Energy Efficiency Regulations, 2016 — 260
Information 260 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected in accordance with the standard set out in column 2 and provided to the Minister in respect of a gas furnace described in column 1. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Information 1 Gas furnaces that have an input rate of ≤ 65.92 kW (225,000 Btu/h), that use single-phase electric current and that are manufactured before December 31, 2009 CSA 2.3 (a) heating capacity, in kW (Btu/h); and (b) annual fuel utilization efficiency. 2 Gas furnaces, other than those that are through-the-wall, that have an input rate of ≤ 65.92 kW (225,000 Btu/h), that use single-phase electric current and that are manufactured on or after December 31, 2009 and before July 3, 2019 CSA P.2 (a) maximum heat input and output nominal capacities, in kW (Btu/h); (b) annual fuel utilization efficiency; (c) information that indicates whether product has an integrated cooling component; (d) if product has an integrated cooling component, information that indicates whether the product is outdoor or through-the-wall; (e) standby power, in W; (f) power burner’s PE and V PE ; and (g) type of fuel used. 2.1 Gas furnaces that have an input rate of ≤ 65.92 kW (225,000 Btu/h), that use single-phase electric current and that are manufactured on or after July 3, 2019 CSA P.2, for information set out in paragraphs (a) to (e) 10 C.F.R. Appendix AA, for information set out in paragraphs (f) and (g) (a) maximum heat input and output nominal capacities, in kW (Btu/h); (b) annual fuel utilization efficiency; (c) information that indicates whether product has an integrated cooling component; (d) if product has an integrated cooling component, information that indicates whether the product is outdoor or through-the-wall; (e) type of fuel used; (f) FER, expressed in W/472 L/s (W/1,000 ft³/min); (g) product’s maximum airflow (Q max ), expressed in L/s (ft³/min); and (h) if applicable, information that indicates whether product is gas furnace for relocatable buildings or is replacement non-condensing gas furnace. 2.2 Gas furnaces that are through-the-wall, that have an input rate of ≤ 65.92 kW (225,000 Btu/h), that use single-phase electric current, that have an integrated cooling component and that are manufactured on or after December 31, 2009 and before January 1, 2024 CSA P.2 for information set out in paragraphs (a) to (c) (a) maximum heat input and output nominal capacities, in kW (Btu/h); (b) annual fuel utilization efficiency; (c) type of fuel used; and (d) if applicable, information that indicates whether product is gas furnace for relocatable buildings or is replacement non-condensing gas furnace. 2.3 Gas furnaces, other than gas furnaces for relocatable buildings or replacement non-condensing gas furnaces, that are space-constrained, that have an input rate of ≤ 65.92 kW (225,000 Btu/h), that have an integrated cooling component and that are manufactured on or after January 1, 2024 CSA P.2 for information set out in paragraphs (a) to (c) (a) maximum heat input and output nominal capacities, in kW (Btu/h); (b) annual fuel utilization efficiency; (c) type of fuel used; and (d) type of blower fan motor, namely brushless permanent magnet, permanent split-capacitor or other. 3 Gas furnaces that have an input rate of ≤ 65.92 kW (225,000 Btu/h) and that use three-phase electric current CSA 2.3 (a) heating capacity, in kW (Btu/h); and (b) annual fuel utilization efficiency or thermal efficiency. 4 Gas furnaces that have an input rate of > 65.92 kW (225,000 Btu/h) but ≤ 117.23 kW (400,000 Btu/h) CSA 2.3 (a) heating capacity, in kW (Btu/h); and (b) thermal efficiency. 5 Gas furnaces for relocatable buildings manufactured on or after January 1, 2024 CSA P.2 for information set out in paragraphs (a) to (c) 10 C.F.R. Appendix AA for information set out in paragraphs (d) and (e) (a) maximum heat input a