GreatNorthCollective/greatnorth-canada-federal-laws-text huggingface dataset:
Energy Efficiency Regulations, 2016 — 120
Definitions 120 The following definitions apply in this Subdivision. CSA C744-04 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2004/CAN/CSA-C744-04 entitled Standard for Packaged Terminal Air Conditioners and Heat Pumps . ( CSA C744-04 ) CSA C744-14 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2014/CAN/CSA-C744-14 entitled Standard for Packaged Terminal Air Conditioners and Heat Pumps . ( CSA C744-14 ) CSA C744-17 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2017/CAN/CSA-C744-17 entitled Packaged terminal air-conditioners and heat pumps . ( CSA C744-17 ) packaged terminal air conditioner means a factory-built packaged terminal air conditioner that (a) consists of a wall sleeve and a separate unencased cooling component and is intended to cool a single room or zone; or (b) consists of a wall sleeve and a separate unencased combination of heating and cooling components and is intended to heat and cool a single room or zone. ( climatiseur terminal autonome ) SOR/2018-201, s. 24
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C744-04 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2004/CAN/CSA-C744-04 entitled Standard for Packaged Terminal Air Conditioners and Heat Pumps . ( CSA C744-04 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C744-14 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2014/CAN/CSA-C744-14 entitled Standard for Packaged Terminal Air Conditioners and Heat Pumps . ( CSA C744-14 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C744-17 means the joint CSA and AHRI standard ANSI/AHRI 310/380-2017/CAN/CSA-C744-17 entitled Packaged terminal air-conditioners and heat pumps . ( CSA C744-17 )
Energy Efficiency Regulations, 2016 — (a)
packaged terminal air conditioner means a factory-built packaged terminal air conditioner that (a) consists of a wall sleeve and a separate unencased cooling component and is intended to cool a single room or zone; or (b) consists of a wall sleeve and a separate unencased combination of heating and cooling components and is intended to heat and cool a single room or zone. ( climatiseur terminal autonome )
Energy Efficiency Regulations, 2016 — 121
Energy-using product 121 (1) A packaged terminal air conditioner is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 122, a packaged terminal air conditioner is not considered to be an energy-using product unless it is manufactured on or after December 31, 1998.
Energy Efficiency Regulations, 2016 — 122
Energy efficiency standards 122 (1) The energy efficiency standards set out in column 2 of the table to this section apply to packaged terminal air conditioners that are manufactured during the periods set out in column 3. Testing standard (2) A packaged terminal air conditioner complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 1 that are applicable to a packaged terminal air conditioner as defined in section 120. TABLE Column 1 Column 2 Column 3 Item Testing Standard Energy Efficiency Standard Period of Manufacture 1 CSA C744-04 CSA C744-04, Table 2 On or after December 31, 1998 and before September 30, 2012 2 CSA C744-14 CSA C744-14, Table 2 On or after September 30, 2012 and before January 1, 2017 3 CSA C744-17 CSA C744-17, Table 2 On or after January 1, 2017 SOR/2018-201, s. 25 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — 123
Information 123 (1) For the purpose of subsection 5(1) of the Act, the following information must be provided to the Minister in respect of a packaged terminal air conditioner: (a) its cooling capacity, expressed in kilowatts (British thermal units per hour); (b) its energy efficiency ratio; and (c) if applicable, identification of the product as a replacement unit. Standard (2) The information must be collected in accordance with (a) CSA C744-04, if the product was manufactured on or after December 31, 1998 and before September 30, 2012; (b) CSA C744-14, if the product was manufactured on or after September 30, 2012 and before January 1, 2017; or (c) CSA C744-17, if the product is manufactured on or after January 1, 2017. SOR/2018-201, s. 26
