GreatNorthCollective/greatnorth-canada-federal-laws-text huggingface dataset:
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
walk-in cooler means an enclosed storage space that has an area of less than 278.71 m 2 (3,000 square feet) and is designed to be cooled to temperatures at or above 0°C and to allow a person to enter, but does not include a walk-in cooler that is designed and marketed exclusively for medical, scientific or research purposes. ( réfrigérateur-chambre )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
walk-in door assembly means an assembly that is installed, or is designed to be installed, in an opening of an interior or exterior wall of a walk-in cooler or walk-in freezer in order to allow access through the opening or to close it off and that consists of the framing material necessary for its attachment and a moveable door panel, including any glass, door plugs or mullions, but does not include a walk-in door assembly that is designed and marketed exclusively for medical, scientific or research purposes. ( assemblage de porte de chambre froide )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
walk-in freezer means an enclosed storage space that has an area of less than 278.71 m 2 (3000 square feet) and is designed to be cooled to temperatures below 0°C and to allow a person to enter, but does not include a walk-in freezer that is designed and marketed exclusively for medical, scientific or research purposes. ( congélateur-chambre )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
walk-in panel means a panel that is installed, or is designed to be installed, as part of the envelope of a walk-in cooler or walk-in freezer, but does not include a walk-in door assembly or a walk-in panel that is designed and marketed exclusively for medical, scientific or research purposes. ( panneau de chambre froide )
Energy Efficiency Regulations, 2016 — (a)
walk-in process cooling refrigeration system means a refrigeration system that (a) is sold as a set with an insulated enclosure and, when assembled with the enclosure, has a cooling capacity of at least 1.035 kW/m 3 (100 Btu/h/ft 3 ) of enclosed internal volume; (b) is a unit cooler — or a dedicated condensing unit exclusively sold as a set that has a dedicated condensing unit and a unit cooler — that has an evaporator coil with a means of forced air circulation and a height that is (i) at least 1.37 metres (4.5 feet), as measured perpendicular to the tubes, and (ii) at least one and a half times the width, as measured parallel to the tubes; or (c) is sold as a set that has a dedicated condensing unit and an evaporator coil that does not have a means of forced air circulation. ( système de réfrigération de type chambre pour refroidissement industriel )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
walk-in refrigeration system means a refrigeration system that is installed, or that is designed to be installed, in a walk-in cooler or walk-in freezer and has a unit cooler or a dedicated condensing refrigeration system. It includes all controls and other components that are integral to its operation but does not include a walk-in process cooling refrigeration system or a walk-in refrigeration system that is designed and marketed exclusively for medical, scientific or research purposes. ( système de réfrigération de chambre froide )
Energy Efficiency Regulations, 2016 — 658
Nameplate required 658 (1) Every walk-in door assembly and walk-in panel that is manufactured on or after June 26, 2017 must be labelled with a nameplate that is attached to the outside of the product in a location that is readily visible prior to assembly of the walk-in cooler or walk-in freezer and that sets out the following information in English and French: (a) the brand name or manufacturer of the product; and (b) a statement indicating whether the product is intended for use in a walk-in cooler, walk-in freezer or both. Additional requirements (2) Every walk-in cooler dedicated condensing refrigeration system that is manufactured on or after January 1, 2020 and every walk-in refrigeration system that is manufactured on or after July 10, 2020 must be labelled with a nameplate that is attached to the outside of the product in a location that is readily visible prior to assembly of the walk-in cooler or the walk-in freezer and that sets out the following information in English and French: (a) the brand name or manufacturer of the product; (b) a statement indicating whether the product is intended for use in a walk-in cooler, walk-in freezer or both; (c) the model number; (d) the product’s date of manufacture, if it is not included in the model number; and (e) a statement indicating that the product is for indoor use only, if applicable. Idem (3) For matched refrigeration systems, the statement referred to in paragraph (2)(e) must appear on the dedicated condensing unit. SOR/2018-201, s. 76 SOR/2019-163, s. 50
