GreatNorthCollective/greatnorth-canada-federal-laws-text huggingface dataset:
Energy Efficiency Regulations, 2016 — 274
Energy efficiency standard 274 (1) The energy efficiency standard that applies to an electric furnace is that its FER must be less than or equal to the FER for product class “Non-Weatherized, Electric Furnace/Modular Blower Fan”, set out in 10 C.F.R. §430.32(y). Testing standard (2) An electric furnace complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by 10 C.F.R. Appendix AA that are applicable to an electric furnace as defined in section 272. SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 275
Information 275 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with 10 C.F.R. Appendix AA and provided to the Minister in respect of an electric furnace: (a) its maximum heat input nominal capacity, expressed in kilowatts (British thermal units per hour); (b) its FER, expressed in watts per 472 L/s (watts per 1000 ft 3 /min); and (c) its maximum airflow (Q max ), expressed in L/s (ft 3 /min). SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 276
Definitions 276 The following definitions apply in this Subdivision. CSA C439-18 means the CSA standard CAN/CSA-C439-18 entitled Laboratory methods of test for rating the performance of heat/energy-recovery ventilators . ( CSA C439-18 ) energy-recovery ventilator means a factory-built packaged unit that has fans or blowers, has a maximum rated airflow of not more than 142 L/s (300 ft 3 /min) at 0°C and transfers heat and moisture between two isolated airstreams. ( ventilateur-récupérateur d’énergie ) heat-recovery ventilator means a factory-built packaged unit that has fans or blowers, has a maximum rated airflow of not more than 142 L/s (300 ft 3 /min) at 0°C and transfers heat between two isolated airstreams. ( ventilateur-récupérateur de chaleur ) sensible heat recovery efficiency means, in respect of an energy-recovery ventilator or a heat-recovery ventilator, the ratio of the net sensible energy recovered by the unit’s supply airstream, as adjusted to account for the unit’s external and internal energy gains and losses, to the maximum sensible energy that would be recovered if the unit had an infinite transfer area. ( efficacité de récupération de chaleur sensible ) SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C439-18 means the CSA standard CAN/CSA-C439-18 entitled Laboratory methods of test for rating the performance of heat/energy-recovery ventilators . ( CSA C439-18 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
energy-recovery ventilator means a factory-built packaged unit that has fans or blowers, has a maximum rated airflow of not more than 142 L/s (300 ft 3 /min) at 0°C and transfers heat and moisture between two isolated airstreams. ( ventilateur-récupérateur d’énergie )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
heat-recovery ventilator means a factory-built packaged unit that has fans or blowers, has a maximum rated airflow of not more than 142 L/s (300 ft 3 /min) at 0°C and transfers heat between two isolated airstreams. ( ventilateur-récupérateur de chaleur )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
sensible heat recovery efficiency means, in respect of an energy-recovery ventilator or a heat-recovery ventilator, the ratio of the net sensible energy recovered by the unit’s supply airstream, as adjusted to account for the unit’s external and internal energy gains and losses, to the maximum sensible energy that would be recovered if the unit had an infinite transfer area. ( efficacité de récupération de chaleur sensible )
Energy Efficiency Regulations, 2016 — 277
Energy-using product 277 (1) An energy-recovery ventilator is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4 and 5, an energy-recovery ventilator is not considered to be an energy-using product unless it is manufactured on or after January 1, 2020. SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 278
Information 278 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with CSA C439-18 and be provided to the Minister in respect of an energy-recovery ventilator: (a) its maximum rated airflow at 0°C; (b) its sensible heat recovery efficiency at 0°C and the associated net supply airflow, expressed in L/s, and electrical power consumption, expressed in watts; and (c) unless the unit is marked for use only where the outdoor design temperature is greater than or equal to -10°C, its sensible heat recovery efficiency at -25°C and the associated net supply airflow, expressed in L/s. SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 279
Energy-using product 279 (1) A heat-recovery ventilator is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4 and 5, a heat-recovery ventilator is not considered to be an energy-using product unless it is manufactured on or after January 1, 2020. SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 280
