GreatNorthCollective/greatnorth-canada-federal-laws-text huggingface dataset:
Energy Efficiency Regulations, 2016 — 201
Energy efficiency standards 201 (1) The energy efficiency standards set out in column 2 of the table to this section apply to packaged terminal heat pumps that are manufactured during the periods set out in column 3. Testing standard (2) A packaged terminal heat pump complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 1 that are applicable to a packaged terminal heat pump as defined in section 199. TABLE Column 1 Column 2 Column 3 Item Testing Standard Energy Efficiency Standard Period of Manufacture 1 CSA C744-04 CSA C744-04, Table 2 On or after December 31, 1998 and before September 30, 2012 2 CSA C744-17 CSA C744-17, Table 2 On or after September 30, 2012 SOR/2019-163, s. 33 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — 202
Information 202 (1) For the purpose of subsection 5(1) of the Act, the following information must be provided to the Minister in respect of a packaged terminal heat pump: (a) its cooling capacity, expressed in kilowatts (British thermal units per hour); (b) its energy efficiency ratio; (c) its heating capacity, expressed in kilowatts (British thermal units per hour); (d) its heating coefficient of performance; and (e) if applicable, identification of the product as a replacement unit. Standard (2) The information must be collected in accordance with (a) CSA C744-04, if the product was manufactured on or after December 31, 1998 and before September 30, 2012; or (b) CSA C744-17, if the product is manufactured on or after September 30, 2012. SOR/2019-163, s. 34
Energy Efficiency Regulations, 2016 — 203
Definitions 203 The following definitions apply in this Subdivision. off mode power consumption means the power consumption when the unit is connected to mains power but is not providing cooling or heating. ( consommation d’énergie en mode arrêt ) single package central heat pump means a single-phase or three-phase air-to-air central heat pump that is a single package unit and that has a cooling capacity of less than 19 kW (65,000 Btu/h), but does not include a single package vertical heat pump. ( thermopompe centrale monobloc ) single package heat pump [Repealed, SOR/2022-265, s. 15] through-the-wall means, in respect of a single package central heat pump, one that has a cooling capacity less than or equal to 8.79 kW (30,000 Btu/h), that is designed to be installed through an exterior wall and that is manufactured prior to January 1, 2023. ( murale ) SOR/2019-163, s. 35 SOR/2022-265, s. 15 SOR/2025-110, s. 33
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
single package central heat pump means a single-phase or three-phase air-to-air central heat pump that is a single package unit and that has a cooling capacity of less than 19 kW (65,000 Btu/h), but does not include a single package vertical heat pump. ( thermopompe centrale monobloc )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
single package heat pump [Repealed, SOR/2022-265, s. 15]
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
through-the-wall means, in respect of a single package central heat pump, one that has a cooling capacity less than or equal to 8.79 kW (30,000 Btu/h), that is designed to be installed through an exterior wall and that is manufactured prior to January 1, 2023. ( murale )
Energy Efficiency Regulations, 2016 — 204
Energy-using product 204 (1) A single package central heat pump is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 205, a single package central heat pump is not considered to be an energy-using product unless it is manufactured on or after February 3, 1995. SOR/2022-265, s. 16
Energy Efficiency Regulations, 2016 — 205
d before January 1, 2023 2 Single package central heat pumps that are through-the-wall CSA C656-05 Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.4 On or after February 3, 1995 and before January 1, 2023 3 Single package central heat pumps that are small-duct and high-velocity CSA C656-14 Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.3 On or after February 3, 1995 and before January 1, 2023 4 Single package central heat pumps, other than those that are space-constrained CSA C656-14 Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.0 On or after January 1, 2023 and before January 1, 2026 5 Single package central heat pumps that are space-constrained CSA C656-14 Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.4 On or after January 1, 2023 and before January 1, 2026 6 Single package central heat pumps, other than those that are space-constrained 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 13.4 Heating seasonal performance factor 2 (Region V) ≥ 5.3 On or after January 1, 2026 7 Single package central heat pumps that are space-constrained 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 13.9 Heating seasonal performance factor 2 (Region V) ≥ 5.3 On or after January 1, 2026 SOR/2019-163, s. 36 SOR/2022-265, s. 17 SOR/2025-110, s. 34
