STC-3000 AC 110-220V Digital LCD Display Temperature Controller Thermostat Regulator Cooler Heater Temperature Sensor (AC 110-220V)
Brand: diymore
Color: Multicoloured

Technical Parameter: Resolution: 0.1°C Power consumption: <3w Sensor: NTC sensor(1pc) Accuracy: +1°C(-50°C~70°C ) Sensor error delay: 1 minute Ambient temperature: 0°C -60°C Storage temperature: -30°C -75°C Relative humidity: 20-85%(No condensate) Temperature measuring range: 50°C -99°C Power supply:110V/220VAC+10%, 50/60Hz Relay contact capacity: Cool(10A/250VAC); Heat(10A/250VAC) Specification: Mounting size: 71(L)*29(W)(mm) Front panel size: 75(L)x34.5(w)(mm) Sensor length: Im (include the probe) Product size: 75(L)x34.5(W)x85(D)(mm) Operation Instruction: 1.Under controller normal working status, press and hold “ ” key for 3s can turn off the controller; Under controller “off” status, press and hold “ ” key for 3s can turn on the controller. 2.Under the controller normal working status, screen displays the current temperature value; the controller can also switch the working mode between heating and cooling. (1)Controller starts refrigerating with cool indicator light on when the measuring temperature ≥ temperature set value + difference value, and the refrigerating relay is connected. The “Cool” indicator light flashes, it indicates the refrigerating equipment is under compressor delay protect status. (2)When the measuring temperature ≤ temperature set value, the cool indicator light on, and refrigerating relay disconnects. System starts heating when the measuring temperature value ≤ the temperature set value-difference value, and the “Heat” indicator light on, and the heat relay connects. When the measuring temperature ≥ temperature set value, the “Heat” indicatorlight is off, and the heat relay disconnects. Package Included: 1X STC-3000 LCD Digital Temperature Controller Thermostat Regulator Cooler Heater Temperature Sensor

★Two Modes: ★Switch the modes between cool and heat. Control temperature by setting the temperature setting value and the difference value.
★Different Functions:★ Temperature calibration; efrigerating control output delay protection.The device has alarm function when temperature exceeds temperature limit or when sensor error.
★Warning: ★Prohibit using the machine under the environment of over damp, high temp., strong electromagnetism interference or strong corrosion.
★Notice: ★The power supply should conform to the voltage value indicated in the instruction.To avoid the interference, the sensor down-lead and power wire should be kept a distance.
★Danger: ★Strictly distinguish the sensor down-lead, power wire and output relay interface from one another, and prohibit wrong connections or overloading the relay. Prohibit connecting the wire terminals without electricity cut-off.