Energy Efficiency Regulations, 2016 — 659
Energy-using product 659 (1) A walk-in door assembly is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 660, a walk-in door assembly is not considered to be an energy-using product unless it is manufactured on or after June 5, 2017. SOR/2018-201, s. 76
Energy Efficiency Regulations, 2016 — 660
Energy efficiency standards 660 (1) The energy efficiency standards set out in column 3 of the table to this section apply to walk-in door assemblies described in column 1 that are manufactured on or after June 5, 2017. Testing standard (2) A walk-in door assembly complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 2 that are applicable to a walk-in door assembly as defined in section 657. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Energy Efficiency Standard 1 Display door assemblies for walk-in coolers 10 C.F.R. Appendix A E daily ≤ 0.4306 × A dd + 0.41 (0.04 × A dd + 0.41) 2 Display door assemblies for walk-in freezers 10 C.F.R. Appendix A E daily ≤ 1.6146 × A dd + 0.29 (0.15 × A dd + 0.29) 3 Freight door assemblies for walk-in coolers 10 C.F.R. Appendix A for E daily 10 C.F.R. Appendix B for RSI-value (R-value) E daily ≤ 0.4306 × A nd + 1.9 (0.04 × A nd + 1.9) RSI-value ≥ 4.40 m²·K/W (25 ft²·°F h/Btu) 4 Freight door assemblies for walk-in freezers 10 C.F.R. Appendix A for E daily 10 C.F.R. Appendix B for RSI-value (R-value) E daily ≤ 1.2917 × A nd + 5.6 (0.12 × A nd + 5.6) RSI-value ≥ 5.64 m²·K/W (32 ft²·°F h/Btu) 5 Passage door assemblies for walk-in coolers 10 C.F.R. Appendix A for E daily 10 C.F.R. Appendix B for RSI-value (R-value) E daily ≤ 0.5382 × A nd + 1.7 (0.05 × A nd + 1.7) RSI-value ≥ 4.40 m²·K/W (25 ft²·°F h/Btu) 6 Passage door assemblies for walk-in freezers 10 C.F.R. Appendix A for E daily 10 C.F.R. Appendix B for RSI-value (R-value) E daily ≤ 1.5069 × A nd + 4.8 (0.14 × A nd + 4.8) RSI-value ≥ 5.64 m²·K/W (32 ft²·°F h/Btu) SOR/2018-201, s. 76 SOR/2022-265, s. 35 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. Appendix B for RSI-value (R-value)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
E daily ≤ 0.4306 × A nd + 1.9 (0.04 × A nd + 1.9)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
RSI-value ≥ 4.40 m²·K/W (25 ft²·°F h/Btu)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
E daily ≤ 1.2917 × A nd + 5.6 (0.12 × A nd + 5.6)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
RSI-value ≥ 5.64 m²·K/W (32 ft²·°F h/Btu)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
E daily ≤ 0.5382 × A nd + 1.7 (0.05 × A nd + 1.7)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
E daily ≤ 1.5069 × A nd + 4.8 (0.14 × A nd + 4.8)
Energy Efficiency Regulations, 2016 — 661
Information 661 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with 10 C.F.R. §431.304 and provided to the Minister in respect of a walk-in door assembly: (a) its E daily ; (b) information that indicates whether it is a display door assembly, freight door assembly or passage door assembly; (c) information that indicates whether it is for use with a walk-in cooler or walk-in freezer; and (d) if the product is a freight door assembly or passage door assembly, its RSI-value (R-value). SOR/2018-201, s. 76 SOR/2022-265, s. 36
Energy Efficiency Regulations, 2016 — 662
Energy-using product 662 (1) A walk-in panel is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 663, a walk-in panel is not considered to be an energy-using product unless it is manufactured on or after June 5, 2017. SOR/2018-201, s. 76
Energy Efficiency Regulations, 2016 — 663
Energy efficiency standards 663 (1) The energy efficiency standards set out in column 2 of the table to this section apply to walk-in panels described in column 1 that are manufactured on or after June 5, 2017. Testing standard (2) A walk-in panel complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by 10 C.F.R. Appendix B that are applicable to a walk-in panel as defined in section 657. TABLE Column 1 Column 2 Item Energy-using Product Energy Efficiency Standard 1 Structural panels for walk-in coolers RSI-value ≥ 4.40 m²·K/W (25 ft²·°F h/Btu) 2 Structural panels for walk-in freezers RSI-value ≥ 5.64 m²·K/W (32 ft²·°F h/Btu) 3 Floor panels RSI-value ≥ 4.93 m²·K/W (28 ft²·°F h/Btu) SOR/2018-201, s. 76 SOR/2022-265, s. 37
