Can we provide a self-assembled or vertical server for placement?
Colobridge technology platform is deployed in data centers in Germany, where a system of cold and hot aisles is used for cooling. The air in the racks moves according to the classic Front-to-Back scheme: cold streams are directed to the space in front of the equipment, and hot streams are taken behind it and directed to heat exchangers. From the heat exchanger, cooled air comes out, ready to be reused. This is an efficient cooling scheme that is technically challenging to implement when placing a vertical or self-assembled server. We only practice rackmount server placement. The equipment must meet the specified electrical and fire safety specifications; it must also have the necessary accessories for installation. Power is connected in accordance with IEC-320-C13 or other standard as approved by Colobridge experts. Physical size requirements for equipment: Maximum width with mounting brackets is 482.6 mm (19 in.); height to accommodate mounting equipment – 44.45 mm (1 unit); distance between 19 profiles – 450 mm; distance between mounting holes – 465 mm.