30
REPORT OF THE KING INSTITUTE, GUINDY
TABLE XIV—cont.
something greater than 60 c.c. Unless otherwise stated, filters refer to slow
sand filters. The expression “Distributary system” includes service reservoirs.
Municipalities.
No.
Source.
Dates of examination and results.
Remarks on supply.
1 Adōni
...
... ... "
10 July 1929 ...
8 Jan. 1930.
Raw water
...
...
...
1 c.c.
...
1 c.c.
... Unsatisfactory. (See report.)
Dy.
system
(Chlorinated
10 c.c.
...
10 c.c.
supply).
2 Anantapur ...
...
... 10 July 1929 ... 8 Jan. 1930.
Infn. gallery ...
...
...
10 c.c.
...
20 c.c
... Fair.
Dy. system
...
...
10 c.c.
...
10 c.c.
3 Bellary ...
...
...
...
9 Apr. 1929 ... 7 Nov. 1929.
Well in the bed of the Hagari.
10 c.c.
...
10 c.c.
... Good.
Dy. system
...
...
...
20 c.c.
...
60 c.c.
4 Berhampur...
... 15 May 1929 ... 14 Nov. 1929.
Tank water
...
...
...
10 c.c.
...
10 c.c.
... Filters efficient. Deterioration observed
Filtered water
...
...
60 c.c.
...
60 c.c.
in transit in November.
Dy. system...
...
60 c.c.
...
10 c.c.
5 Bezwada ...
...
... 20 Sep. 1929 ... 24 Mar. 1930.
Wells
...
...
...
...
20 c.c.
...
60 c.c.
... Good. Free ammonia still persists in
Dy. system
...
...
...
20 c.c.
...
60 c.c.
the well sample. (See report.)
6 Cannanore ...
...
... 31 May 1929 ... 4 Dec. 1929.
Well
...
...
...
0.1 c.c.
...
5 c.c.
... Bad in May but passable in December.
7 Cauvery-Mettur Project
... 1 June 1929 ... 28 Feb. 1930.
Cauvery ri ver . . .
0.1 c.c.
... 0.1 c.c.
... Excellent.
Filtered water (Mechl.)
...
...
10 c.c.
Dy. system
...
...
... >120 c.c.
... >60 c.c.
8 Chidambaram ...
...
..
6 June 1929 ... 21 Nov. 1929.
Tank
...
...
...
...
1 c.c.
...
1 c.c.
F.W. (Mechl.) ... . . .
. . .
60 c.c.
...
60 c.c.
... Excellent
Dy. system
...
...
... >60 c c.
... >60 c.c.
9 Chingleput
... ...
8 May 1929 ...
8 Nov. 1929.
Infn. gallery ...
...
... >60 c.c.
...
20 c.c.
... Good.
Dy. system
...
... >60 c.c.
...
20 c.c.
10 Cocanada ...
5 June 1929 ... 28 Jan. 1930.
Tank
...
...
...
. . .
1 c.c.
...
5 c.c.
F.W.
...
...
...
...
20 c.c.
...
10 c.c.
... Variable. (See report.)
Dy. system
...
...
...
20 c.c.
...
10 c.c.
11 Conjeeveram ...
...
...
8 May 1929 ...
8 Nov. 1929.
Infn. gallery
..
...
...
60 c.c.
...
60 c.c.
... Good.
Dy. system
...
...
... >60 c.c.
...
60 c.c.
12 Coonoor ...
...
... 24 Aug. 1929 ...
7 Mar. 1930.
Upland surface water
. . .
5 c.c.
...
20 c.c.
... Passable.
Below standard in August.
Dy. system
...
...
...
5 c.c.
...
20 c.c.
(See report.)
13 Coimbatore (Temporary 28 Apr. 1929 ... 25 Oct. 1929.
supply.)
River water
...
...
...
0.1 c.c.
...
0.1 c.c.
... Chlorination at head works inefficient.
Dy. system
...
...
...
0.1 c.c.
...
1 c.c.
Treatment at the Service Reservoir
recommended. (See report.)
14 Cuddapah
...
...
... 7 May 1929
... 30 Oct. 1929.
Experimental wells ...
. . .
5 c . c .
...
...
Passable.
Deterioration in transit
Infn. gallery ...
...
. . .
5 c.c.
...
5 c.c.
...
in October.
Dy. system
. . .
5 c.c.
...
1 c.c.
15 Dindigul
...
... 17 Apr. 1929 ... 21 Oct. 1929.
Infn. gallery ...
...
. . .
5 c.c.
...
. . .
Fair in April.
Poor in October owing
Wells
... . . .
. , .
. . .
5 c.c.
to unsatisfactory chlorination. (See
Dy. system
...
... ...
60 c.c.
...
5 c.c.
report.)
16 Ellore ...
...
...
... 15 July 1929 ... 14 Feb. 1930.
Tank
...
...
...
.01 c.c.
. . .
1 c.c.
... Slow sand filters still not functioning
F.W.
...
...
...
...
5 c.c.
..
5 c.c.
efficiently. (See report.)
Dy. system
...
...
...
5 c.c.
...
10 c.c.
17 Erode
...
...
...
. . 2 Aug. 1929 ... 28 Feb. 1930.
River water
...
...
...
.01 c.c.
. . .
0.1 c.c.
... Good in August but unsatisfactory in
Filtered water (Mechl.)
...
20 c.c.
. . .
1 c.c.
February. (See report.)
Dy. system
...
...
...
60 c.c.
...
5 c.c.