Vessel Fire Safety Regulations — 327
327 (1) The primary deck coverings within an accommodation space, service space or wheelhouse must (a) be certified by a product certification body, testing laboratory or recognized organization as (i) having a radiant panel index that does not exceed 20 when tested in accordance with the standard ASTM E162, entitled Standard Test Method for Surface Flammability of Materials Using a Radiant Heat Energy Source , and having a specific optical smoke density of 450 or less when tested in flaming mode in accordance with the standard ASTM E662, entitled Standard Test Method for Specific Optical Density of Smoke Generated by Solid Materials , or (ii) having a critical radiant flux of at least 0.45 W/cm 2 when tested in accordance with the standard ASTM E648, entitled Standard Test Method for Critical Radiant Flux of Floor-Covering Systems Using a Radiant Heat Energy Source , and having a specific optical smoke density of 450 or less when tested in flaming mode in accordance with the standard ASMT E662, entitled Standard Test Method for Specific Optical Density of Smoke Generated by Solid Materials ; or (b) meet the flame spread, smoke, toxicity and non-ignitable requirements set out in Annex 1 to the FTP Code. (2) The surface finish material, other than soft floor coverings, within an accommodation space, service space or wheelhouse must (a) be certified by a product certification body, testing laboratory or recognized organization as (i) having a radiant panel index that does not exceed 20 when tested in accordance with the standard ASTM E162, entitled Standard Test Method for Surface Flammability of Materials Using a Radiant Heat Energy Source , and having a specific optical smoke density of 450 or less when tested in flaming mode in accordance with the standard ASTM E662, entitled Standard Test Method for Specific Optical Density of Smoke Generated by Solid Materials , or (ii) having a critical radiant flux of at least 0.45 W/cm 2 when tested in accordance with the standard ASTM E648, entitled Standard Test Method for Critical Radiant Flux of Floor-Covering Systems Using a Radiant Heat Energy Source , and having a specific optical smoke density of 450 or less when tested in flaming mode in accordance with the standard ASTM E662, entitled Standard Test Method for Specific Optical Density of Smoke Generated by Solid Materials ; or (b) meet the flame spread, smoke, and toxicity requirements set out in Annex 1 to the FTP Code. (3) Soft floor coverings within an accommodation space, service space or wheelhouse must (a) be certified by a product certification body, testing laboratory or recognized organization as (i) having a flame spread rating or index of 300 or less and a smoke developed classification or index of 300 or less, in the case of wool, or a flame spread rating or index of 300 or less and a smoke developed classification or index of 500 or less in the case of nylon or a nylon/wool blend, when tested in accordance with the standard CAN/ULC-S102.2, entitled Standard Method of Test for Surface Burning Characteristics of Flooring, Floor Coverings, and Miscellaneous Materials and Assemblies , published by the Standards Council of Canada, or (ii) having a critical radiant flux of at least 0.45 W/cm 2 when tested in accordance with the standard ASTM E648, entitled Standard Test Method for Critical Radiant Flux of Floor-Covering Systems Using a Radiant Heat Energy Source , and having a specific optical smoke density of 450 or less when tested in flaming mode in accordance with the standard ASTM E662, entitled Standard Test Method for Specific Optical Density of Smoke Generated by Solid Materials ; or (b) meet the flame spread, smoke, and toxicity requirements set out in Annex 1 to the FTP Code.