27
REPORT OF THE KING INSTITUTE, GUINDY
TABLE XIV—cont.
Municipalities—cont.
No.
Source.
Dates of examination and results.
Remarks on supply.
29
Rameswaram
. . . 28 June 1927 . . . 23 Dec. 1927.
Excellent.
Infn. wells . . . >60 c.c. . . .
60 c.c. . . .
Dy. system . . . >60 c.c. . . . >60 c.c.
30
Salem
. . .
28 July 1927 . . . 19 Nov. 1927.
Systematic chlorination reported
throughout the year; yet bad on the
first and good on the second occasion.
Infn. gallery . . .
5 c.c. . . .
5 c.c. . . .
Panaimarattupatti tank . . .
1 c.c. . . .
1 c.c.
Dy. system . . .
1 c.c. . . . >60 c.c.
Arisipalaiyam tank (auxiliary).
1 c.c. . . .
1 c.c.
Do (chlorinated).
. . .
60 c.c.
31
Tanjore
. . .
17 May 1927 . . . 17 Nov. 1927.
Gallery supply indifferent and variable.
Tank water bad.
River water . . .
0.01 c.c. . . .
0.1 c.c. . . .
Infn. gallery . . .
1 c.c. . . .
5 c.c. . . .
Dy. system . . .
1 c.c. . . .
1 c.c.
Sivaganga tank . . .
0 . 1 c . c . . . .
0.1 c.c.
32
Tirupati
. . .
8 Oct. 1927 . . . 21 Feb. 1928.
As supplied after chlorination passable.
Infn. wells . . .
1 0 c . c . . . .
5 c.c. . . .
Dy. system . . .
20 c.c. . . . >60 c.c.
33
Tiruvannāmalai
. . .
9 May 1927 . . .
2 Dec. 1927.
Bad.
Kalyani well . . .
1 c.c. . . .
0.1 c.c. . . .
Dy. system . . .
. . .
0.1 c c. . . .
(See report.)
34
Trichinopoly. . .
21 Oct. 1927 . . .
14 Mar. 1928.
Systematic chlorination continued. In
October the treatment was unsatis
-
factory. Good at the second examina
-
tion. Deterioration in distribution.
Cauvery River . . .
0.1 c.c. . . .
0.1 c.c. . . .
Infn. wells and gallery . . .
20 c.c. . . . >60 c.c.
35
Dy. system . . .
10 c.c. . . .
10 c.c.
Tuticorin
. . .
8 Sep. 1927 . . .
9 Feb. 1928.
Very, bad. No filtration. Chlorination
practised but can never be successful
(for reasons, see report).
Tank . . .
1 c.c. . . .
5 c.c. . . .
Chlorinated water in reser-
voir.
>60 c.c. . . .
60 c.c.
Distribution wells . . .
0.1 c.c. . . .
1 c . c .
36
Vellore
. . .
27 July 1927 . . .
23 Jan. 1928.
Infn. gallery . . .
. . .
10 c.c. . . .
Good.
Dy. system . . .
20 c.c. . . .
20 c.c. . . .
(See report for details about Palar well.)
Well in the bed of the Palar . . .
20 c.c. . . .
. . .
37
Vizagapatam
. . .
25 July 1927 . . .
9 Jan. 1928.
Good.
Tank . . .
1 c.c. . . .
0.1 c.c. . . .
Open trench . . .
1 c . c . . . .
1 c . c .
Filtered water . . .
60 c.c. . . .
60 c.c.
38
Dy. system . . .
20 c.c. . . .
6 0 c . c .
Vizianagram
. . . 24 June 1927 . . .
8 Dec. 1927.
Passable.
Nellimerla River . . .
0.1 c.c. . . .
0.1 c.c. . . .
Infn. gallery . . .
5 c.c. . . .
10 c.c.
Dy. system . . .
1 c.c.
60 c c.
J a i l s .
1
Alipuram . . .
26 May 1927 . . .
25 Nov. 1927.
Bad.
Municipal supply. (Hagari
water).
0 . 1 c . c . . . .
. . .
2
Chlorinated water . . .
10 c.c. . . .
. . .
Fort Ditch water . . .
. . .
0 . 1 c . c .
Mechanical filtered water . . .
. . .
0.1 c.c.
Chlorinated water . . .
. . .
5 c.c.
Bellary Central . . .
26 May 1927 . . .
5 Nov. 1927.
Municipal water chlorinated and used
in this jail is good. Deep well, old
source now unused, bad.
Municipal supply (Hagari
water).
1 c.c. . . .
20 c.c. . . .
Chlorinated water . . .
>60 c.c. . . .
60 c.c.
Deep well . . .
0.1 c.c. . . .
0.1 c.c.
3
Calicut (Special sub-jail) . . .
30 May 1927 . . . 20 Feb. 1928.
Bad. Chlorination recommended.
Well inside the jail . . .
0.1 c.c. . . .
0.1 c.c. . . .
4
Well in Warders' lines
0.1 c.c.
1 c.c.
New sources used in May were bad.
Old sources reverted to in December
good.
Cannanore Central . . .
30 May 1927 . . . 13 Dec. 1927.
Wells in blocks 2, 4 and 9 . . .
1 c.c. . . .
. . .
Tope wells 1, 2 and 3 . . .
. . .
20 c.c.
Chlorinated water . . .
. . .
>60 c.c.