at Browns Ferry Nuclear Power Plant, this type of seal resulted in significant fire damage.