Information 280 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with CSA C439-18 and be provided to the Minister in respect of a heat-recovery ventilator: (a) its maximum rated airflow at 0°C; (b) its sensible heat recovery efficiency at 0°C and the associated net supply airflow, expressed in L/s, and electrical power consumption, expressed in watts; and (c) unless the unit is marked for use only where the outdoor design temperature is greater than or equal to -10°C, its sensible heat recovery efficiency at -25°C and the associated net supply airflow, expressed in L/s. SOR/2019-164, s. 12
Energy Efficiency Regulations, 2016 — 314
Definitions 314 The following definitions apply in this Division. ASHRAE 103 means the ANSI/ASHRAE standard 103-2007 entitled Method of Testing for Annual Fuel Utilization Efficiency of Residential Central Furnaces and Boilers . ( ASHRAE 103 ) automatic water temperature adjustment device means a device that (a) adjusts the temperature of the water supplied by a boiler to ensure that an incremental change in inferred heat load produces a corresponding incremental change in the temperature of the water supplied or, if the boiler fires at a single input rate, automatically allows the burner or heating element to fire only when the device has determined that the inferred heat load cannot be met by the residual heat of the water in the system; and (b) when there is no inferred heat load, limits the water temperature in the boiler to not more than 60°C. ( dispositif automatique de réglage de la température de l’eau ) CSA P.2 means the CSA standard CAN/CSA-P.2-13 entitled Testing Method for Measuring the Annual Fuel Utilization Efficiency of Residential Gas-Fired or Oil-Fired Furnaces and Boilers . ( CSA P.2 ) 10 C.F.R. Appendix A means Appendix A to Subpart E, Part 431 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for the Measurement of Thermal Efficiency and Combustion Efficiency of Commercial Packaged Boilers , as amended from time to time. ( appendice A 10 C.F.R. ) SOR/2019-164, s. 13
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
ASHRAE 103 means the ANSI/ASHRAE standard 103-2007 entitled Method of Testing for Annual Fuel Utilization Efficiency of Residential Central Furnaces and Boilers . ( ASHRAE 103 )
Energy Efficiency Regulations, 2016 — (a)
automatic water temperature adjustment device means a device that (a) adjusts the temperature of the water supplied by a boiler to ensure that an incremental change in inferred heat load produces a corresponding incremental change in the temperature of the water supplied or, if the boiler fires at a single input rate, automatically allows the burner or heating element to fire only when the device has determined that the inferred heat load cannot be met by the residual heat of the water in the system; and (b) when there is no inferred heat load, limits the water temperature in the boiler to not more than 60°C. ( dispositif automatique de réglage de la température de l’eau )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA P.2 means the CSA standard CAN/CSA-P.2-13 entitled Testing Method for Measuring the Annual Fuel Utilization Efficiency of Residential Gas-Fired or Oil-Fired Furnaces and Boilers . ( CSA P.2 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. Appendix A means Appendix A to Subpart E, Part 431 of Title 10 to the United States Code of Federal Regulations , entitled Uniform Test Method for the Measurement of Thermal Efficiency and Combustion Efficiency of Commercial Packaged Boilers , as amended from time to time. ( appendice A 10 C.F.R. )
Energy Efficiency Regulations, 2016 — 315
Definitions 315 The following definitions apply in this Subdivision. CGA P.2 means the CGA standard CGA P.2-1991 entitled Testing Method for Measuring Annual Fuel Utilization Efficiencies of Residential Furnaces and Boilers . ( CGA P.2 ) CSA P.2 [Repealed, SOR/2019-164, s. 14] gas boiler means a boiler that uses exclusively propane or natural gas, is intended for application in a low pressure steam, or hot water, central heating system and has an input rate of not more than 2 930.71 kW (10,000,000 Btu/h). ( chaudière à gaz ) SOR/2019-164, s. 14
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CGA P.2 means the CGA standard CGA P.2-1991 entitled Testing Method for Measuring Annual Fuel Utilization Efficiencies of Residential Furnaces and Boilers . ( CGA P.2 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
gas boiler means a boiler that uses exclusively propane or natural gas, is intended for application in a low pressure steam, or hot water, central heating system and has an input rate of not more than 2 930.71 kW (10,000,000 Btu/h). ( chaudière à gaz )
Energy Efficiency Regulations, 2016 — 315.1
Type 315.1 For the purpose of these Regulations, a gas boiler is one of the following types: (a) household, if it has an input rate of less than 87.92 kW (300,000 Btu/h); or (b) commercial, if it is has an input rate of greater than or equal to 87.92 kW (300,000 Btu/h) but not more than 2 930.71 kW (10,000,000 Btu/h). SOR/2019-164, s. 15
Energy Efficiency Regulations, 2016 — 316
