Storage Tank Systems for Petroleum Products and Allied Petroleum Products Regulations — 14
k Assemblies for Flammable and Combustible Liquids , or CAN/ULC 677, Standard for Fire Tested Aboveground Tank Assemblies for Flammable and Combustible Liquids , whichever is in effect at the time the storage tank system is manufactured, (iv) ULC/ORD-C142.18, Rectangular Steel Aboveground Tanks for Flammable and Combustible Liquids , or CAN/ULC-S601, Standard for Shop Fabricated Steel Aboveground Tanks for Flammable and Combustible Liquids , whichever is in effect at the time the storage tank system is manufactured, (v) ULC/ORD-C142.21, Aboveground Used Oil Systems , or CAN/ULC 652, Standard for Tank Assemblies for the Collection, Storage and Removal of Used Oil , whichever is in effect at the time the storage tank system is manufactured, (vi) ULC/ORD-C142.22, Contained Vertical Steel Aboveground Tank Assemblies for Flammable and Combustible Liquids , or CAN/ULC-S601, Standard for Shop Fabricated Steel Aboveground Tanks for Flammable and Combustible Liquids , whichever is in effect at the time the storage tank system is manufactured. (3) The owner or operator of a storage tank system that has underground tanks that installs those tanks on or after June 12, 2008 must ensure that those tanks bear a certification mark certifying conformity with one of the following standards: (a) for underground steel tanks (i) if used for storing used oil, CAN/ULC 652, Standard for Tank Assemblies for the Collection, Storage and Removal of Used Oil , and (ii) if used for storing other petroleum products or allied petroleum products (A) CAN/ULC-S603, Standard for Steel Underground Tanks for Flammable and Combustible Liquids , or (B) CAN/ULC-S603.1, Standard for External Corrosion Protection Systems for Steel Underground Tanks for Flammable and Combustible Liquids ; (b) for underground reinforced plastic tanks (i) if used for storing used oil, CAN/ULC 652, Standard for Tank Assemblies for the Collection, Storage and Removal of Used Oil , and (ii) if used for storing other petroleum products or allied petroleum products, CAN/ULC-S615, Standard for Fibre Reinforced Plastic Underground Tanks for Flammable and Combustible Liquids , or ANSI/CAN/UL/ULC 1316, Standard for Fibre Reinforced Underground Tanks for Flammable and Combustible Liquid , whichever is in effect at the time the storage tank system is manufactured; and (c) for underground tanks that are double containment linings, ULC/ORD-C58.4, Double Containment Fibre Reinforced Plastic Linings for Flammable and Combustible Liquid Storage Tanks , or CAN/ULC-S669, Standard for Internal Retrofit Systems for Underground Tanks for Flammable and Combustible Liquids , whichever is in effect at the time the storage tank system is manufactured. (4) The owner or operator of a storage tank system that has steel underground tanks that installs those tanks on or after June 12, 2008 must ensure that those tanks are protected from corrosion as follows: (a) those tanks must bear a certification mark certifying conformity with CAN/ULC-S603.1, Standard for External Corrosion Protection Systems for Steel Underground Tanks for Flammable and Combustible Liquids ; or (b) those tanks must have a cathodic protection system designed by a corrosion expert. (5) The owner or operator of a storage tank system that installs piping on or after June 12, 2008 must ensure that (a) the piping does not have buried or concealed mechanical joints; and (b) any piping other than copper piping bears a certification mark certifying conformity with (i) one of the standards referred to in Clauses 5.2.1(1)(a) to (c) and (g) of the CCME Code of Practice, subject to subsection (6.1) of this section, or (ii) ULC/ORD-C971, Nonmetallic Underground Piping for Flammable and Combustible Liquids , CAN/ULC-S660, Standard for Nonmetallic Underground Piping for Flammable and Combustible Liquids , or CAN/ULC-S679, Standard for Metallic and Nonmetallic Underground Piping for Flammable and Combustible Liquids , whichever is in effect at the time the storag