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-14 for seasonal energy efficiency ratio and heating seasonal performance factor
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor (Region V) ≥ 7.0
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-05 for seasonal energy efficiency ratio and heating seasonal performance factor
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor (Region V) ≥ 6.4
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor (Region V) ≥ 6.3
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 5.4
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 11.9
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 5.0
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 5.3
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 13.9
Energy Efficiency Regulations, 2016 — 206
 to (h) (a) type; (b) cooling capacity in kW (Btu/h); (c) heating capacity at 8.3°C (47°F) in kW (Btu/h); (d) seasonal energy efficiency ratio 2; (e) heating seasonal performance factor 2 for Region V; (f) heating capacity at -15°C (5°F) in kW (Btu/h); (g) coefficient of performance at -15°C (5°F); (h) off mode power consumption, in watts; and (i) phase of electric current. 7 Single package central heat pumps that are three-phase and manufactured on or after January 1, 2023 and before January 1, 2026 CSA C656-14 for information set out in paragraphs (a) to (e) (a) product classification set out in column II of Table 1 to CSA C656-14; (b) cooling capacity in kW (Btu/h); (c) heating capacity in kW (Btu/h); (d) seasonal energy efficiency ratio; (e) heating seasonal performance factor; and (f) phase of electric current. 8 Single package central heat pumps that are three-phase and manufactured on or after January 1, 2026 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted for information set out in paragraphs (b) to (g) (a) type; (b) cooling capacity in kW (Btu/h); (c) heating capacity at 8.3°C (47°F) in kW (Btu/h); (d) seasonal energy efficiency ratio 2; (e) heating seasonal performance factor 2 for region V; (f) heating capacity at -15°C (5°F) in kW (Btu/h); (g) coefficient of performance at -15°C (5°F); and (h) phase of electric current. SOR/2019-163, s. 37 SOR/2022-265, s. 17 SOR/2025-110, s. 35
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-14 for information set out in paragraphs (a) to (e)
Energy Efficiency Regulations, 2016 — (e)
(e) heating seasonal performance factor and the region for the factor;
Energy Efficiency Regulations, 2016 — (f)
(f) off mode power consumption, in watts; and
Energy Efficiency Regulations, 2016 — (e)
(e) heating seasonal performance factor and the region for the factor; and
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-05 for information set out in paragraphs (a) to (e)
Energy Efficiency Regulations, 2016 — (c)
(c) heating capacity at 8.3°C (47°F) in kW (Btu/h);
Energy Efficiency Regulations, 2016 — (e)
(e) information that indicates whether the results from the very low temperature heating test (H4) were included in the calculation of the heating seasonal performance factor 2 for Region V;
Energy Efficiency Regulations, 2016 — (f)
(f) heating seasonal performance factor 2 for Region V;
Energy Efficiency Regulations, 2016 — (g)
(g) heating capacity at -15°C (5°F) in kW (Btu/h), if the very low temperature heating test (H4) was conducted;
Energy Efficiency Regulations, 2016 — (h)
(h) coefficient of performance at -15°C (5°F), if the very low temperature heating test (H4) was conducted;
Energy Efficiency Regulations, 2016 — (i)
(i) off mode power consumption, in watts; and
Energy Efficiency Regulations, 2016 — (e)
(e) heating seasonal performance factor 2 for Region V;
Energy Efficiency Regulations, 2016 — (f)
(f) heating capacity at -15°C (5°F) in kW (Btu/h);
Energy Efficiency Regulations, 2016 — (g)
(g) coefficient of performance at -15°C (5°F);
Energy Efficiency Regulations, 2016 — (h)
(h) off mode power consumption, in watts; and
Energy Efficiency Regulations, 2016 — (e)
(e) heating seasonal performance factor; and
Energy Efficiency Regulations, 2016 — (e)
(e) heating seasonal performance factor 2 for region V;
Energy Efficiency Regulations, 2016 — (g)
(g) coefficient of performance at -15°C (5°F); and
Energy Efficiency Regulations, 2016 — 206.1
Early compliance 206.1 A single package central heat pump that is manufactured on or after January 1, 2025 and before January 1, 2026 is deemed to satisfy the requirements of sections 205 and 206 if it satisfies the requirements of those sections that would have applied to the single package central heat pump if it had been manufactured on or after January 1, 2026. SOR/2025-110, s. 36
Energy Efficiency Regulations, 2016 — 207
Definition of single package vertical heat pump 207 In this Subdivision, single package vertical heat pump means a single package commercial heat pump that is encased, that has its major components arranged vertically and that (a) is air-cooled and uses reverse cycle refrigeration as its primary heat source; and (b) is intended for mounting through, or on either side of, an exterior wall.