Energy-using product 316 (1) A gas boiler is prescribed as an energy-using product. Limits (2) However, a gas boiler is not considered to be an energy-using product (a) for the purpose of section 4 unless (i) it is a household gas boiler that is manufactured on or after June 30, 1999, or (ii) it is a commercial gas boiler that is manufactured on or after January 1, 2025; and (b) for the purposes of sections 5 and 317 unless (i) it is a household gas boiler that is manufactured on or after December 31, 1998, or (ii) it is a commercial gas boiler that is manufactured on or after January 1, 2025. SOR/2019-164, s. 16
Energy Efficiency Regulations, 2016 — 317
BLE 2 Item Column 1 Column 2 Energy-using Product Energy Efficiency Standard 1 Commercial gas boilers that have an input rate of ≥ 87.92 kW (300,000 Btu/h) but ≤ 732.68 kW (2,500,000 Btu/h) and are intended for hot water systems Thermal efficiency ≥ 90% 2 Commercial gas boilers that have an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and are intended for hot water systems Combustion efficiency ≥ 90% 3 Commercial gas boilers that have an input rate of ≥ 87.92 kW (300,000 Btu/h) but ≤ 732.68 kW (2,500,000 Btu/h) and are intended for low pressure steam systems Thermal efficiency ≥ 81% 4 Commercial gas boilers that have an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and are intended for low pressure steam systems Thermal efficiency ≥ 82% SOR/2019-164, s. 17 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency ≥ 82%
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency ≥ 82%
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency ≥ 90%
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Equipped with automatic water temperature adjustment device and not operable without the device
Energy Efficiency Regulations, 2016 — 318
Information 318 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected in accordance with the standard set out in column 2 and provided to the Minister in respect of a gas boiler described in column 1. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Information 1 Household gas boilers manufactured on or after December 31, 1998 and before September 1, 2010 CGA P.2 (a) type of fuel used; (b) type of central heating system for which product is intended; (c) input rate, in kW (Btu/h); and (d) annual fuel utilization efficiency. 2 Household gas boilers manufactured on or after September 1, 2010 and before January 15, 2021 and intended for low pressure steam systems CSA P.2 (a) type of fuel used; (b) maximum heat input and output nominal capacities, in kW (Btu/h); and (c) annual fuel utilization efficiency. 3 Household gas boilers manufactured on or after January 15, 2021 and intended for low pressure steam systems CSA P.2 (a) type of fuel used; (b) maximum heat input and output nominal capacities, in kW (Btu/h); (c) annual fuel utilization efficiency; (d) standby power, in W; and (e) off-mode power, in W. 4 Household gas boilers, other than those intended for low pressure steam systems, manufactured on or after September 1, 2010 and before July 1, 2023 CSA P.2 for information set out in paragraphs (a) to (c) (a) type of fuel used; (b) maximum heat input and output nominal capacities, in kW (Btu/h); (c) annual fuel utilization efficiency; and (d) if product is manufactured on or after September 1, 2012 and before July 1, 2023, (i) information that indicates whether product has tankless domestic water heating coils, and (ii) type of automatic water temperature adjustment device it has, if any. 5 Household gas boilers, other than those intended for low pressure steam systems, manufactured on or after July 1, 2023 CSA P.2 for information set out in paragraphs (a) to (e) (a) type of fuel used; (b) maximum heat input and output nominal capacities, in kW (Btu/h); (c) annual fuel utilization efficiency; (d) standby power, in W; (e) off-mode power, in W; (f) information that indicates whether product has tankless domestic water heating coils; and (g) type of automatic water temperature adjustment device it has, if any. 6 Commercial gas boilers manufactured on or after January 1, 2025 10 C.F.R. Appendix A (a) type of central heating system for which product is intended; (b) maximum heat input nominal capacity, in kW (Btu/h); and (c) thermal efficiency or, if product has an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and is intended for hot water systems, combustion efficiency. SOR/2019-164, s. 18 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — (b)
(b) type of central heating system for which product is intended;
Energy Efficiency Regulations, 2016 — (b)
(b) maximum heat input and output nominal capacities, in kW (Btu/h); and
Energy Efficiency Regulations, 2016 — (b)
(b) maximum heat input and output nominal capacities, in kW (Btu/h);
Energy Efficiency Regulations, 2016 — (c)
(c) annual fuel utilization efficiency; and
Energy Efficiency Regulations, 2016 — (d)
(d) if product is manufactured on or after September 1, 2012 and before July 1, 2023,
Energy Efficiency Regulations, 2016 — (i)
(i) information that indicates whether product has tankless domestic water heating coils, and
Energy Efficiency Regulations, 2016 — (ii)
(ii) type of automatic water temperature adjustment device it has, if any.
