Energy Efficiency Regulations, 2016 — 197
Energy efficiency standards 197 (1) The energy efficiency standards set out in column 3 of Table 1 to this section apply to large heat pumps described in column 1 that are manufactured during the periods set out in column 4 and that have no heating section or have an electric heating section. Energy efficiency standards (2) The energy efficiency standards set out in column 3 of Table 2 to this section apply to large heat pumps described in column 1 that are manufactured during the periods set out in column 4 and that have a heating section other than an electric heating section. Testing standard (3) A large heat pump complies with the energy efficiency standard set out in column 3 if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 2 that are applicable to a large heat pump as defined in section 195. TABLE 1 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Large heat pumps that have a cooling capacity of ≥ 19 kW and < 40 kW CSA C746-98 Energy efficiency ratio ≥ 10.1 Heating coefficient of performance ≥ 3.2 with 8.3°C inlet air and ≥ 2.2 with –8.3°C inlet air On or after December 31, 1998 and before January 1, 2010 2 Large heat pumps that have a cooling capacity of ≥ 19 kW and < 40 kW CSA C746-06 for energy efficiency ratio and heating coefficient of performance AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.0 Heating coefficient of performance ≥ 3.3 with 8.3°C inlet air and ≥ 2.25 with –8.3°C inlet air IEER ≥ 11.2 On or after January 1, 2010 and before January 1, 2018 3 Large heat pumps that have a cooling capacity of ≥ 19 kW and < 40 kW CSA C746-17 Energy efficiency ratio ≥ 11.0 Heating coefficient of performance ≥ 3.3 with 8.3°C inlet air and ≥ 2.25 with –8.3°C inlet air IEER ≥ 12.2 On or after January 1, 2018 and before January 1, 2026 4 Large heat pumps that have a cooling capacity of ≥ 19 kW and < 40 kW CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 11.0 Heating coefficient of performance ≥ 3.4 with 8.3°C inlet air and ≥ 2.25 with −8.3°C inlet air IEER ≥ 14.1 On or after January 1, 2026 5 Large heat pumps that have a cooling capacity of ≥ 40 kW and < 70 kW CSA C746-98 Energy efficiency ratio ≥ 9.3 Heating coefficient of performance ≥ 3.1 with 8.3°C inlet air and ≥ 2.0 with −8.3°C inlet air On or after December 31, 1998 and before January 1, 2010 6 Large heat pumps that have a cooling capacity of ≥ 40 kW and < 70 kW CSA C746-06 for energy efficiency ratio and heating coefficient of performance AHRI 340/360 for IEER Energy efficiency ratio ≥ 10.6 Heating coefficient of performance ≥ 3.2 with 8.3°C inlet air and ≥ 2.05 with −8.3°C inlet air IEER ≥ 10.7 On or after January 1, 2010 and before January 1, 2018 7 Large heat pumps that have a cooling capacity of ≥ 40 kW and < 70 kW CSA C746-17 Energy efficiency ratio ≥ 10.6 Heating coefficient of performance ≥ 3.2 with 8.3°C inlet air and ≥ 2.05 with −8.3°C inlet air IEER ≥ 11.6 On or after January 1, 2018 and before January 1, 2026 8 Large heat pumps that have a cooling capacity of ≥ 40 kW and < 70 kW CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 10.6 Heating coefficient of performance ≥ 3.3 with 8.3°C inlet air and ≥ 2.05 with −8.3°C inlet air IEER ≥ 13.5 On or after January 1, 2026 9 Large heat pumps that have a cooling capacity of ≥ 70 kW and < 223 kW CSA C746-06 for energy efficiency ratio and heating coefficient of performance AHRI 340/360 for IEER Energy efficiency ratio ≥ 9.5 Heating coefficient of performance ≥ 3.2 with 8.3°C inlet air and ≥ 2.05 with −8.3°C inlet air IEER ≥ 9.6 On or after January 1, 2010 and before January 1, 2018 10 Large heat pumps that have a cooling capacity of ≥ 70 kW and < 223 kW CSA C746-17 Energy efficiency ratio ≥ 9.5 Heating coefficient of performance ≥ 3.2 with 8.3°C inlet air and ≥ 2.05 with −8.3°C inlet air IEER ≥ 10.6 On or after January 1, 2018 and before