Energy Efficiency Regulations, 2016 — 213
Energy efficiency standards — single-phase 213 (1) The energy efficiency standards set out in column 3 of Table 1 to this section apply to single-phase split system central heat pumps described in column 1 that are manufactured during the periods set out in column 4. Energy efficiency standards — three-phase (1.1) The energy efficiency standards set out in column 3 of Table 2 to this section apply to three-phase split system central heat pumps described in column 1 that are manufactured during the periods set out in column 4. Testing standard (2) A split system central heat pump complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 2 that are applicable to a split system central heat pump as defined in section 211. TABLE 1 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Split system central heat pumps, other than those that are small-duct and high-velocity CSA C656-14 for seasonal energy efficiency ratio and heating seasonal performance factor 10 C.F.R. Appendix M for off mode power consumption Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.1 Off mode power consumption ≤ 33 W On or after December 31, 1998 and before January 1, 2023 2 Split system central heat pumps that are small-duct and high-velocity CSA C656-14 for seasonal energy efficiency ratio and heating seasonal performance factor 10 C.F.R. Appendix M for off mode power consumption Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.3 Off mode power consumption ≤ 30 W On or after December 31, 1998 and before January 1, 2023 3 Split system central heat pumps, other than those that are small-duct and high-velocity or space-constrained 10 C.F.R. Appendix M1 Seasonal energy efficiency ratio 2 ≥ 14.3 Heating seasonal performance factor 2 (Region V) ≥ 6.0 Off mode power consumption ≤ 33 W On or after January 1, 2023 and before January 1, 2025 4 Split system central heat pumps that are small-duct and high-velocity 10 C.F.R. Appendix M1 Seasonal energy efficiency ratio 2 ≥ 12.0 Heating seasonal performance factor 2 (Region V) ≥ 4.9 Off mode power consumption ≤ 30 W On or after January 1, 2023 and before January 1, 2025 5 Split system central heat pumps that are space-constrained 10 C.F.R. Appendix M1 Seasonal energy efficiency ratio 2 ≥ 11.9 Heating seasonal performance factor 2 (Region V) ≥ 5.0 Off mode power consumption ≤ 33 W On or after January 1, 2023 and before January 1, 2025 6 Split system central heat pumps, other than those that are small-duct and high-velocity or space-constrained 10 C.F.R. Appendix M1 with the very low temperature heating test (H4) conducted at -15°C (5°F) Seasonal energy efficiency ratio 2 ≥ 14.3 Heating seasonal performance factor 2 (Region V) ≥ 6.0 Off mode power consumption ≤ 33 W On or after January 1, 2025 7 Split system central heat pumps that are small-duct and high-velocity 10 C.F.R. Appendix M1 with the very low temperature heating test (H4) conducted at -15°C (5°F) Seasonal energy efficiency ratio 2 ≥ 12.0 Heating seasonal performance factor 2 (Region V) ≥ 4.9 Off mode power consumption ≤ 30 W On or after January 1, 2025 8 Split system central heat pumps that are space-constrained 10 C.F.R. Appendix M1 with the very low temperature heating test (H4) conducted at -15°C (5°F) Seasonal energy efficiency ratio 2 ≥ 11.9 Heating seasonal performance factor 2 (Region V) ≥ 5.0 Off mode power consumption ≤ 33 W On or after January 1, 2025 TABLE 2 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Split system central heat pumps, other than those that are small-duct and high-velocity CSA C656-14 Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.1 On or aft