Energy Efficiency Regulations, 2016 — 124
Definitions 124 The following definitions apply in this Subdivision. off mode power consumption means the power consumption when the unit is connected to mains power but is not providing cooling or heating. ( consommation d’énergie en mode arrêt ) single package central air conditioner means a single-phase or three-phase central air conditioner that is a single package unit and that has a cooling capacity of less than 19 kW (65,000 Btu/h). It does not include a single package vertical air conditioner. ( climatiseur central monobloc ) through-the-wall means, in respect of a single package central air conditioner, one that has a cooling capacity less than or equal to 8.79 kW (30,000 Btu/h), is designed to be installed through an exterior wall and is manufactured prior to January 1, 2023. ( mural ) SOR/2019-163, s. 18 SOR/2022-265, s. 5
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
off mode power consumption means the power consumption when the unit is connected to mains power but is not providing cooling or heating. ( consommation d’énergie en mode arrêt )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
single package central air conditioner means a single-phase or three-phase central air conditioner that is a single package unit and that has a cooling capacity of less than 19 kW (65,000 Btu/h). It does not include a single package vertical air conditioner. ( climatiseur central monobloc )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
through-the-wall means, in respect of a single package central air conditioner, one that has a cooling capacity less than or equal to 8.79 kW (30,000 Btu/h), is designed to be installed through an exterior wall and is manufactured prior to January 1, 2023. ( mural )
Energy Efficiency Regulations, 2016 — 125
Energy-using product 125 (1) A single package central air conditioner is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 126, a single package central air conditioner is not considered to be an energy-using product unless it is manufactured on or after February 3, 1995.
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-14 for seasonal energy efficiency ratio
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
10 C.F.R. Appendix M for off mode power consumption
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-05 for seasonal energy efficiency ratio
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 13.4
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 11.7
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-14 for information set out in paragraphs (a) to (c)
Energy Efficiency Regulations, 2016 — (a)
(a) product classification set out in column II of Table 1 to CSA C656-14;
Energy Efficiency Regulations, 2016 — (d)
(d) off mode power consumption, in watts; and
Energy Efficiency Regulations, 2016 — (c)
(c) seasonal energy efficiency ratio; and
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C656-05 for information set out in paragraphs (a) to (c)
Energy Efficiency Regulations, 2016 — (a)
(a) product classification set out in column II of Table 1 to CSA C656-05;
Energy Efficiency Regulations, 2016 — (c)
(c) seasonal energy efficiency ratio 2; and
Energy Efficiency Regulations, 2016 — 127.1
Early compliance 127.1 A single package central air conditioner that is manufactured on or after January 1, 2025 and before January 1, 2026 is deemed to satisfy the requirements of sections 126 and 127 if it satisfies the requirements of those sections that would have applied to the single package central air conditioner if it had been manufactured on or after January 1, 2026. SOR/2025-110, s. 19
Energy Efficiency Regulations, 2016 — 128
Definition of single package vertical air conditioner 128 In this Subdivision, single package vertical air conditioner means a single package commercial air conditioner, with or without heating capability, that has its major components arranged vertically, is air-cooled and encased and is intended for mounting through, or on either side of, an exterior wall. It does not include a single package commercial air conditioner that has reverse cycle refrigeration.