Energy Efficiency Regulations, 2016 — (f)
(f) information that indicates whether product has tankless domestic water heating coils; and
Energy Efficiency Regulations, 2016 — (g)
(g) type of automatic water temperature adjustment device it has, if any.
Energy Efficiency Regulations, 2016 — (a)
(a) type of central heating system for which product is intended;
Energy Efficiency Regulations, 2016 — (b)
(b) maximum heat input nominal capacity, in kW (Btu/h); and
Energy Efficiency Regulations, 2016 — (c)
(c) thermal efficiency or, if product has an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and is intended for hot water systems, combustion efficiency.
Energy Efficiency Regulations, 2016 — 319
Definitions 319 The following definitions apply in this Subdivision. CSA B212 means the CSA standard CSA-B212-93 entitled Seasonal Energy Utilization Efficiencies of Oil-Fired Furnaces and Boilers . ( CSA B212 ) oil-fired boiler means a boiler that is intended for application in a low pressure steam, or hot water, central heating system, has an input rate of less than 2 930.71 kW (10,000,000 Btu/h) and is (a) exclusively oil-fired; or (b) capable of being fired, at the choice of the user, by either oil or another fuel. ( chaudière à mazout ) SOR/2019-164, s. 19
Energy Efficiency Regulations, 2016 — (a)
oil-fired boiler means a boiler that is intended for application in a low pressure steam, or hot water, central heating system, has an input rate of less than 2 930.71 kW (10,000,000 Btu/h) and is (a) exclusively oil-fired; or (b) capable of being fired, at the choice of the user, by either oil or another fuel. ( chaudière à mazout )
Energy Efficiency Regulations, 2016 — 319.1
Type 319.1 For the purpose of these Regulations, an oil-fired boiler is one of the following types: (a) household, if it has an input rate of less than 87.92 kW (300,000 Btu/h); or (b) commercial, if it is has an input rate of greater than or equal to 87.92 kW (300,000 Btu/h) but not more than 2 930.71 kW (10,000,000 Btu/h). SOR/2019-164, s. 20
Energy Efficiency Regulations, 2016 — 320
Energy-using product 320 (1) An oil-fired boiler is prescribed as an energy-using product. Limits (2) However, an oil-fired boiler is not considered to be an energy-using product (a) for the purpose of section 4, unless (i) it is a household oil-fired boiler that is manufactured on or after June 30, 1999, or (ii) it is a commercial oil-fired boiler that is manufactured on or after January 1, 2025; and (b) for the purposes of sections 5 and 321, unless (i) it is a household oil-fired boiler that is manufactured on or after December 31, 1998, or (ii) it is a commercial oil-fired boiler that is manufactured on or after January 1, 2025. SOR/2019-164, s. 21
Energy Efficiency Regulations, 2016 — 321
 oil-fired boilers that have an input rate of ≥ 87.92 kW (300,000 Btu/h) but ≤ 732.68 kW (2,500,000 Btu/h) and are intended for low pressure steam systems Thermal efficiency ≥ 84% 4 Commercial oil-fired boilers that have an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and are intended for low pressure steam systems Thermal efficiency ≥ 85% SOR/2019-164, s. 22 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency ≥ 85%
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency ≥ 86%
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Annual fuel utilization efficiency‍ ≥ 84%
Energy Efficiency Regulations, 2016 — 322
