Utah Code § 15A-5-304 — Utah Code / Title 15A / Chapter 15A-5 / § 15A-5-304
§ 15A-5-304. Amendments and additions to NFPA related to Automatic Fire Sprinkler Systems.
Status: in_force

7/1/2026 (1) NFPA 13, Installation of Sprinkler Systems, 2022 edition, Chapter 16, Section 16.11.2.1, Local Waterflow Alarms, is amended by adding new subsections as follows:"16.11.2.1.1 Single Tenant Occupancies.When a fire alarm system is not required by IFC, Section 907.2, an approved audible/visual waterflow alarm (horn/strobe) shall be provided in the interior of the building, in a normally occupied location, to alert the occupants of the fire sprinkler system activation.16.11.2.1.2 Multi-Tenant Occupancies.When a fire alarm system is not required by IFC, Section 907.2, an approved audible/visual waterflow alarm (horn/strobe) shall be provided in the interior of each tenant space, in a normally occupied location, to alert the occupants of the fire sprinkler system activation.16.11.2.1.3 Exterior Waterflow Alarm.An approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (2) NFPA 13D, Installation of Sprinkler Systems in One- and Two-Family Dwellings and Manufactured Homes, 2022 edition. (a) NFPA 13D, Chapter 7, Section 7.6, Alarms, is amended by adding a new subsection as follows:"7.6.1 Exterior Waterflow Alarm.When an alarm initiating device is included, an approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (b) NFPA 13D, Chapter 7, Section 7.6, Alarms, is amended by adding a new subsection as follows:"7.6.2 Interior Alarm.When an alarm initiating device is included, an interior fire alarm notification appliance is also required to sound throughout the dwelling. An approved audible sprinkler flow alarm to alert the occupants of the dwelling in a normally occupied location when the flow switch is activated must be provided." (3) NFPA, Standard 13R, Installation of Sprinkler Systems in Residential Occupancies up to and Including Four Stories in Height, 2022 edition. (a) NFPA 13R, Chapter 6, Section 6.8, Valves, is amended by adding a new subsection as follows:"6.8.11 Floor/Zone Control Valves.Individual floor/zone control valves shall be used at the riser at each floor for connections to piping serving floor areas in excess of 5,000 square feet or arranged in a manner acceptable to the AHJ." (b) NFPA 13R, Chapter 6, Section 16, Alarms, is amended by adding a new subsection as follows:"6.16.1.1 Local Waterflow Alarms.When a fire alarm system is not required by IFC, Section 907.2, an approved notification appliance indicating waterflow shall be provided in the interior of each residential unit/tenant space, in a normally occupied location, to alert the occupants of the fire sprinkler system activation." (c) NFPA 13R, Chapter 6, Section 16, Alarms, is amended by adding a new subsection as follows:"6.16.1.2 Exterior Waterflow Alarm.An approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (4) NFPA 72, National Fire Alarm and Signaling Code, 2022 edition.NFPA 72, a new Section 18.1.1.1 is added as follows:"The fire code official may modify the requirements of this chapter in areas of educational occupancies used exclusively for special education students."7/1/2026 (1) NFPA 13, Installation of Sprinkler Systems, 2022 edition, Chapter 16, Section 16.11.2.1, Local Waterflow Alarms, is amended by adding new subsections as follows:"16.11.2.1.1 Single Tenant Occupancies.When a fire alarm system is not required by IFC, Section 907.2, an approved audible/visual waterflow alarm (horn/strobe) shall be provided in the interior of the building, in a normally occupied location, to alert the occupants of the fire sprinkler system activation.16.11.2.1.2 Multi-Tenant Occupancies.When a fire alarm system is not required by IFC, Section 907.2, an approved audible/visual waterflow alarm (horn/strobe) shall be provided in the interior of each tenant space, in a normally occupied location, to alert the occupants of the fire sprinkler system activation.16.11.2.1.3 Exterior Waterflow Alarm.An approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (2) NFPA 13D, Installation of Sprinkler Systems in One- and Two-Family Dwellings and Manufactured Homes, 2022 edition. (a) NFPA 13D, Chapter 7, Section 7.6, Alarms, is amended by adding a new subsection as follows:"7.6.1 Exterior Waterflow Alarm.When an alarm initiating device is included, an approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (b) NFPA 13D, Chapter 7, Section 7.6, Alarms, is amended by adding a new subsection as follows:"7.6.2 Interior Alarm.When an alarm initiating device is included, an interior fire alarm notification appliance is also required to sound throughout the dwelling. An approved audible sprinkler flow alarm to alert the occupants of the dwelling in a normally occupied location when the flow switch is activated must be provided." (3) NFPA, Standard 13R, Installation of Sprinkler Systems in Residential Occupancies up to and Including Four Stories in Height, 2022 edition. (a) NFPA 13R, Chapter 6, Section 6.8, Valves, is amended by adding a new subsection as follows:"6.8.11 Floor/Zone Control Valves.Individual floor/zone control valves shall be used at the riser at each floor for connections to piping serving floor areas in excess of 5,000 square feet or arranged in a manner acceptable to the AHJ." (b) NFPA 13R, Chapter 6, Section 16, Alarms, is amended by adding a new subsection as follows:"6.16.1.1 Local Waterflow Alarms.When a fire alarm system is not required by IFC, Section 907.2, an approved notification appliance indicating waterflow shall be provided in the interior of each residential unit/tenant space, in a normally occupied location, to alert the occupants of the fire sprinkler system activation." (c) NFPA 13R, Chapter 6, Section 16, Alarms, is amended by adding a new subsection as follows:"6.16.1.2 Exterior Waterflow Alarm.An approved audible/visual waterflow alarm (horn/strobe) shall be provided on the exterior of the building in a location approved by the AHJ." (4) NFPA 72, National Fire Alarm and Signaling Code, 2022 edition.NFPA 72, a new Section 18.1.1.1 is added as follows:"The fire code official may modify the requirements of this chapter in areas of educational occupancies used exclusively for special education students."