Energy Efficiency Regulations, 2016 — 118
apacity of ≥ 70 kW and < 223 kW and either without a heating section or with an electric heating section CSA C746-17 Energy efficiency ratio ≥ 10.0 IEER ≥ 11.6 On or after January 1, 2018 and before January 1, 2026 11 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and either without a heating section or with an electric heating section CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 10.0 IEER ≥ 13.2 On or after January 1, 2026 12 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-98 Energy efficiency ratio ≥ 10.1 On or after December 31, 1998 and before January 1, 2010 13 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.0 IEER ≥ 11.2 On or after January 1, 2010 and before January 1, 2018 14 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-17 Energy efficiency ratio ≥ 11.0 IEER ≥  12.7 On or after January 1, 2018 and before January 1, 2026 15 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and a heating section other than an electric heating section CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 11.0 IEER ≥  14.6 On or after January 1, 2026 16 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-98 Energy efficiency ratio ≥ 9.5 On or after December 31, 1998 and before January 1, 2010 17 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 10.8 IEER ≥ 11.0 On or after January 1, 2010 and before January 1, 2018 18 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-17 Energy efficiency ratio ≥ 10.8 IEER ≥ 12.2 On or after January 1, 2018 and before January 1, 2026 19 Large air conditioners that have a cooling capacity of ≥ 40 kW and < 70 kW and a heating section other than an electric heating section CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 10.8 IEER ≥ 14.0 On or after January 1, 2026 20 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and a heating section other than an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 9.8 IEER ≥ 9.9 On or after January 1, 2010 and before January 1, 2018 21 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and a heating section other than an electric heating section CSA C746-17 Energy efficiency ratio ≥ 9.8 IEER ≥ 11.4 On or after January 1, 2018 and before January 1, 2026 22 Large air conditioners that have a cooling capacity of ≥ 70 kW and < 223 kW and a heating section other than an electric heating section CSA C746-17 or 10 C.F.R. Appendix A Energy efficiency ratio ≥ 9.8 IEER ≥ 13.0 On or after January 1, 2026 TABLE 2 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and either without a heating section or with an electric heating section CSA C746-98 Energy efficiency ratio ≥ 11.5 On or after December 31, 1998 and before January 1, 2010 2 Large air conditioners that have a cooling capacity of ≥ 19 kW and < 40 kW and either without a heating section or with an electric heating section CSA C746-06 for energy efficiency ratio AHRI 340/360 for IEER Energy efficiency ratio ≥ 11.5 IEER ≥ 11.7 On or after January 1, 20