Energy Efficiency Regulations, 2016 — 664
Information 664 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with 10 C.F.R. Appendix B and provided to the Minister in respect of a walk-in panel: (a) its RSI-value (R-value), (b) information that indicates whether it is a structural panel or floor panel; and (c) if it is a structural panel, information that indicates whether it is for use with a walk-in cooler or walk-in freezer. SOR/2018-201, s. 76 SOR/2022-265, s. 38
Energy Efficiency Regulations, 2016 — 665
Energy-using product 665 (1) A walk-in refrigeration system is prescribed as an energy-using product. Limit (2) However, a walk-in refrigeration system is not considered to be an energy-using product for the purposes of sections 4, 5 and 666 unless (a) it is a walk-in cooler dedicated condensing refrigeration system manufactured on or after January 1, 2020; (b) it is a walk-in freezer dedicated condensing refrigeration system manufactured on or after July 10, 2020; or (c) it is a walk-in cooler or walk-in freezer unit cooler manufactured on or after July 10, 2020. SOR/2018-201, s. 76 SOR/2019-163, s. 51
Energy Efficiency Regulations, 2016 — 666
Energy efficiency standards 666 (1) The energy efficiency standards set out in column 2 of the table to this section apply to walk-in refrigeration systems described in column 1 that are manufactured during the periods set out in column 3. Testing standard (2) A walk-in refrigeration system complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by 10 C.F.R. Appendix C that are applicable to a walk-in refrigeration system as defined in section 657. TABLE Item Column 1 Column 2 Column 3 Energy-using Product Energy Efficiency Standard Period of Manufacture 1 Walk-in cooler dedicated condensing refrigeration systems for use indoors Annual walk-in energy factor ≥ 1.644 W-h/W-h (5.61 Btu/W-h) On or after January 1, 2020 2 Walk-in cooler dedicated condensing refrigeration systems for use outdoors Annual walk-in energy factor ≥ 2.227 W-h/W-h (7.60 Btu/W-h) On or after January 1, 2020 3 Walk-in freezer dedicated condensing refrigeration systems for use indoors with a net refrigeration capacity of < 1900 W (6,500 Btu/h) Annual walk-in energy factor ≥ 9.091 x 10 -5 x q net + 0.530 W-h/W-h (9.091 x 10 -5 x q net + 1.81 Btu/W-h) On or after July 10, 2020 4 Walk-in freezer dedicated condensing refrigeration systems for use indoors with a net refrigeration capacity of ≥ 1900 W (6,500 Btu/h) Annual walk-in energy factor ≥ 0.703 W-h/W-h (2.40 Btu/W-h) On or after July 10, 2020 5 Walk-in freezer dedicated condensing refrigeration system for use outdoors with a net refrigeration capacity of < 1900 W (6,500 Btu/h) Annual walk-in energy factor ≥ 6.522 x 10 -5 x q net + 0.800 W-h/W-h (6.522 x 10 -5 x q net + 2.73 Btu/W-h) On or after July 10, 2020 6 Walk-in freezer dedicated condensing refrigeration systems for use outdoors with a net refrigeration capacity of ≥ 1900 W (6,500 Btu/h) Annual walk-in energy factor ≥ 0.923 W-h/W-h (3.15 Btu/W-h) On or after July 10, 2020 7 Walk-in cooler unit coolers with a fan motor that operates using direct current or has a nominal voltage of not more than 480 V AC Annual walk-in energy factor ≥ 2.638 W-h/W-h (9.00 Btu/W-h) On or after July 10, 2020 8 Walk-in freezer unit coolers with a fan motor that operates using direct current or has a nominal voltage of not more than 480 V AC and with a net refrigeration capacity of < 4540 W (15,500 Btu/h) Annual walk-in energy factor ≥ 1.575 x 10 -5 x q net + 1.146 W-h/W-h (1.575 x 10 -5 x q net + 3.91 Btu/W-h) On or after July 10, 2020 9 Walk-in freezer unit coolers with a fan motor that operates using direct current or has a nominal voltage of not more than 480 V AC and with a net refrigeration capacity of ≥ 4540 W (15,500 Btu/h) Annual walk-in energy factor ≥ 1.216 W-h/W-h (4.15 Btu/W-h) On or after July 10, 2020 SOR/2018-201, s. 76 SOR/2019-163, s. 52 SOR/2022-265, s. 39
Energy Efficiency Regulations, 2016 — 667
Information 667 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with 10 C.F.R. Appendix C and provided to the Minister in respect of a walk-in refrigeration system: (a) its annual walk-in energy factor; (b) information that indicates whether it is designed and marketed for use indoors, outdoors or both; (c) information that indicates if it is for use in a walk-in cooler or walk-in freezer; (d) information that indicates if it has a unit cooler or a dedicated condensing refrigeration system; and (e) if it is a walk-in freezer unit cooler or dedicated condensing refrigeration system, its net refrigeration capacity expressed in watts. SOR/2018-201, s. 76 SOR/2019-163, s. 53
