ARMED SERVICES BOARD OF CONTRACT APPEALS 
Appeals of -- ) 
) 
ECC International Constructors, LLC ) 
) 
) 
Under Contract No. W912ER-10-C-0054 ) 
APPEARANCES FOR THE APPELLANT: 
APPEARANCES FOR THE GOVERNMENT: 
ASBCA Nos. 59138, 59586 
59643,60284 
R. Dale Holmes, Esq. 
Amy M. Kirby, Esq. 
Cohen Seglias Pallas Greenhall 
& Furman PC 
Philadelphia, PA 
Michael P. Goodman, Esq. 
Engineer Chief Trial Attorney 
Sarah L. Hinkle, Esq. 
Matthew Tilghman, Esq. 
Engineer Trial Attorneys 
U.S. Army Engineer District, Middle East 
Winchester, VA 
OPINION BY ADMINISTRATIVE JUDGE MCILMAIL ON THE 
PARTIES' MOTIONS FOR SUMMARY JUDGMENT 
The parties move for summary judgment on issues related to a contract to build a 
compound outside a military base in Afghanistan. The parties have filed voluminous briefs 
with numerous proposed statements of undisputed facts. In an effort to streamline the 
issues and ready the appeals for hearing, this decision will only address select issues that 
pertain to contract interpretation. Matters of contract interpretation are questions of law 
and are amenable for resolution through summary judgment. Vari/ease Technology Group, 
Inc. v. United States, 289 F.3d 795 (Fed. Cir. 2002). Contract interpretation begins with 
examination of the plain language of the written agreement. LAI Services, Inc. v. Gates, 
573 F.3d 1306, 1314 (Fed. Cir. 2009). The terms are given their plain and ordinary 
meaning; if the contract language is clear and unambiguous, the plain language controls, 
and extrinsic evidence is not allowed to contradict the plain language. Coast Federal 
Bank, FSB v. United States, 323 F.3d 1035, 1040 (Fed. Cir. 2003). The contract terms are 
interpreted and read as a whole, giving reasonable meaning to all of its parts, and without 
leaving a "portion of the contract useless, inexplicable, void, or superfluous.'' NVT 
Technologies, Inc. v. United States, 3 70 F .3d 1153, 1159 (Fed. Cir. 2004 ). 

Summary judgment shall be granted if the movant shows that there is no genuine 
dispute as to any material fact and the movant is entitled to judgment as a matter of law. 
Avant Assessment, LLC. ASBCA No. 58867, 15-1 BCA i/ 36,067 at 176.127 (citing FED. R. 
CIV. P. 56(a)). The Board has previously issued a decision in the above-referenced appeals. 
See ECC International Constructors, LLC, ASBCA No. 59138 et al., slip op. (Jan. 24, 2019). 
Familiarity with the facts is presumed. 
"Additional" Voice and Data Outlets 
The following is not in dispute. In 2010, the parties contracted for appellant to 
construct a compound outside the International Security Assistance Force (ISAF) 
military base in Afghanistan (gov't mot. at 2, ,i,i 1-2; app. resp. at 1-2, 11 1-2). The 
contract provides that, with respect to a "Joint Operations Center": 
One secure network outlet, one above secret network outlet 
and one NIPR net outlet per every 4.5 square meters of 
office space. One coax outlet per office. 
(Gov't mot. at 11, ,i 45 (§ 018000.12 10, ,i 10.16); app. resp. at 5, ,i 45) The parties 
disagree on the interpretation of that provision. The government argues that the plain 
language is unambiguous. Appellant contends that adherence to the contract terms 
would require more outlets than necessary for the compound. (Gov't mot. at 40-43;. 
app. resp. at 40-44). We apply the principle of noscitur a sociis, which teaches that "a 
word is known by the company it keeps,'' so as to avoid ascribing to one word a 
meaning so broad that it is inconsistent with its accompanying words. Schlumberger 
Technology Corp. v. United States, 845 F.3d 1158, 1165 (Fed. Cir. 2017). Because the 
provision uses the term "office space'' in one sentence and the term "office" in the 
next, we interpret the term "office space" to mean "the space within an office," within 
the meaning of the provision. Accordingly, the provision requires one secure network 
outlet, one above secret network, and one NIPR net outlet for every 4.5 square meter 
increment of space within an "office" ( defined as any space requiring a coax outlet 
under the provision). To illustrate, if an office measures 4.5 square meters, the office 
shall have one secure network outlet, one above secret network, and one NIPR net 
outlet; if an office measures more than 4.5 square meters but fewer than 9 square 
meters, one of each; if 9 square meters, two of each; and so on. Thus, we find the 
government's argument persuasive and grant summary judgment on this issue. 
Cable Ladder Rack 
The following is not in dispute. The contract provides that: 
UL listed, black painted, cable ladder rack. .. shall be 
installed around the perimeter of the communication 
2 

