REPORT OF THE KING INSTITUTE, GUINDY
29
TABLE XV —cont.
M M u n i c i p a l i t i e s — c o n t .
No.
Source.
Dates of examination and results.
Remarks on suoply.
30 Salem
...
....
...
... 20 Apr. 1928 ...
8 Nov. 1928.
Infn. gallery ...
..
..
5 c.c.
...
5 c.c.
Panaimarattupatti tank
...
1 c.c.
1. c.c.
. . . Indifferent and variable. (See report.)
Dy. system
...
...
...
5 c.c.
...
20 c.c.
Arisipalaiyam tank (auxiliary).
0.1 c.c.
...
1 c.c.
Do
(chlorinated). >60 c.c.
>60 c.c.
..
31 Tanjore ...
...
...
... 25 Apr. 1928 ... 18 Sep. 1928.
River water
...
...
...
0.1 c.c.
...
0 . 1 c.c.
.. Gallery supply very bad at the first, but
passable at the second examination,
Tank water bad.
Infn. gallery ...
...
...
0.1 c . c.
..
10 c.c.
Dy. system
...
...
..
0.1 c.c.
...
10 c.c.
...
Sivaganga tank
...
0.1 c.c.
1 c.c.
32 Tirnpati
...
...
...
6 Sep. 1928
1 Mar 1929.
Infn. wells
...
...
...
10 c.c.
...
10 c.c.
... Passable.
Dy. system
...
...
...
5 c.c.
5 c.c.
33 Tiravannāmalai
...
...
9 May 1928
... 21 Nov. 1928.
Kalyani well ...
...
0.1 c.c.
...
60 c.c.
... Bad at the first, but good at the second
when the water was chlorinated.
Dy. system
...
...
. . .
...
60 c c.
34 Trichinopoly
...
...
... 5 Oct. 1928
...
14 Mar. 1929.
Cauvery River ...
...
...
1 c.c.
...
1 c.c.
... Systematic chlorination continued.
Supply good. Slight deterioration in
distribution noticed in October.
Infn, wells and gallery
... >60 c.c.
... >60 c.c.
...
Dy. system
...
...
...
20 c.c.
... >60 c.c.
.35 Tuticorin
...
...
... 30 Jane 1928 ... 17 Dec. 1928.
Tank
...
...
...
...
0. 1 c.c.
...
0. 1 c.c.
... Very bad. The benefit of reported
chlorination in the service reservoir
did not reach the consumer. (See
report.)
Chlorinated water in
r e s e r -
voir.
>60 c.c.
... >60 c.c.
Distribution wells
...
...
0.1 c.c.
...
1 c.c.
36 Vellare ...
...
...
... 27 July 1928 ...
24 Jan. 1929.
Infn. gallery ...
...
...
10 c.c.
...
60 c.c,
... Gallery supply passable at the first and
good at the second examination. On
both occasions deteriorated in distri.
bution. Well supply fair.
Dy. system
..
...
...
5 c.c.
..,
20 c.c.
Well in the bed of the Palar ...
10 c.c.
... >60 c.c.
37 Vizagapatam
...
...
... 25 June 1928 ... 19 Dec. 1928.
Tank
...
...
...
...
0.1 c.c.
...
1 c.c,
. . . Fair.
Open trench
...
...
...
0.1 c.c.
.
1 c.c.
Filtered water ...
...
...
20 c.c.
...
20 c.c.
Dy. system
...
...
...
60 c.c.
...
20 c.c.
38 Vizianagram ...
...
...
3 May 1928 ... 29 Nov. 1928.
Infn, gallery
...
...
. . .
5 c.c.
. . .
10 c.c.
... Passable
Dy. system
...
...
...
5 c.c.
. . . 10 c.c.
Jails.
1 Alipuram ...
...
. . . 17 Apr. 1928
... 22 Oct. 1928.
Tank
...
...
...
...
0.01 c.c.
...
0.01. c.c.
... Results of filtration poor. Chlorinated
supply good .
Filtered water ...
...
...
1 c.c.
...
10 c.c.
Chlorinated water
...
... >60 c.c.
... >60 c.c.
2 Bellary ( Central) ...
... 17 Apr. 1928 ... 22 Oct. 1928.
Municipal supply
...
...
10 c.c.
...
20 c.c.
... .Jail supply drawn from municipal
water fair and chlorinated was good.
Chlorinated water
...
... >60 c.c.
... >60 c.c.
Deep well
...
...
0.1 c.c.
. . .
...
3 Calicut (Special sub-jail ) ... 25 Aug, 1928 ... 7 Feb. 1928.
Well inside the jail
0.1 c.c.
...
1 c.c.
... Wells highly polluted. The chlorinated
supply was good in February 1929.
Well chlorinated water
...
. . .
>60 c.c.
Well in Warders' lines
1 c . c .
. . .
...
4 Cannanore ( Central) ...
... 15 June 1928
. . . 3 Dec. 1928.
Tope Wells 1
...
. . .
5 c.c.
20 c.c.
... Untreated
well
waters
passable.
Chlorinated water supply good.
Do.
2
...
...
5 c.c.
...
5 c.c
Do.
3
...
...
5 c.c.
20 c.c.
Chlorinated water
...
... 60 c.c.
... >60 c.c.
5 Coimbatore ( Central) ...
... 3 Sep. 1928
... 14 Feb. 1929.
Aeromotar well
...
...
1 c.c.
...
1 c.c.
Do.
chlorinated ... >60 c c.
.., >60 c.c.
... Untreated well water poor. Chlori-
nated supply good.
Garden well
...
...
1 c.c.
...
1 c.c.
Do.
chlorinated
... >60 c.c.
... >60 c.c.
6 Cuddalore (District) ...
... 2 July 1928
..
7 Jan. 1929.
Lake well
...
...
. . . >60 c.c.
..
20 c.c.
... Good,
Chlorinated water
...
... >60 c.c.
... >60 c.c.
5-A