Energy Efficiency Regulations, 2016 — 703
Definitions 703 The following definitions apply in this Division. CSA C802.2 means the CSA standard CAN/CSA-C802.2-00 entitled Minimum Efficiency Values for Dry-Type Transformers . ( CSA C802.2 ) CSA C802.2-12 means the CSA standard CAN/CSA-C802.2-12 entitled Minimum efficiency values for dry-type transformers . ( CSA C802.2-12 ) dry-type transformer means a transformer whose core and windings are in a gaseous or dry compound insulating medium and that is either single-phase with a nominal power of 15 to 833 kVA or three-phase with a nominal power of 15 to 7 500 kVA, has a nominal frequency of 60 Hz and has a high voltage winding of 35 kV or less. It does not include any of the following: (a) an autotransformer; (b) a drive (isolation) transformer that has two or more output windings or a nominal low-voltage line current of more than 1 500 A; (c) a grounding transformer; (d) a rectifier transformer; (e) a sealed transformer; (f) a non-ventilated transformer; (g) a testing transformer; (h) a furnace transformer; (i) a welding transformer; (j) a special impedance transformer; (k) a transformer that has a nominal low-voltage line current of 4 000 A or more; (l) an on-load regulating transformer; (m) a resistance grounding transformer; or (n) a transformer that is in a voltage class greater than 1.2 kV and that has a BIL of less than 20 kV or more than 199 kV. ( transformateur à sec ) 10 C.F.R. Appendix A means Appendix A to Subpart K, Part 431 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for Measuring the Energy Consumption of Distribution Transformers , as amended from time to time. ( appendice A 10 C.F.R. ) transformer means a static-electric device that consists of two or more coils of insulated wire, together with the necessary accessories, and that transfers alternating current by electromagnetic induction from one coil to another to change the original voltage. ( transformateur ) SOR/2018-201, s. 77
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C802.2 means the CSA standard CAN/CSA-C802.2-00 entitled Minimum Efficiency Values for Dry-Type Transformers . ( CSA C802.2 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C802.2-12 means the CSA standard CAN/CSA-C802.2-12 entitled Minimum efficiency values for dry-type transformers . ( CSA C802.2-12 )
Energy Efficiency Regulations, 2016 — (a)
dry-type transformer means a transformer whose core and windings are in a gaseous or dry compound insulating medium and that is either single-phase with a nominal power of 15 to 833 kVA or three-phase with a nominal power of 15 to 7 500 kVA, has a nominal frequency of 60 Hz and has a high voltage winding of 35 kV or less. It does not include any of the following: (a) an autotransformer; (b) a drive (isolation) transformer that has two or more output windings or a nominal low-voltage line current of more than 1 500 A; (c) a grounding transformer; (d) a rectifier transformer; (e) a sealed transformer; (f) a non-ventilated transformer; (g) a testing transformer; (h) a furnace transformer; (i) a welding transformer; (j) a special impedance transformer; (k) a transformer that has a nominal low-voltage line current of 4 000 A or more; (l) an on-load regulating transformer; (m) a resistance grounding transformer; or (n) a transformer that is in a voltage class greater than 1.2 kV and that has a BIL of less than 20 kV or more than 199 kV. ( transformateur à sec )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. Appendix A means Appendix A to Subpart K, Part 431 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for Measuring the Energy Consumption of Distribution Transformers , as amended from time to time. ( appendice A 10 C.F.R. )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
transformer means a static-electric device that consists of two or more coils of insulated wire, together with the necessary accessories, and that transfers alternating current by electromagnetic induction from one coil to another to change the original voltage. ( transformateur )
Energy Efficiency Regulations, 2016 — 704
Energy-using product 704 (1) A dry-type transformer is prescribed as an energy-using product. Limits (2) However, a dry-type transformer is not considered to be an energy-using product (a) for the purposes of sections 4 and 5, if it was manufactured before January 1, 2005; and (b) for the purpose of section 705, if it has a BIL of more than 150 kV and was manufactured before January 1, 2010.