and server rooms .... The cable ladder shall be the Telco 
type as described in the I3A specifications. 
(App. resp. at 63, ,i 287 (§ 018000.12 10, ,110.11.5); gov't resp. at 45, ~ 287) 
The parties disagree on the interpretation of the term "perimeter'· within the 
meaning of that provision, with the government contending that the language is 
unambiguous, and appellant arguing that the term does not mean "entire perimeter 
(app. resp. at 65-68; gov't mot. at 50-52). Among the definitions of the term 
"perimeter" are "the continuous line forming the boundary of a closed geometric 
figure'· and ·'the outermost parts of a boundary of an area or object.'" NEW OXFORD 
AMERICAN DICTIONARY 1303 (3d ed. 2010). Applying those definitions, the perimeter 
of a communications or server room is its boundary; that is, its walls.* Consequently, 
the provision requires the installation of a cable ladder rack around the walls of such a 
room. We see no meaningful distinction between the term "perimeter" and appellant's 
use of the characterization "entire perimeter" (app. resp. at 66); the latter smacks of 
tautology in that it says the same thing twice. See NEW OXFORD AMERICAN 
DICTIONARY 1779. Appellant relies upon the I3A specifications referenced in the 
provision above that depicts a Cable Rack Detail (Typical) that appellant says shows a 
cable ladder installed around only part of the perimeter of the depicted room (app. 
resp. at 63-64, ,r 288; gov't resp. at 45, ,r 288). However, that reference refers to the 
type of cable ladder to be used, not where to install the cable ladder, despite what the 
typical detail may depict. Accordingly, appellant's arguments must fail. 
Fiber Optic Combination Units (FOCU) Size 
The following is not in dispute. The contract provides that: 
The fiber optic cables shall be terminated in floor 
mounted, four post relay rack combination units that 
will allow splicing and patching within the same enclosure. 
The enclosures shall be sized to contain a minimum of 
48 fibers and a maximum of 144 fibers. 
(Gov't mot. at 16, ,r 71 (§ 018000.12 10, ,r 10.4.1); app. resp. at 7, ,r 71). The parties 
disagree on whether the provision requires each "enclosure" to be able to contain 144 
fibers (gov't mot. at 52; app. resp. at 76). The plain unambiguous language of the 
* We exclude from the "perimeter" of the room the door when closed; we presume 
that it would be absurd to interpret the provision to require that a cable ladder 
rack be installed on the inside of the door, and we should avoid such an 
interpretation. Haggar Co. v. Helvering, 308 U.S. 389, 394 (1940). 
3 

provision requires that "enclosures," in general, be sized to contain at least 48 fibers but no 
more than 144 fibers; it does not require that each enclosure be sized to contain 144 fibers. 
Relocation and Disposal of "Spoils" 
Appellant moves for summary judgment that the government constructively 
changed the contract by directing appellant to ·'change the location and relocate all spoils 
disposed at the approved site'' ( app. resp. at 106-07). The government concedes "liability 
for entitlement" on this issue (gov't resp. at 70). We grant summary judgment to 
appellant that the government constructively changed the contract by directing appellant 
(1) to change the location of the spoils disposal site, and (2) to relocate to the changed 
location all spoils already disposed at the previously-approved disposal site. 
CONCLUSION 
The parties' motions are granted and denied to the extent reflected by the 
foregoing opinion; otherwise, the motions are deferred. 
Dated: March 4, 2019 
I concur 
M--
RICHARD SHACKLEFORD 
Administrative Judge 
Acting Chairman 
Armed Services Board 
of Contract Appeals 
4 
TIMOTH P. LMAIL 
Administrative Judge 
Armed Services Board 
of Contract Appeals 
I concur 
OWEN C. WILSON 
Administrative Judge 
Vice Chairman 
Armed Services Board 
of Contract Appeals 

I certify that the foregoing is a true copy of the Opinion and Decision of the 
Armed Services Board of Contract Appeals in ASBCA Nos. 59138, 59586, 59643, 
60284, Appeals of ECC International Constructors, LLC, rendered in conformance 
with the Board's Charter. 
Dated: 
5 
JEFFREY D. GARDIN 
Recorder, Armed Services 
Board of Contract Appeals