Energy Efficiency Regulations, 2016 — 208
Energy-using product 208 (1) A single package vertical heat pump is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 209, a single package vertical heat pump is not considered to be an energy-using product unless it is manufactured on or after January 1, 2011 and has a cooling capacity of less than 70 kW (240,000 Btu/h). SOR/2019-163, s. 38
Energy Efficiency Regulations, 2016 — 209
Energy efficiency standards 209 (1) The energy efficiency standards set out in column 2 of the table to this section apply to single package vertical heat pumps described in column 1 that are manufactured during the periods set out in column 3. Testing standard (2) A single package vertical heat pump complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by CSA C746-17 that are applicable to a single package vertical heat pump as defined in section 207. TABLE Item Column 1 Column 2 Column 3 Energy-using Product Energy Efficiency Standard Period of manufacture 1 Single package vertical heat pumps that have a cooling capacity of < 19 kW (65,000 Btu/h) Energy efficiency ratio ≥ 9.0 Heating coefficient of performance ≥ 3.0 On or after January 1, 2011 and before September 23, 2019 2 Single package vertical heat pumps that have a cooling capacity of < 19 kW (65,000 Btu/h) Energy efficiency ratio ≥ 11.0 Heating coefficient of performance ≥ 3.3 On or after September 23, 2019 3 Single package vertical heat pumps that have a cooling capacity of ≥ 19 kW (65,000 Btu/h) and < 39.5 kW (135,000 Btu/h) Energy efficiency ratio ≥ 8.9 Heating coefficient of performance ≥ 3.0 On or after January 1, 2011 and before October 9, 2015 4 Single package vertical heat pumps that have a cooling capacity of ≥ 19 kW (65,000 Btu/h) and < 39.5 kW (135,000 Btu/h Energy efficiency ratio ≥ 10.0 Heating coefficient of performance ≥ 3.0 On or after October 9, 2015 5 Single package vertical heat pumps that have a cooling capacity of ≥ 39.5 kW (135,000 Btu/h) and < 70 kW (240,000 Btu/h) Energy efficiency ratio ≥ 8.6 Heating coefficient of performance ≥ 2.9 On or after January 1, 2011 and before October 9, 2016 6 Single package vertical heat pumps that have a cooling capacity of ≥ 39.5 kW (135,000 Btu/h) and < 70 kW (240,000 Btu/h) Energy efficiency ratio ≥ 10.0 Heating coefficient of performance ≥ 3.0 On or after October 9, 2016 SOR/2019-163, s. 39
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating coefficient of performance ≥ 3.0
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating coefficient of performance ≥ 3.3
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating coefficient of performance ≥ 2.9
Energy Efficiency Regulations, 2016 — 210
Information 210 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with CSA C746-17 and provided to the Minister in respect of a single package vertical heat pump: (a) its classification set out in columns II and III of Table 2 to CSA C746-17; (b) its cooling capacity, expressed in kilowatts (British thermal units per hour); (c) its energy efficiency ratio; (d) its heating capacity, expressed in kilowatts (British thermal units per hour); and (e) its heating coefficient of performance. SOR/2019-163, s. 40
Energy Efficiency Regulations, 2016 — 211
Definitions 211 The following definitions apply in this Subdivision. off mode power consumption means the power consumption when the unit is connected to mains power but is not providing cooling or heating. ( consommation d’énergie en mode arrêt ) split system central heat pump means a single-phase or three-phase air-to-air central heat pump that is a split system and that has a cooling capacity of less than 19 kW (65,000 Btu/h). ( thermopompe centrale bibloc ) split-system heat pump [Repealed, SOR/2022-265, s. 19] SOR/2019-163, s. 41 SOR/2022-265, s. 19 SOR/2025-110, s. 37
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
