Energy Efficiency Regulations, 2016 — 205
Energy efficiency standards — single-phase 205 (1) The energy efficiency standards set out in column 3 of Table 1 to this section apply to single-phase single package central heat pumps described in column 1 that are manufactured during the periods set out in column 4. Energy efficiency standards — three-phase (1.1) The energy efficiency standards set out in column 3 of Table 2 to this section apply to three-phase single package central heat pumps described in column 1 that are manufactured during the periods set out in column 4. Testing standard (2) A single package central heat pump complies with the energy efficiency standard if it meets that standard when tested in accordance with testing procedures established by the standard set out in column 2 that are applicable to a single package central heat pump as defined in section 203. TABLE 1 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Single package central heat pumps, other than those that are through-the-wall or small-duct and high-velocity CSA C656-14 for seasonal energy efficiency ratio and heating seasonal performance factor 10 C.F.R. Appendix M for off mode power consumption Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.0 Off mode power consumption ≤ 33 W On or after February 3, 1995 and before January 1, 2023 2 Single package central heat pumps that are through-the-wall CSA C656-05 for seasonal energy efficiency ratio and heating seasonal performance factor 10 C.F.R. Appendix M for off mode power consumption Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.4 Off mode power consumption ≤ 33 W On or after February 3, 1995 and before January 1, 2023 3 Single package central heat pumps that are small-duct and high-velocity CSA C656-14 for seasonal energy efficiency ratio and heating seasonal performance factor 10 C.F.R. Appendix M for off mode power consumption Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.3 Off mode power consumption ≤ 30 W On or after February 3, 1995 and before January 1, 2023 4 Single package central heat pumps, other than those that are space-constrained 10 C.F.R. Appendix M1 Seasonal energy efficiency ratio 2 ≥ 13.4 Heating seasonal performance factor 2 (Region V) ≥ 5.4 Off mode power consumption ≤ 33 W On or after January 1, 2023 and before January 1, 2025 5 Single package central heat pumps that are space-constrained 10 C.F.R. Appendix M1 Seasonal energy efficiency ratio 2 ≥ 11.9 Heating seasonal performance factor 2 (Region V) ≥ 5.0 Off mode power consumption ≤ 33 W On or after January 1, 2023 and before January 1, 2025 6 Single package central heat pumps, other than those that are space-constrained 10 C.F.R. Appendix M1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 13.4 Heating seasonal performance factor 2 (Region V) ≥ 5.4 Off mode power consumption ≤ 33 W On or after January 1, 2025 7 Single package central heat pumps that are space-constrained 10 C.F.R. Appendix M1, except that the very low temperature heating test (H4) must be conducted Seasonal energy efficiency ratio 2 ≥ 11.9 Heating seasonal performance factor 2 (Region V) ≥ 5.0 Off mode power consumption ≤ 33 W On or after January 1, 2025 TABLE 2 Column 1 Column 2 Column 3 Column 4 Item Energy-using Product Testing Standard Energy Efficiency Standard Period of Manufacture 1 Single package central heat pumps, other than those that are through-the-wall or small-duct and high-velocity CSA C656-14 Seasonal energy efficiency ratio ≥ 14.0 Heating seasonal performance factor (Region V) ≥ 7.0 On or after February 3, 1995 and before January 1, 2023 2 Single package central heat pumps that are through-the-wall CSA C656-05 Seasonal energy efficiency ratio ≥ 12.0 Heating seasonal performance factor (Region V) ≥ 6.4 On or af