How is the system connected to the heating system?
The SpeeTube heating hoses Ø10 and Ø12 mm are connected to the distributor using PushFit couplings.
There are three types of PushFit couplings: single, double (splitter) and repair couplings. The couplings are 3/4” euroconus fittings.
The PushFit splitter allows for two heating hose groups to be connected to a single distributor group. Two groups connected to a single splitter must be of equal length.
The diameter of the supply and return lines to the central heating boiler or district heating:
distributors for up to 7 groups: minimum Ø 15 mm, connection ½".
distributors for 8 or more groups: minimum Ø 20 mm, connection¾".
The diameter of the supply and return lines to the heat pump or LTHW: ask the supplier for the specific system specifications.
Please note: WARP Systems cannot connect the system to the primary heating source. This must always be done by a certified plumber.