split system central heat pump means a single-phase or three-phase air-to-air central heat pump that is a split system and that has a cooling capacity of less than 19 kW (65,000 Btu/h). ( thermopompe centrale bibloc )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
split-system heat pump [Repealed, SOR/2022-265, s. 19]
Energy Efficiency Regulations, 2016 — 212
Energy-using product 212 (1) A split system central heat pump is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 213, a split system central heat pump is not considered to be an energy-using product unless it is manufactured on or after December 31, 1998. SOR/2022-265, s. 20
Energy Efficiency Regulations, 2016 — 213
lit system central heat pumps, other than those that are small-duct and high-velocity CSA C656-14 Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.1 On or after December 31, 1998 and before January 1, 2026 2 Split system central heat pumps that are small-duct and high-velocity CSA C656-14 Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.3 On or after December 31, 1998 and before January 1, 2026 3 Split system central heat pumps, other than those that are space-constrained or small-duct and high-velocity 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 14.3 Heating seasonal performance factor 2 (Region V) ≥ 6.0 On or after January 1, 2026 4 Split system central heat pumps that are space-constrained 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 13.9 Heating seasonal performance factor 2 (Region V) ≥ 5.6 On or after January 1, 2026 5 Split system central heat pumps that are small-duct and high-velocity 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 14.0 Heating seasonal performance factor 2 (Region V) ≥ 5.5 On or after January 1, 2026 SOR/2019-163, s. 42 SOR/2022-265, s. 21 SOR/2025-110, s. 38
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor (Region V) ≥ 7.1
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 14.3
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 6.0
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 4.9
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 5.6
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 14.0
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Heating seasonal performance factor 2 (Region V) ≥ 5.5
Energy Efficiency Regulations, 2016 — 214.1
Early compliance 214.1 A split system central heat pump that is manufactured on or after January 1, 2025 and before January 1, 2026 is deemed to satisfy the requirements of sections 213 and 214 if it satisfies the requirements of those sections that would have applied to the split system central heat pump if it had been manufactured on or after January 1, 2026. SOR/2025-110, s. 40
Energy Efficiency Regulations, 2016 — 256.1
Definitions 256.1 The following definitions apply in this Division. CSA P.2 means the CSA standard CAN/CSA-P.2-13 entitled Testing method for measuring the annual fuel utilization efficiency of residential gas-fired or oil-fired furnaces and boilers . ( CSA P.2 ) FER means, in respect of a gas furnace, an oil-fired furnace or an electric furnace, the fan energy rating, which is the annual electrical energy consumption of the furnace fan normalized by annual fan operating hours and the product’s maximum airflow (Q max ). ( FER ) 10 C.F.R. Appendix AA means Appendix AA to Subpart B of Part 430 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for Measuring the Energy Consumption of Furnace Fans , as amended from time to time. ( appendice AA 10 C.F.R. ) 10 C.F.R. §430.32(y) means Table 1 to paragraph 430.32(y) of Subpart C, Part 430 of Title 10 to the United States Code of Federal Regulations , as amended from time to time. ( 10 C.F.R. §430.32(y) ) SOR/2018-201, s. 33 SOR/2019-164, s. 2
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA P.2 means the CSA standard CAN/CSA-P.2-13 entitled Testing method for measuring the annual fuel utilization efficiency of residential gas-fired or oil-fired furnaces and boilers . ( CSA P.2 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