Energy Efficiency Regulations, 2016 — 129
Energy-using product 129 (1) A single package vertical air conditioner is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 130, a single package vertical air conditioner is not considered to be an energy-using product unless it is manufactured on or after January 1, 2011 and has a cooling capacity of less than 70 kW (240,000 Btu/h). SOR/2019-163, s. 21
Energy Efficiency Regulations, 2016 — 130
Energy efficiency standards 130 (1) The energy efficiency standards set out in column 2 of the table to this section apply to single package vertical air conditioners described in column 1 that are manufactured during the periods set out in column 3. Testing standard (2) A single package vertical air conditioner complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by CSA C746-17 that are applicable to a single package vertical air conditioner as defined in section 128. TABLE Item Column 1 Column 2 Column 3 Energy-using Product Energy Efficiency Standard Period of Manufacture 1 Single package vertical air conditioners that have a cooling capacity of < 19 kW (65,000 Btu/h) Energy efficiency ratio ≥ 9.0 On or after January 1, 2011 and before September 23, 2019 2 Single package vertical air conditioners that have a cooling capacity of < 19 kW (65,000 Btu/h) Energy efficiency ratio ≥ 11.0 On or after September 23, 2019 3 Single package vertical air conditioners that have a cooling capacity of ≥ 19 kW (65,000 Btu/h) and < 39.5 kW (135,000 Btu/h) Energy efficiency ratio ≥ 8.9 On or after January 1, 2011 and before October 9, 2015 4 Single package vertical air conditioners that have a cooling capacity of ≥ 19 kW (65,000 Btu/h) and < 39.5 kW (135,000 Btu/h) Energy efficiency ratio ≥ 10.0 On or after October 9, 2015 5 Single package vertical air conditioners that have a cooling capacity of ≥ 39.5 kW (135,000 Btu/h) and < 70 kW (240,000 Btu/h) Energy efficiency ratio ≥ 8.6 On or after January 1, 2011 and before October 9, 2016 6 Single package vertical air conditioners that have a cooling capacity of ≥ 39.5 kW (135,000 Btu/h) and < 70 kW (240,000 Btu/h) Energy efficiency ratio ≥ 10.0 On or after October 9, 2016 SOR/2019-163, s. 22
Energy Efficiency Regulations, 2016 — 131
Information 131 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with CSA C746-17 and provided to the Minister in respect of a single package vertical air conditioner: (a) its classification as set out in column II of Table 1 to CSA C746-17; (b) its cooling capacity, expressed in kilowatts (British thermal units per hour); and (c) its energy efficiency ratio. SOR/2019-163, s. 23
Energy Efficiency Regulations, 2016 — 132
Definitions 132 The following definitions apply in this Subdivision. off mode power consumption means the power consumption when the unit is connected to mains power but is not providing cooling or heating. ( consommation d’énergie en mode arrêt ) split system central air conditioner means a single-phase or three-phase central air conditioner that is a split system and that has a cooling capacity of less than 19 kW (65,000 Btu/h). ( climatiseur central bibloc ) split-system central air conditioner [Repealed, SOR/2022-265, s. 9] SOR/2019-163, s. 24 SOR/2022-265, s. 9(E)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
split system central air conditioner means a single-phase or three-phase central air conditioner that is a split system and that has a cooling capacity of less than 19 kW (65,000 Btu/h). ( climatiseur central bibloc )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
split-system central air conditioner [Repealed, SOR/2022-265, s. 9]
Energy Efficiency Regulations, 2016 — 133
Energy-using product 133 (1) A split system central air conditioner is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 134, a split system central air conditioner is not considered to be an energy-using product unless it is manufactured on or after February 3, 1995. SOR/2025-110, s. 20(E)
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
Seasonal energy efficiency ratio 2 ≥ 12.0
Energy Efficiency Regulations, 2016 — 135