Information 322 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected in accordance with the standard set out in column 2 and provided to the Minister in respect of an oil-fired boiler described in column 1. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Information 1 Household oil-fired boilers manufactured on or after December 31, 1998 and before September 1, 2010 CSA B212 (a) input rate, in kW (Btu/h); and (b) seasonal energy utilization efficiency. 2 Household oil-fired boilers manufactured on or after September 1, 2010 and before January 15, 2021 ASHRAE 103 for information set out in paragraphs (a) to (f) (a) type of central heating system for which product is intended; (b) maximum heat input and output nominal capacities, in kW (Btu/h); (c) power burner’s PE; (d) water pump’s BE; (e) average annual electrical energy consumption (E AE ), in kWh; (f) annual fuel utilization efficiency; and (g) if product is manufactured on or after September 1, 2012, (i) information that indicates whether product has tankless domestic water heating coils, and (ii) type of automatic water temperature adjustment device product has, if any. 3 Household oil-fired boilers manufactured on or after January 15, 2021 CSA P.2 for information set out in paragraphs (a) to (e) (a) type of central heating system for which product is intended; (b) maximum heat input and output nominal capacities, in kW (Btu/h); (c) annual fuel utilization efficiency; (d) standby power, in W; (e) off-mode power, in W; (f) information that indicates whether product has tankless domestic water heating coils; and (g) type of automatic water temperature adjustment device product has, if any. 4 Commercial oil-fired boilers manufactured on or after January 1, 2025 10 C.F.R. Appendix A (a) type of central heating system for which product is intended; (b) maximum heat input nominal capacity, in kW (Btu/h); and (c) thermal efficiency or, if product has an input rate of > 732.68 kW (2,500,000 Btu/h) but ≤ 2 930.71 kW (10,000,000 Btu/h) and is intended for hot water systems, combustion efficiency. SOR/2019-164, s. 23 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — (e)
(e) average annual electrical energy consumption (E AE ), in kWh;
Energy Efficiency Regulations, 2016 — (f)
(f) annual fuel utilization efficiency; and
Energy Efficiency Regulations, 2016 — (g)
(g) if product is manufactured on or after September 1, 2012, (i) information that indicates whether product has tankless domestic water heating coils, and (ii) type of automatic water temperature adjustment device product has, if any.
Energy Efficiency Regulations, 2016 — (ii)
(ii) type of automatic water temperature adjustment device product has, if any.
Energy Efficiency Regulations, 2016 — (g)
(g) type of automatic water temperature adjustment device product has, if any.
Energy Efficiency Regulations, 2016 — 323
Definition of electric boiler 323 In this Subdivision, electric boiler means a boiler that uses electric energy as a source of heat, is intended for application in a hot water central heating system, has an input rate of less than 88 kW (300,000 Btu/h) and is not equipped with tankless domestic water heating coils.
Energy Efficiency Regulations, 2016 — 324
Energy-using product 324 (1) An electric boiler is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 325, an electric boiler is not considered to be an energy-using product unless it is manufactured on or after September 1, 2012.
Energy Efficiency Regulations, 2016 — 325
Energy efficiency standard 325 The energy efficiency standard that applies to an electric boiler is that it must be equipped with an automatic water temperature adjustment device without which the boiler is not operable.
Energy Efficiency Regulations, 2016 — 326
Information 326 For the purpose of subsection 5(1) of the Act, the following information must be provided to the Minister in respect of an electric boiler: (a) its input rate, expressed in kilowatts, collected in accordance with ASHRAE 103; and (b) the type of automatic water temperature adjustment device that it has.
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA P.3-15 means the CSA standard CAN/CSA-P.3-15 entitled Testing method for measuring energy consumption and determining efficiencies of gas-fired and fuel oil-fired water heaters . ( CSA P.3-15 )