Utah Code § 15A-3-304 — Utah Code / Title 15A / Chapter 15A-3 / § 15A-3-304
§ 15A-3-304. Amendments to Chapter 4 of IPC.
Status: in_force

7/1/2026 (1) In IPC, Table 403.1, the following changes are made: (a) In row number "3", for in the field for "OTHER", a new footnote h is added. (b) In row number "5", for "Adult day care and child day care" occupancy, in the field for "OTHER", a new footnote h is added. (c) Footnote f is deleted and replaced with the following: "FOOTNOTE f: The required number and type of plumbing fixtures for outdoor public swimming pools shall be in accordance with Utah Administrative Code, R392-302, Design, Construction and Operation of Public Pools." (d) A new footnote g is added as follows: "FOOTNOTE g: When provided, in public toilet facilities, there shall be an equal number of diaper changing facilities in male toilet rooms and female toilet rooms. Diaper changing facilities shall meet the requirements of ASTM F2285-04 (2010) Standard Consumer Safety Performance Specifications for Diaper Changing Tables for Commercial Use." (e) A new footnote h is added to the table as follows: "FOOTNOTE h: Non-residential child care facilities shall comply with the additional sink requirements of Utah Administrative Code, R381-60-9, Hourly Child Care Centers, R381-70-9, Out of School Time Child Care Programs, and R381-100-9, Child Care Centers." (2) In IPC, Section 403.1.1, Exception 2 is deleted and replaced with the following:"2. Where multiple-user facilities are designed to serve all genders, the following shall apply:2.1. The maximum fixture count to serve all genders shall be calculated at 50% of the total occupant load. The maximum fixture count for the multiple user all gender facility shall be calculated at 50% female and 50% male.2.2 The remaining 50% of the required restroom fixtures shall be provided as required by Table 403.1." (3) In IPC, Section 405.3.4, the following sentence is added after the first sentence: "For facilities designed for use by all genders in the same room, the partitions of the stalls shall extend from the floor to the ceiling." (4) In IPC, Section 405.3.5, the following sentence is added at the end of the first paragraph: "For facilities designed for use by all genders in the same room, the partitions of the stalls shall extend from the floor to the ceiling." (5) A new IPC, Section 406.3, is added as follows: "406.3 Automatic clothes washer safe pans. Safe pans, when installed under automatic clothes washers, shall be installed in accordance with Section 504.7." (6) In IPC, Section 412.2, the following is added at the end of the sentence: "-2020." (7) A new IPC, Section 413.5, is added as follows: "413.5 Public toilet rooms. All public toilet rooms shall be equipped with at least one floor drain." (8) A new IPC, Section 413.6, is added as follows: "Prohibition of motor vehicle waste disposal wells. New and existing motor vehicle waste disposal wells are prohibited. A motor vehicle waste disposal well associated with a single family residence is not subject to this prohibition." (9) IPC, Section 423.3, is deleted.7/1/2026 (1) In IPC, Table 403.1, the following changes are made: (a) In row number "3", for in the field for "OTHER", a new footnote h is added. (b) In row number "5", for "Adult day care and child day care" occupancy, in the field for "OTHER", a new footnote h is added. (c) Footnote f is deleted and replaced with the following: "FOOTNOTE f: The required number and type of plumbing fixtures for outdoor public swimming pools shall be in accordance with Utah Administrative Code, R392-302, Design, Construction and Operation of Public Pools." (d) A new footnote g is added as follows: "FOOTNOTE g: When provided, in public toilet facilities, there shall be an equal number of diaper changing facilities in male toilet rooms and female toilet rooms. Diaper changing facilities shall meet the requirements of ASTM F2285-04 (2010) Standard Consumer Safety Performance Specifications for Diaper Changing Tables for Commercial Use." (e) A new footnote h is added to the table as follows: "FOOTNOTE h: Non-residential child care facilities shall comply with the additional sink requirements of Utah Administrative Code, R381-60-9, Hourly Child Care Centers, R381-70-9, Out of School Time Child Care Programs, and R381-100-9, Child Care Centers." (2) In IPC, Section 403.1.1, Exception 2 is deleted and replaced with the following:"2. Where multiple-user facilities are designed to serve all genders, the following shall apply:2.1. The maximum fixture count to serve all genders shall be calculated at 50% of the total occupant load. The maximum fixture count for the multiple user all gender facility shall be calculated at 50% female and 50% male.2.2 The remaining 50% of the required restroom fixtures shall be provided as required by Table 403.1." (3) In IPC, Section 405.3.4, the following sentence is added after the first sentence: "For facilities designed for use by all genders in the same room, the partitions of the stalls shall extend from the floor to the ceiling." (4) In IPC, Section 405.3.5, the following sentence is added at the end of the first paragraph: "For facilities designed for use by all genders in the same room, the partitions of the stalls shall extend from the floor to the ceiling." (5) A new IPC, Section 406.3, is added as follows: "406.3 Automatic clothes washer safe pans. Safe pans, when installed under automatic clothes washers, shall be installed in accordance with Section 504.7." (6) In IPC, Section 412.2, the following is added at the end of the sentence: "-2020." (7) A new IPC, Section 413.5, is added as follows: "413.5 Public toilet rooms. All public toilet rooms shall be equipped with at least one floor drain." (8) A new IPC, Section 413.6, is added as follows: "Prohibition of motor vehicle waste disposal wells. New and existing motor vehicle waste disposal wells are prohibited. A motor vehicle waste disposal well associated with a single family residence is not subject to this prohibition." (9) IPC, Section 423.3, is deleted.