Information 135 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected and provided to the Minister in respect of a split system central air conditioner described in column 1 and, if applicable, the information must be collected in accordance with the standard set out in column 2. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Information 1 Split system central air conditioners that are single-phase and manufactured on or after February 3, 1995 and before January 1, 2023 CSA C656-14 for information set out in paragraphs (a) to (c) 10 C.F.R. Appendix M for off mode power consumption (a) product classification set out in column II of Table 1 to CSA C656-14; (b) cooling capacity in kW (Btu/h); (c) seasonal energy efficiency ratio; (d) off mode power consumption, in watts; and (e) phase of electric current. 2 Split system central air conditioners that are three-phase and manufactured on or after February 3, 1995 and before January 1, 2026 CSA C656-14 for information set out in paragraphs (a) to (c) (a) product classification set out in column II of Table 1 to CSA C656-14; (b) cooling capacity in kW (Btu/h); (c) seasonal energy efficiency ratio; and (d) phase of electric current. 2.1 Split system central air conditioners that are three-phase and manufactured on or after January 1, 2026 10 C.F.R. Appendix F1 for information set out in paragraphs (b) and (c) (a) type; (b) cooling capacity in kW (Btu/h); (c) seasonal energy efficiency ratio 2; and (d) phase of electric current. 3 Split system central air conditioners that are single-phase and manufactured on or after January 1, 2023 10 C.F.R. Appendix M1 for information set out in paragraphs (b) to (d) (a) type; (b) cooling capacity in kW (Btu/h); (c) seasonal energy efficiency ratio 2; (d) off mode power consumption, in watts; and (e) phase of electric current. SOR/2019-163, s. 26 SOR/2022-265, s. 11 SOR/2025-110, s. 20(E) SOR/2025-110, s. 22
Energy Efficiency Regulations, 2016 — 135.1
Early compliance 135.1 A split system central air conditioner that is manufactured on or after January 1, 2025 and before January 1, 2026 is deemed to satisfy the requirements of sections 134 and 135 if it satisfies the requirements of those sections that would have applied to the split system central air conditioner if it had been manufactured on or after January 1, 2026. SOR/2025-110, s. 23
Energy Efficiency Regulations, 2016 — 136
Definition of large condensing unit 136 In this Subdivision, large condensing unit means a commercial or industrial condensing unit that is intended for air conditioning applications and that has a cooling capacity of at least 40 kW (135,000 Btu/h) but not more than 70 kW (240,000 Btu/h). SOR/2018-201, s. 27
Energy Efficiency Regulations, 2016 — 137
Energy-using product 137 (1) A large condensing unit is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 138, a large condensing unit is not considered to be an energy-using product unless it is manufactured on or after December 31, 1998.
Energy Efficiency Regulations, 2016 — 138
Energy efficiency standards 138 (1) The energy efficiency standards set out in column 2 of the table to this section apply to large condensing units described in column 1. Testing standard (2) A large condensing unit complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by CSA C746-98 that are applicable to a large condensing unit as defined in section 136. TABLE Column 1 Column 2 Item Energy-using Product Energy Efficiency Standard 1 Large condensing units that are cooled by air Energy efficiency ratio ≥ 10.1 2 Large condensing units that are cooled by water or evaporation Energy efficiency ratio ≥ 13.1
Energy Efficiency Regulations, 2016 — 139
Information 139 For the purpose of subsection 5(1) of the Act, the following information must be collected in accordance with CSA C746-98 and provided to the Minister in respect of a large condensing unit: (a) its classification as set out in Column II of Table 1 of CSA C746-98; (b) its cooling capacity, expressed in kilowatts (British thermal units per hour); and (c) its energy efficiency ratio.
Energy Efficiency Regulations, 2016 — 140
Definitions 140 The following definitions apply in this Subdivision. ASHRAE 90.1-16 means ANSI/ASHRAE/IES Standard 90.1-2016, entitled Energy Standard for Buildings Except Low-Rise Residential Buildings . ( ASHRAE 90.1-16 ) chiller means a machine, with or without an integral refrigerant condenser, that is designed to use a refrigerant cycle to remove heat from a liquid and to reject the heat to a cooling medium. ( refroidisseur ) CSA C743-02 means the CSA standard CAN/CSA-C743-02 entitled Performance Standard for Rating Packaged Water Chillers . ( CSA C743-02 ) CSA C743-09 means the CSA standard CAN/CSA-C743-09 entitled Performance Standard for Rating Packaged Water Chillers . ( CSA C743-09 ) SOR/2019-163, s. 27
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
ASHRAE 90.1-16 means ANSI/ASHRAE/IES Standard 90.1-2016, entitled Energy Standard for Buildings Except Low-Rise Residential Buildings . ( ASHRAE 90.1-16 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
