Energy Efficiency Regulations, 2016 — 118
.2 IEER ≥ 10.9 On or after January 1, 2018 TABLE 3 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and either without a heating section or with an electric heating section CSA C746-98 Energy efficiency ratio ≥ 11.5 On or after December 31, 1998 and before January 1, 2010 2 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and either without a heating section or with an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.5 IEER ≥ 11.7 On or after January 1, 2010 and before January 1, 2018 3 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and either without a heating section or with an electric heating section CSA C746-17 Energy efficiency ratio ≥ 12.1 IEER ≥ 11.7 On or after January 1, 2018 4 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and either without a heating section or with an electric heating section CSA C746-98 Energy efficiency ratio ≥ 11.0 On or after December 31, 1998 and before January 1, 2010 5 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and either without a heating section or with an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.0 IEER ≥ 11.2 On or after January 1, 2010 and before January 1, 2018 6 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and either without a heating section or with an electric heating section CSA C746-17 Energy efficiency ratio ≥ 12.0 IEER ≥ 11.2 On or after January 1, 2018 7 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-98 Energy efficiency ratio ≥ 11.3 On or after December 31, 1998 and before January 1, 2010 8 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.3 IEER ≥ 11.5 On or after January 1, 2010 and before January 1, 2018 9 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-17 Energy efficiency ratio ≥ 11.9 IEER ≥ 11.5 On or after January 1, 2018 10 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-98 Energy efficiency ratio ≥ 10.8 On or after December 31, 1998 and before January 1, 2010 11 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 10.8 IEER ≥ 11.0 On or after January 1, 2010 and before January 1, 2018 12 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-17 Energy efficiency ratio ≥ 11.8 IEER ≥ 11.0 On or after January 1, 2018 13 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and either without a heating section or with an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.0 IEER ≥ 11.1 On or after January 1, 2010 and before January 1, 2018 14 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and either without a heating section or with an electric heating section CSA C746-17 Energy efficiency ratio ≥ 11.9 IEER ≥ 11.1 On or after January 1, 2018 15 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and a heating section other than an electric heating section CSA C746-06 for energy efficien