Energy Efficiency Regulations, 2016 — 705
Energy efficiency standards — manufactured before January 1, 2016 705 (1) In respect of dry-type transformers that were manufactured on or after January 1, 2005 and before January 1, 2016, the energy efficiency standards set out in column 2 of the table to this section apply to dry-type transformers that were manufactured during the periods set out in column 3. Testing standard (2) A dry-type transformer complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard referred to in column 1 that are applicable to a dry-type transformer as defined in section 703. TABLE Column 1 Column 2 Column 3 Item Testing Standard Energy Efficiency Standard Period of Manufacture 1 CSA C802.2 CSA C802.2, Table 1 On or after January 1, 2005 and before January 1, 2010 2 CSA C802.2-12 CSA C802.2-12, Table 1 On or after January 1, 2010 and before January 1, 2016 SOR/2018-201, s. 78 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — 705.1
Energy efficiency standard — single-phase and 1.2 kV voltage class 705.1 (1) In respect of dry-type transformers that are single-phase, in the 1.2 kV voltage class and manufactured on or after January 1, 2016, the energy efficiency standards set out in column 2 of Table 1 to this section apply to dry-type transformers that have a kVA rating described in column 1. Energy efficiency standards — single-phase and voltage class greater than 1.2 kV (2) In respect of dry-type transformers that are single-phase, in a voltage class greater than 1.2 kV and manufactured on or after January 1, 2016, the energy efficiency standards that are set out in relation to the product’s BIL rating set out in column 2 of Table 2 to this section apply to dry-type transformers that have a kVA rating set out in column 1. Interpolation (3) For the purposes of subsections (1) and (2), if the kVA rating of the product falls between the kVA ratings set out in two consecutive items in column 1 of the applicable table to this section, the energy efficiency standard for the product is an interpolation of the corresponding energy efficiency standards set out in column 2. Testing standard (4) A dry-type transformer complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by 10 C.F.R. Appendix A that are applicable to a dry-type transformer as defined in section 703. TABLE 1 Column 1 Column 2 Item kVA Rating % Efficiency When Tested at 35% of Nominal Load 1 15.0 97.70 2 25.0 98.00 3 37.5 98.20 4 50.0 98.30 5 75.0 98.50 6 100.0 98.60 7 167.0 98.70 8 250.0 98.80 9 333.0 98.90 TABLE 2 Column 1 Column 2 Item kVA Rating % Efficiency When Tested at 50% of Nominal Load 20-45 kV BIL > 45-95 kV BIL > 95-199 kV BIL 1 15.0 98.10 97.86 97.60 2 25.0 98.33 98.12 97.90 3 37.5 98.49 98.30 98.10 4 50.0 98.60 98.42 98.20 5 75.0 98.73 98.57 98.53 6 100.0 98.82 98.67 98.63 7 167.0 98.96 98.83 98.80 8 250.0 99.07 98.95 98.91 9 333.0 99.14 99.03 98.99 10 500.0 99.22 99.12 99.09 11 667.0 99.27 99.18 99.15 12 833.0 99.31 99.23 99.20 SOR/2018-201, s. 79