FER means, in respect of a gas furnace, an oil-fired furnace or an electric furnace, the fan energy rating, which is the annual electrical energy consumption of the furnace fan normalized by annual fan operating hours and the product’s maximum airflow (Q max ). ( FER )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. Appendix AA means Appendix AA to Subpart B of Part 430 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for Measuring the Energy Consumption of Furnace Fans , as amended from time to time. ( appendice AA 10 C.F.R. )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. §430.32(y) means Table 1 to paragraph 430.32(y) of Subpart C, Part 430 of Title 10 to the United States Code of Federal Regulations , as amended from time to time. ( 10 C.F.R. §430.32(y) )
Energy Efficiency Regulations, 2016 — 257
Definitions 257 The following definitions apply in this Subdivision. CSA 2.3 means the CSA standard ANSI Z21.47-2016/CSA 2.3-2016 entitled Gas-Fired Central Furnaces . ( CSA 2.3 ) CSA P.2 [Repealed, SOR/2018-201, s. 34] gas furnace means an automatic operating gas-fired central forced air furnace that uses propane or natural gas and has an input rate of not more than 117.23 kW (400,000 Btu/h). It does not include a furnace for a park model trailer or a recreational vehicle. ( générateur d’air chaud à gaz ) gas furnace for relocatable buildings means a gas furnace that is intended for use in a temporary modular building that can be relocated from one site to another and is marked for use in relocatable buildings. ( générateur d’air chaud à gaz pour bâtiments relocalisables ) manufactured home means a factory-built, single- or multiple-section, one-storey dwelling that (a) is designed and constructed for year-round occupancy; (b) is designed to be transported to its installation site; and (c) is ready for occupancy when it is installed in accordance with the manufacturer’s installation instructions. ( maison usinée ) replacement non-condensing gas furnace means a non-condensing gas furnace that is marked for use as a replacement for a non-condensing gas furnace in a manufactured home. ( générateur d’air chaud à gaz sans condensation de remplacement ) space-constrained , with respect to a gas furnace, means one that (a) uses single-phase electric current; and (b) has an outdoor or indoor unit (i) that has an overall displacement that is — or two or more overall exterior dimensions that are — substantially smaller than those of other units of a similar heating capacity that are usually installed in single-family homes, and (ii) with respect to which an increase in the overall displacement or two or more overall exterior dimensions would result in a considerable increase in the usual cost of installation or in a significant loss in the utility of the product to the consumer. ( à espace restreint ) through-the-wall means, with respect to a gas furnace, one that is designed and marketed to be installed in an opening in an exterior wall that is fitted with a weatherized sleeve. ( mural ) SOR/2018-201, s. 34 SOR/2019-164, s. 3 SOR/2025-110, s. 41
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA 2.3 means the CSA standard ANSI Z21.47-2016/CSA 2.3-2016 entitled Gas-Fired Central Furnaces . ( CSA 2.3 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
gas furnace means an automatic operating gas-fired central forced air furnace that uses propane or natural gas and has an input rate of not more than 117.23 kW (400,000 Btu/h). It does not include a furnace for a park model trailer or a recreational vehicle. ( générateur d’air chaud à gaz )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
gas furnace for relocatable buildings means a gas furnace that is intended for use in a temporary modular building that can be relocated from one site to another and is marked for use in relocatable buildings. ( générateur d’air chaud à gaz pour bâtiments relocalisables )