chiller means a machine, with or without an integral refrigerant condenser, that is designed to use a refrigerant cycle to remove heat from a liquid and to reject the heat to a cooling medium. ( refroidisseur )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C743-02 means the CSA standard CAN/CSA-C743-02 entitled Performance Standard for Rating Packaged Water Chillers . ( CSA C743-02 )
Energy Efficiency Regulations, 2016 — Energy Efficiency Regulations, 2016
CSA C743-09 means the CSA standard CAN/CSA-C743-09 entitled Performance Standard for Rating Packaged Water Chillers . ( CSA C743-09 )
Energy Efficiency Regulations, 2016 — 141
Energy-using product 141 (1) A chiller is prescribed as an energy-using product. Limit (2) However, for the purposes of sections 4, 5 and 142, a chiller is not considered to be an energy-using product unless it has an integral refrigerant condenser and is manufactured on or after October 28, 2004. SOR/2018-201, s. 28
Energy Efficiency Regulations, 2016 — 142
Energy efficiency standards 142 (1) The energy efficiency standards set out in column 2 of the table to this section apply to chillers that are manufactured during the periods set out in column 3. Testing standard (2) A chiller complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 1 that are applicable to a chiller as defined in section 140. TABLE Column 1 Column 2 Column 3 Item Testing Standard Energy Efficiency Standard Period of Manufacture 1 CSA C743-02 CSA C743-02, Tables 9 to 15 On or after October 28, 2004 and before January 1, 2017 2 CSA C743-09 Product’s coefficient of performance and integrated part-load value must meet those applicable to the product in CSA C743-09, Path A or Path B, Table 10 On or after January 1, 2017 and before December 31, 2019 3 ASHRAE 90.1-16, table 6.8.1-3, column 6 Product’s coefficient of performance and integrated part-load value must meet those applicable to the product in ASHRAE 90.1-16, Path A or Path B, Table 6.8.1-3 On or after December 31, 2019 SOR/2019-163, s. 28 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — 143
Information 143 For the purpose of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected in accordance with the standard set out in column 2 and provided to the Minister in respect of a chiller described in column 1. TABLE Item Column 1 Column 2 Column 3 Energy-using Product Testing Standard Information 1 Chillers manufactured on or after October 28, 2004 and before January 1, 2017 CSA C743-02 (a) type; (b) net cooling/heating capacity in kW (tons); (c) coefficient of performance; and (d) integrated part-load value or non-standard part-load value and a list of non-standard conditions. 2 Chillers manufactured on or after January 1, 2017 and before December 31, 2019 CSA C743-09 (a) type; (b) net cooling/heating capacity, in kW (tons); (c) coefficient of performance; (d) compliance path for the energy-efficiency standard, namely, Path A or Path B of Table 10 to CSA C743-09; and (e) integrated part-load value or non-standard part-load value and a list of non-standard conditions. 3 Chillers manufactured on or after December 31, 2019 ASHRAE 90.1-16, Table 6.8.1-3, column 6 (a) type; (b) net cooling/heating capacity in kW (tons); (c) coefficient of performance; (d) compliance path for the energy-efficiency standard, namely, Path A or Path B of Table 6.8.1-3 of ASHRAE 90.1-16; (e) integrated part-load value; and (f) list of non-standard conditions for centrifugal chillers designed for non-standard operation. SOR/2019-163, s. 29 SOR/2022-265, s. 47
Energy Efficiency Regulations, 2016 — (b)
(b) net cooling/heating capacity in kW (tons);
Energy Efficiency Regulations, 2016 — (d)
(d) integrated part-load value or non-standard part-load value and a list of non-standard conditions.
Energy Efficiency Regulations, 2016 — (b)
(b) net cooling/heating capacity, in kW (tons);
Energy Efficiency Regulations, 2016 — (d)
(d) compliance path for the energy-efficiency standard, namely, Path A or Path B of Table 10 to CSA C743-09; and
Energy Efficiency Regulations, 2016 — (e)
(e) integrated part-load value or non-standard part-load value and a list of non-standard conditions.
Energy Efficiency Regulations, 2016 — (d)
(d) compliance path for the energy-efficiency standard, namely, Path A or Path B of Table 6.8.1-3 of ASHRAE 90.1-16;
Energy Efficiency Regulations, 2016 — (f)
(f) list of non-standard conditions for centrifugal chillers designed for non-standard operation.