We assume; P1: Boiler Pressure 12 Kg/cm2 P2: Pressure inside the accumulator 4 - 12 Kg/cm2 P3: Pressure of the process main 4 Kg/cm2 Now, we look into the table below to see how many Kg of steam can be discharged from M3 of water inside the accumulator under certain condition of pressure drop P1 - P3. For the case of EXAMPLE-II, we are given a figure of 69 Kg of steam to be discharged per M3 of water at P1=12 and P3=4. (2)WATER CONTENT OF ACCUMULATOR From the steam flow graph, let us see the shaded area of "CHARGE" and "DISCHARGE".
Ito ay naglalaman ng bumababang pwersa P1 – P3. Para sa kaso ng HALIMBAWA-II, tayo ay nabigyan ng markang 69 Kg ng singaw na ididiskarga sa bawat M3 ng tubig na may P1 = 12 at P3 = 4. (2) LAMAN NA TUBIG NG TAGA-KOLEKTA NG SINGAW Galing sa grap ng agos ng singaw, tunhayan natin ang initiman na bahagi ng “PAGKAKARGA” at “PAGDIDISKARGA.”