Cooper Lighting Recalls Metalux Optimized High Bay LED Light Fixtures Due to Fire Hazard
Agency: CPSC
Recall date: 2026-07-02
Recalling firm: Cooper Lighting, LLC, of Peachtree City, Georgia

This recall involves Metalux Optimized High Bay (OHB) LED light fixtures used indoors in commercial structures with high ceilings such as warehouses and commercial bays. The fixtures are painted white metal and measure between 2 feet and 4 feet in length and between 1 foot and 1.5 feet in width, with a plastic diffuser lens cover. The catalog number and date code are printed on the product label inside of the fixture channel cover, behind the tray and can be accessed by removing two screws. The date code is in a two-digit mm/dd/yy format representing the month, day and year. Catalog Number Date Code OHB-60SE April 2020 through December 2022 OHBL-60SE October 2022 through May 15, 2025 OHBL-100SE October 2022 through May 15, 2025

Hazard: The LED's board can overheat or come into contact with the lens or nearby combustible materials, posing a fire hazard.
Remedy: Consumers should stop using the recalled light fixtures immediately and contact Cooper Lighting to schedule a free repair or replacement. Consumers will be asked to complete a form at www.content.cooperlighting.com/ohb-recall to register the light fixtures and schedule a repair or replacement.; Repair; Replace
Units affected: 42000