Energy Efficiency Regulations, 2016 — 214
Information 214 For the purposes of subsection 5(1) of the Act, the information set out in column 3 of the table to this section must be collected and provided to the Minister in respect of a split system central heat pump described in column 1 and, if applicable, the information must be collected in accordance with the standard set out in column 2. TABLE Column 1 Column 2 Column 3 Item Energy-using Product Testing Standard Information 1 Split system central heat pumps that are single-phase and manufactured on or after December 31, 1998 and before January 1, 2023 CSA C656-14 for information set out in paragraphs (a) to (e) 10 C.F.R. Appendix M for off mode power consumption (a) product classification set out in column II of Table 1 to CSA C656-14; (b) cooling capacity in kW (Btu/h); (c) heating capacity in kW (Btu/h); (d) seasonal energy efficiency ratio; (e) heating seasonal performance factor and the region for the factor; (f) off mode power consumption, in watts; and (g) phase of electric current. 2 Split system central heat pumps that are single-phase and manufactured on or after January 1, 2023 and before January 1, 2025 10 C.F.R. Appendix M1 for information set out in paragraphs (b) to (i) (a) type; (b) cooling capacity in kW (Btu/h); (c) heating capacity at 8.3°C (47°F) in kW (Btu/h); (d) seasonal energy efficiency ratio 2; (e) information that indicates whether the results from the very low temperature heating test (H4) were included in the calculation of the heating seasonal performance factor 2 for Region V; (f) heating seasonal performance factor 2 for Region V; (g) heating capacity at -15°C (5°F) in kW (Btu/h), if the very low temperature heating test (H4) was conducted; (h) coefficient of performance at -15°C (5°F), if the very low temperature heating test (H4) was conducted; (i) off mode power consumption, in watts; and (j) phase of electric current. 3 Split system central heat pumps that are single-phase and manufactured on or after January 1, 2025 10 C.F.R. Appendix M1, except that the very low temperature heating test (H4) must be conducted for information set out in paragraphs (b) to (h) (a) type; (b) cooling capacity in kW (Btu/h); (c) heating capacity at 8.3°C (47°F) in kW (Btu/h); (d) seasonal energy efficiency ratio 2; (e) heating seasonal performance factor 2 for Region V; (f) heating capacity at -15°C (5°F) in kW (Btu/h); (g) coefficient of performance at -15°C (5°F); (h) off mode power consumption, in watts; and (i) phase of electric current. 4 Split system central heat pumps that are three-phase and manufactured on or after December 31, 1998 and before January 1, 2026 CSA C656-14 for information set out in paragraphs (a) to (e) (a) product classification set out in column II of Table 1 to CSA C656-14; (b) cooling capacity in kW (Btu/h); (c) heating capacity in kW (Btu/h); (d) seasonal energy efficiency ratio; (e) heating seasonal performance factor and the region for the factor; and (f) phase of electric current. 5 Split system central heat pumps that are three-phase and manufactured on or after January 1, 2026 10 C.F.R. Appendix F1, except that the very low temperature heating test (H4) must be conducted for information set out in paragraphs (b) to (g) (a) type; (b) cooling capacity in kW (Btu/h); (c) heating capacity at 8.3°C (47°F) in kW (Btu/h); (d) seasonal energy efficiency ratio 2; (e) heating seasonal performance factor 2 for region V; (f) heating capacity at -15°C (5°F) in kW (Btu/h); (g) coefficient of performance at -15°C (5°F); and (h) phase of electric current. SOR/2019-163, s. 43 SOR/2022-265, s. 21 SOR/2025-110, s. 39